Source: https://manualzz.com/doc/52020084/bradford-white-bmgv1600-brute-magnatech-series-hydronic-v.
Timestamp: 2020-06-02 21:09:46+00:00
Document Index: 182331077

Matched Legal Cases: ['arrêt ', 'arrêt ', 'arrêt ', 'arrêt ', 'arrêt ', 'arrêt ']

Bradford White BMGV1600 Brute MagnaTech Series Hydronic Volume Water Heaters (BMGV) User Manual | Manualzz
BMGV4000
Bradford White | BMGV4000 | User manual | Bradford White BMGV1600 Brute MagnaTech Series Hydronic Volume Water Heaters (BMGV) User Manual
User’s Manual Doc. 1294A User’s Manual for
Brute MagnaTech
Modulating Boiler Water Heater Model BMGH1600 Model BMGV1600
1,599 MBTU/h 1,599 MBTU/h
Model BMGH2000
1,999 MBTU/h
Model BMGV2000
Model BMGH2500
2,499 MBTU/h
Model BMGH3000
3,000 MBTU/h
Model BMGH3500
3,500 MBTU/h
Model BMGH4000
4,000 MBTU/h
Model BMGV2500
Model BMGV3000
Model BMGV3500
Model BMGV4000
This product must be installed and serviced by a professional service technician, qualified in hot water boiler and heater installation and maintenance. Improper installation and/or operation could create carbon monoxide gas in flue gases which could cause serious injury, property damage, or death. Improper installation and/or operation will void the warranty.
WARNING If the information in these instructions is not followed exactly, a fire or explosion may result causing property damage, personal injury or death.
WHAT TO DO IF YOU SMELL GAS • Do not try to light any appliance.
AVERTISSEMENT Assurez-vous de bien suivres les instructions données dans cette notice pour réduire au minimum le risque d’incendie ou d’explosion ou pour éviter tout dommage matériel, toute blessure Ne pas entreposer ni utiliser d’essence ou ni d’autres vapeurs ou liquides inflammables dans le à proximité de cet appareil ou de tout autre appareil.
QUE FAIRE SI VOUS SENTEZ UNE ODEUR DE GAZ: • Ne pas tenter d’allumer d’appareils.
• Ne touchez à aucun interrupteur. Ne pas vous servir des téléphones dans le bâtiment où vous vous trovez.
• Appelez immédiatement votre fournisseur de gaz depuis un voisin. Suivez les instructions du fournisseur.
• Si vous ne pouvez rejoindre le fournisseur de gaz, appelez le sservice des incendies.
The MagnaTech
FOR YOUR SAFETY, CONTENTS Familiarizing yourself with the MagnaTech .......................1
PLEASE READ THIS BEFORE OPERATING .................2
What to Do If You Smell Gas .............................................2
Lighting the Unit .................................................................2
Turning Off the Gas to the Unit ..........................................2
POUR VOTRE SÉCURITÉ, LISEZ AVANT DE METTRE EN MARCHE ........................
Que Faire si Vous Sentez une Odeur de Gaz ......................
Instructions de Mise en Marche ..........................................
Fermeture de l’Alimentation en Gaz ...................................
3 Shutting Down the MagnaTech ..........................................4
Restarting the MagnaTech ..................................................4
In the Event of Power Failure .............................................4
THE TOUCH SCREEN AND INDICATORS ....................5
About Lockouts, Holds, and Alerts .....................................6
Care, Inspection, and Service ..............................................7
FAMILIARIZING YOURSELF WITH THE MagnaTech
For full instructions regarding the MagnaTech, please reference the MagnaTech Installation and Operation Manual. Document #1293. If not available at or near the MagnaTech, it can be downloaded at www.bradfordwhite.com
Blower Touch Screen Display Automatic High Limit Reset Manual High Limit Reset Variable Speed Pump Control Voltage Pack
Start-Up and Shutdown Decal Shown without jacket.
Note - Model 3000 shown for reference.
Some components will vary slightly between the various sizes, but the User Interface & Front Panel remain the same. Page 1
Power Switch Door Latch
Manual Gas Valve Automatic Gas Valve Heat Exchanger Condensate Trap Condensing Unit
Start-Up and Shut-Down Decal.
Located on the inside of the right side door.
