Source: http://docplayer.net/23512471-Electrical-safety-regulation-2002.html
Timestamp: 2018-12-13 07:43:22
Document Index: 491777548

Matched Legal Cases: ['ART 1', 'ART 2', 'ART 3', 'ART 4', 'arts 62', 'art\n6', 'ART 5', 'ART 6', 'ART 7', 'art 127', 'ART 8', 'ART 9', 'ART 10', 'ART 11', 'ART 12', 'ART 13', 'ART 14', 'ART 1', 'ART 2', 'ART 3']

ELECTRICAL SAFETY REGULATION PDF
Download "ELECTRICAL SAFETY REGULATION 2002"
1 Queensland Electrical Safety Act 2002 ELECTRICAL SAFETY REGULATION 2002 Reprinted as in force on 1 January 2004 (includes commenced amendments up to 2003 Act No. 63) Reprint No. 1F This reprint is prepared by the Office of the Queensland Parliamentary Counsel Warning This reprint is not an authorised copy
2 Information about this reprint This regulation is reprinted as at 1 January The reprint shows the law as amended by all amendments that commenced on or before that day (Reprints Act 1992 s 5(c)). The reprint includes a reference to the law by which each amendment was made see list of legislation and list of annotations in endnotes. Also see list of legislation for any uncommenced amendments. This page is specific to this reprint. See previous reprints for information about earlier changes made under the Reprints Act A table of reprints is included in the endnotes. Also see endnotes for information about when provisions commenced editorial changes made in earlier reprints. Dates shown on reprints Reprints dated at last amendment All reprints produced on or after 1 July 2002, hard copy and electronic, are dated as at the last date of amendment. Previously reprints were dated as at the date of publication. If a hard copy reprint is dated earlier than an electronic version published before 1 July 2002, it means the legislation was not further amended and the reprint date is the commencement of the last amendment. If the date of a hard copy reprint is the same as the date shown for an electronic version previously published, it merely means that the electronic version was published before the hard copy version. Also, any revised edition of the previously published electronic version will have the same date as that version. Replacement reprint date If the date of a hard copy reprint is the same as the date shown on another hard copy reprint it means that one is the replacement of the other.
3 Queensland ELECTRICAL SAFETY REGULATION 2002 TABLE OF PROVISIONS Section Page PART 1 PRELIMINARY 1 Short title Commencement Purposes How purposes are to be achieved Definitions References to standards and other documents Meaning of qualified business person and qualified technical person.. 15 PART 2 ELECTRICAL WORK Division 1 Preliminary 8 Purpose of divs 2 to Division 2 Basic requirements for electrical work 9 Definition for div Application of div Requirements for electrical work Requirements for performance of live work Division 3 High voltage live line work 13 Performance of high voltage live line work Division 4 Testing of work 14 Testing of electrical equipment after electrical work Certificate of testing and safety Division 5 Requirements applying to employers and self-employed persons 16 Application of div
4 2 17 Testing and maintenance of safety equipment Employer or self-employed person to ensure suitability of testing instruments Division 6 Other requirements 19 Electrical equipment with serious defect not to be connected to electricity source Signs on switches and disconnection points Rescue and resuscitation training Division 7 Documents about electrical work 22 Application of div Who may sign documents about electrical work Division 8 General provisions 24 Misrepresentations about electrical equipment or work PART 3 LICENSING Division 1 Electrical work licences 25 Classes of electrical work licences What electrical mechanic licence authorises What electrical linesperson licence authorises What electrical fitter licence authorises What electrical jointer licence authorises What restricted electrical work licence authorises What electrical work training permit authorises External licence equivalents Division 2 Electrical work licence requirements 33 General requirements Eligibility requirements for electrical mechanic licence Eligibility requirements for electrical linesperson licence Eligibility requirements for electrical fitter licence Eligibility requirements for electrical jointer licence Eligibility requirements for restricted electrical work licence Term of electrical work licence Division 3 Electrical contractor licence requirements 40 Eligibility requirements for electrical contractor licence for individual... 40
5 3 41 Eligibility requirements for electrical contractor licence for partnership Eligibility requirements for electrical contractor licence for corporation Financial and insurance requirements for applicant for electrical contractor licence Change of name of corporation or partnership Change in membership of partnership Term of electrical contractor licence Division 4 Miscellaneous 47 Eligibility requirements for renewal or reinstatement of electrical licence Application requirements Giving chief executive cancelled or suspended licence or licence to be endorsed Replacement of electrical licence Surrender of electrical licence Register of electrical licences Examinations Approved examiners Refund of fees A Operation of trade contractor s licence Advertising by licensed electrical contractor Performing electrical work without electrical licence PART 4 WORKING AROUND ELECTRICAL PARTS Division 1 Preliminary 58 Purpose of pt Definitions for pt Meaning of direct contact Meaning of exclusion zone Division 2 Requirements for working around electrical parts 62 Employer or self-employed person to ensure work is performed in accordance with requirements Work involving direct contact with electrical part Work within exclusion zone for electrical part
