Source: https://id.scribd.com/document/101903106/As-4029-1-1994-Stationary-Batteries-Lead-Acid-Vented-Type
Timestamp: 2019-06-18 07:23:26
Document Index: 801429507

Matched Legal Cases: ['art 1', 'art 1', 'art 1', 'arts 2', 'art 2', 'art 3', 'art 1', 'art 1', 'art 1', 'art 1', 'art 1', 'art 1', 'art 2', 'arty 2010']

As 4029.1-1994 Stationary Batteries - Lead-Acid Vented Type | Battery (Electricity) | Electrical Engineering
As 4029.1-1994 Stationary Batteries - Lead-Acid Vented Type
simpanSimpan As 4029.1-1994 Stationary Batteries - Lead-Acid Ve... Untuk Nanti
Dba5c Untitled
EOS Batteries User Manual
battery specification.docx
Power.bloc OPzV En
NWsp07Hamrick.pdf
As 2149-2003 Starter Batteries - Lead-Acid
IEC 896-2 Standard (GiessPaper2006)
AMTE300 User Manual
Transwiki [Battery, Batteries]
Boatowners Mechanical and Electrical Manual
Lead Acid Batteries_IEC 896 - 1
VRLA Battery Tech Manual
3BUA002198R0001 a en Harmony NTCF2x Battery Replacements
Rechargeable Battery Standards
Pollution Problem is the Current Focus of the Battery Industry Topics
application_guideline_bd_solar_09-2005_pa100a202.pdf
DP-12100 V2.1
EOS-300
Army Aviation Digest - Jun 1978
0B Experimental
AS 4029.
IEC 896-1:1987 IEC 896-1/Amd.1:1988 IEC 896-1/Amd.2:1990
Stationary batteriesLead-acid Part 1: Vented type (based on and including the full text of IEC 896-1)
This Australian Standard was prepared by Committee EL/5, Secondary Batteries. It was approved on behalf of the Council of Standards Australia on 3 August 1994 and published on 5 December 1994.
The following interests are represented on Committee EL/5: Australian Automobile Association Australian Automotive Aftermarket Association Australian Electrical and Electronic Manufacturers Association Australian Lead Development Association Australian Chamber of Commerce and Industry Department of Administrative Services Australian Construction Services Department of Defence, Australia Electricity Supply Association of Australia Federal Chamber of Automobile Industries, Australia Institution of Engineers, Australia Railways of Australia Committee Telecom Australia
Review of Australian Standards. To keep abreast of progress in industry, Australian Standards are subject to periodic review and are kept up to date by the issue of amendments or new edit ions as necessary. It is important therefore that Standards users ensure that they are in possession of the latest edit ion, and any amendments thereto. Full detail s of all Australi an Standards and related publications will be found in the Standards Australi a Catalogue of Publications; this information is supplemented each month by the magazine The Australi an Standard, which subscribing members receive, and which gives detail s of new publications, new edit ions and amendments, and of withdrawn Standards. Suggesti ons for improvements to Australian Standards, addressed to the head off ice of Standards Australi a, are welcomed. Noti fi cati on of any inaccuracy or ambiguity found in an Australian Standard should be made without delay in order that the matter may be investigated and appropriate action taken.
This Standard was issued in draft form for comment as DR 93272.
AS 4029.11994
First publi shed as AS 4029.11994.