A. This appliance is equipped with an ignition device which automatically lights the pilot.
Do not try to light the pilot by hand. B. BEFORE OPERATING smell all around the appliance area for gas. Be sure to smell next to the floor because some gas is heavier than air and will settle on the floor. WHAT TO DO IF YOU SMELL GAS Do not try to light any appliance. Do not touch any electric switch; do not use any phone in your building. Immediately call your gas supplier from a neighbor’s phone. Follow the gas supplier’s instructions. If you cannot reach your gas supplier, call the fire department. C. Use only your hand to turn the gas valve handle. Never use tools. If the valve handle will not turn by hand, don’t try to repair it, call a qualified service technician. Force or attempted repair may result in a fire or explosion. D. Do not use this appliance if any part has been under water. Immediately call a qualified service technician to inspect the appliance and to replace any part of the control system and any gas control which has been under water.
1. STOP! Read the safety information above on this label. 2. Turn off all electric power to the appliance. 3. Set the thermostat to lowest setting. 4. 12.
This appliance is equipped with an ignition device which automatically lights the pilot. Do not try to light the pilot by hand. 5. Open front doors. 6. Turn off manual gas valve. Valve is off when valve handle is at a right angle to gas pipe. 7. Wait five (5) minutes to clear out any gas. Then smell safety information above on this label. If you don’t smell gas, go to next step. 8. Slowly turn manual gas valve to “ON”. Valve handle will be parallel to gas pipe.
9. Replace front panel. 10. Set mechanical thermostats to desired settings.
11. Turn on all electric power to the appliance. Set operating thermostat to desired settings using boiler display. and call your service technician or gas supplier.
1. Turn off all electric power to the appliance if service is to be performed. 2. 3. 5. Open front doors.
Close front doors.
4. Turn off manual gas valve. Valve is off when valve handle is at a right angle to gas pipe.
POUR VOTRE SÉCURITÉ, LISEZ AVANT DE METTRE EN MARCHE
Gas inlet Manual Gas Valve Shown in the “OFF” Position
AVERTISSEMENT: Quiconque ne respecte pas à la lettre les instructions dans la présente notice risque un début d' incendie ou une explosion entraînant des dommages, des blessures ou la mort. A. B.
Cet appareil est équipé d'un dispositif d'allumage qui s'allume automatiquement le pilote. N'essayez pas de lumière le pilote à la main.
AVANT DE FAIRE FONCTIONNER, reniflez tout autour de l’appareil pour déceler une odeur de gaz. Reniflez près du plancher, car certains gaz sont plus lourds que l’air et peuvent s’accumuler au niveau du sol.
QUE FAIRE SI VOUS SENTEZ UNE ODEUR DE GAZ Ne pas tenter d’allumer d’appareil. Ne toucher à aucun interrupteur; ne pas vous servir des téléphones se trouvant dans le bâtiment. Appelez immédiatement votre fournisseur de gaz depuis un voisin. Suivez les instructions du fournisseur. Si vous ne pouvez rejoindre le fournisseur, appelez le service des incendies. N’utilisez que votre main pour fermer la soupape d’arrêt de gaz. N’utilisez jamais d’outils. Si la poignêe de la valve ne tourne pas manuellement, ne tentez pas de la réparer. Communiquez avec un technicien de service qualifié. Le fait de forcer ou de tenter de réparer la poignée pourrait causer un incendie ou une explosion. N’utilisez pas cet appareil s’il a été plongé dans I’eau, même partiellement. Faites inspecter I’appareil par un technicien qualifié et remplacez toute partie du système de contrôle et toute commande qui ont été plongées dans I’eau.
1. ARRÊTEZ ! Lisez les instructions de sécurité sur la portion supérieure.
2. Coupez l’alimentation électrique de l’appareil. 3. Réglez le thermostat à la temperature la plus basse. 4. 5. Ouvrir les portes avant. 6. Mettez la soupape d’ arrêt de gaz à << OFF >>. La valve est en 13.
position << OFF >> lorsque la poignée se trouve à angle droit du tuyau de gaz. 7. Attendez cinq (5) minutes afin que le gaz se dissipe. Si vous croyez sentir une odeur de gaz, ARRÊTEZ ! Reportez-vous aux instructions B ci-dessus, sur cette étiquette. S’il n’y a pas d’odeur de gaz, passez à la prochaine étape. 8. Remettez lentement la soupape d’arrêt de gaz en position << ON >>. La poignée sera parallèle au tuyau de gaz. 9. Replacez le couvercle avant. 10. Set thermostats mécaniques sur les réglages désirés.
