Source: http://readgur.com/doc/196866/aero-residence---martin-%C4%BEadove%C5%88
Timestamp: 2017-01-20 04:00:02+00:00
Document Index: 12688302

Matched Legal Cases: ['čl. 5', 'čl. 2', 'čl. 2', 'čl.10', 'čl. 3', 'čl. 5', 'čl.6', 'čl.8', 'čl.7', 'čl. 4', 'čl.5', 'čl. 5']

aero residence , Martin Ľadoveň
BYTOV&Yacute; DOM - AERO RESIDENCE, MARTIN – ĽADOVEŇ
PROJEKTOV&Aacute; DOKUMENT&Aacute;CIA PRIKLADAN&Aacute; K ŽIADOSTI O VYDANIE &Uacute;ZEMN&Eacute;HO ROZHODNUTIA
OBSAH DOKUMENT&Aacute;CIE
1. IDENTIFIKAČN&Eacute; &Uacute;DAJE STAVBY A INVESTORA
2. Z&Aacute;KLADN&Eacute; &Uacute;DAJE O STAVBE
2.1 STRUČN&Yacute; OPIS STAVBY Z HĽADISKA &Uacute;ČELU A FUNKCIE, POŽIADAVKY NA URBANISTICK&Eacute;,
ARCHITEKTONICK&Eacute; A V&Yacute;TVARN&Eacute; RIEŠENIE S UVEDEN&Iacute;M NAVRHOVAN&Yacute;CH KAPAC&Iacute;T,
2.2 &Uacute;DAJE O STAVBE,
2.3 CHARAKTERISTIKA &Uacute;ZEMIA, DOTKNUT&Yacute;CH OCHRANN&Yacute;CH P&Aacute;SIEM, CHR&Aacute;NEN&Yacute;CH ČAST&Iacute; &Uacute;ZEMIA,
KULT&Uacute;RNYCH PAMIATOK, POŽIADAVKY NA DEMOL&Aacute;CIE, V&Yacute;RUB NARASTENEJ ZELENE (Z&Aacute;BER
POĽNOHOSPOD&Aacute;RSKEJ P&Ocirc;DY ALEBO LESN&Yacute;CH POZEMKOV),
2.4 VPLYV STAVBY, PREV&Aacute;DZKY ALEBO V&Yacute;ROBY NA ŽIVOTN&Eacute; PROSTREDIE, PREDPOKLADAN&Yacute;
SP&Ocirc;SOB OBMEDZENIA ALEBO ODSTR&Aacute;NENIA PR&Iacute;PADN&Yacute;CH NEGAT&Iacute;VNYCH VPLYVOV,
2.5 ODOLNOSŤ A ZABEZPEČENIE Z HĽADISKA POŽIARNEJ OCHRANY A CIVILNEJ OCHRANY.
3. OD&Ocirc;VODNENIE STAVBY A JEJ UMIESTNENIE
4. PODMIEŇUJ&Uacute;CE PREDPOKLADY
4.1 PRELOŽKY INŽINIERSKYCH SIET&Iacute;, OBMEDZENIE EXISTUJ&Uacute;CICH PREV&Aacute;DZOK A IN&Eacute; OPATRENIA
POTREBN&Eacute; NA UVOĽNENIE NAVRHOVAN&Eacute;HO MIESTA STAVBY A JEJ USKUTOČŇOVANIE,
4.2 S&Uacute;VISIACE INVEST&Iacute;CIE A PREDPOKLADY ALEBO N&Aacute;ROKY NA ICH ZABEZPEČENIE,
4.3 PRIPOJENIE NA EXISTUJ&Uacute;CE TECHNICK&Eacute; VYBAVENIE &Uacute;ZEMIA, BILANCIE KAPACITN&Yacute;CH N&Aacute;ROKOV
A MOŽNOSTI,
4.4 VZŤAHY K EXISTUJ&Uacute;CEMU VEREJN&Eacute;MU A OBČIANSKEMU VYBAVENIU &Uacute;ZEMIA, VR&Aacute;TANE
VEREJNEJ DOPRAVY,
B. V&Yacute;KRESY
1. Situ&aacute;cia
2. P&ocirc;dorys 1.P.P. , n&aacute;vrh
3. P&ocirc;dorys 1.N.P. , n&aacute;vrh
4. P&ocirc;dorys 2.N.P., n&aacute;vrh
5. P&ocirc;dorys 3.N.P. , n&aacute;vrh
6. Rez A-A
7. Rez B-B
8. Pohľady, n&aacute;vrh
9. P&ocirc;dorys 1.P.P., stav
10. P&ocirc;dorys 1.N.P., stav
11. Rez B-B, stav
12. Pohľady, stav
13. Vizualiz&aacute;cie objektu
2. fotok&oacute;pia listu vlastn&iacute;ctva
3. fotok&oacute;pia sn&iacute;mku z katastr&aacute;lnej mapy
N&aacute;zov stavby:
Bytov&yacute; dom AERO RESIDENCE
ul. Gogoľova 3, 036 01 Martin - Ľadoveň
Nadstavba a stavebn&eacute; &uacute;pravy
PeP plus, s.r.o., Gogoľova 3, 036 01 Martin
k.&uacute;. Martin, parc. č. C KN 1930/ 37, 46, 47, 50, s&uacute;p. č. 4831
Dokument&aacute;cia pre &uacute;zemn&eacute; rozhodnutie
aplus.sk, s.r.o., Medvedzie S&iacute;dlisko 153/36, 027 44 Tvrdoš&iacute;n
web.: www.aplus.sk, email: [email&#160;protected] fax: 043/370 9028
konateľ: Ing. arch. Martin Pavl&iacute;k, mob.: 0903 768 067
IČO: 46 820 205, DIČ: 202 360 6277
Ing. arch. Martin Pavl&iacute;k,
autorizovan&yacute; architekt SKA, reg. č. 1721 AA
PREHĽAD V&Yacute;CHODISKOV&Yacute;CH PODKLADOV
Podklady na z&aacute;klade ktor&yacute;ch bola spracovan&aacute; dokument&aacute;cia:
• Sn&iacute;mka s katastr&aacute;lnej mapy
• Konzult&aacute;cie s investorom.
• Autorsk&aacute; vizu&aacute;lna obhliadka a zameranie objektu.
• Hmotovo - objemov&aacute; št&uacute;dia (december 2013)
• Fotodokument&aacute;cia
• Konzult&aacute;cie s dotknut&yacute;mi org&aacute;nmi št&aacute;tnej spr&aacute;vy.
• platn&eacute; pr&iacute;slušn&eacute; STN
• stanovisko UHA mesta Martin, č. &Uacute;HAM/1185/2012/OL-115 zo dňa 15.11.2012
PREHĽAD &Uacute;ČASTN&Iacute;KOV KONANIA A DOTKNUT&Yacute;CH ORG&Aacute;NOV
• PeP plus, s.r.o., Gogoľova 3, 036 01 Martin
• Interlink, s.r.o., Gogoľova 3, 036 01 Martin
• Mesto Martin, S.H. Vajansk&eacute;ho 1, 036 49 Martin
• Ostatn&yacute;m &uacute;častn&iacute;kom konania verejnou vyhl&aacute;škou
Dotknut&yacute;m org&aacute;nom :
• Mestsk&yacute; &uacute;rad Martin, odbory:
&Uacute;tvar hl. architekta, &Uacute;tvar hl. inžiniera, od. komun&aacute;lnych služieb, od. majetku a služieb
• Region&aacute;lny &uacute;rad verejn&eacute;ho zdravotn&iacute;ctva Martin
• Okresn&eacute; riaditeľstvo hasičsk&eacute;ho a z&aacute;chr. zboru v Martine
• Okresn&yacute; &uacute;rad Martin, odbory:
Starostlivosti o životn&eacute; prostredie, cestnej dopravy a pozemn&yacute;ch komunik&aacute;ci&iacute;, kr&iacute;zov&eacute;ho riadenia
• Stredoslovensk&aacute; energetika, a.s. Žilina
• SPP - distrib&uacute;cia , a. s. Žilina
• Turčianska vod&aacute;rensk&aacute; spoločnosť, a.s. Martin
• Slovak Telecom, a.s. Bratislava, pobočka Vr&uacute;tky
• Krajsk&yacute; pamiatkov&yacute; &uacute;rad Žilina, pracovisko Martin
• Orange Slovensko, a.s. Bratislava
2.1.1. Z&aacute;kladn&eacute; &uacute;daje charakterizuj&uacute;ce &uacute;zemie a stavieb v ňom
Riešen&eacute; &uacute;zemie je v zmysle platn&eacute;ho &Uacute;zemn&eacute;ho pl&aacute;nu s&iacute;deln&eacute;ho &uacute;tvaru Martin a jeho zmien a doplnkov,
definovan&eacute; ako existuj&uacute;ca plocha b&yacute;vania v bytov&yacute;ch domoch – HBV, spadaj&uacute;ca do regulačn&eacute;ho okrsku č.15,
s regulačn&yacute;m označen&iacute;m HA2.
Navrhovan&eacute; objekty s&uacute; rozdelen&eacute; do samostatn&yacute;ch stavebn&yacute;ch objektov S0-01 až SO-07. Celkov&aacute; v&yacute;mera
riešen&eacute;ho &uacute;zemia je 1196 m2 (vid. Grafick&aacute; časť). Z toho zastavan&eacute; nasledovne:
Bytov&yacute; dom 355 m2, pešie komunik&aacute;cie a spevnen&eacute; plochy 86m2, spevnen&aacute; plocha parkoviska 261 m2 a zeleň
494 m .
Bytov&yacute; dom je nadstavbou a pr&iacute;stavbou existuj&uacute;ceho jednopodlažn&eacute;ho objektu, čiastočne podpivničen&eacute;ho.
Na parcele investora je novovybudovan&aacute; spevnen&aacute; plocha parkoviska s vybudovanou dažďovou kanaliz&aacute;ciou a
ORL, osvetlenia a nov&aacute; pr&iacute;pojka teplovodu. Ostatn&eacute; siete s&uacute; existuj&uacute;ce ponechan&eacute; bez zmeny.
.1.2. Členenie stavby
Objektov&aacute; skladba:
SO 01 Bytov&yacute; dom
SO 02 Spevnen&eacute; plochy – chodn&iacute;ky
SO 03 Spevnen&eacute; plochy - parkovisko
SO 04 Dažďov&aacute; kanaliz&aacute;cia a ORL
SO 05 Sadovn&iacute;cke a parkov&eacute; &uacute;pravy
SO 06 Vonkajšie osvetlenie + d&aacute;tov&eacute; rozvody
SO 07 Pr&iacute;pojka teplovodu
2.1.3. Popis existuj&uacute;ceho stavu
Objekt sa nach&aacute;dza v intravil&aacute;ne mesta Martin na s&iacute;dlisku Ľadoveň, na ul. Gogoľova na parcel&aacute;ch
1930/37, 46, 47 a 50 veden&yacute;ch ako zastavan&aacute; plochy a n&aacute;dvoria.. Ide o stavbu čiastočne podpivničen&uacute; s jedn&yacute;m
nadzemn&yacute;m podlaž&iacute;m a plochou strechou. Objekt bol p&ocirc;vodne kolaudovan&yacute; ako matersk&aacute; škola, ktor&aacute; pozost&aacute;vala
z dvoch čast&iacute; a to, z pavil&oacute;nu materskej šk&ocirc;lky (dnešn&aacute; dvojpodlažn&aacute; administrat&iacute;vna budova spoločnosti
Interlink, s.r.o.), jednopodlažn&eacute;ho hospod&aacute;rskeho pavil&oacute;nu a dvora s detsk&yacute;m ihriskom, ktor&eacute; s&uacute; vo vlastn&iacute;ctve
investora. Kolaudačn&eacute; rozhodnutie nadobudlo &uacute;činnosť 21.8.1985, pod č. &Uacute;PA 23/85/Ing. Ka, vydan&yacute; odborom
v&yacute;stavby v Martine pri MsNV. Je to montovan&aacute; stavba z keramoblokov o skladobnej hr&uacute;bke 320 mm.
V objekte sa nach&aacute;dzaj&uacute; prev&aacute;dzky obchodov, reštaur&aacute;cie a herňa, ale v s&uacute;časnosti je využ&iacute;van&yacute; ako
prev&aacute;dzka služieb. Podzemn&eacute; podlažie obsahuje 5 miestnost&iacute;, ktor&eacute; sl&uacute;žia ako sklady reštaur&aacute;cie a schodisko.
Osadenie do ter&eacute;nu je v priemernej hĺbke nad 2 m so zvislou izol&aacute;ciou, murivo monolitick&eacute;, stropy s rovn&yacute;m
podhľadom, schody s povrchom PVC. Podlahy z cementov&eacute;ho poteru. Podlažie m&aacute; jednoduch&eacute;, oceľov&eacute; okn&aacute; do
anglick&yacute;ch dvorcov, dvere s&uacute; hladk&eacute; dreven&eacute;, rozvod elektriny sveteln&yacute;, 1 x bidet, rozvod studenej vody, ost.
inžinierske rozvody nie s&uacute;. Nadzemn&eacute; podlažie pozost&aacute;va z chodby, 2 x WC, 2 prev&aacute;dzkov&yacute;ch miestnosti ,
v minulosti prenaj&iacute;man&yacute;ch ako predajne, alebo služby, kancel&aacute;rie, kuchynky a samostatnej sprchy, 4 x miestnosť
reštaur&aacute;cie, 4 x sklad reštaur&aacute;cie, 2 x miestnosť herne, mal&yacute; n&aacute;kladn&yacute; v&yacute;ťah do nosnosti 100 kg. Z&aacute;klady
murovan&eacute; so zvislou izol&aacute;ciou. Zvisl&aacute; nosn&aacute; konštrukcia v skladobnej hr&uacute;bke do 40 cm, stropy rovn&eacute; vybudovan&eacute;
po r. 1960. Strecha ploch&aacute;, krytina asfaltov&aacute;. Klampiarske konštrukcie z pozinkovan&eacute;ho plechu žľaby a zvody.
