Source: http://businessdocbox.com/Construction/84908880-1-2-references-1-csa-c22-2-no-0-3-test-methods-for-electrical-wires-and-cables.html
Timestamp: 2020-04-07 19:03:39
Document Index: 70772500

Matched Legal Cases: ['ART 1', 'ART 2', 'ART 3', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'art 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'art 7', 'art 7', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 7', 'ART 7', 'ART 1', 'ART 1']

1.2 REFERENCES.1 CSA C22.2 No.0.3, Test Methods for Electrical Wires and Cables. - PDF Free Download
1.2 REFERENCES.1 CSA C22.2 No.0.3, Test Methods for Electrical Wires and Cables.
Download "1.2 REFERENCES.1 CSA C22.2 No.0.3, Test Methods for Electrical Wires and Cables."
1 Issued 2005/06/01 Section Wire and Cables (0 1000V) Page 1 of 5 PART 1 GENERAL 1.1 RELATED SECTIONS.1 Section Wire and Box Connectors REFERENCES.1 CSA C22.2 No.0.3, Test Methods for Electrical Wires and Cables..2 CAN/CSA C22.2 No. 131, Type TECK 90 Cable. 1.3 PRODUCT DATA.1 Submit product data in accordance with Section Submittal Procedures. PART 2 PRODUCTS 2.1 BUILDING WIRES.1 Conductors: stranded for 10 AWG and larger. Minimum size: 12 AWG..2 Copper conductors: size as indicated, with 600 V insulation of chemically cross linked thermosetting polyethylene material rated RW90 and RWU90 as indicated. Provide RWU90 rated cable for underground wiring..3 Copper conductors: size as indicated, with thermoplastic insulation type TWH rated at Neutral supported cable: 3 phase insulated conductors of aluminum and one neutral conductor of aluminum steel reinforced, size as indicated. Insulation: Type NSF 2 flame retardant rated TECK Cable.1 Cable: to CAN/CSA C22.2 No Conductors:.1 Grounding conductor: copper..2 Circuit conductors: copper, size as indicated..3 Insulation:.1 Type: ethylene propylene rubber..2 Chemically cross linked thermosetting polyethylene rated type RW90, Inner jacket: polyvinyl chloride material.
2 Issued 2005/06/01 Section Wire and Cables (0 1000V) Page 2 of 5.5 Armour: interlocking..6 Overall covering: thermoplastic polyvinyl chloride material..7 Fastenings:.1 One hole steel straps to secure surface cables 50 mm and smaller. Two hole steel straps for cables larger than 50 mm..2 Channel type supports for two or more cables at 1500 mm centers..3 Threaded rods: 6 mm dia. to support suspended channels..8 Connectors:.1 Watertight and/or type approved for TECK cable. 2.3 MINERAL INSULATED CABLES.1 Conductors: solid bare soft annealed copper, size as indicated..2 Insulation: compressed powdered magnesium oxide to form compact homogeneous mass throughout entire length of cable..3 Overall covering: annealed seamless copper sheath, Type M1 rated 600 V, 250EC..4 Overall covering: annealed seamless copper sheath type LWM1 rated 600 V, 250EC..5 Outer jacket: PVC applied over sheath where required..6 Two hour fire rating..7 Connectors: standard as required..8 Termination kits: standard as required. 2.4 ARMOURED CABLES.1 Conductors: insulated, copper, size as indicated..2 Type: AC90..3 Armour: interlocking type fabricated from aluminum strip..4 Type: ACWU90 flame retardant jacket over armour meeting requirements of Vertical Tray Fire Test of CSA C22.2 No. 0.3 with maximum flame travel of 1.2 m..5 Connectors: standard as required. 2.5 ALUMINUM SHEATHED CABLE.1 Conductors: copper, size as indicated.
3 Issued 2005/06/01 Section Wire and Cables (0 1000V) Page 3 of 5.2 Insulation: type RA90 rated Sheath: aluminum applied to form continuous corrugated sheath..4 Outer jacket of PVC applied over sheath for direct burial or wet locations..5 Fastenings for aluminum sheathed cable:.1 One hole steel straps to secure surface cables 25 mm and smaller. Two hole steel straps for cables larger than 25 mm. Use aluminum strap only with single conductor cable..2 Channel type supports for two or more cables at 1500 mm centers..3 Threaded rods: 6 mm dia. to support suspended channels. 2.6 CONTROL CABLES.1 Type LVT: 2 soft annealed copper conductors, sized as indicated, with thermoplastic insulation, outer covering of thermoplastic jacket.low energy 300 V control cable: stranded annealed copper conductors sized as indicated, with PVC insulation type TW 40EC polyethylene insulation with shielding of tape coated with paramagnetic material wire braid over each conductor and overall covering of PVC jacket NON METALLIC SHEATHED CABLE.1 Non metallic sheathed copper cable type: NMD 7 nylon, size as indicated. PART 3 EXECUTION 3.1 INSTALLATION OF BUILDING WIRES.1 Install wiring as follows:.1 In conduit systems in accordance with Section Conduits, Fastenings and Fittings..2 In cable troughs in accordance with Section Cabletroughts..3 In underground ducts in accordance with Section Installation of Cables in Ducts..4 In trenches in accordance with Section Installation of Cables in Trenches..5 In underfloor distribution system in accordance with Section Underfloor Distribution System.6 In cellular floor raceways in accordance with Section Cellular Floor Raceway..7 In surface and lighting fixture raceways in accordance with Section Lighting..8 In wireways and auxiliary gutters in accordance with Section Wireways and Auxiliary Gutters.
