Patent Number: 
Section: claims

1. A nuclear power plant (NPP) containment building separation system configured to divide an NPP containment building into isolated containment building rooms, the containment building separation system configured to be installed on a floor slab between the containment building rooms, and the containment building separation system configured to be at least partly located in a circular gap between the floor slab and a containment building wall, the containment building separation system comprising:at least one isolating valve configured to ensure insulation of (i) a first airspace in a first room of the containment building rooms from (ii) a second airspace in a second room of the containment building rooms, and the at least one isolating valve configured to connect the first airspace and the second airspace in the containment building rooms following a possible pressure drop;a manifold ring connected to each valve of the at least one isolating valve in the containment building separation system;an air supply unit connected to the manifold ring and configured to supply air to the manifold ring; andwherein each valve of the at least one isolating valve is designed as an air-inflated shutter configured: (i) to provide insulation of the first airspace from the second airspace inside the containment building rooms when inflated, (ii) to connect the first airspace and the second airspace when deflated and (iii) to bend in the direction of a lower pressure room following the possible pressure drop, the lower pressure room being selected from the group of rooms consisting of the first room and the second room, and the lower pressure room being the room in the group of rooms where pressure is lower. 2. A containment building separation system according to claim 1, the at least one isolating valve comprising a plurality of isolating valves, the containment building separation system comprising support structure elements configured to be installed on the floor slab dividing the first room and the second room from each other, each of the air-inflated shutters being attached to a corresponding support structure element of the support structure elements. 3. A containment building separation system according to claim 1, wherein the at least one isolating valve comprises a plurality of isolating valves, and wherein the air-inflated shutters adjoin to each other. 4. A containment building separation system according to claim 1, wherein the air supply unit comprises a blower fan or an air blower, and wherein the containment building separation system is configured so that the air from the air supply unit is supplied via ft the blower fan or the air blower. 5. A containment building separation system according to claim 1, comprising at least two air supply units. 6. A containment building separation system according to claim 1, comprising a return valve installed at the outlet of the air supply unit. 7. A containment building separation system according to claim 1, comprising pressure transmitters and a control module for the air supply unit, the pressure transmitters configured to be located in at least one room inside the NPP containment building; the pressure transmitters connected to the control module; and the control module connected to the air supply unit. 8. A containment building separation system according to claim 1, wherein the at least one isolating valve comprises a plurality of isolating valves, and wherein the manifold ring is a circular pipe connected to each of the air-inflated shutters. 9. A containment building separation system according to claim 1, comprising a continuously operating pressure relief nozzle, wherein the manifold ring is equipped with the continuously operating pressure relief nozzle. 10. A containment building separation system according to claim 1, wherein the at least one isolating valve comprises a plurality of isolating valves, and wherein the air-inflated shutters are made of fabric. 11. A containment building separation system according to claim 10, wherein the air-inflated shutters are made of resin-coated fabric.