Source: https://www.psegliny.com/page.cfm/AboutUs/OASISElectricTransmissionInformation/TransmissionOwner
Timestamp: 2018-02-21 15:18:10
Document Index: 334575911

Matched Legal Cases: ['art\n10', 'art\n06', 'art\n05', 'art\n02', 'art\n05', 'art\n07', 'art\n06', 'art\n08', 'art\n08', 'art\n04']

HOME › ABOUT US › OASIS - TRANSMISSION INFO › TRANSMISSION OWNER
Transmission Owner Information Being Released to Market
07/25/15 12:00:00 TVR Guidance – 8KD West Bus (Holtsville) and 8DV Randall Road (Wildwood) DRSS In Service
This TVR guideline is being provided to explain the requirement for generation to resolve specific voltage issues on the LIPA system, assuming 8KD West Bus (Holtsville) DRSS and 8DV Randall Road (Wildwood) – In Service. View Guideline (PDF)
07/25/15 12:00:00 TVR Guidance – 8KD West Bus (Holtsville) DRSS In Service
This TVR guideline is being provided to explain the requirement for generation to resolve specific voltage issues on the LIPA system, assuming 8KD West Bus (Holtsville) DRSS – In Service. View Guideline (PDF)
06/01/15 12:00:00 East End Operating Guideline
This East End Operating Guideline is being provided to explain the requirement for generation to resolve specific voltage issues on the LIPA system. This guideline is in effect for Summer 2015 - View Guideline (PDF)
06/01/15 12:00:00 The Loss of Gas Supply – Long Island (G-R3)
Guideline is provided to indicate the number of Northport Steam units that must run on oil so that the loss of a single gas facility does not result in the uncontrolled loss of electric load within the Long Island zone. - View Guideline (PDF)
07/22/14 12:00:00
TVR Guidance
This TVR guideline is being provided to explain the requirement for generation to resolve specific voltage issues on the LIPA system, assuming West Bus DRSS in service. The new TVR Guideline is effective Tuesday July 22, 2014. - View Requirement (PDF)
06/17/14 12:00:00 TVR Guidance
This interim TVR guideline is being provided to explain the requirement for generation to resolve specific voltage issues on the LIPA system, assuming West Bus DRSS in service. The new TVR Guideline is effective Monday June 16, 2014. - View Requirement (PDF)
05/15/14 12:00:00 Implementation of Local Reliability Rule I-R5 (Loss of Generator Gas Supply)
The Implementation tables for I-R5 are provided to indicate the number of Northport Steam units that must run on oil in order to prevent voltage collapse for the largest gas contingency - View Implementation Table (PDF)
05/02/14 12:00:00 Implementation of Local Reliability Rule I-R5 (Loss of Generator Gas Supply)
11/01/13 12:00:00 Implementation of Local Reliability Rule #I-R5 (Loss of Generator Gas Supply)
The Implementation tables for I-R5 are provided to indicate the number of Northport units that must run on oil in order to prevent voltage collapse for the largest gas contingency. - View Implementation Table (PDF)
6/21/13 12:00:00 Implementation of Local Reliability Rule #I-R5 (Loss of Generator Gas Supply)
The Implementation tables for I-R5 are provided to indicate the number of Northport units that must run on oil in order to prevent voltage collapse for the largest gas contingency - View Implementation Table (PDF)
06/01/13 12:00:00 East End Load Dispatch Guidance
This East End Generation guideline is being provided to explain the requirement for generation to resolve specific voltage issues on the LIPA system. This guidance is in effect for Summer 2013 .- View East End Chart
10/18/12 12:00:00 Implementation of Local Reliability Rule #I-R5 (Loss of Generator Gas Supply)
09/14/12 13:00:00 Interim Implementation of Local Reliability Rule #I-R5 (Loss of Generator Gas Supply)
The Interim Implementation table for I-R5 is being provided to indicate the number of Northport units that must run on oil with NNC out of service assuming only one 345/138kV autotransformer at Newbridge In Service, in order to prevent voltage collapse for the largest gas contingency. - View Implementation Table (PDF)
06/06/12 13:30:00 Local Reliability Rule # I-R5 (Loss of Generator Gas Supply)
The Implementation table for I-R5 is being provided to indicate the number of Northport units that must run on oil to prevent voltage collapse for the largest gas contingency. - View Chart
06/01/12 12:00:00 East End Load Dispatch Guidance
This East End Generation guideline is being provided to explain the requirement for generation to resolve specific voltage issues on the LIPA system. This guidance is in effect for Summer 2012 .- View East End Chart
05/21/12 12:00:00 TVR Guidance
This guideline (TVR) is being provided to explain the requirement for generation to resolve specific voltage issues on the LIPA system. This guidance is in effect for Summer 2012. The use of the table is explained on the bottom of the table. - View East-Holbrook Chart
02/02/12 11:30:00 Northport Nomogram - Light Load Voltage Guidance
The following nomogram summarizes recommended Northport steam unit dispatch for various Neptune import dispatch levels, and is intended to optimize Neptune MW dispatch in order to decrease Northport unit commitment. - View Northport Nomogram
This guidance is in effect for the months of September through April, mainly where light load conditions are seen, for system load levels less than 2,000 MW.