4 Issued 2005/06/01 Section Wire and Cables (0 1000V) Page 4 of 5.9 Overhead service conductors in accordance with Section Service Equipment. 3.2 INSTALLATION OF TECK CABLE V.1 Install cables..1 Group cables wherever possible on channels..2 Install cable in trenches in accordance with Section Lay cable in cabletroughs in accordance with Section Terminate cables in accordance with Section Wire and Box Connectors INSTALLATION OF MINERAL INSULATED CABLES.1 Install cable in trenches in accordance with Section Run cable exposed, securely supported by straps..3 Support 2 h fire rated cables at 1m intervals..4 Make cable terminations by using factory made kits..5 At cable terminations use thermoplastic sleeving over bare conductors..6 Install cable in cabletroughs in accordance with Section Where cables are buried in cast concrete or masonry, sleeve for entry and exit of cables..8 Do not splice cables. 3.4 INSTALLATION OF ARMOURED CABLES.1 Group cables wherever possible..2 Install cable in trenches in accordance with Section Lay cable in cabletroughs in accordance with Section Terminate cables in accordance with Section Wire and Box Connectors INSTALLATION OF ALUMINUM SHEATHED CABLE.1 Group cables wherever possible on channels..1 Install cable in trenches in accordance with Section Lay cable in cabletroughs in accordance with Section
5 Issued 2005/06/01 Section Wire and Cables (0 1000V) Page 5 of 5.3 Terminate cables in accordance with Section Wire and Box Connectors INSTALLATION OF CONTROL CABLES.1 Install control cables in conduit, under floor raceways, cable troughs and underground ducts by direct burial as indicated..2 Ground control cable shield. 3.7 INSTALLATION OF NON METALLIC SHEATHED CABLE.1 Install cables..2 Install straps and box connectors to cables as required. END OF SECTION
SECTION WIRE, CABLE AND BUSWAYS. A. This section specifies providing wire, cable and busways.
SECTION 16120 WIRE, CABLE AND BUSWAYS PART 1 - GENERAL 1.01 DESCRIPTION: A. This section specifies providing wire, cable and busways. B. Definitions: 1. Cable: Cable having low smoke generating characteristics.
ELECTRICAL SAFETY Information Bulletin March 2014 CEC-12 [rev-6] Page 1 of 6 CANADIAN ELECTRICAL CODE SUBJECT: Section 12 Wiring Methods Conductors General Insulation Thickness on Conductors Used in Ungrounded
CONSTRUCTION SPECIFICATION FOR CABLE INSTALLATION
ONTARIO PROVINCIAL STANDARD SPECIFICATION METRIC OPSS 604 NOVEMBER 2004 CONSTRUCTION SPECIFICATION FOR CABLE INSTALLATION TABLE OF CONTENTS 604.01 SCOPE 604.02 REFERENCES 604.03 DEFINITIONS - Not Used
PV Solar Wiring Solutions
Priority Solar Projects Across the US 14 DISTRIBUTION CENTERS PV Solar Wiring Solutions ON TIME ACCURATE FLEXIBLE SERVICE CUSTOM SOLUTIONS Priority Capabilities: Premier Supplier of Wire & Cable Cut to
CONSTRUCTION SPECIFICATION FOR INSTALLATION OF CABLE
ONTARIO PROVINCIAL STANDARD SPECIFICATION METRIC OPSS 604 NOVEMBER 2008 CONSTRUCTION SPECIFICATION FOR INSTALLATION OF CABLE TABLE OF CONTENTS 604.01 SCOPE 604.02 REFERENCES 604.03 DEFINITIONS - Not Used
NORMAS DE REFERENCIA AEIC CS 1: ASTM B
AEIC CS 1: Especificación para Solid-Type Impregnated-Paper-Insulated Metallic Sheathed AEIC CS2: Especificación para Impregnated-Paper and Laminated Paper- Polypropylene Insulated, High- Pressure Pipe-Type
Building Wire CARRYING YOUR ELECTRICITY
Building Wire CARRYING YOUR ELECTRICITY Our Commitment Our commitment to our customers is simple - we deliver even when others can t. As one of Canada s largest wire, cable and data communication distributors
The Contractor shall furnish and install all shielded power cable suitable for use on this project.
