Source: http://docplayer.net/1900848-Section-10-emergency-and-standby-power-systems.html
Timestamp: 2017-07-27 03:22:05
Document Index: 430409504

Matched Legal Cases: ['ART 1', 'ART 1', 'art 1228', 'ART 1', 'ART 1', 'ART 1', 'ART 1']

Section 10: Emergency and Standby Power Systems - PDF
Download "Section 10: Emergency and Standby Power Systems"
Albert Samson Todd
1 Section 10: Emergency and Standby Power Systems Bill Brown, P.E., Square D Engineering Services Introduction Emergency and standby power systems are designed to provide an alternate source of power if the normal source of power, most often the serving utility, should fail. As such, reliability of these types of systems is critical and good design practices are essential. Code and standards A.) Classification of emergency and standby power systems The classification of emergency and standby power systems is as follows: Emergency Power System: Defined in IEEE Std [1] as an independent reserve source of electric energy that, upon failure or outage of the normal source, automatically provides reliable electric power within a specified time to critical devices and equipment whose failure to operate satisfactorily would jeopardize the health and safety of personnel or result in damage to property. The NEC [2] gives a slightly different definition for Emergency Systems as those systems legally required and classed as emergency by municipal, state, federal, or other codes, or by any governmental agency having jurisdiction. These systems are intended to automatically supply illumination, power, or both, to designated areas and equipment in the event of failure of the normal supply or in the event of accident to elements of a system intended to supply, distribute, and control power and illumination essential for safety to human life. Standby Power System: Defined in [1] as an independent reserve source of electric energy that, upon failure or outage of the normal source, provides electric power of acceptable quality so that the user s facilities may continue in satisfactory operation. The NEC [2] divides standby power systems into two categories, as follows: Legally Required Standby Systems: Those systems required and so classed as legally required standby by municipal, state, federal, and other codes or by any governmental agency having jurisdiction. These systems are intended to automatically supply power to selected load (other than those classed as emergency systems) in the event of failure of the normal source. FPN: Legally required standby systems are typically installed to serve loads, such as heating and refrigeration systems, communications systems, ventilation and smoke removal systems, sewage disposal, lighting systems, and industrial processes that, when stopped during any interruption of the normal electrical supply, could create hazards or hamper rescue and fire-fighting operations. Optional Standby Systems: Those systems intended to supply power to public or private facilities or property where life safety does not depend on the performance of the system. Optional standby systems are intended to supply on-site generated power to selected loads either automatically or manually. FPN: Optional standby systems are typically installed to provide an alternate source of electric power for such facilities as industrial and commercial buildings, farms, and residences and to serve loads such as heating and refrigeration systems, data processing and communications systems, and industrial processes that, when stopped during any power outage, could cause discomfort, serious interruption of the process, damage to the product or process, and the like. B.) IEEE Standard IEEE Standard , IEEE Recommended Practice for Emergency and Standby Power Systems for Industrial and Commercial Applications [1], is a general engineering reference for the design of these systems. 12 C.) The National Electrical Code The National Electrical Code [2] contains requirements for emergency systems in Article 700, Legally-Required Standby Systems in Article 701, and Optional Standby Systems in Article 702. In addition, Article 445 (Generators), 517 (Health Care Facilities), 665 (Integrated Electrical Facilities), and 705 (Interconnected Electrical Power Production Sources) are all of particular interest for emergency and standby power systems. The NEC [2] requirements for emergency and standby power systems are discussed in further detail below. D.) NFPA 110 NFPA 110 [3], Standard for Emergency and Standby Power Systems, defines how emergency and standby power systems are to be installed and tested. It contains requirements for energy sources, transfer equipment, and installation and environmental considerations. It divides emergency power systems into Types, Classes, and Levels. The Type refers to the maximum time that an emergency power system can remain unpowered after a failure of the normal source. The Types are listed in table 10-1 [3]: Table 10-1: NFPA 110 emergency power system types (essentially the same as [3] table 4.1(B)) Type U sec sec sec M Power restoration time Basically Uninterruptible (UPS Systems) Manual stationary or nonautomatic no time limit The Class of an emergency power system refers to the minimum time, in hours, for which the system is designed to operate at its rated load without being refueled or recharged. The Classes for emergency power systems are shown in table 10-2 [3]: Table 10-2: NFPA 110 emergency power system classes (essentially the same as [3] table 4.1(B)) Class Power restoration time hr. (5 min.) hr. (15 min.) 2 2 hr. 6 6 hr hr. X Other time, in hours, as required by the application, code, or user. The Level of an emergency power system refers to the level of equipment installation, performance, and maintenance requirements. The Levels for emergency power systems are shown in table 10-3 [3]: Table 10-3: NFPA emergency power system levels Level When Installed 1 When failure of the equipment to perform could result in loss of human life or serious injuries 2 When failure of the equipment to perform is less critical to human life and safety and where the authority having jurisdiction shall permit a higher degree of flexibility than that provided by a level 1 system 23 E.) NFPA 101 NFPA 101 [4], Life Safety Code, addresses those construction, protection, and occupancy features necessary to minimize danger to life from fire, including smoke, fumes, or panic. It defines the requirements for what systems the Emergency Power System will supply. F.) NFPA 99 NFPA 99 defines establishes criteria to minimize the hazards of fire, explosion, and electricity in health care facilities. It defines several specific features of electric power systems for these facilities. Reasons for application Emergency and standby power systems are generally designed into the over-all electrical system for one of the following two reasons: Legal Requirements As required by the NEC [2] NFPA 101 [4], NFPA 99 [5], and other local, state, and federal codes and requirements. These are concerned with the safety of human life, protection of the environment, etc. Economic Considerations Continuous process applications often require a continuous source of electrical power to avoid significant economic loss. In some cases even a momentary loss of power can be disastrous. Co-generation systems which are used to sell power back to the utility as part of an energy management strategy are not discussed in this section. Power sources Generators are by far the most prevalent source of power for emergency and standby power systems. For most commercial and industrial power systems these will be engine-generator sets, with the prime-mover and the generator built into a single unit. For reciprocating engines, diesel engines are the most popular choice of primemover for generators, due to the cost of the diesel engines as compared to other forms of power and the relative ease of application. Gasoline engine generator sets are also available and are generally less expensive than diesel generator sets, but suffer from the disadvantages of higher operating costs, greater fuel storage hazards, and shorter fuel storage life as compared to diesel. Diesel engines can also run on natural gas, although for maximum efficiency specially-tuned engines for natural gas use are available. The other alternative for generators is the turbine generator, typically powered by natural gas. Gas-turbine generator sets are generally lighter in weight than diesel engine-generator sets, run more quietly, and generally require less cooling and combustion air, leading to lower installation costs. However, gas-turbine generator sets are more expensive than diesel engine-generator sets, and require more starting time (normally around 30 s compared to the seconds for diesels). The long starting-time requirement and lack of available small sizes (< 500 kw) makes the gas-turbine generators infeasible in many applications. Generator installations must consider the combustion and cooling air required by the generator and prime mover, as well as the provisions for the removal of exhaust gasses. Noise abatement must also be considered. These considerations increase the installation costs, especially for reciprocating-engine units such as diesel or gasoline engines. Further, the fuel supply must be considered; building code and insurance considerations may force the fuel storage tank to be well removed from the generator(s), usually forcing the addition of a fuel transfer tank near the generator(s). Care must be taken when sizing engine-generator sets for a given application since several ratings exist for the output capability of a given machine. The continuous rating is typically the output rating of the engine-generator set on a continuous basis with a non-varying load. The prime power rating is typically the continuous output rating with varying load. The standby rating is typically the output rating for a limited period of time with varying load. The manufacturer must be consulted to define the capabilities of a given unit. A second alternative for emergency or standby system power is a second utility source. However, the procurement of a second utility source which is sufficiently independent from the normal service may be economically infeasible. 