Source: https://www.scribd.com/document/358313242/T13-ALBANY-PLUS-Tech-pdf
Timestamp: 2019-01-22 01:58:33
Document Index: 336491035

Matched Legal Cases: ['art 2', 'art\n220', 'art 220', 'arth 3', 'art 1', 'arth 3', 'art 2', 'art 2', 'art 2', 'art 2', 'art 2', 'arth 3', 'arth 3', 'art 2', 'art 2', 'arth 3', 'art 2']

T13 ALBANY PLUS Tech.pdf | Ac Power Plugs And Sockets | Electrical Wiring
+44 (0)1268 563720
Socket outlets, switches and other MK wiring accessories can be wall or bench mounted. Do not use a trailing lead for sockets and
connection units or mount any devices where they may be subject to excessive moisture or dampness.
Socket outlets, switches and other MK wiring accessories can be mounted in a variety of MK trunking systems.
13A socket outlets comply with
BS 1363 Part 2:1995.
Replacement fuses to the 3 gang switchsocket
outlets (Logic Plus only) comply with Description
BS 1362:1973.
A range of socket outlets designed for ease of installation and having all the
advantageous design features of the MK range of wiring devices. The 2 gang
TECHNICAL SPECIFICATION sockets with outboard rockers (available in Logic Plus and Albany Plus) are of
ELECTRICAL particular value for use by the infirm and partially sighted whilst the same feature in
VOLTAGE RATING Metalclad Plus is ideal for use with gloved hands.
Non-standard clean earth sockets are for use on installations where restricted
CURRENT RATING access is required and will only accept a 647WHI 13A non-standard plug with
(3 Gang Switchsocket 13A total)
T-shaped earth pin. The sockets have two independent earth terminals so that they
can also be used for ‘clean earth’ installations. The K2746CE and K2947CE also
TERMINAL CAPACITY have two independent earth terminals for ‘clean earth’ installations.
3 x 2.5mm² A variety of sockets (see Technical Specification) are fitted with two earth terminals
on a common busbar to provide a double earth facility for use when installations
2 x 6mm² (standard)
(Dual earth terminals on list Nos. K781, K2657, require a high integrity protective connection as specified within the latest edition of
K2737, K2746, K2757, all standard Edge and Aspect BS 7671 which should be referred to for guidance.
sockets, K733, K2958, K2458, K2947, K2947D6,
K850, K2977, K2477, K3045, K3077, K2945, The products can be quickly installed as replacement for existing 13A sockets or in
K2945D6 and K5357) a new installation.
–5°C to +40°C (Logic Plus 3 gang switchsocket only)
IP RATING The fuse carrier is opened by a fast-acting, screwdriver-operated, worm-drive screw
IP2XD for ease of replacement.
For a full range of corresponding products,
see pages 32-188 in the product selector.
1 gang switchsocket – view from rear
Top-facing, angled, backed-out terminals
make wiring easier and quicker.
l	Moulded ‘on’ indicator flash on plastic l	Additional electrical safety from DP
switches will not rub off – totally safe Switch, neutral ‘make first’, ‘break last’
(Edge™ and Aspect only) l	Switch contacts with silver contacts
on both surfaces for good continuity
Optional neon indicators in the switch
rockers with 175° visibility in the l	Only one size of screwdriver required
horizontal and vertical planes for installation
l	3 pin operated safety shutter l	Selection of products incorporating
dual earth terminals for high integrity
Printed terminal markings on grey rear
mouldings for clearer identification
l	Backed out and captive terminal
l	Top access, angled terminals make
l	‘Clean earth’ sockets available
l	3mm minimum switch contact gap
l	Non-standard ‘clean earth’ sockets
l	Double pole switching
l	Choice of inboard or outboard
– Logic Plus™
2 Gang Switchsocket Outlet with Integrated
Logic Plus™ 13A socket outlets and 2A USB
charging outlets comply with BS 5733 and
IEC 61558-2-16.
Products are CE marked and meet the
requirements of the Low Voltage, EMC, RoHS
13A SOCKET OUTLETS A range of socket outlets designed for ease of installation and having all the
ELECTRICAL advantageous design features of the Logic Plus™ range. Dual USB charging outlets
VOLTAGE RATING offer end users easy access to power for charging a variety of devices such as
220-240V smart phones, tablets and cameras.
Combined total 2A drawn from USB outlets
l Moulded ‘on’ indicator flash on l USB outlets are designed to provide
switches will not rub off – totally safe optimum charging compatibility
l 3 pin operated safety shutter on 13A
socket outlets l Printed terminal markings on grey rear
3 x 2.5mm2 l USB 2.0 and 3.0 compatible
3 x 4mm2 l Top access, angled terminals make
l Can charge a device at up to a full 2A
2 x 6mm2 (stranded) wiring easier and quicker
l If only one device is connected to a
PHYSICAL l 3mm minimum switch contact gap
USB outlet the total output current of
AMBIENT OPERATING TEMPERATURE 2A is available from either outlet l Double pole switching
–5°C to +40°C l If two devices are connected to USB l Additional electrical safety from
IP RATING outlets the the total rated current of 2A neutral ‘make first’, ‘break last’ feature
IP2XD is divided between the two outlets l Switch contacts with silver contacts
l Differing manufacturers devices can on both surfaces for good continuity
be charged simultaneously via the two
2000 metres l Backed out and captive terminal
l If the total charging current exceeds l Dual earthed
Installation the rated level of 2A then the device will
enter a current limiting safety mode
Logic Plus™ socket outlets can be wall or bench l Electronically protected against an
mounted. overload or short circuit on either USB
Do not mount or use as a trailing socket or
where they may be subject to excessive
moisture or damp. Dimensions (mm)
Cable management 146 40
Logic Plus™ socket outlets can be mounted in a
variety of MK trunking systems.
BOX TYPES WITHOUT PATRESS
GANG FLUSH INSULATED METAL
DEPTH 35MM DEPTH 40MM DEPTH 41MM
886 ZIC K2172 WHI
120.6 28 443
Aspect 13A socket outlets and 2A USB
ELECTRICAL advantageous design features of the Aspect range. Dual USB charging outlets offer
VOLTAGE RATING end users easy access to power for charging a variety of devices such as smart
220-240V phones, tablets and cameras.
Combined total 2A drawn from USB outlets FEATURES
STANDBY POWER l Slim screwless frontplate design l Electronically protected against an
150mW overload or short circuit on either USB
l Matching metal rocker switches
TERMINAL CAPACITY l 3 pin operated safety shutter on 13A
Live, neutral & earth l USB outlets are designed to provide
3 x 2.5mm2 optimum charging compatibility
3 x 4mm2 l USB 2.0 and 3.0 compatible across a wide range of devices
2 x 6mm2 (stranded) Can charge a device at up to a full 2A
l l Printed terminal markings on grey rear
PHYSICAL l If only one device is connected to a mouldings for clearer identification
AMBIENT OPERATING TEMPERATURE USB outlet the total output current of l Top access, angled terminals make
–5°C to +40°C 2A is available from either outlet wiring easier and quicker
l If two devices are connected to USB l 3mm minimum switch contact gap
IP2XD outlets the the total rated current of 2A l Double pole switching
is divided between the two outlets
MAX. INSTALLATION ALTITUDE l Additional electrical safety from
l Differing manufacturers devices can
2000 metres neutral ‘make first’, ‘break last’ feature
USB outlets l Switch contacts with silver contacts
Installation l If the total charging current exceeds
the rated level of 2A then the device will l Backed out and captive terminal
Aspect socket outlets can be wall or bench enter a current limiting safety mode screws
mounted. l Dual earthed
Cable management 146.4 40
Aspect socket outlets can be mounted in
a variety of MK trunking systems.
GANG FLUSH
878 ZIC
EMC Compatibility: IEC 61000-6-1 IEC 61000-6-3 Products are CE marked and meet the requirements of the Low Voltage.0 and 3. Dual USB charging outlets offer VOLTAGE RATING end users easy access to power for charging a variety of devices such as smart 220-240V phones. TECHNICAL SPECIFICATION Description 13A SOCKET OUTLETS A range of socket outlets designed for ease of installation and having all the ELECTRICAL advantageous design features of the EdgeTM range. ‘break last’ feature IP RATING IP2XD l Differing manufacturers devices can l Switch contacts with silver contacts be charged simultaneously via the two on both surfaces for good continuity MAX. CURRENT RATING 13A FEATURES Combined total 2A drawn from USB outlets l Matching metal rocker switches l USB Outlets are designed to provide STANDBY POWER optimum charging compatibility 150mW l 3 pin operated safety shutter on 13A across a wide range of devices socket outlets TERMINAL CAPACITY l Printed terminal markings on grey rear Live.5mm2 l Can charge a device at up to a full 2A 3 x 4mm2 l Top access. INSTALLATION ALTITUDE USB outlets l Backed out and captive terminal 2000 metres l If the total charging current exceeds screws the rated level of 2A then the device will l Dual earthed enter a current limiting safety mode Installation l Electronically protected against an EdgeTM socket outlets can be wall or bench overload or short circuit on either USB mounted. neutral & earth l USB 2. outlet Do not mount or use as a trailing socket or where they may be subject to excessive moisture or damp.0 compatible mouldings for clearer identification 3 x 2. RoHS and WEEE directives. Dimensions (mm) Cable management 146 40 EdgeTM socket outlets can be mounted in a variety of MK trunking systems.6 35. BOX TYPES WITHOUT PATRESS 86 GANG FLUSH DEPTH 47MM 2 GANG 878 ZIC 120. Wiring Devices Technical WIRING DEVICES Technical Hotline +44 (0)1268 563720 – Edge™ 2 Gang Switchsocket Outlet with Integrated Dual USB Charging Capability Standards and approvals EdgeTM 13A socket outlets and 2A USB charging outlets comply with BS 5733 and IEC 61558-2-16.7 445 . EMC. angled terminals make 2 x 6mm2 (stranded) l If only one device is connected to a wiring easier and quicker USB outlet the total output current of l 3mm minimum switch contact gap PHYSICAL 2A is available from either outlet AMBIENT OPERATING TEMPERATURE l Double pole switching l If two devices are connected to USB –5°C to +40°C outlets the the total rated current of 2A l Additional electrical safety from is divided between the two outlets neutral ‘make first’. tablets and cameras.
Dual USB charging VOLTAGE RATING outlets offer end users easy access to power for charging a variety of devices such 220-240V as smart phones. Dimensions (mm) Cable management 146.8 SURFACE SURFACE GANG FLUSH INSULATED METAL DEPTH 35MM DEPTH 40MM DEPTH 41MM 2 GANG K2212ALM / 886 ZIC K2172 WHI K2214ALM 120. overload or short circuit on either USB outlet Do not mount or use as a trailing socket or where they may be subject to excessive moisture or damp. ‘break last’ feature IP2XD is divided between the two outlets l Switch contacts with silver contacts l Differing manufacturers devices can on both surfaces for good continuity MAX.0 and 3. RoHS and WEEE directives. angled terminals make l Can charge a device at up to a full 2A 2 x 6mm2 (stranded) wiring easier and quicker l If only one device is connected to a PHYSICAL l 3mm minimum switch contact gap USB outlet the total output current of AMBIENT OPERATING TEMPERATURE 2A is available from either outlet l Double pole switching –5°C to +40°C l If two devices are connected to USB l Additional electrical safety from IP RATING outlets the the total rated current of 2A neutral ‘make first’.6 27. CURRENT RATING 13A FEATURES Combined total 2A drawn from USB outlets l Moulded ‘on’ indicator flash on l USB outlets are designed to provide STANDBY POWER switches will not rub off – totally safe optimum charging compatibility 150mW across a wide range of devices l 3 pin operated safety shutter on 13A TERMINAL CAPACITY socket outlets l Printed terminal markings on grey rear Live. EMC Compatibility: IEC 61000-6-1 IEC 61000-6-3 Products are CE marked and meet the requirements of the Low Voltage. TECHNICAL SPECIFICATION Description 13A SOCKET OUTLETS A range of socket outlets designed for ease of installation and having all the ELECTRICAL advantageous design features of the Albany Plus™ range. Wiring Devices Technical WIRING DEVICES mkelectric.5mm2 l USB 2. neutral & earth mouldings for clearer identification 3 x 2.uk – Albany Plus™ 2 Gang Switchsocket Outlet with Integrated Dual USB Charging Capability Standards and approvals Albany Plus™ 13A socket outlets and 2A USB charging outlets comply with BS 5733 and IEC 61558-2-16. EMC.1 40 Albany Plus™ socket outlets can be mounted in a variety of MK trunking systems.0 compatible 3 x 4mm2 l Top access. BOX TYPES WITHOUT PATRESS 85.co. INSTALLATION ALTITUDE be charged simultaneously via the two 2000 metres l Backed out and captive terminal USB outlets screws l If the total charging current exceeds l Dual earthed the rated level of 2A then the device will Installation enter a current limiting safety mode Albany Plus™ socket outlets can be wall or l Electronically protected against an bench mounted. tablets and cameras.7 446 .