Fas&aacute;dne omietky brizolit. V prev&aacute;dzkov&yacute;ch miestnostiach dvere hladk&eacute; pln&eacute;, okn&aacute; zdvojen&eacute; dreven&eacute;, podlahy
ostatn&yacute;ch miestnost&iacute; PVC v prevažnej časti dlaždice. Vykurovanie je &uacute;stredn&eacute; s liatinov&yacute;mi radi&aacute;tormi.
Elektroinštal&aacute;cia sveteln&aacute;, motorick&aacute; s poist. automatmi, rozvod vody studenej a teplej. V objekte nie je rozvod
plynu, kanaliz&aacute;cia je do verejnej siete. Objekt je napojen&yacute; na telef&oacute;nny rozvod.
Objekt je pr&iacute;stupn&yacute; cez existuj&uacute;ci dvor od ulice Gogoľova a od bytov&eacute;ho domu 3945/1 na ul. Jozefa
Kr&oacute;nera. Vo dvore s&uacute; inštalovan&eacute; lavičky a preliezky, b&yacute;val&eacute;ho detsk&eacute;ho ihriska a pr&iacute;strešok, ktor&yacute; sl&uacute;ži pre
letn&eacute; sedenie reštaur&aacute;cie. Je tu početn&aacute; vzrastl&aacute; zeleň, ktor&aacute; je vhodn&aacute; na ponechanie. Pozemok objektu je
obohnan&yacute; kombinovan&yacute;m oploten&iacute;m, z oceľov&yacute;ch r&aacute;mov s dr&ocirc;tenou v&yacute;plňou, alebo dreven&yacute;m latovan&iacute;m. R&aacute;my s&uacute;
osaden&eacute; do bet&oacute;nov&eacute;ho z&aacute;kladu, ktor&yacute; vystupuje nad ter&eacute;n.
4 |Strana
2.1.4. Stručn&yacute; opis stavby z hľadiska &uacute;čelu a funkcie
Navrhovan&yacute; objekt rieši v&yacute;stavbu bytov&eacute;ho domu s tromi nadzemn&yacute;mi a jedn&yacute;m podzemn&yacute;m poschod&iacute;m a
s 5-timi bytov&yacute;mi jednotkami (1 byt/ 4 obyv.) s počtom 20 obyvateľov. Hlavn&yacute; vstup do objektu je zo spoločn&eacute;ho
dvora na z&aacute;padnej strane objektu a vedľajš&iacute; je na v&yacute;chodnej strane objektu a severnej strane ako servisnoobslužn&yacute; vstup do technickej miestnosti. K južnej fas&aacute;de objektu je pristavan&eacute; hlavn&eacute; schodisko objektu. Objekt
je napojen&yacute; na existuj&uacute;ce siete (vodovod, kanaliz&aacute;cia, strednotlak&yacute; plyn a vedenia silnopr&uacute;du i slabopr&uacute;du.
2.1.5. Urbanistick&eacute; a dopravn&eacute; riešenie
Riešen&eacute; &uacute;zemie je včlenen&eacute; do existuj&uacute;cej štrukt&uacute;ry s&iacute;dliska, kde okolit&uacute; v&yacute;stavbu tvoria prevažne
bytov&eacute; domy do priemernej v&yacute;šky 4 NP. Z južnej strany je k objektu pričlenen&aacute; 2 podlažn&aacute; administrat&iacute;vna
budova, ktor&aacute; v minulosti tvorila s&uacute;časť objektu materskej šk&ocirc;lky. Navrhovan&yacute; objekt a objekt administrat&iacute;vnej
budovy je moment&aacute;lne vz&aacute;jomne prepojen&yacute; presklenou prepojovacou chodbou. T&aacute;to chodba je v n&aacute;vrhu zrušen&aacute;.
Objekty s&uacute; vz&aacute;jomne vzdialen&eacute; 8,1m. V&yacute;chodne od objektu je existuj&uacute;ci 4 NP bytov&yacute; dom vo vzdialenosti 9,6m.
Objekt je dopravne napojen&yacute; z existuj&uacute;cej miestnej komunik&aacute;cie – ul. Gogoľova, peš&iacute; pr&iacute;stup je možn&yacute; aj
od ul. Jozefa Kr&oacute;nera. Parkovanie k objektu bude zabezpečen&aacute; na novovybudovan&yacute;ch parkovac&iacute;ch ploch&aacute;ch,
vystavan&yacute;ch na pozemku investora. Bude tu spolu 12 otvoren&yacute;ch parkovac&iacute;ch miest z toho bude jedno miesto
pre telesne postihnut&eacute;ho. T&aacute;to plocha bude odvodnen&aacute; novou dažďovou kanaliz&aacute;ciou vy&uacute;sten&uacute; cez ORL do
existuj&uacute;cej dažďovej kanaliz&aacute;cii na ul. Gogoľova. Okolo pozemku je existuj&uacute;ci plot, ktor&yacute; ponech&aacute;vame, z d&ocirc;vodu
v&auml;čšieho s&uacute;kromia bud&uacute;cich vlastn&iacute;kov bytov. Pri hlavnom dopravnom vstupe na pozemok je navrhnut&eacute; stojisko
pre kontajner TKO, verejn&eacute; osvetlenie s kamerov&yacute;m syst&eacute;mom a automatickou br&aacute;nou. Ostatn&eacute; existuj&uacute;ce vstupy
na pozemok cez br&aacute;ničky pre peš&iacute;ch ponech&aacute;vame v p&ocirc;vodnej polohe, t.j. jedna zo severu od verejn&eacute;ho chodn&iacute;ka
a jedna z v&yacute;chodu (viac viď. V&yacute;kres 1 Situ&aacute;cia).
2.1.6. Architektonick&eacute; riešenie a dispozičn&eacute; riešenie
Architekt&uacute;ra navrhovan&eacute;ho objektu reflektuje v&yacute;šku okolitej z&aacute;stavby, statick&eacute; možnosti existuj&uacute;cej
konštrukcie objektu, orient&aacute;ciu k svetov&yacute;m stran&aacute;m a požiadavky investora - hlavne požiadavku na maxim&aacute;lne
využitie existuj&uacute;cich konštrukci&iacute; objektu, bez zbytočn&eacute;ho predražovania v&yacute;stavby, zvolen&iacute;m nevhodn&yacute;ch
a komplikovan&yacute;ch materi&aacute;lov, konštrukcii a tvaroslov&iacute;. Z toho d&ocirc;vodu bola zvolen&aacute; navrhovan&aacute; kombin&aacute;cia
tvaroslovia, v&yacute;šky, konštrukcii a celkov&eacute;ho vzhľadu navrhovan&eacute;ho objektu,
Riešen&yacute; objekt bude mať 3 nadzemn&eacute; podlažia a 1 podzemn&eacute; podlažie, v ktorom bude umiestnen&eacute; spoločn&eacute;
domov&eacute; vybavenie. Objekt m&aacute; približne štvorcov&yacute; p&ocirc;dorys.
Na 1.N.P bud&uacute; 2 bytov&eacute; jednotky s dvoj a troj izbov&yacute;mi bytmi a ostatn&eacute; spoločn&eacute; domov&eacute; vybavenie
a v&yacute;menn&iacute;kov&aacute; stanica. Na 2.N.P. bud&uacute; 2 bytov&eacute; jednotky s troma izbami. Na 3.N.P. bude jedna bytov&aacute; jednotka:
trojizbov&yacute; byt.
Dispozičn&eacute; riešenie jednotliv&yacute;ch bytov je v zmysle platn&yacute;ch noriem a legislat&iacute;vy, avšak snahou bolo
vytvoriť priestory v bytoch, ktor&eacute; s&uacute; nadštandardom, ako napr. samostatn&eacute; šatn&iacute;ky, alebo sklady v jednotliv&yacute;ch
bytoch. Každ&yacute; byt je vybaven&yacute; minim&aacute;lne jedn&yacute;m balk&oacute;nom (terasou). Byty na pr&iacute;zem&iacute; (1.N.P.) s&uacute; nadštandardn&eacute;
svetlou v&yacute;škou priestorou, ktor&aacute; je 3,0m z d&ocirc;vodu zachovania p&ocirc;vodnej konštrukcie, ale aj t&yacute;m, že maj&uacute; vlastn&eacute;
Nadštandardom bytov&eacute;ho domu je spoločn&yacute; dvor, ktor&yacute; je od okolit&eacute;ho priestoru chr&aacute;nen&yacute; existuj&uacute;cim
oploten&iacute;m a bohatou existuj&uacute;cou vzrastlou zeleňou.
Pre bytov&yacute; dom je navrhovan&yacute;ch 12 otvoren&yacute;ch parkovac&iacute;ch st&aacute;t&iacute; z čoho 1 st&aacute;tie bude pre telesne
postihnut&eacute;ho. Spoločn&yacute; dvor so zeleňou m&aacute; v&yacute;meru cca 840 m2. Pri hlavnej vstupnej br&aacute;ne zo strany ulice
Gogoľova, bude vybudovan&yacute; kryt&yacute; pr&iacute;strešok pre kontajnery TKO o v&yacute;mere 4,5 m2.
Navrhovanou v&yacute;stavbou vznikne pri navrhnutom riešen&iacute; dispozičn&yacute; priestor o t&yacute;chto v&yacute;mer&aacute;ch:
zastavan&aacute; plocha objektu
spevnen&eacute; plochy parkoviska - n&aacute;vrh
spevnen&eacute; pešie plochy - stav
spevnen&eacute; pešie plochy - n&aacute;vrh
celkov&aacute; &uacute;žitkov&aacute; plocha
plocha::
776,5 m2
Celkov&aacute; obytn&aacute; plocha:
Bližšie v&yacute;mery jednotliv&yacute;ch bytov – viď v&yacute;kresov&aacute; časť
2.2.1. Stavebno - konštrukčn&eacute;,
konštrukčn&eacute;, materi&aacute;lov&eacute; riešenie
Existuj&uacute;ci objekt je postaven&yacute; ako keramoblokov&aacute; konštrukcia o skladobnej hr&uacute;bke 320 mm. Zo severnej
a južnej strany plnostenn&aacute; konštrukcia s osaden&yacute;mi okenn&yacute;mi a dvern&yacute;mi otvormi, Z v&yacute;chodnej a z&aacute;padnej strany
prevažne stĺpov&aacute; konštrukcia vyplnen&aacute; okenn&yacute;mi otvormi o rozmeroch 1450 x 1750 mm, s v&yacute;škou parapetu 1000
mm. Konštrukcia p&ocirc;vodn&eacute;ho objektu bude zachovan&aacute;, bude zateplen&aacute; syst&eacute;mom Nobasil o hr. 200mm a omietan&aacute;
štrukt&uacute;rovanou omietkou.
Nadstavan&aacute; časť objektu je konštrukčne navrhnut&aacute; ako sendvičov&aacute; r&aacute;mov&aacute; konštrukcia. Zvisl&yacute; aj
vodorovn&yacute; nosn&yacute; syst&eacute;m bude tvoriť oceľov&aacute; r&aacute;mov&aacute; konštrukcia profilu H o v&yacute;ške profilu 240mm, čiastočne
ukotven&aacute; do nov&yacute;ch z&aacute;kladov mimo existuj&uacute;ci objekt a čiastočne uložen&aacute; na existuj&uacute;cu konštrukciu objektu.
Obvodov&yacute; nosn&yacute; pl&aacute;šť jednotliv&yacute;ch buniek (bytov&yacute;ch jednotiek) bude tvoren&yacute; z dreven&yacute;ch lepen&yacute;ch
nosn&iacute;kov rozmerov 300x80 mm, ktor&eacute; bud&uacute; zviazan&eacute; veľkoplošn&yacute;mi OSB doskami a zateplen&eacute; izol&aacute;ciami nobasil +
paroz&aacute;brany. Nosn&eacute; a stužuj&uacute;ce steny pristavan&eacute;ho schodiska bud&uacute; z p&oacute;rbet&oacute;nov&yacute;ch tv&aacute;rnic hr. 250mm
zateplen&yacute;ch z dos&aacute;k z kamennej vlny – syst&eacute;m Nobasil, hr. 200mm.