34 Solid-state converters that invert DC voltage from a battery system are another alternative, although they can be difficult to apply and generally are not available in the larger sizes that may be needed for a medium to large emergency or standby system. Because motor starting and block loading can have a big effect on the output voltage and frequency of a small generator such as the engine-generator sets described above, and also because power is not available during the engine starting period, a buffer between the generators and sensitive load equipment is generally required. The Uninterruptible Power Supply (UPS) is usually the buffer of choice for these applications. UPS s are available in several different topologies, but the operational goals are the same regardless of topology: The supply of uninterrupted power to sensitive, critical loads. The most popular topology for a UPS is the double conversion topology, as shown in figure 10-1: Figure 10-1: Double-conversion UPS topology So long as the batteries are properly maintained, the AC output should not be affected by change in frequency or voltage, or even a complete loss, at the input, so long as backup time of the UPS is not exceeded. Other topologies exist, including the line interactive, double-conversion rotary, hybrid rotary, and line-interactive rotary topologies, each with advantages and disadvantages of application. UPS systems do not alleviate the need for a generator or second utility service power source, but they do serve to buffer critical loads from the effects of generator starting time and voltage and frequency variations. Switching devices A means must be provided to switch the critical loads from the normal utility source to the standby power source. Several types of device are available for this. An automatic transfer switch is defined as self-acting equipment for transferring one or more load conductor connections from one power source to another [1]. The automatic transfer switch is the most common means of transferring critical loads to the emergency/standby power supply. An automatic transfer switch consists of a switching means and a control system capable of sensing the normal supply voltage and switching over to the alternate source should the normal source fail. Automatic transfer switches are available in ratings from A, and up to 600V [1]. Because automatic transfer switches are designed to continuously carry the loads they serve, even under normal conditions, care must be used in sizing these so that the potential for failure is minimized. Automatic test switches with adjustable pickup and dropout setpoints and integral testing capability are generally preferred. An automatic transfer switch is generally an open-transition device that will not allow paralleling of the two sources. Manual versions of transfer switches are also available. A one-line representation of an automatic transfer switch is shown in figure Figure 10-2: Automatic transfer switch one-line diagram representation 45 Other options for transferring devices include electrically-operated circuit breakers, as described in System protection section (section7 in this guide). For medium voltage transfers, medium voltage circuit breakers are generally used. Manual versions of circuit-breaker transferring schemes are, of course, also available. Bypass/isolation switches, as their name suggests, are used to bypass an automatic transfer switch (or other switching means) and connect the source directly to the load and allow isolation of the transfer switch for maintenance. Figure 10-3 shows a typical bypass/isolation switch arrangement along with the transfer switch: Figure 10-3: Bypass/isolation switch application In figure 10-3 the bypass blade B serves to bypass the automatic transfer switch, and isolating contacts I serve to isolate the automatic transfer switch. Bypass/isolation switches are typically manually-operated devices. Bypass/isolation switches are available with a test position in which only the ATS-to-load isolation contact (marked with an asterisk [*] in figure 10-3) is open, allowing the transfer switch to be operated without disconnecting the load. Static Transfer Switches are typically used when high-speed (~4ms) operation is required. The most common application is to bypass a UPS so that a UPS failure will not result in interruption of service to the load. System arrangements Various ways of arranging emergency and standby power systems exist. The most common arrangements are given here. A.) Basic arrangement radial system The most basic arrangement for an emergency or standby power system is shown in figure This can be recognized as an extension of the single-source radial system from System arrangements section (section 5 of this guide), figure 5-2, with the transformer omitted. The transfer switch transfers the emergency/standby loads to the alternate source upon failure of the normal source. This arrangement extends the same inherent weaknesses of the radial system to the emergency system, since a single failure of one piece of equipment can result in loss of service to the emergency/standby loads. Note that the single generator shown may be several engine-generator sets operating in parallel, if necessary. This simple system may be expanded to the other system types in Section 5. 56 Figure 10-4: Simple emergency/standby system arrangement B.) More complex systems The basic arrangement from figure 10-4 may be extended to the other system arrangements shown in Section 5. For example, the secondary-selective system, shown in figure 5-8, could be equipped with an emergency system as shown in figure 10-5: Figure 10-5: Example of a more complex emergency/standby system arrangement In figure 10-5, the emergency/standby load at the bottom of the figure will always be supplied by one of the normal sources if possible, and by the generator(s) if not. This will avoid the generator starting time for this load if one utility source were to fail. The two emergency/standby loads in the middle of the figure will be supplied by their respective switchboard busses or by the emergency source. Emergency/standby systems are not limited to the low voltage level. For example, the primary selective/primary loop/secondary selective system shown in figure 5-14 can be expanded to include an emergency system, as shown in figure 10-6: 67 Figure 10-6: Medium voltage emergency/standby system implementation In figure 10-6 there is a great deal of flexibility in the system operation. However, instead of automatic transfer switches metal-clad switchgear is used increasing the complexity of the system. C.) Hospital arrangements NFPA 99 [5] and the NEC [2] have very unique requirements for the design of a hospital emergency system. The emergency system is classified into the essential electrical system, which is comprised of alternate sources of power and all connected distribution systems and ancillary equipment, designed to ensure continuity of electrical power to designated areas and functions of a health care facility during disruption of disruption of normal power sources, and the emergency system itself, which is a system of circuits and equipment intended to supply alternate power to a limited number of prescribed functions vital to the protection of life and safety [2]. The emergency system is a part of the essential electrical system. The minimum arrangement, for hospitals 150 kva or less, is shown in figure The minimum requirement over 150 kva is shown in figure Figure 10-7: Minimum requirement per NEC [2] and NFPA 99 [5] for essential electrical system for hospitals 150 kva or Less (same as [2] FPN figure No.2) 78 Figure 10-7: Minimum Requirement per NEC [2] and NFPA 99 [5] for Essential Electrical system for Hospitals over 150 kva (same as [2] FNP figure No. 1) The essential electrical system supplies the equipment system, defined as a system of circuits and equipment arranged for delayed, automatic, or manual connection to the alternate power source and that serves primarily 3- phase power equipment [2]. The emergency system supplies, which itself part of the essential electrical system, supplies the life safety branch, which is a subsystem of the emergency system consisting of feeders and branch circuits intended to provide adequate power needs to insure safety to patients and personnel [2]. The emergency system also supplies the critical branch, which is a subsystem of the emergency system consisting of feeders and branch circuits supplying energy to task illumination, special power circuits, and selected receptacles serving areas and functions related to patient care [2]. For hospitals of 150 kva and less the equipment system, life safety branch, and critical branch may be on the same transfer switch. Note that the transfer switch(es) for the equipment system above 150 kva is required to be delayed. NEC requirements The following are highlights from the NEC [2] requirements for emergency and standby power systems. This is not intended to list all NEC requirements for these systems, but to illustrate the major points that apply in the most common installations and affect the power system design. For the full text of the complete NEC requirements for these systems, consult the NEC. A.) Emergency systems (Article 700) The NEC definition for an emergency system was given at the beginning of this section. These requirements apply to those systems meeting this definition: Witness Test: The authority having jurisdiction must conduct or witness a test of the complete system and periodically afterward. [700.4 (A)] Emergency systems must be tested periodically on a schedule acceptable to the authority having jurisdiction to ensure the systems are maintained in proper operating condition. A written record must be kept of these tests. [700.4 (B), (C), and (D)] Battery systems that are part of the emergency system must be periodically