Source: https://de.scribd.com/document/110411105/XL-A9100-BTS-Installation-Standard-Ed-01a
Timestamp: 2020-04-08 00:18:11
Document Index: 512610941

Matched Legal Cases: ['art 1', 'art 2', 'art 3', 'art 4', 'art 5', 'art 1', 'art 2', 'art 3', 'art 4', 'art 5']

XL- A9100 BTS Installation Standard_Ed 01a | Cable | Electrical Wiring
speichernXL- A9100 BTS Installation Standard_Ed 01a für später speichern
Liebert PEX Condenser User Manual AP11ENT PEXCondenserV1 UM
Altis Wiring
ADM Standard_specifications (Traffic Control System Section XVII-4)
Protec - Aspirating-Smoke Detection
20130923(1)
u1l9 data exchange - mst
Bending Radii and Pulling Tensions
u1l9 data exchange b h
polar 92 tech manual
8DK 02 05 04 01 00 PCZZA ED 00
ALCATEL-LUCENT INDONESIA
Evolution A9100 BTS Installation Standard
ABSTRACT This document describes the installation standard for indoor and outdoor part of A9100 BTS product
Domain Process Owner Type Originator Distrib. Codes
ALCATEL-LUCENT INDONESIA IMPLEMENTATION INSTRUCTIONS, USER GUIDE DURMAWEL SAHARA Internal: Y/N External: Y/N
ALU - QA XL QA XL - RND
EFFECTIVE DATE : 10 SEPTEMBER 2007
TABLE OF CONTENTS 1 1.1 1.2 INSTALLATION INDOOR ........................................................................4 Indoor Tray (Top View).........................................................................4 GROUNDING SYSTEM ............................................................................6
1.1.1 Indoor Tray (Front View) ......................................................................5 1.2.1 Arrangement of Wiring Copper rod ..........................................................6 1.2.2 Connection Copper rod to Main Grounding Bar (MGB) ...................................7 1.2.3 Connection Grounding at BTS Radio, Transmission and Rectifier to MGB ...........8 1.3 FEEDER ENTRY ...................................................................................9 floor of shelter (Inside view) ..................................................................9 1.3.2 Installation Feeder Entry (height of feeder entry and dimension from base ........ floor of shelter (Inside view) ................................................................ 10 1.3.3 Arrangement of Feeder Entry and Connection Grounding Arrester to Busbar ... 11 1.4 BTS INDOOR ..................................................................................... 12 1.4.1 Connection Wiring Cable at the top BTS Radio.......................................... 12 1.4.2 Connection Wiring Board at BTS Radio Rack ............................................ 13 1.4.4 Connection Wiring Alarm and Traffic Cables at DDF External Alternative 1 ...... 14 1.4.5 Connection Wiring Alarm and Traffic Cables at DDF External Alternative 2 ...... 15 1.4.6 BTS Radio Installation (Side View) ......................................................... 16 1.5 POWER SUPPLY (RECTIFIER) ................................................................. 17 1.5.1 Connection Wiring Power Cable at Power Suply (Rectifier) .......................... 17 2 2.1 INSTALLATION OUTDOOR..................................................................... 18 Installation Position Feeder Coaxial at Vertical Tray of Tower and Installation .... Feeder Clamp .................................................................................. 18 2.1.1 Installation Grounding Kit (at the top and bottom) .................................... 19 2.1.2 Installation Grounding Kit at Feeder Entry (Outdoor) ................................. 20 2.1.3 Installation Labelling, Wiring Jumper Cable and Grounding at Antenna........... 21 3 3.1 3.2 3.3 3.4 3.5