Vn&uacute;torn&eacute; deliace steny bud&uacute; sadrokart&oacute;nov&eacute;. Strecha je riešen&aacute; ako ploch&aacute; jednopl&aacute;šťov&aacute;, čiastočne
prekryt&aacute; konštrukciou ter&aacute;s. Fas&aacute;da je navrhnut&aacute; ako štrukt&uacute;rovan&aacute; omietan&aacute;. Farebnosť bude upresnen&aacute; na
z&aacute;klade vyvzorkovania. Podlahy bud&uacute; zateplen&eacute;, zvukovoizolačn&eacute;, podľa charakteru miestnosti keramick&eacute; dlažby,
pl&aacute;vaj&uacute;ce dreven&eacute; alt. lamin&aacute;tov&eacute; podlahy.
Okn&aacute; s&uacute; navrhovan&eacute; dreven&eacute; vyr&aacute;ban&eacute; na zak&aacute;zku. Všetky okn&aacute; v pr&iacute;zem&iacute; bud&uacute; mať bezpečnostn&eacute; f&oacute;lie
connex. Vstupne dvere do objektu bud&uacute; hlin&iacute;kov&eacute;. Vn&uacute;torn&eacute; vstupn&eacute; dvere do bytov bud&uacute; protipožiarne.
Vn&uacute;torn&eacute; dvere do jednotliv&yacute;ch miestnost&iacute; bud&uacute; dreven&eacute; osaden&eacute; do dreven&yacute;ch z&aacute;rubn&iacute;.
Podrobnejšie stavebno-technick&eacute; riešenie bude upresnen&eacute; v ďalšom stupni projektovej dokument&aacute;cie.
2.2.2. Pr&iacute;stup pre telesne a zmyslovo postihnut&yacute;ch občanov
Charakter stavby vyžaduje splnenie vyhl&aacute;šky č. 532/2002 Z.z. o všeobecn&yacute;ch technick&yacute;ch požiadavk&aacute;ch,
zabezpečuj&uacute;cich už&iacute;vanie stavieb osobami s obmedzenou schopnosťou pohybu a orient&aacute;cie.
Riešenie bytov nevylučuje &uacute;pravu pre ZTP. Vstup do objektu je riešen&yacute; ako bezbari&eacute;rov&yacute; pr&iacute;stup. Byty
na 1.NP. je možn&eacute; riešiť ako bezbari&eacute;rov&eacute;. Všetky n&aacute;stupn&eacute; miesta, pl&aacute;ta a chodby na 1.N.P nie s&uacute; menšie ako
1,5x1,5m. Sklony r&aacute;mp, dimenzie prahov s&uacute; navrhnut&eacute; podľa vyhl&aacute;šky č. 532/2002 Z.z. Požiadavky vyhl&aacute;šky bud&uacute;
splnen&eacute;, podrobnosti a n&aacute;ležitosti bud&uacute; riešen&eacute; v ďalšom stupni PD.
2.2.3. Dopravn&eacute; riešenie
Dopravne je are&aacute;l napojen&yacute; na cestn&uacute; sieť pr&iacute;jazdovou komunik&aacute;ciou, ktor&aacute; je napojen&aacute; na cestu ul.
Gogoľovej cez vjazd, ktor&eacute;ho dopravn&yacute; režim bude usmernen&yacute; dopravn&yacute;m značen&iacute;m.
PRITAŽENIE KOMUNIKAČNEJ SIETE
Uvažovan&aacute; v&yacute;stavba minim&aacute;lnym sp&ocirc;sobom zaťaž&iacute; existuj&uacute;ce komunik&aacute;cie v &uacute;zem&iacute;. Hlavn&yacute; dopravn&yacute;
vjazd do &uacute;zemia je z ul. Gogoľov&aacute;, kde frekvencia automobilovej dopravy je minim&aacute;lna až mierne frekventovan&aacute;
v obdob&iacute; rannej a poobednajšej špičky.
Podkladom pre navrhnut&eacute; riešenie boli odhadovan&eacute;, požadovan&eacute; kapacity parkovac&iacute;ch zariaden&iacute;
odv&iacute;jaj&uacute;ce sa od počtu obyvateľov bytov&eacute;ho domu..
V riešenom &uacute;zem&iacute; je všetka parkovacia kapacita umiestnen&aacute; na povrchu pozemku investora o kapacite
12 PS, kde jedno parkovacie miesto je určen&eacute; pre telesne postihnut&eacute;ho.
V&Yacute;POČET STATICKEJ DOPRAVY
V&yacute;počet je vyhotoven&yacute; podľa STN 73 6110/Z1.
koeficient mestskej polohy riešen&eacute;ho &uacute;zemia
Kmp– ostatn&eacute; &uacute;zemie
Kd s&uacute;činiteľ vplyvu deľby dopravnej pr&aacute;ce
IAD : ostatn&aacute; doprava = 40 : 60
Funkčn&eacute; využitie objektu: b&yacute;vanie - 5bytov
N = 1,1 x Oo
2-izbov&eacute; byty..................1
1,1 . 1,5PM/byt
3-izbov&eacute; byty..................4
1,1 . 2PM/byt
1,1 x 1 x 1,5
1,65 PM
1,1 x 4 x 2
8,8 PM
N = 10,45 miest pre funkciu b&yacute;vanie
Celkov&eacute; n&aacute;roky na statick&uacute; dopravu je 11 miest. Podľa v&yacute;počtu bilancie statickej dopravy je potrebn&eacute;
zabezpečiť minim&aacute;lne 11 parkovac&iacute;ch miest. Podľa ustanoven&iacute; vyhl.č.532/2002 Z.z. je treba navrhn&uacute;ť 4% stoj&iacute;sk
pre vozidl&aacute; telesne postihnut&yacute;ch, ale najmenej 1 parkovacie miesto. Navrhnut&yacute;ch je 12 parkovac&iacute;ch miest, z toho
je pre telesne postihnut&yacute;ch občanov vyhraden&yacute;ch 1 parkovacie miesto. Parametre kolm&yacute;ch parkovac&iacute;ch st&aacute;t&iacute; s&uacute;
navrhnut&eacute; š&iacute;rky 2,5m a dĺžky 5m podľa STN 73 6056 pre vozidl&aacute; skupiny 1, podskupiny 01 a 02 – mal&eacute;, stredn&eacute;
a veľk&eacute; osobn&eacute; automobily. Parkovacie miesto pre telesne postihnut&yacute;ch je š&iacute;rky 3,5m.
Navrhovan&eacute; technick&eacute; prvky vych&aacute;dzaj&uacute; z STN 736110 – Projektovanie miestnych komunik&aacute;ci&iacute;. Polomery
obl&uacute;kov a š&iacute;rky jazdn&yacute;ch pruhov s pr&iacute;slušn&yacute;mi rozš&iacute;reniami s&uacute; navrhnut&eacute; podľa STN 73 6102 tab. č.5. Parkovacie
miesta s&uacute; navrhnut&eacute; podľa STN 73 6056.
Smerov&eacute; vedenie
Pr&iacute;jazdov&aacute; komunik&aacute;cia a vetvy komunik&aacute;ci&iacute; v are&aacute;li s&uacute; riešen&eacute; ako priame.
V&yacute;škov&eacute; vedenie
V&yacute;škovo bude pr&iacute;jazdov&aacute; komunik&aacute;cia na začiatku nav&auml;zovať na kraj jestvuj&uacute;cej cesty ul. Gogoľovej.
Pozdĺžny sklon komunik&aacute;cie bude minim&aacute;lny, podľa okolit&eacute;ho ter&eacute;nu. V mieste napojenia na cestu ul. Gogoľovej
bude pozdĺžny sklon klesať smerom od cesty, aby nevytekali zr&aacute;žkov&eacute; vody na t&uacute;to komunik&aacute;ciu. Pozdĺžne
sklony komunik&aacute;ci&iacute; bud&uacute; prisp&ocirc;soben&eacute; v&yacute;škov&eacute;mu osadeniu stavebn&yacute;ch objektov a konfigur&aacute;cii ter&eacute;nu. Max.
pozdĺžny sklon bude 2,0 %.
Priečne a konštrukčn&eacute; usporiadanie
Konštrukčn&eacute; usporiadanie komunik&aacute;c&iacute;&iacute; je navrhnut&eacute; nasledovne :
Nov&aacute; spevnen&aacute; plocha ako aj parkovacie plochy sa vybuduj&uacute; v nasledovnom zložen&iacute; vrstiev:
PIESKOV&Eacute; L&Ocirc;ŽKO fr. 2/4 (ALT.DRŤ. fr. 4-8)
IZOLAČN&Aacute; F&Oacute;LIA EKOPLAST 806 /FATRAFOL/
VIBROVAN&Yacute; ŠTRK VŠ fr. 0-8 mm
SPODN&Aacute; NOSN&Aacute; VRSTVA ZO ŠTRKODRVA fr. 0-32 mm hr. 200 mm
Dostatočne spev. zemn&aacute; pl&aacute;ň
/spodn&aacute; nosn&aacute; vrstva, zhutniť 45 MPa
hr. 1,5 mm
hr. 250 mm
Nov&aacute; plocha pre chodcov sa vybuduje v nasledovnom zložen&iacute; vrstiev:
DLAŽBOV&Eacute; L&Ocirc;ŽKO /DRVEN&Eacute; ALEBO
ŤAŽEN&Eacute; KAMENIVO fr. 4/8 mm,
JEMN&Aacute; PL&Aacute;Ň/ŠTRKODRVA fr. 8-16 mm,
ZHUTNIŤ 150 MPa
hr. 150 mm
Na krajoch parkoviska bud&uacute; osaden&eacute; cestn&eacute; obrubn&iacute;ky na stojato s v&yacute;škou 100mm nad vozovkou.
Konštrukčn&eacute; vrstvy jednotliv&yacute;ch čast&iacute; komunik&aacute;ci&iacute; s&uacute; navrhnut&eacute; podľa pr&iacute;slušn&yacute;ch STN a Katal&oacute;gu pozemn&yacute;ch
komunik&aacute;ci&iacute;. Je potrebn&eacute;, aby jednotliv&eacute; konštrukčn&eacute; vrstvy boli hutnen&eacute; tak, aby sa dosiahlo maxim&aacute;lnej
pevnosti a t&yacute;m aj maxim&aacute;lnej tvarovej st&aacute;losti podkladn&yacute;ch vrstiev.
Odvodnenie parkoviska bude riešen&eacute; pomocou uličn&eacute;ho vpustu. Uličn&yacute; vpust bude z bet&oacute;novejh skruže
osaden&yacute;ch ťažk&yacute;m liatinov&yacute;m poklopom, čistiacim košom a odkalovac&iacute;m priestorom.
Dopravn&eacute; značenie
Na zvisl&eacute; dopravn&eacute; značky bude použit&yacute; hlin&iacute;k, značky bud&uacute; s reflexnou &uacute;pravou povrchu. Osadia sa
v zmysle STN 01 8020 a Vyhl&aacute;šky č.9/2008 Z.z. Vodorovn&eacute; dopravn&eacute; značenie bude bielej farby, reflexn&eacute;.
Prenosn&eacute; dopravn&eacute; značky musia byť počas celej doby kompletn&eacute;, nesm&uacute; byť znečisten&eacute; a ani inak poškoden&eacute;.
V pr&iacute;pade poškodenia treba ur&yacute;chlene značky obnoviť. Organiz&aacute;cia vykon&aacute;vaj&uacute;ca pr&aacute;ce na vozovke je povinn&aacute;
dočasn&eacute; dopravn&eacute; značenie osadiť v zmysle schv&aacute;len&eacute;ho projektu organiz&aacute;cie dopravy, počas trvania pr&aacute;c ich
udržiavať v riadnom stave a z&aacute;brany za zn&iacute;ženej viditeľnosti označiť červen&yacute;m svetlom. Taktiež je povinn&aacute;
v zmysle z&aacute;kona č 135/61 Z.z. v znen&iacute; neskorš&iacute;ch predpisov, v &uacute;plnom znen&iacute; vyhl&aacute;senom pod č. 55/1984 ZB.,
počas pr&aacute;c priľahl&uacute; komunik&aacute;ciu udržiavať v riadnom stave a v pr&iacute;pade, že d&ocirc;jde k jej znečisteniu z d&ocirc;vodu
vykon&aacute;van&yacute;ch pr&aacute;c, t&uacute;to očistiť bez meškania.
Pred započat&iacute;m stavebn&yacute;ch pr&aacute;c sa priestor cel&eacute;ho staveniska odhumusuje. Zemn&eacute; pr&aacute;ce pozost&aacute;vaj&uacute;
hlavne z v&yacute;kopov&yacute;ch pr&aacute;c a z drobn&yacute;ch ter&eacute;nnych &uacute;prav a dosyp&aacute;vkach za obrubn&iacute;ky . Pred v&yacute;stavbou
komunik&aacute;ci&iacute; bude zrealizovan&aacute; pr&iacute;prava &uacute;zemia, a bude pripraven&aacute; pl&aacute;ň pod v&yacute;stavbu komunik&aacute;ci&iacute;. Z&aacute;kladnou
normou pre navrhovanie a vykon&aacute;vanie zemn&yacute;ch pr&aacute;c je STN 73 3050 Zemn&eacute; pr&aacute;ce. Pl&aacute;ň pod vozovkou mus&iacute; byť
upraven&aacute; v zmysle požiadaviek uveden&yacute;ch v STN 73 6114 Vozovky pozemn&yacute;ch komunik&aacute;ci&iacute; – z&aacute;kladn&eacute;
ustanovenia pre navrhovanie.