maintained. [700.4 (B)] A means for testing all emergency lighting and power systems during maximum anticipated load conditions must be provided. [700.4 (E)] The alternate power source is required to be sized to supply all emergency loads simultaneously. [700.5 (A)] 89 The alternate power source is permitted to supply emergency, legally required standby, and optional standby system loads where the source has adequate capacity or where automatic selective load pickup or load shedding is provided to insure adequate power to the emergency, legally required standby, and optional standby system loads. If these requirements are met the system may also be used for peak load shaving. Peak load shaving operation may satisfy the requirement for periodic testing if acceptable to the authority having jurisdiction. A portable or temporary alternate source must be available if the emergency generator is out of service for repair. [700.5 (B)] Transfer equipment must be automatic, identified for emergency use, and approved by the authority having jurisdiction. Automatic transfer switches must be electrically operated and mechanically held. [700.6 (A) and (C)] Transfer equipment must supply only emergency loads. [700.6 (D)] Audible and visual signal devices must be provided for indication of derangement of the emergency source, that the battery is carrying load, that the battery is not functioning, and to indicate a ground fault in solidly-grounded wye systems of more than 150 V to ground and over 1000 A. The sensor for ground-fault indication must be located at or ahead of the main system disconnecting means for the emergency source. [700.7] A sign must be placed at the service entrance equipment, indicating the type and location of on-site emergency power sources. A sign is also required where the grounded circuit conductor connected to the emergency source is connected to a grounding electrode conductor at a location remote from the emergency source. [700.8] All boxes and enclosures for emergency circuits must be permanently marked so that they will be readily identified as a component of an emergency circuit or system. [700.9 (A)] Wiring from an emergency source or emergency source distribution overcurrent protection to emergency loads must be kept entirely independent of all other wiring and equipment. Exceptions apply where load equipment must have wiring from two sources. [700.9 (B)] For occupancies of not less than 1000 persons or in buildings above 75 ft. in height with assembly, educational, residential, detention/correctional, business, or mercantile occupancy class the feeder circuit wiring must be 1.) installed in spaces or areas that are fully protected by an approved automatic fire suppression system, or 2.) be a listed electrical circuit protective system with a 1-hour fire rating, or 3.) be protected by a listed thermal barrier system for electrical system components, or 4.) be protected by a fire-rated assembly listed to achieve a minimum fire rating of 1 hour, or 5.) be embedded in not less than 50mm of concrete. Feeder circuit equipment must be either in spaces fully protected by a approved automatic fire suppression systems or in spaces with a 1-hour fire resistance rating. [700.9 (D)] In the event of failure of the normal supply to, or within, the building or group of buildings concerned, emergency lighting, power, or both, must be available within the time required by the application but not to exceed 10 seconds. The alternate source of power must be a storage battery, generator set, UPS, separate service, or fuel cell system, each with restrictions on its use. [ (A), (B), (C), (D), and (E)]. Storage batteries must have sufficient capacity to supply and maintain the total load for a minimum period of one hours, without the voltage applied to the load falling below 87% of nominal. The battery charging means must be automatic. [ (A)] Generator sets must have a prime-mover acceptable to the authority having jurisdiction, and means of automatically starting the prime mover on failure of the normal service. If the prime-mover is an internal combustion engine, an on-premises fuel supply must be provided to allow not less than 2 hours full-demand operation of the system. If power is required for operation of fuel transfer pump to deliver fuel to a generator set day tank, this pump must be connected to the emergency power system. Generator sets must not be solely dependent on a public utility gas system for their fuel supply for a municipal water supply for their cooling systems. If dual supplies for these are used, means must be provided to automatically transfer from one supply to the other. If a storage battery is used for control or signal power or as the means of starting the prime mover, it must be equipped with an automatic charging means independent of the generator set. Where power is required for the operation of the dampers used to ventilate the generator set, the dampers must be connected to the emergency system. [ (B) (1), (2), (3), and (4)] 910 If a generator set requires more than 10 seconds to develop power, an auxiliary power supply that energizes the emergency system until the generator can pick up the load is permitted. [ (B) (5)] Outdoor generator sets do not require an additional disconnecting means where the ungrounded conductors serve or pass through the building or structure, so long as they are equipped with a readily-accessible disconnecting means located within sight of the building or structure supplied. [ (B)(6)] UPS s used to provide power for emergency systems must comply with the applicable provisions for battery systems and generators. An additional utility service is permitted to be the power source for the emergency system, if acceptable to the authority having jurisdiction. A separate service drop or service lateral and service conductors sufficiently remote electrically and physically from other service conductors to minimize the possibility of simultaneous interruption of supply must be supplied. [ (D)] Fuel cell systems must be capable of supplying and maintaining the total load for not less then two hours of fulldemand operation. Fuel cell systems must meet the requirements of Parts II through VIII of Article 692 (Fuel Cell Systems). A single fuel cell that serves as the normal source for the building or group of buildings concerned cannot serve as the alternate source. [700.12(E)] Individual unit equipment for emergency illumination must have a rechargeable battery, a battery charging means, provisions for one or more lamps mounted on the equipment or terminals for remote lamps, and a relaying device arranged to energize the lamps automatically upon failure of the supply to the unit equipment. The battery must be capable of supplying the lamps for no less than one hours at not less than 60% of the initial illumination level. [ (F)] Individual unit equipment for emergency illumination must be fixed in place. Flexible cord-and-plug installation is permitted if the cord is no more than 3ft. in length. The branch circuit feeding the unit equipment must be the same as that serving normal lighting in the area and connected ahead of any local switches, and must be clearly identified at the distribution panel. Alternatively, for areas with at least three normal lighting branch circuits the emergency illumination unit equipment may be supplied by a separate branch circuit with a lock-on feature. [ (F)] No appliances or lamps, other than those specified for emergency use, are allowed on emergency lighting circuits. [700.15] Emergency illumination must include all required means of egress lighting, illuminated exit signs, and all other lights specified as necessary to provide required illumination. Failure of any individual lighting element must not leave in total darkness any space that requires emergency illumination. If HID lighting is used as emergency illumination, it must operate until normal illumination has been restored. [700.16] Emergency lighting must have either an emergency lighting supply, with provisions for automatically transferring the emergency lights upon the event of failure of the general lighting system supply, or two or more separate and complete systems with independent power supplies, each providing sufficient current for emergency lighting purposes. If two systems are used, means must be provided for automatically energizing either system upon failure of the other unless they are both kept lighted. [700.17] All branch circuits that supply equipment classed as emergency equipment must have an emergency supply source to which the load will be transferred upon the failure of the normal supply. [700.18] Emergency lighting circuits must be arranged so that only authorized persons have control of emergency lighting. Exceptions apply. [700.20] Switches in series or 3- and 4-way switches cannot be used in emergency lighting circuits. [700.20] Control switches for emergency lighting must be in convenient locations for authorized persons. In assembly occupancies or theaters, audience areas of motion picture studios, and performance areas, a switch for controlling emergency lighting systems must be in the lobby or at a place conveniently accessible thereto. [700.21] Emergency lighting on the exterior of a building that is not required for illumination when there is sufficient daylight may be controlled by an automatic light-actuated device. [700.22] 1011 The branch-circuit overcurrent devices in emergency circuit must be accessible to authorized persons only. [700.25] The alternate source for emergency systems is not required to have ground-fault protection of equipment. Ground-fault indication is required. [700.26] Emergency system(s) overcurrent devices must be selectively coordinated with all supply-side overcurrent protective devices. [700.27] B.) Legally required standby systems (Article 701) System periodic testing and maintenance requirements are essentially the same as for emergency systems, except that the authority having jurisdiction is only required to witness the test upon installation. [701.5] The legally