6 4 Division 3 Consultation with persons in control of electric lines 64A Requirement to consult PART 5 ELECTRICAL INSTALLATIONS Division 1 Performing electrical work 65 Purpose of div Licensed electrical worker to comply with wiring rules Employer to ensure electrical work complies with wiring rules Work involving water equipment Work involving electric motor forming part of vehicle Division 2 Defects and earthing 70 Requirement on person in control to fix defect Earthing Division 3 Electric lines 72 Service line Structure supporting electric line or equipment to comply with wiring rules Obligation to preserve insulation of electric line Trimming of trees near overhead electric line Obligation to ensure safety of disconnected overhead electric line Division 4 Installation of approved safety switches in domestic residences 77 Definitions for div Notice to transferee about approved safety switch Notice to chief executive about approved safety switch and other matters Installation of approved safety switch in particular residences Performing electrical installation work for domestic residences Division 5 Workplace electrical installations Subdivision 1 Preliminary 82 Purpose of div Definitions for div Subdivision 2 All work 84 Application of sdiv Cord extension sets and flexible cables
7 5 Subdivision 3 Class 1 work 86 Application of sdiv Requirements for construction wiring and electrical equipment Subdivision 4 Class 2 work 88 Application of sdiv Double adaptors and piggyback plugs prohibited Specified electrical equipment Safety switches, including portable safety switches Subdivision 5 Class 3 or 4 work 92 Application of sdiv Specified electrical equipment Safety switches, including portable safety switches PART 6 ELECTRICAL EQUIPMENT Division 1 Preliminary 95 Definitions for pt Meanings of prescribed class and type Meaning of relevant standard Queensland approvals External approvals Division 2 Restriction on hire or sale of particular items of electrical equipment 100 Hire or sale of electrical equipment of prescribed class Division 3 Queensland approvals of types of electrical equipment of prescribed classes 101 Application for approval of type of electrical equipment Approval of type of electrical equipment Term of approval Register of approved types of electrical equipment Division 4 Changes to approvals 105 Changing name and address Application to change approval to include new type Changing approval of type of electrical equipment to include new type... 81
8 6 Division 5 Transfer and cancellation of approvals 108 Transfer of approval of type of electrical equipment Cancellation of approval of type of electrical equipment Procedure before cancellation Type approval holder to return type approval certificate for cancelled approval Division 6 Marking of equipment of approved type 112 Marking of item of electrical equipment of approved type Approval by the chief executive not to mark item of electrical equipment.. 84 Division 7 Chief executive may require testing of item of electrical equipment of approved type 114 Chief executive may require item of electrical equipment of approved type to be submitted Procedure for obtaining item of electrical equipment for testing Identification of item of electrical equipment to be tested Cost of testing and examining and liability for damage Return of item of electrical equipment given to chief executive Division 8 Nonprescribed electrical equipment 119 Chief executive may put into effect program for certification Sale of particular nonprescribed electrical equipment prohibited Division 9 Prohibition of hire or sale of particular electrical equipment 121 Chief executive may prohibit the hire, sale or use of electrical equipment on safety grounds Division 10 Second-hand electrical equipment 122 Limitation on sale of second-hand electrical equipment Limitation on offering second-hand electrical equipment for sale Division 11 Labelling and inspection of electrical equipment 124 Labelling faulty portable electrical equipment Division 12 Hire electrical equipment 125 Purpose of div Hiring electrical equipment PART 7 WORKS OF AN ELECTRICITY ENTITY Division 1 Compliance with part 127 Purpose of pt
9 7 128 Compliance with this part Division 2 Earthing and protection 129 Systems of earthing Connection of high voltage circuit to earth Performance and other requirements for works Insulation of stay wire Protection of earth conductors Division 3 Substations 134 Substation requirements Division 4 Electric lines and control cables 134A Application of div Measurement of vertical and horizontal distances Electric lines and control cables Clearance from exposed conductive parts and separation of conductors in same circuit Location of overhead circuit in relation to another overhead circuit Clearance of overhead electric lines from ground Clearance of overhead electric lines from structures Building or adding to structure near electric line Clearance of stay wires and control cables over road Connection to consumer s premises Division 5 Termination requirements for low voltage overhead service lines 144 Termination of low voltage overhead service line Division 6 Service lines generally 145 Fuses and disconnectors for service line Disused service lines to be disconnected Division 7 Maintenance of works 147 Inspection and maintenance of integrity of insulation Trimming of trees near overhead electric line
