Document ID: 02013R0811-20170307
Language: ENG

02013R0811 — EN — 07.03.2017 — 002.001
This text is meant purely as a documentation tool and has no legal effect. The Union's institutions do not assume any liability for its contents. The authentic versions of the relevant acts, including their preambles, are those published in the Official Journal of the European Union and available in EUR-Lex. Those official texts are directly accessible through the links embedded in this document
<table><col/><col/><tr><td><p><a>&#9658;B</a></p></td><td><p>                        COMMISSION DELEGATED REGULATION (EU) No 811/2013</p><p>of 18 February 2013</p><p>supplementing Directive 2010/30/EU of the European Parliament and of the Council with regard to the energy labelling of space heaters, combination heaters, packages of space heater, temperature control and solar device and packages of combination heater, temperature control and solar device</p><p><a>(Text with EEA relevance)</a></p><p>(OJ L 239 6.9.2013, p. 1)</p></td></tr></table>
Amended by:
<table><col/><col/><col/><col/><col/><tr><td><p>&#160;</p></td><td><p>&#160;</p></td><td><p>Official Journal</p></td></tr><tr><td><p>&#160;&#160;No</p></td><td><p>page</p></td><td><p>date</p></td></tr><tr><td><p><a>&#9658;M1</a></p></td><td><p><a>                              COMMISSION DELEGATED REGULATION (EU) No 518/2014&#160;of 5 March 2014</a></p></td><td><p>&#160;&#160;L&#160;147</p></td><td><p>1</p></td><td><p>17.5.2014</p></td></tr><tr><td><p><a>&#9658;M2</a></p></td><td><p><a>                              COMMISSION DELEGATED REGULATION (EU) 2017/254&#160;of 30 November 2016</a></p></td><td><p>&#160;&#160;L&#160;38</p></td><td><p>1</p></td><td><p>15.2.2017</p></td></tr></table>
COMMISSION DELEGATED REGULATION (EU) No 811/2013
of 18 February 2013
supplementing Directive 2010/30/EU of the European Parliament and of the Council with regard to the energy labelling of space heaters, combination heaters, packages of space heater, temperature control and solar device and packages of combination heater, temperature control and solar device
(Text with EEA relevance)
Article 1
Subject matter and scope
1. This Regulation establishes requirements for the energy labelling of, and the provision of supplementary product information on, space heaters and combination heaters with a rated heat output ≤ 70 kW, packages of space heater ≤ 70 kW, temperature control and solar device and packages of combination heater ≤ 70 kW, temperature control and solar device.
2. This Regulation shall not apply to:
(a) heaters specifically designed for using gaseous or liquid fuels predominantly produced from biomass;
(b) heaters using solid fuels;
(c) heaters within the scope of Directive 2010/75/EU of the European Parliament and of the Council ( 1 );
(d) heaters generating heat only for the purpose of providing hot drinking or sanitary water;
(e) heaters for heating and distributing gaseous heat transfer media such as vapour or air;
(f) cogeneration space heaters with a maximum electrical capacity of 50 kW or above.
Article 2
Definitions
In addition to the definitions set out in Article 2 of Directive 2010/30/EC, the following definitions shall apply for the purposes of this Regulation:
(1) ‘heater’ means a space heater or combination heater;
(2) ‘space heater’ means a device that
(a) provides heat to a water-based central heating system in order to reach and maintain at a desired level the indoor temperature of an enclosed space such as a building, a dwelling or a room; and
(b) is equipped with one or more heat generators;
(3) ‘combination heater’ means a space heater that is designed to also provide heat to deliver hot drinking or sanitary water at given temperature levels, quantities and flow rates during given intervals, and is connected to an external supply of drinking or sanitary water;
(4) ‘water-based central heating system’ means a system using water as a heat transfer medium to distribute centrally generated heat to heat emitters for the space heating of buildings, or parts thereof;
(5) ‘heat generator’ means the part of a heater that generates the heat using one or more of the following processes:
(a) combustion of fossil fuels and/or biomass fuels;
(b) use of the Joule effect in electric resistance heating elements;
(c) capture of ambient heat from an air source, water source or ground source, and/or waste heat;
(6) ‘rated heat output’ ( Prated ) means the declared heat output of a heater when providing space heating and, if applicable, water heating at standard rating conditions, expressed in kW; for heat pump space heaters and heat pump combination heaters the standard rating conditions for establishing the rated heat output are the reference design conditions, as set out in Annex VII, Table 10;
(7) ‘standard rating conditions’ means the operating conditions of heaters under average climate conditions for establishing the rated heat output, seasonal space heating energy efficiency, water heating energy efficiency and sound power level;
(8) ‘biomass’ means the biodegradable fraction of products, waste and residues from biological origin from agriculture (including vegetal and animal substances), forestry and related industries including fisheries and aquaculture, as well as the biodegradable fraction of industrial and municipal waste;
(9) ‘biomass fuel’ means a gaseous or liquid fuel produced from biomass;
(10) ‘fossil fuel’ means a gaseous or liquid fuel of fossil origin;
(11) ‘cogeneration space heater’ means a space heater simultaneously generating heat and electricity in a single process;
(12) ‘temperature control’ means the equipment that interfaces with the end-user regarding the values and timing of the desired indoor temperature, and communicates relevant data to an interface of the heater such as a central processing unit, thus helping to regulate the indoor temperature(s);
(13) ‘solar device’ means a solar-only system, a solar collector, a solar hot water storage tank or a pump in the collector loop, which are placed on the market separately;
(14) ‘solar-only system’ means a device that is equipped with one or more solar collectors and solar hot water storage tanks and possibly pumps in the collector loop and other parts, which is placed on the market as one unit and is not equipped with any heat generator except possibly one or more back-up immersion heaters;
(15) ‘solar collector’ means a device designed to absorb global solar irradiance and to transfer the heat energy so produced to a fluid passing through it;
(16) ‘hot water storage tank’ means a vessel for storing hot water for water and/or space heating purposes, including any additives, which is not equipped with any heat generator except possibly one or more back-up immersion heaters;
(17) ‘solar hot water storage tank’ means a hot water storage tank storing heat energy produced by one or more solar collectors;
(18) ‘back-up immersion heater’ means a Joule effect electric resistance heater that is part of a hot water storage tank and generates heat only when the external heat source is disrupted (including during maintenance periods) or out of order, or that is part of a solar hot water storage tank and provides heat when the solar heat source is not sufficient to satisfy required comfort levels;
(19) ‘package of space heater, temperature control and solar device’ means a package offered to the end-user containing one or more space heaters combined with one or more temperature controls and/or one or more solar devices;
(20) ‘package of combination heater, temperature control and solar device’ means a package offered to the end-user containing one or more combination heaters combined with one or more temperature controls, and/or one or more solar devices;
(21) ‘seasonal space heating energy efficiency’ ( η s ) means the ratio between the space heating demand for a designated heating season, supplied by a space heater, a combination heater, a package of space heater, temperature control and solar device or a package of combination heater, temperature control and solar device, and the annual energy consumption required to meet this demand, expressed in %;
(22) ‘water heating energy efficiency’ ( η wh ) means the ratio between the useful energy in the drinking or sanitary water provided by a combination heater or a package of combination heater, temperature control and solar device, and the energy required for its generation, expressed in %;
(23) ‘sound power level’ ( L WA ) means the A-weighted sound power level, indoors and/or outdoors, expressed in dB.
For the purposes of Annexes II to VIII, additional definitions are set out in Annex I.
Article 3
Responsibilities of suppliers and timetable
1. From 26 September 2015 suppliers placing space heaters on the market and/or putting them into service, including those integrated in packages of space heater, temperature control and solar device, shall ensure that:
(a) a printed label complying with the format and content of information set out in point 1.1 of Annex III is provided for each space heater conforming to the seasonal space heating energy efficiency classes set out in point 1 of Annex II, whereby: for heat pump space heaters, the printed label is provided at least in the packaging of the heat generator; for space heaters intended for use in packages of space heater, temperature control and solar device, a second label complying with the format and content of information set out in point 3 of Annex III is provided for each space heater;
(b) a product fiche, as set out in point 1 of Annex IV, is provided for each space heater, whereby: for heat pump space heaters, the product fiche is provided at least for the heat generator; for space heaters intended for use in packages of space heater, temperature control and solar device, a second fiche, as set out in point 5 of Annex IV, is provided;
(c) the technical documentation, as set out in point 1 of Annex V, is provided on request to the authorities of the Member States and to the Commission;
(d) any advertisement relating to a specific space heater model and containing energy-related or price information includes a reference to the seasonal space heating energy efficiency class under average climate conditions for that model;
(e) any technical promotional material concerning a specific space heater model and describing its specific technical parameters includes a reference to the seasonal space heating energy efficiency class under average climate conditions for that model;
(f) an electronic label in the format and containing the information set out in point 1.1 of Annex III is made available to dealers for each space heater model conforming to the seasonal space heating energy efficiency classes set out in point 1 of Annex II;
(g) an electronic product fiche as set out in point 1 of Annex IV is made available to dealers for each space heater model, whereby for heat pump space heaters models, the electronic product fiche is made available to dealers at least for the heat generator.
From 26 September 2019 a printed label complying with the format and content of information set out in point 1.2 of Annex III shall be provided for each space heater conforming to the seasonal space heating energy efficiency classes set out in point 1 of Annex II, whereby: for heat pump space heaters, the printed label shall be provided at least in the packaging of the heat generator.
From 26 September 2019 an electronic label in the format and containing the information set out in point 1.2 of Annex III shall be made available to dealers for each space heater model conforming to the seasonal space heating energy efficiency classes set out in point 1 of Annex II.
2. From 26 September 2015 suppliers placing combination heaters on the market and/or putting them into service, including those integrated in packages of combination heater, temperature control and solar device, shall ensure that:
(a) a printed label complying with the format and content of information set out in point 2.1 of Annex III is provided for each combination heater conforming to the seasonal space heating energy efficiency classes and water heating energy efficiency classes set out in points 1 and 2 of Annex II, whereby: for heat pump combination heaters, the printed label is provided at least in the packaging of the heat generator; for combination heaters intended for use in packages of combination heater, temperature control and solar device, a second label complying with the format and content of information set out in point 4 of Annex III is provided for each combination heater;
(b) a product fiche, as set out in point 2 of Annex IV, is provided for each combination heater, whereby: for heat pump combination heaters, the product fiche is provided at least for the heat generator; for combination heaters intended for use in packages of combination heater, temperature control and solar device, a second fiche, as set out in point 6 of Annex IV, is provided;
(c) the technical documentation, as set out in point 2 of Annex V, is provided on request to the authorities of the Member States and to the Commission;
(d) any advertisement relating to a specific combination heater model and containing energy-related or price information includes a reference to the seasonal space heating energy efficiency class and water heating energy efficiency class under average climate conditions for that model;
(e) any technical promotional material concerning a specific combination heater model and describing its specific technical parameters includes a reference to the seasonal space heating energy efficiency class and water heating energy efficiency class under average climate conditions for that model;
(f) an electronic label in the format and containing the information set out in point 2.1 of Annex III is made available to dealers for each combination heater model conforming to the seasonal space heating energy efficiency classes and water heating energy efficiency classes set out in points 1 and 2 of Annex II;
(g) an electronic product fiche as set out in point 2 of Annex IV is made available to dealers for each combination heater model, whereby for heat pump combination heaters models, the electronic product fiche is made available to dealers at least for the heat generator.
From 26 September 2019 a printed label complying with the format and content of information set out in point 2.2 of Annex III shall be provided for each combination heater conforming to the seasonal space heating energy efficiency classes and water heating energy efficiency classes set out in points 1 and 2 of Annex II, whereby: for heat pump combination heaters, the printed label shall be provided at least in the packaging of the heat generator.
From 26 September 2019 an electronic label in the format and containing the information set out in point 2.2 of Annex III shall be made available to dealers for each combination heater model conforming to the seasonal space heating energy efficiency classes and water heating energy efficiency classes set out in points 1 and 2 of Annex II.
3. From 26 September 2015 suppliers placing temperature controls on the market and/or putting them into service shall ensure that:
(a) a product fiche, as set out in point 3 of Annex IV, is provided;
(b) the technical documentation, as set out in point 3 of Annex V, is provided on request to the authorities of the Member States and to the Commission;
(c) an electronic product fiche, as set out in point 3 of Annex IV, is made available to dealers for each temperature control model.
4. From 26 September 2015 suppliers placing solar devices on the market and/or putting them into service shall ensure that:
(a) a product fiche, as set out in point 4 of Annex IV, is provided;
(b) the technical documentation, as set out in point 4 of Annex V, is provided on request to the authorities of the Member States and to the Commission;
(c) an electronic product fiche, as set out in point 4 of Annex IV, is made available to dealers for each solar device model.
5. From 26 September 2015 suppliers placing packages of space heater, temperature control and solar device on the market and/or putting them into service shall ensure that:
(a) a printed label complying with the format and content of information set out in point 3 of Annex III is provided for each package of space heater, temperature control and solar device conforming to the seasonal space heating energy efficiency classes set out in point 1 of Annex II;
(b) a product fiche, as set out in point 5 of Annex IV, is provided for each package of space heater, temperature control and solar device;
(c) the technical documentation, as set out in point 5 of Annex V, is provided on request to the authorities of the Member States and to the Commission;
(d) any advertisement relating to a specific package of space heater, temperature control and solar device model and containing energy-related or price information includes a reference to the seasonal space heating energy efficiency class under average climate conditions for that model;
(e) any technical promotional material concerning a specific package of space heater, temperature control and solar device model and describing its specific technical parameters includes a reference to the seasonal space heating energy efficiency class under average climate conditions for that model;
(f) an electronic label in the format and containing the information set out in point 3 of Annex III is made available to dealers for each model comprising a package of space heater, temperature control and solar device conforming to the seasonal space heating energy efficiency classes set out in point 1 of Annex II;
(g) an electronic product fiche as set out in point 5 of Annex IV is made available to dealers for each model comprising a package of space heater, temperature control and solar device.
6. From 26 September 2015 suppliers placing packages of combination heater, temperature control and solar device on the market and/or putting them into service shall ensure that:
(a) a printed label complying with the format and content of information set out in point 4 of Annex III is provided for each package of combination heater, temperature control and solar device conforming to the seasonal space heating energy efficiency classes and water heating energy efficiency classes set out in points 1 and 2 of Annex II;
(b) a product fiche, as set out in point 6 of Annex IV, is provided for each package of combination heater, temperature control and solar device;
(c) the technical documentation, as set out in point 6 of Annex V, is provided on request to the authorities of the Member States and to the Commission;
(d) any advertisement relating to a specific package of combination heater, temperature control and solar device model and containing energy-related or price information includes a reference to the seasonal space heating energy efficiency class and water heating energy efficiency class under average climate conditions for that model;
(e) any technical promotional material concerning a specific package of combination heater, temperature control and solar device model and describing its specific technical parameters includes a reference to the seasonal space heating energy efficiency class and water heating energy efficiency class under average climate conditions for that model;
(f) an electronic label in the format and containing the information set out in point 4 of Annex III is made available to dealers for each model comprising a package of combination heater, temperature control and solar device conforming to the seasonal space heating energy efficiency classes and water heating energy efficiency classes set out in points 1 and 2 of Annex II;
(g) an electronic product fiche as set out in point 6 of Annex IV is made available to dealers for each model comprising a package of combination heater, temperature control and solar device.
Article 4
Responsibilities of dealers
1. Dealers of space heaters shall ensure that:
(a) each space heater, at the point of sale, bears the label provided by suppliers in accordance with Article 3(1), as set out in point 1 of Annex III, on the outside of the front of the appliance, in such a way as to be clearly visible;
(b) space heaters offered for sale, hire or hire-purchase, where the end-user cannot be expected to see the space heater displayed, are marketed with the information provided by the suppliers in accordance with point 1 of Annex VI, except where the offer is made through the internet, in which case the provisions in Annex IX shall apply;
(c) any advertisement relating to a specific space heater model and containing energy-related or price information includes a reference to the seasonal space heating energy efficiency class under average climate conditions for that model;
(d) any technical promotional material concerning a specific space heater model and describing its specific technical parameters includes a reference to the seasonal space heating energy efficiency class under average climate conditions for that model.
2. Dealers of combination heaters shall ensure that:
(a) each combination heater, at the point of sale, bears the label provided by suppliers in accordance with Article 3(2), as set out in point 2 of Annex III, on the outside of the front of the appliance, in such a way as to be clearly visible;
(b) combination heaters offered for sale, hire or hire-purchase, where the end-user cannot be expected to see the combination heater displayed, are marketed with the information provided by the suppliers in accordance with point 2 of Annex VI, except where the offer is made through the internet, in which case the provisions in Annex IX shall apply;
(c) any advertisement relating to a specific combination heater model and containing energy-related or price information includes a reference to the seasonal space heating energy efficiency class and water heating energy efficiency class under average climate conditions for that model;
(d) any technical promotional material concerning a specific combination heater model and describing its specific technical parameters includes a reference to the seasonal space heating energy efficiency class and water heating energy efficiency class under average climate conditions for that model.
3. Dealers of packages of space heater, temperature control and solar device shall ensure, based on the label and fiches provided by suppliers in accordance with Article 3(1), (3), (4) and (5), that:
(a) any offer for a specific package includes the seasonal space heating energy efficiency and the seasonal space heating energy efficiency class for that package under average, colder or warmer climate conditions, as applicable, by displaying with the package the label set out in point 3 of Annex III and providing the fiche set out in point 5 of Annex IV, duly filled in according to the characteristics of that package;
(b) packages of space heater, temperature control and solar device offered for sale, hire or hire-purchase, where the end-user cannot be expected to see the package of space heater, temperature control and solar device displayed, are marketed with the information provided in accordance with point 3 of Annex VI, except where the offer is made through the internet, in which case the provisions in Annex IX shall apply;
(c) any advertisement relating to a specific package of space heater, temperature control and solar device model and containing energy-related or price information includes a reference to the seasonal space heating energy efficiency class under average climate conditions for that model;
(d) any technical promotional material concerning a specific package of space heater, temperature control and solar device model and describing its specific technical parameters includes a reference to the seasonal space heating energy efficiency class under average climate conditions for that model.
4. Dealers of packages of combination heater, temperature control and solar device shall ensure, based on the label and fiches provided by suppliers in accordance with Article 3(2), (3), (4) and (6), that:
(a) any offer for a specific package of combination heater, temperature control and solar device includes the seasonal space heating energy efficiency, the water heating energy efficiency, the seasonal space heating energy efficiency class and the water heating energy efficiency class for that package under average, colder or warmer climate conditions, as applicable, by displaying with the package the label set out in point 4 of Annex III and providing the fiche set out in point 6 of Annex IV, duly filled in according to the characteristics of that package;
(b) packages of combination heater, temperature control and solar device offered for sale, hire or hire-purchase, where the end-user cannot be expected to see the package of combination heater, temperature control and solar device displayed, are marketed with the information provided in accordance with point 4 of Annex VI, except where the offer is made through the internet, in which case the provisions in Annex IX shall apply;
(c) any advertisement relating to a specific package of combination heater, temperature control and solar device model and containing energy-related or price information includes a reference to the seasonal space heating energy efficiency class and water heating energy efficiency class under average climate conditions for that model;
(d) any technical promotional material concerning a specific package of combination heater, temperature control and solar device model and describing its specific technical parameters includes a reference to the seasonal space heating energy efficiency class and water heating energy efficiency class under average climate conditions for that model.
Article 5
Measurement and calculation methods
The information to be provided pursuant to Articles 3 and 4 shall be obtained by reliable, accurate and reproducible measurement and calculation methods which take into account the recognised state-of-the-art measurement and calculation methods, as set out in Annex VII.
Article 6
Verification procedure for market surveillance purposes
Member States shall apply the procedure set out in Annex VIII when assessing the conformity of the declared seasonal space heating energy efficiency class, water heating energy efficiency class, seasonal space heating energy efficiency, water heating energy efficiency and sound power level of heaters.
Article 7
Review
The Commission shall review this Regulation in the light of technological progress no later than five years after its entry into force. The review shall in particular assess any significant changes in the market shares of various types of heaters related to the labels set out in points 1.2. and 2.2. of Annex III, the feasibility and usefulness of indicating heater efficiency other than heat pump efficiency based on standardised heating seasons, the appropriateness of the package fiches and labels set out in points 3 and 4 of Annex III and points 5 and 6 of Annex IV, and the appropriateness of including passive flue heat recovery devices in the scope of this Regulation.
Article 8
Entry into force and application
This Regulation shall enter into force on the twentieth day following that of its publication in the Official Journal of the European Union .
This Regulation shall be binding in its entirety and directly applicable in all Member States.
