Source: https://www.ecfr.gov/cgi-bin/text-idx?mc=true&node=se40.23.97_1830&rgn=div8
Timestamp: 2020-07-02 10:20:48
Document Index: 534838851

Matched Legal Cases: ['art 97', '§97', '§97', 'art 75', '§97', '§72', 'art 75', '§97', '§75', '§97', 'art 75', '§97', '§75', '§97', '§97', 'art 75', '§75', '§75', '§97', '§75', '§75', 'art 75', 'art 75', '§97', 'art 75', 'art 75', '§97', '§97', '§75']

Title 40 → Chapter I → Subchapter C → Part 97 → Subpart EEEEE → §97.830
§97.830 General monitoring, recordkeeping, and reporting requirements.
The owners and operators, and to the extent applicable, the designated representative, of a CSAPR NOX Ozone Season Group 2 unit, shall comply with the monitoring, recordkeeping, and reporting requirements as provided in this subpart and subpart H of part 75 of this chapter. For purposes of applying such requirements, the definitions in §97.802 and in §72.2 of this chapter shall apply, the terms “affected unit,” “designated representative,” and “continuous emission monitoring system” (or “CEMS”) in part 75 of this chapter shall be deemed to refer to the terms “CSAPR NOX Ozone Season Group 2 unit,” “designated representative,” and “continuous emission monitoring system” (or “CEMS”) respectively as defined in §97.802, and the term “newly affected unit” shall be deemed to mean “newly affected CSAPR NOX Ozone Season Group 2 unit”. The owner or operator of a unit that is not a CSAPR NOX Ozone Season Group 2 unit but that is monitored under §75.72(b)(2)(ii) of this chapter shall comply with the same monitoring, recordkeeping, and reporting requirements as a CSAPR NOX Ozone Season Group 2 unit.
(a) Requirements for installation, certification, and data accounting. The owner or operator of each CSAPR NOX Ozone Season Group 2 unit shall:
(2) Successfully complete all certification tests required under §97.831 and meet all other requirements of this subpart and part 75 of this chapter applicable to the monitoring systems under paragraph (a)(1) of this section; and
(b) Compliance deadlines. Except as provided in paragraph (e) of this section, the owner or operator of a CSAPR NOX Ozone Season Group 2 unit shall meet the monitoring system certification and other requirements of paragraphs (a)(1) and (2) of this section on or before the latest of the following dates and shall record, report, and quality-assure the data from the monitoring systems under paragraph (a)(1) of this section on and after the latest of the following dates:
(1) May 1, 2017;
(2) 180 calendar days after the date on which the unit commences commercial operation; or
(3) Where data for the unit are reported on a control period basis under §97.834(d)(1)(ii)(B), and where the compliance date under paragraph (b)(2) of this section is not in a month from May through September, May 1 immediately after the compliance date under paragraph (b)(2) of this section.
(4) The owner or operator of a CSAPR NOX Ozone Season Group 2 unit for which construction of a new stack or flue or installation of add-on NOX emission controls is completed after the applicable deadline under paragraph (b)(1), (2), or (3) of this section shall meet the requirements of §75.4(e)(1) through (4) of this chapter, except that:
(i) Such requirements shall apply to the monitoring systems required under §97.830 through §97.835, rather than the monitoring systems required under part 75 of this chapter;
(ii) NOX emission rate, NOX concentration, stack gas moisture content, stack gas volumetric flow rate, and O2 or CO2 concentration data shall be determined and reported, rather than the data listed in §75.4(e)(2) of this chapter; and
(iii) Any petition for another procedure under §75.4(e)(2) of this chapter shall be submitted under §97.835, rather than §75.66 of this chapter.
(c) Reporting data. The owner or operator of a CSAPR NOX Ozone Season Group 2 unit that does not meet the applicable compliance date set forth in paragraph (b) of this section for any monitoring system under paragraph (a)(1) of this section shall, for each such monitoring system, determine, record, and report maximum potential (or, as appropriate, minimum potential) values for NOX concentration, NOX emission rate, stack gas flow rate, stack gas moisture content, fuel flow rate, and any other parameters required to determine NOX mass emissions and heat input in accordance with §75.31(b)(2) or (c)(3) of this chapter, section 2.4 of appendix D to part 75 of this chapter, or section 2.5 of appendix E to part 75 of this chapter, as applicable.
(d) Prohibitions. (1) No owner or operator of a CSAPR NOX Ozone Season Group 2 unit shall use any alternative monitoring system, alternative reference method, or any other alternative to any requirement of this subpart without having obtained prior written approval in accordance with §97.835.
(2) No owner or operator of a CSAPR NOX Ozone Season Group 2 unit shall operate the unit so as to discharge, or allow to be discharged, NOX to the atmosphere without accounting for all such NOX in accordance with the applicable provisions of this subpart and part 75 of this chapter.
(3) No owner or operator of a CSAPR NOX Ozone Season Group 2 unit shall disrupt the continuous emission monitoring system, any portion thereof, or any other approved emission monitoring method, and thereby avoid monitoring and recording NOX mass discharged into the atmosphere or heat input, except for periods of recertification or periods when calibration, quality assurance testing, or maintenance is performed in accordance with the applicable provisions of this subpart and part 75 of this chapter.
(4) No owner or operator of a CSAPR NOX Ozone Season Group 2 unit shall retire or permanently discontinue use of the continuous emission monitoring system, any component thereof, or any other approved monitoring system under this subpart, except under any one of the following circumstances:
(i) During the period that the unit is covered by an exemption under §97.805 that is in effect;
(iii) The designated representative submits notification of the date of certification testing of a replacement monitoring system for the retired or discontinued monitoring system in accordance with §97.831(d)(3)(i).
(e) Long-term cold storage. The owner or operator of a CSAPR NOX Ozone Season Group 2 unit is subject to the applicable provisions of §75.4(d) of this chapter concerning units in long-term cold storage.