Source: http://900igr.net/prezentacija/anglijskij-jazyk/bs-en-iso-14644-3-72742.html
Timestamp: 2019-10-23 19:13:40
Document Index: 542461285

Matched Legal Cases: ['art 3', 'art 0', 'art 1', 'art 2', 'art 3', 'art 4', 'art 0', 'art 1', 'art 2', 'art 3', 'art 4', 'art 1', 'art 3', 'art 4']

BS EN ISO 14644-3 - Презентация 72742
<< Brookhaven Town Burgen und Schl?sser in Deutschland >>
BS EN ISO 14644-3 Metrology & Test Methods
BS EN ISO 14644-3 Metrology & Test Methods Annex A
BS EN ISO 14644-3 Metrology & Test Methods Annex A Test Selection &
BS EN ISO 14644-3 Metrology & Test Methods Annex B
BS EN ISO 14644-3 Metrology & Test Methods Annex C
tel 01483 207236 fax 01483 235384 e-mail wander
Презентация: «BS EN ISO 14644-3». Автор: Gordon Farquharson. Файл: «BS EN ISO 14644-3.ppt». Размер zip-архива: 146 КБ.
содержание презентации «BS EN ISO 14644-3.ppt»
Cleanrooms & associated controlled environments- Part 3: Metrology and test methods
Current Status 1. DIS was issued by ISO in September 02 2. UK comments to BSI to be made by end December 02 3. LBI/30 will consider all UK comments by end January 03 4. BSI vote to CEN/ISO by end February 03 5. DIS is valid and can be referred to and used until it is superseded. 6. Likely time when revised DIS will be available - mid 2004
14644-1:1999 Classification of air cleanliness 14644-2:2000 Specifications for testing and monitoring to prove continued compliance with -1 14644-3:DIS Metrology and test methods 14644-4:2001 Design, construction & start-up 14644-5:FDIS Operations 14644-6:CD Vocabulary/terminology 14644-7:FDIS Separative devices 14644-8:CD Classification of Airborne Molecular Contamination
Current Status of BS 5295 BS 5295 Part 0: General Introduction - Current BS 5295 Part 1: Classification - Withdrawn BS 5295 Part 2: Design - Withdrawn BS 5295 Part 3: Operation - Current BS 5295 Part 4: Compliance - Withdrawn
Current Status of BS 5295 BS 5295 Part 0: General Introduction - Current BS 5295 Part 1: Classification - 14644-1/3 BS 5295 Part 2: Design - 14644-4 BS 5295 Part 3: Operation - Current BS 5295 Part 4: Compliance - 14644-2 Some of BS5295 Part 1 is not addressed currently and PD6609:2000 is being revised to ‘bridge the gap’. Part 3:Operation will be covered by 14644-5:FDIS
This part of BS EN ISO 14644 may be used for the characterisation of a cleanroom as described and specified in other parts of BS EN ISO 14644. Not all cleanroom parameter test procedures are shown. Other standards may be considered to be applicable The annexes to this document are ‘informative’. Ie they are not compulsory, but form a ‘recommendation’ for compliance with the standard. Consequently, throughout the document references are made to ‘or as agreed between customer and supplier’
SUMMARY OF ESSENTIAL CONTENTS: 1. Scope - ISO standard text and also states that alternative methods can be used based on agreement between customer and supplier. 2. Normative - Reference to standards Reference 3. Terms and - Helps understanding, and Definitions allows document to exist alone 4. Testing - Recommended tests with procedures Procedures and apparatus 5. Test Report - Reporting & documentation
Item 4 forms the crux of this section of the standard. Recommended tests are listed in table 1. Each test has a procedure in Annex B and a corresponding set of apparatus in Annex C. The section of the standard referencing the test is also given. Selecting and scheduling of these tests is discussed in Annex A.
ANNEX A (Informative) Choice of recommended tests of an installation and the sequence in which to carry them out A1 Recommended test procedures Choice of tests Table A1: Test checklist for installation properties Table A2: Test checklist for sequencing The checklists are useful in that they can be taken from the standard and used as a tool.
Sequence Checklist
Choose which tests are required Put them in a logical order for your application Where not applicable put N/A Review the schedule of tests
ANNEX B (Informative) - Test Methods B1 Airborne Particle Count (for classification) B2 Ultrafine Particle Count (for characterisation) B3 Macro Particle Count (for characterisation) B4 Airflow Test B5 Pressure Difference Test B6 Installed Filter Leakage Test B7 Flow Visualisation B8 Airflow Direction Test B9 Temperature Test B10 Humidity Test B11 Electrostatic & Ion Generator Test B12 Particle Deposition Test B13 Recovery Test B14 Containment Leak Test
ANNEX B (Informative) - Test Methods Each section comprises items on: Principle - what and why Recommended test procedure - how Recommended apparatus - with what Test report - detailed results
ANNEX B (Informative) - Test Methods B1 Airborne Particle Count (for classification) Airborne test for size distributions with thresholds between 0.1 and 5 microns to certify or verify cleanliness classification
ANNEX B (Informative) - Test Methods B2 Ultrafine Particle Count (for characterisation) Airborne test for particles with size distribution thresholds less than 0.1 micron for characterisation of the cleanroom
ANNEX B (Informative) - Test Methods B3 Macro Particle Count (for characterisation) Airborne tests for particles with size distribution thresholds greater than 5 microns for characterisation of the cleanroom
ANNEX B (Informative) - Test Methods B4 Airflow Test Tests to evaluate airflow velocity, uniformity of airflow velocity and supply air volume depending on classification. Airflow velocity and uniformity tests are described for use principally in unidirectional systems. Air volume tests are described for unidirectional, non unidirectional or supply air duct systems. NB Political correctness avoids terms such as laminar and turbulent flow systems
ANNEX B (Informative) - Test Methods B5 Air Pressure Difference Test Verification of capability of installation to maintain the specified PD between it and it’s surroundings.
