Source: https://www.law.cornell.edu/cfr/text/10/appendix-T_to_subpart_B_of_part_430
Timestamp: 2017-04-26 23:50:14
Document Index: 139866243

Matched Legal Cases: ['art 430', 'art 430', 'art_430', 'art 430', '§ 430', '§ 430', '§ 430', '§ 430', '§ 430', '§ 430']

10 CFR Appendix T to Subpart B of Part 430, Uniform Test Method for Measuring the Water Consumption of Water Closets and Urinals | US Law | LII / Legal Information Institute
CFR › Title 10 › Chapter II › Subchapter D › Part 430 › Subpart B › Appendix T_to_subpart_B_of_part_430 10 CFR Appendix T to Subpart B of Part 430, Uniform Test Method for Measuring the Water Consumption of Water Closets and Urinals
1. Scope: This appendix covers the test requirements used to measure the hydraulic performances of water closets and urinals.
a. The test apparatus and instructions for testing water closets shall conform to the requirements specified in section 7.1, General, sub sections 7.1.1, 7.1.2, 7.1.3, 7.1.4, and 7.1.5 of ASME A112.19.2-2008 (incorporated by reference, see § 430.3). The flushometer valve used in the water consumption test shall represent the maximum design flush volume of the water closet. Measurements shall be recorded at the resolution of the test instrumentation. Calculations of water consumption for each tested unit shall be rounded off to the same number of significant digits as the previous step.
b. The test apparatus and instructions for testing urinals shall conform to the requirements specified in section 8.2, Test Apparatus and General Instructions, sub sections 8.2.1, 8.2.2, and 8.2.3 of ASME A112.19.2-2008 (incorporated by reference, see § 430.3). The flushometer valve used in the water consumption test shall represent the maximum design flush volume of the urinal. Measurements shall be recorded at the resolution of the test instrumentation. Calculations of water consumption for each tested unit shall be rounded off to the same number of significant digits as the previous step.
(i) The measurement of the water flush volume for water closets, expressed in gallons per flush (gpf) and liters per flush (Lpf), shall be conducted in accordance with the test requirements specified in section 7.4, Water Consumption Test, of ASME A112.19.2-2008 (incorporated by reference, see § 430.3). For dual-flush water closets, the measurement of the water flush volume shall be conducted separately for the full-flush and reduced-flush modes and in accordance with the test requirements specified section 7.4, Water Consumption Test, of ASME A112.19.2-2008.
(ii) Static pressure requirements: The water consumption tests of siphonic and blowout water closets shall be conducted at two static pressures. For flushometer valve water closets with a siphonic bowl, the test pressures shall be 80 psi and 35 psi. For flushometer valve water closets with a blowout bowl, the test pressures shall be 80 psi and 45 psi. The test shall be run three times at each pressure as specified in section 7.4.3 “Procedure,” of ASME A112.19.2-2008 (incorporated by reference, see § 430.3). The final measured flush volume for each tested unit shall be the average of the total flush volumes recorded at each test pressure as specified in section 7.4.5 “Performance,” of ASME A112.19.2-2008.
(iii) Flush volume and tank trim component adjustments: For gravity flush tank water closets, trim components that can be adjusted to cause an increase in flush volume, including (but not limited to) the flapper valve, fill valve, and tank water level, shall be set in accordance with the printed installation instructions supplied by the manufacturer. If the installation instructions for the model to be tested do not specify trim setting adjustments, these trim components shall be adjusted to the maximum water use setting so that the maximum flush volume is produced without causing the water closet to malfunction or leak. The water level in the tank shall be set to the maximum water line designated in the printed installation instructions supplied by the manufacturer or the designated water line on the tank itself, whichever is higher. If the printed installation instructions or the water closet tank do not indicate a water level, the water level shall be adjusted to 1±0.1 inches below the top of the overflow tube or 1±0.1 inches below the top rim of the water-containing vessel (for gravity flush tank water closets that do not contain an overflow tube) for each designated pressure specified in Table 5 of ASME A112.19.2-2008 (incorporated by reference, see § 430.3).
b. Urinals - The measurement of water flush volume for urinals, expressed in gallons per flush (gpf) and liters per flush (Lpf), shall be conducted in accordance with the test requirements specified in section 8.6, Water Consumption Test, of ASME A112.19.2-2008 (incorporated by reference, see § 430.3). The final measured flush volume for each tested unit shall be the average of the total flush volumes recorded at each test pressure as specified in section 8.6.4 “Performance,” of ASME A112.19.2-2008.
[ 63 FR 13317, Mar. 18, 1998, as amended at 78 FR 62987, Oct. 23, 2013]