1.3.1 Installation Feeder Entry (height of feeder entry and dimension from base ........
INSTALLATION ANTENNA TYPE APM 40.................................................... 22 Installation Antenna and Mounting Hardware Part 1................................... 22 Installation Antenna and Mounting Hardware Part 2................................... 23 Installation Antenna and Mounting Hardware Part 3................................... 24 Installation Antenna and Mounting Hardware Part 4................................... 25 Installation Antenna and Mounting Hardware Part 5................................... 26
GENERAL MATERIALS .......................................................................... 27 Feeder Entry.................................................................................... 27 Heat Shrinkable Sleeve (Condom).......................................................... 27 Cable Ties (Tie Wrap) Type CS-300X ...................................................... 28 Cable Ties (Tie Wrap) Type CS-390L ...................................................... 28 Cable Ties (Tie Wrap) Type CS-200L ...................................................... 29 Cable Ties (Tie Wrap) Type CS-150T ...................................................... 29 Labelling......................................................................................... 30 Connector ....................................................................................... 30 HHD Cavity Anchor ........................................................................... 31
4.10 Cable Shoe 1x35 ............................................................................... 31 4.11 Protection Edge ................................................................................ 31 4.12 Clamp Copper rod (SIMEL CH 10.70)....................................................... 32 4.13 Clamp Copper rod (SIMEL BB 50-80) ....................................................... 32 APPENDIX ................................................................................................ 33 DOCUMENT MANAGEMENT............................................................................ 33
Indoor Tray (Top View)
ACPDB
Air Inlet Under AC 2
Alarm Above AC 2
PWR SUPPLY AC BELL TYPE CSM 20
70 150 70 150
Clamp (@0.5m) Copper Rod
Hole for Cable Pwr Supply Edge Rubber Protection
Tech room/Shelter Height of Ceiling : 3.00 Height of Tray : 2.40
Holes for Cable Wiring and Edge Rubber Protection
RACK TRANS & DDF
BTS EVO 900 MHz
FEEDER ENTRY
H : 2000
SPARE NA PA QA
INSIDE VIEW (from Inside of Shelter)
Cable Tray Support Tray HHD Molly Anchor
Notes : "A" (See BTS Installtion Side View on Page 16)
1. MW 2. Spare 3. Antenna Sector 1A (NA) 4. Antenna Sector 2A (PA) 5. Antenna Sector 3A (QA) 6. Spare 7. Spare 8. Antenna Sector 1B (NB) 9. Antenna sector 2B (PB) 10.Antenna Sector 3B (QB)
1.1.1 Indoor Tray (Front View)
B ra c k e t T ra y
C a b le T ra y
B ra c k e t T ra y B ra c k e t T ra y
B u s b a r fo r G r o u n d A rr e s te r
G roun d C a b le B C 3 5
C op per R od
C op per R od B ra c k e t T ra y B ra c k e t T ra y
