Source: http://homedocbox.com/Environmental_Safety/81612603-International-standard.html
Timestamp: 2019-09-20 18:44:20
Document Index: 685993501

Matched Legal Cases: ['art 5', 'art 5', 'art 5', 'art 3', 'art 5', 'art 1', 'art 8']

1 INTERNATIONAL STANDARD IEC Second edition Power transformers Part 5: Ability to withstand short circuit This English-language version is derived from the original bilingual publication by leaving out all French-language pages. Missing page numbers correspond to the Frenchlanguage pages. Reference number IEC :2000(E)
2 INTERNATIONAL STANDARD IEC Second edition Power transformers Part 5: Ability to withstand short circuit IEC 2000 Copyright - all rights reserved No part of this publication may be reproduced or utilized in any form or by any means, electronic or mechanical, including photocopying and microfilm, without permission in writing from the publisher. International Electrotechnical Commission, 3, rue de Varembé, PO Box 131, CH-1211 Geneva 20, Switzerland Telephone: Telefax: Web: Commission Electrotechnique Internationale International Electrotechnical Commission Международная Электротехническая Комиссия PRICE CODE For price, see current catalogue S
3 IEC: CONTENTS FOREWORD... 5 Page Clause 1 Scope Normative references Requirements with regard to ability to withstand short circuit General Overcurrent conditions Demonstration of ability to withstand short circuit Thermal ability to withstand short circuit Ability to withstand the dynamic effects of short circuit Annex A (informative) Guidance for the identification of a similar transformer Annex B (normative) Calculation method for the demonstration of the ability to withstand the dynamic effects of short circuit Figure 1 Star/delta connected transformer Figure 2 Star/star auto-transformer Table 1 Recognized minimum values of short-circuit impedance for transformers with two separate windings Table 2 Short-circuit apparent power of the system Table 3 Maximum permissible values of the average temperature of each winding after short circuit Table 4 Values for factor k
4 IEC: INTERNATIONAL ELECTROTECHNICAL COMMISSION POWER TRANSFORMERS Part 5: Ability to withstand short circuit FOREWORD 1) The IEC (International Electrotechnical Commission) is a worldwide organization for standardization comprising all national electrotechnical committees (IEC National Committees). The object of the IEC is to promote international co-operation on all questions concerning standardization in the electrical and electronic fields. To this end and in addition to other activities, the IEC publishes International Standards. Their preparation is entrusted to technical committees; any IEC National Committee interested in the subject dealt with may participate in this preparatory work. International, governmental and non-governmental organizations liaising with the IEC also participate in this preparation. The IEC collaborates closely with the International Organization for Standardization (ISO) in accordance with conditions determined by agreement between the two organizations. 2) The formal decisions or agreements of the IEC on technical matters express, as nearly as possible, an international consensus of opinion on the relevant subjects since each technical committee has representation from all interested National Committees. 3) The documents produced have the form of recommendations for international use and are published in the form of standards, technical specifications, technical reports or guides and they are accepted by the National Committees in that sense. 4) In order to promote international unification, IEC National Committees undertake to apply IEC International Standards transparently to the maximum extent possible in their national and regional standards. Any divergence between the IEC Standard and the corresponding national or regional standard shall be clearly indicated in the latter. 5) The IEC provides no marking procedure to indicate its approval and cannot be rendered responsible for any equipment declared to be in conformity with one of its standards. 6) Attention is drawn to the possibility that some of the elements of this International Standard may be the subject of patent rights. The IEC shall not be held responsible for identifying any or all such patent rights. International Standard IEC has been prepared by IEC technical committee 14: Power transformers. This second edition cancels and replaces the first edition published in 1976 and amendment 2 (1994). This second edition constitutes a technical revision. The text of this standard is based on the following documents: FDIS 14/346/FDIS Report on voting 14/353/RVD Full information on the voting for the approval of this standard can be found in the report on voting indicated in the above table. This publication has been drafted in accordance with the ISO/IEC Directives, Part 3. Annex A is for information only. Annex B forms an integral part of this standard.
5 IEC: The committee has decided that this publication remains valid until At this date, in accordance with the committee s decision, the publication will be reconfirmed; withdrawn; replaced by a revised edition, or amended.
6 IEC: POWER TRANSFORMERS Part 5: Ability to withstand short circuit 1 Scope This part of IEC identifies the requirements for power transformers to sustain without damage the effects of overcurrents originated by external short circuits. It describes the calculation procedures used to demonstrate the thermal ability of a power transformer to withstand such overcurrents and both the special test and the calculation method used to demonstrate its ability to withstand the relevant dynamic effects. The requirements apply to transformers as defined in the scope of IEC Normative references The following normative documents contain provisions which, through reference in this text, constitute provisions of this part of IEC For dated references, subsequent amendments to, or revisions of, any of these publications do not apply. However, parties to agreements based on this part of IEC are encouraged to investigate the possibility of applying the most recent editions of the normative documents indicated below. For undated references, the latest edition of the normative document referred to applies. Members of IEC and ISO maintain registers of currently valid International Standards. IEC :1993, Power transformers Part 1: General IEC :1997, Power transformers Part 8: Application guide IEC 60726:1982, Dry-type power transformers