Source: https://www.ada.gov/kanawhawvattk.htm
Timestamp: 2018-08-15 07:51:31
Document Index: 736777006

Matched Legal Cases: ['§ 35', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 35', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 7', '§ 7', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 7', '§ 4', '§ 7', '§ 7', '§ 7', '§ 4', '§ 7', '§ 7', '§ 4', '§ 7', '§ 4', '§ 7', '§ 4', '§ 4', '§ 4', '§ 4', '§ 35', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4']

Settlement Agreement between the United States and and Kanawha County, West Virginia, Attachment (K)
Attachment K – Existing Facilities
1. Please Note: Paragraph 51 of the Settlement Agreement requires that within three months of the effective date of this Agreement, the County provide signage as necessary to comply with 28 C.F.R. § 35.163(b), after having surveyed all facilities that are the subject of this Agreement for the purpose of identifying those that have multiple entrances not all of which are accessible.
2. Within 12 months of the effective date of this Agreement, the County will complete the following modifications to Patchwork, located at 1583 Lee Street, One United Way Square, Charleston.
1) The route from the sidewalk to the sleeping area has changes in direction that do not comply with Figure 7. Provide at least one accessible route within the boundary of the site connecting these elements that, to the maximum extent feasible, coincides with the route for the general public. The accessible route must have a minimum clear width of 36 inches, or a minimum clear width of 42 inches if there is a turn around an obstruction less than 48 inches wide; have passing spaces at least 60 inches by 60 inches at least every 200 feet; have a minimum clear headroom of 80 inches; have a surface that is firm, stable, and slip resistant; have, in the absence of a curb ramp, ramp, elevator, or platform lift, no level changes in excess of ½ inch vertically; and have a running slope of less than 1:20 (5%) (or have been constructed as a fully accessible ramp) and a cross slope of less than 1:50 (2%). Standards §§ 4.3, 4.5, Fig. 7.
B. Ramp (Back Entrance)
1) The ramp is inaccessible because there is inadequate space at the change in direction, the handrails do not comply with the Standards, and the ramp lacks edge protection. Provide a ramp that is at least 36 inches wide with a slope not exceeding 1:12 and a cross slope not exceeding 1:50; with level landings at least as wide as the ramp and 60 inches long at the top and bottom of the ramp; with level landings measuring at least 60 inches by 60 inches when the ramp changes direction; and edge protection that is at least 2 inches high at the drop off sides. Provide handrails that are between 1¼ inches and 1½ inches in diameter such that the inside handrail is continuous and both handrails have a continuous gripping surface along both sides of the ramp extending at least 12 inches beyond the top and bottom of the ramp parallel with the ground surface; the handrails do not rotate within their fittings; and both handrails are mounted between 34 inches and 38 inches above the ramp surface, with ends rounded or returned smoothly to the floor, wall, or post. Ensure that the ramp and approaches are designed so that water will not accumulate on walking surfaces. Standards §§ 4.3.8, 4.8.
C. Exterior Entrances
1) The building is inaccessible because there is no accessible signage at the inaccessible entrance directing people with disabilities to the accessible entrance and no accessible signage at the accessible entrance. Provide accessible directional signage with the International Symbol of Accessibility at inaccessible entrances directing users to the accessible entrance, and provide accessible signage with the International Symbol of Accessibility at all permanent accessible entrances. Standards §§ 4.1.3(8)(d), 4.13, 4.30.
2) The door opening is 29½ inches wide. Provide a door with a clear opening of 32 inches with the door open 90 degrees, measured between the face of the door and the opposite stop. Standards § 4.13.5, Fig. 24.
3) The door is inaccessible because there is excessive change in level at the threshold and the threshold is not beveled. Provide an accessible door with a threshold that is no greater than ¼ inch, or is no greater than ½ inch and is beveled with a slope no greater than 1:2. Standards §§ 4.13.8, 4.5.2.
4) The door is inaccessible because knob hardware is used. Provide a door with hardware that is easy to grasp with one hand and that does not require tight grasping, pinching, or twisting of the wrist to operate. Lever-operated mechanisms, push-type mechanisms, and U-shaped handles are acceptable designs. Standards § 4.13.9.
D. Unisex, Single-user Toilet Room
1) The toilet room lacks accessible signage. Provide a toilet room sign with the International Symbol of Accessibility and raised and Braille characters. The sign shall be mounted on the wall adjacent to the latch side of the door with the centerline of the sign at 60 inches above the finished floor and situated such that a person can approach within 3 inches of the sign without encountering an obstruction or standing within a door swing. Standards §§ 4.1.2(7)(d), 4.30.1, 4.30.4, 4.30.5, 4.30.6, 4.30.7.
3) The bottom of the lavatory apron is 27 inches above the finished floor. Provide a lavatory with the top of its rim or counter 34 inches or less above the finished floor; the bottom edge of the apron at least 29 inches above the finished floor; and knee and toe clearances that comply with Fig. 31. Standards § 4.19.2, Fig. 31.
5) The top of the toilet seat is 15½ inches above the finished floor. Provide a toilet with a seat that measures 17 to 19 inches above the finished floor. Standards § 4.16.3, Fig. 29(b).
6) The toilet is inaccessible because the flush control is on the closed side. Provide a flush control mounted on the “open” side of the toilet’s clear floor space; 44 inches or less above the finished floor; and requiring a maximum of 5 pounds of force to operate; or provide an automatic flush device. Standards §§ 4.16.5, 4.27.4.
7) The side grab bar at the toilet is inaccessible because it is mounted at a diagonal, the distance of its further end to the rear wall is 46 inches, there are items interfering with its use, and the height ranges between 21 and 42 inches above the finished floor. Provide a side grab bar that is at least 42 inches in overall length, with the far end mounted at least 54 inches from the rear wall and the closer end 12 inches or less from the rear wall; mounted 33 to 36 inches above the finished floor; with a diameter between 1¼ and 1½ inches; with 1½ inches between the grab bar and the wall; and at least 1½ inches between the grab bar and any other object, such as the toilet paper dispenser. Standards §§ 4.16.4, 4.26.2, Fig. 29.
8) No rear grab bar is provided. Provide a rear grab bar that is at least 36 inches in overall length, with the closer end no more than 6 inches from the side wall; mounted 33 to 36 inches above the finished floor; with a diameter between 1¼ and 1½ inches; with 1½ inches between the grab bar and the wall; and at least 1½ inches between the grab bar and any other object, such as a toilet seat cover dispenser. Standards §§ 4.16.4, 4.26.2, Fig. 29.
E. Shower Stall
1) The shower stall is 30 inches deep by 33 inches wide. Provide a shower in this room that is exactly 36 inches wide and 36 inches deep with a 48 inch long and 36 inch wide clear floor space alongside the shower opening, and an L-shaped shower seat mounted on the wall opposite the controls and extending the full depth of the stall; OR a shower that is at least 30 inches deep and 60 inches wide with no curb or threshold and with a 36 inch deep and 60 inch wide clear floor space at the shower opening. Ensure that the shower has grab bars, controls, a shower spray unit, and a seat, curb, and enclosure, if provided, that comply fully with the Standards and with Figs. 35, 36, and 37, as applicable. Standards § 4.21, Figs. 35, 36, 37.
3. Within 6 months of the effective date of the Agreement, the County will complete the following modifications to Dunbar Athletic Boosters, located at 2605 Charles Avenue, Dunbar.
1) The van accessible parking reserved for persons with disabilities lacks the appropriate signage. At van accessible spaces, provide a “Van-Accessible” sign located below the International Symbol of Accessibility such that the sign cannot be obstructed by vehicles parked in the space. Standards §§ 4.6.4, 4.30.7(1).