Section 16122 PRIMARY POWER CABLES PART 1 GENERAL: WORK INCLUDED The Contractor shall furnish and install all shielded power cable suitable for use on this project. RELATED WORK Section 16020: Tests SUBMITTALS
SECTION GROUNDING AND BONDING
SECTION 16060 PART 1 GENERAL 1.01 DESCRIPTION A. Section includes requirements for an electrical grounding system, including electrodes, grounding rods, connectors, insulators, equipment grounding and
AFC Cable Systems, Inc. Product Specification This product specification is written according to the Construction Specifications Institute MasterFormat, 2014 Update. SECTION 260519.13 METAL CLAD CABLE-MC
*** Supercedes: BECO E and COM , , & ***
7/27/09 Page 1 of 9 R5 *** Supercedes: BECO E2.9-27.4 and COM 1-0696, 2-0196, & 5-0385 *** 1.0 Scope #2 AWG to 1000 KCMIL CONCENTRIC NEUTRAL JACKETED CABLES RATED 5-35 kv These Specifications cover single
ONTARIO PROVINCIAL STANDARD SPECIFICATION OPSS.PROV 604 NOVEMBER 2017 CONSTRUCTION SPECIFICATION FOR INSTALLATION OF CABLE TABLE OF CONTENTS 604.01 SCOPE 604.02 REFERENCES 604.03 DEFINITIONS - Not Used
TS 804 CABLES TABLE OF CONTENTS TRAFFIC SIGNAL EQUIPMENT POLE WIRING DIAGRAM LOCATIONS WITH CENTRE MEDIANS
TORONTO TRANSPORTATION January 2012 TS 804 CABLES TABLE OF CONTENTS 1. DRAWINGS TTD 804.001 TTD 804.002 TTD 804.003 TTD 804.005 TTD 804.006 TTD 804.007 TTD 804.010 TTD 804.015 TTD 804.020 TTD 804.025 TTD
SECTION WIRE AND CABLE Raceways and Conduit Motor Power and Control Wiring.
SECTION 16120 WIRE AND CABLE PART 1 GENERAL 1.01 SUMMARY A. Related Sections: 1. 16112 - Raceways and Conduit. 2. 16155 - Motor Power and Control Wiring. 1.02 SYSTEM DESCRIPTION A. Performance Requirements:
The City of Winnipeg Common Work Results For Electrical Section Specification Page 1 of 9 Bid Opportunity No
The City of Winnipeg Common Work Results For Electrical Section 260501 Specification Page 1 of 9 PART 1 - GENERAL 1.1 Related Sections.1 This section covers items common to sections of Division 26..2 The
WIRE AND CABLE Raceways and Conduit Motor Power and Control Wiring.
SECTION A. ASTM B3 - Standard Specification for Soft or Annealed Copper Wire; 2013.
PART 1 GENERAL 1.1 SECTION INCLUDES SECTION 26 0519 A. Single conductor building wire. B. Metal-clad cable. C. Wiring connectors. D. Electrical tape. E. Wire pulling lubricant. F. Cable ties. 1.2 RELATED
SECTION GROUNDING AND BONDING FOR ELECTRONIC SAFETY AND SECURITY
PART 1 - GENERAL 1.1 DESCRIPTION SECTION 28 05 26 GROUNDING AND BONDING FOR ELECTRONIC SAFETY AND SECURITY SPEC WRITER NOTE: Delete // // if not applicable to project. Also delete any other item or paragraph
Pan Am Pool Section Electrical Distribution Upgrade Page 1 Bid Opportunity November 2013 COMMON WORK RESULTS FOR ELECTRICAL
Pan Am Pool Section 26 05 00 Electrical Distribution Upgrade Page 1 COMMON WORK RESULTS FOR ELECTRICAL Part 1 General 1.1 SUMMARY.1 Section Includes:.1 General requirements that are common to NMS sections
Kaf-Tech Product Specification
Kaf-Tech Product Specification This product specification is written according to the Construction Specifications Institute MasterFormat, 2014 Update. SECTION 260519.13 METAL CLAD CABLE-LUMINARY CABLE
Section ARMORED MEDIUM VOLTAGE CABLES SHIELDED 3 CONDUCTOR POWER CABLE - INTERLOCKED ARMOR
PART 1 - GENERAL Section 26 05 15 SHIELDED 3 CONDUCTOR POWER CABLE - INTERLOCKED ARMOR 1.1 Cable shall be 15 kv, shielded, three conductor with ground, stranded copper, with continuously welded and corrugated
SECTION MEDIUM-VOLTAGE CABLES PART 1 GENERAL
SECTION 260513 - MEDIUM-VOLTAGE CABLES PART 1 GENERAL 1.1 SECTION INCLUDES A. Medium voltage cable. B. Cable terminations. C. This specification describes single conductor EPR (Ethylene-propylene-rubber)
3. Intermediate metal conduit (IMC). 4. Electric metallic tubing (EMT). 5. Flexible metal conduit (FLEX). 6. Polyvinyl chloride conduit (PVC).