Zemn&aacute; pl&aacute;ň pod vozovkou mus&iacute; byť zhutnen&aacute; tak, aby modul deform&aacute;cie podložia dosiahol E def2 = 50
Mpa. Pomer E def2 / E def1 mus&iacute; byť menš&iacute; ako 2,5. Vo vrstve n&aacute;sypu a vrstve z&aacute;rezu m&ocirc;žu byť použit&eacute; len
zeminy vhodn&eacute; (STN 73 6133 Teleso pozemn&yacute;ch komunik&aacute;ci&iacute;), s maxim&aacute;lnou objemovou hmotnosťou v&auml;čšou ako
1650 kg/m3. Upraven&eacute; podložie sa mus&iacute; zhutniť hladk&yacute;m valcom. Miera zhutnenia pre s&uacute;držn&eacute; a nes&uacute;držn&eacute;
zeminy je stanoven&aacute; v STN 73 6133 Teleso pozemn&yacute;ch komunik&aacute;ci&iacute; (tabuľka 4 a 5). Pl&aacute;ň mus&iacute; byť zhotoven&aacute;
v priečnom sklone podľa projektovej dokument&aacute;cie, tak aby bolo vždy zabezpečen&eacute; jej odvodnenie. Dokončen&aacute;
pl&aacute;ň mus&iacute; byť zhotoviteľom chr&aacute;nen&aacute; – nesm&uacute; byť na nej skl&aacute;dky materi&aacute;lov ani parkovanie vozidiel. Obmedzen&eacute;
musia byť aj prejazdy vozidiel.
Riešen&eacute; &uacute;zemie je v zastavanej časti mesta na s&iacute;dlisku Ľadoveň, ktor&aacute; sa nach&aacute;dza v juhov&yacute;chodnej
časti mesta Martina (koordin&aacute;ty 49&deg; 3.102', 18&deg; 55.571') v nadmorskej v&yacute;ške 416 m n. m. V &uacute;zem&iacute; nie s&uacute; potrebn&eacute;
asan&aacute;cie ani z&aacute;bery p&ocirc;dy, nakoľko sa jedn&aacute; o druh pozemku: Zastavan&eacute; plochy a n&aacute;dvoria.
2.3.1. Ochrann&eacute; p&aacute;sma
V riešenom &uacute;zem&iacute; sa nenach&aacute;dzaj&uacute; ochrann&eacute; &uacute;zemia ani chr&aacute;nen&eacute; časti &uacute;zemia. Je nutn&eacute; rešpektovať
ochrann&eacute; p&aacute;sma II. stupňa pr&iacute;rodn&yacute;ch liečiv&yacute;ch zdrojov a pr&iacute;rodn&yacute;ch miner&aacute;lnych zdrojov v Martine a ochrann&eacute;
p&aacute;sma existuj&uacute;cich inžiniersk&yacute;ch siet&iacute; v zmysle platnej legislat&iacute;vy a to n&aacute;sledovne:
Ochrann&eacute; p&aacute;smo II. stupňa pr&iacute;rodn&yacute;ch liečiv&yacute;ch zdrojov a pr&iacute;rodn&yacute;ch miner&aacute;lnych zdrojov v Martine
V zmysle vyhl&aacute;šky MZ SR č. 341/2010 Z.z. z 5. 8. 2010
V zmysle pr&iacute;slušnej telekomunikačnej vyhl&aacute;šky a noriem STN predstavuj&uacute; ochrann&eacute; p&aacute;sma telekomunikačn&yacute;ch
• 1 m pre miestne telekomunikačn&eacute; k&aacute;ble a rozvody
• 1,5 m a 3 m pre diaľkov&eacute; a spojovacie vedenia
V pr&iacute;pade križovania a s&uacute;behu tel. veden&iacute; so silov&yacute;m veden&iacute;m mus&iacute; byť dodržan&aacute; norma STN 73 6005
o priestorovej &uacute;prave veden&iacute; technick&eacute;ho vybavenia a norma STN 33 40 50 ods.3.3.1. o podzemn&yacute;ch
telekomunikačn&yacute;ch vedeniach. Pred začat&iacute;m v&yacute;kopov&yacute;ch pr&aacute;c je nutn&eacute; zameranie a vyt&yacute;čenie podzemn&yacute;ch inž.
Vodohospod&aacute;rske siete
• vodovod DM150 – 1,50 m od okraja potrubia vodorovne na obidve strany
• kanaliz&aacute;cia DN300 - 1,50 m od okraja potrubia vodorovne na obidve strany
Ochrann&eacute; p&aacute;sma v tepl&aacute;renstve
Z&aacute;kon 657/2004 o tepelnej energetike
• Ochrann&eacute; p&aacute;smo rozvodu tepla za odovzd&aacute;vacou stanicou je vymedzen&eacute; zvisl&yacute;mi rovinami veden&yacute;mi po
jeho obidvoch stran&aacute;ch vo vodorovnej vzdialenosti meranej kolmo na toto zariadenie len v pr&iacute;pade, že
by mohlo d&ocirc;jsť k ohrozeniu plynulosti dod&aacute;vky tepla a bezpečnosti prev&aacute;dzky zariadenia, a to najviac v
zastavanom &uacute;zem&iacute; na každ&uacute; stranu 1m a mimo zastavan&eacute;ho &uacute;zemia na jednu stranu 3 m a na druh&uacute;
stranu 1 m, podľa určenia držiteľa povolenia na rozvod tepla.
Ochrann&eacute; p&aacute;sma elektronick&yacute;ch komunik&aacute;ci&iacute;
Z&aacute;kon č. 610 / 2003 Z.z. o elektronick&yacute;ch komunik&aacute;ci&aacute;ch
• Ochrann&eacute; p&aacute;smo vedenia je širok&eacute; 1,5 m od osi jeho trasy a prebieha po celej dĺžke jeho trasy. Hĺbka a
v&yacute;ška ochrann&eacute;ho p&aacute;sma je 2 m od &uacute;rovne zeme, ak ide o podzemn&eacute; vedenie a v okruhu 2 m, ak ide o
nadzemn&eacute; vedenie.
Rozsah a charakteristiku všetk&yacute;ch ochrann&yacute;ch p&aacute;siem riešen&eacute;ho &uacute;zemia pozri pr&iacute;slušn&uacute; kap. predmetnej
spr&aacute;vy. Konštatujeme, že počas v&yacute;stavby objektov nie je nutn&eacute; stanovovať mimoriadne dočasn&eacute;, ochrann&eacute;
hygienick&eacute; p&aacute;sma. Ochrann&eacute; p&aacute;sma jestvuj&uacute;cich dočasn&yacute;ch i trval&yacute;ch nadzemn&yacute;ch a podzemn&yacute;ch I.S. a ich
s&uacute;visiacich zariaden&iacute; bud&uacute; počas v&yacute;stavby rešpektovan&eacute; v rozsahu pr&iacute;slušnej legislat&iacute;vy resp. bude s nimi
nakladan&eacute; v zmysle projektov&eacute;ho riešenia. Zvl&aacute;štne a osobitn&eacute; opatrenia počas v&yacute;stavby, v dotyku s
inžiniersk&yacute;mi sieťami, rev&iacute;zn&yacute;mi šachtami a ostatn&yacute;mi objektami a zariadeniami napr. v majetku napr. SPP, a.s.
SSE, a.s. resp. Turčianskej vod&aacute;renskej spoločnosti, a.s. bud&uacute; upresnen&eacute; v samostatn&yacute;ch projektov&yacute;ch riešeniach
ďaľšieho stupňa projektovej pr&iacute;pravy (napr. problematika trval&eacute;ho pr&iacute;stupu majiteľov a spr&aacute;vcov I.S. k objektom
a technick&yacute;m zariadeniam počas v&yacute;stavby, poloha dočasn&yacute;ch objektov navrhovan&eacute;ho zariadenia staveniska voči
ochrann&yacute;m p&aacute;smam t&yacute;chto zariaden&iacute; a pod.).
.2. Sadovn&iacute;cke &uacute;pravy
V s&uacute;časnosti je parcela veden&aacute; podľa v&yacute;pisu KN ako zastavan&aacute; plocha a n&aacute;dvorie. Okolie objektu je
obrasten&eacute; vzrastlou zeleňou spont&aacute;lne sadenou. Z d&ocirc;vodu v&yacute;stavby nov&yacute;ch parkovac&iacute;ch miest bude nutn&yacute; v&yacute;rub
drev&iacute;n o celkovom počte 7 ks. Na tento v&yacute;rub bol vydan&yacute; s&uacute;hlas, viď. pr&iacute;loha C. Doklady.
Likvid&aacute;cia a ochrana zelene:
V s&uacute;časnosti sa na pozemku nenach&aacute;dza žiadna hodnotn&aacute; zeleň. Nebude sa teda realizovať ochrana existuj&uacute;cej
Pr&iacute;prava p&ocirc;dy:
na ploche sadov&yacute;ch &uacute;prav bude rozprestren&aacute; ornica v hr. 150mm. Pred osaden&iacute;m bude p&ocirc;da ošetren&aacute; herbic&iacute;dom.
Tr&aacute;vnik:
bude založen&yacute; v&yacute;sevom v kvalite parkov&eacute;ho tr&aacute;vnika.
bud&uacute; vys&aacute;dzan&eacute; v celkovom počte podľa požiadaviek Povolenia na v&yacute;rub (viď. pr&iacute;loha) do j&aacute;m zodpovedaj&uacute;cej
veľkosti s 50% v&yacute;menou p&ocirc;dy zmesou kvalitnej ornice a z&aacute;hradnej zeminy v pomere 3:1. Použit&eacute; bud&uacute; v&yacute;pestky
s obvodom kmeňa 140-160-180mm a v&yacute;škou podľa charakteru v&yacute;pestku. Stromy bud&uacute; ukotven&eacute; kolmi.
Kry: bud&uacute; vysaden&eacute; do čierneho &uacute;horu zabezpečen&eacute; chemick&yacute;m ošetren&iacute;m po v&yacute;sadbe, do j&aacute;m s v&yacute;menou 50%
podobne ako u stromov.
Všetky pr&aacute;ce bud&uacute; realizovan&eacute; podľa pr&iacute;slušn&yacute;ch noriem STN.
SP&Ocirc;SOB OBMEDZENIA ALEBO ODSTR&Aacute;NENIA PR&Iacute;PADN&Yacute;CH
PR&Iacute;PADN&Yacute;CH NEGAT&Iacute;VNYCH VPLYVOV,
2.4.1 Odpadov&eacute; hospod&aacute;rstvo
V zmysle Vyhl&aacute;šky MŽP SR č. 284/2001 Z.z., ktorou sa ustanovuje Katal&oacute;g odpadov, vznikn&uacute; druhy
odpadov, zaraden&yacute;ch do kateg&oacute;rie nebezpečn&yacute;ch odpadov (N) a ostatn&yacute;ch odpadov (O).
Pri v&yacute;stavbe vznikne odpad jednak v r&aacute;mci pr&iacute;pravy &uacute;zemia a jednak pri samotnej v&yacute;stavbe objektu. Hlavn&yacute;
objem odpadu vznikne pri pr&iacute;prave &uacute;zemia a pri v&yacute;kopov&yacute;ch pr&aacute;cach. Časť v&yacute;kopovej zeminy bude použit&aacute; na
sp&auml;tn&eacute; z&aacute;sypy a sadov&eacute; &uacute;pravy.
Predpokladan&eacute; druhy odpadov vznikaj&uacute;cich
vznikaj&uacute;cich pri v&yacute;stavbe:
Č. druhu
N&aacute;zov druhu odpadu
k&aacute;ble in&eacute; ako uveden&eacute; v 17 04 10
v&yacute;kopov&aacute; zemina in&aacute; ako uveden&aacute; v 17 05 05
Zmiešan&eacute; odpady zo stavieb a demol&aacute;ci&iacute; in&eacute; ako uveden&eacute; v 17
09 01, 17 09 02 a 17 09 03
vznikaj&uacute;cich počas prev&aacute;dzky:
Maxim&aacute;lne obsadenie bytov&yacute;ch domov je 20 obyvateľov. Pri predpokladanom obsaden&iacute; a množstve
odpadu na obyvateľa t&yacute;ždenne 55l, vych&aacute;dza celkov&eacute; množstvo zmiešan&eacute;ho komun&aacute;lneho odpadu na cca. 1100L.
Pri frekvencii odvozu 2x t&yacute;ždne by mala kapacita odpadov&yacute;ch n&aacute;dob dosahovať min 550 L. Navrhnut&yacute; je
priestor s možnosťou umiestnenia kontajnera 1x800l o objeme 800l.
Nakladanie s odpadmi sa mus&iacute; riadiť platnou pr&aacute;vnou &uacute;pravou na &uacute;seku odpadov&eacute;ho hospod&aacute;rstva
(z&aacute;kon č. 223/2001 Z.z. o odpadoch v znen&iacute; neskorš&iacute;ch predpisov), ktor&aacute; požaduje predch&aacute;dzať vzniku odpadov
a obmedzovať ich množstvo, ako i odpady zhodnocovať recykl&aacute;ciou a op&auml;tovn&yacute;m využit&iacute;m. Zneškodňovanie
odpadov sp&ocirc;sobom, ktor&yacute; neohrozuje zdravie ľud&iacute; a nepoškodzuje životn&eacute; prostredie je možn&eacute; vtedy, ak sa ned&aacute;
použiť in&yacute;, vhodnejš&iacute; sp&ocirc;sob nakladania s odpadmi. Z uveden&eacute;ho vypl&yacute;va, že zneškodňovanie odpadov
skl&aacute;dkovan&iacute;m by mal byť posledn&yacute; sp&ocirc;sob, ako sa bude s odpadmi nakladať.