2) The signage designating parking as reserved for persons with disabilities is too low. At each space designated as reserved for persons with disabilities, provide a vertical sign with the International Symbol of Accessibility located such that it cannot be obstructed by vehicles parked in the space. Standards §§ 4.6.4, 4.30.7(1).
3) The parking reserved for persons with disabilities is inaccessible because the spaces are not level. Provide designated accessible parking spaces and access aisles that are flat and level, with slopes and cross-slopes not exceeding 1:50 in all directions, with surfaces that are firm, stable, and slip-resistant. Standards §§ 4.3.6, 4.5.1, 4.6.3.
4) The parking lot is inaccessible because there are no access aisles. At each standard accessible space, provide an access aisle at least 60 inches wide. At each van accessible space, provide an access aisles at least 96 inches wide. Ensure that all access aisles are flat and level, with slopes and cross-slopes not exceeding 1:50 in all directions, and that their surfaces are firm, stable, and slip-resistant. Standards §§ 4.1.2(5), 4.6.3, Fig. 9.
B. Women’s Toilet Rooms with Stalls
2) The door, which is accessed through a front approach, is inaccessible because it lacks sufficient maneuvering clearance on the pull side. On the pull side of the door, provide maneuvering clearance at least 60 inches deep and provide a minimum of 18 inches (24 inches is preferred) of maneuvering clearance on the latch side of the door. Standards § 4.13.6, Fig. 25(a).
4) The paper towel dispenser is inaccessible because the controls are mounted 54 inches above the finished floor and require a forward reach. Provide a paper towel dispenser with the controls a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
5) The toilet is inaccessible because its centerline measures 31 inches from the side wall. Provide a toilet with a centerline that measures 18 inches from the near side wall. Standards § 4.17.3, Fig. 30.
6) The rear grab bar at the toilet is inaccessible because the closer end is mounted 9 inches from the side wall. Provide a rear grab bar that is at least 36 inches in overall length, with the closer end no more than 6 inches from the side wall; mounted 33 to 36 inches above the finished floor; with a diameter between 1¼ and 1½ inches; with 1½ inches between the grab bar and the wall; and at least 1½ inches between the grab bar and any object beside or below it and at least 18 inches between the grab bar and any object above it. Standards §§ 4.17.6, 4.26.2, Figs. 30, 39.
8) The toilet paper dispenser is inaccessible because it is not mounted under the side grab bar. Provide a toilet paper dispenser that is mounted with its top at least 1½ inches under the side grab bar and 36 inches or less from the rear wall and is centered at least 19 inches above the finished floor. Standards § 4.17.3, Fig. 30(d).
3) The lavatory is inaccessible because the hardware requires twisting of the wrist to operate. Provide a lavatory with a faucet that can be operated with 5 pounds of force or less and can be used with one hand and without tight grasping, pinching, or twisting of the wrist (lever-operated, push-type, and electronically controlled mechanisms are examples of acceptable designs). Standards §§ 4.19.5, 4.27.4.
5) The toilet is inaccessible because its centerline measures 30 inches from the side wall. Provide a toilet with a centerline that measures 18 inches from the near side wall. Standards § 4.17.3, Fig. 30.
6) The rear grab bar at the toilet is inaccessible because the closer end is mounted 11 inches from the side wall. Provide a rear grab bar that is at least 36 inches in overall length, with the closer end no more than 6 inches from the side wall; mounted 33 to 36 inches above the finished floor; with a diameter between 1¼ and 1½ inches; with 1½ inches between the grab bar and the wall; and at least 1½ inches between the grab bar and any object beside or below it and at least 18 inches between the grab bar and any object above it. Standards §§ 4.17.6, 4.26.2, Figs. 30, 39.
7) The toilet paper dispenser is inaccessible because it is not mounted under the side grab bar. Provide a toilet paper dispenser that is mounted with its top at least 1½ inches under the side grab bar and 36 inches or less from the rear wall and is centered at least 19 inches above the finished floor. Standards § 4.17.3, Fig. 30(d).
1) The telephone is inaccessible because it lacks volume control and is not hearing aid compatible. Provide an accessible telephone with a clear floor space of at least 30 inches by 48 inches that allows either a forward or parallel approach by a person using a wheelchair such that bases, enclosures, and fixed seats do not impede approaches to the telephone; with the highest operable part of the telephone mounted no more than 48 inches above the floor for a front approach or no more than 54 inches above the floor for a side approach; that is hearing aid compatible and has a volume control mechanism; with telephone books, if provided, located between 15 and 48 inches above the finished floor for a front approach or between 9 and 54 inches above the finished floor for a side approach; with a cord of at least 29 inches long from the telephone to the handset; and with signage that complies with the Standards. Standards §§ 4.31, 4.30.7(2).
1) The drinking fountain has a spout that is 39 inches above the finished floor. Provide a fountain that has a spout height no higher than 36 inches, measured from the finished floor or ground surface to the spout outlet, and that otherwise complies with the Standards. Alternatively, provide a fountain accessible to people who use wheelchairs and a cup dispenser, or by such other means as would achieve the required accessibility. Standards §§ 4.1.3(10)(a), 4.15, 4.27.4, Fig. 27.
2) The drinking fountain is inaccessible because the knee space width measures 17¼ inches and the knee space depth measures 6½ inches. Provide a drinking fountain with clear knee space between the bottom of the apron and the finished floor or ground of at least 27 inches high, 30 inches wide, and 17 to 19 inches deep; and a minimum clear floor space of 30 inches by 48 inches to allow a person in a wheelchair to approach the unit facing forward. Standards § 4.15.5(1), Figs. 27(a), (b).
4. Except as noted, within 6 months of the effective date of the Agreement, the County will complete the following modifications to Kanawha-Charleston Board of Health, located at 108 Lee Street, Charleston.
1) Although the front parking lot has a total of 15 parking spaces, there is no van accessible parking space. On the shortest accessible route to the accessible entrance, provide 1 van accessible space designated as reserved for people with disabilities. Ensure that van accessible spaces are a minimum of 96 inches wide and served by access aisles at least 96 inches wide. At all spaces designated as reserved for persons with disabilities, provide vertical signs with the International Symbol of Accessibility located such that they cannot be obstructed by parked vehicles. At van accessible spaces, provide an additional “Van-Accessible” sign located below the International Symbol of Accessibility. Ensure that all spaces and access aisles for persons with disabilities are flat and level, with slopes and cross-slopes not exceeding 1:50 in all directions, and that their surfaces are firm, stable, and slip-resistant. Standards §§ 4.1.2(5), 4.6, 4.30.7(1).
2) Although the rear parking lot has a total of 40 parking spaces, there is no van accessible parking space and the standard accessible space lacks signage. On the shortest accessible route to the accessible entrance, provide 1 van accessible space and 1 standard space designated as reserved for people with disabilities. Ensure that standard accessible spaces are a minimum of 96 inches wide and served by access aisles at least 60 inches wide. Ensure that van accessible spaces are a minimum of 96 inches wide and served by access aisles at least 96 inches wide. At all spaces designated as reserved for persons with disabilities, provide vertical signs with the International Symbol of Accessibility located such that they cannot be obstructed by parked vehicles. At van accessible spaces, provide an additional “Van-Accessible” sign located below the International Symbol of Accessibility. Ensure that all spaces and access aisles for persons with disabilities are flat and level, with slopes and cross-slopes not exceeding 1:50 in all directions, and that their surfaces are firm, stable, and slip-resistant. Standards §§ 4.1.2(5), 4.6, 4.30.7(1).