11. Rétablissez l’alimentation électrique à l’appareil. 12. Réglez le thermostat de fonctionnement désirée à l'aide paramètres affichage chaudière.
communiquez avec votre technicien de service ou le fournisseur de gaz. Entrée de Gaz Manule se Valve de Gaz Trouvant en Position “OFF” Si l’appareil ne fonctionne pas, suivez les directives relatives à la fermeture de l’alimentation en gaz et
FERMENTURE DE L’ALIMENTATION EN GAZ INSTRUCTIONS DE MISE EN MARCHE
1. Coupez toute alimentation électrique à l’appareil si celui-ci doit faire l’objet d’un entretien .
2. 3. Ouvrir les portes avant.
Réglez le thermostat au réglage le plus bas.
4. Mettez la soupape d’arrêt de gaz à << OFF >>. La valve est en position << OFF >> lorsque la poignée se trouve à angle droit du tuyau de gaz. 5. Fermez les portes avant. H2363600-
for gas, 1. Turn off all electric power to the appliance if service is to be performed.
3. 4. Turn off manual gas valve. Valve is off when valve handle is at a right angle to gas pipe. 5. Open front doors.
TO TURN OFF GAS TO APPLIANCE POUR VOTRE SÉCURITÉ, LISEZ AVANT DE METTRE EN MARCHE
Gas inlet Manual Gas Valve Shown in the “OFF” Position Page 3
2. Coupez l’alimentation électrique de l’appareil. 3. Réglez le thermostat à la temperature la plus basse. 4. Cet appareil est équipé d'un dispositif d'allumage qui s'allume automatiquement le pilote. N'essayez pas de lumière le pilote à la main. 5. Ouvrir les portes avant. 6. Mettez la soupape d’ arrêt de gaz à << OFF >>. La valve est en position << OFF >> lorsque la poignée se trouve à angle droit du tuyau de gaz. 7. Attendez cinq (5) minutes afin que le gaz se dissipe. Si vous croyez sentir une odeur de gaz, ARRÊTEZ ! Reportez-vous aux instructions B ci-dessus, sur cette étiquette. S’il n’y a pas d’odeur de gaz, passez à la prochaine étape. 8. Remettez lentement la soupape d’arrêt de gaz en position << ON >>. La poignée sera parallèle au tuyau de gaz. 9. Replacez le couvercle avant. 10. Set thermostats mécaniques sur les réglages désirés.
11. Rétablissez l’alimentation électrique à l’appareil. 13.
SHUTTING DOWN THE MAGNATECH
It may sometimes be necessary to shut down the MagnaTech. Here are the steps required to do this: 1. Switch off the main electrical disconnect switch.
2. Open the front access doors and close the main manual gas valve. 3. If freezing is anticipated, drain the MagnaTech. (Also be sure to protect the piping in the building from freezing.) The steps listed above may require qualified service personnel.
RESTARTING THE MAGNATECH
It may be necessary to restart the MagnaTech – for example, after a power interruption. Here are the steps required to do this: 1 Reset any errors using the user interface. See the section on “About Lockouts, Holds, and Alerts.” 2 Turn up the thermostat to call for heat.
3. In approximately 2 seconds, the blower will operate. Ignition should occur after 35-40 seconds. It may take as long as 2-1/2 minutes.
4. If ignition does not occur, wait 5 minutes and then repeat steps 1 through 3.
5. If, after three attempts, the unit still does not light, shut down the boiler and call your service technician.
The MagnaTech will not operate during an electrical power outage. If there is an extended power outage with danger of freezing, then the MagnaTech (and all other water systems) should be completely drained. Before draining the unit, turn off the gas and turn off the main power switch. When you replace the unit in service, refer to the “Installation and Operation Manual” for instructions on filling and purging.
Power Switch Touch Screen Display
Each MagnaTech has one burner and one burner controller. A complete lead lag system can include up to eight MagnaTechs. After the system starts, the Touch Screen will automatically present the Home screen:
The icon for each burner controller will appear in one of four colors: Blue Red Gray Gray and crossed out Yellow Normal operation Lockout Standby mode (Burner switch off) Communication problem Hold state. This could be Anti short cycle, fan speed transitions, etc.