required standby system alternate power source is permitted to supply both legally required standby system and optional standby system loads, provided that it either has enough capacity to handle all connected loads or that automatic selective load pickup and load shedding is provided that will ensure adequate power to the legally required standby circuits. [701.6] Requirements for transfer equipment are essentially the same as for emergency systems, except that no restriction is placed upon the use of transfer equipment use for other systems in addition to the legally required standby system. [701.7] Audible and visual signal devices must be provided for indication of derangement of the standby source, that the standby source is carrying load, and that the battery charger is not functioning. [701.8] Signage requirements are essentially the same as for emergency systems. [701.9] Wiring for legally required standby systems is permitted to occupy the same raceways, cables, boxes, and cabinets with other general wiring. [701.10] In the event of failure of the normal supply to, or within, the building or group of buildings concerned, legally required standby power must be available within the time required by the application but not to exceed 60 seconds. The alternate source of power must be a storage battery, generator set, UPS, separate service, connection ahead of the service disconnecting means, or fuel cell system, each with restrictions on its use. [ (A), (B), (C), (D), (E), and (F)] The requirements for storage batteries, generator sets, UPS s, separate utility service, and fuels cells as the standby power source are essentially the same as for emergency systems, except the requirements for fuel transfer pumps and ventilation dampers to be connected to the system for generator sets. [ (A)] Where acceptable to the authority having jurisdiction, connections ahead of but not within the same cabinet, enclosure, or vertical switchboard section as the service disconnecting means may serve as the standby power source. This connection ahead of the normal service must be sufficiently separated from the normal main service disconnecting means to prevent simultaneous interruption of supply. [ (D)] The requirements for individual unit equipment for legally required standby illumination are essentially the same as for emergency illumination individual unit equipment. [ (G)] Legally-required standby system overcurrent protection requirements are essentially the same as for emergency systems, except that ground-fault indication is not required. [701.15, , ] C.) Optional standby systems (Article 702) Transfer equipment is required, except in the case of temporary connection of a portable generator where conditions of maintenance and supervision ensure that only qualified persons service the installation and where normal supply is physically isolated by a lockable disconnect means or by disconnection of supply conductors. [702.6] Audible and visual signal devices must be provided for indication of derangement of the standby source and to indicate that the optional standby source is carrying load. [702.7] 1112 Signage requirements are essentially the same as for emergency and legally required standby systems. [702.8] Wiring for optional standby systems is permitted to occupy the same raceways, cables, boxes, and cabinets with other general wiring. [702.9] Where a portable optional standby source is used as a separately derived system, it must be grounded to a grounding electrode in accordance with Article Where a portable optional standby source is used as a non-seperately derived system, the equipment grounding conductor must be bonded to the system grounding electrode. [702.10] Outdoor generator sets do not require an additional disconnecting means where the ungrounded conductors serve or pass through the building or structure, so long as they are equipped with a readily-accessible disconnecting means located within sight of the building or structure supplied. [702.11] D.) Health care facility essential electrical systems (Article 517 part III) The essential electrical system is required to serve a limited amount of lighting and power service, which is considered essential for life safety and orderly cessation of procedures during the time normal service is interrupted for any reason. This includes clinics, medical and dental offices, outpatient facilities, nursing homes, limited care facilities, hospitals, ad other health care facilities serving patients. [517.25] The essential electrical system must meet the requirements of Article 700 (Emergency Systems), except as amended by Article 517. [517.26] Hospitals (Articles ) The essential electrical systems for hospitals must comprised of two separate systems: The emergency system and the equipment system. The emergency system must be limited to circuits essential to life safety and to critical patient care, designated as the life safety branch and the critical branch. The equipment system must supply major electrical equipment necessary for patient care and basic hospital operation. [ (B) (1), (2), and (3)] The number of transfer switches used must be based on reliability, design, and load considerations. One transfer switch is permitted to serve one or more branches or systems in a facility with a maximum demand on the essential electrical system of 150 kva. [ (B) (4)] Other loads not specifically mentioned in Article 517 must be served with their own transfer switches. These loads must not be transferred to the essential electrical system generating equipment if the transfer will overload the equipment, and they must be automatically shed upon generating equipment overloading. [ (B)(5)] The life safety and critical branch circuit wiring must be kept independent of all of other wiring and equipment and must not enter the same raceways, boxes, or cabinets with each other or other wiring. Exceptions apply where transfer or load equipment must have wiring from two sources. Wiring for the equipment system is permitted to occupy the same raceways boxes, or cabinets of other circuits that are not part of the emergency system. [ (C)] All wiring of the emergency system must be mechanically protected. Nonflexible metal raceways, type MI cable, or Schedule 80 rigid nonmetallic conduit are permitted, except that nonmetallic raceways cannot be used for branch circuits that supply patient care areas. Schedule 40 rigid nonmetallic conduit, flexible nonmetallic or jacketed metallic raceways, or jacketed metallic cable assemblies listed for installation in concrete may be used if encased in no less than 2 in. of concrete. Listed flexible metal raceways and listed metal sheathed cable assemblies may be used under certain conditions. Flexible power cords of appliances or other utilization equipment and secondary circuits of Class 2 or Class 3 communications or signaling systems are exempted from being run in metal raceways. [ (C) (3)] Generator sizing may be based upon demand calculations rather than on the entire load operating simultaneously as required in [ (D)] All receptacles supplied by the emergency system must have a distinctive color or marking. [ (E)] 1213 The life safety branch is permitted to supply only illumination of egress means, exit signs, alarm and alerting systems, communications systems used during emergency conditions, task illumination at the generator set location, elevator cab lighting, control, communications, and signal systems, and automatic doors. [517.32] The critical branch is permitted to supply task illumination and selected receptacles in critical care areas, isolated power systems in special environments, task illumination and selected receptacles for selected patient care areas, general care beds, selected labs, additional patient care task illumination and receptacles as needed, nurse call systems, blood, bone, and tissue banks, telephone equipment rooms and closets, etc. (complete list given in the NEC text). [517.33] The critical branch may be subdivided into two or more branches. [ (B)] Delayed automatic connection to the equipment system must be provided for central suction systems, sump pumps, compressed air systems, smoke control and stair pressurizing systems, kitchen hood supply or exhaust systems, and supply, return, and exhaust ventilating systems for selected locations (complete list given in NEC text). [ (A)] Delayed automatic or manual connection to the equipment system must be provided for selected heating equipment, selected elevators, hyperbaric and hypobaric facilities, automatically operated doors, selected electrically-heated autoclaving equipment, and other selected equipment. [complete list given in NEC text and NFPA 99: (9)] [ (B)] Generator accessories, such as the transfer fuel pump, electrically operated louvers, and other accessories essential for generator operation, must be arranged for non-delayed automatic connection to the alternate power source via the equipment system. A minimum of two sources of power are required, one normal, one alternate. The alternate source may be generator(s) on the premises, an external utility service if the normal service is a generator(s) on the premises, or a battery system. Nursing homes and limited care facilities (Article ) Applicability depends upon the type of care given at the facility. Specific exceptions are listed for certain types of facilities (see NEC text for details). If a nursing home provides inpatient hospital care, it must conform to the requirements for hospitals. Nursing homes and limited care facilities that are contiguous or located on the same site with a hospital are permitted to have their essential electrical systems supplied by the hospital. [517.40] The essential electrical system must be comprised of two separate branches: The life safety branch and the critical branch. [ (A)] Requirements for transfer switches are essentially the same as for hospitals. [ (C)] The life safety branch must be kept entirely independent of all other wiring and equipment and must not enter the same raceways, boxes, or cabinets with other