INSTALLATION ALTITUDE be charged simultaneously via the two 2000 metres l Backed out and captive terminal USB outlets screws l If the total charging current exceeds l Metallic powder paint finish is Installation the rated level of 2A then the device will corrosion and scratch resistant enter a current limiting safety mode Metalclad Plus™ socket outlets can be wall or l Dual earthed l Electronically protected against an bench mounted. EMC Compatibility: IEC 61000-6-1 IEC 61000-6-3 Products are CE marked and meet the requirements of the Low Voltage. Dimensions (mm) Cable management 146 40 Metalclad Plus™ socket outlets can be mounted in a variety of MK trunking systems. Dual USB charging VOLTAGE RATING outlets offer end users easy access to power for charging a variety of devices such 220-240V as smart phones. overload or short circuit on either USB l High impact resistance outlet Do not mount or use as a trailing socket or where they may be subject to excessive moisture or damp.7 447 . BOX TYPES WITHOUT PATRESS 85. EMC. Wiring Devices Technical WIRING DEVICES Technical Hotline +44 (0)1268 563720 – Metalclad Plus™ 2 Gang Switchsocket Outlet with Integrated Dual USB Charging Capability Standards and approvals Metalclad Plus™ 13A socket outlets and 2A USB charging outlets comply with BS 5733 and IEC 61558-2-16. neutral & earth mouldings for clearer identification 3 x 2. tablets and cameras. TECHNICAL SPECIFICATION Description 13A SOCKET OUTLETS A range of socket outlets designed for ease of installation and having all the ELECTRICAL advantageous design features of the Metalclad Plus™ range.8 GANG FLUSH SURFACE DEPTH 35MM DEPTH 38MM 2 GANG K830 ALM (without knockouts) 886 ZIC K897 ALM and K897 WHI (with 8 x 20mm knockouts) 120. RoHS and WEEE directives.0 compatible 3 x 4mm2 l Top access. CURRENT RATING 13A FEATURES Combined total 2A drawn from USB outlets l Moulded ‘on’ indicator flash on l USB outlets are designed to provide STANDBY POWER switches will not rub off – totally safe optimum charging compatibility 150mW across a wide range of devices l 3 pin operated safety shutter on 13A TERMINAL CAPACITY socket outlets l Printed terminal markings on grey rear Live.0 and 3. angled terminals make l Can charge a device at up to a full 2A 2 x 6mm2 (stranded) wiring easier and quicker l If only one device is connected to a l 3mm minimum switch contact gap PHYSICAL USB outlet the total output current of AMBIENT OPERATING TEMPERATURE 2A is available from either outlet l Double pole switching –5°C to +40°C l If two devices are connected to USB l Additional electrical safety from IP RATING outlets the the total rated current of 2A neutral ‘make first’.6 27. ‘break last’ feature is divided between the two outlets IP2XD l Switch contacts with silver contacts l Differing manufacturers devices can on both surfaces for good continuity MAX.5mm2 l USB 2.
i. If it does not. This CURRENT RATING makes them ideal for use where it would be hazardous for equipment to suddenly 13A resistive energise after return of mains power. such as use with rotating machinery and heat Rated tripping current 10mA/30mA developing apparatus. The Sentrysocket BS EN 50082-1:1998 units are not suitable for mounting in damp environments or outdoors.c.T rcd protected disappear. Sentrysockets products can be wall or bench mounted.e. do not use. Press Reset (R) after testing.e. T Red : ON Black: OFF test before use sentrysocket ALWAYS TEST BEFORE USE Press Test (T) button.6 120.3 26. white off (tripped) 86 86 red on on active control device trips with T loss of mains 10mA tripping current R sentrysocket rcd protected 448 120. TERMINAL CAPACITY 3 x 4mm2 for 1 gang Passive control circuits 2 x 4mm2 for 2 gang Incorporate a ‘Stay-set’ mechanism and is mains failure proof. it will function PHYSICAL under all the normal conditions expected of an RCD and will not trip in the event of a power cut.co. TECHNICAL SPECIFICATION Active control circuits ELECTRICAL Incorporate a ‘Re-set’ mechanism and are mains failure sensitive. Flag below Reset (R) button.uk Sentrysocket Compliance with EC Directives. Albany Plus™ and Metalclad pole switching enhanced RF Immunity performance Plus™ Sentrysockets can be mounted in a variety of MK trunking systems.c. the event of a power cut or a sudden. commercial and light industrial applications. Installation Flush mounting steel wall box Dimensions (mm) It should be noted that some of the conduit Single socket Double socket entries may be restricted. BS EN 61543:1996.c. Red flag should press button . BS 7288:1990 particularly when they are in damp environments or outdoors. depending upon their 146 146 3. l	Masterseal Plus products are ideal MAX. Wiring Devices Technical WIRING DEVICES mkelectric. i. but will also trip in 240V a. is part of a complete range of fixed and also comply with the requirements of portable wiring devices and circuit protection devices suitable for use in domestic. INSTALLATION ALTITUDE commercial and light industrial for use with equipment subject to wet 2000 metres applications weather or high humidity Sentrysockets are not suitable for connection across l	Active and passive control circuit l	Part of a complete range of MK circuit two lines of a 127V line to Neutral Voltage System applications protection devices l	Flexible and versatile in use l	They are a. double sockets are single l	Double Socket products have an Logic Plus™.5 positions and the depth of box used. Sentrysocket RCD SP Double Sockets Sentrysocket. l	sensitive for residual current Single Sockets have double pole Cable management switching. incorporating an RCD. IP RATING FEATURES IP2XD IP66 (K56301/K56231/K56233) l	Suitable for most residential. Do not mount or use as a trailing socket or where they maybe subject to excessive moisture or dampness. This makes it suitable for use with freezers or in inaccessible or AMBIENT OPERATING TEMPERATURE –5°C to +40°C unmanned locations.6 9 . dramatic reduction in mains voltage. and pulsating d. they will RATED VOLTAGE function under all the normal conditions expected of an RCD. Standards and approvals All Sentrysockets comply with the following EC Directives and are CE marked: Low Voltage Directive Electromagnetic Compatibility Directive (89/336/EEC) Sentrysocket RCD DP Single Sockets comply Description with the requirements of the following standards: Sentrysocket provides a high level of protection against electrocution and gives further protection when used with appliances vulnerable to insulation damage.
If the switch fails to 4. and contact your local electrician. the product 1. On mains failure.	Ensure that no appliance is connected to the Sentrysocket. that the Sentrysocket trips within the specified time: ≤ 200 ms AT RATED TRIP CURRENT If all the operations in steps 2 to 8 above give correct results.	Reset all tripped RCD’s including the Sentrysocket. Sentrysocket is faulty and should 7. or your local MK stockist. a Sentrysocket with Active Control Circuit will trip. Note: If a fault is identified at any stage of installation testing procedure do not use Sentrysocket. If no faults have been found then installation testing has been completed successfully.	Switch off the mains supply switch disconnector.	A Sentrysocket with Active Control Circuit should trip while a 3. do not use the Sentrysocket product and seek RCD is in series then there is no guarantee as to which device professional advice or contact the MK Technical Sales and will trip first).	Connect an RCD Tester to either socket outlet and ensure that switched on.	Switch off the Mains Supply Switch Disconnector. To test that the Sentrysocket is functioning correctly: 3. the ≤ 40 ms AT 5 x RATED TRIP CURRENT Sentrysocket RCD socket outlet is safe to use.	Ensure that no appliance is connected to the Sentrysocket. In Switch Sentrysocket on: The switch should remain closed this state the socket outlets are disconnected from the supply.	Switch Sentrysocket on: Connect an RCD tester and ensure Sentrysocket with Passive Control Circuit should not trip. 4. not reversed or the Supply N connection is not open circuit.	If the Sentrysocket stays on. present at the socket outlet.	Reset – Press the button marked R again. it is faulty and should not be used – see note below.	Reset the Sentrysocket as in step 2 above. indicating that the socket After installation. 449 . turn the mains electricity supply on. the Sentrysocket is faulty and should not be used.	Test – Press the TEST button marked T (for Test). If the Sentrysocket does not trip and there is mains voltage 6. the contact status remain closed. Wiring Devices Technical WIRING DEVICES Technical Hotline +44 (0)1268 563720 Sentrysocket Installation Double Socket Testing After installation. and the red flag will appear in the window. steps 1 to 4 below: Socket Testing 1. If the Active Control device does not trip. not be used. should trip with the contact status indicator showing black.	Reset – Press the button marked R (for Reset) – the contact Single Socket Testing status indicator should show red. 2. 8. the Sentrysocket trips with the specified times below: ≤ 200 ms AT RATED TRIP CURRENT 2. If the Sentrysocket does not trip within the specified times then If the procedures in steps 2 to 8 above are not completed the product is faulty and should not be used (If more than one correctly. turn the mains electricity supply on. 5. Flush mounting steel wall box It should be noted that some of the conduit entries may be restricted. Service department on +44 (0)1268 563720. check that the Supply L and N connections are indicator should show red. whilst a Sentrysocket with Passive Control Circuit will not trip. To test that the Sentrysocket is functioning correctly follow the depending upon their positions and the depth of box used. press the test button: The ≤ 40 ms AT 5 x RATED TRIP CURRENT switch will open and the white flag will appear In the window. If the Sentrysocket is correctly connected and still trips after being 5. outlets are now live (if the switches are in the ON positions).
TECHNICAL SPECIFICATION ELECTRICAL CURRENT RATING 13A maximum total for 2 sockets VOLTAGE RATING 250V a.c. Overload current causes temperature rise. Filter cassettes are supplied with sockets and have an LED which shows green IP RATING under normal conditions but will turn red or extinguish when a replacement cassette IP2XD (K1800WHI) is required.uk Filtered Switchsocket Outlets (Logic Plus and Albany Plus) Standards and approvals Filtered socket outlets comply with BS 5733:2010.5mm² l	Audio visual and hi-fi equipment 3 x 1. INSTALLATION ALTITUDE replacement necessity. Wiring Devices Technical WIRING DEVICES mkelectric.5mm² PHYSICAL These products can be quickly installed as replacements for existing twin 13A AMBIENT OPERATING TEMPERATURE sockets or in a new installation. designed to combat 0. mouldings for clearer identification changes from green to red when l	replacement required Reduces risk of damage to equipment and down time l	Simple replacement of cassettes l	Reduces risk of data loss l	10 year guarantee (except filter l	cassette) 2 way filtering – into appliance and back into mains supply l	3mm minimum switch contact gap l	Additional electrical safety from DP l	Backed out and captive terminal Switch. resulting in automatic ‘trip out’. latest edition of BS 7671. ‘break last’ screws feature 450 . SUPPRESSION 150 kHz – 30 MHz (transients) Such systems include: MAXIMUM ENERGY ABSORPTION l	Computer or microprocessor based equipment 140 Joules L – N 140 Joules L – E l	Telecommunications systems TERMINAL CAPACITY l	Electronic measurement equipment 2 x 6mm² l	Cash registers 3 x 4mm² 3 x 2.co. neutral ‘make first’. It can be de-activated if required.5 mA interference to or data losses on sensitive electrical products and systems due to mains borne voltage spikes and RFI. An alarm will also beep at 5 second intervals to indicate MAX. The overload device will re-set as Filter cassettes the temperature falls. Description EARTH LEAKAGE A range of sockets in the Logic Plus and Albany Plus styles. -5°C to +40°C Fitted with two earth terminals to provide a double earth facility for use when THERMAL OVERLOAD installations require a high integrity protective connection as specified within the The K1826 and K2826 filter socket incorporates a thermal overload device in the RFI filter section. 2000 metres FEATURES l	Moulded ‘on’ indicator flash on l	Double pole switches switches will not rub off – totally safe l	Dual earth terminals for high integrity l	3 pin operated safety shutter earthing l	Printed terminal markings on grey rear l	Clearly visible LED on filter cassette.