ANNEX I
Definitions applicable for Annexes II to VIII
For the purposes of Annexes II to VIII the following definitions shall apply:
Definitions related to heaters:
(1) ‘boiler space heater’, for the purposes of Figures 1 to 4 in Annex IV referred to as ‘boiler’, means a space heater that generates heat using the combustion of fossil fuels and/or biomass fuels, and/or using the Joule effect in electric resistance heating elements;
(2) ‘boiler combination heater’, for the purposes of Figures 1 to 4 in Annex IV referred to as ‘boiler’, means a boiler space heater that is designed to also provide heat to deliver hot drinking or sanitary water at given temperature levels, quantities and flow rates during given intervals, and is connected to an external supply of drinking or sanitary water;
(3) ‘heat pump space heater’, for the purposes of Figures 1 and 3 in Annex IV referred to as ‘heat pump’, means a space heater using ambient heat from an air source, water source or ground source, and/or waste heat for heat generation; a heat pump space heater may be equipped with one or more supplementary heaters using the Joule effect in electric resistance heating elements or the combustion of fossil and/or biomass fuels;
(4) ‘heat pump combination heater’, for the purposes of Figures 1 and 3 in Annex IV referred to as ‘heat pump’, means a heat pump space heater that is designed to also provide heat to deliver hot drinking or sanitary water at given temperature levels, quantities and flow rates during given intervals, and is connected to an external supply of drinking or sanitary water;
(5) ‘supplementary heater’ means a non-preferential heater that generates heat in cases where the heat demand is greater than the rated heat output of the preferential heater;
(6) ‘rated heat output of supplementary heater’ ( Psup ) means the declared heat output of the supplementary heater when providing space heating and, if applicable, water heating at standard rating conditions, expressed in kW; if the supplementary heater is a heat pump space heater or heat pump combination heater, the standard rating condition for establishing the rated heat output of supplementary heater is the outdoor temperature Tj = + 7 °C;
(7) ‘outdoor temperature’ ( T j ) means the dry bulb outdoor air temperature, expressed in degrees Celsius; the relative humidity may be indicated by a corresponding wet bulb temperature;
(8) ‘annual energy consumption’ ( Q HE ) means the annual energy consumption of a heater required for space heating to meet the reference annual heating demand for a designated heating season, expressed in kWh in terms of the final energy and/or in GJ in terms of GCV ;
(9) ‘standby mode’ means a condition where the heater is connected to the mains power source, depends on energy input from the mains power source to work as intended and provides only the following functions, which may persist for an indefinite time: reactivation function, or reactivation function and only an indication of enabled reactivation function, and/or information or status display;
(10) ‘standby mode power consumption’ ( P SB ) means the power consumption of a heater in standby mode, expressed in kW;
(11) ‘conversion coefficient’ ( CC ) means a coefficient reflecting the estimated 40 % average EU generation efficiency referred to in Directive 2012/27/EU of the European Parliament and of the Council ( 2 ); the value of the conversion coefficient is CC = 2,5;
(12) ‘gross calorific value’ ( GCV ) means the total amount of heat released by a unit quantity of fuel when it is burned completely with oxygen and when the products of combustion are returned to ambient temperature; this quantity includes the condensation heat of any water vapour contained in the fuel and of the water vapour formed by the combustion of any hydrogen contained in the fuel;
Definitions related to boiler space heaters, boiler combination heaters and cogeneration space heaters:
(13) ‘seasonal space heating energy efficiency in active mode’ ( η son ) means
— for fuel boiler space heaters and fuel boiler combination heaters, a weighted average of the useful efficiency at rated heat output and the useful efficiency at 30 % of the rated heat output, expressed in %;
— for electric boiler space heaters and electric boiler combination heaters, the useful efficiency at rated heat output, expressed in %;
— for cogeneration space heaters not equipped with supplementary heaters, the useful efficiency at rated heat output, expressed in %;
— for cogeneration space heaters equipped with supplementary heaters, a weighted average of the useful efficiency at rated heat output with supplementary heater disabled, and the useful efficiency at rated heat output with supplementary heater enabled, expressed in %;
(14) ‘useful efficiency’ ( η ) means the ratio of the useful heat output and the total energy input of a boiler space heater, boiler combination heater or cogeneration space heater, expressed in %, whereby the total energy input is expressed in terms of GCV and/or in terms of final energy multiplied by CC ;
(15) ‘useful heat output’ ( P ) means the heat output of a boiler space heater, boiler combination heater or cogeneration space heater transmitted to the heat carrier, expressed in kW;
(16) ‘electrical efficiency’ ( η el ) means the ratio of the electricity output and the total energy input of a cogeneration space heater, expressed in %, whereby the total energy input is expressed in terms of GCV and/or in terms of final energy multiplied by CC ;
(17) ‘ignition burner power consumption’ ( P ign ) means the power consumption of a burner intended to ignite the main burner, expressed in W in terms of GCV ;
(18) ‘condensing boiler’ means a boiler space heater or boiler combination heater in which, under normal operating conditions and at given operating water temperatures, the water vapour in the combustion products is partially condensed, in order to make use of the latent heat of this water vapour for heating purposes;
(19) ‘auxiliary electricity consumption’ means the annual electricity required for the designated operation of a boiler space heater, boiler combination heater or cogeneration space heater, calculated from the electric power consumption at full load ( elmax ), at part load ( elmin ), in standby mode and default operating hours at each mode, expressed in kWh in terms of final energy;
(20) ‘standby heat loss’ ( P stby ) means the heat loss of a boiler space heater, boiler combination heater or cogeneration space heater in operating modes without heat demand, expressed in kW;
Definitions related to heat pump space heaters and heat pump combination heaters:
(21) ‘rated coefficient of performance’ ( COP rated ) or ‘rated primary energy ratio’ ( PER rated ) means the declared heat capacity, expressed in kW, divided by the energy input, expressed in kW in terms of GCV and/or in kW in terms of final energy multiplied by CC , for heating provided at standard rating conditions;
(22) ‘reference design conditions’ means the combination of the reference design temperature, the maximum bivalent temperature and the maximum operation limit temperature, as set out in Annex VII, Table 10;
(23) ‘reference design temperature’ ( Tdesignh ) means the outdoor temperature, expressed in degrees Celsius, as set out in Annex VII, Table 10, at which the part load ratio is equal to 1;
(24) ‘part load ratio’ ( pl(T j ) ) means the outdoor temperature minus 16 °C divided by the reference design temperature minus 16 °C;
(25) ‘heating season’ means a set of operating conditions for average, colder and warmer climate conditions, describing per bin the combination of outdoor temperatures and the number of hours these temperatures occur per season;
(26) ‘bin’ ( bin j ) means a combination of an outdoor temperature and bin hours, as set out in Annex VII, Table 12;
(27) ‘bin hours’ ( H j ) means the hours per heating season, expressed in hours per year, at which an outdoor temperature occurs for each bin, as set out in Annex VII, Table 12;
(28) ‘part load for heating’ ( Ph(T j ) ) means the heating load at a specific outdoor temperature, calculated as the design load multiplied by the part load ratio and expressed in kW;
(29) ‘seasonal coefficient of performance’ ( SCOP ) or ‘seasonal primary energy ratio’ ( SPER ) means the overall coefficient of performance of a heat pump space heater or heat pump combination heater using electricity or the overall primary energy ratio of a heat pump space heater or heat pump combination heater using fuels, representative of the designated heating season, calculated as the reference annual heating demand divided by the annual energy consumption;
(30) ‘reference annual heating demand’ ( Q H ) means the reference heating demand for a designated heating season, to be used as the basis for calculating SCOP or SPER and calculated as the product of the design load for heating and the annual equivalent active mode hours, expressed in kWh;
(31) ‘annual equivalent active mode hours’ ( H HE ) means the assumed annual number of hours a heat pump space heater or heat pump combination heater has to provide the design load for heating to satisfy the reference annual heating demand, expressed in h;
(32) ‘active mode coefficient of performance’ ( SCOP on ) or ‘active mode primary energy ratio’ ( SPER on ) means the average coefficient of performance of the heat pump space heater or heat pump combination heater using electricity in active mode or the average primary energy ratio of the heat pump space heater or heat pump combination heater using fuels in active mode for the designated heating season;
(33) ‘supplementary capacity for heating’ ( sup(Tj) ) means the rated heat output Psup of a supplementary heater that supplements the declared capacity for heating to meet the part load for heating, if the declared capacity for heating is less than the part load for heating, expressed in kW;
(34) ‘bin-specific coefficient of performance’ ( COPbin(T j ) ) or ‘bin-specific primary energy ratio’ ( PERbin(T j ) ) means the coefficient of performance of the heat pump space heater or heat pump combination heater using electricity or primary energy ratio of the heat pump space heater or heat pump combination heater using fuel specific for every bin in a season, derived from the part load for heating, declared capacity for heating and declared coefficient of performance for specified bins and calculated for other bins by interpolation or extrapolation, corrected where necessary by the degradation coefficient;
(35) ‘declared capacity for heating’ ( Pdh(T j ) ) means the heating capacity a heat pump space heater or heat pump combination heater is able to deliver, for an outdoor temperature, expressed in kW;
(36) ‘capacity control’ means the ability of a heat pump space heater or heat pump combination heater to change its capacity by changing the volumetric flow rate of at least one of the fluids needed to operate the refrigeration cycle, to be indicated as ‘fixed’ if the volumetric flow rate cannot be changed or ‘variable’ if the volumetric flow rate is changed or varied in series of two or more steps;
(37) ‘design load for heating’ ( Pdesignh ) means the rated heat output ( Prated ) of a heat pump space heater or heat pump combination heater at the reference design temperature, whereby the design load for heating is equal to the part load for heating with outdoor temperature equal to reference design temperature, expressed in kW;
(38) ‘declared coefficient of performance’ ( COPd(T j ) ) or ‘declared primary energy ratio’ ( PERd(T j ) ) means the coefficient of performance or primary energy ratio at a limited number of specified bins;
(39) ‘bivalent temperature’ ( T biv ) means the outdoor temperature declared by the supplier for heating at which the declared capacity for heating equals the part load for heating and below which the declared capacity for heating requires supplementary capacity for heating to meet the part load for heating, expressed in degrees Celsius;
(40) ‘operation limit temperature’ ( TOL ) means the outdoor temperature declared by the supplier for heating, below which the air-to-water heat pump space heater or air-to-water heat pump combination heater will not be able to deliver any heating capacity and the declared capacity for heating is equal to zero, expressed in degrees Celsius;
(41) ‘heating water operation limit temperature’ ( WTOL ) means the outlet water temperature declared by the supplier for heating, above which the heat pump space heater or heat pump combination heater will not be able to deliver any heating capacity and the declared capacity heating is equal to zero, expressed in degrees Celsius;
(42) ‘cycling interval capacity for heating’ ( Pcych ) means the integrated heating capacity over the cycling test interval for heating, expressed in kW;
(43) ‘cycling interval efficiency’ ( COPcyc or PERcyc ) means the average coefficient of performance or average primary energy ratio over the cycling test interval, calculated as the integrated heating capacity over the interval, expressed in kWh, divided by the integrated energy input over that same interval, expressed in kWh in terms of GCV and/or in kWh in terms of final energy multiplied by CC ;
(44) ‘degradation coefficient’ ( Cdh ) means the measure of efficiency loss due to cycling of a heat pump space heater or heat pump combination heater; if Cdh is not determined by measurement then the default degradation coefficient is Cdh = 0,9;
(45) ‘active mode’ means the condition corresponding to the hours with a heating load for the enclosed space and activated heating function; this condition may involve cycling of the heat pump space heater or heat pump combination heater to reach or maintain a required indoor air temperature;
(46) ‘off mode’ means a condition in which the heat pump space heater or heat pump combination heater is connected to the mains power source and is not providing any function, including conditions providing only an indication of off mode condition and conditions providing only functionalities intended to ensure electromagnetic compatibility pursuant to Directive 2004/108/EC of the European Parliament and of the Council ( 3 );
(47) ‘thermostat-off mode’ means the condition corresponding to the hours with no heating load and activated heating function, whereby the heating function is switched on but the heat pump space heater or heat pump combination heater is not operational; cycling in active mode is not considered as thermostat-off mode;
(48) ‘crankcase heater mode’ means the condition in which a heating device is activated to avoid the refrigerant migrating to the compressor so as to limit the refrigerant concentration in oil when the compressor is started;
(49) ‘off mode power consumption’ ( P OFF ) means the power consumption of a heat pump space heater or heat pump combination heater in off mode, expressed in kW;
(50) ‘thermostat-off mode power consumption’ ( P TO ) means the power consumption of the heat pump space heater or heat pump combination heater while in thermostat-off mode, expressed in kW;
(51) ‘crankcase heater mode power consumption’ ( P CK ) means the power consumption of the heat pump space heater or heat pump combination heater while in crankcase heater mode, expressed in kW;
(52) ‘low-temperature heat pump’ means a heat pump space heater that is specifically designed for low-temperature application, and that cannot deliver heating water with an outlet temperature of 52 °C at an inlet dry (wet) bulb temperature of – 7 °C (– 8 °C) in the reference design conditions for average climate;
(53) ‘low-temperature application’ means an application where the heat pump space heater delivers its declared capacity for heating at an indoor heat exchanger outlet temperature of 35 °C;
(54) ‘medium-temperature application’ means an application where the heat pump space heater or heat pump combination heater delivers its declared capacity for heating at an indoor heat exchanger outlet temperature of 55 °C;
Definitions related to water heating in combination heaters:
(55) ‘load profile’ means a given sequence of water draw-offs, as specified in Annex VII, Table 15; each combination heater meets at least one load profile;
(56) ‘water draw-off’ means a given combination of useful water flow rate, useful water temperature, useful energy content and peak temperature, as specified in Annex VII, Table 15;
(57) ‘useful water flow rate’ ( f ) means the minimum flow rate, expressed in litres per minute, for which hot water is contributing to the reference energy, as specified in Annex VII, Table 15;
(58) ‘useful water temperature’ ( T m ) means the water temperature, expressed in degrees Celsius, at which hot water starts contributing to the reference energy, as specified in Annex VII, Table 15;
(59) ‘useful energy content’ ( Q tap ) means the energy content of hot water, expressed in kWh, provided at a temperature equal to, or above, the useful water temperature, and at water flow rates equal to, or above, the useful water flow rate, as specified in Annex VII, Table 15;
(60) ‘energy content of hot water’ means the product of the specific heat capacity of water, the average temperature difference between the hot water output and cold water input, and the total mass of the hot water delivered;
(61) ‘peak temperature’ ( T p ) means the minimum water temperature, expressed in degrees Celsius, to be achieved during water draw-off, as specified in Annex VII, Table 15;
(62) ‘reference energy’ ( Q ref ) means the sum of the useful energy content of water draw-offs, expressed in kWh, in a particular load profile, as specified in Annex VII, Table 15;
(63) ‘maximum load profile’ means the load profile with the greatest reference energy that a combination heater is able to provide while fulfilling the temperature and flow rate conditions of that load profile;
(64) ‘declared load profile’ means the load profile applied when determining water heating energy efficiency;
(65) ‘daily electricity consumption’ ( Q elec ) means the consumption of electricity for water heating over 24 consecutive hours under the declared load profile, expressed in kWh in terms of final energy;
(66) ‘daily fuel consumption’ ( Q fuel ) means the consumption of fuels for water heating over 24 consecutive hours under the declared load profile, expressed in kWh in terms of GCV and, for the purposes of point 5(f) in Annex VII, expressed in GJ in terms of GCV ;
(67) ‘annual electricity consumption’ ( AEC ) means the annual electricity consumption of a combination heater for water heating under the declared load profile and under given climate conditions, expressed in kWh in terms of final energy;
(68) ‘annual fuel consumption’ ( AFC ) means the annual fossil fuel and/or biomass fuel consumption of a combination heater for water heating under the declared load profile and under given climate conditions, expressed in GJ in terms of GCV ;
Definitions related to solar devices:
(69) ‘annual non-solar heat contribution’ ( Q nonsol ), means the annual contribution of electricity (expressed in kWh in terms of primary energy) and/or fuels (expressed in kWh in terms of GCV ) to the useful heat output of a package of combination heater, temperature control and solar device, taking into account the annual amount of heat captured by the solar collector and the heat losses of the solar hot water storage tank;
(70) ‘collector aperture area’ ( A sol ), for the purposes of Figures 1 to 4 in Annex IV referred to as ‘collector size’, means the maximum projected area through which unconcentrated solar radiation enters the collector, expressed in m 2 ;
(71) ‘collector efficiency’ ( η col ) means the efficiency of the solar collector at a temperature difference between the solar collector and the surrounding air of 40 K and a global solar irradiance of 1 000 W/m 2 , expressed in %;
(72) ‘standing loss’ ( S ) means the heating power dissipated from a solar hot water storage tank at given water and ambient temperatures, expressed in W;
(73) ‘storage volume’ ( V ), for the purposes of Figures 1 to 4 in Annex IV referred to as ‘tank volume’, means the rated volume of a solar hot water storage tank, expressed in litres or m 3 ;
(74) ‘auxiliary electricity consumption’ ( Q aux ), for the purpose of Figure 5 in Annex IV referred to as ‘auxiliary electricity’, means the annual electricity consumption of a solar-only system that is due to the pump power consumption and the standby power consumption, expressed in kWh in terms of final energy;
(75) ‘pump power consumption’ ( solpump ) means the rated electrical power consumption of the pump in the collector loop of a solar-only system, expressed in W;
(76) ‘standby power consumption’ ( solstandby ) means the rated electrical power consumption of a solar-only system when the pump and the heat generator are inactive, expressed in W;
Other definitions:
(77) ‘average climate conditions’, ‘colder climate conditions’ and ‘warmer climate conditions’ mean the temperature and global solar irradiance conditions characteristic for the cities of Strasbourg, Helsinki and Athens, respectively;
(78) ‘model identifier’ means the code, usually alphanumeric, which distinguishes a specific space heater, combination heater, temperature control, solar device, package of space heater, temperature control and solar device, or package of combination heater, temperature control and solar device model from other models with the same trade mark, supplier’s name or dealer’s name.
ANNEX II
Energy efficiency classes
1. SEASONAL SPACE HEATING ENERGY EFFICIENCY CLASSES
The seasonal space heating energy efficiency class of a heater, with the exception of low-temperature heat pumps and heat pump space heaters for low-temperature application, shall be determined on the basis of its seasonal space heating energy efficiency as set out in Table 1.
The seasonal space heating energy efficiency classes of a low-temperature heat pump and a heat pump space heater for low-temperature application shall be determined on the basis of its seasonal space heating energy efficiency as set out in Table 2.
The seasonal space heating energy efficiency of a heater shall be calculated in accordance with points 3 and 4 of Annex VII, for heat pump space heaters, heat pump combination heaters and low-temperature heat pumps under average climate conditions.
Table 1
Seasonal space heating energy efficiency classes of heaters, with the exception of low-temperature heat pumps and heat pump space heaters for low-temperature application
<table><col/><col/><tbody><tr><td><p>Seasonal space heating energy efficiency class</p></td><td><p>Seasonal space heating energy efficiency<span>&#951;<span>s</span></span> in %</p></td></tr><tr><td><p>A<span>+++</span></p></td><td><p><span>&#951;<span>s</span></span> &#8805; 150</p></td></tr><tr><td><p>A<span>++</span></p></td><td><p>125 &#8804;<span>&#951;<span>s</span></span> &lt; 150</p></td></tr><tr><td><p>A<span>+</span></p></td><td><p>98 &#8804;<span>&#951;<span>s</span></span> &lt; 125</p></td></tr><tr><td><p>A</p></td><td><p>90 &#8804;<span>&#951;<span>s</span></span> &lt; 98</p></td></tr><tr><td><p>B</p></td><td><p>82 &#8804;<span>&#951;<span>s</span></span> &lt; 90</p></td></tr><tr><td><p>C</p></td><td><p>75 &#8804;<span>&#951;<span>s</span></span> &lt; 82</p></td></tr><tr><td><p>D</p></td><td><p>36 &#8804;<span>&#951;<span>s</span></span> &lt; 75</p></td></tr><tr><td><p>E</p></td><td><p>34 &#8804;<span>&#951;<span>s</span></span> &lt; 36</p></td></tr><tr><td><p>F</p></td><td><p>30 &#8804;<span>&#951;<span>s</span></span> &lt; 34</p></td></tr><tr><td><p>G</p></td><td><p><span>&#951;<span>s</span></span> &lt; 30</p></td></tr></tbody></table>
Table 2
Seasonal space heating energy efficiency classes of low-temperature heat pumps and heat pump space heaters for low-temperature application
<table><col/><col/><tbody><tr><td><p>Seasonal space heating energy efficiency class</p></td><td><p>Seasonal space heating energy efficiency<span>&#951;<span>s</span></span> in %</p></td></tr><tr><td><p>A<span>+++</span></p></td><td><p><span>&#951;<span>s</span></span> &#8805; 175</p></td></tr><tr><td><p>A<span>++</span></p></td><td><p>150 &#8804;<span>&#951;<span>s</span></span> &lt; 175</p></td></tr><tr><td><p>A<span>+</span></p></td><td><p>123 &#8804;<span>&#951;<span>s</span></span> &lt; 150</p></td></tr><tr><td><p>A</p></td><td><p>115 &#8804;<span>&#951;<span>s</span></span> &lt; 123</p></td></tr><tr><td><p>B</p></td><td><p>107 &#8804;<span>&#951;<span>s</span></span> &lt; 115</p></td></tr><tr><td><p>C</p></td><td><p>100 &#8804;<span>&#951;<span>s</span></span> &lt; 107</p></td></tr><tr><td><p>D</p></td><td><p>61 &#8804;<span>&#951;<span>s</span></span> &lt; 100</p></td></tr><tr><td><p>E</p></td><td><p>59 &#8804;<span>&#951;<span>s</span></span> &lt; 61</p></td></tr><tr><td><p>F</p></td><td><p>55 &#8804;<span>&#951;<span>s</span></span> &lt; 59</p></td></tr><tr><td><p>G</p></td><td><p><span>&#951;<span>s</span></span> &lt; 55</p></td></tr></tbody></table>
2. WATER HEATING ENERGY EFFICIENCY CLASSES
The water heating energy efficiency class of a combination heater shall be determined on the basis of its water heating energy efficiency as set out in Table 3.
The water heating energy efficiency of a combination heater shall be calculated in accordance with point 5 of Annex VII.