1) Along the accessible route from the parking to the front entrance, there is a hole in the pavement in front of the exterior entrance door. Provide at least one accessible route within the boundary of the site connecting these elements that, to the maximum extent feasible, coincides with the route for the general public. The accessible route must have a minimum clear width of 36 inches, or a minimum clear width of 42 inches if there is a turn around an obstruction less than 48 inches wide; have passing spaces at least 60 inches by 60 inches at least every 200 feet; have a minimum clear headroom of 80 inches; have a surface that is firm, stable, and slip resistant; have, in the absence of a curb ramp, ramp, elevator, or platform lift, no level changes in excess of ½ inch vertically; and have a running slope of less than 1:20 (5%) (or have been constructed as a fully accessible ramp) and a cross slope of less than 1:50 (2%). Standards §§ 4.3, 4.5, Fig. 7.
2) The curb cut does not have flared sides. Provide a curb ramp that is at least 36 inches wide, has a maximum slope of 1:12, is located so that it cannot be obstructed by parked vehicles, and has a stable, firm, and slip-resistant surface with a detectable warning extending the full width and depth of the ramp. If the curb ramp is located where pedestrians must walk across it, provide either flared sides (with a maximum slope of 1:10) or handrails or guardrails to protect against cross traffic. Standards § 4.3.8, 4.7, Fig. 12.
3) The rear ramp is inaccessible because it lacks edge protection. Provide edge protection at least 2 inches high at the drop off sides. Standards § 4.8.7.
4) The ramp is inaccessible because the handrails are not continuous. Provide handrails that are between 1¼ inches and 1½ inches in diameter with a continuous gripping surface along both sides of the ramp, extending at least 12 inches beyond the top and bottom of the ramp parallel with the ground surface. Ensure that handrails are mounted between 34 inches and 38 inches above the ramp surface and 1½ inches from the wall, with ends rounded or returned smoothly to the floor, wall, or post, and that they do not rotate within their fittings. Standards § 4.8.5.
C. Exterior Entrance and Doors
1) The building is inaccessible because it lacks directional signage at the inaccessible entrances directing the public to the accessible entrance. Provide accessible directional signage with the International Symbol of Accessibility at inaccessible entrances directing users to the accessible entrance, and provide accessible signage with the International Symbol of Accessibility at all permanent accessible entrances. Standards §§ 4.1.3(8)(d), 4.13, 4.30.
2) At the rear entrance, the clear space on the pull side of the door is obstructed by a trash can. On the pull side of the door, provide maneuvering clearance at least 60 inches deep and provide a minimum of 18 inches (24 inches is preferred) of maneuvering clearance on the latch side of the door. Standards § 4.13.6, Fig. 25(a).
3) The signage provided throughout the facility is inaccessible. Provide permanent room signage with upper case, sans serif or simple serif type letters and numerals, meeting the requirements of the Standards for character height, raised characters, finish and contrast, accompanied by Grade 2 Braille; mounted on the wall adjacent to the latch side of the door or on the nearest adjacent wall at a height of 60 inches above the finished floor to the centerline of the sign; and located so that a person may approach within 3 inches of the signage without encountering protruding objects or standing within the swing of a door. Standards §§ 4.30.1, 4.30.4, 4.30.5, 4.30.6.
D. First Floor Conference Room
1) The first floor conference room door is inaccessible because knob hardware is used. Provide a door with hardware that is easy to grasp with one hand and that does not require tight grasping, pinching, or twisting of the wrist to operate. Lever-operated mechanisms, push-type mechanisms, and U-shaped handles are acceptable designs. Standards § 4.13.9.
2) The conference room is inaccessible to people with hearing impairments because there is no permanent or portable ALS available. Provide a permanently installed assistive listening system (ALS) or a portable ALS with an adequate number of electrical outlets or other supplementary wiring necessary to support a portable assistive listening system. Also provide 2 for use by the general public and signage indicating their availability. 28 C.F.R. § 35.160. Standards §§ 4.30, 4.33.
E. Second Floor Conference Room
1) No accessible coat hook has been provided. Provide a coat hook at a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.25.2, 4.25.3, 4.2.4, 4.2.5, 4.2.6.
F. Elevators - two side by side
1) Hoistway signage is not provided on both door jambs. Provide signage at hoistway entrances with raised and Braille floor designations on both jambs such that the centerline of the characters is 60 inches above the finished floor and the characters are 2 inches high. Standards § 4.10.5, Fig. 20.
2) The elevator is inaccessible because after reopening, the doors stay open only 2 seconds. Provide doors that open and close automatically with a reopening device that will stop and reopen the car door and hoistway door automatically if the door becomes obstructed by an object or person. Ensure that the device is capable of completing these operations without requiring contact for obstructions passing through the opening at heights of 5 inches and 29 inches above the finished floor; that door reopening devices remain effective for at least 20 seconds, after which the doors may close; that the minimum time from notification that a car is answering a call until the doors of that car start to close is 5 seconds; and that the minimum time for elevator doors to remain fully open in response to a car call is 3 seconds. Standards §§ 4.10.6, 4.10.7, 4.10.8, Figs. 20, 21.
3) The elevator is inaccessible because the car control buttons do not have Braille and raised characters to the left of the buttons, and the main floor is not designated with a star. Provide car control buttons that are at least ¾ inch in their smallest dimension and are raised or flush and that are designated by Braille and by raised standard alphabet characters for letters, arabic characters for numerals, or standard symbols. Ensure that the call button for the main entry floor is designated by a raised star at the left of the floor designation; that all raised designations for control buttons are placed immediately to the left of the buttons to which they apply; that floor buttons are provided with visual indicators to show when each call is registered and are extinguished when each call is answered; that all floor buttons are no higher than 54 inches above the finished floor for a side approach and no more than 48 inches above the finished floor for a front approach; and that emergency controls, including the emergency alarm and emergency stop, are grouped at the bottom of the panel and have their centerlines no less than 35 inches above the finished floor. Standards § 4.10.12, Fig. 23.
4) The emergency control panel door requires pinching to operate. Provide a way to operate the emergency communications that can be used with one hand and without tight grasping, pinching, or twisting of the wrist (lever-operated, push-type, and electronically controlled mechanisms are examples of acceptable designs). Standards § 4.27.4.
5) The elevator is inaccessible because, although emergency communications are provided, they do not work without voice communication. Provide a two-way communication system such that it does not require voice communication, the highest operable part is a maximum of 48 inches above the finished floor of the car, and it is identified by a raised symbol and lettering located adjacent to the device. If the system uses a handset, ensure that the length of the cord from the panel to the handset is at least 29 inches. If the system is located in a closed compartment, ensure that the compartment door hardware operates without tight grasping, pinching or twisting of the wrist. Standards § 4.10.14.
1) The toilet rooms throughout the public health building contain a number of inaccessible elements and are not accessible to people with disabilities. The County will provide an accessible unisex toilet room such that all of the room’s elements, including signage, door, door hardware, clear floor space, water closet, urinal (if provided), grab bars, lavatory, mirror, controls, and dispensers, comply with the Standards and ensure that the toilet room is publicly located. Standards §§ 4.13, 4.16, 4.18, 4.19, 4.26, 4.27, 4.30, Figs. 28, 29.
H. Women’s Toilet Room with Stalls - First Floor
2) The toilet room door is inaccessible because the pressure required to open the door is 12 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards § 4.13.11(2)(b).