Locking screw The MK Filtered Switchsocket. 451 . before fitting it into the socket. and then gently pulling the cassette upwards. 2. When the filter cassette needs replacing. is optional. When this occurs the spike filer performance of the MK Filtered Switchsocket outlet can be restored by replacing the filter cassette. If these pins are damaged. and gently pushing it down while turning the screw clockwise until the filter cassette is flush with the surface.	Fit the new filter cassette by carefully sliding it into the aperture beep every five seconds may also be heard. The audible sound indicating that the filter cassette needs replacing. Audible warning l	it is important that all connections are made as instructed. 3. (see Figure 2a). the green indicator on the Replacement Filer Cassette will glow red or go out.	The filter cassette can be removed and replaced without switching off the mains or removing any plugs from the filter socket. an audible 4. Unpack the new filer cassette and check that the pins along the bottom edge are not bent or broken. connected equipment. The performance of these devices will eventually degrade with use to a level where they will no longer provide adequate protection. do not fit the replacement cassette. in common with many other filters uses Voltage Dependant Resistors for spike suppression purposes. It may be prevented by removing the small connector on the two end pins. (see Figure 2b). l	this product should be installed by a competent person. Product and packaging can safely be disposed of via standard refuse facilities at the end of its useful life. They will not completely remove the interference from the supply. contact MK Technical Sales Service Department on +44 (0)1268 563720. these Filter Sockets will reduce the magnitude the screw any further as this will cause distortion of the plastic of RFI and spikes and consequently their ability to interfere with mouldings.	Only fit the MK Replacement Filter Cassette (K1800WHI). If incassette doubt. Wiring Devices Technical WIRING DEVICES Technical Hotline +44 (0)1268 563720 Filtered Switchsocket Outlets Filter indicator Product features Audible warning Figure 2 connector Ensure that the connecting pins protruding from the bottom of Replacement the replacement Filter Cassette are not damaged or bent before filter installation. Figure 2b connector 1. Do not turn Note: As with all filters.	Remove the filter cassette by turning the jacking screw anti- clockwise to partially eject it (see Figure 2). Filter indicator Figure Filter 1 indicator Audible warning Audible warning connector Figure 2a connector Replacement filter cassette Locking screw Installation Replaceable Spike Filter Cassette Note: To ensure a safe installation.
5mm² 2 x 2. 3 x 2. “break last” feature on switched sockets 452 .co.5mm² 2 x 4mm² 2 x 6mm² (stranded) 15A sockets: FEATURES 3 x 2.c. TECHNICAL SPECIFICATION ELECTRICAL VOLTAGE RATING 250V a. 1 x 4mm² These products can be quickly installed as replacements for existing socket outlets 5A sockets: or in new installations. INSTALLATION ALTITUDE l	Additional electrical safety from 2000 metres neutral “make first”. 3mm minimum l	Printed terminal markings on grey rear IP RATING l	Double pole switching mouldings for clearer identification IP2XD l	Terminal screws backed out MAX.5mm² l	Top access terminals make wiring l	Switch contacts with silver contact 3 x 4mm² 2 x 6mm² (stranded) easier and quicker points on both surfaces for good l	continuity PHYSICAL Integral ON indicator on plastic switches will not rub off – totally safe l	5A and 15A sockets contain a 3 pin AMBIENT OPERATING TEMPERATURE l	operated safety shutter. -5°C to +40°C Switch contact gap.uk Round Pin Socket Outlets Standards and approvals Round pin socket outlets comply with BS 546:1950. TERMINAL CAPACITIES 2A sockets: Description 7 x 1mm² A range of round pin socket outlets designed for ease of installation and having all 4 x 1. Wiring Devices Technical WIRING DEVICES mkelectric.5mm² the advantages and design features of the MK range of wiring devices.
neutral & earth 3 x 2. Wiring Devices Technical WIRING DEVICES Technical Hotline +44 (0)1268 563720 Non UK Socket Outlets Standards and approvals 15A AMERICAN (Logic Plus*) 15A American sockets comply with SASO 2004:2003 16A 2P+E German sockets comply with IEC 60884-1:2006 TECHNICAL SPECIFICATION ELECTRICAL 15A AMERICAN BOX TYPES VOLTAGE RATING FLUSH 127V a.5mm² 2 x 4mm² 1 x 6mm² (stranded) 16A 2P+E GERMAN (Logic Plus*) MAX. CURRENT RATING 16A TERMINAL CAPACITY BOX TYPES Live. GANG FLUSH SURFACE (FOR EXTRA WIRING SPACE) CURRENT RATING 1 GANG 861ZIC 866ZIC K2140WHI 15A 2 GANG 862ZIC 886ZIC K2142WHI TERMINAL CAPACITY Live.c. neutral & earth GANG FLUSH SURFACE 4 x 1. IP2XD *15A American Sockets and 16A 2P+E German Sockets are also MAX. INSTALLATION ALTITUDE 2000 metres 16A 2P+E GERMAN SOCKET VOLTAGE RATING 250V a.c. INSTALLATION ALTITUDE available in a modular format for MK decorative wiring device ranges.5mm² 1 GANG 861ZIC K2140WHI 1 x 4mm² 2 GANG 862ZIC K2142WHI PHYSICAL AMBIENT OPERATING TEMPERATURE -5°C to +40°C IP RATING Note: 16A 2P+E German Outlet: These products are NOT suitable for 25mm deep boxes.5mm² 2 x 2. 2000 metres 453 .
toilets.uk Three Pole Fan Isolators Standards and approvals Comply with BS EN 60669-2-4:2005 TECHNICAL SPECIFICATION ELECTRICAL VOLTAGE RATING 250V a. 2 x 4mm² 1 x 6mm² The fan isolator can be used as a double pole or triple pole isolator. INSTALLATION ALTITUDE L1 L2 N 2000 metres Rear view of To Fan Unit without Timer Fan Isolator (see Fan Unit Intructions) N L (switched) N L Features Supply TOP l	Switchlock list no. timer controlled fans are often linked into the lighting circuit for energy TERMINAL CAPACITY 4 x 1mm² saving and convenience. storerooms and CIRCUIT CURRENT (Inc) basements where there is little or no natural light. RECOMMENDED SCPD GE Power Controls TIA32M40 32A IEC269-2-1 Fuse-link Wiring diagrams PHYSICAL AMBIENT OPERATING TEMPERATURE Two pole switching for fan units without timers -5°C to +40°C N L IP RATING Supply TOP IP4X L1 L2 N MAX. In such an installation there is often a need for the lighting 4 x 1. Wiring Devices Technical WIRING DEVICES mkelectric.5mm² routine maintenance and repairs can be carried out in complete safety.co.c.5mm² circuit to remain live to provide light whilst the fan unit is externally isolated so that 3 x 2. 3000A For example. CURRENT RATING Description 10A The MK Three Pole Fan Isolator provides a safe and simple method of isolating RATED CONDITIONAL SHORT mechanical fan units and is particularly useful in bathrooms. In addition it includes a clear on/off indicator and the frontplate features a fan isolator symbol for CONTACT GAP 4mm switch contact gap easy circuit identification. K4858 is available to allow L1 L2 N the isolator to be locked in the disconnected L1 L2 N position to facilitate fan maintenance To Fan Unit without Timer Rear view of (see Fan Unit Intructions) Fan Isolator N L (switched) Three pole switching for fan units incorporating timers N L Supply TOP L1 L2 N L1 L2 N To Fan Unit with Timer (see Fan Unit Intructions) Rear view of Fan Isolator N L (unswitched) L (switched) N L Supply TOP L1 L2 N L1 L2 N To Fan Unit with Timer Rear view of (see Fan Unit Intructions) Fan Isolator N L (unswitched) L (switched) 454 .
5 x 1. For installation in any other room where a wash basin or shower cubicle is installed then refer to the current IET wiring regulations. INSTALLATION ALTITUDE 2000 metres The fuse carrier is captive and opened by a fast acting. 455 . or 2 x 2. fused. Wiring Devices Technical WIRING DEVICES Technical Hotline +44 (0)1268 563720 – Logic Plus™ Shaver Socket Outlets Standards and approvals Shaver socket outlets comply with BS 4573:1970 and IEC 60884-1:2006. -5°C to +40°C Australian 6. and engagement face dimensions comply with BS 4573:1970.5mm². 3 x 1.6 flat blades each set at 30° to the vertical on a nominal pitch of IP RATING 13.7mm (230V socket). Input Designed for ease of installation and having many of the advantageous features of MAXIMUM LOAD the Logic PlusTM range. screwdriver operated worm drive screw for ease of replacement. IP2XD AS C112:1964. PHYSICAL European 4mm dia pins on 17 to 19mm pitch (230V socket) to IEC 83:1975 AMBIENT OPERATING TEMPERATURE Standard C5. Plug pin apertures.6mm pitch (230V socket) to BS 4573:1970. Non-isolated. TECHNICAL SPECIFICATION ELECTRICAL VOLTAGE RATING Description 200-250V a. condensation or damp conditions. shaver socket outlets must never be installed in any location subject to splashes. 200 mA (internal thermister trip current) TERMINAL CAPACITIES The shaver socket outlet accommodates the following plugs: Each terminal will accommodate 1 x 4mm². FEATURES l	Top access terminals make wiring l	White printed terminal markings quicker and easier on grey rear mouldings for clearer l	identification Only one size of screwdriver required for installation l	Front plate fixing screws retained on l	rear case moulding Terminal screws supplied ‘backed out’ and held captive within the terminal moulding Installation This shaver socket must not be used in bathrooms and washrooms.5 solid conductors British 5mm dia pins on 16.c. MAX.
Designed for ease of installation and having many of the advantageous design features of the MK range of wiring devices.c.7mm (230V socket) AS/NZS 3112:2000 l	American 6. TECHNICAL SPECIFICATION May be used in bathrooms and washrooms – must only be installed in accordance ELECTRICAL with the latest edition of BS 7671.c.6 x 1. VOLTAGE RATING K701: 230V a. Input (will operate at 110-130V a. INSTALLATION ALTITUDE 2000 metres 456 .co.5 x 1. IP RATING IP41 (In Zone 2 if fixed where direct spray from showers is unlikely) MAX. on insertion of plug rear case moulding (internal thermister trip current) l	Choice of 230V or 115V output socket l	Integral over current device to protect MAXIMUM LOAD transformer positions 20VA No load voltage < 275V l	Safety interlocked shutters to prevent l	Suitable for use with electric insertion of two plugs simultaneously toothbrush chargers TERMINAL CAPACITIES Each terminal will accommodate 1 x 4mm² or 2 x 2.6 flat blades each set at 30° to the vertical on a nominal pitch of 13.uk Shaver/Toothbrush Supply Units Standards and approvals Shaver/Toothbrush supply units comply with BS 61558-2-5:1998 Accommodates plugs as follows: l	British 5mm dia pins on 16.) FEATURES 230V or 115V nominal outputs l	Top access terminal screws make l	Only one size of screwdriver required CURRENT RATING wiring quicker and easier for installation K701: 200mA max.c. Wiring Devices Technical WIRING DEVICES mkelectric.c.) K706: 127V a. Input (will operate at 220-250V a. (internal thermister trip current) l	Automatic primary supply switching l	Front plate fixing screws retained on K706: 400mA max. l	European 4mm dia pins on 17 to 19mm pitch (230V socket) to BS EN 50075 l	Australian 6.6 flat horizontal blades on 12.7mm pitch (115V socket) to UL498 / Description NEMA WD6.5mm² solid conductors PHYSICAL Installation AMBIENT OPERATING TEMPERATURE -5°C to +40°C Shaver/Toothbrush supply unit should be wall mounted.6mm pitch (230V socket) to BS 4573:1970.