Table 3
Water heating energy efficiency classes of combination heaters, categorised by declared load profiles, η wh in %
<table><col/><col/><col/><col/><col/><col/><col/><col/><col/><tbody><tr><td><p>&#160;</p><div/></td><td><p>3XS</p></td><td><p>XXS</p></td><td><p>XS</p></td><td><p>S</p></td><td><p>M</p></td><td><p>L</p></td><td><p>XL</p></td><td><p>XXL</p></td></tr><tr><td><p>A<span>+++</span></p></td><td><p><span>&#951;<span>wh</span></span> &#8805; 62</p></td><td><p><span>&#951;<span>wh</span></span> &#8805; 62</p></td><td><p><span>&#951;<span>wh</span></span> &#8805; 69</p></td><td><p><span>&#951;<span>wh</span></span> &#8805; 90</p></td><td><p><span>&#951;<span>wh</span></span> &#8805; 163</p></td><td><p><span>&#951;<span>wh</span></span> &#8805; 188</p></td><td><p><span>&#951;<span>wh</span></span> &#8805; 200</p></td><td><p><span>&#951;<span>wh</span></span> &#8805; 213</p></td></tr><tr><td><p>A<span>++</span></p></td><td><p>53 &#8804;<span>&#951;<span>wh</span></span> &lt; 62</p></td><td><p>53 &#8804;<span>&#951;<span>wh</span></span> &lt; 62</p></td><td><p>61 &#8804;<span>&#951;<span>wh</span></span> &lt; 69</p></td><td><p>72 &#8804;<span>&#951;<span>wh</span></span> &lt; 90</p></td><td><p>130 &#8804;<span>&#951;<span>wh</span></span> &lt; 163</p></td><td><p>150 &#8804;<span>&#951;<span>wh</span></span> &lt; 188</p></td><td><p>160 &#8804;<span>&#951;<span>wh</span></span> &lt; 200</p></td><td><p>170 &#8804;<span>&#951;<span>wh</span></span> &lt; 213</p></td></tr><tr><td><p>A<span>+</span></p></td><td><p>44 &#8804;<span>&#951;<span>wh</span></span> &lt; 53</p></td><td><p>44 &#8804;<span>&#951;<span>wh</span></span> &lt; 53</p></td><td><p>53 &#8804;<span>&#951;<span>wh</span></span> &lt; 61</p></td><td><p>55 &#8804;<span>&#951;<span>wh</span></span> &lt; 72</p></td><td><p>100 &#8804;<span>&#951;<span>wh</span></span> &lt; 130</p></td><td><p>115 &#8804;<span>&#951;<span>wh</span></span> &lt; 150</p></td><td><p>123 &#8804;<span>&#951;<span>wh</span></span> &lt; 160</p></td><td><p>131 &#8804;<span>&#951;<span>wh</span></span> &lt; 170</p></td></tr><tr><td><p>A</p></td><td><p>35 &#8804;<span>&#951;<span>wh</span></span> &lt; 44</p></td><td><p>35 &#8804;<span>&#951;<span>wh</span></span> &lt; 44</p></td><td><p>38 &#8804;<span>&#951;<span>wh</span></span> &lt; 53</p></td><td><p>38 &#8804;<span>&#951;<span>wh</span></span> &lt; 55</p></td><td><p>65 &#8804;<span>&#951;<span>wh</span></span> &lt; 100</p></td><td><p>75 &#8804;<span>&#951;<span>wh</span></span> &lt; 115</p></td><td><p>80 &#8804;<span>&#951;<span>wh</span></span> &lt; 123</p></td><td><p>85 &#8804;<span>&#951;<span>wh</span></span> &lt; 131</p></td></tr><tr><td><p>B</p></td><td><p>32 &#8804;<span>&#951;<span>wh</span></span> &lt; 35</p></td><td><p>32 &#8804;<span>&#951;<span>wh</span></span> &lt; 35</p></td><td><p>35 &#8804;<span>&#951;<span>wh</span></span> &lt; 38</p></td><td><p>35 &#8804;<span>&#951;<span>wh</span></span> &lt; 38</p></td><td><p>39 &#8804;<span>&#951;<span>wh</span></span> &lt; 65</p></td><td><p>50 &#8804;<span>&#951;<span>wh</span></span> &lt; 75</p></td><td><p>55 &#8804;<span>&#951;<span>wh</span></span> &lt; 80</p></td><td><p>60 &#8804;<span>&#951;<span>wh</span></span> &lt; 85</p></td></tr><tr><td><p>C</p></td><td><p>29 &#8804;<span>&#951;<span>wh</span></span> &lt; 32</p></td><td><p>29 &#8804;<span>&#951;<span>wh</span></span> &lt; 32</p></td><td><p>32 &#8804;<span>&#951;<span>wh</span></span> &lt; 35</p></td><td><p>32 &#8804;<span>&#951;<span>wh</span></span> &lt; 35</p></td><td><p>36 &#8804;<span>&#951;<span>wh</span></span> &lt; 39</p></td><td><p>37 &#8804;<span>&#951;<span>wh</span></span> &lt; 50</p></td><td><p>38 &#8804;<span>&#951;<span>wh</span></span> &lt; 55</p></td><td><p>40 &#8804;<span>&#951;<span>wh</span></span> &lt; 60</p></td></tr><tr><td><p>D</p></td><td><p>26 &#8804;<span>&#951;<span>wh</span></span> &lt; 29</p></td><td><p>26 &#8804;<span>&#951;<span>wh</span></span> &lt; 29</p></td><td><p>29 &#8804;<span>&#951;<span>wh</span></span> &lt; 32</p></td><td><p>29 &#8804;<span>&#951;<span>wh</span></span> &lt; 32</p></td><td><p>33 &#8804;<span>&#951;<span>wh</span></span> &lt; 36</p></td><td><p>34 &#8804;<span>&#951;<span>wh</span></span> &lt; 37</p></td><td><p>35 &#8804;<span>&#951;<span>wh</span></span> &lt; 38</p></td><td><p>36 &#8804;<span>&#951;<span>wh</span></span> &lt; 40</p></td></tr><tr><td><p>E</p></td><td><p>22 &#8804;<span>&#951;<span>wh</span></span> &lt; 26</p></td><td><p>23 &#8804;<span>&#951;<span>wh</span></span> &lt; 26</p></td><td><p>26 &#8804;<span>&#951;<span>wh</span></span> &lt; 29</p></td><td><p>26 &#8804;<span>&#951;<span>wh</span></span> &lt; 29</p></td><td><p>30 &#8804;<span>&#951;<span>wh</span></span> &lt; 33</p></td><td><p>30 &#8804;<span>&#951;<span>wh</span></span> &lt; 34</p></td><td><p>30 &#8804;<span>&#951;<span>wh</span></span> &lt; 35</p></td><td><p>32 &#8804;<span>&#951;<span>wh</span></span> &lt; 36</p></td></tr><tr><td><p>F</p></td><td><p>19 &#8804;<span>&#951;<span>wh</span></span> &lt; 22</p></td><td><p>20 &#8804;<span>&#951;<span>wh</span></span> &lt; 23</p></td><td><p>23 &#8804;<span>&#951;<span>wh</span></span> &lt; 26</p></td><td><p>23 &#8804;<span>&#951;<span>wh</span></span> &lt; 26</p></td><td><p>27 &#8804;<span>&#951;<span>wh</span></span> &lt; 30</p></td><td><p>27 &#8804;<span>&#951;<span>wh</span></span> &lt; 30</p></td><td><p>27 &#8804;<span>&#951;<span>wh</span></span> &lt; 30</p></td><td><p>28 &#8804;<span>&#951;<span>wh</span></span> &lt; 32</p></td></tr><tr><td><p>G</p></td><td><p><span>&#951;<span>wh</span></span> &lt; 19</p></td><td><p><span>&#951;<span>wh</span></span> &lt; 20</p></td><td><p><span>&#951;<span>wh</span></span> &lt; 23</p></td><td><p><span>&#951;<span>wh</span></span> &lt; 23</p></td><td><p><span>&#951;<span>wh</span></span> &lt; 27</p></td><td><p><span>&#951;<span>wh</span></span> &lt; 27</p></td><td><p><span>&#951;<span>wh</span></span> &lt; 27</p></td><td><p><span>&#951;<span>wh</span></span> &lt; 28</p></td></tr></tbody></table>
3. ENERGY EFFICIENCY CLASSES OF SOLAR HOT WATER STORAGE TANKS, IF (PART OF) A SOLAR DEVICE
The energy efficiency class of a solar hot water storage tank, if (part of) a solar device, shall be determined on the basis of its standing loss as set out in Table 4.
Table 4
Energy efficiency classes of solar hot water storage tanks, if (part of) a solar device
<table><col/><col/><tbody><tr><td><p>Energy efficiency class</p></td><td><p>Standing loss<span>S</span> in Watts, with storage volume<span>V</span> in litres</p></td></tr><tr><td><p>A+</p></td><td><p><img/></p></td></tr><tr><td><p>A</p></td><td><p><img/></p></td></tr><tr><td><p>B</p></td><td><p><img/></p></td></tr><tr><td><p>C</p></td><td><p><img/></p></td></tr><tr><td><p>D</p></td><td><p><img/></p></td></tr><tr><td><p>E</p></td><td><p><img/></p></td></tr><tr><td><p>F</p></td><td><p><img/></p></td></tr><tr><td><p>G</p></td><td><p><img/></p></td></tr></tbody></table>
ANNEX III
The labels
1. SPACE HEATERS
1.1. Label 1
1.1.1. Boiler space heaters in seasonal space heating energy efficiency classes A ++ to G
(a) The following information shall be included in the label:
I. supplier’s name or trade mark;
II. supplier’s model identifier;
III. the space heating function;
IV. the seasonal space heating energy efficiency class, determined in accordance with point 1 of Annex II; the head of the arrow containing the seasonal space heating energy efficiency class of the boiler space heater shall be placed at the same height as the head of the relevant energy efficiency class;
V. the rated heat output in kW, rounded to the nearest integer;
VI. the sound power level L WA , indoors, in dB, rounded to the nearest integer.
(b) The design aspects of the label for boiler space heaters shall be in accordance with point 5 of this Annex.
1.1.2. Cogeneration space heaters in seasonal space heating energy efficiency classes A ++ to G
(a) The following information shall be included in the label:
I. supplier’s name or trade mark;
II. supplier’s model identifier;
III. the space heating function;
IV. the seasonal space heating energy efficiency class, determined in accordance with point 1 of Annex II; the head of the arrow containing the seasonal space heating energy efficiency class of the cogeneration space heater shall be placed at the same height as the head of the relevant energy efficiency class;
V. the rated heat output, including the rated heat output of any supplementary heater, in kW, rounded to the nearest integer;
VI. the sound power level L WA , indoors, in dB, rounded to the nearest integer;
VII. the additional electricity generation function.
(b) The design aspects of the label for cogeneration space heaters shall be in accordance with point 6 of this Annex.
1.1.3. Heat pump space heaters, except low-temperature heat pumps, in seasonal space heating energy efficiency classes A ++ to G
(a) The following information shall be included in the label:
I. supplier’s name or trade mark;
II. supplier’s model identifier;
III. the space heating function for medium- and low-temperature application, respectively;
IV. the seasonal space heating energy efficiency class under average climate conditions for medium- and low-temperature application, respectively, determined in accordance with point 1 of Annex II; the head of the arrow containing the seasonal space heating energy efficiency class of the heat pump space heater for medium- and low-temperature application, respectively, shall be placed at the same height as the head of the relevant energy efficiency class;
V. the rated heat output, including the rated heat output of any supplementary heater, in kW, under average, colder and warmer climate conditions for medium- and low-temperature application, respectively, rounded to the nearest integer;
VI. European temperature map displaying three indicative temperature zones;
VII. the sound power level L WA , indoors (if applicable) and outdoors, in dB, rounded to the nearest integer.
(b) The design aspects of the label for heat pump space heaters shall be in accordance with point 7 of this Annex. By way of exception, where a model has been granted an ‘EU Ecolabel’ under Regulation (EC) No 66/2010 of the European Parliament and of the Council ( 4 ), a copy of the EU Ecolabel may be added.
1.1.4. Low-temperature heat pumps in seasonal space heating energy efficiency classes A ++ to G
(a) The following information shall be included in the label:
I. supplier’s name or trade mark;
II. supplier’s model identifier;
III. the space heating function for low-temperature application;
IV. the seasonal space heating energy efficiency class under average climate conditions, determined in accordance with point 1 of Annex II; the head of the arrow containing the seasonal space heating energy efficiency class of the low-temperature heat pump shall be placed at the same height as the head of the relevant energy efficiency class;
V. the rated heat output, including the rated heat output of any supplementary heater, in kW, under average, colder and warmer climate conditions, rounded to the nearest integer;
VI. European temperature map displaying three indicative temperature zones;
VII. the sound power level L WA , indoors (if applicable) and outdoors, in dB, rounded to the nearest integer.
(b) The design aspects of the label for low-temperature heat pumps shall be in accordance with point 8 of this Annex. By way of exception, where a model has been granted an ‘EU Ecolabel’ under Regulation (EC) No 66/2010 of the European Parliament and of the Council, a copy of the EU Ecolabel may be added.
1.2. Label 2
1.2.1. Boiler space heaters in seasonal space heating energy efficiency classes A +++ to D
(a) The information listed in point 1.1.1(a) of this Annex shall be included in the label.
(b) The design aspects of the label for boiler space heaters shall be in accordance with point 5 of this Annex.
1.2.2. Cogeneration space heaters in seasonal space heating energy efficiency classes A +++ to D
(a) The information listed in point 1.1.2(a) of this Annex shall be included in the label.
(b) The design aspects of the label for cogeneration space heaters shall be in accordance with point 6 of this Annex.
1.2.3. Heat pump space heaters, except low-temperature heat pumps, in seasonal space heating energy efficiency classes A +++ to D
(a) The information listed in point 1.1.3(a) of this Annex shall be included in the label.
(b) The design aspects of the label for heat pump space heaters shall be in accordance with point 7 of this Annex.
1.2.4. Low-temperature heat pumps in seasonal space heating energy efficiency classes A +++ to D
(a) The information listed in point 1.1.4(a) of this Annex shall be included in the label.
(b) The design aspects of the label for low-temperature heat pumps shall be in accordance with point 8 of this Annex.
2. COMBINATION HEATERS
2.1. Label 1
2.1.1 Boiler combination heaters in seasonal space heating energy efficiency classes A ++ to G and in water heating energy efficiency classes A to G
(a) The following information shall be included in the label:
I. supplier’s name or trade mark;
II. supplier’s model identifier;
III. the space heating function and the water heating function, including the declared load profile expressed as the appropriate letter in accordance with Table 15 of Annex VII;
IV. the seasonal space heating energy efficiency class and the water heating energy efficiency class, determined in accordance with points 1 and 2 of Annex II; the head of the arrows containing the seasonal space heating energy efficiency class and water heating energy efficiency class of the boiler combination heater shall be placed at the same height as the head of the relevant energy efficiency class;
V. the rated heat output in kW, rounded to the nearest integer;
VI. the sound power level L WA , indoors, in dB, rounded to the nearest integer.
VII. for boiler combination heaters able to work only during off-peak hours, the pictogram referred to in point 9(d)(11) of this Annex may be added.
(b) The design aspects of the label for boiler combination heaters shall be in accordance with point 9 of this Annex.
2.1.2. Heat pump combination heaters in seasonal space heating energy efficiency classes A ++ to G and in water heating energy efficiency classes A to G
(a) The following information shall be included in the label:
I. supplier’s name or trade mark;
II. supplier’s model identifier;
III. the space heating function for medium-temperature application and the water heating function, including the declared load profile expressed as the appropriate letter in accordance with Table 15 of Annex VII;
IV. the seasonal space heating energy efficiency class under average climate conditions for medium-temperature application and the water heating energy efficiency class under average climate conditions, determined in accordance with points 1 and 2 of Annex II; the head of the arrows containing the seasonal space heating energy efficiency class and water heating energy efficiency class of the heat pump combination heater shall be placed at the same height as the head of the relevant energy efficiency class;
V. the rated heat output, including the rated heat output of any supplementary heater, in kW, under average, colder and warmer climate conditions, rounded to the nearest integer;
VI. European temperature map displaying three indicative temperature zones;
VII. the sound power level L WA , indoors (if applicable) and outdoors, in dB, rounded to the nearest integer;
VIII.
for heat pump combination heaters able to work only during off-peak hours, the pictogram referred to in point 10(d)(12) of this Annex may be added.
(b) The design aspects of the label for heat pump combination heaters shall be in accordance with point 10 of this Annex.
2.2. Label 2
2.2.1. Boiler combination heaters in seasonal space heating energy efficiency classes A +++ to D and in water heating energy efficiency classes A + to F
(a) The information listed in point 2.1.1(a) of this Annex shall be included in the label.
(b) The design aspects of the label for boiler combination heaters shall be in accordance with point 9 of this Annex.
2.2.2. Heat pump combination heaters in seasonal space heating energy efficiency classes A +++ to D and in water heating energy efficiency classes A + to F
(a) The information listed in point 2.1.2(a) of this Annex shall be included in the label.
(b) The design aspects of the label for heat pump combination heaters shall be in accordance with point 10 of this Annex.
3. PACKAGES OF SPACE HEATER, TEMPERATURE CONTROL AND SOLAR DEVICE
Label for packages of space heater, temperature control and solar device in seasonal space heating energy efficiency classes A +++ to G
(a) The following information shall be included in the label:
I. dealer’s and/or supplier's name or trade mark;
II. dealer’s and/or supplier's model(s) identifier;
III. the space heating function;
IV. the seasonal space heating energy efficiency class of the space heater, determined in accordance with point 1 of Annex II;
V. indication of whether a solar collector, hot water storage tank, temperature control and/or supplementary space heater may be included in the package of space heater, temperature control and solar device;
VI. the seasonal space heating energy efficiency class of the package of space heater, temperature control and solar device, determined in accordance with point 5 of Annex IV; the head of the arrow containing the seasonal space heating energy efficiency class of the package of space heater, temperature control and solar device shall be placed at the same height as the head of the relevant energy efficiency class.
(b) The design aspects of the label for packages of space heater, temperature control and solar device shall be in accordance with point 11 of this Annex. For packages of space heater, temperature control and solar device in seasonal space heating energy efficiency classes A +++ to D, the last classes E to G in the A +++ to G scale may be omitted.
4. PACKAGES OF COMBINATION HEATER, TEMPERATURE CONTROL AND SOLAR DEVICE
Label for packages of combination heater, temperature control and solar device in seasonal space heating and water heating energy efficiency classes A +++ to G
(a) The following information shall be included in the label:
I. dealer’s and/or supplier's name or trade mark;
II. dealer’s and/or supplier's model(s) identifier;
III. the space heating function and the water heating function, including the declared load profile expressed as the appropriate letter in accordance with Table 15 of Annex VII;
IV. the seasonal space heating and water heating energy efficiency classes of the combination heater, determined in accordance with points 1 and 2 of Annex II;
V. indication of whether a solar collector, hot water storage tank, temperature control and/or supplementary heater, may be included in the package of combination heater, temperature control and solar device;
VI. the seasonal space heating energy efficiency class of the package of combination heater, temperature control and solar device, determined in accordance with point 6 of Annex IV; the head of the arrow containing the seasonal space heating energy efficiency class of the package of combination heater, temperature control and solar device shall be placed at the same height as the head of the relevant energy efficiency class;
VII. the water heating energy efficiency class of the package of combination heater, temperature control and solar device, determined in accordance with point 6 of Annex IV; the head of the arrow containing the water heating energy efficiency class of the package of combination heater, temperature control and solar device shall be placed at the same height as the head of the relevant energy efficiency class.
(b) The design aspects of the label for packages of combination heater, temperature control and solar device shall be in accordance with point 12 of this Annex. For packages of combination heater, temperature control and solar device in seasonal space heating and/or water heating energy efficiency classes A +++ to D, the last classes E to G in the A +++ to G scale may be omitted.