Medzi prvorad&eacute; &uacute;lohy pri zah&aacute;jen&iacute; prev&aacute;dzky bude patriť vybavenie s&uacute;hlasu na nakladanie
s nebezpečn&yacute;mi odpadmi, spracovanie pokynov v pr&iacute;pade hav&aacute;rie, spracovanie programu odpadov&eacute;ho
hospod&aacute;rstva a zabezpečenie z&aacute;kladn&yacute;ch zml&uacute;v s opr&aacute;vnen&yacute;mi organiz&aacute;ciami na odber a n&aacute;sledn&eacute; zhodnotenie
alebo zneškodnenie odpadov.
Odpad bude likvidovan&yacute; prostredn&iacute;ctvom centr&aacute;lneho zvozu technick&yacute;ch služieb – predpoklad&aacute; sa 2 x
t&yacute;ždne. Odvoz komun&aacute;lneho odpadu bude v ďalšej f&aacute;ze projektu ošetren&yacute; zmluvou s technick&yacute;mi službami mesta
2.4.2. Starostlivosť o bezpečnosť pr&aacute;ce a technick&yacute;ch zariaden&iacute;
Pri realiz&aacute;cii stavby je dod&aacute;vateľ povinn&yacute; dodržiavať všetky normy a predpisy vypl&yacute;vaj&uacute;ce z vyhl&aacute;šky S&Uacute;BP
a SB&Uacute; č. 374/1990 Zb. o bezpečnosti pr&aacute;ce a technick&yacute;ch zariaden&iacute; pri stavebn&yacute;ch pr&aacute;cach, pokyny BOZ pri pr&aacute;ci
vo vodohospod&aacute;rskych objektoch. Ďalej je potrebn&eacute; dodržiavať podmienky pr&iacute;slušn&yacute;ch org&aacute;nov a organiz&aacute;cii.
Počas v&yacute;stavby bud&uacute; rešpektovan&eacute; všetky existuj&uacute;ce podzemn&eacute; i nadzemn&eacute; vedenia, ktor&eacute; je potrebn&eacute; pred
zah&aacute;jen&iacute;m stavby vyt&yacute;čiť.
Neoddeliteľnou s&uacute;časťou BOZ a hygieny pracovn&eacute;ho prostredia je z&aacute;sada d&ocirc;sledn&eacute;ho dodržiavania čistoty
a poriadku na pracovisku.
S&uacute;visiace pr&aacute;vne a in&eacute; predpisy:
Vyhl&aacute;ška S&Uacute;BP a SB&Uacute; č.111/1975 Zb. v znen&iacute; vyhl&aacute;šky č.483/1990 Zb., o evidencii a registr&aacute;cii pracovn&yacute;ch &uacute;razov
a o hl&aacute;sen&iacute; prev&aacute;dzkov&yacute;ch neh&ocirc;d (hav&aacute;ri&iacute;) a por&uacute;ch technick&yacute;ch zariaden&iacute;
Z&aacute;kon č.20/1996 Zb., v znen&iacute; z&aacute;kona SNR č.96/1992 Zb. o starostlivosti o zdravie ľudu a z&aacute;konn&eacute; opatrenia SNR
č.305/1992 Zb.
Vyhl&aacute;ška MZd č.45/1996 Zb., o vytv&aacute;ran&iacute; a ochrane zdrav&yacute;ch životn&yacute;ch podmienok
Vyhl&aacute;ška Ministerstva zdravotn&iacute;ctva SSR č.17/1977 o ochrane zdravia pred nepriazniv&yacute;mi &uacute;činkami hluku
a vibr&aacute;ci&iacute;
Vyhl&aacute;ška Ministerstva stavebn&iacute;ctva č.77/1965 Zb. o v&yacute;cviku sp&ocirc;sobilosti a registr&aacute;cii obsl&uacute;h stavebn&yacute;ch strojov
Z&aacute;kon č.53/1975 Zb. o pokut&aacute;ch za porušenie pr&aacute;vnych predpisov o vytv&aacute;ran&iacute; a ochrane zdrav&yacute;ch životn&yacute;ch
Vyhl&aacute;ška S&Uacute;BP č.59/1982 Zb., v znen&iacute; vyhl&aacute;šky č.484/1990 Zb., ktorou sa určuj&uacute; z&aacute;kladn&eacute; požiadavky na
zaistenie bezpečnosti pr&aacute;ce a technick&yacute;ch zariaden&iacute;
Smernice – z&aacute;v&auml;zn&eacute; opatrenie č.17/1990 Vestn&iacute;ka MZd SSR o posudzovan&iacute; zdravotnej sp&ocirc;sobilosti na pr&aacute;cu (reg.
v čiastke 24/1970 Zb.) v znen&iacute; Smernice MZd SSR z 15.dec.1971 (reg. v čiastke 13/1972 Zb.).
Smernica MLVH SSR č.7200/4/221/1983 pre poskytovanie osobn&yacute;ch ochrann&yacute;ch pracovn&yacute;ch prostriedkov (a
Podnikov&eacute; regulat&iacute;vy o poskytovan&iacute; OOPP pracovn&iacute;kom)
Zborn&iacute;k vybran&yacute;ch predpisov bezpečnosti a ochrany zdravia pri pr&aacute;ci vo vodohospod&aacute;rskych organiz&aacute;ci&aacute;ch
z r.1990 a jeho Dodatok č.1 z janu&aacute;ra 1993
Vyhl&aacute;ška S&Uacute;BP a SB&Uacute; č.374/1990 Zb. o bezpečnosti pr&aacute;ce a technick&yacute;ch zariaden&iacute; pri stavebn&yacute;ch pr&aacute;cach
(nahr&aacute;dza Bezpečnostn&eacute; predpisy B1 až B6).
Nariadenie vl&aacute;dy SR
č. 159/2001 o bezpečnostn&yacute;ch a zdravotn&yacute;ch požiadavk&aacute;ch pri použ&iacute;van&iacute; pracovn&yacute;ch prostriedkov
č.201/2001 o min. bezpečnostn&yacute;ch požiadavk&aacute;ch pracoviska
č.204/2001 o min. bezpečnostn&yacute;ch požiadavk&aacute;ch pri pr&aacute;ci s bremenom
č.247/2001 o min. bezpečnostn&yacute;ch požiadavk&aacute;ch pri pr&aacute;ci so zobrazovac&iacute;mi jednotkami
č.510/2001 o min. bezpečnostn&yacute;ch požiadavk&aacute;ch na stavenisko
č.504/2002 o podmienkach poskytovania ostatn&yacute;ch ochrann&yacute;ch prostriedkov
2.5.1. POŽIARNA OCHRANA
Všeobecne, s&uacute;visiace normy a predpisy
S&uacute;visiace normy a predpisy
-Vyhl&aacute;ška MV SR č. 94/2004 Z.z., ktorou sa ustanovuj&uacute; technick&eacute; požiadavky na protipožiarnu bezpečnosť pri
v&yacute;stavbe a pri už&iacute;van&iacute; stavieb + Vyhl&aacute;ška MV SR č. 307/2007 Z.z., ktor&aacute; ju men&iacute; a dopĺňa + Vyhl&aacute;ška MV SR
č.225/2012 z 25.6.2012.
-STN 92 0201-1 Požiarna bezpečnosť stavieb. Spoločn&eacute; ustanovenia. Časť 1: Požiarne riziko, veľkosť požiarneho
-STN 92 0201-2 Požiarna bezpečnosť stavieb. Spoločn&eacute; ustanovenia. Časť 2: Stavebn&eacute; konštrukcie.
-STN 92 0201-3 Požiarna bezpečnosť stavieb. Spoločn&eacute; ustanovenia. Časť 3: &Uacute;nikov&eacute; cesty a evaku&aacute;cia os&ocirc;b.
-STN 92 0201-4 Požiarna bezpečnosť stavieb. Spoločn&eacute; ustanovenia. Časť 4: Odstupov&eacute; vzdialenosti.
-STN 92 0241 - Požiarna bezpečnosť stavieb. Obsadenie stavieb osobami.
-Vyhl&aacute;ška MV SR č. 699/2004 Z.z. o zabezpečen&iacute; stavby vodou na hasenie požiarov.
-STN 92 0400 - Požiarna bezpečnosť stavieb. Z&aacute;sobovanie vodou na hasenie požiarov.
-STN 92 0202-1 - Požiarna bezpečnosť stavieb. Vybavovanie stavieb hasiacimi pr&iacute;strojmi.
-STN EN 1838 - Požiadavky na osvetlenie. N&uacute;dzov&eacute; osvetlenie
-STN 92 0205 - Spr&aacute;vanie sa stavebn&yacute;ch v&yacute;robkov v požiari. Zachovanie funkčnej odolnosti elektrick&yacute;ch
k&aacute;blov&yacute;ch syst&eacute;mov.
STN 92 0203 - Požiarna bezpečnosť stavieb. Trval&aacute; dod&aacute;vka elektrickej energie.
Z&aacute;sadn&aacute; koncepcia riešenia protipožiarnej bezpečnosti (PB) obytn&eacute;ho domu „AERO RESIDENCE“
vych&aacute;dza z platn&eacute;ho k&oacute;dexu predpisov a noriem protipožiarnej bezpečnosti a je zameran&aacute; na plnenie troch
z&aacute;kladn&yacute;ch požiadaviek PB:
1/- zabr&aacute;nenie rozš&iacute;renia sa pr&iacute;padn&eacute;ho požiaru do v&auml;čš&iacute;ch rozmerov, č&iacute;m sa minimalizuj&uacute; škody na majetku,
zn&iacute;ži ohrozenie os&ocirc;b a umožn&iacute; sa efekt&iacute;vny hasebn&yacute; z&aacute;sah (dosiahne sa požadovan&yacute;m a optim&aacute;lnym rozdelen&iacute;m
stavby na požiarne &uacute;seky, zabezpečen&iacute;m stavby adekv&aacute;tnymi požiarnotechnick&yacute;mi zariadeniami, dodržan&iacute;m
potrebn&yacute;ch požiarnych odolnost&iacute; stavebn&yacute;ch konštrukci&iacute;, zabr&aacute;nen&iacute;m prenosu požiaru zo susedn&yacute;ch stavieb
a dodržan&iacute;m odstupov&yacute;ch vzdialenost&iacute; medzi jednotliv&yacute;mi požiarnymi &uacute;sekmi),
2/- zabezpečenie bezpečnej evaku&aacute;cie os&ocirc;b v pr&iacute;pade požiaru (stanovenie počtu, dĺžok a š&iacute;rok &uacute;nikov&yacute;ch ciest,
vytvorenie chr&aacute;nen&yacute;ch &uacute;nikov&yacute;ch ciest a dostatočnej kapacity &uacute;nikov&yacute;ch v&yacute;chodov),
3/- vytvorenie podmienok pre &uacute;činn&yacute; hasebn&yacute; z&aacute;sah (z&aacute;sahov&eacute; cesty, zabezpečenie stavby vodou pre hasenie
požiarov a potrebn&yacute;mi požiarnotechnick&yacute;mi zariadeniami).
Pre &uacute;čely &uacute;zemn&eacute;ho rozhodnutia je rozhoduj&uacute;ce z hľadiska PB v tomto stupni pos&uacute;denie:
- odstupov&yacute;ch vzdialenost&iacute;,
- zabezpečenia vody pre hasenie,
- pr&iacute;jazdu a pr&iacute;stupu k stavbe pre hasebn&yacute; z&aacute;sah.
Popis stavby a jej priestorov
Uvažuje sa s nadstavbou a pr&iacute;stavbou existuj&uacute;ceho objektu s tromi nadzemn&yacute;mi podlažiami a jedn&yacute;m
podzemn&yacute;m podlaž&iacute;m. Prv&eacute; nadzemn&eacute; podlažie je určen&eacute; na viac&uacute;čelov&eacute; využitie, ako z&aacute;zemie domu s dvoma
bytov&yacute;mi jednotkami, v ostatn&yacute;ch nadzemn&yacute;ch podlažiach sa bud&uacute; nach&aacute;dzať troj izbov&eacute; byty. Maxim&aacute;lne
p&ocirc;dorysn&eacute; rozmery s&uacute; 16,5 m x 22 m. Z hľadiska stavebn&eacute;ho riešenia s&uacute; nosn&eacute; obvodov&eacute; steny p&ocirc;vodn&eacute;ho
objektu z keramoblokov o skladobnej hr&uacute;bke 320 mm, stropn&eacute; dosky železobet&oacute;nov&eacute;. Nov&eacute; konštrukcie tvoria
dreven&yacute; r&aacute;m s teploizolačnou v&yacute;plňou, sp&aacute;jan&yacute;ch veľkoform&aacute;tov&yacute;mi doskami a kompletne omietnut&yacute;ch, osaden&yacute;ch
na oceľov&yacute;ch konštrukciach, ktor&eacute; s&uacute; chr&aacute;nen&eacute; protipožiarn&yacute;m n&aacute;teromu. Stavby nemusia byť v s&uacute;lade s STN 92
0201-2, čl. 5.5.5 c.) vybaven&eacute; požiarnymi p&aacute;smi. Požiarna v&yacute;ška „h“ je v s&uacute;lade s STN 92 0201-2, čl. 2.2.6 je 11,5
m. Povrchov&uacute; &uacute;pravu strechy tvor&iacute; nehorľav&aacute; krytina. V s&uacute;lade s STN 92 0201-2, čl. 2.6.7 b.) sa jedn&aacute; o dva
nehorľav&eacute; konštrukčn&eacute; celky.
