Document ID: chunk:federal_register_of_legislation:F2017C01062:body:0:p3
Version: federal_register_of_legislation:F2017C01062
Segment Type: other
Provision Reference: 
Character Range: 5921–9934

270 V
70°T                                     0          375 V
80°T                                     0          450 V
90°T                                     0          490 V
100°T                                    0          500 V
110°T                                    0          475 V
120°T                                    0          420 V
128°T                                    0          400 V
130°T                                    0          335 V
140°T                                    0          220 V
150°T                                    0          100 V
160°T                                    0          145 V
170°T                                    0          320 V
180°T                                    0          500 V
190°T                                    0          670 V
200°T                                    0          810 V
210°T                                    0          915 V
220°T                                    0          980 V
230°T                                    0          1.01 kV
240°T                                    0          1.02 kV
250°T                                    0          1.01 kV
260°T                                    0          995 V
270°T                                    0          980 V
274°T                                    0          1 kV
280°T                                    0          980 V
290°T                                    0          985 V
300°T                                    0          1 kV
310°T                                    0          1.015 kV
320°T                                    0          1.02 kV
330°T                                    0          1.005 kV
340°T                                    0          960 V
350°T                                    0          875 V

Special Conditions :-
   1.  The direction of minimum CMF is to lie within 1 degree of 43°T and 153°T.
   2.  The minimum CMF is to lie in the range 70V to 100V.
   3.  Maximum CMFs of 100 V on a bearing of 45°T, 400 V on a bearing of 128°T and 1000 V on a bearing of 274°T are not to be exceeded to provide protection to Armidale (NSW), Queenstown (NZL) and to Collie (WA) respectively.

Attachment 1.3

LICENCE AREA PLAN : Colac Radio
Category : Commercial
General Area Served : Colac (VIC)
Service Licence Number : SL10309

TECHNICAL SPECIFICATION - FM Radio
Specification Number : TS6754001

Transmitter Site :-
Nominal location : Broadcast / Comms Tower
 Ace Radio Bcers Site
 off Warrion Hill Rd
 WARRION HILL
Australian Map Grid : Zone Easting Northing
Reference 54 721300 5766130
Site Tolerance : Refer to Broadcasting Services
 (Technical Planning) Guidelines 2017

Emission :-
Frequency Band & Mode VHF-FM
Carrier Frequency : 106.3 MHz
Polarisation Mixed
Maximum antenna height 30 m

Output Radiation Pattern :-
Bearing or Sector (Clockwise direction)  Maximum ERP
0°T - 75°T                               100 W
75°T - 120°T                             1 kW
120°T - 125°T                            2 kW
125°T - 150°T                            5 kW
150°T - 174°T                            10 kW
174°T - 320°T                            1 kW
320°T - 360°T                            100 W

Attachment 1.4

LICENCE AREA PLAN : Colac Radio
Category : Commercial
General Area Served : Apollo Bay (VIC)
Service Licence Number : SL10309

TECHNICAL SPECIFICATION - FM Radio
Specification Number : TS10009649

Transmitter Site :-
Nominal location : Country Fire Authority Tower
 WYELANGTA
Australian Map Grid : Zone Easting Northing
Reference 54 713100 5717500
Site Tolerance : Refer to Broadcasting Services
 (Technical Planning) Guidelines 2017

Emission :-
Frequency Band & Mode VHF-FM
Carrier Frequency : 95.9 MHz
Polarisation Mixed
Maximum antenna height 100 m

Output Radiation Pattern :-
Bearing or Sector (Clockwise direction)  Maximum ERP
0°T - 90°T                               50 W
90°T - 160°T                             250 W
160°T - 360°T                            50 W