To check the operation of an individual burner, press the large icon on the Home screen. The system will present a Status Summary screen for that burner:
ABOUT LOCKOUTS, HOLDS, AND ALERTS
The system responds to three kinds of trouble indications: • A”lockout” is caused by a serious problem that might involve a safety issue. Once the controller enters a lockout, the burners will shut down, and will not be allowed to run again until the cause of the problem is corrected, and you reset the control system.
• The system may enter a “hold” for a period of time before locking out. This allows the controller to see if the error becomes resolved prior to the hard lockout.
• An “alert” indicates that some feature of the control system’s operation was not correct, delayed, or waiting for a response. This does not necessarily indicate a problem.
If a problem occurs while the system is starting up, the system will declare a Hold or Lockout:
If a problem occurs while the system is running, a Bell symbol will appear in the upper left corner of the screen, and the system will present a note across the bottom of the screen. If you tap the bar which includes the message, the system will present more information about the problem. Press the OK button to indicate that you have seen the Lockout or Alert.
If an audible alarm on the display is active, tap the Bell symbol to stop it.
Each error message includes a number. For a more detailed description of each message, see the “Installation and Operation Manual.”
Keep the area around the MagnaTech clear and free from combustible materials, gasoline and other flammable vapors and liquids. Clean the jacket surfaces with a damp cloth and mild soap. Do not use flammable cleaning materials. Keep the vent terminal free of obstructions. Do not pile snow against the vent terminal.
You should visually inspect the vent pipe once a year. Should any corrosion or leaks exist, have the affected parts replaced.
Once each year a qualified service agency should conduct a detailed inspection of all flue product carrying areas of the boiler and vent system. Follow the service instructions in the “Installation and Operating Instructions Manual” for the MagnaTech.
Caution Do not use this boiler if any part has been under water. Immediately call a qualified service technician to inspect the boiler. Any part of the control system and any gas control which has been under water must be replaced.
WARNING If the unit overheats or the gas supply fails to shut off, do not turn off or disconnect the electrical supply to the pump. Instead, shut off the gas supply at a location external to the MagnaTech.
En cas de surchauffe ou si l’admission de gaz ne peut être coupée, ne pas couper ni débrancher l’alimentation électrique de la pompe. Fermer plutôt le robinet d’admission de gaz à l’extérieur de l’appareil.
Contact your installing contractor, gas utility, Bradford White dealer, or check www.
BradfordWhite.com for the nearest authorized representative in your area.
HLW 200 Lafayette St.
Middleville, MI 49333 Warranty: (800) 531-2111
Litho in U.S.A. © Bradford White 1507 Document 1294A-BW
Bradford White BMGH1600 Brute MagnaTech-HTD Series Hydronic Boilers (BMGH) User Manual
Bradford White BMGV1600 Brute MagnaTech Series Hydronic Volume Water Heaters (BMGV) User Manual
Raypak 504-2004 Types H MVB Information Manual
Bradford White BMGV1600 Brute MagnaTech-HTD Series Hydronic Volume Water Heaters (BMGV) Spec Sheet
Bradford White BMGH1600 Brute MagnaTech Series Hydronic Boilers (BMGH) Spec Sheet
Bradford White BMGH1600 Brute MagnaTech Series Hydronic Boilers (BMGH) Manual
User`s Manual for
Bradford White BNTV1700 User`s manual
Bradford White BMGV1600 Brute MagnaTech Series Hydronic Volume Water Heaters (BMGV) Spec Sheet
Bradford White BMGV1600 Brute MagnaTech-HTD Series Hydronic Volume Water Heaters (BMGV) Manual
1260A-BW - Bradford White
1345-BW - Bradford White
Bradford White BNTH-285 Brute Series Hydronic Boilers (BNTH) 285-850 User Manual
Pipeliner II Model 609A Orbital Weld Head
User`s Manual for Modulating Boiler Model NTH Water
NEOTHERM® LC
product range - Automated Arc Systems
Use with • Pipeliner Orbital FCAW Weld Head
Tubesheet Heads 424-425-430 W-87