10 8 PART 8 ELECTRICITY SUPPLY Division 1 Connection to source of electricity 149 Electrical installation with serious defect not to be connected to electricity source Electrical installation not to be connected to electricity source if work not tested Electrical installation not to be initially connected to electricity source without examination and testing Reconnection of electrical installation to electricity source High voltage or hazardous area electrical installation not to be connected to electricity source without inspection Licensed electrical contractor not to connect electricity source without being satisfied of compliance with Act and regulation Disconnection and reconnection of low voltage electrical installation Division 2 Private generating plant 156 Generating plant for emergency supply Generating plant for interconnection to works of electricity entity Division 3 Testing 158 Certificate by licensed electrical contractor of test Certificate of testing and compliance Performance of examination or test Reasons to be given for not connecting to source of electricity after examination Keeping copy of report Division 4 Requests and advice to distribution entities 163 Request to distribution entity for examination of electrical work Telling distribution entity of need for change to metering PART 9 SAFETY MANAGEMENT SYSTEMS Division 1 Prescribed electricity entities 165 Prescribed electricity entities Division 2 Requirements for safety management systems 166 Safety management system requirements PART 10 ACCREDITED AUDITORS 167 Appointment Refund of part of fee
11 9 169 Term of office as accredited auditor PART 11 CATHODIC PROTECTION SYSTEMS Division 1 Preliminary 170 Definitions for pt Electrical terms apply for direct current Exclusion from application Division 2 Installation and design 173 Installation of cathodic protection system only if preliminary steps taken Correct design and installation of cathodic protection system Division 3 Operating requirements 175 Operation of cathodic protection system only on conditions Division 4 Testing requirements 176 Tests before registration or operation of system Further tests during period of registration of system Further tests during operation of system Further tests of new foreign structure if required by the chief executive Records of tests to be kept Testing by chief executive Division 5 System requirements 182 Electrical limits Maximum potential change Tolerances Identification of anode groundbed Division 6 Registration of registrable systems 186 Register Application for registration of registrable system Registration of registrable system Term of registration Change of name and address Cancellation of registration Taking away or making a registered system inoperable Change to registered system to be notified
12 10 PART 12 INCIDENT NOTIFICATION AND REPORTING 194 Definitions for pt Meaning of distribution entity for incident or event Employer or self-employed person to advise chief executive of serious electrical incident or dangerous electrical event Recording serious electrical incident or dangerous electrical event Distribution entity to advise chief executive of serious electrical incident or dangerous electrical event Action required by distribution entity on report of electric shock Report of incident records Scene not to be interfered with Requirement on distribution entity to take action in interests of electrical safety PART 13 MISCELLANEOUS PROVISIONS Division 1 Electrical safety contributions 203 Context of div Definitions for div Fixing electrical safety contribution for each distribution entity for current financial year Payment of electrical safety contribution by instalments Division 2 Mines and petroleum plants 207 Application of regulation at mine or petroleum plant Division 3 Other matters 208 Climbing poles of electricity entity prohibited Obligations of employer about supervising training person Inspection of entries in registers Provision of information by retail entity A Person chief executive may appoint as inspector B Fees PART 14 TRANSITIONAL PROVISIONS Division 1 Interpretation 212 Definitions for pt Division 2 Electrical licences 213 Equivalent licences to previous licences
13 Eligibility for electrical jointer licence Eligibility for electrical linesperson licence Division 3 Matters in place before commencement 216 Registered cathodic protection system Approval of type of prescribed electrical article Clearances for lines built before 1 January Termination of low voltage overhead service line built before 1 January Clearances for lines built before commencement Division 4 Transitional provisions for rural industry 221 Requirements not applying until 1 March Requirements not applying until 1 March Requirements not applying until 1 March SCHEDULE EXTERNAL LICENCES AND ELECTRICAL WORK LICENCE EQUIVALENTS SCHEDULE EXCLUSION ZONES FOR ELECTRICAL PARTS SCHEDULE PRESCRIBED CLASSES OF ELECTRICAL EQUIPMENT AND RELEVANT STANDARDS SCHEDULE CLEARANCE OF OVERHEAD ELECTRIC LINES (OTHER THAN LOW VOLTAGE SERVICE LINES) SCHEDULE CLEARANCE OF LOW VOLTAGE OVERHEAD SERVICE LINES SCHEDULE PRESCRIBED ELECTRICITY ENTITIES SCHEDULE FEES SCHEDULE CLASSES OF ELECTRICAL EQUIPMENT FOR FEES SCHEDULE DICTIONARY
14 12 ENDNOTES 1 Index to endnotes Date to which amendments incorporated Key Table of reprints List of legislation List of annotations