SECTION 16111 CONDUITS PART 1 - GENERAL 1.01 DESCRIPTION A. General: Provide conduits, complete, as shown, specified or required per Contract Documents. Principal items include: 1. Rigid aluminum conduit.
DIVISION 26 RACEWAYS AND BOXES FOR ELECTRICAL SYSTEMS PART 1 - GENERAL RELATED DOCUMENTS
PART 1 - GENERAL 01.01 RELATED DOCUMENTS A. Drawings and general provisions of Contract, including General and Supplementary Conditions and Division 1 Specification sections, apply to work of this Section.
NEC 2014 Code Changes Articles 280.21-300.50 CHANGES FROM 2011 TO 2014 CODE ARE IN RED Chapter 2 - Wiring and Protection ARTICLE 280 Surge Arresters, Over 1000 volts II. Instillation III. Connecting Surge
Cables ELE E L CT E C R T R IC I C A A L L
E LECTRICAL ELECTRICAL Cables July 28, 2009 CONDUMEX INCORPORATED WIRE & CABLE PRODUCT INDEX BUILDING WIRE MTW/THHN/THWN 600 VOLTS COPPER 14 AWG SOLID 750 MCM STRANDED UL 83 XHHW-2 600 VOLTS COPPER 14
SECTION 16450 GROUNDING PART 1 - GENERAL 1.1 DESCRIPTION A. This section specifies general grounding and bonding requirements of electrical and telecommunication installations for personnel safety, equipment
SECTION 26 05 26 - GROUNDING AND BONDING FOR ELECTRICAL SYSTEMS PART 1 - GENERAL 1.1 RELATED DOCUMENTS A. Drawings and general provisions of the Contract, including General and Supplementary Conditions
SPECIFICATION FOR THHN/THWN-2/THW/THWN/TW ARROW ROUTE, FONTANA CA
SPECIFICATION FOR THHN/THWN-2/THW/THWN/TW THHN/THWN-2/THW/THWN/TW Listed E-492385 / E-472248 APPLICATIONS THHN/THWN-2 building wire is primarily used for general purpose applications in conduit and cable
YF /8" YF /2" YF /4"
Wire Over-Braided Flexible Conduit ( YF-705 ) most suitable for demanding industrial wiring applications. *Galvanized steel helically wound with PVC coating and wire over-braid. *Trade size: 3/8"~2" (square
A. American Society for Testing and Materials (ASTM): Specification for Concentric-Lay-Stranded Copper Conductors, Hard, Medium-Hard or Soft.
SECTION 260000 ELECTRICAL PART 1- GENERAL 2.1 SUMMARY : Provide complete distribution systems for electrical power as shown on the drawings or required by other sections of these specifications. A. Work
GLENWOOD PLACE 2 MAR 2015
PART 1 - GENERAL 1.01 SUMMARY: SECTION 16110 RACEWAYS A. Description: 1. Provide continuous conduit systems - beginning at the service point, to all distribution equipment and to every outlet and piece
SECTION WIRES AND CABLES
SECTION 16120 - WIRES AND CABLES PART 1 - GENERAL 1.01 RELATED DOCUMENTS A. General: Drawings and general provisions of the Contract, including General and Supplementary Conditions and Division 1 Specification
SECTION 16060 GROUNDING AND BONDING PART 1 - GENERAL 1.1 RELATED DOCUMENTS A. Drawings and general provisions of the Contract, including General and Supplementary Conditions and Division 1 Specification
DESIGN GUIDELINES WIRING AND CONDUITS PAGE 1 of 7
DESIGN GUIDELINES WIRING AND CONDUITS PAGE 1 of 7 1.1. REFERENCE STANDARDS 1.1.1. Publications listed below (including amendments, addenda, revisions, supplements and errata) form a part of this specification
26/35kV Copper XLPE Insulation Electric Cable
26/35kV Copper XLPE Insulation Electric Cable Specifications 1.1~35kv XLPE insulated power cable 2.Standard: IEC,VDE,BS,UL,AS/NZS Black PVC sheath XLPE insulated armored copper power cable YJV22 YJV32
USACE / NAVFAC / AFCEC / NASA UFGS-26 05 19.10 10 (May 2016) ----------------------------------- Preparing Activity: USACE Superseding UFGS-26 05 19.00 10 (November 2008) UNIFIED FACILITIES GUIDE SPECIFICATIONS