<table><col/><col/><tr><td><p>5.</p></td><td><p>The design of the label for boiler space heaters shall be the following:</p><img/><p>Whereby:</p><div><div><span>(a)&#160;</span></div><div><p>The label shall be at least 105 mm wide and 200 mm high. Where the label is printed in a larger format, its content shall nevertheless remain proportionate to the specifications above.</p></div></div><div><div><span>(b)&#160;</span></div><div><p>The background shall be white.</p></div></div><div><div><span>(c)&#160;</span></div><div><p>Colours are coded as CMYK &#8212; cyan, magenta, yellow and black, following this example: 00-70-X-00: 0 % cyan, 70 % magenta, 100 % yellow, 0 % black.</p></div></div><div><div><span>(d)&#160;</span></div><div><p>The label shall fulfil all of the following requirements (numbers refer to the figure above):</p><div><div><span><img/>&#160;</span></div><div><p><span>EU label border stroke:</span> 4 pt, colour: cyan 100 %, round corners: 3,5 mm.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>EU logo:</span> Colours: X-80-00-00 and 00-00-X-00.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Energy label:</span> Colour: X-00-00-00. Pictogram as depicted: EU logo + energy label: width: 86 mm, height: 17 mm.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Sub-logos border:</span> 1 pt, colour: cyan 100 %, length: 86 mm.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Space heating function:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Pictogram</span> as depicted.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>A<span>++</span>-G and A<span>+++</span>-D scales, respectively:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Arrow:</span> height: 5 mm, gap: 1,3 mm, colours:</div><div><div>Highest class: X-00-X-00,</div><div>Second class: 70-00-X-00,</div><div>Third class: 30-00-X-00,</div><div>Fourth class: 00-00-X-00,</div><div>Fifth class: 00-30-X-00,</div><div>Sixth class: 00-70-X-00,</div><div>Seventh class: 00-X-X-00,</div><div>Eighth class: 00-X-X-00,</div><div>Last class: 00-X-X-00,</div></div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 14 pt, capitals, white, &#8216;+&#8217; symbols: superscript, aligned on a single row;</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Arrow:</span> height: 7 mm, gap: 1 mm, colours:</div><div><div>Highest class: X-00-X-00,</div><div>Second class: 70-00-X-00,</div><div>Third class: 30-00-X-00,</div><div>Fourth class: 00-00-X-00,</div><div>Fifth class: 00-30-X-00,</div><div>Sixth class: 00-70-X-00,</div><div>Last class: 00-X-X-00,</div></div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 16 pt, capitals, white, &#8216;+&#8217; symbols: superscript, aligned on a single row.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Seasonal space heating energy efficiency class:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Arrow:</span> width: 22 mm, height: 12 mm, 100 % black,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 24 pt, capitals, white, &#8216;+&#8217; symbols: superscript, aligned on a single row.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Sound power level, indoors</span>:</p><div><div><span>&#8212;&#160;</span></div><div><div><span>Pictogram</span> as depicted,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Border:</span> 2 pt, colour: cyan 100 %, round corners: 3,5 mm,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Value &#8216;YZ&#8217;:</span> Calibri bold 20 pt, 100 % black,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text &#8216;dB&#8217;:</span> Calibri regular 15 pt, 100 % black.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Rated heat output:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Border:</span> 2 pt &#8211; colour: cyan 100 % &#8211; round corners: 3,5 mm,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Value &#8216;YZ&#8217;:</span> Calibri bold 45 pt, 100 % black,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text &#8216;kW&#8217;:</span> Calibri regular 30 pt, 100 % black.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Year of label introduction and number of Regulation:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 10 pt.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Supplier&#8217;s name or trademark.</span></p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Supplier&#8217;s model identifier:</span></p><p>The supplier&#8217;s name or trade mark and model identifier shall fit in a space of 86 &#215; 12 mm.</p></div></div></div></div></td></tr></table>
<table><col/><col/><tr><td><p>6.</p></td><td><p>The design of the label for cogeneration space heaters shall be the following:</p><img/><p>Whereby:</p><div><div><span>(a)&#160;</span></div><div><p>The label shall be at least 105 mm wide and 200 mm high. Where the label is printed in a larger format, its content shall nevertheless remain proportionate to the specifications above.</p></div></div><div><div><span>(b)&#160;</span></div><div><p>The background shall be white.</p></div></div><div><div><span>(c)&#160;</span></div><div><p>Colours are coded as CMYK &#8212; cyan, magenta, yellow and black, following this example: 00-70-X-00: 0 % cyan, 70 % magenta, 100 % yellow, 0 % black.</p></div></div><div><div><span>(d)&#160;</span></div><div><p>The label shall fulfil all of the following requirements (numbers refer to the figure above):</p><div><div><span><img/>&#160;</span></div><div><p><span>EU label border stroke:</span> 4 pt, colour: cyan 100 %, round corners: 3,5 mm.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>EU logo:</span> Colours: X-80-00-00 and 00-00-X-00.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Energy label:</span> Colour: X-00-00-00. Pictogram as depicted: EU logo + energy label: width: 86 mm, height: 17 mm.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Sub-logos border:</span> 1 pt, colour: cyan 100 %, length: 86 mm.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Space heating function:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Pictogram</span> as depicted.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>A<span>++</span>-G and A<span>+++</span>-D scales, respectively:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Arrow:</span> height: 5 mm, gap: 1,3 mm, colours:</div><div><div>Highest class: X-00-X-00,</div><div>Second class: 70-00-X-00,</div><div>Third class: 30-00-X-00,</div><div>Fourth class: 00-00-X-00,</div><div>Fifth class: 00-30-X-00,</div><div>Sixth class: 00-70-X-00,</div><div>Seventh class: 00-X-X-00,</div><div>Eighth class: 00-X-X-00,</div><div>Last class: 00-X-X-00,</div></div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 14 pt, capitals, white, &#8216;+&#8217; symbols: superscript, aligned on a single row;</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Arrow:</span> height: 7 mm, gap: 1 mm, colours:</div><div><div>Highest class: X-00-X-00,</div><div>Second class: 70-00-X-00,</div><div>Third class: 30-00-X-00,</div><div>Fourth class: 00-00-X-00,</div><div>Fifth class: 00-30-X-00,</div><div>Sixth class: 00-70-X-00,</div><div>Last class: 00-X-X-00,</div></div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 16 pt, capitals, white, &#8216;+&#8217; symbols: superscript, aligned on a single row.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Seasonal space heating energy efficiency class:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Arrow:</span> width: 22 mm, height: 12 mm, 100 % black,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 24 pt, capitals, white, &#8216;+&#8217; symbols: superscript, aligned on a single row.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Sound power level, indoors:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Pictogram</span> as depicted,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Border:</span> 2 pt, colour: cyan 100 %, round corners: 3,5 mm,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Value &#8216;YZ&#8217;:</span> Calibri bold 20 pt, 100 % black,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text &#8216;dB&#8217;:</span> Calibri regular 15 pt, 100 % black.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Rated heat output:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Border:</span> 2 pt, colour: cyan 100 %, round corners: 3,5 mm,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Value &#8216;YZ&#8217;:</span> Calibri bold 45 pt, 100 % black,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text &#8216;kW&#8217;:</span> Calibri regular 30 pt, 100 % black.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Electricity function:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Pictogram</span> as depicted,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Border:</span> 2 pt, colour: cyan 100 %, round corners: 3,5 mm.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Year of label introduction and number of Regulation:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 10 pt.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Supplier&#8217;s name or trademark.</span></p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Supplier&#8217;s model identifier:</span></p><p>The supplier&#8217;s name or trade mark and model identifier shall fit in a space of 86 &#215; 12 mm.</p></div></div></div></div></td></tr></table>
<table><col/><col/><tr><td><p>7.</p></td><td><p>The design of the label for heat pump space heaters shall be the following:</p><img/><p>Whereby:</p><div><div><span>(a)&#160;</span></div><div><p>The label shall be at least 105 mm wide and 200 mm high. Where the label is printed in a larger format, its content shall nevertheless remain proportionate to the specifications above.</p></div></div><div><div><span>(b)&#160;</span></div><div><p>The background shall be white.</p></div></div><div><div><span>(c)&#160;</span></div><div><p>Colours are coded as CMYK &#8212; cyan, magenta, yellow and black, following this example: 00-70-X-00: 0 % cyan, 70 % magenta, 100 % yellow, 0 % black.</p></div></div><div><div><span>(d)&#160;</span></div><div><p>The label shall fulfil all of the following requirements (numbers refer to the figure above):</p><div><div><span><img/>&#160;</span></div><div><p><span>EU label border stroke:</span> 4 pt, colour: cyan 100 %, round corners: 3,5 mm.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>EU logo:</span> Colours: X-80-00-00 and 00-00-X-00.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Energy label:</span> Colour: X-00-00-00. Pictogram as depicted: EU logo + energy label: width: 86 mm, height: 17 mm.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Sub-logos border:</span> 1 pt, colour: cyan 100 %, length: 86 mm.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Space heating function:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Pictogram</span> as depicted.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Medium- and low-temperature application:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Text &#8216;55 &#176;C&#8217; and &#8216;35 &#176;C&#8217;:</span> Calibri regular 14 pt, 100 % black.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>A<span>++</span>-G and A<span>+++</span>-D scales, respectively:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Arrow:</span> height: 5 mm, gap: 1,3 mm, colours:</div><div><div>Highest class: X-00-X-00,</div><div>Second class: 70-00-X-00,</div><div>Third class: 30-00-X-00,</div><div>Fourth class: 00-00-X-00,</div><div>Fifth class: 00-30-X-00,</div><div>Sixth class: 00-70-X-00,</div><div>Seventh class: 00-X-X-00,</div><div>Eighth class: 00-X-X-00,</div><div>Last class: 00-X-X-00,</div></div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 14 pt, capitals, white, &#8216;+&#8217; symbols: superscript, aligned on a single row;</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Arrow:</span> height: 7 mm, gap: 1 mm, colours:</div><div><div>Highest class: X-00-X-00,</div><div>Second class: 70-00-X-00,</div><div>Third class: 30-00-X-00,</div><div>Fourth class: 00-00-X-00,</div><div>Fifth class: 00-30-X-00,</div><div>Sixth class: 00-70-X-00,</div><div>Last class: 00-X-X-00,</div></div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 16 pt, capitals, white, &#8216;+&#8217; symbols: superscript, aligned on a single row.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Seasonal space heating energy efficiency class:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Arrow:</span> width: 19 mm, height: 12 mm, 100 % black,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 24 pt, capitals, white, &#8216;+&#8217; symbols: superscript, aligned on a single row.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Sound power level, indoors (if applicable) and outdoors:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Pictogram</span> as depicted,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Border:</span> 2 pt, colour: cyan 100 %, round corners: 3,5 mm,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Value &#8216;YZ&#8217;:</span> Calibri bold 20 pt, 100 % black,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text &#8216;dB&#8217;:</span> Calibri regular 15 pt, 100 % black.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Rated heat output:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Border:</span> 2 pt, colour: cyan 100 %, round corners: 3,5 mm,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Values &#8216;YZ&#8217;:</span> Calibri at least 15 pt, 100 % black,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text &#8216;kW&#8217;:</span> Calibri regular 15 pt, 100 % black.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>European temperature map and colour squares:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Pictogram</span> as depicted,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div>Colours:</div><div><div>Dark blue: 86-51-00-00,</div><div>Middle blue: 53-08-00-00,</div><div>Light blue: 25-00-02-00.</div></div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Year of label introduction and number of Regulation:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 10 pt.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Supplier&#8217;s name or trademark.</span></p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Supplier&#8217;s model identifier:</span></p><p>The supplier&#8217;s name or trade mark and model identifier shall fit in a space of 86 &#215; 12 mm.</p></div></div></div></div></td></tr></table>
<table><col/><col/><tr><td><p>8.</p></td><td><p>The design of the label for low-temperature heat pumps shall be the following:</p><img/><p>Whereby:</p><div><div><span>(a)&#160;</span></div><div><p>The label shall be at least 105 mm wide and 200 mm high. Where the label is printed in a larger format, its content shall nevertheless remain proportionate to the specifications above.</p></div></div><div><div><span>(b)&#160;</span></div><div><p>The background shall be white.</p></div></div><div><div><span>(c)&#160;</span></div><div><p>Colours are coded as CMYK &#8212; cyan, magenta, yellow and black, following this example: 00-70-X-00: 0 % cyan, 70 % magenta, 100 % yellow, 0 % black.</p></div></div><div><div><span>(d)&#160;</span></div><div><p>The label shall fulfil all of the following requirements (numbers refer to the figure above):</p><div><div><span><img/>&#160;</span></div><div><p><span>EU label border stroke:</span> 4 pt, colour: cyan 100 %, round corners: 3,5 mm.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>EU logo:</span> Colours: X-80-00-00 and 00-00-X-00.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Energy label:</span> Colour: X-00-00-00. Pictogram as depicted: EU logo + energy label: width: 86 mm, height: 17 mm.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Sub-logos border:</span> 1 pt, colour: cyan 100 %, length: 86 mm.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Space heating function:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Pictogram</span> as depicted.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Low-temperature application:</span></p><p><span>Text &#8216;35 &#176;C&#8217;:</span> Calibri regular 14 pt, 100 % black.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>A<span>++</span>-G and A<span>+++</span>-D scales, respectively:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Arrow:</span> height: 5 mm, gap: 1,3 mm, colours:</div><div><div>Highest class: X-00-X-00,</div><div>Second class: 70-00-X-00,</div><div>Third class: 30-00-X-00,</div><div>Fourth class: 00-00-X-00,</div><div>Fifth class: 00-30-X-00,</div><div>Sixth class: 00-70-X-00,</div><div>Seventh class: 00-X-X-00,</div><div>Eighth class: 00-X-X-00,</div><div>Last class: 00-X-X-00,</div></div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 14 pt, capitals, white, &#8216;+&#8217; symbols: superscript, aligned on a single row;</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Arrow:</span> height: 7 mm, gap: 1 mm &#8211; colours:</div><div><div>Highest class: X-00-X-00,</div><div>Second class: 70-00-X-00,</div><div>Third class: 30-00-X-00,</div><div>Fourth class: 00-00-X-00,</div><div>Fifth class: 00-30-X-00,</div><div>Sixth class: 00-70-X-00,</div><div>Last class: 00-X-X-00,</div></div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 16 pt, capitals, white, &#8216;+&#8217; symbols: superscript, aligned on a single row.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Seasonal space heating energy efficiency class:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Arrow:</span> width: 22 mm, height: 12 mm, 100 % black,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 24 pt, capitals, white, &#8216;+&#8217; symbols: superscript, aligned on a single row.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Sound power level, indoors (if applicable) and outdoors:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Pictogram</span> as depicted,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Border:</span> 2 pt, colour: cyan 100 %, round corners: 3,5 mm,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Value &#8216;YZ&#8217;:</span> Calibri bold 20 pt, 100 % black,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text &#8216;dB&#8217;:</span> Calibri regular 15 pt, 100 % black.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Rated heat output:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Border:</span> 2 pt, colour: cyan 100 %, round corners: 3,5 mm,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Values &#8216;YZ&#8217;:</span> Calibri at least 18 pt, 100 % black,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text &#8216;kW&#8217;:</span> Calibri regular 13,5 pt, 100 % black.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>European temperature map and colour squares:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Pictogram</span> as depicted,</div><div>Colours:</div><div><div>Dark blue: 86-51-00-00,</div><div>Middle blue: 53-08-00-00,</div><div>Light blue: 25-00-02-00.</div></div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Year of label introduction and number of Regulation:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 10 pt.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Supplier&#8217;s name or trademark.</span></p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Supplier&#8217;s model identifier:</span></p><p>The supplier&#8217;s name or trade mark and model identifier shall fit in a space of 86 &#215; 12 mm.</p></div></div></div></div></td></tr></table>
<table><col/><col/><tr><td><p>9.</p></td><td><p>The design of the label for boiler combination heaters shall be the following:</p><img/><p>Whereby:</p><div><div><span>(a)&#160;</span></div><div><p>The label shall be at least 105 mm wide and 200 mm high. Where the label is printed in a larger format, its content shall nevertheless remain proportionate to the specifications above.</p></div></div><div><div><span>(b)&#160;</span></div><div><p>The background shall be white.</p></div></div><div><div><span>(c)&#160;</span></div><div><p>Colours are coded as CMYK &#8212; cyan, magenta, yellow and black, following this example: 00-70-X-00: 0 % cyan, 70 % magenta, 100 % yellow, 0 % black.</p></div></div><div><div><span>(d)&#160;</span></div><div><p>The label shall fulfil all of the following requirements (numbers refer to the figure above):</p><div><div><span><img/>&#160;</span></div><div><p><span>EU label border stroke:</span> 4 pt, colour: cyan 100 %, round corners: 3,5 mm.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>EU logo:</span> Colours: X-80-00-00 and 00-00-X-00.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Energy label:</span> Colour: X-00-00-00. Pictogram as depicted: EU logo + energy label: width: 86 mm, height: 17 mm.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Sub-logos border:</span> 1 pt, colour: cyan 100 %, length: 86 mm.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Space heating function:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Pictogram</span> as depicted.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Water heating function:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Pictogram</span> as depicted, including the declared load profile expressed as the appropriate letter in accordance with Table 15 of Annex VII: Calibri bold 16 pt, 100 % black.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>A<span>++</span>-G and A-G, A<span>+++</span>-D or A<span>+</span>-F scales, respectively:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Arrow:</span> height: 5 mm, gap: 1,3 mm, colours:</div><div><div>Highest class: X-00-X-00,</div><div>Second class: 70-00-X-00,</div><div>Third class: 30-00-X-00,</div><div>Fourth class: 00-00-X-00,</div><div>Fifth class: 00-30-X-00,</div><div>Sixth class: 00-70-X-00,</div><div>Seventh class: 00-X-X-00,</div><div>Eighth class: 00-X-X-00,</div><div>Last class: 00-X-X-00,</div></div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 14 pt, capitals, white, &#8216;+&#8217; symbols: superscript, aligned on a single row;</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Arrow:</span> height: 7 mm, gap: 1 mm, colours:</div><div><div>Highest class: X-00-X-00,</div><div>Second class: 70-00-X-00,</div><div>Third class: 30-00-X-00,</div><div>Fourth class: 00-00-X-00,</div><div>Fifth class: 00-30-X-00,</div><div>Sixth class: 00-70-X-00,</div><div>Last class: 00-X-X-00,</div></div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 16 pt, capitals, white, &#8216;+&#8217; symbols: superscript, aligned on a single row.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Seasonal space heating and water heating energy efficiency classes:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Arrow:</span> width: 14 mm, height: 9 mm, 100 % black,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 18 pt, capitals, white, &#8216;+&#8217; symbols: superscript, aligned on a single row.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Rated heat output:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Border:</span> 2 pt, colour: cyan 100 %, round corners: 3,5 mm,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Value &#8216;YZ&#8217;:</span> Calibri bold 37,5 pt, 100 % black,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text &#8216;kW&#8217;:</span> Calibri regular 18 pt, 100 % black.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Sound power level, indoors:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Pictogram</span> as depicted,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Border:</span> 2 pt, colour: cyan 100 %, round corners: 3,5 mm,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Value &#8216;YZ&#8217;:</span> Calibri bold 20 pt, 100 % black,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text &#8216;dB&#8217;:</span> Calibri regular 15 pt, 100 % black.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>If applicable, off-peak fitness:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Pictogram</span> as depicted,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Border:</span> 2 pt &#8211; colour: cyan 100 % &#8211; round corners: 3,5 mm.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Year of label introduction and number of Regulation:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 10 pt.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Supplier&#8217;s name or trademark.</span></p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Supplier&#8217;s model identifier:</span></p><p>The supplier&#8217;s name or trade mark and model identifier shall fit in a space of 86 &#215; 12 mm.</p></div></div></div></div></td></tr></table>
<table><col/><col/><tr><td><p>10.</p></td><td><p>The design of the label for heat pump combination heaters shall be the following:</p><img/><p>Whereby:</p><div><div><span>(a)&#160;</span></div><div><p>The label shall be at least 105 mm wide and 200 mm high. Where the label is printed in a larger format, its content shall nevertheless remain proportionate to the specifications above.</p></div></div><div><div><span>(b)&#160;</span></div><div><p>The background shall be white.</p></div></div><div><div><span>(c)&#160;</span></div><div><p>Colours are coded as CMYK &#8212; cyan, magenta, yellow and black, following this example: 00-70-X-00: 0 % cyan, 70 % magenta, 100 % yellow, 0 % black.</p></div></div><div><div><span>(d)&#160;</span></div><div><p>The label shall fulfil all of the following requirements (numbers refer to the figure above):</p><div><div><span><img/>&#160;</span></div><div><p><span>EU label border stroke:</span> 4 pt, colour: cyan 100 %, round corners: 3,5 mm.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>EU logo:</span> Colours: X-80-00-00 and 00-00-X-00.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Energy label:</span> Colour: X-00-00-00. Pictogram as depicted: EU logo + energy label: width: 86 mm, height: 17 mm.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Sub-logos border:</span> 1 pt, colour: cyan 100 %, length: 86 mm.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Space heating function</span>:</p><div><div><span>&#8212;&#160;</span></div><div><div><span>Pictogram</span> as depicted.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Water heating function:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Pictogram</span> as depicted, including the declared load profile expressed as the appropriate letter in accordance with Table 15 of Annex VII: Calibri bold 16 pt, 100 % black.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>A<span>++</span>-G and A-G, A<span>+++</span>-D or A<span>+</span>-F scales, respectively:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Arrow:</span> height: 5 mm, gap: 1,3 mm, colours:</div><div><div>Highest class: X-00-X-00,</div><div>Second class: 70-00-X-00,</div><div>Third class: 30-00-X-00,</div><div>Fourth class: 00-00-X-00,</div><div>Fifth class: 00-30-X-00,</div><div>Sixth class: 00-70-X-00,</div><div>Seventh class: 00-X-X-00,</div><div>Eighth class: 00-X-X-00,</div><div>Last class: 00-X-X-00,</div></div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 14 pt, capitals, white, &#8216;+&#8217; symbols: superscript, aligned on a single row;</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Arrow</span>: height: 7 mm, gap: 1 mm, colours:</div><div><div>Highest class: X-00-X-00,</div><div>Second class: 70-00-X-00,</div><div>Third class: 30-00-X-00,</div><div>Fourth class: 00-00-X-00,</div><div>Fifth class: 00-30-X-00,</div><div>Sixth class: 00-70-X-00,</div><div>Last class: 00-X-X-00,</div></div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 16 pt, capitals, white, &#8216;+&#8217; symbols: superscript, aligned on a single row.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Seasonal space heating and water heating energy efficiency classes:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Arrow:</span> width: 14 mm, height: 9 mm, 100 % black,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 18 pt, capitals, white, &#8216;+&#8217; symbols: superscript, aligned on a single row.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Rated heat output:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Border:</span> 2 pt, colour: cyan 100 %, round corners: 3,5 mm,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Values &#8216;YZ&#8217;:</span> Calibri at least 12 pt, 100 % black,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text &#8216;kW&#8217;:</span> Calibri regular 10 pt, 100 % black.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>European temperature map and colour squares:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Pictogram</span> as depicted,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div>Colours:</div><div><div>Dark blue: 86-51-00-00,</div><div>Middle blue: 53-08-00-00,</div><div>Light blue: 25-00-02-00.</div></div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Sound power level, indoors (if applicable) and outdoors:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Pictogram</span> as depicted,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Border:</span> 2 pt, colour: cyan 100 %, round corners: 3,5 mm,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Value &#8216;YZ&#8217;:</span> Calibri bold 15 pt, 100 % black,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text &#8216;dB&#8217;:</span> Calibri regular 10 pt, 100 % black.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>If applicable, off-peak fitness:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Pictogram</span> as depicted,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Border:</span> 2 pt, colour: cyan 100 %, round corners: 3,5 mm.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Year of label introduction and number of Regulation:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 10 pt.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Supplier&#8217;s name or trademark.</span></p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Supplier&#8217;s model identifier:</span></p><p>The supplier&#8217;s name or trade mark and model identifier shall fit in a space of 86 &#215; 12 mm.</p></div></div></div></div></td></tr></table>