Push carrier back until engaging with jacking screw. Do not over tighten the screw. central heating boilers and other fixed VOLTAGE RATING appliances.	Unscrew the fuse carrier screw to partially eject the carrier. 4. water heaters. Wiring Devices Technical WIRING DEVICES Technical Hotline +44 (0)1268 563720 13A Connection Units. screwdriver operated worm 3 x 2. Connection units: min: 2 core. If in doubt.5mm max: 3 core. 0. 250V a. A tamper-proof version is also available. 3. Neon indicators are integrally wired into the product 2 x 6mm² stranded 2 x 4mm² and do not require separate connection when installing. All 20A DP Switches comply with BS EN 60669-1:1999. The ranges are designed for ease of instal­la­tion and have the advantageous design CURRENT RATING features of the MK range of wiring devices. INSTALLATION ALTITUDE Installation 2000 metres Wiring Products must be installed in accordance with current IET Regulations. List No. 457 .	Carefully lever the carrier out further to remove the fuse.	Consistent fuse blowing could mean a faulty appliance. The design gives 175° 3 x 2. 20A Switches and Flex Outlets Standards and approvals All Connection Units comply with BS 1363-4:1995. Fuses comply with BS 1362:1973. consult a qualified electrician.5mm² drive for ease of replacement. they are positioned centrally and Supply terminal: uppermost on the face plate. 5. 1.5mm² visibility in the horizon­tal and vertical planes.5mm The products are equipped with very strong. Connection Units: 13A DP switches: 20A Neon indicators Flex outlets: 20A Products are available with Neon indicators included in the rockers of the switched TERMINAL CAPACITY connection units. min: 3 core. IP RATING With flex outlet: IP2XD Without flex outlet: IP4X MAX. Description TECHNICAL SPECIFICATION A range of 13A fused connection units and 20A DP switches designed for the ELECTRICAL connection of refrigerators.5mm Flex outlets max: 3 core. K2000. AMBIENT OPERATING TEMPERATURE -5°C to +40°C Flex outlet plate An unfused flex outlet with cord grip and 3 pairs of terminals. quick and easy. Load terminals: Fuse carriers 2 x 6mm² stranded 2 x 4mm² These are captive and are opened by a fast acting. Changing Fuses 1. 2.	Always replace with a BS 1362 type fuse (as used in 13A plugs) of the correct rating. Flex Outlet complies with BS EN 60670-22:2006. 2. CORD GRIP CAPACITY Fuse carriers can be locked open using a padlock. Note: The carrier does not come fully out. push-fit nylon cord grips making PHYSICAL installation safe. In the case of unswitched units. 1. Screw the carrier down until flush with surface of the plate.5mm Bottom outlet types are supplied with blanking plug allowing use where the bottom 20A DP switches & flex outlet plate: outlet is not required.c.
‘break last’ feature Bottom outlet and cord grip l	Secure cable and flexible cord connection l	All terminal and fixing screws operated by one- size (4mm) screwdriver l	Backed out and captive terminal screws Note: These switches are not recommended for switching large banks of PCs Front outlet cord grip Lockable fuse carrier K1090WHI Flex Outlet Supply and non flexible load cables 458 . 20A Switches and Flex Outlets FEATURES l	Optional indicators in the switch rockers with 175° visibility in the horizontal and vertical planes l	Worm-drive operated fuse carriers for additional security (tamper-proof version available) l	Fuse carrier lockable in open position l	All supply and load cables can be cut and Supply and load cable cords cut stripped to the same length and stripped to same length l	Integrally wired Neon indicators save installation time Blanking plug for l	Push-fit cord grips. quicker bottom outlet installation l	Angled.co. for safer. neutral ‘make first’. Wiring Devices Technical WIRING DEVICES mkelectric. top mounted terminal screws simplify wiring l	Moulded ‘on’ indicator flash on switches cannot rub off – totally safe l	Captive fuse carrier l	Additional electrical safety from DP Switch.uk 13A Connection Units.
e. Wiring Devices Technical WIRING DEVICES Technical Hotline +44 (0)1268 563720 20A Key Operated Fire Alarm Isolator Switch TECHNICAL SPECIFICATION ELECTRICAL VOLTAGE RATING 250V a.c. IP2XD MAX.5mm² 3 x 4mm² 2 x 6mm² Description PHYSICAL The isolators comply with BS 60669-2-4:2005 AMBIENT OPERATING TEMPERATURE –5°C to +40°C The Isolator is intended for use with building alarm systems that are required to IP RATING comply with BS 5839 Part 1. Neutral & Earth 3 x 2. INSTALLATION ALTITUDE 2000 metres FEATURES l The built in lock ensures power cannot l Double Pole switching be provided without the key being l Only one size of screwdriver required operated. for added security. a common key profile. 459 . the keys are different to those used on all other MK Key Operated Switched Products. However. CURRENT RATING 20A TERMINAL CAPACITIES Live. making it safe to carry out for installation maintenance to fire alarms l Printed terminal markings on grey rear of the switch moulding for clearer identification Note: The lock fitted to these isolators is universal for all MK 20A Isolators in the range i.
Cooker Connection Unit MAX. units etc. CURRENT RATING 32A Switch 45A Cooker Control Unit 45A Cooker Connection Unit 50A Switch (Resistive Load) SWITCH 3mm contact gap Description Double pole operation – except socket switch on Cooker Control Units A range of switches and cooker control units suitable for the switching of all TERMINAL CAPACITY 50A SWITCHES domestic. Wiring Devices Technical WIRING DEVICES mkelectric. heaters.uk High Current Switches and Cooker Control Units Standards and approvals All DP switches in the range comply with BS EN 60669-1:1999. commercial and industrial appliances where higher current ratings are Cooker Control Units. Metal units are particularly suitable for 4 x 4mm² refurbishment projects. and Cooker Connection Units: required.c.co. cookers. 3 x 6mm² 1 x 10mm² 1 x 16mm² FEATURES TERMINAL CAPACITY.e. INSTALLATION ALTITUDE 2000 metres 460 . 50A Switch.5mm² l	Positive switch action l	Metal front plates available 2 x 4mm² l	Positive double pole switching l	Replaceable neon indicators 1 x 6mm² l	Toggle action switches l	Wide product choice PHYSICAL AMBIENT OPERATING TEMPERATURE -5°C to +40°C Note: These switches are not recommended for IP RATING switching large banks of PCs IP2XD Cooker Control Units IP4X 32A Switch. Cooker Connection Unit comply with BS EN 60670-22:2006 TECHNICAL SPECIFICATION ELECTRICAL VOLTAGE RATING 250V a. 32A SWITCH 3 x 2. i. All Cooker Control Units in the range comply with BS 4177:1992.
CURRENT RATING 10A – no derating when used on fluorescent or inductive loads Description 20A – no derating when used on fluorescent MK plateswitches are designed to blend in with the decor. They are designed for easy installation in plasterdepth boxes and are suitable for controlling lighting circuits in domestic. Designed to complement the Logic Plus 1.5mm² A textured. polycarbonate moulding allowing the glow of the neon to be seen 3 x 2. 1 x 6mm² It is easy to install in existing locations.000 operations for mechanical life tested to l	Positive switch action 40. whilst complementing or inductive loads a wide range of other MK wiring devices. Wiring Devices Technical WIRING DEVICES Technical Hotline +44 (0)1268 563720 Plateswitches Standards and approvals All MK plateswitches comply with BS EN 60669-1:1999. screws l	Neon locator available making switch easy to find in darkened rooms (Logic PlusTM only) 461 . 2.5mm² at almost any angle.000 operations at 10A rating tested to 10. or 3 gang 2 x 4mm² plateswitches. commercial and industrial applications. For 3 gang applications using a 25mm deep CONTACT GAP 3mm switch contact gap box simplifies wiring. PHYSICAL AMBIENT OPERATING TEMPERATURE -5°C to +40°C FEATURES IP RATING l	Two way switches can be wired as one or two IP2XD way MAX. INSTALLATION ALTITUDE l	Matching Grid switches available in 10 or 2000 metres 20A ratings l	3mm switch contact gap Operational testing (all plateswitches): tested to 100. TECHNICAL SPECIFICATION ELECTRICAL VOLTAGE RATING 250V a.000 l	Top access. backed out and captive terminal operations at 20A rating. Push / Retractive switch types are not intended for fluorescent loads.c. TERMINAL CAPACITY Neon locator 4 x 1mm² 4 x 1.
L SW.L 1 2 Two-way switches 1 2 N N Lamp/s N Lamp/s SW.L 2 1 2 N L SW.B. Common 2 1 Common 462 Two-way Intermediate Two-way L 2 1 switch 1 2 switch 1 2 switch .L Lamp/s Dotted lines show alternative switch positionsLamp/s Dotted lines show alternative switch positions Lamp/s Dotted lines show alternative Dotted switch lines show positionsswitch positions alternative Dotted lines show alternative switch positions Two-way switching – 3 wire control tching ng tching Common Common Common 2 2 1 1 Common Common Common tching Two-way 1 Intermediate Two-way tching LL 2 2 1 1 1 2 switch Common Two-way Common switch 22 22 Two-way switches 1 11 switch Intermediate 1 switch 2 1 1 2 switch Common Two-way Common 2 switch Two-way Intermediate Two-way NL Two-way switch 2 1 switch Intermediate Two-way 1 2 1 switch 1 2 switch N L switch 2 2 switch SW.co. Wiring Devices Technical WIRING DEVICES mkelectric.uk ing Plateswitches Common L 1 Wiring N diagrams Lamp/s One-way switching ng ing ing Common Common Common Common ing 1 2 Two-way switches LL 1 2 1 1 Common NL N 1 Lamp/s Lamp/s N Dotted lines Lamp/s show alternative switch positions Two-way switchingLamp/s – 2 wire control ng ng Common Common ng Common Common ng ing Common Common LL 1 1 2 Two-way switches 2 Commonswitches 2 Two-way 2Common 1 1 Common L 1 2 Two-way switches 1 2 NL N 1 1 2 Two-way switches 2 1 N SW.L Lamp/s Dotted lines show alternative switch positions Dotted lines show alternative switch positions Lamp/s Dotted lines show alternative switch positions N.L 2 1 1 N N Lamp/s Lamp/s Lamp/s SW.L Dotted lines show alternative switch positions Dotted lines show alternative switch positions Lamp/s Dotted lines show alternative switch positions Lamp/s Dotted lines show alternative switch positions Dotted lines show alternative switch positions Two-way switching plus intermediate switching – 3 wire control tching tching Common Common Common 2 22 1 11 Common Common Common Two-way Intermediate Two-way tching LL Two-way 2 1 switch Intermediate 1 Two-way 1 2 switch Two-way 2 1 Intermediate 2 switch Two-way 12 switch Common 21 switch 22 11 switch switch 11 switch Common 22 switch NN L SW. The above diagrams are to tching show wiring layout.L Lamp/s N Lamp/s Dotted lines show alternative switch positions Dotted lines show alternative switch positions Lamp/s Dotted lines Lamp/s show alternative switch positionsLamp/s Dotted lines show alternative switch positions Two-way switching plus intermediate switching ng – 2 wire control ng ng Common Common Common Common tching ng Common Common 2 Common 1 Common LL 1 2 Two-way switches 1 2 1 Commonswitches 1 2 Two-way 2 Common L 1 Two-way 2 Two-way switches 2 Intermediate Two-way 2 1 1 switch L 1 switch switch N SW.L 1 Two-way 2 switch 2 Intermediate 1 switch 1 2 Two-way switch Lamp/s N Lamp/s SW. Terminal positions may alter.