05/25/11 12:00:00 TVR Guidance
This guideline (TVR) is being provided to explain the requirement for generation to resolve specific voltage issues on the LIPA system. This guidance is in effect for summer 2011. The use of the table is explained on the bottom of the table. - View East-Holbrook Chart
05/25/11 12:00:00 East End Load Dispatch Guidance
This East End Generation guideline is being provided to explain the requirement for generation to resolve specific voltage issues on the LIPA system. This guidance is in effect for summer 2011 .- View East End Chart
07/06/10 10:00:00 Local Reliability Rule # I-R5 (Loss of Generator Gas Supply)
06/09/10 14:00:00 TVR Guidance
This guideline (TVR) is being provided to explain the requirement for generation to resolve specific voltage issues on the LIPA system. This guidance is in effect for summer 2010. The use of the table is explained on the bottom of the table. - View East-Holbrook Chart
06/09/10 14:00:00 East End Load Dispatch Guidance
This East End Generation guideline is being provided to explain the requirement for generation to resolve specific voltage issues on the LIPA system.- View East End Chart
08/07/09 15:00:00 TVR Guidance
This guideline (TVR) is being provided to explain the requirement for generation to resolve specific voltage issues on the LIPA system. This guidance is in effect from May 15, 2009 thru September 18, 2009. The use of the table is explained on the bottom of the table accessible through this link - View East-Holbrook Chart
08/07/09 15:00:00 East End Load Dispatch Guidance
This East End Generation guideline is being provided to explain the requirement for generation to resolve specific voltage issues on the LIPA system. View East End Chart
04/02/08 09:33:00 The following information is being provided to clarify information located in the NYISO Transmission and Dispatching Operations Manual Attachment B.5 - Applications of Reliability Rules and Cost Allocation Responsibility. ARR 22 and ARR 28 utilize the terms "Light Load" and "Peak Load". Light Load is defined as load less than 1900 MW. Peak Load is defined as load greater than 5300 MW. These values can vary based on transmission lines in service and time of load.
04/02/08 09:33:00 The following information is being provided to clarify information located in the NYISO Transmission and Dispatching Operations Manual Attachment B.5 - Applications of Reliability Rules and Cost Allocation Responsibility. ARR 28-D states a requirement to dispatch one Barrett unit in service at light load conditions. This requirement is no longer necessary.
4/23/07 14:35:00 In advance of NYISO Operating Committee approval, LIPA is making the public the following information related to the proposed local reliability rule NYSRC I-R3: Considering the loss of gas supply as a single contingency that will impact the electric system, the number of gas fired generators must be limited above certain critical system load levels. When the Neptune HVDC tie is not in-service then, at load levels above 3900 MW no more than two Northport units can be gas fired. At load levels above 2750 MW, and up to 3900 MW, no more than three Northport units can be gas fired. With the Neptune HVDC tie inservice then, at load levels above 3100 MW no more than two Northport units can be gas fired.
Last Updated 02/22/2017 8:53 AM