Hlavn&eacute; typy priestorov
Z hľadiska protipožiarnej bezpečnosti sa v stavb&aacute;ch nach&aacute;dzaj&uacute; priestory s bežn&yacute;m požiarnym rizikom.
V každej stavbe sa nach&aacute;dzaj&uacute; 2 - 3 izbov&eacute; byty (obytn&eacute; bunky), ktor&eacute; tvoria v s&uacute;lade s vyhl&aacute;škou MV
SR 94/2004, pr&iacute;loha č.1 vždy samostatn&eacute; požiarne &uacute;seky.
V zmysle &sect;94 (5) vyhl&aacute;šky MV SR č. 94/2004 Z.z. ide pri oboch obytn&yacute;ch domoch a jednom
polyfunkčnom dome o stavby na b&yacute;vanie skupiny B. Každ&yacute; byt predstavuje jednu obytn&uacute; bunku, ktor&aacute; v zmysle
Pr&iacute;lohy 1, bod 4. vyhl&aacute;šky MV SR č. 94/2004 Z.z. mus&iacute; tvoriť samostatn&yacute; požiarny &uacute;sek (P&Uacute;).
Elektrick&eacute; prev&aacute;dzky:
Elektrick&eacute; prev&aacute;dzky (elektromery) bud&uacute; požiarne oddelen&eacute; od ostatn&yacute;ch priestorov a bud&uacute; navrhovan&eacute;
v s&uacute;lade s čl.10.2 STN 33 3220 a STN 92 0203.
Všetky typy šachiet (inštalačn&yacute;ch i v&yacute;ťahov&yacute;ch) musia byť požiarne oddelen&eacute; od ostatn&yacute;ch požiarnych
&uacute;sekov, ktor&yacute;mi prech&aacute;dzaj&uacute;. Preto jednotliv&eacute; šachty bud&uacute; tvoriť samostatn&eacute; požiarne &uacute;seky. Šachty VZT
a šachty elektro musia tvoriť samostatn&eacute; P&Uacute;, nem&ocirc;žu sa zlučovať s in&yacute;mi profesiami. Požiadavky na požiarne
odolnosti stien a uz&aacute;verov šachiet sa určia podľa susedn&yacute;ch požiarnych &uacute;sekov. Obostavan&yacute; priestor, ktor&yacute;
prech&aacute;dza len jedn&yacute;m podlaž&iacute;m, t.j. zospodu i zhora m&aacute; požiarny strop, t. j. neprestupuje cez požiarne stropy,
nie je šachtou. Je len priestorom rozvodov, ktor&yacute; je s&uacute;časťou toho P&Uacute;, v ktorom sa nach&aacute;dza.
Strojovne VZT musia tvoriť samostatn&eacute; požiarne &uacute;seky. Pokiaľ sl&uacute;žia len pre jeden požiarny &uacute;sek,
m&ocirc;žu byť jeho s&uacute;časťou. Jednotky požiarneho vetrania nesm&uacute; byť s&uacute;časťou in&yacute;ch strojovn&iacute; VZT ani in&yacute;ch
priestorov, m&ocirc;žu byť umiestnen&eacute; v samostatnej miestnosti tvoriacej samostatn&yacute; požiarny &uacute;sek (P&Uacute;). na streche
alebo priamo v CH&Uacute;C. Každ&aacute; jednotka požiarneho vetrania je s&uacute;časťou toho P&Uacute; CH&Uacute;C, ktor&yacute; vetr&aacute;.
Delenie stavby do požiarnych &uacute;sekov
&uacute;sekov
Posudzovan&eacute; stavby bud&uacute; delen&eacute; do samostatn&yacute;ch požiarnych &uacute;sekov podľa požiadaviek vyhl&aacute;šky MV
SR č. 94/2004.
- jednotliv&eacute; obytn&eacute; bunky – byty,
- domov&aacute; vybavenosť stavby pre b&yacute;vanie,
- in&eacute; priestory, umiestnen&eacute; v stavbe pre b&yacute;vanie,
- chr&aacute;nen&eacute; &uacute;nikov&eacute; cesty,
- čiastočne chr&aacute;nen&eacute; &uacute;nikov&eacute; cesty (= samostatn&eacute; P&Uacute; bez požiarneho rizika),
- šachty evakuačn&yacute;ch v&yacute;ťahov, inštalačn&eacute; šachty,
- elektrick&eacute; stanice,
- n&aacute;hradn&eacute; zdroje a ostatn&eacute; priestory so zariadeniami, pri ktor&yacute;ch je požadovan&aacute; činnosť pri požiari,
Požiarne riz
iko, stupeň protipožiarnej bezpečnosti
V nasleduj&uacute;com prehľade je uveden&eacute; ku každ&eacute;mu hlavn&eacute;mu typu požiarneho &uacute;seku (P&Uacute;) s&uacute;časne požiarne
riziko a z neho vypl&yacute;vaj&uacute;ce zatriedenia do stupňa protipožiarnej bezpečnosti (resp. taxat&iacute;vne zatriedenie) podľa
STN 92 0201-2.
P&Uacute; obytn&yacute;ch buniek
V zmysle STN 92 0201-2 čl. 3.4 s&uacute; P&Uacute; jednotliv&yacute;ch obytn&yacute;ch buniek (bytov) zatrieden&eacute; taxat&iacute;vne podľa
podlažnosti danej stavby. V stavb&aacute;ch od 3 do 8 nadzemn&yacute;ch podlaž&iacute; - II&deg;PB, v stavb&aacute;ch do 3 nadzemn&yacute;ch
podlaž&iacute; - I&deg;PB.
V zmysle STN 92 0201-1 pr&iacute;lohy K je pre byty možn&eacute; uvažovať bez v&yacute;počtu s pv = 50 kg/m2 a a = 1,0.
Veľkosť požiarnych &uacute;sekov tvoriacich obytn&eacute; bunky je vyhovuj&uacute;ca.
Chr&aacute;nen&eacute; &uacute;nikov&eacute; cesty (CH&Uacute;C)
V stavbe je navrhnut&aacute; chr&aacute;nen&eacute; &uacute;nikov&aacute; cesta typu B. Minim&aacute;lny stupeň protipožiarnej bezpečnosti
CH&Uacute;C B s predpokladan&yacute;m časom evaku&aacute;cie do 15 min&uacute;t je podľa STN 92 0200-2, tab.1- III&deg;PB.
Požiadavky na stavebn&eacute; konštrukcie
Požiadavky na požiarne odolnosti jednotliv&yacute;ch stavebn&yacute;ch konštrukci&iacute; sa určuj&uacute; podľa zatriedenia do
stupňa protipožiarnej bezpečnosti (&deg;PB) STN 92 0201-2, tab. 1.
U všetk&yacute;ch stavebn&yacute;ch v&yacute;robkov (požiarne uz&aacute;very, požiarne steny, požiarne stropy, nosn&aacute; konštrukcia
stavby) dodržanie všetk&yacute;ch požiadaviek na požiarne odolnosti stavebn&yacute;ch konštrukci&iacute; a požadovan&eacute; konštrukčn&eacute;
druhy či stupne horľavosti materi&aacute;lov mus&iacute; dokladovať v&yacute;robca, resp. dod&aacute;vateľ. U stavebn&yacute;ch v&yacute;robkov sa
postupuje podľa z&aacute;kona NR SR č. 90/1998 Z. z. o stavebn&yacute;ch v&yacute;robkoch v znen&iacute; neskorš&iacute;ch predpisov a z&aacute;kona
NR SR č. 264/1999 Z. z. o technick&yacute;ch požiadavk&aacute;ch na v&yacute;robky a o posudzovan&iacute; zhody a o zmene a doplnen&iacute;
niektor&yacute;ch z&aacute;konov v znen&iacute; neskorš&iacute;ch predpisov. V zmysle &sect; 8 vyhl&aacute;šky MV SR č. 94/2004 Z.z. sa požiarna
odolnosť navrhovan&yacute;ch konštrukci&iacute; určuje na z&aacute;klade počiatočnej sk&uacute;šky typu alebo v&yacute;počtom podľa technickej
normy (napr. eurok&oacute;dy 2,3,4,5,6, t.j. P ENV 1994-1-2, P ENV 1992-1-2, P ENV 1993-1-3, P ENV 1995-1-2, P ENV
1996-1-2). Klasifik&aacute;cia požiarnych charakterist&iacute;k stavebn&yacute;ch v&yacute;robkov a prvkov stavieb mus&iacute; zodpovedať
požiadavk&aacute;m STN EN 13501-1.
Krit&eacute;ria požiarnej odolnosti stavebn&yacute;ch konštrukci&iacute; s&uacute; tak&eacute;to:
R – vyjadruje krit&eacute;rium nosnosti a stability. Tam, kde konštrukcie zaisťuj&uacute;ce stabilitu stavby tvoria
s&uacute;časne požiarne steny, požiarne stropy či obvodov&eacute; steny alebo s&uacute; ich s&uacute;časťou, musia s&uacute;časne spĺňať aj
ďalšie predp&iacute;san&eacute; krit&eacute;ri&aacute; na celistvosť (E), tepeln&uacute; izol&aacute;ciu (I) či izol&aacute;ciu riaden&uacute; radi&aacute;ciou (W) podľa
požiadaviek pre t&uacute; - ktor&uacute; konštrukciu.
- nosn&eacute; konštrukcie zaisťuj&uacute;ce stabilitu stavby:
Ide o konštrukcie, ktor&yacute;ch porušen&iacute;m by došlo k porušeniu stability stavby alebo jej časti:
III&deg; PB v nadzemn&yacute;ch podlažiach
II&deg; PB v nadzemn&yacute;ch podlažiach
I&deg; PB v nadzemn&yacute;ch podlažiach
Nosn&eacute; konštrukcie zaisťuj&uacute;ce stabilitu stavby musia podľa &sect; 38 ods. 4 vyhl&aacute;šky MV SR č. 94/2004 Z.z.
spĺňať podmienku, aby požiarna odolnosť nosn&yacute;ch konštrukci&iacute; na nižšom podlaž&iacute; nebola nižšia, ako je
požadovan&aacute; požiarna odolnosť od nich z&aacute;visl&yacute;ch zvisl&yacute;ch nosn&yacute;ch konštrukci&iacute; na vyššom podlaž&iacute;. Minim&aacute;lna
požiadavka na nosn&eacute; konštrukcie stavieb (R) je vzhľadom na najnižš&iacute; stupeň PB chr&aacute;nen&yacute;ch &uacute;nikov&yacute;ch ciest typu
B III&deg; PB – 60 min&uacute;t.
- požiarne stropy:
Všetky požiarne stropy bud&uacute; s&uacute;časne konštrukciami zaisťuj&uacute;cimi stabilitu stavby, preto musia plniť
krit&eacute;ria REI v min&uacute;tach nasledovne:
R60+EI45
R60+EI30
- požiarne steny:
Požiarne steny sa musia vždy st&yacute;kať (hore i dole) s požiarnymi stropmi. Nenosn&eacute; požiarne steny musia
plniť krit&eacute;ria EI, nosn&eacute; REI v min&uacute;tach:
- obvodov&eacute; steny:
Nosn&eacute; obvodov&eacute; steny zaisťuj&uacute;ce stabilitu stavby
Nosn&eacute; obvodov&eacute; steny zaisťuj&uacute;ce stabilitu stavby patria medzi konštrukcie, ktor&eacute; v danom pr&iacute;pade
musia bez ohľadu na miesto plniť krit&eacute;rium R. Okrem toho z vn&uacute;tornej strany musia plniť aj nasledovn&eacute; krit&eacute;rium
EW s odolnosťami podľa P&Uacute;, v ktorom sa nach&aacute;dzaj&uacute;, nakoľko s&uacute; považovan&eacute; za požiarne uzavret&eacute; plochy:
III&deg;PB v nadzemn&yacute;ch podlažiach
REW60
R60+EW45
R60+EW30
Obvodov&eacute; steny zasahuj&uacute;ce do požiarne nebezpečn&eacute;ho priestoru sa vyhotovuj&uacute; z konštrukčn&yacute;ch prvkov
druhu D1.
- nosn&eacute; konštrukcie striech bez požiarne deliacej funkcie:
Nosn&eacute; konštrukcie striech musia spĺňať krit&eacute;rium R.
III, II&deg;PB v nadzemn&yacute;ch podlažiach
- požiarne p&aacute;sy:
Požiarne p&aacute;sy sa v posudzovan&yacute;ch stavb&aacute;ch vzhľadom na ich požiarnu v&yacute;šku „h“ (&lt;12 m) nepožaduj&uacute;.
- požiarne uz&aacute;very:
V stavbe SO-01 sa bud&uacute; nach&aacute;dzať požiarne uz&aacute;very typu EW a EI.