to 253V a. conforming to BS EN 60064:1996 rated at 230/240V and BS EN 60432-1 Standards and do not have any added features. Fluorescent Loads. suitable for use with normal tungsten filament lamps.g. (For LED Intelligent Dimmer) MAINS SUPPLY VOLTAGE RANGE MK dimmer switches can fall into one of four categories 216V a. All MK Intelligent Dimmer Switches employ one pole change over switches to Warning: These dimmer switches are not suitable facilitate two way switching.c. PHYSICAL *Non-UK Dimmer Switches AMBIENT OPERATING TEMPERATURE 0°C to +40°C Dimmer switches belonging to this category only conform to the relevant parts of BS EN 66069-2-1. Electromagnetic Compatibility Directive 89/336/EEC They also comply with BS EN 60669-2-1 and IEC 60669-2-1 (LED Intelligent Dimmer only) *Non-UK dimmer switches see note below TECHNICAL SPECIFICATION ELECTRICAL MAINS SUPPLY VOLTAGE 230V a. for overload protection.c. Loads suitable for use with standard dimmer switches above are IP RATING also suitable for use with this category of dimmer switch. including Energy Saving Lamps. MAX. incorporating GU10 bases. K1501 WHI LV. Wiring Devices Technical WIRING DEVICES Technical Hotline +44 (0)1268 563720 Dimmer Switches Standards and approvals All CE marked Logic Plus™ dimmer switches comply with the EC Low Voltage Directive: 73/23/EEC. Please check with lamp micro-controller based electronic circuitry and use current sensing to compute the manufacturer to determine suitability.c.2 rated at 230/240V. Non-UK) Description 220V a.c. to 240V a. 1)	Standard Dimmer Switches 200V a. Note: Transformer must be suitable for dimming depending on the extent of overload as shown in the table below.c.c. LED INTELLIGENT DIMMERS: Standard Dimmer Switches are not suitable for use with transformers for Low Voltage Fused GLS Tungsten Filament lamps to Lighting or Fluorescent Loads. IP2XD Only one Dimmer Switch can be used in a two-way switching circuit.c. INTELLIGENT DIMMERS AND ability to control dimmable transformers for low voltage. e. e. (Nominal. BS EN 60064:1996 and BS EN 60432-1. soft start. including Energy Saving Lamps. to 250V a. state of the art. These products show progressive reaction to overload conditions. Dimmable wire wound or electronic Low Voltage Transformers of good quality. List numbers using phase delay (leading edge) and NOT only belonging to this category are identified by the suffix letters LV. Can also be Intelligent and LED Intelligent Dimmer Switches used with good quality mains voltage halogen lamps Dimmer Switches belonging to this category.c 2)	Intelligent Dimmer Switches 198V a.c. employ the latest.g. to 264V a. load conditions. (For LED Intelligent Dimmer) 3)	Non-UK Dimmer Switches MAINS SUPPLY FREQUENCY 4)	LED Intelligent Dimmer Switches 50Hz ±3Hz 60Hz ±3Hz Standard Dimmer Switches TYPE OF LOADS Dimmer Switches belonging to this category employ simpler electronic circuitry and STANDARD DIMMERS the CE marked products make use of thermal switches to conform to the very stringent Fused GLS Tungsten Filament lamps only to requirements of the Standard BS EN 60669-2-1. etc.c. phase cut (trailing edge) type of dimmers. INSTALLATION ALTITUDE 2000 metres 463 . (Nominal) 220V a. They are only BS EN 60064:1996 and BS EN 60432-1:2000. for use with Fluorescent Lamps or Energy Saving MK Intelligent and LED Intelligent Dimmer Switches are not suitable for use with Lamps.
The next time the dimmer is turned on the lamp will automatically brighten to the maximum level before dimming to the brightness level corresponds to the knob level. Follow the steps below to adjust the minimum brightness level. The dimmer will exit programming mode automatically without saving the new setting if there is no dimmer knob movement for 15 seconds. Set the dimmer knob to minimum level. Push to switch OFF Step 3 – Success indication (Programming Complete) 7. NOTE: Some LED lamps may not work properly if the brightness level is set too low thus it is recommended to keep the brightness level of the lamp at a visible level. Push to switch OFF Min 3. Rotate the dimmer knob anticlockwise to adjust the lamp to the desired brightness level. Step 1 – Access To Programming Mode 1. 2.uk Minimum Brightness Adjustment for LED Intelligent Dimmers The light output of some LED lamps may appear to be too dim or invisible when the dimmer knob is at the minimum dim level. the light level of each gang has to be adjusted separately. Step 2 – Adjust Brightness Level and Exit Programming Mode 5. Dimmer enters programming mode. Wiring Devices Technical WIRING DEVICES mkelectric. This feature is primarily for adjusting the minimum brightness level of the LED lamp although it can be used for other load types. Confirm the new setting and exit programming mode by turning OFF the dimmer. For a double gang dimmer. Turning/pushing the dimmer knob before the end of automatic brightening will end access to programming mode 4. Push the dimmer knob so that it is in OFF state. Push to switch ON Max Min Max NOTE: Wait for 3 seconds. Turn on the dimmer and immediately rotate the knob 3 times in full rotary span within 5 seconds. 464 .co. 6. Turn anticlockwise to adjust Min the brightness level. the lamp will then dim to minimun before automatically brightening to about 30% level. The dimmer will restore its factory default light level.
VA RATING OF DIMMER) ELECTRONIC OR GLS AND MAINS WIRE WOUND LV LED TRANSFORMERS LEDS VOLTAGE HALOGEN TRANSFORMERS single dimmer 40-300W 40-240W/VA – 4 – INTELLIGENT double dimmer 2 x 40-300W 2 x 40-240W/VA – 4 per dimmer – DIMMER SWITCHES single dimmer 60-500W 60-400W/VA – 5 – single dimmer 40-250W – – – – STANDARD DIMMER double dimmer 2 x 40-250W – – – – SWITCHES single dimmer 65-450W – – – – single dimmer 40-300W 40-240W/VA 4-70W 4 10 LED INTELLIGENT DIMMER SWITCHES double dimmer 2 x 40-300W 2 x 40-240W/VA 2 x 4-70W 4 per dimmer 10 per dimmer Do not connect more than the maximum number of transformers stated for each dimmer. In addition.c. Please note the dimmer may be substituted for any Fluorescent Two-Way dimmer switches. Standard Dimmer Switches l	Can be used with good quality mains voltage halogen lamps l	Suitable only for use with fused GLS Tungsten Filament lamps to incorporating GU10 bases.m. Halogen lamps which inherently have a very high inrush current at LED Intelligent dimmer switches are suitable for dimmable LED bulbs switch on for incandescent replacement. . The Soft Start feature is also l	Suitable for dimming Low Voltage Halogen lamps via good quality. L 1 HF Fluorescent + 1-10V 2 DIMMING 465 Ballast – CONTROLLER N 3 . particularly beneficial when used to dim Mains Voltage Tungsten fully dimmable electronic or wire-wound transformers. which gradually increases the light output from the load incorporate the following advanced features over 1 to 3 seconds after switch on. r. minimum level 2 way switch > 750W switch off > 500W switch off > 600W switch off L1 L1 N Load C Supply 230V a. Wiring Devices Technical WIRING DEVICES Technical Hotline +44 (0)1268 563720 Dimmer Switches FEATURES Intelligent and LED Intelligent Dimmer Switches l	Soft Start. DO NOT connect earth to dimmer.c. OF TRANSFORMERS AND LEDS (1 GANG) (TOTAL RATING MUST NOT EXCEED MAX.50Hz L2 DIMMER 60-500W nominal 40-300W nominal 40-300W nominal N Load C 60-625W function without 40-375W function without 40-375W function without dimming dimming dimming Two-way switching > 625-750W dim to 68V±8V > 375-500W dim to 68V±8V > 375-600W dim to (only one dimmer can be used) r.s. . One-way switching OVERLOAD MANAGEMENT L L1 60-500W CIRCUIT 40-300W CIRCUIT LED INTELLIGENT DIMMER Supply 230V a.s. Please check with lamp manufacturer to BS EN 60064 and BS EN 60432-1 determine suitability l	One way dimmer switches incorporate manual soft start l	Load current sensing: l	Incorporate thermal switches for protection against overload These dimmers continuously monitor the load current to help protect against overheating in wire wound transformers and to prevent overloading of the dimmer for long term reliability LOAD TYPES AND LOADINGS DIMMER SERIES DIMMER SIZE RATING MAX NO.50Hz L2 L2 DIMMER L C Wires must be connected to the correct dimmer terminals.m.
(150x50mm aperture) 1G LJU6C Frontplate l	1G LJU6C frontplate accepts two LJU6C l	Accept industry standard (Euro) and modules (27 x 37mm aperture) LJU6C snapfit modules l	1/2 .co. 2G and 3G Euro frontplates l	3G Euro frontplate accepts 6 Euro l	Modules. Wiring Devices Technical WIRING DEVICES mkelectric. (100 x 50mm aperture) 466 . FEATURES l	1G. (50 x 50mm aperture) l	1 module LJU6C Blank available l	2G Euro frontplate accepts 4 Euro modules. 1 and 2 module Euro Blanks l	1G Euro frontplate accepts 2 Euro available modules.uk Euro and LJU6C Data Frontplates Standards and approvals BS 5733:2010 Description Frontplates used for mounting snapfit modules.
neutral & earth Live. INSTALLATION MAX.c. neutral & earth Live.c.c. Wiring Devices Technical WIRING DEVICES Technical Hotline +44 (0)1268 563720 Power Modules Standards and approvals Description K5830: BS 1363 Part 2:1995 A range of euro modules designed to provide a variety of power options. neutral & earth Live. INSTALLATION MAX.c.5mm² 3 x 4mm² 3 x 4mm² Live & neutral CHARGING 2 x 6mm² (stranded) 2 x 6mm² (stranded) 1 x 4mm² 1 x 6mm² 1 x 6mm² (stranded) 3 x 2.5mm² 4 x 1.5mm² CAPACITY 3 x 4mm² 3 x 4mm² 2 x 2. 250V a. INSTALLATION MAX.0 Type A. INSTALLATION MAX. 127V a.5mm² 3 x 2. RATING 13A 5A 16A 16A 15A 2 x 5V d.c.5mm² 3 x 2. PHYSICAL USB 3. FREQUENCY TERMINAL CAPACITY TERMINAL CAPACITY TERMINAL CAPACITY TERMINAL CAPACITY TERMINAL CAPACITY 50-60Hz MAX CURRENT Live. K5831: IEC 60884-1:2006 K5832: SASO 2204:2003 K5833: BS 546:1950 K5834: French National Standard NF C 61-314 TECHNICAL SPECIFICATION 13A UK 5A UK 16A GERMAN 16A FRENCH/BELGIAN 15A AMERICAN 2A USB CHARGING MODULE ELECTRICAL ELECTRICAL ELECTRICAL ELECTRICAL ELECTRICAL ELECTRICAL VOLTAGE RATING VOLTAGE RATING VOLTAGE RATING VOLTAGE RATING VOLTAGE RATING INPUT OUTPUT 250V a. 250V a.5mm² SOCKETS PHYSICAL PHYSICAL PHYSICAL PHYSICAL PHYSICAL USB 2.c. INSTALLATION IP3xC ALTITUDE ALTITUDE ALTITUDE ALTITUDE ALTITUDE MAX.0 AMBIENT OPERATING AMBIENT OPERATING AMBIENT OPERATING AMBIENT OPERATING AMBIENT OPERATING AMBIENT TEMPERATURE TEMPERATURE TEMPERATURE TEMPERATURE TEMPERATURE OPERATING -5°C to +40°C -5°C to +40°C -5°C to +40°C -5°C to +40°C -5°C to +40°C TEMPERATURE IP RATING IP RATING IP RATING IP RATING IP RATING 0°C to +40°C IP2XD IP2XD IP2XD IP2XD IP2XD IP RATING MAX.5mm² 3 x 2. 250V a. neutral & earth Live.c. 2000 metres 2000 metres 2000 metres 2000 metres 2000 metres INSTALLATION ALTITUDE 2000 metres Dimensions (mm) 13A UK 5A UK 16A German 16A French/ 15A American 2A USB Charging Module Belgian 50 50 50 50 50 50 50 50 50 50 50 50 25 34 25 29 40 39 K5830 K5833 K5831 K5834 K5832 K5837 BOX TYPES BOX TYPES BOX TYPES BOX TYPES BOX TYPES MK EURO FRONT BOX TYPES PLATE THICKNESS MINIMUM MINIMUM MINIMUM MINIMUM MINIMUM > 7mm Min 35mm 35MM 35MM 46MM 46MM 35MM < 7mm Min 46mm EXTRA WIRING SPACE EXTRA WIRING SPACE EXTRA WIRING SPACE 46MM 46MM 46MM 467 . VOLTAGE RATING VOLTAGE CURRENT RATING CURRENT RATING CURRENT RATING CURRENT RATING CURRENT RATING 220-240V a. neutral & earth Combined total TERMINAL of 2A 3 x 2.