4) The soap dispenser is inaccessible because the controls are mounted 46½ inches above the finished floor over an obstruction measuring 26½ inches. Provide a such that the controls comply with Fig. 5 for a forward reach or with Fig. 6 for a side reach and such that it is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach, respectively, by a person using a wheelchair. Standards §§ 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
5) The paper towel dispenser is inaccessible because the controls are mounted 52½ inches above the finished floor over an obstruction measuring 26½ inches. Provide a paper towel dispenser such that the controls comply with Fig. 5 for a forward reach or with Fig. 6 for a side reach and such that it is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach, respectively, by a person using a wheelchair. Standards §§ 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
6) The lavatory is inaccessible because the hot water pipes are not insulated or otherwise configured to protect against contact. Provide hot water and drain pipes that are insulated or otherwise configured to protect against contact. Standards § 4.19.4.
7) Although an ambulatory stall is provided, there is no standard accessible stall provided. Provide a “standard” accessible toilet stall at least 60 inches wide and at least 59 inches deep (or at least 56 inches deep with a wall-mounted toilet) such that all of the stall’s elements, including stall door, stall door hardware, water closet, size and arrangement, toe clearances, grab bars, controls, and dispensers, comply with the Standards. Standards §§ 4.13, 4.16, 4.17, 4.26, 4.27, Fig. 30.
I. Men’s Toilet Room with Stalls - First Floor
4) The soap dispenser is inaccessible because the controls are mounted 46 inches above the finished floor over an obstruction measuring 27½ inches. Provide a soap dispenser such that the controls comply with Fig. 5 for a forward reach or with Fig. 6 for a side reach and such that it is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach, respectively, by a person using a wheelchair. Standards §§ 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
5) The paper towel dispenser is inaccessible because the controls are mounted 52 inches above the finished floor over an obstruction measuring 27½ inches. Provide a paper towel dispenser such that the controls comply with Fig. 5 for a forward reach or with Fig. 6 for a side reach and such that it is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach, respectively, by a person using a wheelchair. Standards §§ 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
7) Although an alternate stall is provided, there is no standard accessible stall provided. Provide a “standard” accessible toilet stall at least 60 inches wide and at least 59 inches deep (or at least 56 inches deep with a wall-mounted toilet) such that all of the stall’s elements, including stall door, stall door hardware, water closet, size and arrangement, toe clearances, grab bars, controls, and dispensers, comply with the Standards. Standards §§ 4.13, 4.16, 4.17, 4.26, 4.27, Fig. 30.
J. Single-User Toilet Room - Back of Exam Rooms
1) The door to the toilet room is inaccessible because it has an opening width of only 29¾ inches. Provide a door with a clear opening of 32 inches with the door open 90 degrees, measured between the face of the door and the opposite stop. Standards § 4.13.5, Fig. 24.
2) There is insufficient turning space within the toilet room. Provide an unobstructed turning space at least 60 inches in diameter or a T-shaped space complying with Fig. 3(b). Standards §§ 4.22.3, 4.2.3, Fig. 3.
3) The toilet room door is inaccessible because knob hardware is used. Provide a door with hardware that is easy to grasp with one hand and that does not require tight grasping, pinching, or twisting of the wrist to operate. Lever-operated mechanisms, push-type mechanisms, and U-shaped handles are acceptable designs. Standards § 4.13.9.
4) The door, which is accessed through a front approach, is inaccessible because it has only 4 inches of maneuvering space on the pull side of the door. On the pull side of the door, provide maneuvering clearance at least 60 inches deep and provide a minimum of 18 inches (24 inches is preferred) of maneuvering clearance on the latch side of the door. Standards § 4.13.6, Fig. 25(a).
5) The toilet room door swings into the required clear floor space at the lavatory. Ensure that no door swings into the required clear floor space at any accessible fixture. Standards § 4.22.2.
6) No accessible mirror has been provided. Provide a mirror with the bottom edge of its reflecting surface no more than 40 inches above the finished floor. Standards § 4.19.6.
7) The soap dispenser is inaccessible because the controls are mounted at 50 inches above the finished floor and requires a forward reach of 18¼ inches over an obstruction. Provide a soap dispenser such that the controls comply with Fig. 5 for a forward reach or with Fig. 6 for a side reach and such that it is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach, respectively, by a person using a wheelchair. Standards §§ 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
8) The paper towel dispenser is inaccessible because the controls are mounted at 53 inches above the finished floor with a forward reach of 18¼ inches over an obstruction required. Provide a paper towel dispenser such that the controls comply with Fig. 5 for a forward reach or with Fig. 6 for a side reach and such that it is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach, respectively, by a person using a wheelchair. Standards §§ 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
9) The lavatory is inaccessible because the bottom edge is 28 inches above the finished floor. Provide a lavatory with the top of its rim or counter 34 inches or less above the finished floor; the bottom edge of the apron at least 29 inches above the finished floor; and knee and toe clearances that comply with Fig. 31. Standards § 4.19.2, Fig. 31.
10) The lavatory is inaccessible because the hot water pipes are not insulated or otherwise configured to protect against contact. Provide hot water and drain pipes that are insulated or otherwise configured to protect against contact. Standards § 4.19.4.
11) The lavatory is inaccessible because it lacks adequate clear floor space. Provide a lavatory with clear floor space at least 30 inches wide and 48 inches deep centered on the lavatory. Standards § 4.19.3, Fig. 32.
12) The designated accessible toilet stall is inaccessible because the toilet lacks clear floor space. Provide a toilet stall that is at least 60 inches wide and at least 56 inches deep for a wall-mounted toilet or at least 59 inches deep for a floor-mounted toilet, such that the centerline of the toilet is exactly 18 inches from the near side wall or partition, and there is at least 9 inches of toe clearance above the floor at the front partition if the stall is no more than 60 inches deep. Standards § 4.17, Fig. 30.
13) The toilet is inaccessible because its centerline measures 16½ inches from the side wall. Within 18 months of the effective date of this Agreement, provide a toilet with a centerline that measures 18 inches from the near side wall. Standards § 4.17.3, Fig. 30.
14) There are no grab bars provided. Provide a rear grab bar that is at least 36 inches in overall length, with the closer end no more than 6 inches from the side wall, and a side grab bar that is at least 40 inches in overall length, with the far end mounted at least 54 inches from the rear wall and the closer end 12 inches or less from the rear wall. Ensure that the grab bars are mounted 33 to 36 inches above the finished floor; with a diameter between 1¼ and 1½ inches; with 1½ inches between the grab bar and the wall; and at least 1½ inches between the grab bar and any object beside or below it and at least 18 inches between the grab bar and any object above it. Standards §§ 4.17.6, 4.26.2, Figs. 30, 39.
K. Single - User Toilet Room - Front of Exam Rooms
1) The door to the toilet room is inaccessible because it has an opening width of only 29½ inches. Provide a door with a clear opening of 32 inches with the door open 90 degrees, measured between the face of the door and the opposite stop. Standards § 4.13.5, Fig. 24.
2) The toilet room door is inaccessible because knob hardware is used. Provide a door with hardware that is easy to grasp with one hand and that does not require tight grasping, pinching, or twisting of the wrist to operate. Lever-operated mechanisms, push-type mechanisms, and U-shaped handles are acceptable designs. Standards § 4.13.9.
3) The door, which is accessed through a front approach, is inaccessible because it has only 4 inches of maneuvering space on the pull side. On the pull side of the door, provide maneuvering clearance at least 60 inches deep and provide a minimum of 18 inches (24 inches is preferred) of maneuvering clearance on the latch side of the door. Standards § 4.13.6, Fig. 25(a).
4) The toilet room door swings into the required clear floor space at the lavatory. Ensure that no door swings into the required clear floor space at any accessible fixture. Standards § 4.22.2.
5) No accessible mirror has been provided. Provide a mirror with the bottom edge of its reflecting surface no more than 40 inches above the finished floor. Standards § 4.19.6.