ISBN 0 7262 9209 5
ii PREFACE
This Standard was prepared by the Joint Standards Australia/Standards New Zealand Committee EL/5 on Secondary Batteries. This Standard is the result of a consensus among Australian and New Zealand representatives on the Joint Committee to produce it as an Australian Standard. Apart from the exceptions described below, this Standard is based on and has been reproduced from IEC 896-1, Stationary lead-acid batteries. General requirements and methods of test, Part 1: Vented types (1987), Amendment No. 1 to IEC 896-1 (1988), and Amendment No. 2 to IEC 896-1 (1990). Amendments Nos 1 and 2 are bound at the end of this Standard. The text affected by an Amendment is marked in the source document with double margin bars. It is Part 1 of a three-part Standard, Parts 2 and 3 of which are (a) AS 4029.2, Stationary batteries Lead-acid Part 2: Valve-regulated sealed type; and (b) AS 4029.3, Stationary batteries Lead-acid Part 3: Pure lead positive pasted plate type. For the purposes of this Australian Standard, the IEC text is modified as follows: (a) The IEC text is amended, supplemented or replaced as set out in Appendix ZZ. The changes are indicated by a marginal bar against each clause, table or figure affected by a reference to Appendix ZZ. (b) New Clause 10A, Life on overcharge, and new Clause 17A, Life on overcharge test, have been added to this Standard. Both appear in Appendix ZZ. (c) References to other publications are replaced by references to Australian Standards as follows: Reference to International Standard IEC 50 50.151 51 International Electrotechnical Vocabulary Chapter 151: Electrical and magnetic devices Direct acting indicating analogue electrical measuring instruments and their accessories Expression of the performance of electrical and electronic measuring equipment Graphical symbols for use on equipment. Index, survey and compilation of the single sheets Digital electronic d.c. voltmeters and d.c. electronic analogue-to-digital converters 1104 Australian Standard AS 1852 1852.151 1042 International Electrotechnical Vocabulary Electric and magnetic devices Direct-acting indicating electrical measuring instruments and their accessories
Informative symbols for use on electrical and electronic equipment
The following Australian documents are referred to in this Standard: AS 1216 1216.1 2149 2668 2669 2676 2676.1 2700
Classification, hazard identification and information systems for dangerous goods Part 1: Classification and class labels for dangerous goods Starter batteries Lead-acid Water for use in secondary batteries Sulphuric acid for use in lead-acid batteries Guide to the installation, maintenance, testing and replacement of secondary batteries in buildings Part 1: Vented cells Colour standards for general purposes Electrical installationsSecondary batteries installed in buildings Part 1: Vented cells Secondary batteries for use with stand-alone power systems Part 1: General requirements
3011 3011.1 4086 4086.1
Copyri ght
Users of Standards are reminded that copyri ght subsists in all Standards Austr alia publi cati ons and software. Except where the Copyri ght Act all ows and except where provided for below no publi cati ons or software produced by Standards Austr alia may be reproduced, stored in a retr ieval system in any form or transmitt ed by any means without prior permission in writ ing from Standards Australi a. Permission may be conditi onal on an appropri ate royalty payment. Requests for permission and informati on on commercial soft ware royalti es should be dir ected to the head off ice of Standards Australi a. Standards Austr alia will permit up to 10 percent of the technical content pages of a Standard to be copied for use exclusively in-house by purchasers of the Standard wit hout payment of a royalty or advice to Standards Austr alia. Standards Austr alia wil l also permit the inclusion of it s copyright material in computer soft ware programs for no royalt y payment provided such programs are used exclusively in-house by the creators of the programs. Care should be taken to ensure that materi al used is fr om the curr ent edit ion of the Standard and that it is updated whenever the Standard is amended or revised. The number and date of the Standard should therefore be clearly identif ied. The use of materi al in print form or in computer software programs to be used commercially, with or without payment, or in commercial contracts is subject to the payment of a royalty. This policy may be vari ed by Standards Austr alia at any ti me.
SECTION ONE GENERAL Page
Scope . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 1 Object . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 1
SECTION TWO GENERAL
Mechanical strength . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 1 Electrolyte levels . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 1 Definition Electrolyte reserve . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 2
SECTION THREE FUNCTIONAL
CHARACTERISTICS AND SPECIFIC REQUIREMENTS
Marking . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . Suitability for floating battery operation . . . . . . . . . . Endurance . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . Charge retention . . . . . . . . . . . . . . . . . . . . . . . . . . Short-circuit current and internal resistance . . . . . . .
.. ... ............ .. .. ... .. .. . .. . .. .. ... . ... ...................... .. . ... . .. ... ... .. . .. .. .. . ... .. . .. .. .. . .. ... .
..... . .. .. . ...... .. ... . . . .. ..