K5864 .LJU6C K5846 . K5846S . Installation details and wiring diagram illustrations l	Do A not unwind the twists in the wire pairs by more B C D than 13mm max.5e LJU6C K5745 RJ45 Cat. Suitable for use in all LJU6C and Euro frontplates. 568A 568B 1 P2 P3 E F 1 GWHITE / green WHITE / orange H P3 P1 P4 P2 P1 P4 1 2 3 GREEN / white WHITE / orange ORANGE / white WHITE/ green D E 4 5 F WHITE / blue BLUE / white BLUE / white WHITE / blue G 568A H 568B 6 ORANGE / white GREEN / white Pair 1 – BLUE/white & WHITE/blue 7 WHITE / brown WHITE / brown 1 Pair 2 – ORANGE/white & WHITE/orange Pair 3 – GREEN/white & WHITE/green 8 BROWN / white BROWN / white Pair 4 – BROWN/white & WHITE/brown 2 A B C D 1 2 8 7 Euro and LJU6C modules are to be wired as follows 2 1 1 6 5 3 2 5 2 4 6 3 4 1 2 8 1 7 50057132 50057133 6 4 2 2 1 3 5 1 7 1 7 2 8 1 6 6 4 5 3 2 5 3 5 3 4 6 3 4 2 RJ45 Cat.uk RJ45 Data Outlets Standards and approvals ISO/IEC 11801 EN 50173 TIA 568 EN 41003 Installation Description l	Maximum cable length 90m. l	Cable B bend radii.co.6 Screened K5746S . Aafter installation.Euro 50057136 32 1 8 2 . 1 TIA WIRING SCHEME COLOUR CODES PIN NO.5e Euro K5845 RJ45 Cat.7kg.5e Screened 468 4 50057139 K5845S . Wiring Devices Technical WIRING DEVICES mkelectric. available in the Logic Plus range.6 Euro .Angled K5746 . E l	F G H Maximum pull force 8.LJU6C. l	Do not over tighten cable ties.Angled K5844 3 RJ45 Cat.Euro Angled RJ45 Cat.Euro 500571323 50057133 2 2 8 1 3 7 1 2 8 6 4 7 1 2 3 5 4 3 4 4 6 5 5 50057134 4 3 RJ45 Cat. 40mm during installation. 20mm C D Cat 5e and Cat 6 modules suitable for use in structured cabling distribution systems.Euro.5e Euro .
They FREQUENCY RANGE contain the required surge protector (for line protection against electrical surges) BNC connector: 0 to 4GHz and ringing capacitor. systems compatibility Belden 9907 Master Sockets: For use as the first socket outlet on a direct exchange. IMPEDANCE Secondary Sockets: for use as extension sockets when connected on the same line BNC Connector: 50. K5821. INSTALLATION ALTITUDE 2000 metres FEATURES l	Meet all relevant BS and cabling Data sockets standards l	Latest specification for high l	Interchangeable modules clip into performance systems frontplates l	Wide range of data connectors l	Front fixing facilitates easy exchange available of modules For information on TV Satellite and l	Part of a complete range of products FM Modules see pages 471-473 for telephone and data processing requirements Telephone sockets l	Quick. PHYSICAL Wire pull-out force: 10. CW1308. K5801 and K5787. CW1316 URM43. OF CABLES PER TERMINATION Telephone: 2 RJ11/12: 1 Installation (Telephone socket modules) BNC 50 Ohms impedance cable – RG58. K186 and K170 MAX. nominal as a Master Socket.5 Newtons when installed correctly. CABLE TYPES BNC Euro modules with a 50Ohm crimp connector suitable for use with RG58. AMBIENT OPERATING TEMPERATURE -5°C to +40°C Wiring regulation restrictions IP RATING Domestic Installations: The total REN (Ring Equivalent Number) value of all IP2XD – K5820. URM43 Product performance. NO. simple and reliable IDC connectors l	Can be specified for all applications 469 . RG141. CW1293. IP4X – K180. URM76 and Beldon 9907 type co-axial cables are also available. TECHNICAL SPECIFICATION Description ELECTRICAL A range of telephone. TERMINATION TYPE Telephone module – IDC Installation tools required IDC Connectors (telephone & RJ45 outlets) BNC module – Crimped connection MK insertion tool List No. K5887 complies with FCC68 and EN 41003. RJ11/12. Telephone: CW1311. BS 5733: 2010 (where applicable). K188. Wiring Devices Technical WIRING DEVICES Technical Hotline +44 (0)1268 563720 Telephone. 400NAT.2 Data sockets K5801. BNC Data and Blank Modules Standards and approvals Telephone sockets K5820 and K5821 comply with the following: BS 6312: 2. telephone equipment connected on a line must not exceed 4. data and blank modules to fit Euro and LJ6UC front plates.
WIRE	WIRE 1	WHITE / green	WHITE 2	WHITE / orange	BLACK MODIFICATION TEXT: R MK ELECTRIC (MALAYSIA) SDN. Wiring Devices Technical WIRING DEVICES mkelectric.15 50057130 FIRST ANGLE PROJECTION 2 8 6 PACKAGING SPEC No: DRAWING No. MENARA EON BANK ECC ENGINEERING STANDARDS 288. JALAN RAJA LAUT 470 50350 KUALA LUMPUR HONEYWELL CONFIDENTIAL AND PROPR .08 1 6 PERMIT No: 5 2 52 3 5 RADII ±0. BNC Data and1 Blank Modules A B C D Telephone Wiring Scheme 1	GREEN / white 2	BLUE / white 1 3	ORANGE / white 4	5	WHITE / orange WHITE / blue 6 1 2 1 2 8 7 6 1 6 1 5 2 6	WHITE / green 5 2 5 52 3 4 3 4 3 4 43 6 Note: Main wire colour is shown in capitals K5820 K5821 50057130 50057131 50057132 50057130 First Socket Outlet Extension Outlet Master Secondary 1 2 3 4 5 6 1 2 3 4 5 6 3 2 6 1 6 1 5 2 5 2 4 3 4 3 C D E F G H 2 1 2 50057130 6 5 50057131 1 3 1 2 3 4 6 3 4 RJ11/12 Wiring Scheme 3 PIN	STRIPPED COLOUR	50057138 SOLID COLOUR 50055 NO. 6 1 1 HOLE DIA ±0. A B C A B 50057131 50057132 50057133 50057138 MODIFICATION TEXT: R MK ELECTRIC (MALAYSIA) SD C/O SYMPHONY CORPORAT 22ND FLOOR.50 3 4 4 K5787 DRAWN BY: DRAWN BY DATE: K5887 PROJ NO. BHD DIMENSIONS AND TOLERANCES PER C/O SYMPHONY CORPORATEHOUSE SDN.BHD BRITISH STANDARDS AND 3	BLUE / white	RED 22ND FLOOR.uk A B C D A E B F Telephone. JALAN RAJA LAUT 4	WHITE / blue	GREEN 50350 KUALA LUMPUR MATERIAL TITLE 5	ORANGE / white	YELLOW 5 HONEYWELL CONFIDENTIAL AND PROPRIETARY 6	GREEN / white	BLUE PROTECTED BY GENERAL TOLERANCES: FINISH SUB TITLE Note: Main wire colour is shown in capitals 1 7 DIN ISO 16016 LINEAR ±0.co. MENARA EON 288. RJ11/12.05 2 5 UNITS IMPRESSIONS: 4 3 4 3 6 MM 4 ANGULAR ±0.
inner conductor 0. CABLE SPECIFICATION The F-type Satellite Socket may be used for connection of CATV.3. CW1293.2.65mm² solid or stranded cable PHYSICAL AMBIENT OPERATING TEMPERATURE --5°C to +40°C IP RATING IP2XD MAX. CABLE SPECIFICATION Co-axial cable: inner core diameter – 0. television and data Protected. BS 5733:2010 (where applicable). TV/FM and Satellite Socket Outlets Standards and approvals Telephone and TV sockets comply with the following: Telephone sockets K422 and K427 BS 6312: 2. CW1308. termination point of a public telecommunications system and any piece of approved telecommunications apparatus. Wiring Devices Technical WIRING DEVICES Technical Hotline +44 (0)1268 563720 Telephone. TELEPHONE SOCKETS. pages 46-48. refer to the Modular Data section.1.08 to 0. MATV and CW1311. OF CABLES PER TERMINATION 2 RE-USABILITY >9 reterminations (should not be reterminated with FEATURES smaller diameter wire) l	Single screw termination on TV outlets l	Part of a complete range of products TV SOCKETS l	for telephone. 10. A part of the very wide range of products to meet the latest technical requirements clauses 10. ELECTRICAL Telephone and TV sockets fit into plaster depth boxes (except for RJ11). BS 5733:2010 (where applicable) and IEC65. The master and secondary telephone sockets K422 and Satellite TV sockets K427 comply with relevant approvals for direct and indirect connections between a BS 5733:2010 (where applicable). INSTALLATION ALTITUDE 2000 metres 471 .5-1. TV sockets Description BS 3041 Part 2:1977 / IEC 169-2:1977. CABLE SPECIFICATION Capable of taking 0. CW1316 satellite TV installations. fully enclosed PCBs Cable specification: CT100 or equivalent Any standard processing requirements l	Meet all relevant BS requirements LOW-LOSS TV CO-AXIAL CABLE: l	Angled connector on TV outlets Outside 4-8mm diameter. simple and reliable terminal l	Sockets fit in plaster depth boxes diameter connection (except K4817) INSERTION LOSS l	IDC connectors on telephone outlets Insertion loss data available on request ‘F’ TYPE SATELLITE SOCKET (K3525). NO. and the standards applicable to modern technology in the installation of telephone and television equipment.5-2mm l	Quick. K4817: BS 5733:2010 (where applicable) and FCC68.2mm RJ11 (K4817). For applications requiring twin or dual telephone TECHNICAL SPECIFICATION outlets.
Telephone Wiring 3 4 Scheme IDC 2 5 1	GREEN / white terminals 1 6 2	BLUE / white 3	ORANGE / white 4	WHITE / orange 5	WHITE / blue 6	WHITE / green Cable Tie Note: Main wire colour is shown in capitals fixing point Cable tie First Socket Outlet Extension Outlet Master Secondary 1 2 3 4 5 6 1 2 3 4 5 6 472 . Wiring regulation restrictions Domestic installations Any number of MK sockets may be installed thereafter. Secondary Sockets For use as extension sockets when connected on the same line as a Master Socket. They contain surge protector (for line protection against electrical surges) and ringing capacitor.co. 400NAT (not supplied with product). Installation tools required MK IDC insertion tool List No.uk Telephone. systems compatibility Master Sockets: for use as the first socket outlet on a direct exchange or PABX line. Wiring Devices Technical WIRING DEVICES mkelectric. with a total REN (Ring Equivalent Number) value of all telephone equipment connected on a line not exceeding 4. TV/FM and Satellite Socket Outlets Installation (Telephone sockets) Product performance.
g.g. (These products are not supplied by MK). (typically located in the loft or garage) (red lines in wiring diagram). The decoded satellite signal is then fed into the VCR along with the TV signal from the Triplexer. where masthead/headend equipment is controlled by 4 receiver/decoder equipment). aerial downlead. Wiring Devices Technical WIRING DEVICES Technical Hotline +44 (0)1268 563720 Digital TV and Telephone Outlets (Logic Plus and Modular Datacoms) Installation (TV sockets) DAB TV Product performance. Method of installation of TV and FM aerial connection by using MK co- When tightening the screening braid clamps axial socket outlet and only one downlead. TV Cable Routing and Use of Cable Clamp 4 VID TV Sharp bends in the cable must be avoided SKY/DIG during installation. (e. systems compatibility FM Isolated Outlets are intended for use where 1 safety isolation (rated at 2000V ac) is required to provide protection against faults occurring within any mains powered product used on different 3 TV DIST parts of the distribution system. 2 The separated satellite signal is then fed to the decoder. SAT 1 TV 4 Diplexer Outlets are used in distribution TV HI-FI systems where both TV and FM band signals VID are combined on a single aerial downlead. The first combines the TV TV outlets or modules must not be installed and FM signals and the second adds the Sky signal to the TV/FM in the same enclosure as equipment rated in signal and provides a DC control path to power the LNB unit on excess of 50V. ensure that the cable is firmly gripped and that the inner insulation is not squashed flat beyond Conventional distribution system for TV and FM signals using a single a slight oval shape. They are not suitable for use in systems where DC signals SAT 2 are passed through the socket. The single aerial down lead feeds into the triplexer (black lines in wiring diagram). The filtering in the diplexer separates the appropriate signals and feeds them through to the relevant 2 output connection port. mains rated 13A sockets or the satellite dish. The output signal from the VCR then feeds into the TV and also back to the single outlet and onto the distribution amplifier (black lines in wiring diagram). The single TV/FM socket is fitted with a cable clamp that can be fixed on either side of the termination position to facilitate this. (e. The single cable back-feed then feeds back to the input of a multi 3 way distribution amplifier. Each individual output from the distribution amplifier is then fed 4 to the individual rooms in the house to a standard TV (single or diplexer) outlet to which the TV/VCR and/or Hi-Fi can be connected (blue lines in wiring diagram). 473 . switches). The signals from the TV and FM aerials and the satellite dish are Safety Information 1 combined together using two products.
