Document ID: chunk:federal_register_of_legislation:F2019L00490:clause:2_11
Version: federal_register_of_legislation:F2019L00490
Segment Type: clause
Provision Reference: sch 2 cl 11
Character Range: 96556–98671

11  Alternative test methods for VRF type multi-split outdoor units and products > 30kW
 (1) This section applies in relation to all tests undertaken for the purposes of Part 3 and Part 5 of this Determination.
 (2) This section applies to:
 (a) variable refrigerant flow (VRF) type multi-split outdoor units; and
 (b) products that:
 (i) are in a product class other than 3, 4, 22 or 23; and
 (ii) have a rated standard cooling full capacity or, for heating‑only products, a rated standard heating full capacity, of more than 30kW.
 (3) Subject to this section and section 4 of this Schedule, tests for the purposes of Part 3 and Part 5 of this Determination may be undertaken according to the methods set out in the following:
 (a) EN 14511:2018;
 (b) a standard based on ISO 5151:2017 (non-ducted air conditioners, any VRF multi‑split and fixed head multi-split outdoor unit greater than 30kW rated standard cooling full capacity or, for heating‑only products, rated standard heating full capacity);
 (c) a standard based on ISO 13253:2017 (ducted air conditioners);
 (d) a standard based on ISO 15042:2017 (multi-split outdoor units);
 (e) AHRI 1230:2010.
 (4) Subject to this section, information set out in any of the following certificates may be relied on for the purposes of Part 3 and Part 5 of this Determination without further testing being conducted:
 (a) an AHRI certificate, being a certified test certificate from the Air-Conditioning, Heating, and Refrigeration Institute;
Note: Further information on AHRI certification could, in 2019, be found at www.ahrinet.org.
 (b) a Eurovent certificate, being a certified test certificate from the European Association of Air Handling and Refrigerating Equipment Manufacturers.
Note: Further information on Eurovent certification could, in 2019, be found at www.eurovent‑certification.com.
 (5) A standard or certificate mentioned in this section may be relied on only in relation to testing at:
 (a) an electrical supply voltage of 230V single-phase or 400V three‑phase; and
 (b) a frequency of 50Hz; and
 (c) the H1, H2, H3 or T1 temperature conditions.