Document ID: chunk:federal_register_of_legislation:F2014L01684:reg:2
Version: federal_register_of_legislation:F2014L01684
Segment Type: reg
Provision Reference: reg 2
Character Range: 120574–121448

2  Prevention of accidental personal contact with LV power terminations

  The conductors and terminations of telecommunications cables are to be located in the same enclosure as uninsulated or single insulated conductors and terminations of LV power cables, but:
 (a) accidental contact with the LV conductors and terminations by any part of the body of or by any tool used by persons working on the telecommunications cables is prevented by means of a physical barrier or obstruction; or
 (b) if both the telecommunications cables and the LV power cables are terminated on building control or monitoring equipment the telecommunications cables and LV power cables are installed in a restricted access location where only persons who are qualified or authorised to install or maintain both LV electrical installations and telecommunications installations can gain access.