6) The paper towel dispenser is inaccessible because the controls are mounted at 53 inches above the finished floor with a forward reach of 18½ inches over an obstruction required. Provide a paper towel dispenser such that the controls comply with Fig. 5 for a forward reach or with Fig. 6 for a side reach and such that it is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach, respectively, by a person using a wheelchair. Standards §§ 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
7) The lavatory is inaccessible because the bottom edge is 27½ inches above the finished floor. Provide a lavatory with the top of its rim or counter 34 inches or less above the finished floor; the bottom edge of the apron at least 29 inches above the finished floor; and knee and toe clearances that comply with Fig. 31. Standards § 4.19.2, Fig. 31.
9) The lavatory is inaccessible because it lacks adequate clear floor space. Provide a lavatory with clear floor space at least 30 inches wide and 48 inches deep centered on the lavatory. Standards § 4.19.3, Fig. 32.
10) The designated accessible toilet stall is inaccessible because the toilet lacks clear floor space . Provide a toilet stall that is at least 60 inches wide and at least 56 inches deep for a wall-mounted toilet or at least 59 inches deep for a floor-mounted toilet, such that the centerline of the toilet is exactly 18 inches from the near side wall or partition, and there is at least 9 inches of toe clearance above the floor at the front partition if the stall is no more than 60 inches deep. Standards § 4.17, Fig. 30.
11) The toilet is inaccessible because its centerline measures 14½ inches from the side wall. Provide a toilet with a centerline that measures 18 inches from the near side wall. Standards § 4.17.3, Fig. 30.
12) There are no grab bars provided. Provide a rear grab bar that is at least 36 inches in overall length, with the closer end no more than 6 inches from the side wall, and a side grab bar that is at least 40 inches in overall length, with the far end mounted at least 54 inches from the rear wall and the closer end 12 inches or less from the rear wall. Ensure that the grab bars are mounted 33 to 36 inches above the finished floor; with a diameter between 1¼ and 1½ inches; with 1½ inches between the grab bar and the wall; and at least 1½ inches between the grab bar and any object beside or below it and at least 18 inches between the grab bar and any object above it. Standards §§ 4.17.6, 4.26.2, Figs. 30, 39.
L. Dressing Room - Changing Area in Clinic (1st Floor)
1) None of the dressing rooms are accessible because they lack adequate clear floor space. Provide at least one accessible dressing room in this area on an accessible route with accessible signage indicating its location. Ensure that accessible dressing rooms fitted with swinging or sliding doors contain sufficient clear floor space to allow a person using a wheelchair to make a 180-degree turn inside the room and that no door swings into any part of the turning space. Ensure that private accessible dressing rooms fitted with curtained openings at least 32 inches wide contain either a clear space of 60 inches in diameter, or a “T” shaped turning space that complies with Fig. 3(b). Provide a bench 24 inches by 48 inches fixed to the wall along the longer dimension and mounted between 17 and 19 inches above the finished floor to the top of the bench. If mirrors are provided in dressing rooms of the same use, provide one full-length mirror, measuring at least 18 inches wide by 54 inches high, mounted in a position affording a view to a person on the bench as well as to a person in a standing position. Standards §§ 4.35, 4.30, 4.26.3, 4.2, 4.3, Fig. 3.
M. Main Lobby (1st Floor - 2 fountains)
1) Fountain Next to Support Column
a) The drinking fountain has a spout that is 37½ inches above the finished floor. Provide a fountain that has a spout height no higher than 36 inches, measured from the finished floor or ground surface to the spout outlet, and that otherwise complies with the Standards. Standards §§ 4.15, 4.27.4, Fig. 27.
2) Fountain to the Left
a) The route to the left of fountain 1 is inaccessible because the drinking fountain protrudes into the main walkway and would not be detectable to a blind person using a cane. Provide a circulation path at this location such that no objects with their bottom leading edges measuring between 27 inches and 80 inches above the finished floor protrude more than 4 inches into walks, halls, corridors, passageways, or aisles. Free-standing objects mounted on posts or pylons may overhang 12 inches maximum from 27 inches to 80 inches above the ground or finished floor. Standards § 4.4.
3) Fountain Closer to Exam Rooms
a) The drinking fountain has a spout that is 42 inches above the finished floor. Provide a fountain that has a spout height no higher than 36 inches, measured from the finished floor or ground surface to the spout outlet, and that otherwise complies with the Standards. Alternatively, provide a fountain accessible to people who use wheelchairs and a cup dispenser, or by such other means as would achieve the required accessibility. Standards §§ 4.1.3(10)(a), 4.15, 4.27.4, Fig. 27.
b) The drinking fountain is inaccessible because there is 20½ inches of knee space and a front approach is not possible. Provide a drinking fountain with clear knee space between the bottom of the apron and the finished floor or ground of at least 27 inches high, 30 inches wide, and 17 to 19 inches deep; and a minimum clear floor space of 30 inches by 48 inches to allow a person in a wheelchair to approach the unit facing forward. Standards § 4.15.5(1), Figs. 27(a), (b).
c) The route past the exam rooms is inaccessible because the drinking fountain protrudes into the main walkway and would not be detectable to a blind person using a cane. Provide a circulation path at this location such that no objects with their bottom leading edges measuring between 27 inches and 80 inches above the finished floor protrude more than 4 inches into walks, halls, corridors, passageways, or aisles. Free-standing objects mounted on posts or pylons may overhang 12 inches maximum from 27 inches to 80 inches above the ground or finished floor. Standards § 4.4.
N. Drinking Fountain Near Elevators (1st Floor)
1) The route near the elevators is inaccessible because the drinking fountain protrudes into the main walkway and would not be detectable to a blind person using a cane. Provide a circulation path at this location such that no objects with their bottom leading edges measuring between 27 inches and 80 inches above the finished floor protrude more than 4 inches into walks, halls, corridors, passageways, or aisles. Free-standing objects mounted on posts or pylons may overhang 12 inches maximum from 27 inches to 80 inches above the ground or finished floor. Standards § 4.4.
O. Drinking Fountain - Second Floor
1) The drinking fountain has a spout that is 37½ inches above the finished floor. Provide a fountain that has a spout height no higher than 36 inches, measured from the finished floor or ground surface to the spout outlet, and that otherwise complies with the Standards. Alternatively, provide a fountain accessible to people who use wheelchairs and a cup dispenser, or by such other means as would achieve the required accessibility. Standards §§ 4.1.3(10)(a), 4.15, 4.27.4, Fig. 27.
2) The drinking fountain is inaccessible because the controls require 6 pounds of force to operate. Provide a drinking fountain with controls mounted on or near the front edge that are operable with one hand, that require 5 pounds of force or less to operate, and that can be operated without tight grasping, pinching, or twisting of the wrist. Standards §§ 4.15.4, 4.27.4.
3) The bottom edge of the fountain is 27½ inches above the finish floor and protrudes more than 4 inches into the circulation path. As a result, the fountain is a protruding object that is not cane-detectable from both sides. Provide a circulation path at this location such that no objects with their bottom leading edges measuring between 27 inches and 80 inches above the finished floor protrude more than 4 inches into walks, halls, corridors, passageways, or aisles. Free-standing objects mounted on posts or pylons may overhang 12 inches maximum from 27 inches to 80 inches above the ground or finished floor. Standards § 4.4.
4) Although an accessible drinking fountain is provided, there is no drinking fountain provided for people who have difficulty bending or stooping. Provide a drinking fountain that is accessible to people who have difficulty bending or stooping. This can be accommodated by the use of a “hi-lo” fountain; by providing one fountain accessible to those who use wheelchairs and one fountain at a standard height convenient for those who have difficulty bending; by providing a fountain accessible to people who use wheelchairs and a cup dispenser, or by such other means as would achieve the required accessibility for each group of people. Standards § 4.1.3(10)(a).