<table><col/><col/><tr><td><p>11.</p></td><td>The design of the label for packages of space heater, temperature control and solar device shall be the following:<img/><p>Whereby:</p><div><div><span>(a)&#160;</span></div><div><p>The label shall be at least 210 mm wide and 297 mm high. Where the label is printed in a larger format, its content shall nevertheless remain proportionate to the specifications above.</p></div></div><div><div><span>(b)&#160;</span></div><div><p>The background shall be white.</p></div></div><div><div><span>(c)&#160;</span></div><div><p>Colours are coded as CMYK &#8212; cyan, magenta, yellow and black, following this example: 00-70-X-00: 0 % cyan, 70 % magenta, 100 % yellow, 0 % black.</p></div></div><div><div><span>(d)&#160;</span></div><div><p>The label shall fulfil all of the following requirements (numbers refer to the figure above):</p><div><div><span><img/>&#160;</span></div><div><p><span>EU label border stroke:</span> 6 pt, colour: cyan 100 %, round corners: 3,5 mm.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>EU logo:</span> Colours: X-80-00-00 and 00-00-X-00.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Energy label:</span> Colour: X-00-00-00. Pictogram as depicted: EU logo + energy label: width: 191 mm, height: 37 mm.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Sub-logos border:</span> 2 pt, colour: cyan 100 %, length: 191 mm.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Space heating function:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Pictogram</span> as depicted.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Space heater:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Pictogram</span> as depicted,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div>Seasonal space heating energy efficiency class of space heater:</div><div><div><span>Arrow:</span> width: 24 mm, height: 14 mm, 100 % black;</div><div><span>Text:</span> Calibri bold 28 pt, capitals, white, &#8216;+&#8217; symbols: superscript, aligned on a single row,</div></div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Border:</span> 3 pt, colour: cyan 100 %, round corners: 3,5 mm.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Package with solar collector, hot water storage tank, temperature control and/or supplementary heater:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Pictograms</span> as depicted,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>                                                      &#8216;+&#8217; symbol:</span> Calibri bold 50 pt, cyan 100 %,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Boxes:</span> width: 12 mm, height: 12 mm, border: 4 pt, cyan 100 %,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Border:</span> 3 pt, colour: cyan 100 %, round corners: 3,5 mm.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>A<span>+++</span>-G scale with border:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Arrow:</span> height: 15 mm, gap: 3 mm, colours:</div><div><div>Highest class: X-00-X-00,</div><div>Second class: 70-00-X-00,</div><div>Third class: 30-00-X-00,</div><div>Fourth class: 00-00-X-00,</div><div>Fifth class: 00-30-X-00,</div><div>Sixth class: 00-70-X-00,</div><div>Seventh class: 00-X-X-00,</div><div>If applicable, last classes: 00-X-X-00,</div></div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 30 pt, capitals, white, &#8216;+&#8217; symbols: superscript, aligned on a single row,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Border:</span> 3 pt, colour: cyan 100 %, round corners: 3,5 mm.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Seasonal space heating energy efficiency class for package of space heater, temperature control and solar device:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Arrow:</span> width: 33 mm, height: 19 mm, 100 % black,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 40 pt, capitals, white, &#8216;+&#8217; symbols: superscript, aligned on a single row.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Year of label introduction and number of Regulation:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 12 pt.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Dealer&#8217;s and/or supplier's name or trademark.</span></p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Dealer&#8217;s and/or supplier's model identifier:</span></p><p>The dealer&#8217;s and/or supplier&#8217;s name or trade mark and model identifier shall fit in a space of 191 &#215; 19 mm.</p></div></div></div></div></td></tr></table>
<table><col/><col/><tr><td><p>12.</p></td><td>The design of the label for packages of combination heater, temperature control and solar device shall be the following:<img/><p>Whereby:</p><div><div><span>(a)&#160;</span></div><div><p>The label shall be at least 210 mm wide and 297 mm high. Where the label is printed in a larger format, its content shall nevertheless remain proportionate to the specifications above.</p></div></div><div><div><span>(b)&#160;</span></div><div><p>The background shall be white.</p></div></div><div><div><span>(c)&#160;</span></div><div><p>Colours are coded as CMYK &#8212; cyan, magenta, yellow and black, following this example: 00-70-X-00: 0 % cyan, 70 % magenta, 100 % yellow, 0 % black.</p></div></div><div><div><span>(d)&#160;</span></div><div><p>The label shall fulfil all of the following requirements (numbers refer to the figure above):</p><div><div><span><img/>&#160;</span></div><div><p><span>EU label border stroke:</span> 6 pt, colour: cyan 100 %, round corners: 3,5 mm.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>EU logo:</span> Colours: X-80-00-00 and 00-00-X-00.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Energy label:</span> Colour: X-00-00-00. Pictogram as depicted: EU logo + energy label: width: 191 mm, height: 37 mm.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Sub-logos border:</span> 2 pt, colour: cyan 100 %, length: 191 mm.</p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Combination heater:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Pictograms</span> as depicted; for water heating function, including the declared load profile expressed as the appropriate letter in accordance with Table 15 of Annex VII: Calibri bold 16 pt, 100 % black.</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div>Seasonal space heating and water heating energy efficiency class of combination heater:</div><div><div><span>Arrow:</span> width: 19 mm, height: 11 mm, 100 % black,</div><div><span>Text:</span> Calibri bold 23 pt, capitals, white, &#8216;+&#8217; symbols: superscript, aligned on a single row,</div></div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Border:</span> 3 pt, colour: cyan 100 %, round corners: 3,5 mm.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Package with solar collector, hot water storage tank, temperature control and/or supplementary heater:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Pictograms</span> as depicted,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>                                                      &#8216;+&#8217; symbol:</span> Calibri bold 50 pt, cyan 100 %,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Boxes:</span> width: 12 mm, height: 12 mm, border: 4 pt, cyan 100 %,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Border:</span> 3 pt, colour: cyan 100 %, round corners: 3,5 mm.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Space heating function:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Pictogram</span> as depicted.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>A<span>+++</span>-G scale with border:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Arrow:</span> height: 6,5 mm, gap: 1 mm, colours:</div><div><div>Highest class: X-00-X-00,</div><div>Second class: 70-00-X-00,</div><div>Third class: 30-00-X-00,</div><div>Fourth class: 00-00-X-00,</div><div>Fifth class: 00-30-X-00,</div><div>Sixth class: 00-70-X-00,</div><div>Seventh class: 00-X-X-00,</div><div>If applicable, last classes: 00-X-X-00,</div></div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 16 pt, capitals, white, &#8216;+&#8217; symbols: superscript, aligned on a single row,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Border:</span> 3 pt, colour: cyan 100 %, round corners: 3,5 mm.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Seasonal space heating and water heating energy efficiency class, respectively, for package of combination heater, temperature control and solar device:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Arrow:</span> width: 24 mm, height: 14 mm, 100 % black,</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 28 pt, capitals, white, &#8216;+&#8217; symbols: superscript, aligned on a single row.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Water heating function:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Pictogram</span> as depicted, including the declared load profile expressed as the appropriate letter in accordance with Table 15 of Annex VII: Calibri bold 22 pt, 100 % black.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Year of label introduction and number of Regulation:</span></p><div><div><span>&#8212;&#160;</span></div><div><div><span>Text:</span> Calibri bold 12 pt.</div></div></div></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Dealer&#8217;s and/or supplier's name or trademark.</span></p></div></div><div><div><span><img/>&#160;</span></div><div><p><span>Dealer&#8217;s and/or supplier's model identifier:</span></p><p>The dealer&#8217;s and/or supplier&#8217;s name or trade mark and model identifier shall fit in a space of 191 &#215; 19 mm.</p></div></div></div></div></td></tr></table>
ANNEX IV
Product fiche
1. SPACE HEATERS
1.1. The information in the product fiche of the space heater shall be provided in the following order and shall be included in the product brochure or other literature provided with the product:
(a) supplier’s name or trademark;
(b) supplier’s model identifier;
(c) the seasonal space heating energy efficiency class of the model, determined in accordance with point 1 of Annex II;
(d) the rated heat output, including the rated heat output of any supplementary heater, in kW, rounded to the nearest integer (for heat pump space heaters under average climate conditions);
(e) the seasonal space heating energy efficiency in %, rounded to the nearest integer and calculated in accordance with points 3 and 4 of Annex VII (for heat pump space heaters under average climate conditions);
(f) the annual energy consumption in kWh in terms of final energy and/or in GJ in terms of GCV , rounded to the nearest integer and calculated in accordance with points 3 and 4 of Annex VII (for heat pump space heaters under average climate conditions);
(g) the sound power level L WA , indoors, in dB, rounded to the nearest integer (for heat pump space heaters if applicable);
(h) any specific precautions that shall be taken when the space heater is assembled, installed or maintained;
in addition, for cogeneration space heaters:
(i) the electrical efficiency in %, rounded to the nearest integer;
in addition, for heat pump space heaters:
(j) the rated heat output, including the rated heat output of any supplementary heater, in kW, under colder and warmer climate conditions, rounded to the nearest integer;
(k) the seasonal space heating energy efficiency in %, under colder and warmer climate conditions, rounded to the nearest integer and calculated in accordance with point 4 of Annex VII;
(l) the annual energy consumption in kWh in terms of final energy and/or in GJ in terms of GCV , under colder and warmer climate conditions, rounded to the nearest integer and calculated in accordance with point 4 of Annex VII;
(m) the sound power level L WA , outdoors, in dB, rounded to the nearest integer.
1.2. One fiche may cover a number of space heater models supplied by the same supplier.
1.3. The information contained in the fiche may be given in the form of a copy of the label, either in colour or in black and white. Where this is the case, the information listed in point 1.1 not already displayed on the label shall also be provided.
2. COMBINATION HEATERS
2.1. The information in the product fiche of the combination heater shall be provided in the following order and shall be included in the product brochure or other literature provided with the product:
(a) supplier’s name or trademark;
(b) supplier’s model identifier;
(c) for space heating, the medium-temperature application (and for heat pump combination heaters the low-temperature application, if applicable); for water heating, the declared load profile, expressed as the appropriate letter and typical usage in accordance with Table 15 of Annex VII;
(d) the seasonal space heating energy efficiency class and the water heating energy efficiency class of the model, determined in accordance with points 1 and 2 of Annex II;
(e) the rated heat output, including the rated heat output of any supplementary heater, in kW, rounded to the nearest integer (for heat pump combination heaters under average climate conditions);
(f) for space heating, the annual energy consumption in kWh in terms of final energy and/or in GJ in terms of GCV , rounded to the nearest integer and calculated in accordance with points 3 and 4 of Annex VII (for heat pump combination heaters under average climate conditions); for water heating, the annual electricity consumption in kWh in terms of final energy and/or the annual fuel consumption in GJ in terms of GCV , rounded to the nearest integer and calculated in accordance with point 5 of Annex VII (for heat pump combination heaters under average climate conditions);
(g) the seasonal space heating energy efficiency in %, rounded to the nearest integer and calculated in accordance with points 3 and 4 of Annex VII (for heat pump combination heaters under average climate conditions); the water heating energy efficiency in %, rounded to the nearest integer and calculated in accordance with point 5 of Annex VII (for heat pump combination heaters under average climate conditions);
(h) the sound power level L WA , indoors, in dB, rounded to the nearest integer (for heat pump combination heaters if applicable);
(i) if applicable, an indication that the combination heater is able to work only during off-peak hours;
(j) any specific precautions that shall be taken when the combination heater is assembled, installed or maintained;
in addition, for heat pump combination heaters:
(k) the rated heat output, including the rated heat output of any supplementary heater, in kW, under colder and warmer climate conditions, rounded to the nearest integer;
(l) for space heating, the annual energy consumption in kWh in terms of final energy and/or in GJ in terms of GCV , under colder and warmer climate conditions, rounded to the nearest integer and calculated in accordance with point 4 of Annex VII; for water heating, the annual electricity consumption in kWh in terms of final energy and/or the annual fuel consumption in GJ in terms of GCV , under colder and warmer climate conditions, rounded to the nearest integer and calculated in accordance with point 5 of Annex VII;
(m) the seasonal space heating energy efficiency in %, under colder and warmer climate conditions, rounded to the nearest integer and calculated in accordance with point 4 of Annex VII; the water heating energy efficiency in %, under colder and warmer climate conditions, rounded to the nearest integer and calculated in accordance with point 5 of Annex VII;
(n) the sound power level L WA , outdoors, in dB, rounded to the nearest integer.
2.2. One fiche may cover a number of combination heater models supplied by the same supplier.
2.3. The information contained in the fiche may be given in the form of a copy of the label, either in colour or in black and white. Where this is the case, the information listed in point 2.1 not already displayed on the label shall also be provided.
3. TEMPERATURE CONTROLS
3.1. The information in the product fiche of the temperature control shall be provided in the following order and shall be included in the product brochure or other literature provided with the product:
(a) supplier’s name or trade mark;
(b) supplier’s model identifier;
(c) the class of the temperature control;
(d) the contribution of the temperature control to seasonal space heating energy efficiency in %, rounded to one decimal place.
3.2. One fiche may cover a number of temperature control models supplied by the same supplier.
4. SOLAR DEVICES
4.1. The information in the product fiche of the solar device shall be provided in the following order and shall be included in the product brochure or other literature provided with the product (for pumps in the collector loop if applicable):
(a) supplier’s name or trade mark;
(b) supplier’s model identifier;
(c) the collector aperture area in m 2 , to two decimal places;
(d) the collector efficiency in %, rounded to the nearest integer;
(e) the energy efficiency class of the solar hot water storage tank, determined in accordance with point 3 of Annex II;
(f) the standing loss of the solar hot water storage tank in W, rounded to the nearest integer;
(g) the storage volume of the solar hot water storage tank in litres and m 3 ;
(h) the annual non-solar heat contribution Q nonsol in kWh in terms of primary energy for electricity and/or in kWh in terms of GCV for fuels, for the load profiles M, L, XL and XXL under average climate conditions, rounded to the nearest integer;
(i) the pump power consumption in W, rounded to the nearest integer;
(j) the standby power consumption in W, to two decimal places;
(k) the annual auxiliary electricity consumption Q aux in kWh in terms of final energy, rounded to the nearest integer.
4.2. One fiche may cover a number of solar device models supplied by the same supplier.
5. PACKAGES OF SPACE HEATER, TEMPERATURE CONTROL AND SOLAR DEVICE
The fiche for packages of space heater, temperature control and solar device shall contain the elements set out in Figure 1, Figure 2, Figure 3 and Figure 4, respectively, for evaluating the seasonal space heating energy efficiency of a package of space heater, temperature control and solar device, including the following information:
— I: the value of the seasonal space heating energy efficiency of the preferential space heater, expressed in %;
— II: the factor for weighting the heat output of preferential and supplementary heaters of a package as set out in Tables 5 and 6 of this Annex, respectively;
— III: the value of the mathematical expression:
, whereby Prated is related to the preferential space heater;
— IV: the value of the mathematical expression
, whereby Prated is related to the preferential space heater;
in addition, for preferential heat pump space heaters:
— V: the value of the difference between the seasonal space heating energy efficiencies under average and colder climate conditions, expressed in %;
— VI: the value of the difference between the seasonal space heating energy efficiencies under warmer and average climate conditions, expressed in %.
6. PACKAGES OF COMBINATION HEATER, TEMPERATURE CONTROL AND SOLAR DEVICE
The fiche for packages of combination heater, temperature control and solar device shall contain the elements set out in points (a) and (b):
(a) the elements set out in Figure 1 and Figure 3, respectively, for evaluating the seasonal space heating energy efficiency of a package of combination heater, temperature control and solar device, including the following information:
— I: the value of the seasonal space heating energy efficiency of the preferential combination heater, expressed in %;
— II: the factor for weighting the heat output of the preferential and supplementary heaters of a package as set out in Tables 5 and 6 of this Annex, respectively;
— III: the value of the mathematical expression:
, whereby Prated is related to the preferential combination heater;
— IV: the value of the mathematical expression
, whereby Prated is related to the preferential combination heater;
in addition, for preferential heat pump combination heaters:
— V: the value of the difference between the seasonal space heating energy efficiencies under average and colder climate conditions, expressed in %;
— VI: the value of the difference between the seasonal space heating energy efficiencies under warmer and average climate conditions, expressed in %;
(b) the elements set out in Figure 5 for evaluating the water heating energy efficiency of a package of combination heater, temperature control and solar device, where the following information shall be included:
— I: the value of the water heating energy efficiency of the combination heater, expressed in %;
— II: the value of the mathematical expression
, where Q ref is taken from Table 15 in Annex VII and Q nonsol from the product fiche of the solar device for the declared load profile M, L, XL or XXL of the combination heater;
— III: the value of the mathematical expression
, expressed in %, where Q aux is taken from the product fiche of the solar device and Q ref from Table 15 in Annex VII for the declared load profile M, L, XL or XXL.
Table 5
For the purposes of Figure 1 of this Annex, weighting of preferential boiler space heater or boiler combination heater and supplementary heater ( *1 )
<table><col/><col/><col/><tbody><tr><td><p><img/> &#160;<a>(<span>*2</span>)</a></p></td><td><p>II, package without hot water storage tank</p></td><td><p>II, package with hot water storage tank</p></td></tr><tr><td><p>0</p></td><td><p>0</p></td><td><p>0</p></td></tr><tr><td><p>0,1</p></td><td><p>0,30</p></td><td><p>0,37</p></td></tr><tr><td><p>0,2</p></td><td><p>0,55</p></td><td><p>0,70</p></td></tr><tr><td><p>0,3</p></td><td><p>0,75</p></td><td><p>0,85</p></td></tr><tr><td><p>0,4</p></td><td><p>0,85</p></td><td><p>0,94</p></td></tr><tr><td><p>0,5</p></td><td><p>0,95</p></td><td><p>0,98</p></td></tr><tr><td><p>0,6</p></td><td><p>0,98</p></td><td><p>1,00</p></td></tr><tr><td><p>&#8805; 0,7</p></td><td><p>1,00</p></td><td><p>1,00</p></td></tr><tr><td><div><a>(<span>*1</span>)&#160;&#160;&#160;</a><p>The intermediate values are calculated by linear interpolation between the two adjacent values.</p></div><div><a>(<span>*2</span>)&#160;&#160;&#160;</a><p><span>Prated</span> is related to the preferential space heater or combination heater.</p></div></td></tr></tbody></table>
Table 6
For the purposes of Figures 2 to 4 of this Annex, weighting of preferential cogeneration space heater, heat pump space heater, heat pump combination heater or low-temperature heat pump and supplementary heater ( *1 )
<table><col/><col/><col/><tbody><tr><td><p><img/> &#160;<a>(<span>*2</span>)</a></p></td><td><p>II, package without hot water storage tank</p></td><td><p>II, package with hot water storage tank</p></td></tr><tr><td><p>0</p></td><td><p>1,00</p></td><td><p>1,00</p></td></tr><tr><td><p>0,1</p></td><td><p>0,70</p></td><td><p>0,63</p></td></tr><tr><td><p>0,2</p></td><td><p>0,45</p></td><td><p>0,30</p></td></tr><tr><td><p>0,3</p></td><td><p>0,25</p></td><td><p>0,15</p></td></tr><tr><td><p>0,4</p></td><td><p>0,15</p></td><td><p>0,06</p></td></tr><tr><td><p>0,5</p></td><td><p>0,05</p></td><td><p>0,02</p></td></tr><tr><td><p>0,6</p></td><td><p>0,02</p></td><td><p>0</p></td></tr><tr><td><p>&#8805; 0,7</p></td><td><p>0</p></td><td><p>0</p></td></tr><tr><td><div><a>(<span>*1</span>)&#160;&#160;&#160;</a><p>The intermediate values are calculated by linear interpolation between the two adjacent values.</p></div><div><a>(<span>*2</span>)&#160;&#160;&#160;</a><p><span>Prated</span> is related to the preferential space heater or combination heater.</p></div></td></tr></tbody></table>
Figure 1
For preferential boiler space heaters and preferential boiler combination heaters, element of the fiche for a package of space heater, temperature control and solar device and a package of combination heater, temperature control and solar device, respectively, indicating the seasonal space heating energy efficiency of the package offered
Figure 2
For preferential cogeneration space heaters, element of the fiche for a package of space heater, temperature control and solar device indicating the seasonal space heating energy efficiency of the package offered
Figure 3
For preferential heat pump space heaters and preferential heat pump combination heaters, element of the fiche for a package of space heater, temperature control and solar device and a package of combination heater, temperature control and solar device, respectively, indicating the seasonal space heating energy efficiency of the package offered
Figure 4
For preferential low-temperature heat pumps, element of the fiche for a package of space heater, temperature control and solar device indicating the seasonal space heating energy efficiency of the package offered
Figure 5
For preferential boiler combination heaters and preferential heat pump combination heaters, element of the fiche for a package of combination heater, temperature control and solar device indicating the water heating energy efficiency of the package offered
ANNEX V
Technical documentation
1. SPACE HEATERS
For space heaters, the technical documentation referred to in Article 3(1)(c) shall include:
(a) the name and address of the supplier;
(b) a description of the space heater model sufficient for its unambiguous identification;
(c) where appropriate, the references of the harmonised standards applied;
(d) where appropriate, the other technical standards and specifications used;
(e) the identification and signature of the person empowered to bind the supplier;
(f) technical parameters:
— for boiler space heaters and cogeneration space heaters, the technical parameters set out in Table 7, measured and calculated in accordance with Annex VII;
— for heat pump space heaters, the technical parameters set out in Table 8, measured and calculated in accordance with Annex VII;
— for heat pump space heaters where the information relating to a specific model comprising a combination of indoor and outdoor units has been obtained by calculation on the basis of design and/or extrapolation from other combinations, the details of such calculations and/or extrapolations, and of any tests undertaken to verify the accuracy of the calculations, including details of the mathematical model for calculating the performance of such combinations and details of the measurements taken to verify this model;
(g) any specific precautions that shall be taken when the space heater is assembled, installed or maintained.