wiring. Exceptions apply where transfer or load equipment must have wiring from two sources. [ (D)] Requirements for receptacle identification are essentially the same as for hospitals. [ (E)] The life safety branch must be automatically restored via the alternate power source within 10 seconds after interruption of the normal source. [517.42] The life safety branch must supply only illumination of means of egress, exit signs, alarm and alerting systems, communications systems used during emergency conditions, dining and recreation areas, task illumination at the generator set location, and elevator cab lighting, control, communications, and signal systems. Delayed automatic connection to the critical branch must be provided for task illumination and selected receptacles in selected patient care areas, sump pumps and other equipment required to operate for the safety of major apparatus and associated control systems and alarms, smoke control and stair pressurization systems, kitchen hood supply and/or exhaust systems if required to operate during a fire in or under the hood, and supply, return, and exhaust ventilating systems for airborne infections isolation rooms (complete list given in NEC text). [517.43(A)] 1314 Delayed automatic connection to the critical branch must be provided for heating equipment to provide heating for patient rooms (exceptions apply), elevator service and additional illumination, receptacles, and equipment. [ (B)] The alternate source of power must be a generator(s) located on the premises unless the normal source is a generator(s) on the premises, in which case the alternate source may be either another generator set or external utility service. In certain cases a battery system may be used (see NEC text). [ (B)] Other health care facilities (Article ) The essential electrical system must be a battery or generator system, if required per NFPA 99. Where electrical life support equipment is required or critical care areas are present, the requirements for hospitals apply. The requirements of Article 700 apply to battery systems. Generator systems must be as described for hospitals. References [1] IEEE Recommended Practice for Emergency and Standby Power Systems for Industrial and Commercial Applications, IEEE Std , December [2] [3] [4] The National Electrical Code, NFPA 70, The National Fire Protection Association, Inc., 2005 Edition. Standard for Emergency and Standby Power Systems, NFPA 110, The National Fire Protection Association, 2005 Edition. Life Safety Code, NFPA 101, The National Fire Protection Association, 2003 Edition. [5] Standard for Health Care Facilities, NFPA 99, The National Fire Protection Association, 2005 Edition. 14 View more
Mike Holt s Illustrated Guide to NEC Requirements for Generators and Standby Power Systems Rule 220.87, Articles 445, 700, 701, and 702 Based on the 2011 NEC Extracted from Mike Holt s Illustrated Guides More information ELECTRICAL EMERGENCY SYSTEM PLAN REVIEW OVERVIEW OF CODE REQUIREMENTS
ELECTRICAL EMERGENCY SYSTEM PLAN REVIEW What to Look for during Plan Review OVERVIEW OF CODE REQUIREMENTS First determine the type of emergency power system; is the system designed for Emergency or Legally More information The State Fire Marshal's Office and the VDH/Office of Licensure and Certification. Generator Testing in Nursing Facilities
Generator Testing in Nursing Facilities Introduction Recent emergencies and natural disasters have emphasized the need to ensure that nursing facilities have an adequate EPSS in place should the loss of More information Errata NFPA 70. Proposed 2014 Edition
Errata NFPA 70 National Electrical Code (Report on Proposals) Reference: 12-109 (Log #1618) Panel Meeting Action Proposed 2014 Edition The National Electrical Code Technical Correlating Committee notes More information ELECTRICAL - WIRING DESIGN AND PROTECTION SELF INSPECTION CHECKLIST
Name of School: OPTIONAL INFORMATION Date of Inspection: Vocational Program/Course/Room: Signature of Inspector: ELECTRICAL - WIRING DESIGN AND PROTECTION SELF INSPECTION CHECKLIST Guidelines: This checklist More information INSPECTION AND TESTING OF EMERGENCY GENERATORS
INSPECTION AND TESTING OF EMERGENCY GENERATORS Certification requirements NFPA 101(00), Sec. 7.9.2.3 requires that emergency generators be installed, tested and maintained in accordance with NFPA 110, More information Top Commercial / Residential Electrical Requirements *
Department of Community Development Building Division 4800 West 92 nd Avenue Westminster, Colorado 80031 For Information call (303) 658-2075 Fax (303) 706-3922 www.westminsterpermits.com Top Commercial More information SECTION.3400 - MECHANICAL: ELECTRICAL: PLUMBING
SECTION.3400 - MECHANICAL: ELECTRICAL: PLUMBING 10A NCAC 13D.3401 HEATING AND AIR CONDITIONING Heating and cooling systems shall meet the American Society of Heating, Refrigerating, and Air Conditioning More information GROWTH MANAGEMENT DEPARTMENT 201 SE 3 rd ST, (Second Floor), Ocala, FL 34471 (352) 629-8421; FAX: (352) 629-8264
BUILDING CODE GUIDELINES FOR ELECTRICAL INSPECTIONS Building Code compliance is the obligation of design professionals and/or contractors. Plan Review and Inspection Guidelines are intended to be used More information Ontario Electrical Safety Code 25 th Edition/ 2012
Ontario Electrical Safety Code 25 th Edition/ 2012 Ted Olechna Director, Codes and Standard Chief Engineer 1 What I Will Cover ESA s role is as the regulator Highlight of 2012 Code changes The Code and More information Understanding Emergency Power Off (EPO)
Understanding Emergency Power Off (EPO) White Paper #22 Executive Summary Emergency Power Off (EPO) is the capability to power down a piece of electronic equipment or an entire installation from a single More information Tech Report 2: Electrical System Existing Conditions
, Tech Report 2: Electrical System Existing Conditions Oct 12, 2013 Yucheng Lu Lighting/Electrical AE Faculty Consultant: Dr. Shawn Good Executive Summary This report is a summary of my study about the More information Unified requirements for systems with voltages above 1 kv up to 15 kv
(1991) (Rev.1 May 2001) (Rev.2 July 2003) (Rev.3 Feb 2015) Unified requirements for systems with voltages above 1 kv up to 15 kv 1. General 1.1 Field of application The following requirements apply to More information Questions and Answers for Heating and A/C Contractors
1. How do we accomplish grounding of furnaces and / or water heaters on two wire circuits? 250.134 Equipment Fastened in Place or Connected by Permanent Wiring Methods (Fixed) Grounding. Unless grounded More information 12 SOLAR PHOTOVOLTAIC POWER SUPPLY SYSTEMS by John Ware. PV modules are current-limiting
12 SOLAR PHOTOVOLTAIC POWER by John Ware IT IS PLANNED for BS 7671:2008 to include a new Section 712 providing additional requirements for safety applicable to solar photovoltaic (pv) power supply systems. More information 527 CMR: BOARD OF FIRE PREVENTION REGULATIONS
527 CMR 31.00: CARBON MONOXIDE ALARMS Section 31.01: Purpose and Scope 31.02: Definitions 31.03: General Installation Provisions 31.04: Specific Installation Provisions 31.05: Carbon Monoxide Protection: More information City of Riverside Building & Safety Division Phone: (951) 826-5697 www.riversideca.gov
City of Riverside Building & Safety Division Phone: (951) 826-5697 www.riversideca.gov PHOTOVOLTAIC PERMITTING GUIDELINES The information provided in this document is general and is intended only as a More information Fire Alarm System Plans Review Checklist Property location Date of Review
Fire Alarm System Plans Review Checklist Property location Date of Review 1. Is application completed in entirety? 2. Are the plans review fee submitted with the application? 3. Does floor plan include More information Inverter / Charger Installation General Operations and AC and DC Connections
Inverter / Charger Installation General Operations and AC and DC Connections The Inverter is just one piece. Sometimes, a tendency is to mount the inverter and batteries, and make it work It is better More information ELECTRICAL INSPECTION BULLETIN (Effective 2000-03-01)
ELECTRICAL INSPECTION BULLETIN (Effective 2000-03-01) Rule 28-900 Standby Generator Installations Due to the increasing number of standby generator installations being established to maintain continuity More information Electrical. This section applies to the design and installation of building power distribution systems.
Basis of Design This section applies to the design and installation of building power distribution systems. Design Criteria This section contains the architectural, structural and mechanical provisions More information FLORIDA ATLANTIC UNIVERSITY FIRE ALARM SYSTEM INSTALLATION MANUAL
FLORIDA ATLANTIC UNIVERSITY FIRE ALARM SYSTEM INSTALLATION MANUAL January, 2003 Environmental Health and Safety Florida Atlantic University 777 Glades Rd. Boca Raton, FL 33431 Phone: 561-297-3129 Fax: More information INSTALLATION GUIDELINES for SOLAR PHOTOVOLTAIC SYSTEMS 1
City of Cotati Building Division 201 W. Sierra Ave. Cotati, CA 94931 707 665-3637 Fax 792-4604 INSTALLATION GUIDELINES for SOLAR PHOTOVOLTAIC SYSTEMS 1 Any PV system on a new structures should be included More information CITY OF PHILADELPHIA DEPARTMENT OF LICENSES AND INSPECTIONS ANNUAL CERTIFICATION FOR FIRE ALARM SYSTEMS
CITY OF PHILADELPHIA DEPARTMENT OF LICENSES AND INSPECTIONS ANNUAL CERTIFICATION FOR FIRE ALARM SYSTEMS PROPERTY ADDRESS (BRT Address Required) TESTING CONTRACTOR (Name and Address) License No. ANNUAL More information Electrical Contractors. and the. New Jersey. Rehabilitation Code
Electrical Contractors and the New Jersey Rehabilitation Code Alan Chech Electrical Seminars 609-890-7072 www.alanchech.com Information is based on the presently adopted electrical subcode NEC 2005. Current More information Article 10 - ADMINISTRATIVE SECTION
Article 10 - ADMINISTRATIVE SECTION 10.1 TITLE These Administrative Regulations along with the requirements included in the 2011 Edition of the National Electrical Code (NFiPA-70-2011) as adopted by the More information ELECTRICAL SYSTEMS A.