C la m p ( @ 1 m ) G r o u n d c a b le B c 35
B TS E v o liu m
M a in G r o u n d B a r (M G B )
R e c tifie r
IN S ID E T E C H N IC A L R O O M
1.2.1 Arrangement of Wiring Copper rod
Cable Tray Support Tray
HHD Molly Anchor
Connection Copper rod to Main Grounding Bar (MGB)
D C Fa n
B us bar
Copper Rod Clamp simel CH Copper Rod Copper Rod
Busbar Cable Tray Cable Grounding
to Main Grounding Bar
Scale : NTS G rou nd C a b le B C 3 5 C o ppe r Rod
to Copper Rod
to Busbar
Cable Grounding Cable Shoe SS Bolt M8
M a in G r o u n d . B a r
M a in G ro u n d . B a r
Copper Rod Clamp simel CH Copper Rod Cable Tray Bracket Tray HHD Molly Anchor
Busbar Cable Shoe Cable Tray Bracket Tray HHD Molly Anchor
Ground Cable BC 35
Cable Shoe SS Bolt M8 Main Grounding Bar (MGB)
Connection Grounding at BTS Radio, Transmission and Rectifier to MGB
D C Fan
C la m p ( @ 1 m ) G r o u n d c a b le Y /G B C 3 5
Copper Rod Clamp simel CH Cable Tray
Cable Grounding BC35
IDU Rack 19"
BTS E v o liu m
R a d io T r a n s m is s i o n
NOTES : This is Temporary Standard, The New Standard is on going validation by ALU & XL
1.3.1 Installation Feeder Entry (height of hole feeder entry and dimension from base floor of shelter (Inside View)
1 1 2 5 3 4 5 6 7 8 9 10 20 11 12 13 25 14
15 16 30 17 18 19 20
MW RACK 19"
55 31 32 33 60 34 35 36 37 38 70 39 40 41 75 42 43 44 80 45
INSIDE VIEW (From The Inside Technical Room/Shelter)
FFEDER ENTRY
1. MW 2. Spare 3. Antenna Sector 1A (NA) 4. Antenna Sector 2A (PA) 5. Antenna Sector 3A (QA) 6. Spare 7. Spare 8. Antena Sector 1B (NB) 9. Antenna Sector 2B (PB) 10. Antenna Sector 3B (QB)
1.3.2 Installation Feeder Entry (height of hole feeder entry and dimension from base floor of shelter (Inside View Isometric)
D C F an
B u sb a r
Grounding Cable Y/G 1x35
1. MW 2. Spare 3. Antenna Sector 1A (NA) 4. Antenna Sector 2A (PA) 5. Antenna Sector 3A (QA) 6. Spare 7. Spare 8. Antenna Sector 1B (NB) 9. Antenna Sector 2B (PB) 10. Antenna Sector 3B (QB)
INSIDE VIEW ISOMETRIC
Scale ~ NTS
1.3.3 Arrangement of Feeder Entry and Connection Grounding Arrester to Busbar
C o n n e c to r 1 / 2 " - 7 / 1 6 m a le
L ig h tn in g A r r e ste r C la m p F e e d e r T y p e D o u b le C o n n e c to r 7 / 8 " - 7 / 1 6 fe m a le C o a x ia l F e e d e r 7 / 8 " (6 fe e d e r) Label B ra c k e t L Label C a b le J u m p e r 1 / 2 " to B T S R a d io
C a b le E n try
QA NA QB PB PA
G r o u n d in g B u sb a r
C op per rod G r o u n d in g C a b le A r r e st e r
C o p p e r b a r in sta lle d d ir e c tly to M a in G r o u n d B a r (M G B )
C a b le g r o u n d B C 3 5 in sta lle d d ir e c tly to M a in G ro u n d B a r (M G B )
BTS INDOOR
1.4.1 Connection Wiring Cable at the top BTS Radio
EDGE RUBBER PROTECTION CABLE TRAY HOLES FOR CABLE WIRING
Ground Cable Y/G BC 35
METAL SHIELD CONNECT TO BTS
ALARM CABLE GREY
Cable Power (Blue Color) Cable Power (Blue Color) Cable Traffic (Grey Color)
EDGE RUBBER PROTECTION METAL SHIELD
Cable Black (Black) Cable Power (Blue)
Power Cable (black)
Cable Abis (Grey) Cable Alarm (Grey)
DETAIL WARING CABLE ALARAM, PCM, POWER & GROUNDING
1.4.2 Connection Wiring Cables at BTS Radio Rack
P ANT A P ANT B Q ANT A