TECHNICAL SPECIFICATION SINGLE OUTLETS TV/FM IEC Male or Female DC-950MHz SATF-Type DC-1. 5-65MHz 470-862MHz Telephone secondary outlets are provided on some products for connection of telephone or for interactive TV applications. Wiring Devices Technical WIRING DEVICES mkelectric. an established range FM suitable for VHF TV. or more complex installations. The filtering in the diplexer splits out the appropriate SAT signal and feeds it to the relevant output connection. FM/DAB Diplexer: 87.5-108MHz combined TV and FM signals. Diplexer: A DC control path is provided in the SAT signal path through the triplexer. BS EN 60169-24 and BS 6312 Part 2 Modular products are Euro compatible. FM and SAT signals.co. TV/FM/DAB/SAT PRODUCTS FOR Triplexer modules are for connecting to a single co-axial aerial down lead carrying DIGITAL RADIO combined TV. for use Triplexer: with Sky+. Diplexer: n/a Triplexer: 950-2300MHz A DC control path is provided in the TV signal path through the diplexer.5-230MHz Triplexer: 87. Diplexer: 87.75GHz DIPLEXER AND TRIPLEXER PRODUCTS TV Diplexer: 5-65MHz 470-862MHz Triplexer: Description 5-65MHz 470-862MHz There are two ranges of diplexer and triplexer products. Radio and Telephone Outlets Standards and approvals All Logic Plus TV Outlets comply with BS 5733 and BS EN 50083 where applicable.5-108MHz Diplexer modules are for connecting to a single co-axial aerial down lead carrying Triplexer: 87.uk Digital TV. The filtering in the triplexer splits out the TV appropriate signal and feeds it to the relevant output connection. 5-65MHz 470-862MHz The quad outlet contains a triplexer together with a separate satellite output. Also IEC 169-2. and a range suitable for digital radio (DAB).5-230MHz FEATURES SAT OR SAT1 Diplexer: n/a l	Non Isolated l	Selected products with BT secondary Triplexer: 950-2300MHz outlets for interactive TV applications l	Fully screened SAT2 l	Selected products with supplementry l	Earth terminal provided on TV modules Diplexer: n/a TV outlet for back-feed for further Triplexer: 5-2300MHz distribution BOX TYPES FLUSH FLUSH (FOR EXTRA WIRING SPACE) SURFACE INSULATED SURFACE METAL 1 GANG 861ZIC 866ZIC K2140WHI K2211ALM/K2213ALM 2 GANG 862ZIC 886ZIC K2142WHI K2212ALM/K2214ALM Minimum recommended box depth 32mm Note: Edge mounted modular products require 46mm box 474 .
Wiring Devices Technical WIRING DEVICES Technical Hotline +44 (0)1268 563720 Digital TV/FM and Telephone Outlets (Logic Plus and Modular Datacoms) Installation Telephone Outlet Connection l	When installing the TV co-axial cable ensure Carefully strip 50mm of the telephone cable outer sheath to expose the inner that all cable bends are smooth so that the insulated conductors. (i. Screening braid to remain in place over the inner insulation Telephone Wiring Earth terminal Scheme 3 4 1	GREEN / white IDC 2 5 terminals 1 6 Cable 2	BLUE / white clamping plate 3	ORANGE / white 4	WHITE / orange Foil EMC screening 5	WHITE / blue gasket 6	WHITE / green Clamping plate fixing Note: Main wire colour is shown in capitals Cable Tie Co-axial screws fixing point cable Earth terminal Cable tie First Socket Outlet Extension Outlet Master Secondary View with cable clamp removed 1 2 3 4 5 6 1 2 3 4 5 6 Cable clamp Co-axial Clamping cable fixing screws 475 . Additional secondary extension outlets should be wired in parallel with the existing installation via the IDC terminals.5 6. (In the case of 2G products both TV modules should be earthed). affected Pins 1 and 6 are frequently unused. pin 1 to pin1. the installer must ensure that a suitable earth conductor is present to connect to the earth terminal. Using the insertion tool supplied. this should be l	Use CT100 cable (or equivalent) retained on any new or extended installation. etc). In the event that the earth terminal is required to be used. 4 wire cable may be used in these installations. TV Co-axial cable stripping details In the event that the earth terminal is required to be used.e. (In the 6. the installer must ensure that a suitable earth conductor is present to connect to the earth terminal. pin 2 to pin 2. l	Not suitable for loop-in loop-out installations If an existing installation uses a different wiring colour code system. 400NAT) inner insulation is not crushed or squashed.5 case of 2G products both TV modules should be earthed). carefully push each lead into the appropriate IDC terminals according to the wiring otherwise the TV signal quality may be colour code stated in the telephone Wiring Scheme diagram. (MK List no.
(100mm x 50mm SWITCHED SOCKET SPECIFICATION aperture) SWITCHED SOCKET SPECIFICATION Compliant to BS 1363 Part 2: 1995 Compliant to BS 1363 Part 2: 1995 ELECTRICAL ELECTRICAL VOLTAGE RATING VOLTAGE RATING 250V a.5mm² 3 x 4mm² 3 x 4mm² 2 x 6mm² (standard) 2 x 6mm² (standard) PHYSICAL PHYSICAL AMBIENT OPERATING TEMPERATURE AMBIENT OPERATING TEMPERATURE -5°C to +40°C -5°C to +40°C IP RATING IP RATING IP2XD IP2XD MAX. 35mm deep. Euro modules. Satellite outlet.uk – Logic Plus™ Combination Plates 2/4-gang Stacked Combination Plate 4 Gang Plate Description 2 Gang Plate Description The 4-gang Combination Plate carries 2x 2-gang The 2-gang Combination Plate carries a 2-gang 13A DP switched sockets.c. INSTALLATION ALTITUDE MAX. Refers to BS 7671 IET Wiring regulations for detail regulations for detail l	When removing the fixing screws and front plate l	When removing the fixing screws and front plate from an installation to gain access to low voltage from an installation to gain access to low voltage modules. 250V a. single TV (IEC Female) 4-module Euro area capable of accommodating and an additional Telephone socket. there is a 4-module Euro area capable of accommodating any additional Quad TV.c. FM/DAB. which is 47mm deep which is 47mm deep l	These back boxes should always be used to ensure l	These back boxes should always be used to ensure alignment of the fixing screws is correct and proper alignment of the fixing screws is correct and proper segmentation between mains and low voltage segmentation between mains and low voltage products is maintained products is maintained l	Mains operated products and extra low voltage l	Mains operated products and extra low voltage modules must not be installed within the same modules must not be installed within the same front plate aperture. Refers to BS 7671 IET Wiring front plate aperture. to 4 x 50mm high by 25mm wide requirements of BS 5733 2010. Additionally. CURRENT RATING CURRENT RATING 13 Amp 13 Amp TERMINAL CAPACITY TERMINAL CAPACITY Live. Neutral & Earth Live. any additional telephone or media products from the Euro modular range. FM/ 13A DP switched sockets and an additional DAB. As used on K3566 WHI BT Telephone Socket As used on K3566 WHI TECHNICAL SPECIFICATION TECHNICAL SPECIFICATION 4-module Euro Housing FRONTPLATE FRONTPLATE The frontplate complies with the mechanical strength This portion of the plate accepts up The frontplate complies with the mechanical strength requirements of BS 5733 2010. Satellite outlet telephone or media products from the Euro & additional TV Socket modular range. and for greater wiring space 854ZIC. which is with these plates. please be aware that there will also be access to the mains supply access to the mains supply 476 . and for greater wiring space 854ZIC. These are 853ZIC. please be aware that there will also be modules. INSTALLATION ALTITUDE 2000 metres 2000 metres Note Note l	Pre-configured back boxes available shall be used l	Pre-configured back boxes available shall be used with these plates.5mm² 3 x 2. Neutral & Earth 3 x 2. plus a Quad TV. These are 853ZIC.co. Wiring Devices Technical WIRING DEVICES mkelectric. which is 35mm deep.
materials.5mm² stylish and practical wiring device solution. AMBIENT OPERATING TEMPERATURE Alternatively. the MK Design Service to deliver variation in colours.e. neutral & earth 3 x 2. please be aware that there will also be access to K24209 858ZIC the mains supply All pre-fitted sockets come complete and are fitted with two earth terminals on a K24210 869ZIC common busbar to provide a double earth facility for use when installations require a high integrity protective connection as specified within BS 7671. Euro Power Modules i. back boxes must be installed 10mm sub flush to the wall Combination Plate 47mm surface List Number Mounting Box l	Mains operated products and extra low voltage modules must not be installed K24206 870ZIC within the same frontplate aperture. Euro apertures can also be converted to grid-switch. IET Wiring Bespoke requirements can be achieved through Regulations. Description CURRENT RATING A range of combination plates designed for ease of installation and having all the 13A advantageous design features of the Aspect range. TERMINAL CAPACITY These combination socket outlets provide interior designers and installers with a Live. finishes and markings. For more information please visit www. INSTALLATION ALTITUDE 2000 metres These back boxes should always be used to ensure alignment of the fixing screws is correct and proper segregation between mains and extra low voltage products is maintained MOUNTING BOXES l	For Aspect products. for example allows for (Dual earth terminals) the inclusion of up to eight single Euro modules. TECHNICAL SPECIFICATION ELECTRICAL VOLTAGE RATING 250V a.mkelectric. The range also has larger euro module 3 x 4mm² frontplates to house eight and twelve single euro modules without the inclusion of 2 x 6mm² (stranded) fixed socket outlets. German.co. The K24209 combination socket outlet. MAX.uk or call 01268 563720 477 . which could include datacoms. plus TV and Satellite modules. PHYSICAL telecoms.c. French/Belgium and American –5°C to +40°C socket outlets may be used. IP RATING IP2XD Note: l	Pre-configured back boxes are designed for use with the combination plates. K24209 and K24210 comply with BS 5733:2010. Refer to BS 7671: 2008 for details K24207 870ZIC l	When removing the fixing screws and frontplate from an installation to gain K24208 868ZIC access to low voltage modules. Wiring Devices Technical WIRING DEVICES Technical Hotline +44 (0)1268 563720 – Aspect Combination Plate Standards and approvals All Aspect 13A socket outlets comply with BS 1363: Part 2:1995.