SECTION 26 0526 - GROUNDING AND BONDING FOR ELECTRICAL SYSTEMS PART 1 - GENERAL 1.1 RELATED DOCUMENTS A. Drawings and general provisions of the Contract, including General and Supplementary Conditions
System No. C-AJ-8073 September 07, 2004 F Rating 2 Hr T Ratings 0, 3/4 and 2 Hr C-AJ-8073 1 of 5 1. Floor or Wall Assembly Min 4-1/2 in. thick reinforced normal weight (140-150 pcf) concrete. Wall may
SECTION INSULATED WIRE AND CABLE
SECTION 16120 INSULATED WIRE AND CABLE PART 1 GENERAL 1.01 DESCRIPTION A. This section covers the contract item Insulated Wire and Cable, which includes the following items with accessories, and appurtenances:
CONSTRUCTION SPECIFICATION FOR GROUNDING
ONTARIO PROVINCIAL STANDARD SPECIFICATION METRIC OPSS 609 NOVEMBER 2001 CONSTRUCTION SPECIFICATION FOR GROUNDING TABLE OF CONTENTS 609.01 SCOPE 609.02 REFERENCES 609.03 DEFINITIONS - Not Used 609.04 DESIGN
A. All materials shall be listed by an OSHA approved Nationally Recognized Testing Laboratory (NRTL).
16120 WIRE AND CABLE ************************************************************************************************************* SPECIFIER: CSI MasterFormat 2004 number: 26 05 19 An optional keynote
SECTION 260526 - GROUNDING AND BONDING FOR ELECTRICAL SYSTEMS PART 1 - GENERAL 1.1 RELATED DOCUMENTS A. Drawings and general provisions of the Contract apply to this Section. 1.2 SUMMARY A. This Section
WIRING METHODS CHAPTER 38
CHAPTER 38 WIRING METHODS SECTION E3801 GENERAL REQUIREMENTS E3801.1 Scope. This chapter covers the wiring methods for services, feeders and branch circuits for electrical power and distribution. E3801.2
System No. SP777 (FOR HORIZONTAL OR VERTICAL SEPARATIONS)
System No. SP777 (FOR HORIZONTAL OR VERTICAL SEPARATIONS) F Rating - hr FT Rating - 0, /, 1 and 1-1/ hr (See Item ) FH Rating - hr FTH Rating - 0, /, 1 and 1-1/ hr (See Item ) A B A B C C SECTION A-A CONFIGURATION
BASIC CONCEPTS IN ELECTRICAL DESIGN. Prepared by Engr. John Paul Timola
BASIC CONCEPTS IN ELECTRICAL DESIGN Prepared by Engr. John Paul Timola ELECTRICAL CONDUCTORS AND INSULATORS Electrical Conductors substances that offer a very low resistance to current flow. Insulators
PART 1 - GENERAL 1.1 RELATED DOCUMENTS SECTION 25 05 26 GROUNDING AND BONDING A. Drawings and general provisions of the Contract, including General and Supplementary Conditions and Division 1 Specification
Title: YALE OFFICE OF FACILITIES PROCEDURE MANUAL Chapter: 01 - Yale Design Standard Division: Electrical Standards
Date Description of Change Pages / Sections Modified ID 6/15/16 Updated format, division title, and removed references to other sections. - mgl44 A. Summary This section contains design criteria for the
Conductor Shield A combination of semi-conducting tape and extruded thermosetting semi-conducting material meeting UL 1309, IEEE 1580 and UL1072.
37-105VFD MMV-VFD Power Cable Three : kv - 15kV 133% Level Rated 90 C s (3) Soft annealed flexible stranded tinned copper per IEEE 150 Table 11. Extruded thermosetting 90 C Ethylene Propylene Rubber (EPR),
6. SECONDARY SERVICES (under 600 volts) 6.1 AVAILABILITY For the electrical characteristics of available secondary services see Section 3.4.
6. SECONDARY SERVICES (under 600 volts) 6.1 AVAILABILITY For the electrical characteristics of available secondary services see Section 3.4. 6.2 OVERHEAD SERVICES Wiring of any premises for connection
Change History Date Description of Change Pages / Sections Modified Change Approver Initials 6/15/16 Updated division section from 16124 to 2605 - mgl44 13, removed references to other section 10/17/14
Una e mpre sa Vi akab l e GLOSSARY.