SECTION FOUR GENERAL
Accuracy of measuring instruments . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 4 Preparation of cells and batteries for testing . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 5
SECTION FIVE TEST
Capacity test . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 5 Test of suitability for floating battery operation . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 6 DIFFERENCES BETWEEN THIS STAND AR D AND IEC 896-1 (1987), INCLUD ING AMEND MENTS Nos 1 AND 2 . . . . . . . . . . . . . . . . . . . . . . . . . . . .
APPEND IX ZZ
1 AUSTRALIAN STANDARD
Stationary batteriesLead acid Part 1: Vented type
SECTION ONE GENERAL
1. Scope This standard is applicable to lead-acid cells and batteries which are designed for service in fixed location (i.e. not habitually to be moved from place to place) and which are permanently connected to the load and to the d.c. power supply. Batteries operating in such applications are called stationary batteries. Any type or construction of lead-acid battery may be used for stationary battery applications. This Part 1 of the standard is applicable to vented types only. A Part 2 will be prepared for valve-regulated types . 2. Object The object of this standard is to specify general requirements and the main characteristics, together with corresponding test methods associated with all types and construction modes of lead-acid stationary batteries, excluding valve-regulated types. Recommendations on the use of tests for stationary battery application are given in Table 1. Recommendations relating the type of cell or monobloc to the use of tests are given in Table 11. Statements and claims of basic performance data by the manufacturer shall correspond to those tests. The tests may also be used for type qualification .
SECTION TWO GENERAL REQUIREMENTS AND DEFINITIONS 3. Mechanical strength Stationary cells or batteries shall be designed to withstand mechanical stresses during normal transportation and handling. Resistance to earthquakes, if required, shall be particularly specified. 4. Electrolyte levels 4.1 Each cell shall be equipped with a device to indicate the minimum and maximum electrolyte levels.
AS 4029.1-1994, Stationary batteries - Lead-acid Vented type
Dokumen Serupa dengan As 4029.1-1994 Stationary Batteries - Lead-Acid Vented Type
arteepu37022
Anonymous 0BYsFuV
giangnam45
HenriqueSpall
sandeep parti
Rohit Bhogle
Srikanth Bang
GebatteryBenny
kakakhel21
Mo'men Nabil
THE RIGHT CHOICE OF STANDBY BATTERY FOR CRITICAL APPLICATIONS
Md Abdul Raheman
11 - Cellyte 6 -12tlg i & o Manual May 2008
myron1532
Charging Information for Lead Acid Batteries – Battery University
gases y ventilación 6739
Ashish Sansoha
New Batt Ecar Whitepaper
3.5 GL for Selction of Auxilaries for SHP Staions
Shrijana Gairhe
Dn_6933 - Baterias
Alexander Rosero Urbano
12V-45Ah
Riduan Othman
plc two hour primer.pdf
Khaleel Ahmad Masa'id
Levitt Et Al the Behavioralist Goes to School AEJ Pol 2016
luisarrodrigues
HDL50-A the System
Antonio Raúl KG
lokenders801
Intial Public Offer Icici 2012
M.Phil Computer Science Network Security Projects
Director Sales Effectiveness Operations in Minneapolis St Paul MN Resume Juliane Janey
JulianeJaney
mishti3001
Corporation Full Text Batch 4
Alexis Capuras Enriquez
Oce 70507051 Operator Manual
DATA SHEET 542R T-2010233
Catch Me if You Can Skrip - CUT
Aditya Gilank Pratama
CRF Works Certain Guidelines
TDCReleaseNotes1-11
Salah Ali
IBM Cognos BI Dimensional Functions
Anderson Batista de Aguiar
Senior Cache MUMPS Software Application Developer in Dallas Ft Worth TX Resume Keith Fitzgerald
KeithFitzgerald
Oracle Projets Suite Setup Checklist
Solvent Cementing Literature as on Website
NaeemSiddiqui
SOL ONE Specification
Henrry Ochoa
ACHE-15.pdf
sanjeevnn
Revit Pure BASICS Railings
What's New-AX for Retail R2 Release
sandeep_golchha
Audit Form 14
Sagar A Shah
CME Config
VA - Beach Party 2010
Drug Development China
Java3.pdf