Source: http://delcode.delaware.gov/title16/c073/
Timestamp: 2018-02-24 09:33:30
Document Index: 576258124

Matched Legal Cases: ['§ 7301', '§ 7302', '§ 7303', '§ 7304', '§ 7305', '§ 7306', '§ 7307', '§ 7308', '§ 7309', '§ 7310', '§ 7311', '§ 7312', '§ 7313', '§ 7314', '§ 7301', '§ 1', '§ 1', '§ 3454', '§ 3924', '§ 7301', '§ 7302', '§ 7303', '§ 7304', '§ 3', '§ 3456', '§ 3926', '§ 7304', '§ 1', '§ 7305', '§ 2', '§ 2', '§ 3455', '§ 3925', '§ 7305', '§ 2', '§ 7306', '§ 7307', '§ 7308', '§ 6', '§ 7309', '§ 7310', '§ 7311', '§ 8', '§ 7312', '§ 2', '§ 7313', '§ 7314', '§ 7311', '§ 7312']

TITLE 16 - CHAPTER 73. PRODUCTS UTILIZING PETROLEUM DERIVATIVES
§ 7301 § 7302 § 7303 § 7304 § 7305 § 7306 § 7307 § 7308 § 7309 § 7310 § 7311 § 7312 § 7313 § 7314
§ 7301 Selling without fire test; method of testing.
(a) No person shall sell or offer for sale, within the limits of this State, any kerosene, headlight or other oil for illuminating purposes produced from petroleum, which will not bear the fire test of at least 115° Fahrenheit.
(b) The fire test shall be determined by the use of the Tagliabue instrument or apparatus in method and manner as follows: Partially fill the metal cup with water about 60° Fahrenheit temperature, leaving room for displacement by the glass oil cup; fill the glass oil cup with the oil to be tested, to within 1/4 of an inch of the top of the cup, remove all oil from the top edge of the cup using soft paper for such purpose; see that the surface of oil in the cup is free from air bubbles; suspend the thermometer with the bulb just below the surface of the oil; heat with a small alcohol flame; when the thermometer indicates 100° Fahrenheit; remove flame and allow temperature to run up to 103° Fahrenheit; at which point try for flash with small bead of fire on the end of a string, or otherwise, held not less than 1/4 of an inch above the surface of the oil; if the oil does not flash or if it flashes and does not continue to burn, replace flame, work temperature up 4° Fahrenheit more, then remove flame, allow temperature to run up 3° Fahrenheit more and again try to flash; if the oil flashes, or if it flashes and does not continue to burn, repeat this operation until 114° Fahrenheit are reached, at which point, if the oil does not flash or if it flashes and does not continue to burn, it shall be deemed and considered as of not less than 115° fire test; but the oil thus tested shall not be deemed or considered as of not less than 115° fire test if it flashes and continues to burn at 114° Fahrenheit or at a lower temperature.
(c) The temperature in making the test, as set forth in subsection (b) of this section, shall not be raised or allowed to rise in any instance faster than 2° Fahrenheit per minute.
14 Del. Laws, c. 411, § 1; 24 Del. Laws, c. 161, § 1; Code 1915, § 3454; Code 1935, § 3924; 16 Del. C. 1953, § 7301.;
§ 7302 Tests by State Chemist; fees.
§ 7303 Report of test failures to Attorney General.
§ 7304 Civil liability.
If any person sustains property damage or personal injury by reason of a violation of this chapter by another person, the person guilty of the violation shall be liable to the person injured for damages sustained thereby.
14 Del. Laws, c. 411, § 3; Code 1915, § 3456; Code 1935, § 3926; 16 Del. C. 1953, § 7304; 70 Del. Laws, c. 186, § 1.;
§ 7305 Legislative intent.
It is hereby declared that modern, efficient, safety-tested portable oil-fueled heaters may be offered for sale, sold and used in this State. However, fire hazards and other dangers to the health, safety and welfare of the inhabitants of this State may exist in the absence of legislation the purpose of which is to reasonably assure that portable oil-fueled heaters offered for sale to, sold to and used by inhabitants of this State are modern, efficient and safety tested. It is the intent of the General Assembly to hereinafter set forth such legislation.
14 Del. Laws, c. 411, § 2; 24 Del. Laws, c. 161, § 2; Code 1915, § 3455; Code 1935, § 3925; 16 Del. C. 1953, § 7305; 63 Del. Laws, c. 117, §§ 2, 3.;
§ 7306 Definitions.
(1) "1-K" or "K-1 kerosene" means kerosene that has been distilled from petroleum to meet the current specifications of A.S.T.M. (American Society for Testing of Materials) #D3699 (1978) for 1-K.
(2) "2-K" or "K-2 kerosene" means kerosene that has been distilled from petroleum to meet the current specifications of A.S.T.M. #D3699 (1978) for 2-K.