15 s 1 13 s 4 ELECTRICAL SAFETY REGULATION 2002 [as amended by all amendments that commenced on or before 1 January 2004] PART 1 PRELIMINARY 1 Short title This regulation may be cited as the. 2 Commencement This regulation commences on 1 October Purposes The purposes of this regulation include the following (a) (b) (c) (d) (e) ensuring the electrical safety of licensed electrical workers, other workers, licensed electrical contractors, consumers and the general public; enhancing consumer protection in relation to electrical work; stopping cathodic protection systems from damaging or interfering with the property of others; ensuring a safe supply of electricity; ensuring electrical equipment hired or sold is electrically safe. 4 How purposes are to be achieved The ways adopted by this regulation for the achievement of its purposes include the following (a) prescribing matters in support of the electrical licensing arrangements established under the Act;
16 s 5 14 s 6 (b) (c) (d) (e) (f) (g) (h) (i) prescribing requirements for working around exposed parts; prescribing requirements for electrical installations; prescribing matters about electrical equipment, including (i) requirements for electrical equipment; and (ii) requirements for particular electrical equipment to be approved by the chief executive; and (iii) requirements about the hiring, selling, testing and using of electrical equipment; and (iv) requiring particular electrical equipment to be approved and marked for compliance with prescribed standards; and (v) requirements for the testing of electrical equipment; prescribing requirements and procedures for the design, building and maintenance of electric lines and the works of electricity entities; prescribing requirements for the performance of electrical work; providing for the preparation, lodging and auditing of safety management plans; prescribing requirements for the operation of cathodic protection systems and requirements for particular systems to be registered by the chief executive; prescribing notification and reporting requirements for serious electrical incidents and dangerous electrical events. 5 Definitions (1) The dictionary in schedule 9 defines particular words used in this regulation. (2) If a word used in this regulation is not defined in the dictionary, and is not defined in the Act, but is used in the wiring rules, it must, to the greatest practicable extent, be taken to have the same meaning in this regulation as it has in the wiring rules. 6 References to standards and other documents (1) In this regulation, unless otherwise stated
17 s 7 15 s 7 (a) a reference to a standard using the designation made up of AS and a number is a reference to the standard as in force from time to time under that designation; and Example (b) AS 3127 is a reference to the standard that is currently in force under that designation. a reference to a joint standard using the designation made up of AS/NZS and a number is a reference to the joint standard as in force from time to time under that designation; and Example (c) AS/NZS is a reference to the joint standard that is currently in force under that designation. a reference to a standard or other document using ESAA as part of its name is a reference to the standard or other document as first published under the name quoted; and Example A reference to the document known as the ESAA Live Line Guideline (2000) is a reference to that guideline as first published under that name. (d) subject to paragraphs (a) to (c), a reference to a standard or other document is a reference to the standard or other document as in force from time to time. (2) Subsection (1)(a), (b) and (d) applies regardless of the edition or year of the standard, joint standard or other document. Example of operation of subsection (2) In this regulation, a reference to AS/NZS 3000 is a reference to that standard as amended from time to time, and as remade from time to time. (3) Bracketed words appearing after a standard s designation are included for information purposes only. 7 Meaning of qualified business person and qualified technical person (1) A qualified business person, for an individual, partnership or corporation, is an individual who satisfies the chief executive that he or she (a) is a fit and proper person; and
18 s 7 16 s 7 (b) is competent to perform the business aspects of performing electrical work as, or for, a licensed electrical contractor; and (c) either (i) has satisfactorily finished a course of instruction, or an examination required by the chief executive, on business aspects of performing electrical work; or (ii) has been operating a business for the last 5 years. (2) A qualified technical person, for an individual, partnership or corporation, is an individual who satisfies the chief executive that he or she (a) is a fit and proper person; and (b) has held for at least a year, or a shorter period considered acceptable by the chief executive, and still holds, an electrical work licence or an external contracting authority; and (c) is competent to perform electrical work as, or for, a licensed electrical contractor; and (d) has satisfactorily finished a course of instruction, or an examination required by the chief executive, on technical aspects of performing electrical work. (3) Despite subsections (1) and (2), for a person who is an individual to be a qualified business person or qualified technical person (a) for an individual who holds, or has applied for, an electrical contractor licence, the person must also be, or be an employee of, the individual; or (b) for a partnership that holds, or has applied for, an electrical contractor licence, the person must also be a member or an employee of the partnership; or (c) for a corporation that holds, or has applied for, an electrical contractor licence, the person must also be an executive officer, a member or an employee of the corporation. (4) In deciding whether a person who is an individual is a fit and proper person, the chief executive may only consider (a) the standard of honesty and integrity demonstrated by the person in commercial and other activities in which the person has been involved; and