N ANT A N ANT B Q ANT B
TO P C O NNEC TO R BTS
Abis 4 XBCB XRT XGPS Abis 3 Abis 2 Abis 1
Abis 4 Abis 3 Abis 2 Abis 1
XGND GND
4 ABIS RELAYS
XCLK2 XCLK1 XCLK1 IN / OUT IN OUT
BTS INT
ALARMS INPUTS/OUTPUTS
S R 3
S R 4
S R 5
G S O 0 4 C AB L E fro m A N C G to T o p C on n. BT S
Q AN T A
TXAIN1 ANT A RX0AOUT1
P ANT A
RX1AOUT1 TXAIN2
RX0AOUT2 RX1AOUT2 RX0BOUT2 RX1BOUT2
TXAOUT
RX0AOUT2 RX1AOUT2 RX0BOUT2
TXBIN2
RX1BOUT2
RX0BOUT1 RX1BOUT1 ON OM ALARM TXBIN1 ON
RX0BOUT1 RX1BOUT1 TXBIN1
TXBOUT
Q AN T B
G S O 0 3 C AB L E fro m T R E to A N C G
P ANT B
S e c t or 3
S e c t or 2
R X C A BL E
from T R E to A N C G
POWER ENABLE OFF TEST OFF TEST
RX1 RSL OP PWR TX BCCH FAULT Y
T RE 1
RSL OP PWR
TX BCCH FAULT Y
A B IS C A B LE fro m S U M A to A bis P ort
A B I S 1/2
B T S C O N N E C T O N A R E A
N ANT A
B T S T E R M I N A L
M N E M O
RX0BOUT1 RX1BOUT1
AB IS 1
TXBIN1
O M L O & M O M U P S 1
ON OM ALARM
AB IS 2
T RAN S F AU LT
N ANT B
S e c t or 1
1.4.3 Connection Wiring Alarm and Traffic Cables at DDF External Alternative 1
CABLE TRAY INDOOR
Alarm cable Abis cable
1 1 2 5 3 4 5 10 6 7
P1 P2 3 4 5 P6
TX Channel 1-6 ALU
DDF ALU
13 P14 15
RX Channel 1-6 ALU
Alarm 1 ALU Alarm 2 ALU
DDF Additional
IDU IDU RADIO RACK 19"
1.4.4 Connection Wiring Alarm and Traffic Cables at DDF External Alternative 2
1 1 2 5 3 4 5 10
Alarm ALU
15 8 9 10 11 12 13 14 15 30 16 17
1.4.5 BTS Radio Installation (Side View)
BTS EVO
ISOMETRIK VIEW
Scale ~ 1:15
HHD Molly Anchor Rail Z Support
DETAIL RAIL Z SUPPORT
1.5.1 Connection Wiring Power Cable at Power supply (Rectifier)
EDGE RUBBER PROTECTION
COPPER ROD CABLE TRAY
CABLE POWER BLACK CABLE POWER BLUE
COPPER BAR TERMINAL GROUNDING RECTIFIER
Power Cable Cable Pin Lug Black Cable Blue Cable
MCB 50A
NC 50 N ON
NC 50 N NC 50 N ON C50 ON C50 NC 50 N NC 50 N NC 50 N NC 50 N NC 50 N NC 50 N NC 50 N NC 50 N ON C50 ON C50 ON C50 ON C50 ON C50 ON C50 ON C50 ON C50
Installation Position Feeder Coaxial at Vertical Tray of Tower and Installation Feeder Clamp
To Antenna Sector 2A (PA) To Antenna Sector 1B (NB) To Antenna Sector 1A (NA) To Antenna Sector 2B (PB). To Antenna Sector 3A (QA). To Antenna Sector 3B (QB).
COAXIAL FEEDER 7/8"
FEEDER CLAMP FOR 7/8" Every 0.8 ~ 1.0 meter
2.1.1 Installation Grounding Kit (at the top and bottom)
L i g h t n i n g P r o t e c t i o n
A NTE NN A S UPPO R T (B A C K T O b A CK T O T O W ER M G B IS O L A T O R IS O L A T O R
G R O U N D IN G K IT (B A C K T O B A CK )
G R O U N D IN G T O A N T E N N A S EC T O R (B A C K T O B A CK )
B U SB A R 1
BU S BA R T R AY
BUSBAR 1
T O T O W ER M G B
IS O L A T O R
SP A R E
D E T A IL B U S B A R A T V E R T IC A L T R A Y
BU S BA R
D E T A IL B U S B A R 3 A T H O R IZ O N T A L T R A Y
BUS BAR 2
2.1.2 Installation Grounding Kit at Feeder Entry (Outdoor)
Antenna Sector Antenna Sector Antenna Sector Antenna Sector Antenna Sector Antenna Sector
3B (QB) 3A (QA) 2B (NB) 2A (PA) 1B (NB) 1A (NA)
Coaxial Feeder Feedery Entry Heat Shrinkable (Condom) Grounding Kits Label
QA PA QB PB NB NA
Vertical Tray Cable Ground Kits Grounding Kits
Cover Feeder Holes
Coaxial Feeder 7/8" Horizontal Tray CableGround