P. Medication Counter (1st Floor)
1) The counter is 41½ inches above the finished floor. Staff report that they provide assistance to people who use wheelchairs. Provide a counter on an accessible route such that a portion of the counter is at least 36 inches wide and no more than 36 inches above the finished floor, or provide an auxiliary counter with a maximum height of 36 inches in close proximity to the main counter, or provide equivalent facilitation. Equivalent facilitation may be provided in the form of a folding shelf attached to the main counter, an auxiliary table nearby, a clip board made available to the public, or other means. Standards §§ 7.2(2), 4.3.
Q. Sewage Systems Office Counter
1) The counter is inaccessible because it is mounted 42½ inches above the finished floor. Provide a counter on an accessible route such that a portion of the counter is at least 36 inches wide and no more than 36 inches above the finished floor, or provide an auxiliary counter with a maximum height of 36 inches in close proximity to the main counter, or provide equivalent facilitation. Equivalent facilitation may be provided in the form of a folding shelf attached to the main counter, an auxiliary table nearby, a clip board made available to the public, or other means. Standards §§ 7.2(2), 4.3.
2) The counter protrudes into the walkway and would not be detectable to a blind person using a cane. Provide a circulation path at this location such that no objects with their bottom leading edges measuring between 27 inches and 80 inches above the finished floor protrude more than 4 inches into walks, halls, corridors, passageways, or aisles. Free-standing objects mounted on posts or pylons may overhang 12 inches maximum from 27 inches to 80 inches above the ground or finished floor. Providing a cane-detectable barrier is an acceptable solution. Standards § 4.4.
R. Administration Office (2nd Floor)
1) The administration office is inaccessible because knob hardware is used. Provide a door with hardware that is easy to grasp with one hand and that does not require tight grasping, pinching, or twisting of the wrist to operate. Lever-operated mechanisms, push-type mechanisms, and U-shaped handles are acceptable designs. Standards § 4.13.9.
2) The door, which is accessed through a front approach, is inaccessible because it has only 13½ inches of maneuvering clearance on the pull side. On the pull side of the door, provide maneuvering clearance at least 60 inches deep and provide a minimum of 18 inches (24 inches is preferred) of maneuvering clearance on the latch side of the door. Standards § 4.13.6, Fig. 25(a).
S. Sewage Systems Office (2nd Floor)
1) The sewage system office door is inaccessible because knob hardware is used. Provide a door with hardware that is easy to grasp with one hand and that does not require tight grasping, pinching, or twisting of the wrist to operate. Lever-operated mechanisms, push-type mechanisms, and U-shaped handles are acceptable designs. Standards § 4.13.9.
2) The door, which is accessed through a front approach, is inaccessible because it has only 16 inches of maneuvering clearance on the pull side. On the pull side of the door, provide maneuvering clearance at least 60 inches deep and provide a minimum of 18 inches (24 inches is preferred) of maneuvering clearance on the latch side of the door. Standards § 4.13.6, Fig. 25(a).
T. Exam Rooms (1st Floor)
1) The exam room doors are inaccessible because knob hardware is used. Provide a door with hardware that is easy to grasp with one hand and that does not require tight grasping, pinching, or twisting of the wrist to operate. Lever-operated mechanisms, push-type mechanisms, and U-shaped handles are acceptable designs. Standards § 4.13.9.
U. Clinic Laboratory (1st Floor)
1) The laboratory door is inaccessible because knob hardware is used. Provide a door with hardware that is easy to grasp with one hand and that does not require tight grasping, pinching, or twisting of the wrist to operate. Lever-operated mechanisms, push-type mechanisms, and U-shaped handles are acceptable designs. Standards § 4.13.9.
5. Except as noted, within 9 months of the effective date of the Agreement, the County will complete the following modifications to Kanawha County Courthouse (National Register of Historic Places), located at 407 Virginia Street, East, Charleston.
1) The parking reserved for persons with disabilities lacks appropriate signage. At all spaces designated as reserved for persons with disabilities, provide vertical signs with the International Symbol of Accessibility located such that they cannot be obstructed by parked vehicles. At van accessible spaces, provide an additional “Van-Accessible” sign located below the International Symbol of Accessibility. Standards §§ 4.6.4, 4.30.7(1).
B. Accessible entrance from parking
1) The door, which is accessed through a front approach, is inaccessible because it has only 12 inches of maneuvering clearance on the pull side. On the pull side of the door, provide maneuvering clearance at least 60 inches deep and provide a minimum of 18 inches (24 inches is preferred) of maneuvering clearance on the latch side of the door. Standards § 4.13.6, Fig. 25(a).
1) The ramp is inaccessible because it has a handrail on only one side, which is 43 inches above the ramp surface, and lacks edge protection. Provide a ramp that is at least 36 inches wide with a slope not exceeding 1:12 and a cross slope not exceeding 1:50; with level landings at least as wide as the ramp and 60 inches long at the top and bottom of the ramp; and with edge protection at least 2 inches high at the drop off sides. Provide handrails that are between 1¼ inches and 1½ inches in diameter with a continuous gripping surface along both sides of the ramp, extending at least 12 inches beyond the top and bottom of the ramp parallel with the ground surface. Ensure that handrails are mounted between 34 inches and 38 inches above the ramp surface and 1½ inches from the wall, with ends rounded or returned smoothly to the floor, wall, or post, and that they do not rotate within their fittings. Ensure that the ramp and approaches are designed so that water will not accumulate on walking surfaces. Standards §§ 4.3.8, 4.8.
D. Drinking Fountains Outside Record Room (1st Floor Hallway)
1) The drinking fountain has a spout that is 37 inches above the finished floor. Provide a fountain that has a spout height no higher than 36 inches, measured from the finished floor or ground surface to the spout outlet, and that otherwise complies with the Standards. Alternatively, provide a fountain accessible to people who use wheelchairs and a cup dispenser, or by such other means as would achieve the required accessibility. Standards §§ 4.1.3(10)(a), 4.15, 4.27.4, Fig. 27.
2) The drinking fountain is inaccessible because it lacks adequate knee space depth. Provide a drinking fountain with clear knee space between the bottom of the apron and the finished floor or ground of at least 27 inches high, 30 inches wide, and 17 to 19 inches deep; and a minimum clear floor space of 30 inches by 48 inches to allow a person in a wheelchair to approach the unit facing forward. Standards § 4.15.5(1), Figs. 27(a), (b).
3) Although an accessible drinking fountain is provided, there is no drinking fountain provided for people who have difficulty bending or stooping. Provide a drinking fountain that is accessible to people who have difficulty bending or stooping. This can be accommodated by the use of a “hi-lo” fountain; by providing one fountain accessible to those who use wheelchairs and one fountain at a standard height convenient for those who have difficulty bending; by providing a fountain accessible to people who use wheelchairs and a cup dispenser, or by such other means as would achieve the required accessibility for each group of people. Standards § 4.1.3(10)(a).
E. Drinking Fountain Outside Purchasing Department
1) Although a drinking fountain is provided, there is no accessible drinking fountain because the water height measures 1½ inches. Provide at least one drinking fountain with a spout height no higher than 36 inches, measured from the finished floor or ground surface to the spout outlet; and a spout located at the front of the unit that directs the water flow in a trajectory that is nearly parallel to the front of the unit and is positioned so the flow of water is within 3 inches of the front edge of the fountain and at least 4 inches high. Ensure that fountain controls are operable with one hand, require 5 or less to operate without tight grasping, pinching, or twisting of the wrist; and are front mounted or side mounted near the front edge. Additionally, provide a drinking fountain that is accessible to people who have difficulty bending or stooping. This can be accommodated by the use of a “hi-lo” fountain; by providing one fountain accessible to those who use wheelchairs and one fountain at a standard height convenient for those who have difficulty bending; by providing a fountain accessible to people who use wheelchairs and a cup dispenser; or by such other means as would achieve the required accessibility for each group of people. Standards §§ 4.15, 4.27.4, Fig. 27.