2. COMBINATION HEATERS
For combination heaters, the technical documentation referred to in Article 3(2)(c) shall include:
(a) the name and address of the supplier;
(b) a description of the combination heater model sufficient for its unambiguous identification;
(c) where appropriate, the references of the harmonised standards applied;
(d) where appropriate, the other technical standards and specifications used;
(e) the identification and signature of the person empowered to bind the supplier;
(f) technical parameters:
— for boiler combination heaters, the technical parameters set out in Table 7, measured and calculated in accordance with Annex VII;
— for heat pump combination heaters, the technical parameters set out in Table 8, measured and calculated in accordance with Annex VII;
— for heat pump combination heaters where the information relating to a specific model comprising a combination of indoor and outdoor units has been obtained by calculation on the basis of design and/or extrapolation from other combinations, the details of such calculations and/or extrapolations, and of any tests undertaken to verify the accuracy of the calculations, including details of the mathematical model for calculating the performance of such combinations and details of the measurements taken to verify this model;
(g) any specific precautions that shall be taken when the combination heater is assembled, installed or maintained.
Table 7
Technical parameters for boiler space heaters, boiler combination heaters and cogeneration space heaters
<table><col/><col/><col/><col/><col/><col/><col/><col/><col/><tbody><tr><td><p>Model(s): [information identifying the model(s) to which the information relates]</p></td></tr><tr><td><p>Condensing boiler: [yes/no]</p></td></tr><tr><td><p>Low-temperature&#160;<a>(<span>*2</span>)</a> boiler: [yes/no]</p></td></tr><tr><td><p>B11 boiler: [yes/no]</p></td></tr><tr><td><p>Cogeneration space heater: [yes/no]</p></td><td><p>If yes, equipped with a supplementary heater: [yes/no]</p></td></tr><tr><td><p>Combination heater: [yes/no]</p></td></tr><tr><td><p><span>Item</span></p></td><td><p><span>Symbol</span></p></td><td><p><span>Value</span></p></td><td><p><span>Unit</span></p></td><td><p>&#160;</p><div/></td><td><p><span>Item</span></p></td><td><p><span>Symbol</span></p></td><td><p><span>Value</span></p></td><td><p><span>Unit</span></p></td></tr><tr><td><p><span>Rated heat output</span></p></td><td><p><span>Prated</span></p></td><td><p>x</p></td><td><p>kW</p></td><td><p><span>Seasonal space heating energy efficiency</span></p></td><td><p><span>&#951;<span>s</span></span></p></td><td><p>x</p></td><td><p>%</p></td></tr><tr><td><p>For boiler space heaters and boiler combination heaters: Useful heat output</p></td><td><p>For boiler space heaters and boiler combination heaters: Useful efficiency</p></td></tr><tr><td><p>At rated heat output and high-temperature regime&#160;<a>(<span>*1</span>)</a></p></td><td><p><span>P<span>4</span></span></p></td><td><p>x,x</p></td><td><p>kW</p></td><td><p>At rated heat output and high-temperature regime&#160;<a>(<span>*1</span>)</a></p></td><td><p><span>&#951;<span>4</span></span></p></td><td><p>x,x</p></td><td><p>%</p></td></tr><tr><td><p>At 30 % of rated heat output and low-temperature regime&#160;<a>(<span>*2</span>)</a></p></td><td><p><span>P<span>1</span></span></p></td><td><p>x,x</p></td><td><p>kW</p></td><td><p>At 30 % of rated heat output and low-temperature regime&#160;<a>(<span>*2</span>)</a></p></td><td><p><span>&#951;<span>1</span></span></p></td><td><p>x,x</p></td><td><p>%</p></td></tr><tr><td><p>For cogeneration space heaters: Useful heat output</p></td><td><p>For cogeneration space heaters: Useful efficiency</p></td></tr><tr><td><p>At rated heat output of cogeneration space heater with supplementary heater disabled</p></td><td><p><span>P<span>CHP100+Sup0</span></span></p></td><td><p>x,x</p></td><td><p>kW</p></td><td><p>At rated heat output of cogeneration space heater with supplementary heater disabled</p></td><td><p><span>&#951;<span>CHP100+Sup0</span></span></p></td><td><p>x,x</p></td><td><p>%</p></td></tr><tr><td><p>At rated heat output of cogeneration space heater with supplementary heater enabled</p></td><td><p><span>P<span>CHP100+Sup100</span></span></p></td><td><p>x,x</p></td><td><p>kW</p></td><td><p>At rated heat output of cogeneration space heater with supplementary heater enabled</p></td><td><p><span>&#951;<span>CHP100+Sup100</span></span></p></td><td><p>x,x</p></td><td><p>%</p></td></tr><tr><td><p>For cogeneration space heaters: Electrical efficiency</p></td><td><p>Supplementary heater</p></td></tr><tr><td><p>At rated heat output of cogeneration space heater with supplementary heater disabled</p></td><td><p><span>&#951;<span>el,CHP100+Sup0</span></span></p></td><td><p>x,x</p></td><td><p>%</p></td><td><p>Rated heat output</p></td><td><p><span>Psup</span></p></td><td><p>x,x</p></td><td><p>kW</p></td></tr><tr><td><p>At rated heat output of cogeneration space heater with supplementary heater enabled</p></td><td><p><span>&#951;<span>el,CHP100+Sup100</span></span></p></td><td><p>x,x</p></td><td><p>%</p></td><td><p>Type of energy input</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>Auxiliary electricity consumption</p></td><td><p>Other items</p></td></tr><tr><td><p>At full load</p></td><td><p><span>elmax</span></p></td><td><p>x,x</p></td><td><p>kW</p></td><td><p>Standby heat loss</p></td><td><p><span>P<span>stby</span></span></p></td><td><p>x,x</p></td><td><p>kW</p></td></tr><tr><td><p>At part load</p></td><td><p><span>elmin</span></p></td><td><p>x,x</p></td><td><p>kW</p></td><td><p>Ignition burner power consumption</p></td><td><p><span>P<span>ign</span></span></p></td><td><p>x,x</p></td><td><p>kW</p></td></tr><tr><td><p>In standby mode</p></td><td><p><span>P<span>SB</span></span></p></td><td><p>x,xxx</p></td><td><p>kW</p></td><td><p>Annual energy consumption</p></td><td><p><span>Q<span>HE</span></span></p></td><td><p>x</p></td><td><p>kWh or GJ</p></td></tr><tr><td><p>Sound power level, indoors</p></td><td><p><span>L<span>WA</span></span></p></td><td><p>x</p></td><td><p>dB</p></td></tr><tr><td><p>For combination heaters:</p></td></tr><tr><td><p><span>Declared load profile</span></p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>Water heating energy efficiency</span></p></td><td><p><span>&#951;<span>wh</span></span></p></td><td><p>x</p></td><td><p>%</p></td></tr><tr><td><p>Daily electricity consumption</p></td><td><p><span>Q<span>elec</span></span></p></td><td><p>x,xxx</p></td><td><p>kWh</p></td><td><p>Daily fuel consumption</p></td><td><p><span>Q<span>fuel</span></span></p></td><td><p>x,xxx</p></td><td><p>kWh</p></td></tr><tr><td><p>Annual electricity consumption</p></td><td><p><span>AEC</span></p></td><td><p>x</p></td><td><p>kWh</p></td><td><p>Annual fuel consumption</p></td><td><p><span>AFC</span></p></td><td><p>x</p></td><td><p>GJ</p></td></tr><tr><td><p>Contact details</p></td><td><p>Name and address of the supplier.</p></td></tr><tr><td><div><a>(<span>*1</span>)&#160;&#160;&#160;</a><p>High-temperature regime means 60 &#176;C return temperature at heater inlet and 80 &#176;C feed temperature at heater outlet.</p></div><div><a>(<span>*2</span>)&#160;&#160;&#160;</a><p>Low temperature means for condensing boilers 30 &#176;C, for low-temperature boilers 37 &#176;C and for other heaters 50 &#176;C return temperature (at heater inlet).</p></div></td></tr></tbody></table>
Table 8
Technical parameters for heat pump space heaters and heat pump combination heaters
<table><col/><col/><col/><col/><col/><col/><col/><col/><col/><tbody><tr><td><p>Model(s): [information identifying the model(s) to which the information relates]</p></td></tr><tr><td><p>Air-to-water heat pump: [yes/no]</p></td></tr><tr><td><p>Water-to-water heat pump: [yes/no]</p></td></tr><tr><td><p>Brine-to-water heat pump: [yes/no]</p></td></tr><tr><td><p>Low-temperature heat pump: [yes/no]</p></td></tr><tr><td><p>Equipped with a supplementary heater: [yes/no]</p></td></tr><tr><td><p>Heat pump combination heater: [yes/no]</p></td></tr><tr><td><p>Parameters shall be declared for medium-temperature application, except for low-temperature heat pumps. For low-temperature heat pumps, parameters shall be declared for low-temperature application.</p></td></tr><tr><td><p>Parameters shall be declared for average, colder and warmer climate conditions.</p></td></tr><tr><td><p><span>Item</span></p></td><td><p><span>Symbol</span></p></td><td><p><span>Value</span></p></td><td><p><span>Unit</span></p></td><td><p>&#160;</p><div/></td><td><p><span>Item</span></p></td><td><p><span>Symbol</span></p></td><td><p><span>Value</span></p></td><td><p><span>Unit</span></p></td></tr><tr><td><p><span>Rated heat output</span>&#160;<a>(<span>*1</span>)</a></p></td><td><p><span>Prated</span></p></td><td><p>x</p></td><td><p>kW</p></td><td><p><span>Seasonal space heating energy efficiency</span></p></td><td><p><span>&#951;<span>s</span></span></p></td><td><p>x</p></td><td><p>%</p></td></tr><tr><td><p>Declared capacity for heating for part load at indoor temperature 20 &#176;C and outdoor temperature<span>T<span>j</span></span></p></td><td><p>Declared coefficient of performance or primary energy ratio for part load at indoor temperature 20 &#176;C and outdoor temperature<span>T<span>j</span></span></p></td></tr><tr><td><p><span>T<span>j</span></span> = &#8211; 7 &#176;C</p></td><td><p><span>Pdh</span></p></td><td><p>x,x</p></td><td><p>kW</p></td><td><p><span>T<span>j</span></span> = &#8211; 7 &#176;C</p></td><td><p><span>COPd or PERd</span></p></td><td><p>x,xx or x,x</p></td><td><p>&#8211; or %</p></td></tr><tr><td><p><span>T<span>j</span></span> = + 2 &#176;C</p></td><td><p><span>Pdh</span></p></td><td><p>x,x</p></td><td><p>kW</p></td><td><p><span>T<span>j</span></span> = + 2 &#176;C</p></td><td><p><span>COPd or PERd</span></p></td><td><p>x,xx or x,x</p></td><td><p>&#8211; or %</p></td></tr><tr><td><p><span>T<span>j</span></span> = + 7 &#176;C</p></td><td><p><span>Pdh</span></p></td><td><p>x,x</p></td><td><p>kW</p></td><td><p><span>T<span>j</span></span> = + 7 &#176;C</p></td><td><p><span>COPd or PERd</span></p></td><td><p>x,xx or x,x</p></td><td><p>&#8211; or %</p></td></tr><tr><td><p><span>T<span>j</span></span> = + 12 &#176;C</p></td><td><p><span>Pdh</span></p></td><td><p>x,x</p></td><td><p>kW</p></td><td><p><span>T<span>j</span></span> = + 12 &#176;C</p></td><td><p><span>COPd or PERd</span></p></td><td><p>x,xx or x,x</p></td><td><p>&#8211; or %</p></td></tr><tr><td><p><span>T<span>j</span></span> = bivalent temperature</p></td><td><p><span>Pdh</span></p></td><td><p>x,x</p></td><td><p>kW</p></td><td><p><span>T<span>j</span></span> = bivalent temperature</p></td><td><p><span>COPd or PERd</span></p></td><td><p>x,xx or x,x</p></td><td><p>&#8211; or %</p></td></tr><tr><td><p><span>T<span>j</span></span> = operation limit temperature</p></td><td><p><span>Pdh</span></p></td><td><p>x,x</p></td><td><p>kW</p></td><td><p><span>T<span>j</span></span> = operation limit temperature</p></td><td><p><span>COPd or PERd</span></p></td><td><p>x,xx or x,x</p></td><td><p>&#8211; or %</p></td></tr><tr><td><p>For air-to-water heat pumps:<span>T<span>j</span></span> = &#8211; 15 &#176;C (if<span>TOL</span> &lt; &#8211; 20 &#176;C)</p></td><td><p><span>Pdh</span></p></td><td><p>x,x</p></td><td><p>kW</p></td><td><p>For air-to-water heat pumps:<span>T<span>j</span></span> = &#8211; 15 &#176;C (if<span>TOL</span> &lt; &#8211; 20 &#176;C)</p></td><td><p><span>COPd or PERd</span></p></td><td><p>x,xx or x,x</p></td><td><p>&#8211; or %</p></td></tr><tr><td><p>Bivalent temperature</p></td><td><p><span>T<span>biv</span></span></p></td><td><p>x</p></td><td><p>&#176;C</p></td><td><p>For air-to-water heat pumps: Operation limit temperature</p></td><td><p><span>TOL</span></p></td><td><p>x</p></td><td><p>&#176;C</p></td></tr><tr><td><p>Cycling interval capacity for heating</p></td><td><p><span>Pcych</span></p></td><td><p>x,x</p></td><td><p>kW</p></td><td><p>Cycling interval efficiency</p></td><td><p><span>COPcyc or PERcyc</span></p></td><td><p>x,xx or x,x</p></td><td><p>&#8211; or %</p></td></tr><tr><td><p>Degradation co-efficient&#160;<a>(<span>*2</span>)</a></p></td><td><p><span>Cdh</span></p></td><td><p>x,x</p></td><td><p>&#8212;</p></td><td><p>Heating water operating limit temperature</p></td><td><p><span>WTOL</span></p></td><td><p>x</p></td><td><p>&#176;C</p></td></tr><tr><td><p>Power consumption in modes other than active mode</p></td><td><p>Supplementary heater</p></td></tr><tr><td><p>Off mode</p></td><td><p><span>P<span>OFF</span></span></p></td><td><p>x,xxx</p></td><td><p>kW</p></td><td><p>Rated heat output&#160;<a>(<span>*2</span>)</a></p></td><td><p><span>Psup</span></p></td><td><p>x,x</p></td><td><p>kW</p></td></tr><tr><td><p>Thermostat-off mode</p></td><td><p><span>P<span>TO</span></span></p></td><td><p>x,xxx</p></td><td><p>kW</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>Standby mode</p></td><td><p><span>P<span>SB</span></span></p></td><td><p>x,xxx</p></td><td><p>kW</p></td><td><p>Type of energy input</p></td></tr><tr><td><p>Crankcase heater mode</p></td><td><p><span>P<span>CK</span></span></p></td><td><p>x,xxx</p></td><td><p>kW</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>Other items</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>Capacity control</p></td><td><p>fixed/variable</p></td><td><p>For air-to-water heat pumps: Rated air flow rate, outdoors</p></td><td><p>&#8212;</p></td><td><p>x</p></td><td><p>m<span>3</span>/h</p></td></tr><tr><td><p>Sound power level, indoors/outdoors</p></td><td><p><span>L<span>WA</span></span></p></td><td><p>x / x</p></td><td><p>dB</p></td><td><p>For water- or brine-to-water heat pumps: Rated brine or water flow rate, outdoor heat exchanger</p></td><td><p>&#8212;</p></td><td><p>x</p></td><td><p>m<span>3</span>/h</p></td></tr><tr><td><p>Annual energy consumption</p></td><td><p><span>Q<span>HE</span></span></p></td><td><p>x</p></td><td><p>kWh or GJ</p></td></tr><tr><td><p>For heat pump combination heater:</p></td></tr><tr><td><p><span>Declared load profile</span></p></td><td><p>x</p></td><td><p>&#160;</p><div/></td><td><p><span>Water heating energy efficiency</span></p></td><td><p><span>&#951;<span>wh</span></span></p></td><td><p>x</p></td><td><p>%</p></td></tr><tr><td><p>Daily electricity consumption</p></td><td><p><span>Q<span>elec</span></span></p></td><td><p>x,xxx</p></td><td><p>kWh</p></td><td><p>Daily fuel consumption</p></td><td><p><span>Q<span>fuel</span></span></p></td><td><p>x,xxx</p></td><td><p>kWh</p></td></tr><tr><td><p>Annual electricity consumption</p></td><td><p><span>AEC</span></p></td><td><p>x</p></td><td><p>kWh</p></td><td><p>Annual fuel consumption</p></td><td><p><span>AFC</span></p></td><td><p>x</p></td><td><p>GJ</p></td></tr><tr><td><p>Contact details</p></td><td><p>Name and address of the supplier.</p></td></tr><tr><td><div><a>(<span>*1</span>)&#160;&#160;&#160;</a><p>For heat pump space heaters and heat pump combination heaters, the rated heat output<span>Prated</span> is equal to the design load for heating<span>Pdesignh</span>, and the rated heat output of a supplementary heater<span>Psup</span> is equal to the supplementary capacity for heating<span>sup(Tj)</span>.</p></div><div><a>(<span>*2</span>)&#160;&#160;&#160;</a><p>If<span>Cdh</span> is not determined by measurement then the default degradation coefficient is<span>Cdh</span> = 0,9.</p></div></td></tr></tbody></table>
3. TEMPERATURE CONTROLS
For temperature controls, the technical documentation referred to in Article 3(3)(b) shall include:
(a) the name and address of the supplier;
(b) a description of the temperature control model sufficient for its unambiguous identification;
(c) where appropriate, the references of the harmonised standards applied;
(d) where appropriate, the other technical standards and specifications used;
(e) the identification and signature of the person empowered to bind the supplier;
(f) technical parameters:
— the class of the temperature control;
— the contribution of the temperature control to seasonal space heating energy efficiency in %, rounded to one decimal place;
(g) any specific precautions that shall be taken when the temperature control is assembled, installed or maintained.
4. SOLAR DEVICES
For solar devices, the technical documentation referred to in Article 3(4)(b) shall include:
(a) the name and address of the supplier;
(b) a description of the solar device model sufficient for its unambiguous identification;
(c) where appropriate, the references of the harmonised standards applied;
(d) where appropriate, the other technical standards and specifications used;
(e) the identification and signature of the person empowered to bind the supplier;
(f) technical parameters (for pumps in the collector loop if applicable):
— the collector aperture area A sol in m 2 , to two decimal places;
— the collector efficiency η col in %, rounded to the nearest integer;
— the energy efficiency class of the solar hot water storage tank, determined in accordance with point 3 of Annex II;
— the standing loss S of the solar hot water storage tank in W, rounded to the nearest integer;
— the storage volume V of the solar hot water storage tank in litres and m 3 ;
— the annual non-solar heat contribution Q nonsol in kWh in terms of primary energy for electricity and/or in kWh in terms of GCV for fuels, for the load profiles M, L, XL and XXL under average climate conditions, rounded to the nearest integer;
— the pump power consumption solpump in W, rounded to the nearest integer;
— the standby power consumption solstandby in W, to two decimal places;
— the annual auxiliary electricity consumption Q aux in kWh in terms of final energy, rounded to the nearest integer;
(g) any specific precautions that shall be taken when the solar device is assembled, installed or maintained.
5. PACKAGES OF SPACE HEATER, TEMPERATURE CONTROL AND SOLAR DEVICE
For packages of space heater, temperature control and solar device, the technical documentation referred to in Article 3(5)(c) shall include:
(a) the name and address of the supplier;
(b) a description of the package of space heater, temperature control and solar device model sufficient for its unambiguous identification;
(c) where appropriate, the references of the harmonised standards applied;
(d) where appropriate, the other technical standards and specifications used;
(e) the identification and signature of the person empowered to bind the supplier;
(f) technical parameters:
— the seasonal space heating energy efficiency in %, rounded to the nearest integer;
— the technical parameters set out in points 1, 3 and 4 of this Annex;
(g) any specific precautions that shall be taken when the package of space heater, temperature control and solar device is assembled, installed or maintained.
6. PACKAGES OF COMBINATION HEATER, TEMPERATURE CONTROL AND SOLAR DEVICE
For packages of combination heater, temperature control and solar device, the technical documentation referred to in Article 3(6)(c) shall include:
(a) the name and address of the supplier;
(b) a description of the package of combination heater, temperature control and solar device model sufficient for its unambiguous identification;
(c) where appropriate, the references of the harmonised standards applied;
(d) where appropriate, the other technical standards and specifications used;
(e) the identification and signature of the person empowered to bind the supplier;
(f) technical parameters:
— the seasonal space heating energy efficiency and water heating energy efficiency in %, rounded to the nearest integer;
— the technical parameters set out in points 2, 3 and 4 of this Annex;
(g) any specific precautions that shall be taken when the package of combination heater, temperature control and solar device is assembled, installed or maintained.
