Document ID: chunk:federal_register_of_legislation:F2022L00182:schedule:1
Version: federal_register_of_legislation:F2022L00182
Segment Type: schedule
Provision Reference: sch 1
Character Range: 13973–16345

Schedule 1—Product classes and minimum energy performance standards

Note: See section 9 and section 12.

 (1) For section 9 of this Determination, a numbered product class identified in the following table consists of products that:
 (a) are the kind of product indicated; and
 (b) have the characteristics indicated; and
 (c) have a value of R in the indicated range; and
 (d) are not excluded by section 10 of this Determination.
 (2) For this Schedule, R is:
 (a) the rated standard cooling full capacity; or
 (b) for heating‑only products—the rated standard heating full capacity.
 (3) For the purposes of determining the relevant product class, the amount R must be rounded to the nearest 0.1kW.
Note 1: In the case of reverse cycle products, the relevant Minimum Energy Performance Standards (MEPS) for heating and cooling are both based on the product's rated standard cooling full capacity (even if the product's rated standard heating full capacity is different from its standard cooling full capacity).

Note 2: The numbering of the product classes follows on consecutively from the numbering of the product classes in the Air Conditioners up to 65kW Determination.

Kind of product                                                                  Product class  Characteristics                                                                   Value of R  MEPS value
Air‑to‑air unitary air conditioners                                              24             Ducted or non‑ducted                                                              65kW <      R              2.90
Air‑to‑air single-split systems                                                  25             Ducted or non‑ducted                                                              65kW <      R              2.90
Air‑to‑air single‑split outdoor units                                            26             Whether supplied or offered for supply to create a ducted or a non-ducted system  65kW <      R              2.90
(not supplied or offered for supply as part of a single‑split system)
Air‑to‑air multi-split outdoor units                                             27                                                                                               65kW <      R              2.90
(whether or not supplied or offered for supply as part of a multi-split system)