(3) "Approved" means acceptable to the authority having jurisdiction over the sale and use of portable oil-fueled heaters as hereinafter set forth.
(4) "Listed" means any portable oil-fueled heater which has been evaluated with respect to reasonably foreseeable hazards to life and property by any 1 of the following nationally recognized testing or inspection agencies: Underwriters Laboratories, Inc., Canadian Standards Association, Factory Mutual System, Applied Research Laboratories of Florida, Inc., Electrical Testing Laboratory and which has been authorized by the State Fire Prevention Commission as being reasonably safe for its specific purpose and shown in a list published by such agency and bears the mark, name or symbol of such agency as indication that it has been so authorized. Such evaluation shall include but not be limited to evaluation of the requirements hereinafter set forth. Similar evaluations by a nationally recognized testing or inspection agency other than the above mentioned which are approved by the State Fire Marshal may be listed as well.
(5) "Oil" means any liquid fuel with a flash point of greater than 100 degrees Fahrenheit, including but not limited to kerosene.
(6) "Portable oil-fueled heater" means any nonflue-connected, self-contained, self-supporting, oil-fueled, heating appliance equipped with an integral reservoir, designed to be carried from 1 location to another.
(7) "Structure" means any building or completed construction of any kind, including but not limited to, private dwellings or to any structure used for business, commercial or industrial purposes, but not including buildings under construction or buildings used solely for agricultural purposes.
§ 7307 Sale and use of portable oil-fueled heaters.
§ 7308 Requirements for approved portable oil-fueled heaters.
(1) Approved portable oil-fueled heaters must have labeling affixed thereto such as to caution and inform concerning:
a. Provision of an adequate source of ventilation when the heater is in operation;
b. Use of only suitable fuel for the heater;
c. Proper manner of refueling;
d. Proper placement and handling of the heater when in operation; and
e. Proper procedures for lighting, flame regulation and extinguishing the heater.
(2) Approved portable oil-fueled heaters must be packaged with instructions such as to inform concerning proper maintenance and operation.
(3) Approved portable oil-fueled heaters must be constructed with a low center of gravity and minimum tipping angle of 33 degrees from the vertical with an empty reservoir.
(4) Approved portable oil-fueled heaters must have an automatic safety shut-off device or inherent design feature which eliminates fire hazards in the event of tipover and otherwise conform with the standards set forth in National Fire Protection Association (NFPA) No. 31.
(5) Approved portable oil-fueled heaters must not produce carbon monoxide at rates which create a hazard when operated as intended and instructed.
63 Del. Laws, c. 117, § 6.;
§ 7309 Storage of kerosene.
Any portable containers in which kerosene is stored must not be red in color, nor may they be made of glass. They must be clearly marked "kerosene."
§ 7310 Authority of State Fire Prevention Commission.
§ 7311 Penalties; jurisdiction.
Whoever violates this chapter shall be fined not more than $200 for each offense. The Superior Court shall have jurisdiction to adjudicate offenses under this chapter.
63 Del. Laws, c. 117, § 8.;
§ 7312 Kerosene labeling requirements.
1-K and 2-K kerosene which is kept, offered, exposed for sale or sold within the State shall be properly identified as meeting A.S.T.M. standards. Such identification requirements shall apply to every dispenser and delivery ticket (manifest or invoice) accompanying the transfer of kerosene which is kept, offered, exposed for sale or sold in the State. Furthermore, dispensers or retail pumps of kerosene fuels other than 1-K must bear the following warning label in a conspicuous place: A.S.T.M. grade 2-K kerosene is not suitable for use in unvented (flueless) portable heaters. Evidence for the quality of 1-K or 2-K from the supplier of kerosene shall be maintained at the retail sales location and shall be available for state inspection during normal business hours.
64 Del. Laws, c. 31, § 2.;
§ 7313 Kerosene inspection, sampling and testing.
The weights and measures section of the State Department of Agriculture shall be responsible for the inspection, sampling and testing of kerosene sold by dealers within the State to determine compliance with labeling requirements. Tests shall be conducted on kerosene kept, offered, exposed for sale or sold within the State in order to determine if the product specifications meet the minimum specifications of the type of product being sold. A "stop sale" shall be issued immediately by the Department of Agriculture for all kerosenes found to be mislabeled or misrepresented.
§ 7314 Penalties.
Notwithstanding § 7311 of this title, persons who do not comply with labeling and/or certification provisions of §§ 7312 and 7313 of this title shall be punished by a fine of not less than $25 or more than $200, or by imprisonment for not more than 1 month, or by both such fine and imprisonment; and upon a subsequent conviction thereof, they shall be punished by a fine of not less than $50 or more than $500, or by imprisonment for not more than 6 months, or by both such fine and imprisonment. The Superior Court shall have jurisdiction to adjudicate offenses under this section.