19 s 8 17 s 11 (b) any failure by the person to perform commercial or statutory obligations and the reasons for the failure. PART 2 ELECTRICAL WORK Division 1 Preliminary 8 Purpose of divs 2 to 5 Divisions 2 to 5 each prescribe a way of discharging the electrical safety obligation of an employer or self-employed person to ensure the person s business or undertaking is conducted in a way that is electrically safe. Division 2 Basic requirements for electrical work 9 Definition for div 2 In this division electrical work does not include high voltage live line work. 10 Application of div 2 This division applies to the performance of electrical work for the purposes of the business or undertaking of an employer or self-employed person. 11 Requirements for electrical work (1) An employer or self-employed person must ensure that, unless the circumstances required under this division for the performance of live work apply, live work is not performed. Maximum penalty 40 penalty units. (2) Without limiting what the employer or self-employed person must do to ensure compliance with subsection (1), the employer or self-employed person must ensure that
20 s s 12 (a) (b) each exposed part is treated as if it is energised until it is isolated and proved not to be energised; and each high voltage exposed part is earthed. 12 Requirements for performance of live work (1) The following circumstances are required for the performance of live work (a) it is not practicable to perform the electrical work other than by live work because of 1 or more of the following (i) it is necessary in the interests of safety, whether or not electrical safety, for the work to be performed while the electrical equipment the subject of the electrical work is energised; Example for subparagraph (i) It may be necessary in the interests of road safety for a set of traffic lights to remain operating while electrical work is performed on the lights. (ii) a supply of electricity is necessary for the proper performance of the electrical work; (iii) there is no reasonable alternative to performing the electrical work by live work; Example for subparagraph (iii) It may be necessary, to avoid widespread outages, to perform electrical work on works of an electricity entity by live work. (b) the employer or self-employed person has prepared a written risk assessment of the performance of the live work; (c) the employer or self-employed person authorises the performance of the live work only after consultation with the person in control of the electrical equipment the subject of the electrical work; (d) the person who performs the live work has appropriate qualifications and training for the performance of the live work; (e) testing equipment appropriate to the performance of the live work has been given to the person performing the electrical work, the testing equipment has been properly maintained, and
21 s s 12 the person performing the electrical work makes proper use of the testing equipment in performing the work; (f) (g) (h) (i) (j) clothing and personal protective equipment appropriate to the performance of the live work has been given to the person performing the electrical work and the person performing the electrical work makes proper use of the clothing and equipment in performing the work; the isolation point of the electricity supply for the electrical equipment the subject of the electrical work has been clearly identified and, except for electric line work, is able to be reached quickly without the need to climb over or shift obstructions; the area where the electrical work is performed is clear of obstructions to the extent necessary for easy access to and from the area; there is a safety observer observing the performance of the electrical work, unless the work involves testing electrical equipment; the performance of the electrical work is in accordance with a safe system of work. Example of what a safe system of work could include for paragraph (j) A safe system could include preventing persons from accessing the area where live work is being performed if the persons are not needed for the performance of the work. (2) In this section safe system of work, for live work on a low voltage electrical installation, includes, but is not limited to, a system of work that complies with the provisions of AS/NZS 4836 (Safe working on low voltage electrical installations) about ensuring the safety of persons while performing live work. safety observer, in relation to the observing of the performance of electrical work, means a person (a) who is competent to help with the electrical work; and (b) who is competent to rescue the person performing the electrical work and to provide resuscitation; and (c) whose competence for paragraph (b) has been assessed in the last 6 months.