Do not mount or use as a trailing socket or where they may be subject to excessive moisture or dampness.3 173.uk – Aspect Combination Plate Features l Metal-capped rockers designed l Switch contacts with silver to match the chosen front plate contacts on both surfaces for finish good continuity l 3 pin operated safety shutter l Dual earth terminals on pre-fitted l Printed terminal markings on sockets are for high integrity grey rear mouldings for clearer earthing identification l Backed out and captive terminal l Top access.co. Aspect combination plates are supplied with clip on segregator.3 478 . angled terminals screws on pre-fitted sockets make wiring easier and quicker l Pre-configured backboxes to l 3mm minimum switch contact gap ensure alignment of the fixing screws is correct and proper l Double pole switching segregation between circuits is l Additional electrical safety from maintained to comply with neutral ‘make first’.3 320.6 86 86 K24209 K24210 146. Dimensions (mm) K24206 and K24207 K24208 233. Wiring Devices Technical WIRING DEVICES mkelectric. ‘break last’ BS 7671 17th Edition wiring feature regulations Installation Aspect socket outlets can only be mounted on a wall.4 206.3 173. Install corresponding back box 10mm sub flush to finished wall surface.
telecoms. 479 . plus TV and Satellite modules. CURRENT RATING 13A TERMINAL CAPACITY Live.co.mkelectric. IET Wiring Regulations. finishes and markings. K14209 and K14210 comply with BS 5733:2010. The K14100 combination socket outlet. Euro Power Modules i.uk or call 01268 563720 Combination plates allow the use of a variety of power and data modules making them ideal for hotels. for example allows for MAX. Refer to BS 7671: 2008 for details l	When removing the fixing screws and frontplate from an installation to gain K14209 858ZIC access to low voltage modules. For more information please visit www.5mm² 3 x 4mm² 2 x 6mm² (stranded) Description (Dual earth terminals) A range of combination plates designed for ease of installation and having all the PHYSICAL advantageous design features of the Edge range. Wiring Devices Technical WIRING DEVICES Technical Hotline +44 (0)1268 563720 – Edge™ Combination Plate Standards and approvals All Edge 13A socket outlets comply with BS 1363: Part 2:1995. Euro apertures can also be converted to grid-switch. German. K14200 K14201 K14202 These back boxes should always be used to ensure alignment of the fixing K14205 K14206 K14207 screws is correct and proper segregation between mains and extra low voltage K14100 K14101 K14102 products is maintained K14216 867ZIC l	For Edge products. back boxes must be installed flush to the wall surface K14217 867ZIC l	Mains operated products and extra low voltage modules must not be installed K14208 868ZIC within the same frontplate aperture. please be aware that there will also be access to K14210 869ZIC the mains supply Bespoke requirements can be achieved through All pre-fitted sockets come complete and are fitted with two earth terminals on a the MK Design Service to deliver variation in common busbar to provide a double earth facility for use when installations require colours. which could include datacoms. French/Belgium and American MOUNTING BOXES socket outlets may be used.e. AMBIENT OPERATING TEMPERATURE –5°C to +40°C These combination socket outlets provide interior designers and installers with a IP RATING stylish and practical wiring device solution. neutral & earth 3 x 2. INSTALLATION ALTITUDE 2000 metres the inclusion of up to eight single Euro modules.c. Combination 35mm 47mm Plate Note: Mounting Box Mounting Box List Number l	Pre-configured back boxes are designed for use with the combination plates. TECHNICAL SPECIFICATION ELECTRICAL VOLTAGE RATING 250V a. The range also has larger euro module IP2XD frontplates to house eight and twelve single euro modules without the inclusion of fixed socket outlets. materials. a high integrity protective connection as specified within BS 7671. Alternatively.
3 293.8 86 86 K14209 K14210 K14100 146.co.3 442.3 173. Dimensions (mm) K14216 and K14217 K14200 233. Wiring Devices Technical WIRING DEVICES mkelectric. angled terminals screws on pre-fitted sockets make wiring easier and quicker l Pre-configured backboxes to l 3mm minimum switch contact gap ensure alignment of the fixing screws is correct and proper l Double pole switching segregation between circuits is l Additional electrical safety from maintained to comply with neutral ‘make first’.3 173.9 86 86 480 .6 407.uk – Edge™ Combination Plate Features l Metal-capped rockers designed l Switch contacts with silver to match the chosen front plate contacts on both surfaces for finish good continuity l 3 pin operated safety shutter l Dual earth terminals on pre-fitted l Printed terminal markings on sockets are for high integrity grey rear mouldings for clearer earthing identification l Backed out and captive terminal l Top access. ‘break last’ BS 7671 17th Edition wiring feature regulations Installation Edge socket outlets can be mounted on either a wall or suitable bench mounted trunking. Do not mount or use as a trailing socket or where they may be subject to excessive moisture or dampness.4 206.6 173.3 K14208 K14205 320.
481 .5mm² lobbies. However. the keys are different to those used on MK Key Operated Fire Alarm Isolator Switches.e. Wiring Devices Technical WIRING DEVICES Technical Hotline +44 (0)1268 563720 – Edge™ Key Operated Switchsocket Outlet Standards and approvals All Edge 13A socket outlets comply with BS 1363: Part 2:1995. Do not mount or use as a MAX. TECHNICAL SPECIFICATION ELECTRICAL VOLTAGE RATING 250V a. The built-in lock ensures that power cannot Live. 2000 metres Features l Built in lock ensures power l Double pole switching cannot be provided without key l Only one size of screwdriver operation required for installation l Printed terminal markings on l Dual earth terminals for high grey rear mouldings for clearer integrity earthing identification Note: The lock fitted to each socket is universal. a common key profile. Description CURRENT RATING 13A The Key Operated 13 amp socket is designed for ease of installation and has all TERMINAL CAPACITY the design features of the Edge range. INSTALLATION ALTITUDE trailing socket or where they may be subject to excessive moisture or dampness. neutral & earth be provided without key operation making it ideal for communal areas such as hotel 3 x 2. i. for added security. –5°C to +40°C Installation IP RATING IP2XD Edge socket outlets can be wall or bench mounted.c. 1 x 6mm² (stranded) (Dual earth terminals) The product can be quickly installed as replacement for existing 2 gang 13 amp PHYSICAL sockets or in a new installation (assuming suitable 47mm deep mounting box is in AMBIENT OPERATING TEMPERATURE position). The key can be removed from the lock in the on or off position leaving the 2 x 4mm² socket with or without power supply.
uk – Edge™ EdgeTM Technical: General information Mounting Boxes Fixing Screws Due to the slimline design MK Edge accessories The surface head of Edge fixing screws is require deeper back boxes than standard. then it is recommended that a box depth of 47mm is used. To prevent damage to the fixing screw comply with BS 4662. Television and 35mm Data Outlets Cooker Control and 50A 47mm Switches Shaver Supply Units 47mm 32A Triple Pole and Neutral List no. the box must always be a screwdriver with a maximum blade of 3.5mm installed flush or sub flush to the surface to a is used. maximum depth of 6mm. To ensure products can extreme care is required. They treated and compliment the finish of the are designed to fit into folded metal boxes that frontplate. 482 . The recommended depth of boxes for the different types of wiring accessories are as follows: MOUNTING BOXES Product Box Depth Socket Outlets 35mm Lockable Socket 47mm Lockable Switch 47mm German style 2 pole + E Socket Outlet mounted in 47mm Euro Frame Connection Units 47mm Plateswitches 35mm Grid System Switches* 35mm Dimmer Switches 35mm Telephone. It is recommended that be correctly installed. 5268ALM Switch *Note: If Grid system accessories are to be fitted and the installation requires the attachment of conduit via nuts inside the mounting box.co. Wiring Devices Technical WIRING DEVICES mkelectric.
plate and ramp on Figure 5 support frame periodic cleaning should only consist of polishing with a dry lint Figure Figure 445 free soft cloth. if thick wallpapers are cut such that towards the the supportwall frame wall they fit around the support frame and therefore remain under Gently lever Figure 2 away from the edge of the frontplate. plus a Adjust North/South separate frontplate. North/South Figure 1b to Figure 1b Force applied 3. which will lever the plate away from other clip the first clip.	Where no gasket is used.	Carefully slide the blade upwards and then gently lift the up to disengage handle away from the wall.	Make sure not to crush or deform the spring steel clips situated in this direction towards the direction Adjust wall along one edge of the product support frame. so as to prevent Frontplate Installation wall plate and ramp on damage or distortion to the product or support frame.	On uneven walls. or damage to the Figure 3 3 FIGURE between notch in wall and/or product could result. wall wall between between notch notch in in plate plate and and ramp ramp onon see pages 98-128 in the product selector. FIGURE Gently lever away from Blade to be wall between notch in Figure 4 plate and ramp on Figure 5 Slide screwdriver support frame to the left to disengage other clip Gently Gently lever lever away away from from Blade Blade toto be be For a full range of corresponding products. Figure 4 Gently lever away from Blade to be Cleaning Frontplates wall between notch in In order to protect the quality surface finish of the front plate.	With the first clip released. support frame Figure 32 Gently lever Figure 2 FIGURE 2 away from wall Frontplate Removal Blade to be Slide screwdriver between notch in up to disengage Figure 2 plate and ramp on 1. The product is mounted to the wall. in in this thiswith Figure 1bplate towards plate Force towards the aperture applied the align direction direction wall towards wall the aperture Apply a 1. Figure Figure 33 5.	Turn off the power supply. full plate engagement with the clips Force applied wall Blade to be towards the may be restricted. wall Apply a force force Forceinapplied this 2.4.	The frontplate is supplied loose to aid installation. Frontplate Removal Gently lever Slide supportscrewdriver support frame frame 483 Figure 5 to the left to away from Blade to be disengage between notch otherinclip wall . make sure the screwdriver does not go support frame wall Blade to be between the spring steel ramp and the wall. other clip support frame Figure 3 Gently Gently lever lever 2.	A gasket is also supplied with each product.	Using the gasket with all switches and the German socket. North/South toto align force in Force this applied align with with plate plate 5. after Apply Apply aa force forceto Force to align Force applied with applied North/South wiring. plate and ramp on support Slide frame screwdriver Figure 4 4. See Fig.	Carefully slide a screwdriver between the ramp on the main away away from from body of the product and the notch in the lower right hand edge wall wall Blade Blade toto be be Slide betweenscrewdriver of the plate. which may prove align with plate towards the aperture 1B FIGURE Apply Apply aa wall useful on uneven walls. and the front plate clipped onto the frame. support the plate with one hand and Slide Slide screwdriver screwdriver continue to move the blade to the left under. force force in in this this Figure 2 direction direction Figure 1b 4. between notch in Note: When installing Aspect do not over tighten screws. even when there is a mismatch Figure 2 Gently lever North/Southaway to from of as much as 1mm between the distance the main body of the align with plate wall Blade to be product is from the wall and that of the front plate. See note 5 below. will Adjust Adjust North/South Apply a ensure full compliance with the appropriate standards. between notchnotch in in up to and plate disengage Gently lever plate and rampramp onon away from other clipframe support 3.	Both standards set out to guarantee full engagement of the aperture directionthe towards aperture Adjust wall frontplate on uneven surfaces. aperture between notch in Force Force applied applied plate and ramp on towards 6. North/South to align with plate aperture Figure 1a Wiring Devices Technical Apply a force Force applied Adjust WIRING DEVICES in this towards the North/South Technical Hotline direction wall to align with +44 (0)1268 563720 plate aperture – Aspect Figure Apply a1a Figure direction force in this 1b Force applied Adjust towards the North/South wall Apply to aligna with force in this plate aperture direction Aspect Installation Figure Figure 1a Adjust 1a Apply a forceto North/South Figure 1b Force Adjustapplied Adjust in thiswith plate align towards North/South North/Souththe direction aperture wall to to align Apply aligna with with The MK ‘Aspect’ range of products consists of the main product Figure 1a plate plate aperture force in this aperture FIGURE 1A direction Adjust complete with its support frame and clipping medium. Figure 4 FIGURE Figure 34 up up to to disengage disengage Gently lever other clip other clipto be Blade away from Data products in euromounting frames wall between notch in Slide screwdriver Products operating at extra low voltage levels (<50v) must not plate and ramp on up to disengage support frame be mounted in the same Euro enclosures as equipment rated in other clip excess of 50v.
Telephone Secondary and Data Sockets To provide customers with a high level of flexibility the voice and data decorative wiring devices are available in modular formats. Wiring Devices Technical WIRING DEVICES mkelectric.uk Decorative Technical: General information Earthing: All Metal Frontplate Products To comply with the latest edition of the BS 7671 IET regulations: the metal front plate must be earthed. For example to produce a Telephone Secondary Socket the following items are required: RANGE PRODUCTS REQUIRED Albany Plus K181 K5821 Aspect K24181 K5821 Edge K14181 K5821 Or RANGE PRODUCTS REQUIRED Albany Plus K182 K5821 2 x K186 Aspect K24182 K5821 2 x K186 Edge K14182 K5821 2 x K186 484 . All earth terminals provided must be connected to the protective earth conductor.co.
Documents Similar To T13 ALBANY PLUS Tech.pdf
Manual Accuvac Rescue