Source: https://www.ecfr.gov/cgi-bin/text-idx?mc=true&node=se40.23.97_1930&rgn=div8
Timestamp: 2020-07-14 07:29:07
Document Index: 622125610

Matched Legal Cases: ['art 97', '§97', '§97', 'art 75', '§97', '§72', 'art 75', '§97', '§75', '§75', '§97', 'art 75', '§97', '§97', '§75', '§97', '§97', 'art 75', '§75', '§75', '§97', '§75', '§75', 'art 75', '§97', 'art 75', 'art 75', '§97', 'art 75', '§97', '§75']

Title 40 → Chapter I → Subchapter C → Part 97 → Subpart FFFFF → §97.930
§97.930 General monitoring, recordkeeping, and reporting requirements.
The owners and operators, and to the extent applicable, the designated representative, of a Texas SO2 Trading Program unit, shall comply with the monitoring, recordkeeping, and reporting requirements as provided in this subpart and subparts F and G of part 75 of this chapter. For purposes of applying such requirements, the definitions in §97.902 and in §72.2 of this chapter shall apply, the terms “affected unit,” “designated representative,” and “continuous emission monitoring system” (or “CEMS”) in part 75 of this chapter shall be deemed to refer to the terms “Texas SO2 Trading Program unit,” “designated representative,” and “continuous emission monitoring system” (or “CEMS”) respectively as defined in §97.902. The owner or operator of a unit that is not a Texas SO2 Trading Program unit but that is monitored under §75.16(b)(2) of this chapter shall comply with the same monitoring, recordkeeping, and reporting requirements as a Texas SO2 Trading Program unit.
(a) Requirements for installation, certification, and data accounting. The owner or operator of each Texas SO2 Trading Program unit shall:
(1) Install all monitoring systems required under this subpart for monitoring SO2 mass emissions and individual unit heat input (including all systems required to monitor SO2 concentration, stack gas moisture content, stack gas flow rate, CO2 or O2 concentration, and fuel flow rate, as applicable, in accordance with §§75.11 and 75.16 of this chapter);
(2) Successfully complete all certification tests required under §97.931 and meet all other requirements of this subpart and part 75 of this chapter applicable to the monitoring systems under paragraph (a)(1) of this section; and
(3) Record, report, and quality-assure the data from the monitoring systems under paragraph (a)(1) of this section.
(b) Compliance deadlines. Except as provided in paragraph (e) of this section, the owner or operator of a Texas SO2 Trading Program unit shall meet the monitoring system certification and other requirements of paragraphs (a)(1) and (2) of this section on or before the later of the following dates and shall record, report, and quality-assure the data from the monitoring systems under paragraph (a)(1) of this section on and after:
(1) For a Texas SO2 Trading Program unit under §97.904(a), January 1, 2019; or
(2) For a Texas SO2 Trading Program unit under §97.904(b), January 1 of the first control period for which the unit is a Texas SO2 Trading Program unit.
(3) The owner or operator of a Texas SO2 Trading Program unit for which construction of a new stack or flue or installation of add-on SO2 emission controls is completed after the applicable deadline under paragraph (b)(1) or (2) of this section shall meet the requirements of §75.4(e)(1) through (4) of this chapter, except that:
(i) Such requirements shall apply to the monitoring systems required under §97.930 through §97.935, rather than the monitoring systems required under part 75 of this chapter;
(ii) SO2 concentration, stack gas moisture content, stack gas volumetric flow rate, and O2 or CO2 concentration data shall be determined and reported, rather than the data listed in §75.4(e)(2) of this chapter; and
(iii) Any petition for another procedure under §75.4(e)(2) of this chapter shall be submitted under §97.935, rather than §75.66 of this chapter.
(c) Reporting data. The owner or operator of a Texas SO2 Trading Program unit that does not meet the applicable compliance date set forth in paragraph (b) of this section for any monitoring system under paragraph (a)(1) of this section shall, for each such monitoring system, determine, record, and report maximum potential (or, as appropriate, minimum potential) values for SO2 concentration, stack gas flow rate, stack gas moisture content, fuel flow rate, and any other parameters required to determine SO2 mass emissions and heat input in accordance with §75.31(b)(2) or (c)(3) of this chapter or section 2.4 of appendix D to part 75 of this chapter, as applicable.
(d) Prohibitions. (1) No owner or operator of a Texas SO2 Trading Program unit shall use any alternative monitoring system, alternative reference method, or any other alternative to any requirement of this subpart without having obtained prior written approval in accordance with §97.935.
(2) No owner or operator of a Texas SO2 Trading Program unit shall operate the unit so as to discharge, or allow to be discharged, SO2 to the atmosphere without accounting for all such SO2 in accordance with the applicable provisions of this subpart and part 75 of this chapter.
(3) No owner or operator of a Texas SO2 Trading Program unit shall disrupt the continuous emission monitoring system, any portion thereof, or any other approved emission monitoring method, and thereby avoid monitoring and recording SO2 mass discharged into the atmosphere or heat input, except for periods of recertification or periods when calibration, quality assurance testing, or maintenance is performed in accordance with the applicable provisions of this subpart and part 75 of this chapter.
(4) No owner or operator of a Texas SO2 Trading Program unit shall retire or permanently discontinue use of the continuous emission monitoring system, any component thereof, or any other approved monitoring system under this subpart, except under any one of the following circumstances:
(i) During the period that the unit is covered by an exemption under §97.905 that is in effect;
(ii) The owner or operator is monitoring emissions from the unit with another certified monitoring system approved, in accordance with the applicable provisions of this subpart and part 75 of this chapter, by the Administrator for use at that unit that provides emission data for the same pollutant or parameter as the retired or discontinued monitoring system; or
(iii) The designated representative submits notification of the date of certification testing of a replacement monitoring system for the retired or discontinued monitoring system in accordance with §97.931(d)(3)(i).
(e) Long-term cold storage. The owner or operator of a Texas SO2 Trading Program unit is subject to the applicable provisions of §75.4(d) of this chapter concerning units in long-term cold storage.