GLOSSARY www.centelsa.com.co CONDUCTORS Cu Copper conductors. CuSn Tinned copper conductor. ACDSR Rectangular soft bare copper wire. ACDSRP Paper insulated rectangular soft bare copper wire. ACDD Bare
SECTION RACEWAYS
SECTION 16110 RACEWAYS PART 1 GENERAL 1.1 SYSTEM DESCRIPTION A. Provide a complete raceway system suitable for receiving wire and cable and continuous from outlet to outlet. System shall be complete with
CONSTRUCTION SPECIFICATION FOR THE INSTALLATION OF SIGN LUMINAIRES
ONTARIO PROVINCIAL STANDARD SPECIFICATION METRIC OPSS 612 SEPTEMBER 1984 CONSTRUCTION SPECIFICATION FOR THE INSTALLATION OF SIGN LUMINAIRES 612.01 SCOPE 612.02 REFERENCES 612.03 Not Used 612.04 Not Used
The General Provisions of the Contract, including General, Supplementary and Special Conditions, apply to the work specified in this Section.
SECTION 16450 - ELECTRICAL WIRING PART 1 - GENERAL 1.01 RELATED DOCUMENTS The General Provisions of the Contract, including General, Supplementary and Special Conditions, apply to the work specified in
SECTION ELECTRICAL SITE UTILITIES
SECTION 16402 ELECTRICAL SITE UTILITIES PART 1 GENERAL 1.01 SUMMARY A. Section Includes: Electrical site utilities and coordination of requirements with the utility company and service specifications.
DRAFT TANZANIA STANDARD. Part 7: Underground Power Cables for rated voltages 0.6kV/1kV (Um 1.2kV)
EDC3 (5239) P3 Mini-Grid Systems DRAFT TANZANIA STANDARD Part 7: Underground Power Cables for rated voltages 0.6kV/1kV (Um 1.2kV) TANZANIA BUREAU OF STANDARDS TBS 2017 First Edition 2017 Table of Contents
600 VOLT 600V, 3 CONDUCTOR (WITH GROUND), FR-EPR OR FR-XLPE INSULATION, PVC JACKET SPECIFICATIONS (FLAME RETARDANT POWER CABLE) (UL TYPE TC-ER) TYPE C3 SPEC 70.0100 PROJECT 196116 REFERENCE: LATEST EDITIONS
SOUTH CAROLINA ELECTRIC COOPERATIVES' PRIMARY UNDERGROUND POWER CABLE SPECIFICATION
SOUTH CAROLINA ELECTRIC COOPERATIVES' PRIMARY UNDERGROUND POWER CABLE SPECIFICATION 1.0 SCOPE 1.1 This specification covers the construction, mechanical, and electrical requirements of single conductor,
1. Approved Manufacturers: Carlon Electrical Products, Cantex, or approved equal.
PART 1: GENERAL 1.01 Scope of Standard A. This standard provides general guidance concerning the specific preferences of Texas State University for for Electrical System. B. Texas State University recognizes
A. Section Includes: Electrical site utilities and coordination of requirements with the utility company and service specifications.
16402 ELECTRICAL SITE UTILITIES ************************************************************************************************************* SPECIFIER: CSI MasterFormat 2004 number: 33 50 00. *************************************************************************************************************
Standard of Practice - Campus Electrical Distribution System
A26.3 Standard of Practice - Campus Electrical Distribution System NOTE: Significant revisions or additions to the previous standards are highlighted in italics. GENERAL Designers shall verify that all
SECTION ELECTRICAL CABLE. 1. Trench excavation, backfill, and compaction; Section
02735-1 of 5 SECTION 02735 ELECTRICAL CABLE 02735.01 GENERAL A. Description Electrical cable installation shall include, but not necessarily be limited to, furnishing and placing electrical cable as shown
System No. C-AJ-8048
System No. C-AJ-8048 F Rating - 2 Hr T Ratings - 0, 1/2, 3/4, 1 and 1-1/2 Hr (See Item 2) L Rating At Ambient Less Than 1 CFM / Sq. Ft. L Rating At 400 F 5 CFM / Sq. Ft. System No. C-AJ-8048 System No.