3) There is no drinking fountain provided for people who have difficulty bending or stooping. Provide a drinking fountain that is accessible to people who have difficulty bending or stooping. This can be accommodated by the use of a “hi-lo” fountain; by providing one fountain accessible to those who use wheelchairs and one fountain at a standard height convenient for those who have difficulty bending; by providing a fountain accessible to people who use wheelchairs and a cup dispenser, or by such other means as would achieve the required accessibility for each group of people. Standards § 4.1.3(10)(a).
F. Drinking Fountain Sheriff’s Department Hallway
1) The drinking fountain is inaccessible because it lacks adequate knee depth. Provide a drinking fountain with clear knee space between the bottom of the apron and the finished floor or ground of at least 27 inches high, 30 inches wide, and 17 to 19 inches deep; and a minimum clear floor space of 30 inches by 48 inches to allow a person in a wheelchair to approach the unit facing forward. Standards § 4.15.5(1), Figs. 27(a), (b).
G. Record Room
1) The record room door is inaccessible because the pressure required to open the door is 16 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards § 4.13.11(2)(b).
3) Two of the record aisles are 28 inches wide because of desks protruding into the path of travel. Provide an accessible route between all aisles with a minimum clear width of 36 inches, except at doors, where the width may decrease to 32 inches. Standards §§ 4.3.3, 4.13.5.
4) The main counter is 43¾ inches above the finished floor and the lowered portion of the counter is 42 inches above the finished floor. Provide a counter on an accessible route such that a portion of the counter is at least 36 inches wide and no more than 36 inches above the finished floor, or provide an auxiliary counter with a maximum height of 36 inches in close proximity to the main counter, or provide equivalent facilitation. Equivalent facilitation may be provided in the form of a folding shelf attached to the main counter, an auxiliary table nearby, a clip board made available to the public, or other means. Standards §§ 7.2(2), 4.3.
H. Recording Room
1) The recording room door is inaccessible because the pressure required to open the door is 13 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards § 4.13.11(2)(b).
2) The main counter is 43 inches above the finished floor and the lowered portion of the counter is 37 inches above the finished floor. Provide a counter on an accessible route such that a portion of the counter is at least 36 inches wide and no more than 36 inches above the finished floor, or provide an auxiliary counter with a maximum height of 36 inches in close proximity to the main counter, or provide equivalent facilitation. Equivalent facilitation may be provided in the form of a folding shelf attached to the main counter, an auxiliary table nearby, a clip board made available to the public, or other means. Standards §§ 7.2(2), 4.3.
I. Real Estate Window
1) The counter is inaccessible because it is mounted 42 inches above the finished floor. Provide a counter on an accessible route such that a portion of the counter is at least 36 inches wide and no more than 36 inches above the finished floor, or provide an auxiliary counter with a maximum height of 36 inches in close proximity to the main counter, or provide equivalent facilitation. Equivalent facilitation may be provided in the form of a folding shelf attached to the main counter, an auxiliary table nearby, a clip board made available to the public, or other means. Standards §§ 7.2(2), 4.3.
J. Treasurer’s Department
2) The counter is inaccessible because it is mounted 45½ inches above the finished floor. Provide a counter on an accessible route such that a portion of the counter is at least 36 inches wide and no more than 36 inches above the finished floor, or provide an auxiliary counter with a maximum height of 36 inches in close proximity to the main counter, or provide equivalent facilitation. Equivalent facilitation may be provided in the form of a folding shelf attached to the main counter, an auxiliary table nearby, a clip board made available to the public, or other means. Standards §§ 7.2(2), 4.3.
K. County Commission Court Room
L. Purchasing Department (2nd Floor)
1) The purchasing department door is inaccessible because the pressure required to open the door is 10 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards § 4.13.11(2)(b).
2) The counter is inaccessible because it is mounted 42 inches above the finished floor. Provide a counter on an accessible route such that a portion of the counter is at least 36 inches wide and no more than 36 inches above the finished floor, or provide an auxiliary counter with a maximum height of 36 inches in close proximity to the main counter, or provide equivalent facilitation. Equivalent facilitation may be provided in the form of a folding shelf attached to the main counter, an auxiliary table nearby, a clip board made available to the public, or other means. Standards §§ 7.2(2), 4.3.
M. Kanawha County Commission (2nd Floor Room 230)
2) The main counter is 37½ inches above the finished floor and the auxiliary counter is 39 inches above the finished floor. Provide a counter on an accessible route such that a portion of the counter is at least 36 inches wide and no more than 36 inches above the finished floor, or provide an auxiliary counter with a maximum height of 36 inches in close proximity to the main counter, or provide equivalent facilitation. Equivalent facilitation may be provided in the form of a folding shelf attached to the main counter, an auxiliary table nearby, a clip board made available to the public, or other means. Standards §§ 7.2(2), 4.3.
N. Sheriff’s Department (2nd Floor Room 280)
1) The sheriff’s department door is inaccessible because the pressure required to open the door is 15 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards § 4.13.11(2)(b).
2) The main counter is 48 inches above the finished floor and the auxiliary counter is 48 inches above the finished floor. Provide a counter on an accessible route such that a portion of the counter is at least 36 inches wide and no more than 36 inches above the finished floor, or provide an auxiliary counter with a maximum height of 36 inches in close proximity to the main counter, or provide equivalent facilitation. Equivalent facilitation may be provided in the form of a folding shelf attached to the main counter, an auxiliary table nearby, a clip board made available to the public, or other means. Standards §§ 7.2(2), 4.3.
O. Fiduciary/Probate
1) The door is inaccessible because the pressure required to open the door is 14 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards § 4.13.11(2)(b).
2) The main counter is inaccessible because it is mounted 48½ inches above the finished floor. Provide a counter on an accessible route such that a portion of the counter is at least 36 inches wide and no more than 36 inches above the finished floor, or provide an auxiliary counter with a maximum height of 36 inches in close proximity to the main counter, or provide equivalent facilitation. Equivalent facilitation may be provided in the form of a folding shelf attached to the main counter, an auxiliary table nearby, a clip board made available to the public, or other means. Standards §§ 7.2(2), 4.3.
3) Single User Toilet Room Near Courtroom 4
a) The single user toilet contains the following inaccessible elements: it lacks accessible signage with raised letters and Braille conveying the same information as is conveyed in the pictogram and mounted to the latch side of the door with its centerline at 60 inches above the finished floor; the force required to open the door exceeds 5 pounds; the top of the lavatory is too high at 35½ inches above the finished floor and, if lowered, the bowl of the lavatory will obstruct knee/toe clearance; the toilet paper dispenser is mounted 18 inches above the finished floor, and the rear grab bar is not 36 inches long. Provide an accessible unisex toilet room in this location such that all of the room’s elements, including signage, door, door hardware, clear floor space, water closet, urinal (if provided), grab bars, lavatory, mirror, controls, and dispensers, comply with the Standards. Standards §§ 4.13, 4.16, 4.18, 4.19, 4.26, 4.27, 4.30, Figs. 28, 29.
b) The toilet is inaccessible because its centerline is 17 inches from the near side wall. Within 18 months of the effective date of this Agreement, provide a toilet with a centerline that measures 18 inches from the near side wall. Standards § 4.16.2, Fig. 28.