ANNEX VI
Information to be provided in the cases where end-users cannot be expected to see the product displayed, except on the internet
1. SPACE HEATERS
1.1. The information referred to in Article 4(1)(b) shall be provided in the following order:
(a) the seasonal space heating energy efficiency class of the model, determined in accordance with point 1 of Annex II;
(b) the rated heat output, including the rated heat output of any supplementary heater, in kW, rounded to the nearest integer (for heat pump space heaters, under average climate conditions);
(c) the seasonal space heating energy efficiency in %, rounded to the nearest integer and calculated in accordance with points 3 and 4 of Annex VII (for heat pump space heaters, under average climate conditions);
(d) the annual energy consumption in kWh in terms of final energy and/or in GJ in terms of GCV , rounded to the nearest integer and calculated in accordance with points 3 and 4 of Annex VII (for heat pump space heaters, under average climate conditions);
(e) the sound power level L WA , indoors, in dB, rounded to the nearest integer (for heat pump space heaters if applicable);
in addition, for cogeneration space heaters:
(f) the electrical efficiency in %, rounded to the nearest integer;
in addition, for heat pump space heaters:
(g) the rated heat output, including the rated heat output of any supplementary heater, in kW, under colder and warmer climate conditions, rounded to the nearest integer;
(h) the seasonal space heating energy efficiency in %, under colder and warmer climate conditions, rounded to the nearest integer and calculated in accordance with point 4 of Annex VII;
(i) the annual energy consumption in kWh in terms of final energy and/or in GJ in terms of GCV , under colder and warmer climate conditions, rounded to the nearest integer and calculated in accordance with point 4 of Annex VII;
(j) the sound power level L WA , outdoors, in dB, rounded to the nearest integer;
in addition, for low-temperature heat pumps:
(k) an indication that the low-temperature heat pump is only suitable for low-temperature application;
1.2. The size and font in which the information referred in point 1.1 is printed or shown shall be legible.
2. COMBINATION HEATERS
2.1. The information referred to in Article 4(2)(b) shall be provided in the following order:
(a) for space heating, the medium-temperature application; for water heating, the declared load profile, expressed as the appropriate letter and typical usage in accordance with Table 15 of Annex VII;
(b) the seasonal space heating energy efficiency class and the water heating energy efficiency class of the model, determined in accordance with points 1 and 2 of Annex II;
(c) the rated heat output, including the rated heat output of any supplementary heater, in kW, rounded to the nearest integer (for heat pump combination heaters, under average climate conditions);
(d) for space heating, the annual energy consumption in kWh in terms of final energy and/or in GJ in terms of GCV , rounded to the nearest integer and calculated in accordance with points 3 and 4 of Annex VII (for heat pump combination heaters, under average climate conditions); for water heating, the annual electricity consumption in kWh in terms of final energy and/or the annual fuel consumption in GJ in terms of GCV , rounded to the nearest integer and calculated in accordance with point 5 of Annex VII (for heat pump combination heaters, under average climate conditions);
(e) the seasonal space heating energy efficiency in %, rounded to the nearest integer and calculated in accordance with points 3 and 4 of Annex VII (for heat pump combination heaters, under average climate conditions); the water heating energy efficiency in %, rounded to the nearest integer and calculated in accordance with point 5 of Annex VII (for heat pump combination heaters, under average climate conditions);
(f) the sound power level L WA , indoors, in dB, rounded to the nearest integer (for heat pump combination heaters if applicable);
(g) if applicable, an indication that the combination heater is able to work only during off-peak hours;
in addition, for heat pump combination heaters:
(h) the rated heat output, including the rated heat output of any supplementary heater, in kW, under colder and warmer climate conditions, rounded to the nearest integer;
(i) for space heating, the annual energy consumption in kWh in terms of final energy and/or in GJ in terms of GCV , under colder and warmer climate conditions, rounded to the nearest integer and calculated in accordance with point 4 of Annex VII; for water heating, the annual electricity consumption in kWh in terms of final energy and/or the annual fuel consumption in GJ in terms of GCV , under colder and warmer climate conditions, rounded to the nearest integer and calculated in accordance with point 5 of Annex VII;
(j) the seasonal space heating energy efficiency in %, under colder and warmer climate conditions, rounded to the nearest integer and calculated in accordance with point 4 of Annex VII; the water heating energy efficiency in %, under colder and warmer climate conditions, rounded to the nearest integer and calculated in accordance with point 5 of Annex VII;
(k) the sound power level L WA , outdoors, in dB, rounded to the nearest integer.
2.2. The size and font in which the information referred in point 2.1 is printed or shown shall be legible.
3. PACKAGES OF SPACE HEATER, TEMPERATURE CONTROL AND SOLAR DEVICE
3.1. The information referred to in Article 4(3)(b) shall be provided in the following order:
(a) the seasonal space heating energy efficiency class of the model, determined in accordance with point 1 of Annex II;
(b) the seasonal space heating energy efficiency in %, rounded to the nearest integer;
(c) the elements set out in Figure 1, Figure 2, Figure 3 and Figure 4, respectively, of Annex IV.
3.2. The size and font in which the information referred in point 3.1 is printed or shown shall be legible.
4. PACKAGES OF COMBINATION HEATER, TEMPERATURE CONTROL AND SOLAR DEVICE
4.1. The information referred to in Article 4(4)(b) shall be provided in the following order:
(a) the seasonal space heating energy efficiency class and the water heating energy efficiency class of the model, determined in accordance with points 1 and 2 of Annex II;
(b) the seasonal space heating energy efficiency and the water heating energy efficiency in %, rounded to the nearest integer;
(c) the elements set out in Figure 1 and Figure 3, respectively, of Annex IV;
(d) the elements set out in Figure 5 of Annex IV.
4.2. The size and font in which the information referred in point 4.1 is printed or shown shall be legible.
ANNEX VII
Measurements and calculations
<table><col/><col/><tr><td><p>1.</p></td><td><p>For the purposes of compliance and verification of compliance with the requirements of this Regulation, measurements and calculations shall be made using harmonised standards the reference numbers of which have been published for this purpose in the<span>Official Journal of the European Union</span>, or using other reliable, accurate and reproducible methods that take into account the generally recognised state-of-the-art methods. They shall meet the conditions and technical parameters set out in points 2 to 6.</p></td></tr></table>
<table><col/><col/><tr><td><p>2.</p></td><td><span>General conditions for measurements and calculations</span><div><p>(a)<span>&#160;</span>For the purposes of the measurements set out in points 3 to 7, the indoor ambient temperature shall be set at 20 &#176;C.</p></div><div><p>(b)<span>&#160;</span>For the purposes of the calculations set out in points 3 to 7, electricity consumption shall be multiplied by a conversion coefficient<span>CC</span> of 2,5, unless the annual electricity consumption is expressed in final energy for the end-user, as set out in points 3(b), 4(g), 5(e) and 6.</p></div><div><p>(c)<span>&#160;</span>For heaters equipped with supplementary heaters, the measurement and calculation of rated heat output, seasonal space heating energy efficiency, water heating energy efficiency, sound power level and emissions of nitrogen oxides shall take account of the supplementary heater.</p></div><div><p>(d)<span>&#160;</span>Declared values for rated heat output, seasonal space heating energy efficiency, water heating energy efficiency, annual energy consumption and sound power level shall be rounded to the nearest integer.</p></div></td></tr></table>
<table><col/><col/><tr><td><p>3.</p></td><td><span>Seasonal space heating energy efficiency and consumption of boiler space heaters, boiler combination heaters and cogeneration space heaters</span><div><p>(a)<span>&#160;</span>The seasonal space heating energy efficiency<span>&#951;<span>s</span></span> shall be calculated as the seasonal space heating energy efficiency in active mode<span>&#951;<span>son</span></span>, corrected by contributions accounting for temperature controls, auxiliary electricity consumption, standby heat loss, ignition burner power consumption (if applicable) and, for cogeneration space heaters, corrected by adding the electrical efficiency multiplied by a conversion coefficient<span>CC</span> of 2,5.</p></div><div><p>(b)<span>&#160;</span>The annual energy consumption<span>Q<span>HE</span></span> in kWh in terms of final energy and/or in GJ in terms of<span>GCV</span> shall be calculated as the ratio of the reference annual heating demand and the seasonal space heating energy efficiency.</p></div></td></tr></table>
<table><col/><col/><tr><td><p>4.</p></td><td><span>Seasonal space heating energy efficiency and consumption of heat pump space heaters and heat pump combination heaters</span><div><p>(a)<span>&#160;</span>For establishing the rated coefficient of performance<span>COP<span>rated</span></span> or rated primary energy ratio<span>PER<span>rated</span></span>, or the sound power level, the operating conditions shall be the standard rating conditions set out in Table 9 and the same declared capacity for heating shall be used.</p></div><div><p>(b)<span>&#160;</span>The active mode coefficient of performance<span>SCOP<span>on</span></span> for average, colder and warmer climate conditions shall be calculated on the basis of the part load for heating<span>Ph(T<span>j</span>)</span>, the supplementary capacity for heating<span>sup(T<span>j</span>)</span> (if applicable), and the bin-specific coefficient of performance<span>COPbin(Tj)</span> or bin-specific primary energy ratio<span>PERbin(T<span>j</span>)</span>, weighted by the bin-hours for which the bin conditions apply, using the following conditions:</p></div><div><div><span>&#8212;&#160;</span></div><div><div>the reference design conditions set out in Table 10;</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div>the European reference heating season under average, colder and warmer climate conditions set out in Table 12;</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div>if applicable, the effects of any degradation of energy efficiency caused by cycling, depending on the type of control of the heating capacity.</div></div></div><div><p>(c)<span>&#160;</span>The reference annual heating demand<span>Q<span>H</span></span> shall be the design load for heating<span>Pdesignh</span> for average, colder and warmer climate conditions, multiplied by the annual equivalent active mode hours<span>H<span>HE</span></span> of 2&#160;066 , 2&#160;465  and 1&#160;336  for average, colder and warmer climate conditions, respectively.</p></div><div><p>(d)<span>&#160;</span>The annual energy consumption<span>Q<span>HE</span></span> shall be calculated as the sum of:</p></div><div><div><span>&#8212;&#160;</span></div><div><div>the ratio of the reference annual heating demand<span>Q<span>H</span></span> and the active mode coefficient of performance<span>SCOP<span>on</span></span> or active mode primary energy ratio<span>SPER<span>on</span></span>; and</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div>the energy consumption for off, thermostat-off, standby, and crankcase heater mode during the heating season.</div></div></div><div><p>(e)<span>&#160;</span>The seasonal coefficient of performance<span>SCOP</span> or seasonal primary energy ratio<span>SPER</span> shall be calculated as the ratio of the reference annual heating demand<span>Q<span>H</span></span> and the annual energy consumption<span>Q<span>HE</span></span>.</p></div><div><p>(f)<span>&#160;</span>The seasonal space heating energy efficiency<span>&#951;<span>s</span></span> shall be calculated as the seasonal coefficient of performance<span>SCOP</span> divided by the conversion coefficient<span>CC</span> or the seasonal primary energy ratio<span>SPER</span>, corrected by contributions accounting for temperature controls and, for water-/brine-to-water heat pump space heaters and heat pump combination heaters, the electricity consumption of one or more ground water pumps.</p></div><div><p>(g)<span>&#160;</span>The annual energy consumption<span>Q<span>HE</span></span> in kWh in terms of final energy and/or GJ in terms of<span>GCV</span> shall be calculated as the ratio of the reference annual heating demand<span>Q<span>H</span></span> and the seasonal space heating energy efficiency<span>&#951;<span>s</span></span>.</p></div></td></tr></table>
<table><col/><col/><tr><td><p>5.</p></td><td><span>Water heating energy efficiency of combination heaters</span><p>The water heating energy efficiency<span>&#951;<span>wh</span></span> of a combination heater shall be calculated as the ratio between the reference energy<span>Q<span>ref</span></span> and the energy required for its generation under the following conditions:</p><div><div><span>(a)&#160;</span></div><div><p>measurements shall be carried out using the load profiles set out in Table 15;</p></div></div><div><div><span>(b)&#160;</span></div><div><p>measurements shall be carried out using a 24-hour measurement cycle as follows:</p><div><div><span>&#8212;&#160;</span></div><div><div>00:00 to 06:59: no water draw-off;</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div>from 07:00: water draw-offs according to the declared load profile;</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div>from end of last water draw-off until 24:00: no water draw-off;</div></div></div></div></div><div><div><span>(c)&#160;</span></div><div><p>the declared load profile shall be the maximum load profile or the load profile one below the maximum load profile;</p></div></div><div><div><span>(d)&#160;</span></div><div><p>for heat pump combination heaters, the following additional conditions apply:</p><div><div><span>&#8212;&#160;</span></div><div><div>heat pump combination heaters shall be tested under the conditions set out in Table 9;</div></div></div><div><div><span>&#8212;&#160;</span></div><div><div>heat pump combination heaters which use ventilation exhaust air as the heat source shall be tested under the conditions set out in Table 11;</div></div></div></div></div><div><div><span>(e)&#160;</span></div><div><p>the annual electricity consumption<span>AEC</span> in kWh in terms of final energy shall be calculated as daily electricity consumption<span>Q<span>elec</span></span> in kWh in terms of final energy multiplied by 220;</p></div></div><div><div><span>(f)&#160;</span></div><div><p>the annual fuel consumption<span>AFC</span> in GJ in terms of<span>GCV</span> shall be calculated as daily fuel consumption<span>Q<span>fuel</span></span> multiplied by 220.</p></div></div></td></tr></table>
<table><col/><col/><tr><td><p>6.</p></td><td><span>Conditions for measurements and calculations of solar devices</span><p>The solar collector, solar hot water storage tank and pump in the collector loop (if applicable) shall be tested separately. Where the solar collector and solar hot water storage tank cannot be tested separately, they shall be tested in combination.</p><p>The results shall be used for the determination of the standing loss<span>S</span> and the calculations of the collector efficiency<span>&#951;<span>col</span></span>, the annual non-solar heat contribution<span>Q<span>nonsol</span></span> for the load profiles M, L, XL and XXL under the average climate conditions set out in Tables 13 and 14, and the annual auxiliary electricity consumption<span>Q<span>aux</span></span> in kWh in terms of final energy.</p><p><br/></p><div><p><br/></p><p><span>Table 9</span></p><p><span>Standard rating conditions for heat pump space heaters and heat pump combination heaters</span></p><table><col/><col/><col/><col/><col/><col/><col/><tbody><tr><td><p>Heat source</p></td><td><p>Outdoor heat exchanger</p></td><td><p>Indoor heat exchanger</p></td></tr><tr><td><p>Climate condition</p></td><td><p>Inlet dry bulb (wet bulb) temperature</p></td><td><p>Heat pump space heaters and heat pump combination heaters, except low-temperature heat pumps</p></td><td><p>Low-temperature heat pumps</p></td></tr><tr><td><p>Inlet temperature</p></td><td><p>Outlet temperature</p></td><td><p>Inlet temperature</p></td><td><p>Outlet temperature</p></td></tr><tr><td><p>Outdoor air</p></td><td><p>Average</p></td><td><p>+ 7 &#176;C</p><p>(+ 6 &#176;C)</p></td><td><p>+47  &#176;C</p></td><td><p>+55  &#176;C</p></td><td><p>+30  &#176;C</p></td><td><p>+35  &#176;C</p></td></tr><tr><td><p>&#160;</p><div/></td><td><p>Colder</p></td><td><p>+ 2 &#176;C</p><p>(+ 1 &#176;C)</p></td></tr><tr><td><p>&#160;</p><div/></td><td><p>Warmer</p></td><td><p>+ 14 &#176;C</p><p>(+ 13 &#176;C)</p></td></tr><tr><td><p>Exhaust air</p></td><td><p>All</p></td><td><p>+ 20 &#176;C</p><p>(+ 12 &#176;C)</p></td></tr><tr><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>Inlet / outlet temperature</p></td></tr><tr><td><p>Water</p></td><td><p>All</p></td><td><p>+ 10 &#176;C /</p><p>+ 7 &#176;C</p></td></tr><tr><td><p>Brine</p></td><td><p>All</p></td><td><p>0 &#176;C/&#8211; 3 &#176;C</p></td></tr></tbody></table></div><p><br/></p><div><p><br/></p><p><span>Table 10</span></p><p><span>Reference design conditions for heat pump space heaters and heat pump combination heaters, temperatures in dry bulb air temperature (wet bulb air temperature indicated in brackets)</span></p><table><col/><col/><col/><col/><tbody><tr><td><p>Climate condition</p></td><td><p>Reference design temperature</p></td><td><p>Bivalent temperature</p></td><td><p>Operation limit temperature</p></td></tr><tr><td><p><span>Tdesignh</span></p></td><td><p><span>T<span>biv</span></span></p></td><td><p><span>TOL</span></p></td></tr><tr><td><p>Average</p></td><td><p>&#8211; 10 (&#8211; 11) &#176;C</p></td><td><p>maximum + 2 &#176;C</p></td><td><p>maximum &#8211; 7 &#176;C</p></td></tr><tr><td><p>Colder</p></td><td><p>&#8211; 22 (&#8211; 23) &#176;C</p></td><td><p>maximum &#8211; 7 &#176;C</p></td><td><p>maximum &#8211; 15 &#176;C</p></td></tr><tr><td><p>Warmer</p></td><td><p>+ 2 (+ 1) &#176;C</p></td><td><p>maximum + 7 &#176;C</p></td><td><p>maximum + 2 &#176;C</p></td></tr></tbody></table></div><p><br/></p><div><p><br/></p><p><span>Table 11</span></p><p><span>Maximum ventilation exhaust air available [m<span>3</span>/h], with humidity of 5,5 g/m<span>3</span></span></p><table><col/><col/><col/><col/><col/><col/><col/><col/><tbody><tr><td><p>Declared load profile</p></td><td><p>XXS</p></td><td><p>XS</p></td><td><p>S</p></td><td><p>M</p></td><td><p>L</p></td><td><p>XL</p></td><td><p>XXL</p></td></tr><tr><td><p>Maximum ventilation exhaust air available</p></td><td><p>109</p></td><td><p>128</p></td><td><p>128</p></td><td><p>159</p></td><td><p>190</p></td><td><p>870</p></td><td><p>1&#160;021</p></td></tr></tbody></table></div><p><br/></p><div><p><br/></p><p><span>Table 12</span></p><p><span>European reference heating season under average, colder and warmer climate conditions for heat pump space heaters and heat pump combination heaters</span></p><table><col/><col/><col/><col/><col/><tbody><tr><td><p><span>bin<span>j</span></span></p></td><td><p><span>T<span>j</span></span> [&#176;C]</p></td><td><p>Average climate conditions</p></td><td><p>Colder climate conditions</p></td><td><p>Warmer climate conditions</p></td></tr><tr><td><p><span>H<span>j</span></span> [h/annum]</p></td><td><p><span>H<span>j</span></span> [h/annum]</p></td><td><p><span>H<span>j</span></span> [h/annum]</p></td></tr><tr><td><p>1 to 8</p></td><td><p>&#8211;30 to &#8211;23</p></td><td><p>0</p></td><td><p>0</p></td><td><p>0</p></td></tr><tr><td><p>9</p></td><td><p>&#8211;22</p></td><td><p>0</p></td><td><p>1</p></td><td><p>0</p></td></tr><tr><td><p>10</p></td><td><p>&#8211;21</p></td><td><p>0</p></td><td><p>6</p></td><td><p>0</p></td></tr><tr><td><p>11</p></td><td><p>&#8211;20</p></td><td><p>0</p></td><td><p>13</p></td><td><p>0</p></td></tr><tr><td><p>12</p></td><td><p>&#8211;19</p></td><td><p>0</p></td><td><p>17</p></td><td><p>0</p></td></tr><tr><td><p>13</p></td><td><p>&#8211;18</p></td><td><p>0</p></td><td><p>19</p></td><td><p>0</p></td></tr><tr><td><p>14</p></td><td><p>&#8211;17</p></td><td><p>0</p></td><td><p>26</p></td><td><p>0</p></td></tr><tr><td><p>15</p></td><td><p>&#8211;16</p></td><td><p>0</p></td><td><p>39</p></td><td><p>0</p></td></tr><tr><td><p>16</p></td><td><p>&#8211;15</p></td><td><p>0</p></td><td><p>41</p></td><td><p>0</p></td></tr><tr><td><p>17</p></td><td><p>&#8211;14</p></td><td><p>0</p></td><td><p>35</p></td><td><p>0</p></td></tr><tr><td><p>18</p></td><td><p>&#8211;13</p></td><td><p>0</p></td><td><p>52</p></td><td><p>0</p></td></tr><tr><td><p>19</p></td><td><p>&#8211;12</p></td><td><p>0</p></td><td><p>37</p></td><td><p>0</p></td></tr><tr><td><p>20</p></td><td><p>&#8211;11</p></td><td><p>0</p></td><td><p>41</p></td><td><p>0</p></td></tr><tr><td><p>21</p></td><td><p>&#8211;10</p></td><td><p>1</p></td><td><p>43</p></td><td><p>0</p></td></tr><tr><td><p>22</p></td><td><p>&#8211;9</p></td><td><p>25</p></td><td><p>54</p></td><td><p>0</p></td></tr><tr><td><p>23</p></td><td><p>&#8211;8</p></td><td><p>23</p></td><td><p>90</p></td><td><p>0</p></td></tr><tr><td><p>24</p></td><td><p>&#8211;7</p></td><td><p>24</p></td><td><p>125</p></td><td><p>0</p></td></tr><tr><td><p>25</p></td><td><p>&#8211;6</p></td><td><p>27</p></td><td><p>169</p></td><td><p>0</p></td></tr><tr><td><p>26</p></td><td><p>&#8211;5</p></td><td><p>68</p></td><td><p>195</p></td><td><p>0</p></td></tr><tr><td><p>27</p></td><td><p>&#8211;4</p></td><td><p>91</p></td><td><p>278</p></td><td><p>0</p></td></tr><tr><td><p>28</p></td><td><p>&#8211;3</p></td><td><p>89</p></td><td><p>306</p></td><td><p>0</p></td></tr><tr><td><p>29</p></td><td><p>&#8211;2</p></td><td><p>165</p></td><td><p>454</p></td><td><p>0</p></td></tr><tr><td><p>30</p></td><td><p>&#8211;1</p></td><td><p>173</p></td><td><p>385</p></td><td><p>0</p></td></tr><tr><td><p>31</p></td><td><p>0</p></td><td><p>240</p></td><td><p>490</p></td><td><p>0</p></td></tr><tr><td><p>32</p></td><td><p>1</p></td><td><p>280</p></td><td><p>533</p></td><td><p>0</p></td></tr><tr><td><p>33</p></td><td><p>2</p></td><td><p>320</p></td><td><p>380</p></td><td><p>3</p></td></tr><tr><td><p>34</p></td><td><p>3</p></td><td><p>357</p></td><td><p>228</p></td><td><p>22</p></td></tr><tr><td><p>35</p></td><td><p>4</p></td><td><p>356</p></td><td><p>261</p></td><td><p>63</p></td></tr><tr><td><p>36</p></td><td><p>5</p></td><td><p>303</p></td><td><p>279</p></td><td><p>63</p></td></tr><tr><td><p>37</p></td><td><p>6</p></td><td><p>330</p></td><td><p>229</p></td><td><p>175</p></td></tr><tr><td><p>38</p></td><td><p>7</p></td><td><p>326</p></td><td><p>269</p></td><td><p>162</p></td></tr><tr><td><p>39</p></td><td><p>8</p></td><td><p>348</p></td><td><p>233</p></td><td><p>259</p></td></tr><tr><td><p>40</p></td><td><p>9</p></td><td><p>335</p></td><td><p>230</p></td><td><p>360</p></td></tr><tr><td><p>41</p></td><td><p>10</p></td><td><p>315</p></td><td><p>243</p></td><td><p>428</p></td></tr><tr><td><p>42</p></td><td><p>11</p></td><td><p>215</p></td><td><p>191</p></td><td><p>430</p></td></tr><tr><td><p>43</p></td><td><p>12</p></td><td><p>169</p></td><td><p>146</p></td><td><p>503</p></td></tr><tr><td><p>44</p></td><td><p>13</p></td><td><p>151</p></td><td><p>150</p></td><td><p>444</p></td></tr><tr><td><p>45</p></td><td><p>14</p></td><td><p>105</p></td><td><p>97</p></td><td><p>384</p></td></tr><tr><td><p>46</p></td><td><p>15</p></td><td><p>74</p></td><td><p>61</p></td><td><p>294</p></td></tr><tr><td><p>Total hours:</p></td><td><p>4&#160;910</p></td><td><p>6&#160;446</p></td><td><p>3&#160;590</p></td></tr></tbody></table></div><p><br/></p><div><p><br/></p><p><span>Table 13</span></p><p><span>Average daytime temperature [&#176;C]</span></p><table><col/><col/><col/><col/><col/><col/><col/><col/><col/><col/><col/><col/><col/><tbody><tr><td><p>&#160;</p><div/></td><td><p>January</p></td><td><p>February</p></td><td><p>March</p></td><td><p>April</p></td><td><p>May</p></td><td><p>June</p></td><td><p>July</p></td><td><p>August</p></td><td><p>September</p></td><td><p>October</p></td><td><p>November</p></td><td><p>December</p></td></tr><tr><td><p>Average climate