I=Inspected NI=Not Inspected NP=Not Present R=Not Functioning or In Need of Repair I NI NP R Inspection Item II. ELECTRICAL SYSTEMS A. Service Entrance and Panels Comments: Items noted during the visual More information FIRE ALARM AND DETECTION SYSTEMS SECTION 16721
PART 1 - GENERAL 1.01 WORK INCLUDED FIRE ALARM AND DETECTION SYSTEMS SECTION 16721 A. Provide a complete fully addressable, power limited, fire detection and evacuation system. The system shall be connected More information Fire Pump Plan Review March 2010
Fire Pump Plan Review March 2010 Date of Review: / / Permit Number: Business/Building Name: Address of Project: Designer Name: Designer s Phone: Contractor: Contractor s Phone: Occupancy Classification: More information Continuous Power... Continuous Protection
Series 165 We Keep Your Power On Continuous Power... Continuous Protection An Automatic Transfer Switch helps prevent... Your business or home from losing power during bad weather or utility power equipment More information County of Riverside Building and Safety Department
County of Riverside Building and Safety Department Mike Lara Director Photovoltaic Permitting Guidelines The information provided in this document is general and is intended only as a guide. Each project More information TAMARAC FIRE RESCUE INSTRUCTIONS FOR FIRE ALARM PRE-SUBMITTAL CHECKLIST
TAMARAC FIRE RESCUE INSTRUCTIONS FOR FIRE ALARM PRE-SUBMITTAL CHECKLIST In order to provide a comprehensive plan review in a timely manner, and to insure the design and installation of fire alarm systems More information 5-8.1.4* Any required illumination shall be arranged so that the failure of any single lighting unit shall not leave any area in darkness.
NFPA 101 Life Safety Code Section 5-8 Illumination of Means of Egress 5-8.1 General. 5-8.1* Illumination of means of egress shall be provided in accordance with this section for every building and structure More information Common Electrical Hazards in the Workplace Including Arc Flash. Presented by Ken Cohen, PhD, PE & CIH (Ret.)
Common Electrical Hazards in the Workplace Including Arc Flash Presented by Ken Cohen, PhD, PE & CIH (Ret.) 1 What s New In February 1972, OSHA incorporated the 1971 edition of the National Fire Protection More information NFPA and Beyond
NFPA 20 2016 and Beyond Gayle Pennel, P.E. - Aon Fire Protection Engineering Aon Fire Protection Engineering Corporation NFPA 20-2016 Major Changes Automatic Supervision of Pressure Transducers Connectivity More information CLARK COUNTY FIRE DEPARTMENT Fire Hazard & Prevention Services
CLARK COUNTY FIRE DEPARTMENT Fire Hazard & Prevention Services 575 E. Flamingo Road, Las Vegas, NV 89119 (702) 455-7316 FAX (702) 455-7347 105.8a-6.1 TITLE: FIRE ALARM SYSTEM REQUIREMENTS SCOPE: This guideline More information Fire Alarm System Plans Submittal Guidelines For New and Existing Systems
Fire Alarm System Plans Submittal Guidelines For New and Existing Systems SCOPE The Temecula Fire Prevention Bureau (TFPB) has established the following requirements for the submittal of all fire alarms, More information ELECTRICAL CONTRACTORS THE UNIVERSITY OF TENNESSEE KNOXVILLE, TENNESSEE SECTION 16050 PAGE 1
KNOXVILLE, TENNESSEE SECTION 16050 PAGE 1 PART 1 - GENERAL 1.01 RELATED DOCUMENTS: SECTION 16050 A. Drawings and general provisions of Contract, including General and Supplementary Conditions and Division-1 More information Bold items are particular to the City of Euless
EULESS FIRE DEPARTMENT FIRE MARSHAL S OFFICE INFORMATION LINE: Revised 2/12 Fire Chief Wes Rhodes Fire Marshal Paul Smith EFD-FMO 3-2 2009 International Fire & Building Code as Amended NFPA Standards Adopted More information FACILITY FIRE PREVENTION AND EMERGENCY PREPAREDNESS INSPECTION CHECKLIST
FACILITY FIRE PREVENTION AND EMERGENCY PREPAREDNESS INSPECTION CHECKLIST Date of Inspection: Conducted by: Location: Reviewed by: Date of Review: Comments or additional corrective action taken as a result More information ELECTRICAL REQUIREMENTS FOR HEALTH CARE FACILITIES
ELECTRICAL REQUIREMENTS FOR HEALTH CARE FACILITIES Review Guide for: Hospitals Nursing Facilities Clinics Office of Statewide Health Planning and Development Facilities Development Division www.oshpd.ca.gov More information 2014 NEC Guide Lines for Home Owner Doing Electrical Work on their Property
2014 NEC Guide Lines for Home Owner Doing Electrical Work on their Property A brief summary of the most used code references for residential wiring State of Idaho Division of Building Safety Electrical More information Significant Changes in the 2011 NEC Prepared by Bryan Holland City of North Port
Significant Changes in the 2011 NEC Prepared by Bryan Holland City of North Port Code-Wide Code Change Section 90.5(C). Fine Print Notes are now referred to as "Informational Notes." The purpose, intent, More information Prime Power Services, Inc. Georgia, Carolinas 800 741 0128. NFPA 110 Standards for Emergency & Stand by Generators June 1, 2010
Prime Power Services, Inc. Georgia, Carolinas 800 741 0128 NFPA 110 Standards for Emergency & Stand by Generators June 1, 2010 NFPA Disclaimer The views and opinions expressed in this seminar are purely More information EMERGENCY LIGHTING AND CONTROL
I. Overview Emergency lighting control options are rapidly expanding in response to growing needs by design professionals and building owners to save energy and achieve aesthetic and functional design More information What are the basic electrical safety issues and remedies in solar photovoltaic installations?
