Patent Number: 
Section: claims

1. A steam generating unit of dual circuit reactor with blowdown and drain system, comprising:four identical horizontally arranged steam generators enclosed into a protection tight volume,each steam generator having hot and cold headers of a primary circuit with pockets and salt compartment;each steam generator being connected to a steam header, feed water supply pipeline, and blowdown lines;each steam generator being connected to the blowdown lines from the salt compartment, from a lower part of the steam generator and from said pockets of the primary circuit headers;wherein all the blowdown lines of each steam generator are combined into a single blowdown header of a steam generator with further combination into a common blowdown header of the steam generators that is connected to an inlet of a regenerative heat exchanger;wherein a discharge line of the regenerative heat exchanger is connected to a blowdown aftercooler; anda discharge line of the blowdown aftercooler is taken out of the protection tight volume and connected to an active water treatment system; and the active water treatment system being equipped with a discharge line of a treated blowdown water of the steam generators connected with at least, one treated blowdown water pump which is further equipped with a pressure line being brought into the protection tight volume and connected to an inlet of an intertubular space of the regenerative heat exchanger;wherein an outlet of the intertubular space of the regenerative heat exchanger is connected to the feed water supply pipelines of the steam generators via a common pipeline for the treated blowdown water supply and pipelines for treated blowdown water supply of each steam generator. 2. The unit according to claim 1, wherein the discharge line of the blowdown aftercooler outside the protection tight volume, is provided with a steam generator drain and discharge pipeline connected to a water drain tank. 3. The unit according to claim 1, wherein the discharge line of the treated blowdown water of the steam generators is provided with three pumps—an operating pump, a standby pump and a repair pump.