P. Home Confinement
1) The door is inaccessible because the pressure required to open the door is 18 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards § 4.13.11(2)(b).
Q. Courtroom 4
1) The door is inaccessible because the pressure required to open the door is 15 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards § 4.13.11(2)(b).
2) The courtrooms are inaccessible to persons with hearing impairments because, although they have fixed seats and accommodate at least 50 persons, there are no assistive listening systems for persons who are hard of hearing. Provide a permanently installed assistive listening system (ALS) or a portable ALS with an adequate number of electrical outlets or other supplementary wiring necessary to support a portable assistive listening system. Also provide 2 receivers as required by Section 4.1.3(19)(b) for use by the general public and signage indicating their availability. 28 C.F.R. § 35.160, Standards §§ 4.1.3(19)(b), 4.30, 4.33.
3) The court room is inaccessible because there are no wheelchair seating areas. Provide 2 wheelchair seating areas as required by Standards § 4.1.3(19)(a), each with a minimum clear ground or floor space of 33 inches wide by 48 inches deep for forward or rear access, or 33 inches wide by 60 inches deep for side access. Ensure that the ground or floor at all wheelchair locations is level, firm, stable, and slip resistant; that wheelchair seating areas are an integral part of the fixed seating plan and are located so as to provide people with physical disabilities a choice of lines of sight comparable to those available for members of the general public; that wheelchair seating areas adjoin an accessible route that also serves as a means of egress in case of emergency; and that at least one fixed companion seat is provided next to each wheelchair seating area. Standards §§ 4.1.3(19)(a), 4.5, 4.33, Fig. 46.
R. Telephone - Outside Treasurer’s Department
1) The telephone is inaccessible because the highest operable part is mounted 56 inches above the finished floor. Provide an accessible telephone with a clear floor space of at least 30 inches by 48 inches that allows either a forward or parallel approach by a person using a wheelchair such that bases, enclosures, and fixed seats do not impede approaches to the telephone; with the highest operable part of the telephone mounted no more than 48 inches above the floor for a front approach or no more than 54 inches above the floor for a side approach; that is hearing aid compatible and has a volume control mechanism; with telephone books, if provided, located between 15 and 48 inches above the finished floor for a front approach or between 9 and 54 inches above the finished floor for a side approach; with a cord of at least 29 inches long from the telephone to the handset; and with signage that complies with the Standards. Standards §§ 4.31, 4.30.7(2).
S. Telephone - Record Room
1) There are 3 telephones dispersed throughout the record rooms. Two of the phones are atop records shelves and one is mounted to the wall 58 inches above the finished floor to the highest operable part. The phones are not hearing aid compatible and they lack signage. Provide an accessible telephone with a clear floor space of at least 30 inches by 48 inches that allows either a forward or parallel approach by a person using a wheelchair such that bases, enclosures, and fixed seats do not impede approaches to the telephone; with the highest operable part of the telephone mounted no more than 48 inches above the floor for a front approach or no more than 54 inches above the floor for a side approach; that is hearing aid compatible and has a volume control mechanism; with telephone books, if provided, located between 15 and 48 inches above the finished floor for a front approach or between 9 and 54 inches above the finished floor for a side approach; with a cord of at least 29 inches long from the telephone to the handset; and with signage that complies with the Standards. Standards §§ 4.31, 4.30.7(2).
T. Women’s Toilet Room with Stalls (1st Floor)
2) The toilet room door is inaccessible because the pressure required to open the door is 15 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards § 4.13.11(2)(b).
5) The toilet is inaccessible because its centerline measures 16 inches from the side wall. Within 18 months of the effective date of this Agreement, provide a toilet with a centerline that measures 18 inches from the near side wall. Standards § 4.17.3, Fig. 30.
6) No accessible coat hook has been provided. Provide a coat hook at a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.25.2, 4.25.3, 4.2.4, 4.2.5, 4.2.6.
7) The toilet paper dispenser is inaccessible because it is mounted 16½ inches above the finished floor and 44¼ inches from the rear wall. Provide a toilet paper dispenser that is mounted with its top at least 1½ inches under the side grab bar and 36 inches or less from the rear wall and is centered at least 19 inches above the finished floor. Standards § 4.17.3, Fig. 30(d).
8) The rear grab bar at the toilet is inaccessible because the overall length measures 30½ inches and the toilet seat cover dispenser interferes with the use of the grab bar. Provide a rear grab bar that is at least 36 inches in overall length, with the closer end no more than 6 inches from the side wall; mounted 33 to 36 inches above the finished floor; with a diameter between 1¼ and 1½ inches; with 1½ inches between the grab bar and the wall; and at least 1½ inches between the grab bar and any object beside or below it and at least 18 inches between the grab bar and any object above it. Standards §§ 4.17.6, 4.26.2, Figs. 30, 39.
9) The lock in the standard accessible stall is inaccessible because the controls are mounted at 55 inches above the finished floor. Provide a lock with the controls a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
U. Men’s Toilet Room with Stalls (1st Floor)
5) The toilet paper dispenser is inaccessible because it is mounted 44 inches from the rear wall. Provide a toilet paper dispenser that is mounted with its top at least 1½ inches under the side grab bar and 36 inches or less from the rear wall and is centered at least 19 inches above the finished floor. Standards § 4.17.3, Fig. 30(d).
6) The rear grab bar at the toilet is inaccessible because the overall length measures 30½ inches. Provide a rear grab bar that is at least 36 inches in overall length, with the closer end no more than 6 inches from the side wall; mounted 33 to 36 inches above the finished floor; with a diameter between 1¼ and 1½ inches; with 1½ inches between the grab bar and the wall; and at least 1½ inches between the grab bar and any object beside or below it and at least 18 inches between the grab bar and any object above it. Standards §§ 4.17.6, 4.26.2, Figs. 30, 39.
V. Records Room Unisex Toilet Rooms
W. Commissioner’s Area Unisex Toilet Room
1) There is no signage directing people with disabilities to the accessible toilet rooms. Provide accessible directional signage with the International Symbol of Accessibility at inaccessible toilet rooms indicating the location of the nearest accessible toilet room, and provide accessible signage with the International Symbol of Accessibility at all accessible toilet rooms. Signage indicating the location of this accessible toilet room may also be placed in the elevator. Standards §§ 4.1.2(7)(d), 4.1.6(3)(e)(iii), 4.30.1, 4.30.2, 4.30.3, 4.30.5, 4.30.7.
X. Planning Department Unisex Toilet Room
1) There is no signage directing people with disabilities to the accessible toilet room. Provide accessible directional signage with the International Symbol of Accessibility at inaccessible toilet rooms indicating the location of the nearest accessible toilet room, and provide accessible signage with the International Symbol of Accessibility at all accessible toilet rooms. Signage indicating the location of this accessible toilet room may also be placed in the elevator. Standards §§ 4.1.2(7)(d), 4.1.6(3)(e)(iii), 4.30.1, 4.30.2, 4.30.3, 4.30.5, 4.30.7.
Y. Property Department Single User Toilet Room
1) The route through the toilet room is inaccessible because the cabinet near the door is a protruding object and would not be detectable to a blind person using a cane. Provide a circulation path at this location such that no objects with their bottom leading edges measuring between 27 inches and 80 inches above the finished floor protrude more than 4 inches into walks, halls, corridors, passageways, or aisles. Free-standing objects mounted on posts or pylons may overhang 12 inches maximum from 27 inches to 80 inches above the ground or finished floor. Standards § 4.4.
2) The rear grab bar at the toilet is inaccessible because it is less than 36 inches long. Provide a rear grab bar that is at least 36 inches in overall length with the closer end no more than 6 inches from the side wall. Standards § 4.16.4, Fig. 29.