EI = br&aacute;niaci š&iacute;reniu tepla – tieto musia byť navrhovan&eacute; medzi bežn&yacute;mi požiarnymi &uacute;sekmi a &uacute;sekmi CH&Uacute;C,
obmedzuj&uacute;ci š&iacute;renie tepla – medzi obytn&yacute;mi bunkami a ČCH&Uacute;C a CH&Uacute;C a ČCH&Uacute;C,
Požadovan&eacute; požiarne odolnosti požiarnych uz&aacute;verov:
III&deg; PB v podzemn&yacute;ch podlažiach
Všetky uveden&eacute; typy požiarnych uz&aacute;verov musia byť vybaven&eacute; automatick&yacute;m zatv&aacute;rac&iacute;m zariaden&iacute;m (C0
až C5), okrem dver&iacute; do bytov a technick&yacute;ch priestorov dočasn&yacute;m pracovn&yacute;m miestom, ktor&eacute; sa uzamykaj&uacute;.
Pre všetky typy požiarnych uz&aacute;verov platia s&uacute;časne požiadavky vyhl&aacute;šky MV SR č. 478/2008 Z.z.. Tu
s&uacute; uveden&eacute; o. i. požiadavky na sprievodn&uacute; dokument&aacute;ciu ku každ&eacute;mu požiarnemu uz&aacute;veru, požiadavky na &uacute;držbu,
opravy a kontroly a podmienky prev&aacute;dzkovania.
Požiadavky na konštrukcie s požadovanou požiarnou odolnosťou:
Skutočn&aacute; požiarna odolnosť konštrukcie nesmie byť v žiadnom mieste konštrukcie (ani v zoslabenej
časti n&iacute;k, šp&aacute;r, pri prestupoch a pod.) menšia ako je požiadavka na ňu kladen&aacute;. Prestupy všetk&yacute;ch rozvodov a
inštal&aacute;ci&iacute; cez požiarne deliace konštrukcie bud&uacute; pri realiz&aacute;cii stavby podľa &sect; 40 vyhl&aacute;šky MV SR č. 94/2004 Z.z.
požiarne utesnen&eacute; materi&aacute;lmi, resp. konštrukciami rovnak&eacute;ho druhu ako požiarne deliaca konštrukcia, ktorou
prestupuj&uacute; (t.j. v danom pr&iacute;pade vždy D1) a s požiarnou odolnosťou rovnou požadovanej odolnosti požiarne
deliacej konštrukcie, ktorou prestupuj&uacute;, nepožaduje sa však vyššia odolnosť ako EI 90D1.
Prestupy s plochou utesňovan&eacute;ho otvoru viac ako 0,04 m2 sa označuj&uacute; čitateľn&yacute;m n&aacute;pisom PRESTUP,
umiestnen&yacute;m priamo na konštrukčnom prvku prestupu alebo v jeho tesnej bl&iacute;zkosti.
&Uacute;nikov&eacute; cesty
Pre &uacute;čely tohto stupňa projektovej dokument&aacute;cie bolo stanoven&eacute; predbežn&eacute; pos&uacute;denie &uacute;nikov&yacute;ch ciest
podľa vyhl&aacute;šky MV SR č. 94/2004 Z.z. STN 92 0201-3.
Obsadenie stavieb osobami podľa STN 92 0241 je spracovan&eacute; za &uacute;čelom preverenia kapacity
navrhovan&yacute;ch &uacute;nikov&yacute;ch ciest.
Pre stanovenie času evaku&aacute;cie uvažuje špecialista PO v bytovom dome pre b&yacute;vanie z celkov&eacute;ho počtu
os&ocirc;b 100% os&ocirc;b s obmedzenou schopnosťou pohybu (osoby nad 60 rokov a osoby s pohybov&yacute;mi probl&eacute;mami.).
Bytov&yacute; dom 3 NP – nepriaznivejšia varianta
Projektovan&eacute; kapacity
3i x 1 = (4 x 1,5)x1 = 6
3i x 2 = (4 x 1,5)x2 = 12
&uacute;nik priamo do exteri&eacute;ru
CH&Uacute;C B
Osoby podľa
STN92 0241
18 dole schodami
E.s = 18 . 2,8 = 50,4 (nadzemn&eacute; podlažia)
u = E.s/Ku (tu - lu/vu) = 50,4 / 30 x (15 – 35/25) = 0,12 min = 1,5 &lt; 2,0 – vyhovuje
V bytovom dome sa nach&aacute;dza jedna CH&Uacute;C typu B so š&iacute;rkou ramien 1,1 m.
V s&uacute;lade s vyhl&aacute;škou MV SR 94/2004, &sect;58e.), mus&iacute; byť stavba s viac ako 2 nadzemn&yacute;mi podlažiami
v ktor&yacute;ch sa trvale, alebo pravidelne zdržuje viac ako 10 s obmedzenou schopnosťou pohybu zabezpečen&aacute;
evakuačn&yacute;m v&yacute;ťahom. Evakuačn&yacute; v&yacute;ťah mus&iacute; byť v s&uacute;lade s vyhl&aacute;škou MV SR 94/2004 &sect;58, umiestnen&yacute;
v chr&aacute;nenej &uacute;nikovej ceste typu B. Minim&aacute;lna činnosť vetracieho zariadenia CH&Uacute;C ako z&aacute;sahovej cesty mus&iacute; byť
Počet, druh a dĺžky &uacute;nikov&yacute;ch ciest
&Uacute;nikov&aacute; cesta je trvalo voľn&aacute; komunik&aacute;cia alebo priestor v stavbe, ktor&yacute; umožňuje bezpečn&uacute; evaku&aacute;ciu
os&ocirc;b zo stavby alebo z požiarneho &uacute;seku ohrozen&eacute;ho požiarom až na voľn&eacute; priestranstvo. &Uacute;nikov&eacute; cesty sa
podľa stupňa ochrany, ktor&yacute; poskytuj&uacute; unikaj&uacute;cim osob&aacute;m, členia na nechr&aacute;nen&eacute;, čiastočne chr&aacute;nen&eacute; a chr&aacute;nen&eacute;.
a.) Druh a počty &uacute;nikov&yacute;ch ciest
V posudzovanej stavbe je potrebn&eacute; zabezpečiť &uacute;nik osob&aacute;m, ktor&yacute;ch podrobn&eacute; počty bud&uacute; stanoven&eacute; až
v ďalšom stupni PD. Pre &uacute;nik bud&uacute; navrhnut&eacute; z obytn&eacute;ho domu chr&aacute;nen&eacute; &uacute;nikov&eacute; cesty (CH&Uacute;C) a nechr&aacute;nen&eacute;
&uacute;nikov&eacute; cesty (N&Uacute;C), ktor&eacute; ved&uacute; v r&aacute;mci požiarnych &uacute;sekov do chr&aacute;nen&yacute;ch, pr&iacute;p. čiastočne chr&aacute;nen&yacute;ch &uacute;nikov&yacute;ch
ciest alebo (v 1.NP) priamo von zo stavby.
Podľa &sect;54 vyhl&aacute;šky MV SR č. 94/2000 Z.z. mus&iacute; spoločn&aacute; komunik&aacute;cia, do ktorej ved&uacute; dvere
z jednotliv&yacute;ch obytn&yacute;ch buniek, tvoriť:
chr&aacute;nen&uacute; &uacute;nikov&uacute; cestu alebo
samostatn&yacute; požiarny &uacute;sek bez požiarneho rizika (ČCH&Uacute;C).
b.) Nechr&aacute;nen&eacute; &uacute;nikov&eacute; cesty (N&Uacute;C):
Nechr&aacute;nen&eacute; &uacute;nikov&eacute; cesty ved&uacute; v r&aacute;mci jednotliv&yacute;ch požiarnych &uacute;sekov po v&yacute;chod do ČCH&Uacute;C, CH&Uacute;C, resp.
po v&yacute;chod zo stavby. Začiatok &uacute;nikovej cesty z bytov sa v s&uacute;lade s vyhl&aacute;škou MV SR 225/2012, &sect; 65, odsek 5
považuje od osi v&yacute;chodu z bytu.
c.) Čiastočne chr&aacute;nen&eacute; &uacute;nikov&eacute; cesty (ČCH&Uacute;C):
(ČCH&Uacute;C):
ČCH&Uacute;C s&uacute; samostatn&eacute; požiarne &uacute;seky chodieb, ktor&eacute; s&uacute; bez požiarneho rizika. Ak vedie ČCH&Uacute;C len
jedn&yacute;m smerom do CH&Uacute;C, m&ocirc;že byť jej dĺžka max. 20 m, ak vedie dvoma smermi, smie byť najviac 40 m. Minim&aacute;lna
dovolen&aacute; š&iacute;rka ČCH&Uacute;C je z hľadiska PB obecne stanoven&aacute; na 1,5 u (0,825 m, v dver&aacute;ch 0,8 m) avšak pre stavby
pre b&yacute;vanie s&uacute; požadovan&eacute; nasledovn&eacute; podmienky:
b&yacute;vanie: všetky komunik&aacute;cie musia mať svetlosť najmenej 1,1 m, pričom v dver&aacute;ch m&ocirc;že byť z&uacute;ženie na 0,9 m
(podľa STN 73 4301),
ČCH&Uacute;C mus&iacute; byť požiarny &uacute;sek bez požiarneho rizika, preto okrem podlahovej krytiny a dver&iacute; tu nesm&uacute;
byť navrhovan&eacute; žiadne horľav&eacute; materi&aacute;ly. Elektrick&eacute; rozvody v šacht&aacute;ch a elektrick&eacute; rozv&aacute;dzače na chodb&aacute;ch
musia byť od ČCH&Uacute;C požiarne oddelen&eacute;.
d.) Chr&aacute;nen&eacute; &uacute;nikov&eacute; cesty
cesty (CH&Uacute;C):
- s&uacute; počas požadovan&eacute;ho času evaku&aacute;cie a z&aacute;sahu bezpečn&eacute; (chr&aacute;nen&eacute;) komunik&aacute;cie s vy&uacute;sten&iacute;m do vonkajšieho
priestranstva. CH&Uacute;C musia tvoriť samostatn&eacute; požiarne &uacute;seky, požiarne oddelen&eacute; od ostatn&yacute;ch priestorov stavby
konštrukciami druhu D1 a musia mať zabezpečen&eacute; požadovan&eacute; vetranie v pr&iacute;pade požiaru. V CH&Uacute;C sa preto
nesm&uacute; nach&aacute;dzať žiadne horľav&eacute; materi&aacute;ly (povolen&eacute; s&uacute; len madl&aacute;, podlahov&eacute; krytiny, dvere a okn&aacute; - &sect;53
vyhl&aacute;šky MV SR č. 94/2004 Z.z.).
V CH&Uacute;C nesm&uacute; byť umiestnen&eacute;:
rozvody horľav&eacute;, resp. rozvody horľav&yacute;ch l&aacute;tok,
VZT (okrem VZT zabezpečuj&uacute;cich vetranie t&yacute;chto priestorov),
elektrick&eacute; rozvody a rozv&aacute;dzače, okrem t&yacute;ch, ktor&eacute; sl&uacute;žia len pre prev&aacute;dzku CH&Uacute;C,
dymovody, rozvody strednotlakovej a vyskokotlakovej pary,
rozvody toxick&yacute;ch alebo inak nebezpečn&yacute;ch l&aacute;tok.
Rozvody: (okrem rozvodov horľav&yacute;ch l&aacute;tok a l&aacute;tok toxick&yacute;ch alebo inak nebezpečn&yacute;ch) m&ocirc;žu byť
v priestore CH&Uacute;C umiestnen&eacute;, ak bud&uacute; požiarne oddelen&eacute; konštrukciami druhu D1 s dvojn&aacute;sobnou odolnosťou ako
je doba evaku&aacute;cie danou CH&Uacute;C (najmenej však 30 min) - &sect;75 vyhl&aacute;šky MV SR č. 94/2004 Z.z.).
V posudzovan&yacute;ch stavb&aacute;ch (bytov&eacute; domy a polyfunkčn&aacute; stavba) sa uvažuje s CH&Uacute;C typu B.
CH&Uacute;C typu B mus&iacute; byť vybaven&aacute; samostatne vetran&yacute;m schodiskom a požiarnymi predsieňami. Uvažuje sa, že pri
požiari bud&uacute; CH&Uacute;C B vetran&eacute; umel&yacute;m resp. prirodzen&yacute;m vetran&iacute;m. CH&Uacute;C mus&iacute; byť zabezpečen&aacute; n&uacute;dzov&yacute;m
osvetlen&iacute;m (&sect;51 ods.8 vyhl&aacute;šky MV SR č. 94/2004 Z.z.).
Požiarna predsieň v CH&Uacute;C typu B mus&iacute; byť od schodiska oddelen&aacute; dverami odoln&yacute;mi voči prieniku dymu
(S) so samozatv&aacute;račom (C).
e.) Vetranie CH&Uacute;C:
CH&Uacute;C
Vzhľadom na skutočnosť, že CH&Uacute;C sl&uacute;žia aj ako z&aacute;sahov&eacute; cesty, mus&iacute; byť činnosť vetrac&iacute;ch zariaden&iacute;
v CH&Uacute;C B pri požiari zabezpečen&aacute; minim&aacute;lne 45 min&uacute;t.
