Document ID: chunk:federal_register_of_legislation:F2016C00264:clause:6_10:p1
Version: federal_register_of_legislation:F2016C00264
Segment Type: clause
Provision Reference: sch 6 cl 10 (pt 1/2)
Character Range: 11883–14544

10  Equipment unit requirements

Note: See section 16 to identify the applicable efficiency factor document referred to in this section.
 (1) Each equipment unit installed as part of the project must comply with the requirements in this section at the time the equipment unit is commissioned.
 (2) The equipment unit must be new.
 (3) The model of the equipment unit must be on the GEMS Register.
 (4) A liquid-chilling package must be of a model whose integrated part load value on the GEMS Register is equal to or greater than the high efficiency threshold specified for such a model in the efficiency factor document.
 (5) An air conditioner that:
 (a) can be used only for cooling; or
 (b) can be used for both heating and cooling, but is installed in NCC climate zones 1 to 3;
  must be of a model whose annual energy efficiency ratio for cooling on the GEMS Register is equal to or greater than the high efficiency threshold specified for such a model in the efficiency factor document.
 (6) An air conditioner that:
 (a) can be used for both heating and cooling; and
 (b) is installed in NCC climate zones 4 to 8;
  must be of a model:
 (c) whose annual energy efficiency ratio for cooling on the GEMS Register is equal to or greater than the high efficiency threshold specified for such a model in the efficiency factor document; and
 (d) whose annual coefficient of performance for heating on the GEMS Register is equal to or greater than the high efficiency threshold specified for such a model in the efficiency factor document.
 (7) An air conditioner that can be used only for heating must be of a model whose annual coefficient of performance for heating on the GEMS Register is equal to or greater than the high efficiency threshold specified for such a model in the efficiency factor document.
 (8) A close control air conditioner must be of a model whose sensible energy efficiency ratio on the GEMS Register is equal to or greater than the high efficiency threshold specified for such a model in the efficiency factor document.
 (9) A refrigerated display cabinet must be of a model whose efficiency value is equal to or lower than the high efficiency threshold specified for such a model in the efficiency factor document.
Note: The efficiency value of a refrigerated display cabinet is a parameter for which a lower number represents greater efficiency (see next subsection).
 (10) For this determination, the efficiency value of a model of refrigerated display cabinet on the GEMS Register is the amount, in kWh/day/m2 worked out using the following equation (equation 1):
  where:
  energy consumption is daily total energy consumption, in