Document ID: chunk:federal_register_of_legislation:F2024L01263:clause:2_8
Version: federal_register_of_legislation:F2024L01263
Segment Type: clause
Provision Reference: sch 2 cl 8
Character Range: 76280–79100

8                                           clause 5.3.3.2                     omitting the clause, substituting:
                                                                               "5.3.3.2 Closed refrigerated cabinets
                                                                               (a) The test for closed refrigerated cabinets shall always be carried out on the complete cabinet, regardless of the number of doors or lids. Each door or lid shall be opened six times per hour. Doors that are used for service, cleaning or loading of the cabinet only shall not be opened during this test. Where more than one door or lid pertains to the cabinet under test, the sequence in which the doors and lids are opened shall be staggered, i.e. in the case of two doors: door 1 at 0 min, door 2 at 5 min, door 1 at 10 min, door 2 at 15 min, etc. Hinged lids and doors shall be opened beyond an angle of 60°. Sliding glass doors or lids shall be opened beyond 80 % of the maximum area which can be opened. The door or lid shall be opened for a total of 6 s. During this opening period, the doors or lids shall be kept open beyond the minimum required opening for 4 s. Prior to the start of the 12-h period of door opening, each door or lid shall be opened once for 3 min. Where a cabinet is provided with more than one door or lid, each door or lid shall be opened once for 3 min consecutively. Within the test period, the doors or lids shall be opened cyclically for 12 h within 24 h. The 12-h cycle of door or lid opening shall start at the beginning of the test period.
                                                                               (b) If the refrigerated cabinet is fitted with a lighting system, this shall be switched on 1 h before starting the opening cycle. During the test, lighting pertaining to the cabinet shall be lit continuously and anti-sweat heaters shall run for the duration of the test period unless controlled by a time-clock, smart sensor or similar automatic device. Where a cabinet is fitted with an automated lighting control, the tests shall be conducted using the pre-set lighting regime.
                                                                               (c) In all test conditions, maximum energy consumption and minimum efficiency should be determined as worst case."

 (2) For:
 (a) items 5 and 7 of the table to subsection 14(2); and
 (b) to the extent they apply to low sales volume RSCs:
 (i) subsection 26 (4);
 (ii) subsection 28(2);
  ISO 23953-2:2015 applies as if, in addition to the variations of subclause (1), the following apply:
 (c) references to "Commercial Refrigerated Display Cabinets" were to low sales volume RSCs;
 (d) for normal duty or heavy duty RSCs, tests were required to be undertaken at test room climate class 4.