conditions</p></td><td><p>+2,8</p></td><td><p>+2,6</p></td><td><p>+7,4</p></td><td><p>+12,2</p></td><td><p>+16,3</p></td><td><p>+19,8</p></td><td><p>+21,0</p></td><td><p>+22,0</p></td><td><p>+17,0</p></td><td><p>+11,9</p></td><td><p>+5,6</p></td><td><p>+3,2</p></td></tr></tbody></table></div><p><br/></p><div><p><br/></p><p><span>Table 14</span></p><p><span>Average global solar irradiance [W/m<span>2</span>]</span></p><table><col/><col/><col/><col/><col/><col/><col/><col/><col/><col/><col/><col/><col/><tbody><tr><td><p>&#160;</p><div/></td><td><p>January</p></td><td><p>February</p></td><td><p>March</p></td><td><p>April</p></td><td><p>May</p></td><td><p>June</p></td><td><p>July</p></td><td><p>August</p></td><td><p>September</p></td><td><p>October</p></td><td><p>November</p></td><td><p>December</p></td></tr><tr><td><p>Average climate conditions</p></td><td><p>70</p></td><td><p>104</p></td><td><p>149</p></td><td><p>192</p></td><td><p>221</p></td><td><p>222</p></td><td><p>232</p></td><td><p>217</p></td><td><p>176</p></td><td><p>129</p></td><td><p>80</p></td><td><p>56</p></td></tr></tbody></table></div><p><br/></p><div><p><br/></p><p><span>Table 15</span></p><p><span>Water heating load profiles of combination heaters</span></p><table><col/><col/><col/><col/><col/><col/><col/><col/><col/><col/><col/><col/><col/><col/><tbody><tr><td><p>h</p></td><td><p><span>3XS</span></p></td><td><p><span>XXS</span></p></td><td><p><span>XS</span></p></td><td><p><span>S</span></p></td></tr><tr><td><p><span>Q<span>tap</span></span></p></td><td><p><span>f</span></p></td><td><p><span>T<span>m</span></span></p></td><td><p><span>Q<span>tap</span></span></p></td><td><p><span>f</span></p></td><td><p><span>T<span>m</span></span></p></td><td><p><span>Q<span>tap</span></span></p></td><td><p><span>f</span></p></td><td><p><span>T<span>m</span></span></p></td><td><p><span>Q<span>tap</span></span></p></td><td><p><span>f</span></p></td><td><p><span>T<span>m</span></span></p></td><td><p><span>T<span>p</span></span></p></td></tr><tr><td><p><span>kWh</span></p></td><td><p>l/min</p></td><td><p>&#176;C</p></td><td><p><span>kWh</span></p></td><td><p>l/min</p></td><td><p>&#176;C</p></td><td><p><span>kWh</span></p></td><td><p>l/min</p></td><td><p>&#176;C</p></td><td><p><span>kWh</span></p></td><td><p>l/min</p></td><td><p>&#176;C</p></td><td><p>&#176;C</p></td></tr><tr><td><p>07:00</p></td><td><p><span>0,015</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p><span>0,105</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>07:05</p></td><td><p><span>0,015</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>07:15</p></td><td><p><span>0,015</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>07:26</p></td><td><p><span>0,015</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>07:30</p></td><td><p><span>0,015</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p><span>0,105</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p><span>0,525</span></p></td><td><p>3</p></td><td><p>35</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>07:45</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>08:01</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>08:05</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>08:15</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>08:25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>08:30</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>08:45</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>09:00</p></td><td><p><span>0,015</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>09:30</p></td><td><p><span>0,015</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p><span>0,105</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>10:00</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>10:30</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>11:00</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>11:30</p></td><td><p><span>0,015</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p><span>0,105</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>11:45</p></td><td><p><span>0,015</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p><span>0,105</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>12:00</p></td><td><p><span>0,015</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p><span>0,105</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>12:30</p></td><td><p><span>0,015</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p><span>0,105</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>12:45</p></td><td><p><span>0,015</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p><span>0,105</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p><span>0,525</span></p></td><td><p>3</p></td><td><p>35</p></td><td><p><span>0,315</span></p></td><td><p>4</p></td><td><p>10</p></td><td><p>55</p></td></tr><tr><td><p>14:30</p></td><td><p><span>0,015</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>15:00</p></td><td><p><span>0,015</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>15:30</p></td><td><p><span>0,015</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>16:00</p></td><td><p><span>0,015</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>16:30</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>17:00</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>18:00</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>18:15</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>40</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>18:30</p></td><td><p><span>0,015</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p><span>0,105</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>19:00</p></td><td><p><span>0,015</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p><span>0,105</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>19:30</p></td><td><p><span>0,015</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p><span>0,105</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>20:00</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>20:30</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>1,05</span></p></td><td><p>3</p></td><td><p>35</p></td><td><p><span>0,42</span></p></td><td><p>4</p></td><td><p>10</p></td><td><p>55</p></td></tr><tr><td><p>20:45</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>20:46</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>21:00</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>21:15</p></td><td><p><span>0,015</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p><span>0,105</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>21:30</p></td><td><p><span>0,015</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>0,525</span></p></td><td><p>5</p></td><td><p>45</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>21:35</p></td><td><p><span>0,015</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p><span>0,105</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>21:45</p></td><td><p><span>0,015</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p><span>0,105</span></p></td><td><p>2</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p><span>Q<span>ref</span></span></p></td><td><p>0,345</p></td><td><p>2,100</p></td><td><p>2,100</p></td><td><p>2,100</p></td></tr></tbody></table></div><p><br/></p><div><p><br/></p><p><span>Continued Table 15</span></p><p><span>Water heating load profiles of combination heaters</span></p><table><col/><col/><col/><col/><col/><col/><col/><col/><col/><col/><col/><col/><col/><tbody><tr><td><p>h</p></td><td><p><span>M</span></p></td><td><p><span>L</span></p></td><td><p><span>XL</span></p></td></tr><tr><td><p><span>Q<span>tap</span></span></p></td><td><p><span>f</span></p></td><td><p><span>T<span>m</span></span></p></td><td><p><span>T<span>p</span></span></p></td><td><p><span>Q<span>tap</span></span></p></td><td><p><span>f</span></p></td><td><p><span>T<span>m</span></span></p></td><td><p><span>T<span>p</span></span></p></td><td><p><span>Q<span>tap</span></span></p></td><td><p><span>f</span></p></td><td><p><span>T<span>m</span></span></p></td><td><p><span>T<span>p</span></span></p></td></tr><tr><td><p><span>kWh</span></p></td><td><p>l/min</p></td><td><p>&#176;C</p></td><td><p>&#176;C</p></td><td><p><span>kWh</span></p></td><td><p>l/min</p></td><td><p>&#176;C</p></td><td><p>&#176;C</p></td><td><p><span>kWh</span></p></td><td><p>l/min</p></td><td><p>&#176;C</p></td><td><p>&#176;C</p></td></tr><tr><td><p>07:00</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>07:05</p></td><td><p><span>1,4</span></p></td><td><p>6</p></td><td><p>40</p></td><td><p>&#160;</p><div/></td><td><p><span>1,4</span></p></td><td><p>6</p></td><td><p>40</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>07:15</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>1,82</span></p></td><td><p>6</p></td><td><p>40</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>07:26</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>07:30</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>07:45</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p><span>4,42</span></p></td><td><p>10</p></td><td><p>10</p></td><td><p>40</p></td></tr><tr><td><p>08:01</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>08:05</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>3,605</span></p></td><td><p>10</p></td><td><p>10</p></td><td><p>40</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>08:15</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>08:25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>08:30</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>08:45</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>09:00</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>09:30</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>10:00</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>10:30</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>10</p></td><td><p>40</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>10</p></td><td><p>40</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>10</p></td><td><p>40</p></td></tr><tr><td><p>11:00</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>11:30</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>11:45</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>12:00</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>12:30</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>12:45</p></td><td><p><span>0,315</span></p></td><td><p>4</p></td><td><p>10</p></td><td><p>55</p></td><td><p><span>0,315</span></p></td><td><p>4</p></td><td><p>10</p></td><td><p>55</p></td><td><p><span>0,735</span></p></td><td><p>4</p></td><td><p>10</p></td><td><p>55</p></td></tr><tr><td><p>14:30</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>15:00</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>15:30</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>16:00</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>16:30</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>17:00</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>18:00</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>18:15</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>40</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>40</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>40</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>18:30</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>40</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>40</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>40</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>19:00</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>19:30</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>20:00</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>20:30</p></td><td><p><span>0,735</span></p></td><td><p>4</p></td><td><p>10</p></td><td><p>55</p></td><td><p><span>0,735</span></p></td><td><p>4</p></td><td><p>10</p></td><td><p>55</p></td><td><p><span>0,735</span></p></td><td><p>4</p></td><td><p>10</p></td><td><p>55</p></td></tr><tr><td><p>20:45</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>20:46</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>4,42</span></p></td><td><p>10</p></td><td><p>10</p></td><td><p>40</p></td></tr><tr><td><p>21:00</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>3,605</span></p></td><td><p>10</p></td><td><p>10</p></td><td><p>40</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>21:15</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>21:30</p></td><td><p><span>1,4</span></p></td><td><p>6</p></td><td><p>40</p></td><td><p>&#160;</p><div/></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td><td><p><span>4,42</span></p></td><td><p>10</p></td><td><p>10</p></td><td><p>40</p></td></tr><tr><td><p>21:35</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>21:45</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p><span>Q<span>ref</span></span></p></td><td><p>5,845</p></td><td><p>11,655</p></td><td><p>19,07</p></td></tr></tbody></table></div><p><br/></p><div><p><br/></p><p><span>Continued Table 15</span></p><p><span>Water heating load profiles of combination heaters</span></p><table><col/><col/><col/><col/><col/><tbody><tr><td><p>h</p></td><td><p><span>XXL</span></p></td></tr><tr><td><p><span>Q<span>tap</span></span></p></td><td><p><span>f</span></p></td><td><p><span>T<span>m</span></span></p></td><td><p><span>T<span>p</span></span></p></td></tr><tr><td><p><span>kWh</span></p></td><td><p>l/min</p></td><td><p>&#176;C</p></td><td><p>&#176;C</p></td></tr><tr><td><p>07:00</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>07:05</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>07:15</p></td><td><p><span>1,82</span></p></td><td><p>6</p></td><td><p>40</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>07:26</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>07:30</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>07:45</p></td><td><p><span>6,24</span></p></td><td><p>16</p></td><td><p>10</p></td><td><p>40</p></td></tr><tr><td><p>08:01</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>08:05</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>08:15</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>08:25</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>08:30</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>08:45</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>09:00</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>09:30</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>10:00</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>10:30</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>10</p></td><td><p>40</p></td></tr><tr><td><p>11:00</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>11:30</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>11:45</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>12:00</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>12:30</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>12:45</p></td><td><p><span>0,735</span></p></td><td><p>4</p></td><td><p>10</p></td><td><p>55</p></td></tr><tr><td><p>14:30</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>15:00</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>15:30</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>16:00</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>16:30</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>17:00</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>18:00</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>18:15</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>40</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>18:30</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>40</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>19:00</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>19:30</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>20:00</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>20:30</p></td><td><p><span>0,735</span></p></td><td><p>4</p></td><td><p>10</p></td><td><p>55</p></td></tr><tr><td><p>20:45</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>20:46</p></td><td><p><span>6,24</span></p></td><td><p>16</p></td><td><p>10</p></td><td><p>40</p></td></tr><tr><td><p>21:00</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>21:15</p></td><td><p><span>0,105</span></p></td><td><p>3</p></td><td><p>25</p></td><td><p>&#160;</p><div/></td></tr><tr><td><p>21:30</p></td><td><p><span>6,24</span></p></td><td><p>16</p></td><td><p>10</p></td><td><p>40</p></td></tr><tr><td><p>21:35</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p>21:45</p></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td><td><p>&#160;</p><div/></td></tr><tr><td><p><span>Q<span>ref</span></span></p></td><td><p>24,53</p></td></tr></tbody></table></div></td></tr></table>
ANNEX VIII
Product compliance verification by market surveillance authorities
The verification tolerances set out in this Annex relate only to the verification of the measured parameters by Member State authorities and shall not be used by the supplier as an allowed tolerance to establish the values in the technical documentation. The values and classes on the label or in the product fiche shall not be more favourable for the supplier than the values reported in the technical documentation.
When verifying the compliance of a product model with the requirements laid down in this Delegated Regulation, for the requirements referred to in this Annex, the authorities of the Member States shall apply the following procedure:
(1) The Member State authorities shall verify one single unit of the model.
(2) The model shall be considered to comply with the applicable requirements if:
(a) the values given in the technical documentation pursuant to Article 5(b) of Directive 2010/30/EU (declared values), and, where applicable, the values used to calculate these values, are not more favourable for the supplier than the corresponding values given in the test reports pursuant to point (iii) of the abovementioned Article; and
(b) the values published on the label and in the product fiche are not more favourable for the supplier than the declared values, and the indicated energy efficiency class is not more favourable for the supplier than the class determined by the declared values; and
(c) when the Member State authorities test the unit of the model, the determined values (the values of the relevant parameters as measured in testing and the values calculated from these measurements) comply with the respective verification tolerances as given in Table 16.
(3) If the results referred to in points 2(a) or (b) are not achieved, the model shall be considered not to comply with this Delegated Regulation.
(4) If the result referred to in point 2(c) is not achieved, the Member State authorities shall select three additional units of the same model for testing.
(5) The model shall be considered to comply with the applicable requirements if for these three units, the arithmetical mean of the determined values complies with the respective tolerances given in Table 16.
(6) If the result referred to in point 5 is not achieved, the model shall be considered not to comply with this Delegated Regulation.
(7) The Member State authorities shall provide all relevant information to the authorities of the other Member States and to the Commission without delay after a decision being taken on the non-compliance of the model according to points 3 and 6.
The Member State authorities shall use the measurement and calculation methods set out in Annex VII.
The Member State authorities shall only apply the verification tolerances that are set out in Table 16 and shall only use the procedure described in points 1 to 7 for the requirements referred to in this Annex. No other tolerances, such as those set out in harmonised standards or in any other measurement method, shall be applied.
Table 16
Verification tolerances
<table><col/><col/><tbody><tr><td><p>Parameters</p></td><td><p>Verification tolerances</p></td></tr><tr><td><p>Space-heating energy efficiency,<span>&#951;<span>s</span></span></p></td><td><p>The determined value shall not be lower than the declared value by more than 8 %.</p></td></tr><tr><td><p>Water-heating energy efficiency,<span>&#951;<span>wh</span></span></p></td><td><p>The determined value shall not be lower than the declared value by more than 8 %.</p></td></tr><tr><td><p>Sound power level</p></td><td><p>The determined value shall not exceed the declared value by more than 2 dB(A).</p></td></tr><tr><td><p>Class of the temperature control</p></td><td><p>The class of the temperature controls corresponds to the declared class of the unit.</p></td></tr><tr><td><p>Collector efficiency,<span>&#951;<span>col</span></span></p></td><td><p>The determined value shall not be lower than the declared value by more than 5 %.</p></td></tr><tr><td><p>Standing loss,<span>S</span></p></td><td><p>The determined value shall not exceed the declared value by more than 5 %.</p></td></tr><tr><td><p>Auxiliary electricity consumption,<span>Q<span>aux</span></span></p></td><td><p>The determined value shall not exceed the declared value by more than 5 %.</p></td></tr></tbody></table>
ANNEX IX
Information to be provided in the case of sale, hire or hire-purchase through the internet
(1) For the purpose of points 2 to 5 of this Annex the following definitions shall apply:
(a) ‘display mechanism’ means any screen, including tactile screen, or other visual technology used for displaying internet content to users;
(b) ‘nested display’ means visual interface where an image or data set is accessed by a mouse click, mouse roll-over or tactile screen expansion of another image or data set;
(c) ‘tactile screen’ means a screen responding to touch, such as that of a tablet computer, slate computer or a smartphone;
(d) ‘alternative text’ means text provided as an alternative to a graphic allowing information to be presented in non-graphical form where display devices cannot render the graphic or as an aid to accessibility such as input to voice synthesis applications.
(2) The appropriate label made available by suppliers in accordance with Article 3 or in the case of a package where appropriate duly filled in based on the label and fiches provided by suppliers in accordance with Article 3, shall be shown on the display mechanism in proximity to the price of the product or package in accordance with the timetable set out in Article 3. If both a product and a package are shown, but with a price indicated only for the package, only the package label shall be displayed. The size shall be such that the label is clearly visible and legible and shall be proportionate to the size specified in Annex III. The label may be displayed using a nested display, in which case the image used for accessing the label shall comply with the specifications laid down in point 3 of this Annex. If nested display is applied, the label shall appear on the first mouse click, mouse roll-over or tactile screen expansion on the image.
(3) The image used for accessing the label in the case of nested display shall:
(a) be an arrow in the colour corresponding to the energy efficiency class of the product or package on the label;
(b) indicate on the arrow the energy efficiency class of the product or package in white in a font size equivalent to that of the price; and
(c) have one of the following two formats:
(4) In the case of nested display, the sequence of display of the label shall be as follows:
(a) the image referred to in point 3 of this Annex shall be shown on the display mechanism in proximity to the price of the product or package;
(b) the image shall link to the label;
(c) the label shall be displayed after a mouse click, mouse roll-over or tactile screen expansion on the image;
(d) the label shall be displayed by pop up, new tab, new page or inset screen display;
(e) for magnification of the label on tactile screens, the device conventions for tactile magnification shall apply;
(f) the label shall cease to be displayed by means of a close option or other standard closing mechanism;
(g) the alternative text for the graphic, to be displayed on failure to display the label, shall be the energy efficiency class of the product or package in a font size equivalent to that of the price.
<note>
(5) The appropriate product fiche made available by suppliers in accordance with Article 3 shall be shown on the display mechanism in proximity to the price of the product or package. The size shall be such that the product fiche is clearly visible and legible. The product fiche may be displayed using a nested display, in which case the link used for accessing the fiche shall clearly and legibly indicate ‘Product fiche’. If nested display is used, the product fiche shall appear on the first mouse click, mouse roll-over or tactile screen expansion on the link.
( 1 ) OJ L 334, 17.12.2010, p. 17.
( 2 ) OJ L 315, 14.11.2012, p. 1.
( 3 ) OJ L 390, 31.12.2004, p. 24.
( 4 ) OJ L 27, 30.1.2010, p. 1.
</note>