ANNEX B (Informative) - Test Methods B6 Installed Filter Leakage Test Particle Counter and Photometer tests are both described Photometer method for ISO 5 and less (ie typically non-unidirectional), and for MPPS Filters with penetrations > 0.005% (H14 and lower to BS EN 1822) Acceptance criteria is 0.01% for all grades. DPC method more sensitive unidirectional systems. Evaluation of scan rate and allowable particle counts is based on BS EN 1822 part 4 and DIN 24184.
ANNEX B (Informative) - Test Methods B6 Installed Filter Leakage Test Note error on B6.3.5 formula for scan rate Sr <= Cc.Ps.K.Dp.Fs/Np is equivalent to Sr = 472 Cc.Ps.K.Dp/Np Units should be (cm/s)
ANNEX B (Informative) - Test Methods B7 Flow Visualisation Tests to demonstrate airflow characteristics in the installation. Techniques described are by thread, tracer injection or image processing (CFD)
ANNEX B (Informative) - Test Methods B8 Airflow Direction Test Tests to demonstrate airflow directional characteristics in the installation. Techniques described are by thread, tracer injection or image processing (CFD)
ANNEX B (Informative) - Test Methods B9 Temperature Test Tests to demonstrate temperature characteristics in the installation. Techniques described are for general or more exacting measurement requirements.
ANNEX B (Informative) - Test Methods B10 Humidity Test Tests to demonstrate the humidity characteristics of the installation using measurements of dew point or relative humidity Humidity tests should be performed in conjunction with the temperature test.
ANNEX B (Informative) - Test Methods B11 Electrostatic & Ion Generator Test Tests to evaluate the level of electrostatic charge and dissipation rate in the installation. Techniques for the measurement of surface voltage and resistance as well as ioniser performance are suggested
ANNEX B (Informative) - Test Methods B12 Particle Deposition Test Tests to evaluate the level of particulates that can be deposited on work or surfaces in the installation. Techniques using witness plates or a fall out photometer are suggested.
ANNEX B (Informative) - Test Methods B13 Recovery Test Test to evaluate the capability of the clean air system to recover from a particle generating event principally in non-unidirectional applications.
ANNEX B (Informative) - Test Methods B14 Containment Leak Test Test to evaluate the intrusion of contaminated air from surrounding areas using DPC or Photometer methods.
Annex C (Informative) - Test Instruments Describes test apparatus that should be used for the corresponding recommended tests in Annex B. There is a recommendation that apparatus should be subject to agreement between the customer and the supplier. The information provided is not limiting, it represents a sensible minimum requirement. Ie Equipment that becomes available through improvements in measurement technology are not restricted by this Annex. Equally alternate equipment may be suitable and may be used subject to agreement.
Annex C (Informative) - Test Instruments - example C1. Discrete Particle Counter (DPC). C2. Condensation Nucleus Counter (CNC). C3. Microscope, Cascade Impactor, DPC, Time of Flight. C4. Anemometers - Thermal, Ultrasonic, Vane, Pitot, Hood. C5. Manometers - Electronic, Inclined, Mechanical. C6. Photometer, DPC, Aerosol Generator, C7. Anemometers, Tracers, Aerosol generator. C8. Anemometers, Tracers, Aerosol generator. C9. Liquid in Glass thermometer, Electronic thermometer. C10. Humidity meters; Capacitive, Hair. C11. Voltmeter, Ohmmeter, Charged plate monitor. C12. Microscope, Fall-out Meter. C13. Discrete Particle Counter (DPC). C14. Discrete Particle Counter (DPC), Photometer, Aerosol Generator.
UK public comments on this section to BSI need to be made in written form and in an approved format by end December 02 otherwise they will not be considered.
ter.kuile@vokes.com
This presentation has been prepared and delivered by:- Wander ter Kuile McLeod Russel UK Ltd c/o Vokes Ltd Henley Park Guildford Surrey, GU3 2AF UK
«BS EN ISO 14644-3»
http://900igr.net/prezentacija/anglijskij-jazyk/bs-en-iso-14644-3-72742.html
900igr.net > Презентации по английскому языку > Без темы > BS EN ISO 14644-3