SECTION 26 05 26 GROUNDING AND BONDING FOR ELECTRICAL SYSTEMS PART 1 GENERAL 1.1 DESCRIPTION A. Scope: 1. CONTRACTOR shall provide labor, materials, equipment, and incidentals as shown, specified, and
B. Provide a complete conduit system with associated couplings, connectors, and fittings.
SECTION 26 05 33 PART 1 - GENERAL 1.01 WORK INCLUDED A. Comply with the provisions of Sections 260500. B. Provide a complete conduit system with associated couplings, connectors, and fittings. 1.02 RELATED
SECTION LOW-VOLTAGE ELECTRICAL POWER CONDUCTORS AND CABLES (24 Volt AC/DC or Less)
SECTION 260523 LOW-VOLTAGE ELECTRICAL POWER CONDUCTORS AND CABLES (24 Volt AC/DC or Less) PART 1 - GENERAL 1.1 SUMMARY A. Related Documents: 1. Drawings and general provisions of the Subcontract apply
Engineering Data for Copper and Aluminum Conductor Electrical Cables
2018 Edition Engineering Data for Copper and Aluminum Conductor Electrical Cables THE OKONITE COMPANY Okonite Cables...A higher Standard! The Okonite Company, 2018 Okonite Cables Table of Contents SECTION
SECTION A. Underwriters Laboratories, Inc., listed and NEC approved
PART 1 GENERAL 1.01 DESCRIPTION A. Provide all raceways, fittings, and boxes of specified type required for complete project. Install all systems in raceways unless specifically noted otherwise. Provide
Article 324: Flat Conductor Cable (FCC) 1.! Type FCC (flat conductor cable) cable wiring system is designed for installations under.
Part F: Code Book Questions Article 324: Flat Conductor Cable (FCC) 1.! Type FCC (flat conductor cable) cable wiring system is designed for installations under.! (a) tile! (c) carpet squares! (b) carpet!
FieldLink for PROFIBUS Applications
FieldLink for PROFIBUS s The Automation & Drives business unit of LEONI has developed FieldLink bus cables in accordance with the PROFIBUS specifications. The FieldLink bus cable product range for PROFIBUS
SECTION EARTHING AND EARTH FAULT PROTECTION
SECTION 16660 PART 1 - GENERAL 1.01 DESCRIPTION A. The work to be performed includes, but is not necessarily limited to, all work involved with the construction and assembly of a complete electrical earthing
Suggested Specifications for Service Entrance Fittings All service fittings shall be approved for the purpose by a nationally recognized testing laboratory, inspection agency or product evaluation organization.
New Conduit Specification
New Conduit Specification Combines Portions of Sections 715, 783 & 992 into New Section 630. Coordinated Effort Between Traffic Operations, ITS, Lighting, Construction, and Industry New Conduit Specification
TI 20 PVC TI 20 INSULATED TELEPHONE WIRE
TI 20 PVC TI 20 INSULATED TELEPHONE WIRE Standard: Nominal voltage: Temperature range - fixed laying: Cable Structure: Application: Packing: 2x0,5 0,4 2,6 3,6 7,2 2x0,6 0,4 2,8 5,2 9,1 2x0,8 0,4 3,2 9,2
CONSTRUCTION SPECIFICATION FOR TRAFFIC ACTUATION EQUIPMENT
ONTARIO PROVINCIAL STANDARD SPECIFICATION METRIC OPSS 623 JANUARY 1990 CONSTRUCTION SPECIFICATION FOR TRAFFIC ACTUATION EQUIPMENT 623.01 SCOPE 623.02 REFERENCES 623.05 MATERIALS TABLE OF CONTENTS 623.05.01
Selection of the Correct Optical Cable Outer Jacket for the Application
Application Notes Selection of the Correct Optical Cable Outer Jacket for the Application Issued December 2012 Abstract The cable jacket provides the first line of defense against the surrounding environment.
Change History Date Description of Change Pages / Sections Modified Change Approver Initials 8/1/17 Update sections Materials and Special Requirements 3 F. 2. 4 H. 2.; 10. & 11(added) 6/15/16 Updated division
8. REVENUE METERING. Operational Excellence Model. 8.1 Introduction
8. 8.1 Introduction The purpose of this section is to outline requirements of the customer, as set forth herein by PSEG Long Island, as they pertain to Electric Revenue Metering at Primary and Secondary
CONSULTANT PROCEDURES & DESIGN GUIDELINES Electrical Manholes and Handholes UNIVERSITY OF MISSOURI
GENERAL: The scope of this document is to provide instruction for the installation of concrete electric manholes. DESIGN GUIDELINES: 1. Materials for Manhole 1.1. Cast-in-Place or Pre-Cast concrete may
15 kv EPR Insulated, Jacketed, URD Cable
15 kv EPR Insulated, Jacketed, URD Cable 1000 kcm Copper Conductor with Tape Shield Page 1 of 11 Table Of Contents 1 GENERAL... 3 2 STANDARDS... 3 3 APPROVED CABLE MANUFACTURERS... 3 4 REEL SPECIFICATIONS...