22 s s 13 Division 3 High voltage live line work 13 Performance of high voltage live line work (1) A person must not perform high voltage live line work unless the person s performance of the work (a) is authorised in writing by the person in control of the electrical equipment the subject of the work; and (b) is in accordance with a high voltage live line work management plan. Maximum penalty 40 penalty units. (2) A person in control of electrical equipment may authorise a person s performance of high voltage live line work in relation to the electrical equipment only if (a) the person in control is satisfied the person (i) has successfully finished an appropriate course of training; and (ii) has been assessed by the provider of the course as competent to perform the work; and (b) the written authorisation states the voltages of the electrical equipment on which the high voltage live line work may be performed. (3) If the written authorisation provides for the performance of work on more than 1 occasion, the entity that gives the authorisation must, while the authorisation is in force, cause the person authorised to perform the high voltage live line work to be regularly assessed to ensure the person remains competent to perform the work. Maximum penalty 40 penalty units. (4) In this section high voltage live line work management plan means a plan for the performance of high voltage live line work that (a) includes procedures developed in accordance with the ESAA Live Line Guideline (2000); and (b) is developed in conjunction with all of the following
23 s s 14 (c) (i) representatives of workers who are to perform high voltage live line work in accordance with the plan; (ii) if the high voltage live line work involves the works of an electricity entity the electricity entity; (iii) other persons who might reasonably be expected to have an interest in the performance of the high voltage live line work; and has been approved by a person who (i) is an electrical engineer who has expertise as a professional engineer in the performance of high voltage live line work; or (ii) has expertise the person in control of the electrical equipment the subject of the high voltage live line work decides is equivalent to the expertise mentioned in subparagraph (i). Division 4 Testing of work 14 Testing of electrical equipment after electrical work (1) This section applies if electrical work is performed on electrical equipment. (2) A person who performs part or all of the electrical work, and is responsible for bringing the electrical equipment to a state of readiness for connection to a source of electricity for use for its intended purpose, must ensure the electrical equipment is tested, as required under subsections (5) and (6). Maximum penalty 40 penalty units. (3) A licensed electrical contractor or electricity entity who performs the electrical work of connecting the electrical equipment to a source of electricity for use for its intended purpose must ensure the electrical equipment is tested as required under subsections (5) and (6). Maximum penalty 40 penalty units. (4) Subsection (3) does not require a distribution entity to ensure the testing of the electrical equipment if
24 s s 15 (a) the electrical work is, or is part of, electrical work performed on an electrical installation; and (b) a licensed electrical contractor has given the distribution entity a certificate under section about the testing of the electrical work performed on the electrical installation. (5) The testing of the electrical equipment must be directed at ensuring that the electrical equipment, to the extent it is affected by the electrical work, is electrically safe. (6) If the electrical equipment is energised for testing, the person who performs the test must ensure persons not necessary for the testing are electrically safe. 15 Certificate of testing and safety (1) This section applies if a licensed electrical contractor performs electrical work that must be tested under this division. (2) The contractor must, as soon as practicable after the testing, ensure that the person for whom the electrical work was performed is given a certificate complying with this section. Maximum penalty 40 penalty units. (3) The certificate must state the following (a) the name and address of the person for whom the work was performed; (b) the electrical equipment tested; (c) the day the electrical equipment was tested; (d) the number of the electrical contractor licence under which the electrical equipment was tested. (4) The certificate must certify that the electrical equipment, to the extent it is affected by the electrical work, is electrically safe. (5) A licensed electrical contractor must keep a copy of a certificate given under this section for at least 5 years after the certificate is given. Maximum penalty for subsection (5) 20 penalty units. 1 Section 158 (Certificate by licensed electrical contractor of test)