What are the basic electrical safety issues and remedies in solar photovoltaic installations? Presented by: Behzad Eghtesady City of Los Angeles Department of Building and Safety Topics Covered Photovoltaic More information Carbon Monoxide Detection in Commercial Buildings (
1 Technical Guideline for School Districts and BOCES to comply with regulations for Carbon Monoxide Detection in Commercial Buildings (Section 1228.4 of Part 1228 of Title 19 NYCRR). General: This document More information Important New Code Requirements for SCCR Labeling of Data Center Equipment
Important New Code Requirements for SCCR Labeling of Data Center Equipment Michael P. Murphy D V L G r o u p 1 1 5 S i n c l a i r R o a d B r i s t o l, P A 1 8 9 6 3 Short Circuit Current Ratings (SCCR) More information INSTRUCTIONS FOR BUILDINGS WITH FIRE PROTECTION EQUIPMENT
INSTRUCTIONS FOR BUILDINGS WITH FIRE PROTECTION EQUIPMENT FIRE EXTINGUISHERS,SPRINKLER SYSTEMS AND FIRE ALARMS Attachment #1 Inspection of Fire Extinguishers Fire Extinguishers must be tested according More information Circuit Breakers and Switchgear. Thomas Greer Director of Engineering TLG Services
Circuit Breakers and Switchgear Thomas Greer Director of Engineering TLG Services Presentation Outline Switchgear Definition Overcurrent Protection Devices Circuit Breaker Trip Curves and Coordination More information 2011/2008/2005 NATIONAL ELECTRICAL CODE SOLAR PV CODE COMPLIANCE REFERENCE
2011/2008/2005 NATIONAL ELECTRICAL CODE SOLAR PV CODE COMPLIANCE REFERENCE PAGE 1 OF 5 This Reference provides a very comprehensive list of aspects of a solar PV installation that could be reviewed, clarifying More information DORMA MODEL PS-406BB POWER SUPPLY INSTALLATION INSTRUCTIONS
Features: INSTALLATION Install in accordance with NFPA 70. DORMA MODEL PS-406BB POWER SUPPLY INSTALLATION INSTRUCTIONS Up to 1.95 Amps Load Capacity Class 2 Rated Outputs Overload, Over Voltage, and Short More information FIRE-FIGHTING DESIGN BRIEF REPORT
P a g e 1 SECTION 04 (Doc.No.A/DBR 001) FIRE-FIGHTING DESIGN BRIEF REPORT P a g e 2 1.0 SCOPE 2.0 STANDARDS AND CODES 3.0 TYPES OF SYSTEM PROPOSED 4.0 FIRE HYDRANT SYSTEM 5.0 AUTOMATIC SPRINKLER SYSTEM More information FIRE ALARM SYSTEM RECORD OF COMPLETION
FUNDAMENTALS OF FIRE ALARM SYSTEMS 72 33 FIRE ALARM SYSTEM RECORD OF COMPLETION To be completed by the system installation contractor at the time of system acceptance and approval. 1. PROTECTED PROPERTY More information SOLAR PHOTOVOLTAIC (PV) SYSTEMS ELECTRICAL CODE COMPLIANCE AND INSPECTION CHECKLIST
SOLAR PHOTOVOLTAIC (PV) SYSTEMS ELECTRICAL CODE COMPLIANCE AND INSPECTION CHECKLIST This checklist contains common electrical code requirements for PV systems, based on the 2008 National Electrical Code More information Bypass transfer switch mechanisms
Power topic #6013 Technical information from Cummins Power Generation transfer switch mechanisms > White paper By Gary Olson, Director, Power Systems Development This paper describes the configuration More information c. As mandated by law, facilities must obtain and maintain valid zoning permits as well as permits for intended use.
Walmart Standards for Suppliers Section 7. Health and Safety 7. Health and Safety Suppliers must provide workers with a safe and healthy work environment. Suppliers must take proactive measures to prevent More information FIRE ALARM SYSTEM RECORD OF COMPLETION
FIRE ALARM SYSTEM RECORD OF COMPLETION To be completed by the system installation contractor at the time of system acceptance and approval. 1. Protected Property Information Name of property: Description More information HERNANDO COUNTY FIRE ALARM GUIDELINES
HERNANDO COUNTY FIRE ALARM GUIDELINES To be used for all commercial building fire alarm system plan review. The procedures set forth in this document are the minimum requirements necessary to ensure a More information SOLAR PV STANDARD ELECTRICAL PLAN Microinverter Systems for Single Family Dwellings
*** Provide this document to the inspector along with ALL system installation instructions *** Project Address: Scope: Standard plan for the installation of grounded microinverter solar PV systems, not More information LTR Series Uninterruptible Power Systems 700 VA - 2.1 KVA. General Specification
08/17/12 Rev2 LTR Series General Specification 700 VA to 2.1 KVA 1.0 General LTR Series Uninterruptible Power Systems 700 VA - 2.1 KVA General Specification This specification describes the features and More information MOBILE FIRE - RESCUE DEPARTMENT FIRE CODE ADMINISTRATION
MOBILE FIRE - RESCUE DEPARTMENT FIRE CODE ADMINISTRATION Fire Pump Plan Review 2009 International Fire Code and NFPA 20 Date of Review / / BLD201 - Project Address: Project Name: Contractor s Business More information Interfacing Elevators with Fire Alarm and Sprinklers
Interfacing Elevators with Fire Alarm and Sprinklers IEEE Atlanta Chapter May 15, 2006 Brian K Fabel, PE Agenda Today s Codes NFPA, ASME, IBC/IFC Conflicts/Issues Tomorrow s Codes? Applicable Codes NFPA More information SECTION 16720 - FIRE AND SMOKE ALARM SYSTEM. City of San Diego, CWP Guidelines
PART 1 -- GENERAL 1.1 WORK OF THIS SECTION SECTION 16720 - City of San Diego, CWP Guidelines A. The WORK of this Section includes providing manual and automatic fire alarm and smoke detection systems meeting More information P 602. This generator set has been designed to meet ISO 8528 regulation. This generator set is manufactured in facilities certified to ISO 9001.
This generator set has been designed to meet ISO 88 regulation. This generator set is manufactured in facilities certified to ISO 900. This generator set is available with CE certification. Enclosed product More information ELECTRICAL GUIDELINES FOR SINGLE-FAMILY HOME OWNERS:
ELECTRICAL GUIDELINES FOR SINGLE-FAMILY HOME OWNERS: Chapter 12 of the Burlington Code of ordinances allows owner occupants of single family homes to do their own wiring if they choose. If you choose to More information MASTER ELECTRICIAN CODE EXAMINATION EXAMINATION REFERENCE MATERIAL AND CONTENT OUTLINE. Answers to sample questions: CONTENT OUTLINE
Answers to sample questions: Question Answer Reference 1 4 Section 362.12(6) 2 2 Table 310-16; 310.15(B)(2)(a) 3 4 Table. 250-66 4 2 Table 430.250 & 430.52 5 2 American Electrician Handbook, Figure 7-159 More information DELAWARE STATE FIRE MARSHAL FIRE ALARM SYSTEM CERTIFICATE OF INSTALLATION
Phone System Owner Phone System Engineered by: of Record Drawings: of System Manuals: of Test Reports: System Installer 1. GENERAL INFORMATION Phone Delaware License No: Certificate Holder No. System Supplier More information Building Permit Application
Building Permit Application Administrative Use Only PARENT PERMIT NUMBER (Required if part of another project) PERMITTEE: PERMITTEE ADDRESS: E-MAIL ADDRESS: ARCHITECT/ENGINEER: PHONE: PHONE: ARCHITECT/ENGINEER More information ASCO SERIES 185 Power Transfer Switches
ASCO SERIES 185 Power Transfer Switches 4-hour protection no matter when trouble strikes ASCO Series 185 Power Transfer Switches An Automatic Transfer Switch helps prevent... Your business or home from More information RESIDENTIAL ELECTRICAL REQUIREMENTS (REVISED 3/28/2008) PERMIT REQUIREMENTS:
RESIDENTIAL ELECTRICAL REQUIREMENTS (REVISED 3/28/2008) PERMIT REQUIREMENTS: Signed completed Electrical Permit application form. Minnesota law requires all electrical work is to be performed by licensed, More information Wiring for Health Care Facilities NEC Article 517
Wiring for Health Care Facilities NEC Article 517 I. General Scope: This article applies to electrical construction and installation criteria for facilities that provide services for human beings. II. More information Paralleling Switchgear
Paralleling Switchgear By Maurice D Mello, P.Eng. Systems Engineer, GE Consumer & Industrial, Canada What is Paralleling? Paralleling is the operation in which multiple power sources, usually two or more More information Element D Services Electrical
Service and PART 1 - GENERAL 1.01 OVERVIEW A. This Section includes design standards and requirements for electrical service and distribution. This is a design standard and is not intended to be used as More information ZENITH ZTS-MV MEDIUM VOLTAGE TRANSFER SWITCHGEAR
ZENITH ZTS-MV MEDIUM VOLTAGE TRANSFER SWITCHGEAR 1 RATING 1.1 The automatic switchgear shall be rated for a line voltage of, phase,, wire, Hertz with a maximum ampere rating of, interrupting current rating More information SECTION 16721 FIRE ALARM AND DETECTION SYSTEM
1. GENERAL 1.1. Related Documents: 1.2. Scope: 1.1.1. The general provisions of the Contract, including General and Supplementary Conditions and General Requirements apply to the work specified in this More information Fusible Disconnect Switch
Circuit Breakers Circuit breakers are used in panelboards and switchboards to provide circuit protection and provide a means of energizing and de-energizing a circuit. Siemens Sentron molded case circuit More information CyberFortress Data Center at Innovation Park Infrastructure and Topology Guide. Innovation Park Charlotte. NC 28262. DRAFT V0.
