Source: http://codeofchina.com/standard/GB16895.3-2004.html
Timestamp: 2020-03-30 14:03:44
Document Index: 110888898

Matched Legal Cases: ['art 5', 'art 5', 'art 5', 'art 5', 'art 4', 'art 5', 'art 4', 'art 1', 'art 5', 'art 5', 'art 5', 'art 5']

GB 16895.3-2004 English Version, GB 16895.3-2004 Electrical installations of buildings—Part 5-54:Selection and erection of electrical equipment—Earthing arrangements,protective conductors and protective bonding conductors (English Version) - Code of China
2020-3-30 3.215.182.81
Position: Chinese Standard in English/GB 16895.3-2004
GB 16895.3-2004 Electrical installations of buildings—Part 5-54:Selection and erection of electrical equipment—Earthing arrangements,protective conductors and protective bonding conductors (English Version)
Standard No.: GB 16895.3-2004 Status: valid remind me the status change
Implemented on: 2005-2-1 Delivery: via email in 1 business day
Add GB 16895.3-2004 to Cart
Detail of GB 16895.3-2004
Introduction of GB 16895.3-2004
Contents of GB 16895.3-2004
Standard No.: GB 16895.3-2004
English Name: Electrical installations of buildings—Part 5-54:Selection and erection of electrical equipment—Earthing arrangements,protective conductors and protective bonding conductors
Chinese Name: 建筑物电气装置 第5-54部分：电气设备的选择和安装--接地配置、保护导体和保护联结导体
Issued on: 2004-05-14
Implemented on: 2005-2-1
Superseding: GB 16895.3-1997 Electrical installations of buildings―Part 5: Selection and erection of electrical equipment Chapter 54: Earthing arrangements and protective conductors
This Part of series standard "Electrical Installations of Buildings" addresses the earthing arrangements, protective conductors and protective bonding conductors in order to satisfy the safety of the electrical installation.
Foreword	III 541 General 541.1 Scope 541.2 Normative references 541.3 Definitions 542 Earthing arrangements 542.1 General requirements 542.2 Earth electrodes 542.3 Earthing conductors 542.4 Main earthing terminal 543 Protective conductors 543.1 Minimum cross-sectional areas 543.2 Types of protective conductors 543.3 Electrical continuity of protective conductors 543.4 PEN conductors 543.5 Combined protective and functional earthing 543.6 Arrangement of protective conductors 543.7 Reinforced protective conductors for protective conductor currents exceeding 10 mA 544 Protective bonding conductors (equipotential bonding conductors) 544.1 Protective bonding conductors for the connection to the main earthing terminal 544.2 Protective bonding conductors for supplementary bonding Appendix A (Normative) Method for Deriving the Factor k in 543.1.2 (see also IEC 60724 and IEC 60949) Appendix B (Informative) Illustration of Earthing Arrangements, Protective Conductors and Protective Bonding Conductors Table 54.1 Common Minimum Sizes for Earth Electrodes of Commonly Used Material from the Point of View of Corrosion and Mechanical Strength where Embedded in the Soil Table 54.2 Minimum Cross-sectional areas of Earthing Conductors Buried in the Soil Table 54.3 Minimum Cross-sectional Area of Protective Conductors Table A.54.1 Value of Parameters for Different Materials Table A.54.2 Values of k for Insulated Protective Conductors not Incorporated in Cables and not Bunched with other Cables Table A.54.3 Values of k for Bare Protective Conductors in Contact with Cable Covering but not Bunched with other Cables Table A.54.4 Values of k for Protective Conductors as a Core Incorporated in a Cable or Bunched with other Cables or Insulated Conductors Table A.54.5 Values of k for Protective Conductors as a Metallic Layer of a Cable e.g. Armour, Metallic Sheath, Concentric Conductor, etc. Table A.54.6 Value of k for Bare Conductors where there is no Risk of Damage to any Neighbouring Material by the Temperature Indicated Bibliography
* GB 16895.5-2012 Low-voltage electrical installations—Part 4-43:Protection for safety—Protection against overcurrent
* GB 16895.6-2000 Electric installations of buildings - Part 5: Selection and erection of electrical equipment - Chapter 52: Wiring systems
* GB/T 17045-2008 Protection against electric shock - Common aspects for installation and equipment
Referred in GB 16895.3-2004:
GB 16895.3-2004 is referred in:
* GB 14050-2008 Types and safety technical requirements of system earthing
* GB/T 10060-2011 Code for acceptance of electric lifts installation
* GB 16895.21-2011 Low-voltage electrical installations—Part 4-41:Protection for safety—Protection against electric shock
* GB/T 18487.1-2015 Electric vehicle conductive charging system―Part 1:General requirements
* GB 12668.501-2013 Adjustable Speed Electrical Power Drive Systems - Part 5-1: Safety Requirements - Electrical, Thermal and Energy
* GB/T 16895.18-2010 Electrical installations of buildings—Part 5-51:Selection and erection of electrical equipment—Common rules
*GB/T 21431-2008 Technical specifications for inspection of lightning protection system in building
Standard No. GB 16895.3-2004
Implemented on 2005-2-1
GB 16895.3-2004
Electrical installations of buildings—Part 5-54:Selection and erection of electrical equipment—Earthing arrangements,protective conductors and protective bonding conductors
建筑物电气装置 第5-54部分：电气设备的选择和安装--接地配置、保护导体和保护联结导体
GB 16895.3-1997 Electrical installations of buildings―Part 5: Selection and erection of electrical equipment Chapter 54: Earthing arrangements and protective conductors
GB 16895.3-2004, GB/T 16895.3-2004, GBT 16895.3-2004, GB16895.3-2004, GB 16895.3, GB16895.3, GB/T16895.3-2004, GB/T 16895.3, GB/T16895.3, GBT16895.3-2004, GBT 16895.3, GBT16895.3