25 s s 18 Division 5 Requirements applying to employers and self-employed persons 16 Application of div 5 This division applies to the performance of electrical work for the purposes of the business or undertaking of an employer or self-employed person. 17 Testing and maintenance of safety equipment (1) An employer or self-employed person must ensure that (a) safety equipment is used in the performance of electrical work; and (b) the safety equipment is (i) a suitable type for the electrical work being performed; and (ii) maintained so that it is suitable for use in the electrical work being performed; and (iii) if it is safety equipment that can not be visually confirmed as being correctly functioning and safe tested at least every 6 months to ensure it provides the protection it is intended to provide; and (iv) labelled to state the day on or before which it is next due for testing; and (v) in good repair and condition. Maximum penalty 40 penalty units. (2) The employer or self-employed person must keep records of the tests performed under subsection (1)(b)(iii) for at least 5 years. Maximum penalty for subsection (2) 20 penalty units. 18 Employer or self-employed person to ensure suitability of testing instruments (1) This section applies to the following (a) an employer of a person required to perform tests on electrical work or safety equipment;
26 s s 20 (b) a self-employed person required to perform tests on electrical work or safety equipment. (2) The employer or self-employed person must ensure (a) the test instruments used for the testing are designed for, and capable of correctly performing, the required tests; and (b) if a testing instrument can not be visually confirmed as being correctly functioning and safe that the instrument is tested at least every 6 months to ensure it is in proper working order; and (c) records of tests performed are kept for at least 5 years. Maximum penalty for subsection (2) 40 penalty units. Division 6 Other requirements 19 Electrical equipment with serious defect not to be connected to electricity source If an item of electrical equipment has a serious defect, a licensed electrical worker must not connect the equipment to a source of electricity for use for its intended purpose. Maximum penalty 40 penalty units. 20 Signs on switches and disconnection points (1) This section applies if (a) a licensed electrical worker is performing electrical work; and (b) to perform the work, the worker has de-energised, or otherwise isolated from electricity, an item of electrical equipment that is the subject of the electrical work or that is near where the electrical work is being performed; and (c) to de-energise, or otherwise isolate, the item of electrical equipment, the licensed electrical worker has operated a device; and (d) while the worker is performing the work, the worker does not have the device under the worker s sole effective control. (2) The licensed electrical worker must ensure that there is attached to the device, in a prominent position, a warning sign that is suitable in the
27 s s 20 circumstances, having regard to AS 1319 (Safety signs for the occupational environment). Maximum penalty 40 penalty units. (3) The electrical worker must also ensure that (a) the device, when in the open position, is locked; or Examples for paragraph (a) Using a personal lock to lock an air conditioner isolator in the open position Using a locking device that stops a miniature circuit breaker from being closed (b) Placing a lockable shroud on the male inlet plug of electrical equipment. other precautions are taken to stop the device being accidentally closed. Examples for paragraph (b) Disengaging a circuit breaker so that the circuit breaker is separated from the busbars Removing circuit cables from the fuse or circuit breaker Insertion of a mechanical restriction. Maximum penalty 40 penalty units. (4) If the electrical work is being performed for the purposes of the business or undertaking of an employer or self-employed person, the employer or self-employed person must ensure that (a) the licensed electrical worker has all the signs and equipment necessary for the worker to comply with subsections (2) and (3); and (b) the signs and equipment are used in the way required under the subsections. Maximum penalty 40 penalty units. (5) In this section device means a circuit-breaker, disconnection point, fuse or switch.