PRODUCT SELECTION LOCATOR
PRODUCT SELECTION LOCATOR SECTION SPECIFICATION 1 300V Instrumentation Cables 1000 2 600V Instrumentation Cables 2000 3 600V Flexible Control and Power Cables 3000 4 600V Multi Conductor Control and Power
This section applies to the design and installation relating to wire and cable systems and terminations. 16G Figure 1 16G Figure 2
Wire, Cable and Terminations Basis of Design This section applies to the design and installation relating to wire and cable systems and terminations. Design Criteria Medium Voltage Review and modify the
System No. C-AJ-8096
F Rating -- Hr T Rating -- 0, / and Hr (See Item ) B B E E G G F F A A C C D D 4B 4A SECTION A-A SECTION B-B July 0, 005 Page: of 5 F Rating -- Hr T Rating -- 0, / and Hr (See Item ) B A SECTION C-C SECTION
PART 7 Technical Specification for Overhead and Underground Service Connection works for the Year
PART 7 Technical Specification for Overhead and Underground Service Connection works for the Year 2016-17 Technical Specification for Overhead and Underground Service Connection works for the Year 2016-17
CITY OF OCEANSIDE. Electrical Lines, Plumbing and Mechanical Burial & Support Requirements. Informational Bulletin
Electrical Lines, Plumbing and Mechanical Burial & Support Requirements Informational Bulletin MINIMUM BURIAL DEPTH REQUIREMENTS 2016 CALIFORNIA ELECTRICAL CODE (CEC) Burial depth shall be per Table 300.5,
A. Product Data: For surface pathways, wireways and fittings, floor boxes, hinged-cover enclosures, and cabinets.
ALLIANT ENERGY CENTER PAVILIONS Project No. 2013 027 SECTION 27 05 28 - PART 1 - GENERAL 1.1 RELATED DOCUMENTS A. Drawings and general provisions of the Contract, including General and Supplementary Conditions
NEC Ampacity Data Table (B)(2)(b) Ambient Temperature Correction Factors Based on 40 C (104 F)
05-01-2018 NEC Ampacity Data Table 310.15(B)(2)(b) Ambient Temperature Crection Facts Based on 40 C (104 F) F ambient temperatures other than 40 C (104 F), multiply the allowable ampacities specified in
CONDUIT AND FITTINGS Rigid Steel Conduit 3801 Rigid PVC Conduit 3803 HDPE Conduit 3803 Flexible Non Metallic Liquid Tight Conduit Type LFNC-B 3804 PVC Coated Urethane Lined Galvanized Rigid Steel Conduit
8.1.2 Under no circumstances shall a service entrance be left unmetered. Notify the Company if an unmetered service is encountered.
2012 Edition Redbook 8.0 REVENUE METERING 8.1 INTRODUCTION The purpose of this section is to outline requirements of the Customer, as set forth herein by LIPA, as they pertain to Electric Revenue Metering
CS-21 STREET STRUCTURES TABLE OF CONTENTS
TABLE OF CONTENTS CS-21.0 Street Structures... 1 CS-21.1 Road Signs... 1 CS-21.2 Safety Barriers... 1 CS-21.3 Bollards and Removable Bollards... 1 CS-21.4 Pedestrian Barrier Rails and Handrails... 1 CS-21.5
Cable Jointing Manual. Jointing Procedures. Module 18. Concentric Cables
Cable Jointing Manual Jointing Procedures Module 18 Concentric Cables Version: 1.0 Date of Issue: June 2008 Author: Richard Summers Job Title: Cables Specialist Approver: Keith Nutter Job Title: Network
SPECIAL SPECIFICATION 6499 Environmentally controlled Communications Building
2004 Specifications CSJ 0720-03-095 SPECIAL SPECIFICATION 6499 Environmentally controlled Communications Building 1. Description. Furnish and install Environmentally Controlled Communications Building
SECTION 16120 PART 1 - GENERAL 1.01 DESCRIPTION A. The work to be performed includes, but is not necessarily limited to, all work involved with the supply and installation of wires and cables and the associated
A. All materials shall be tested and listed by an OSHA approved Nationally Recognized Testing Laboratory (NRTL).
16450 GROUNDING ************************************************************************************************************* SPECIFIER: CSI MasterFormat 2004 number: 26 05 26 An optional keynote to the
CONTENTS. B. System Design and Performance Requirements
16060 Grounding and Bonding This document provides design standards only, and is not intended for use, in whole or in part, as a specification. Do not copy this information verbatim in specifications or
NEMA Standards Publication No. WC ICEA Publication No. S
NEMA Standards Publication No. WC 71-1999 ICEA Publication No. S-96-659-1999 Standard for Nonshielded Cables Rated 2001-5000 Volts for use in the Distribution of Electric Energy Published by National Electrical