Innovation Park Charlotte. NC 28262 DRAFT V0.1 Page 2 CyberFortress Data Center at Innovation Park BECO South purchased Innovation Park in March 2010 and immediately launched a dramatic top-to-bottom $30M More information Unitil Energy Systems, Inc. Interconnection Standards For Inverters Sized Up To 100 kva
Unitil Energy Systems, Inc. Interconnection Standards For Inverters Sized Up To 100 kva Issued: August 2009 SIZED UP TO 100 KVA TABLE OF CONTENTS 1.0 Introduction... 1 1.1 Applicability... 1 1.2 Definitions... More information Electrical Grounding. Appendix C
Appendix C Electrical Grounding Low-Voltage Equipment Grounding The most frequently cited Office of Safety and Health Administration (OSHA) electrical violation is improper occupational grounding of equipment More information 2012 Canadian Electrical Code, Part I (CEC) Top Fifteen changes
2012 Canadian Electrical Code, Part I (CEC) Top Fifteen changes 1) Tamper resistant receptacles. 2009 CEC Required in dwelling units 2012 CEC Expanded to child care facilities First introduced in the 2009 More information Suitable for Emergency, Peak and Prime Power System Applications. Low Voltage Automatic Transfer Switch Systems
Suitable for Emergency, Peak and Prime Power System Applications Low Voltage Automatic Transfer Switch Systems THE POWER AUTHORITY THE POWER AUTHORITY ASCO s experience and commitment to excellence in More information Dennis Fire Department Fire Prevention Mark Dellner Fire Chief
Dennis Fire Department Fire Prevention Mark Dellner Fire Chief FIRE SAFETY INSPECTION GUIDELINES FOR COMMERCIAL PROPERTIES (MA Fire Prevention Regulations 527 CMR, MGL Chapter 148) FIRE PREVENTION CHECKLIST- More information UPS Applications and VRLA Battery Sizing
TECHNICAL BULLETIN 41-7334 UPS Applications and VRLA Battery Sizing 41-7334/0213/CD www.cdtechno.com The uninterruptable power system (UPS) is used to protect critical equipment and processes from the More information Commercial/Industrial Electricity
1 ELC 210 Commercial/Industrial Electricity Course Package Presented and Approved July 31, 2008 2 Contact person(s) DAVE WHITE Date of proposal to JULY 31, 2008 Curriculum Committee NEW COURSE PACKAGE More information FIRE SAFETY REGISTER. Premises Name: Premises Address: Fire Safety Manager: Contact No. Kerry County Fire Service www.kerrycoco.ie
FIRE SAFETY REGISTER Premises Name: Premises Address: Fire Safety Manager: Contact No. Kerry County Fire Service www.kerrycoco.ie 1 CONTENTS Section Title Page 1.0 Introduction 3 2.0 Guidance for the completion More information SECTION EMERGENCY GENERATOR
SECTION 26 32 13.13 EMERGENCY GENERATOR PART 1: GENERAL 1.01 SCOPE OF WORK A. Provide complete factory assembled generator set equipment with digital (microprocessor-based) electronic generator set controls, More information Module 4, Lesson 12 Fire Alarm Systems
Student Manual Module 4, Lesson 12 Fire Alarm Systems Performance Objectives At the conclusion of this lesson, you will be able to: Identify the components and functions of a fire alarm system and determine More information PLEASE NOTE. For more information concerning the history of these regulations, please see the Table of Regulations.
PLEASE NOTE This document, prepared by the Legislative Counsel Office, is an office consolidation of this regulation, current to August 1, 2013. It is intended for information and reference purposes only. More information Arc Terminator Active Arc-Resistant Switchgear
Arc Terminator Active Arc-Resistant Switchgear Increasing safety and productivity by extinguishing internal arcing faults within the switchgear. The Square D Arc Terminator from Schneider Electric offers More information Winnipeg Fire Department Fire Prevention Branch
Winnipeg Fire Department Fire Prevention Branch Manitoba Fire Code Life-Safety Equipment Maintenance Requirements The Fire Prevention Branch of the Winnipeg Fire Department has prepared this document of More information MISCELLANEOUS ELECTRICAL JOBS REQUIRING PERMITS
MISCELLANEOUS ELECTRICAL JOBS REQUIRING PERMITS 01. SAFETY INSPECTION of service equipment at FPL Power Source 02. Construction GFI power outlets (Temp Pole for Construction) 03. 90 day temporary power More information Fire Alarm System Standpipes Sprinkler Systems Fire Drills Commercial Cooking Hood and more
FIRE PROTECTION SYSTEMS Fire protection systems, measures and equipment are all related to the safety of the occupants and the protection of the property. As part of a building design and its intended More information SmartPro 230V 3kVA 2.25kW Line-Interactive UPS, Extended Run, SNMP, Webcard, Tower, USB, DB9 Serial
SmartPro 230V 3kVA 2.25kW Line-Interactive UPS, Extended Run, SNMP, Webcard, Tower, USB, DB9 Serial MODEL NUMBER: SMARTINT3000VS Highlights 3kVA / 3000VA / 2250W line interactive tower UPS system 230V More information SECTION (16289) - SURGE PROTECTION FOR LOW VOLTAGE ELECTRICAL POWER CIRCUITS
SECTION 26 43 13 (16289) - SURGE PROTECTION FOR LOW VOLTAGE ELECTRICAL POWER CIRCUITS PART 1 GENERAL 1.01 SUMMARY A. Section Includes: 1. Transient Voltage Surge Suppressors for Low-Voltage Power, Control, More information INDUSTRY WIDE LABOR-MANAGEMENT SAFETY COMMITTEE SAFETY BULLETIN #23
INDUSTRY WIDE LABOR-MANAGEMENT SAFETY COMMITTEE SAFETY BULLETIN #23 GUIDELINES FOR WORKING WITH PORTABLE POWER DISTRIBUTION SYSTEMS AND OTHER ELECTRICAL EQUIPMENT "ADDENDUM C" WORKING WITH 480 VOLT SYSTEMS More information PORTABLE GENERATORS AND OSHA CONSTRUCTION REGULATIONS
PORTABLE GENERATORS AND OSHA CONSTRUCTION REGULATIONS Monograph by: John Grizzy Grzywacz, Professor OSHA National Training Institute Arlington Heights, Illinois Contributing: Michael Kovacic, President More information DOMESTIC ELECTRICAL INSTALLATION CERTIFICATE (Requirements for Electrical Installations BS 7671 IEE Wiring Regulations)
DOMESTIC ELECTRICAL INSTALLATION CERTIFICATE (Requirements for Electrical Installations BS 7671 IEE Wiring Regulations) DETAILS OF THE CLEINT Client and address ADDRESS OF THE INSTALLATION Installation More information Bulletin Swimming pool, hot tub and spa installations Section 68 Issued August 2013 Supersedes Bulletin
Bulletin 68-7-9 Swimming pool, hot tub and spa installations Section 68 Issued August 2013 Supersedes Bulletin 68-7-8 Scope (1) Swimming pools - general (2) Grounding & bonding (a) Bonding for pool structures More information MONTGOMERY COUNTY EXECUTIVE REGULATION Offices of the County Executive. 101 Monroe Street. Rockville, Maryland 20850
Montgomery County Regulation on: ADOPTION OF THE 2008 NATIONAL ELECTRICAL CODE DEPARTMENT OF PERMITTING SERVICES Issued by County Executive Regulation # 15-09 Authority: Code Section 17-2 and 17-3 Supersedes: More information 2017 © DocPlayer.net Privacy Policy | Terms of Service | Feedback