Document ID: chunk:federal_register_of_legislation:F2015L01712:clause:7_5:p2
Version: federal_register_of_legislation:F2015L01712
Segment Type: clause
Provision Reference: sch 7 cl 5 (pt 2/4)
Character Range: 7355–10180

a centrifugal backward‑curved fan;
 (e) a centrifugal radial bladed fan;
 (f) a centrifugal forward‑curved fan.
eligible small motor type: each of the following is an eligible small motor type:
 (a) a shaded pole motor;
 (b) a permanent split capacitor motor.
fan air power has the same meaning as in AS/NZS ISO 12759:2013.
fan impeller power means the mechanical power transferred to the fan impeller, calculated in accordance with AS/NZS ISO 12759:2013.
fan shaft power means the mechanical power transferred to the fan shaft, calculated in accordance with AS/NZS ISO 12759:2013.
fan static air power has the same meaning as in AS/NZS ISO 12759:2013.
freezer cabinet means a cabinet that meets the definition of a refrigerated display cabinet as defined in AS 1731.6-2003, and that has a temperature class of L1 or L2.
heating/cooling ventilation fan means a fan that:
 (a) services the space heating, space cooling or ventilation systems of a building; and
 (b) is designed or configured to operate only when the space heating or space cooling applications are heating or cooling the spaces enclosed by the building envelope.
Note: An example is a boiler draught fan that is dedicated to providing supply air to heating or cooling system, and that does not also serve a general ventilation purpose.
high efficiency fan installation—see subsection 9(3).
housing means a casing around the impeller that guides the gas stream towards, through and from the impeller.
impeller means the part of the fan that imparts energy into the gas flow.
installation category means one of the following installation categories:
 (a) installation category A;
 (b) installation category B;
 (c) installation category C;
 (d) installation category D.
installation category A means an arrangement where the fan is installed with free inlet and outlet conditions.
installation category B means an arrangement where the fan is installed with a free inlet and with a duct fitted to its outlet.
installation category C means an arrangement where the fan is installed with a duct fitted to its inlet and with free outlet conditions.
installation category D means an arrangement where the fan is installed with a duct fitted to its inlet and outlet.
installed HE fan (short for installed high efficiency fan)—see subsection 9(5).
installed SM fan (short for installed small motor fan)—see subsection 9(7).
mixed‑flow fan—see section 6.
motor efficiency has the same meaning as in AS/NZS ISO 12759:2013.
motor input power has the same meaning as in AS/NZS ISO 12759:2013.
multi‑speed control means a control system where the motor is able to run at a number of discrete speeds, and is automatically changed from one speed to another according to temperature, pressure, humidity, or feedback from carbon monoxide or carbon dioxide sensors and that may