28 s s Rescue and resuscitation training An employer must ensure workers who are required to perform, or help in performing, electrical work are competent in rescue and resuscitation in accordance with recognised practices in the electricity industry. Maximum penalty 40 penalty units. Division 7 Documents about electrical work 22 Application of div 7 This division applies to the performance of electrical work as part of the business or undertaking of a licensed electrical contractor. 23 Who may sign documents about electrical work A person must not sign a document required under the Act, or by an electricity entity, about the performance of electrical work unless the person is (a) if the electrical work was performed as part of the business or undertaking of a licensed electrical contractor who is an individual a qualified technical person for the individual; or (b) if the electrical work was performed as part of the business or undertaking of a licensed electrical contractor that is a partnership a qualified technical person for the partnership; or (c) if the electrical work was performed as part of the business or undertaking of a licensed electrical contractor that is a corporation a qualified technical person for the corporation. Maximum penalty 20 penalty units. Division 8 General provisions 24 Misrepresentations about electrical equipment or work (1) A person must not, in trade or commerce, represent that someone who is not a licensed electrical worker may lawfully
29 s s 26 (a) connect to a source of electricity an item of electrical equipment that may only be connected to a source of electricity by a licensed electrical worker; or (b) do electrical work that may only be done by a licensed electrical worker. Maximum penalty 40 penalty units. (2) An employer must take all reasonable steps to ensure the employer s workers do not contravene subsection (1). Maximum penalty for subsection (2) 40 penalty units. PART 3 LICENSING Division 1 Electrical work licences 25 Classes of electrical work licences The following classes of electrical work licences may be issued (a) (b) (c) (d) (e) (f) electrical mechanic licence; electrical linesperson licence; electrical fitter licence; electrical jointer licence; restricted electrical work licence; electrical work training permit. 26 What electrical mechanic licence authorises Subject to particular conditions or restrictions included in the licence, an electrical mechanic licence authorises the holder to perform all electrical work. Examples of what the holder of an electrical mechanic licence may do installing or changing an electrical installation or electric line
30 s s 30 maintaining, repairing, or connecting to a source of electricity, an item of electrical equipment. 27 What electrical linesperson licence authorises Subject to particular conditions or restrictions included in the licence, an electrical linesperson licence authorises the holder to perform all electric line work. Examples of what the holder of an electrical linesperson licence may do electrical work in the building or maintenance of an overhead electric line electrical work in the building or maintenance of street lighting connected to an overhead or underground electric line tests to ensure overhead electric lines are correctly connected. 28 What electrical fitter licence authorises Subject to particular conditions or restrictions included in the licence, an electrical fitter licence authorises the holder to perform all electrical equipment work. Example of what the holder of an electrical fitter licence may do Electrical work, whether in a workshop or on site, of building, manufacturing, fitting, assembling, erecting, operating, testing or repairing electrical equipment. 29 What electrical jointer licence authorises Subject to particular conditions or restrictions included in the licence, an electrical jointer licence authorises the holder to perform electrical work to the extent of the following (a) (b) installing, jointing and terminating cables to the extent the work requires specialised knowledge or skill; electrical equipment work necessary for the work mentioned in paragraph (a). 30 What restricted electrical work licence authorises (1) A restricted electrical work licence authorises the holder to perform electrical work only of a particular type stated in the licence.
31 s s 33 Example of what the holder of a restricted electrical work licence may do A restricted electrical work licence may restrict the holder to the performance of electrical work incidental or special to a particular calling. (2) A restricted electrical work licence (a) does not entitle the holder to another electrical licence; and (b) must not be taken into account in deciding whether the holder is qualified to obtain or hold another electrical licence. 31 What electrical work training permit authorises (1) An electrical work training permit authorises the holder to perform electrical work stated in the permit in accordance with the conditions about training stated in the permit. (2) An electrical work training permit (a) (b) does not entitle the holder to another electrical licence; and must not be taken into account in deciding whether the holder is qualified to obtain or hold another electrical licence. 32 External licence equivalents An external licence mentioned in schedule 1 is equivalent to the electrical work licence stated in the schedule for the external licence. Division 2 Electrical work licence requirements 33 General requirements (1) This section states requirements that apply generally for the issue of an electrical work licence, other than an electrical work training permit, to an applicant for the licence. (2) The chief executive must be satisfied that (a) (b) the applicant satisfies the eligibility requirements stated for the licence in this division; and the applicant is adequately able to understand, and read and write in, the English language without the aid of an interpreter.
No. 84 5755 EXTRAORDINARY GAZETTE THE SOUTH AUSTRALIAN GOVERNMENT GAZETTE. www.governmentgazette.sa.gov.au PUBLISHED BY AUTHORITY
No. 84 5755 EXTRAORDINARY GAZETTE THE SOUTH AUSTRALIAN GOVERNMENT GAZETTE www.governmentgazette.sa.gov.au PUBLISHED BY AUTHORITY ALL PUBLIC ACTS appearing in this GAZETTE are to be considered official,