Document ID: chunk:federal_register_of_legislation:F2019L00490:clause:2_15
Version: federal_register_of_legislation:F2019L00490
Segment Type: clause
Provision Reference: sch 2 cl 15
Character Range: 104394–105108

15  Specific requirements for single‑split outdoor units
 (1) This section applies in relation to all tests undertaken for the purposes of Part 3 and Part 5 of this Determination.
 (2) A single‑split outdoor unit must be tested using a representative indoor unit. The representative indoor unit must:
 (a) be of the same type of indoor air distribution as the outdoor unit is being supplied or offered to be supplied for (i.e. ducted or non‑ducted); and
 (b) be specified by make and model number and be readily available for possible check-testing purposes; and
 (c) be the same for all cooling and heating tests; and
 (d) be configured with a remote control, unless the controls are integral to the indoor unit.