CABLE TIES (Tie Wrap) CABLE TIES
Heat Shringkable Sleeve(Condom)
NA NB 10 c m
HORIZONTAL TRAY Isolator Busbar GROUNDING KITS SS Bolt M8 Cable Shoe
DETAIL BUSBAR AT HORIZONTAL TRAY & GROUNDING KIT
2.1.3 Installation Labelling, Wiring Jumper Cable and Grounding at Antenna
NB PA
LABE L T IE W R A P F EE D ER C AB LE
T IE W R A P F EE D E R C AB LE
T IE W R A P G R O U N D IN G C A B L E
NB PB QB NA PA QA
T IE W R A P G R O U N D IN G C A B L E LABE L
To TO WER M GB IS O L A TO R IS O L A TO R
G R O U N D IN G K IT A N T E N N A S E C T O R (B A C K T O B A C K ) (B A C K T O B A C K )
INSTALLATION ANTENNA TYPE APM40
Installation Antenna and Mounting Hardware Part 1
Installation Antenna and Mounting Hardware Part 2
Installation Antenna and Mounting Hardware Part 3
Installation Antenna and Mounting Hardware Part 4
Installation Antenna and Mounting Hardware Part 5
Feeder Entry :
Material from Steel grade ST 41 Dimension : 280 x 3 x 520
Heat Shrinkable Sleeve (Condom) :
Material from Rubber Raychem Code : 75/22 ER 3310
Cable Ties (Tie Wrap) Type CS-300X :
Code Material SIGMA TIES CS 300X Dimension : 7.6 x 270 Function : Installation Outdoor (at Top Antenna)
Cable Ties (Tie wrap) Type CS-390L :
Code Material SIGMA TIES CS 390L Dimension : 4.8 x 270 Function : Installation Indoor (at Jumper Cable)
Cable Ties (Tie wrap) CS 200L :
Code Material SIGMA TIES CS 200L Dimension : 3.6 x 180 Function : Installation Indoor (at Alarm & PCM Cable)
Cable Ties (Tie wrap) CS 150 T :
Code Material SIGMA TIES CS 150L Dimension : 3.6 x 140 Function : Installation Indoor (for Connection cable at top BTS radio)
Labelling, material from Acrilique Function : Label Identification
1/2 DIN Male
O-Ring CONNECTOR 7/8 RFS
7/8 DIN Female
HHD Cavity Anchor :
Cable Shoe :
HHD CAVITY ANCHOR Specification Screw 5x45mm (Hilti) Function : Fixation for equipment, accessories and bracket cable tray at Gypsum wall.
Cable Shoe 1x35mm
Protection Edge :
PROTECTION EDGE Specification from Rubber L2000mm
4.12 Clamp Copper rod (SIMEL CH 10.70) :
Clamp Copper rod (SIMEL BB 50- 80) :
RELEVANT DOCUMENTS AND WEB SITES
# [1] [2] Title of the document/web site Mounting HW APM40, Radio Frequency Systems Evolution A9100 BTS Installation Manual Reference/Web link http://www.rfsworld.com/
3BK 17226 0001 RJZZA Ed.09
Wording ALU Definition Alcatel-Lucent
Location of the reference of this document (electronic copy): ISO9000\3.Work Instruction
Short description of significant changes to previous edition: Edition Originated Effective Date Originator Date 00 15 Aug 07 01 Sept 07 Durmawel Sahara
Dokumente ähnlich wie XL- A9100 BTS Installation Standard_Ed 01a
Jose P. Bambalan Jr.
api-297574260
jmt996
Vertex 7200
jjhkkhjjh
54-SMSS-2, REV. 1
Cost Analysis44 Tiny Canuck
Architectural Utilities 2 - Electrical and Mechanical Equipment_1-10
Leonezza Leones
Mehr von naypcuoi
Đề Homework Day4
Hội Thoại Tiếng Anh Cho Người Mất Gốc
Jacky Nicolson
VTDL_GLAP08_SSR
Cell_Iub_cong.xlsx
110VDC_50A_6KW
syedrahma
Youth Identity 2016 SOW
Document Vendor Lighting Protection Eritech
personal philosophy of facilitation - portfolio
api-302539316
5000506[1]
MichiGoGD
Quick Reference - G3430-90009