Document ID: chunk:federal_register_of_legislation:F2019L00490:clause:6_30:p2
Version: federal_register_of_legislation:F2019L00490
Segment Type: clause
Provision Reference: sch 6 cl 30 (pt 2/2)
Character Range: 64367–65664

3 cooling temperature bins, for the hot, average and cold zones. AS/NZS 3823.4.2:2014 has 3 heating temperature bins, for the hot, average and cold zones.
Unitary single duct air conditioners
 (4) For section 6 of Schedule 3, for a unitary single duct air conditioner within product classes 3 or 4, the Cooling Season Total Energy Consumption and (if applicable) Heating Season Total Energy Consumption must be calculated for each climate zone by multiplying the rated power input specified by subsection (5) or subsection (6) by the hours of operation set out in the following table:

Zone     Cooling hours  Heating hours
Hot      2247           277
Average  840            1291
Cold     545            2660

 (5) A wall mounted unitary single duct air conditioner in product class 3 must use the rated power input derived from the standard cooling capacity test at full load.
 (6) A portable unitary single duct air conditioner in product class 4 must use the rated power input derived from:
 (a) if the duration of the supplementary water tank is 4 hours or longer—the standard cooling full capacity test using the supplementary water tank in accordance with the additional requirements of Appendix B of AS/NZS 3823.1.5:2015; and
 (b) otherwise—the standard cooling capacity test at full load.