Source: https://www.law.cornell.edu/cfr/text/40/appendix-Table_3_to_subpart_JJJJJJ_of_part_63
Timestamp: 2017-10-18 13:23:38
Document Index: 780441040

Matched Legal Cases: ['art 63', 'art 63', 'art_63', 'art 63', '§ 63', '§ 63', '§ 63', '§ 63', '§ 63', '§ 63', '§ 63', '§ 63']

40 CFR Appendix Table 3 to Subpart JJJJJJ of Part 63, Operating Limits for Boilers With Emission Limits | US Law | LII / Legal Information Institute
CFR › Title 40 › Chapter I › Subchapter C › Part 63 › Subpart JJJJJJ › Appendix Table_3_to_subpart_JJJJJJ_of_part_63
40 CFR Appendix Table 3 to Subpart JJJJJJ of Part 63, Operating Limits for Boilers With Emission Limits
b. Maintain the 30-day rolling average total secondary electric power of the electrostatic precipitator at or above the minimum total secondary electric power as defined in § 63.11237.
3. Wet scrubber control Maintain the 30-day rolling average pressure drop across the wet scrubber at or above the minimum scrubber pressure drop as defined in § 63.11237 and the 30-day rolling average liquid flow rate at or above the minimum scrubber liquid flow rate as defined in § 63.11237 .
4. Dry sorbent or activated carbon injection control Maintain the 30-day rolling average sorbent or activated carbon injection rate at or above the minimum sorbent injection rate or minimum activated carbon injection rate as defined in § 63.11237 . When your boiler operates at lower loads, multiply your sorbent or activated carbon injection rate by the load fraction (e.g., actual heat input divided by the heat input during the performance stack test; for 50 percent load, multiply the injection rate operating limit by 0.5).
6. Fuel analysis Maintain the fuel type or fuel mixture (annual average) such that the mercury emission rate calculated according to § 63.11211(c) are less than the applicable emission limit for mercury.
8. Oxygen analyzer system For boilers subject to a CO emission limit that demonstrate compliance with an oxygen analyzer system as specified in § 63.11224(a) , maintain the 30-day rolling average oxygen level at or above the minimum oxygen level as defined in § 63.11237 . This requirement does not apply to units that install an oxygen trim system since these units will set the trim system to the level specified in § 63.11224(a)(7) .
[ 78 FR 7519, Feb. 1, 2013]