Uvažuje sa, že v obytnom dome bude vetranie priestorov CH&Uacute;C zabezpečen&eacute; prirodzen&yacute;m vetran&iacute;m
v s&uacute;lade s požiadavkami STN 92 0201-3, čl. 5.5.1.3 Nepredpoklad&aacute; sa, že by čas evaku&aacute;cie os&ocirc;b v CH&Uacute;C trval
viac ako 15 min&uacute;t.
Druh&yacute;m n&aacute;hradn&yacute;m zdrojom pre požiarnotechnick&eacute; zariadenia, zabezpečuj&uacute;ce činnosť požiarnych
ventil&aacute;torov v CH&Uacute;C a chod evakuačn&yacute;ch v&yacute;ťahov sa predpoklad&aacute; UPS, ktor&aacute; mus&iacute; byť od ostatn&yacute;ch priestorov
požiarne oddelen&aacute;.
f/ Požiadavky na &uacute;nikov&eacute; cesty:
Požiadavky na &uacute;nikov&eacute; cesty podľa &sect;70-74 vyhl&aacute;šky MV SR č. 94/2004 Z.z., STN 92 0201-3 a vyhl&aacute;šky
MV SR č. 285/2001 Z.z:
Schodisk&aacute; na &uacute;nikovej ceste pre viac ako 50 os&ocirc;b musia mať sklon viac ako 25&deg;a menej ako 35&deg;.
V danom pr&iacute;pade je požiadavka dodržan&aacute; u oboch schod&iacute;sk CH&Uacute;C i u všetk&yacute;ch vonkajš&iacute;ch vyrovn&aacute;vac&iacute;ch
schod&iacute;sk.
Podlaha na oboch stran&aacute;ch dver&iacute; na &uacute;nikovej ceste mus&iacute; byť aspoň v š&iacute;rke dvern&eacute;ho kr&iacute;dla v rovnakej
v&yacute;škovej &uacute;rovni (bez zv&yacute;šen&yacute;ch prahov).
Smer &uacute;niku mus&iacute; byť vyznačen&yacute; na všetk&yacute;ch &uacute;nikov&yacute;ch cest&aacute;ch všade tam, kde nie je priamo viditeľn&yacute;
v&yacute;chod na voľn&eacute; priestranstvo. Značky, ktor&eacute; maj&uacute; byť viditeľn&eacute; z diaľky, sa umiestňuj&uacute; do v&yacute;šky 2,5 m alebo
nad zariaďovanie predmety, značky, ktor&eacute; s&uacute; viditeľn&eacute; zbl&iacute;zka, maj&uacute; byť vo v&yacute;ške oč&iacute; (1,5 m od podlahy).
Označenie sa navrhuje podľa pr&iacute;lohy k nariadeniu vl&aacute;dy SR č. 387/2006 Z.z.
Dvere na všetk&yacute;ch &uacute;nikov&yacute;ch cest&aacute;ch:
musia sa otv&aacute;rať v smere &uacute;niku a musia sa otv&aacute;rať poot&aacute;čan&iacute;m dvern&eacute;ho kr&iacute;dla v postrann&yacute;ch
z&aacute;vesoch alebo v čapoch. Na ďalšej &uacute;nikovej ceste m&ocirc;žu byť aj dvere k&yacute;vav&eacute; (v danej stavbe nie s&uacute; v&ocirc;bec
navrhovan&eacute;) alebo vodorovne posuvn&eacute; (nie však iba automatick&eacute;, ale aj s ručn&yacute;m ovl&aacute;dan&iacute;m). Podmienka sa
nevzťahuje len na vonkajšie dvere, zo stavby pre b&yacute;vanie a na vonkajšie dvere, ktor&yacute;mi unik&aacute; najviac 100 os&ocirc;b
zo stavby na voľn&eacute; priestranstvo (v danom pr&iacute;pade sa teda sm&uacute; opačne otv&aacute;rať všetky v&yacute;chody zo stavby na
voľn&eacute; priestranstvo).
Každ&eacute; dvern&eacute; kr&iacute;dlo, ktor&eacute; sa započ&iacute;tava do š&iacute;rky &uacute;nikovej cesty (bez ohľadu na počet unikaj&uacute;cich os&ocirc;b) a je
pri prev&aacute;dzke zabezpečen&eacute; (zaisten&eacute;, zamknut&eacute;), mus&iacute; byť na strane v smere &uacute;niku opatren&eacute; stavebn&yacute;m
kovan&iacute;m podľa STN EN 179 alebo STN EN 1125, t.j. jedn&yacute;m z dvoch druhov bezpečnostn&eacute;ho mechanizmu.
Bezpečnostn&yacute; mechanizmus podľa vyhl&aacute;šky MV SR č. 285/2001 Z.z. (panikov&yacute; alebo n&uacute;dzov&yacute; v&yacute;chodov&yacute; uz&aacute;ver) je
zariadenie, umožňuj&uacute;ce osob&aacute;m použiť požiarny uz&aacute;ver či obyčajn&eacute; dvere na &uacute;nikovej ceste v pr&iacute;pade, ak je
tento pri bežnej prev&aacute;dzke uzamknut&yacute;. Umožňuje otvorenie uzamknut&yacute;ch dver&iacute; bez použitia kľ&uacute;ča alebo in&yacute;ch
n&aacute;strojov v čase do 1 sekundy.
N&uacute;dzov&yacute; uz&aacute;ver sa vyhotovuje tak, aby sa po otvoren&iacute; automaticky vr&aacute;til do zaistenej polohy a bol pripraven&yacute;
na opakovan&eacute; použitie. Konštrukcia mus&iacute; byť riešen&aacute; tak, aby sa uvoľnenie n&uacute;dzov&eacute;ho uz&aacute;veru nemohlo
zablokovať p&ocirc;soben&iacute;m sily v smere v&yacute;chodu kdekoľvek na povrch dver&iacute;. Vonkajš&iacute; ovl&aacute;dac&iacute; uz&aacute;ver (bez ohľadu
na to, či je zamknut&yacute; alebo odomknut&yacute;) nesmie znemožniť otvorenie n&uacute;dzov&eacute;ho uz&aacute;veru zvn&uacute;tra (v smere &uacute;niku).
N&uacute;dzov&yacute; uz&aacute;ver mus&iacute; byť vyhotoven&yacute; podľa STN EN 179.
Pre všetky typy požiarnych uz&aacute;verov a bezpečnostn&yacute;ch mechanizmov platia aj požiadavky vyhl&aacute;šky MV
SR č. 478/2008 Z.z., kde s&uacute; uveden&eacute; aj požiadavky na označenie uz&aacute;verov, sprievodn&uacute; dokument&aacute;ciu ku každ&eacute;mu
požiarnemu uz&aacute;veru, požiadavky na &uacute;držbu, opravy a kontroly a podmienky prev&aacute;dzkovania.
Odstupov&eacute; vzdialenosti
Najnepriaznivejšie odstupov&eacute; vzdialenosti od stavieb s&uacute; určen&eacute; podľa STN 92 0201-4, tab.3 a tab.6.
Podrobn&eacute; riešenie odstupov&yacute;ch vzdialenost&iacute; bude spracovan&eacute; v ďalšom stupni projektovej dokument&aacute;cie.
Bytov&yacute; dom:
(1.NP)
% požiarne otvorenej plochy:
Dĺžka požiarneho &uacute;seku:
Odstupov&aacute; vzdialenosť:
73 kg.m-2
Obytn&eacute; bunky
13 m (najnepriaznivejš&iacute; byt)
Vzduchotechnick&eacute; zariadenia
Všetky rozvody a zariadenia VZT musia spĺňať požiadavky STN 73 0872.
Všeobecn&eacute; z&aacute;sadn&eacute; požiadavky:
- v každom mieste prestupu VZT zariadenia alebo potrubia cez požiarne deliacu konštrukciu, t.j.
požiarny strop alebo požiarnu stenu, mus&iacute; byť osaden&aacute; požiarna klapka (čl.6), okrem pr&iacute;padu keď je potrubie v
celej dĺžke prechodu cez in&eacute; požiarne &uacute;seky chr&aacute;nen&eacute; požiarnou izol&aacute;ciou (triedy reakcie na oheň A1 alebo A2, v
CH&Uacute;C v&yacute;lučne A1 najviac A2 s1,d0, a to aj v mieste prestupu, ak t&uacute;to ochranu neposkytuje samotn&aacute; požiarne
deliaca konštrukcia.
- utesnenie prestupov VZT potrubia (čl.8) mus&iacute; byť v danom pr&iacute;pade vždy hmotou triedy reakcie na
oheň A1 najviac A2 s1,d0 lebo všetky požiarne deliace konštrukcie stavby s&uacute; nehorľav&eacute; druhu D1) s požiarnou
odolnosťou rovnou požadovanej odolnosti steny, nepožaduje sa však vyššia ako 90 min.
- v mieste prestupu mus&iacute; byť vždy nehorľav&eacute; potrubie (čl.7), a to min. vo vzdialenosti 0,5 m na každ&uacute;
stranu od požiarnej klapky. V CH&Uacute;C musia byť potrubia len nehorľav&eacute; (z materi&aacute;lov triedy reakcie na oheň A1
najviac A2 s1,d0, resp. konštrukcie druhu D1),
- všetky potrubia VZT, ktor&eacute; nesl&uacute;žia pre vetranie CH&Uacute;C, musia byť od priestoru CH&Uacute;C požiarne
oddelen&eacute; konštrukciou druhu D1. Požiarne vetranie, t.j. vetranie všetk&yacute;ch priestorov CH&Uacute;C je navrhovan&eacute; n&uacute;ten&eacute;
a bude zabezpečen&eacute; samostatn&yacute;mi zariadeniami, ktor&eacute; musia byť od ostatn&yacute;ch požiarnych &uacute;sekov požiarne
oddelen&eacute;. Ventil&aacute;tory umiestnen&eacute; na streche musia byť v dostatočnej vzdialenosti od in&yacute;ch zariaden&iacute;. Ovl&aacute;danie
jednotiek požiarneho vetrania v CH&Uacute;C bude manu&aacute;lne.
Elektrick&eacute; prev&aacute;dzky, zariadenia a rozvody
Všetky elektrick&eacute; zariadenia musia byť navrhnut&eacute; v s&uacute;lade s určen&yacute;m prostred&iacute;m podľa platn&yacute;ch
predpisov elektro. Protokol o vplyvoch na elektrick&eacute; zariadenia bude s&uacute;časťou dokument&aacute;cie pre stavebn&eacute;
povolenie v časti elektro.
Prestupy k&aacute;blov cez požiarne deliace konštrukcie, rovnako ako všetky ostatn&eacute; prestupy, musia byť
deliacej konštrukcie, ktorou prestupuj&uacute;. Elektrick&eacute; rozvody musia byť v stavbe veden&eacute; v s&uacute;lade s platn&yacute;mi
normami elektro (musia byť dodržan&eacute; podmienky pre dovolen&yacute; s&uacute;beh rozvodov a ich vz&aacute;jomn&eacute; vzdialenosti).
Požiadavky na funkčn&uacute; odolnosť tr&aacute;s k&aacute;blov na trval&uacute; dod&aacute;vku elektrickej energie podľa pr&iacute;lohy A,
STN 92 0203:
n&uacute;dzov&eacute; osvetlenie minim&aacute;lne
60 min&uacute;t,
vetranie chr&aacute;nen&yacute;ch &uacute;nikov&yacute;ch ciest
45 min&uacute;t CH&Uacute;C B,
evakuačn&yacute; v&yacute;ťah
45 min&uacute;t
Požiadavky na k&aacute;ble:
Stavby na b&yacute;vanie (komunikačn&eacute; priestory)
B2ca -s1,d1,a1
Riešenie n&aacute;hradn&eacute;ho zdroja pre evakuačn&eacute; v&yacute;ťahy bude predmetom v ďalšom stupni projektovej
N&uacute;dzov&eacute; osvetlenie v zmysle požiadaviek &sect; 73 vyhl&aacute;šky MV SR č. 94/2004 Z.z. bude zrealizovan&eacute;
v schodisk&aacute;ch posudzovanej stavby po celej ich dĺžke.
Hlasov&aacute; signaliz&aacute;cia požiaru
Hlasovou signaliz&aacute;ciou požiaru (dom&aacute;ci rozhlas) sa v stavb&aacute;ch pre b&yacute;vanie nepožaduje (&sect;90 ods.1d,
Pr&iacute;jazdy, pr&iacute;stupy a z&aacute;sahov&eacute; cesty
Podmienky pre pr&iacute;jazd mobilnej hasičskej techniky k posudzovanej stavbe bude zabezpečen&eacute; po
komunik&aacute;ci&aacute;ch minim&aacute;lnej š&iacute;rky min. 3,5 m a s &uacute;nosnosťou najmenej 80 kN na zaťaženie jednou n&aacute;pravou.
N&aacute;stupn&eacute; plochy nemusia byť vybudovan&eacute;. Stavby s&uacute; zabezpečen&eacute; vn&uacute;torn&yacute;mi z&aacute;sahov&yacute;mi cestami,
ktor&eacute; predstavuj&uacute; v s&uacute;lade s &sect; 83 vyhl&aacute;šky MV SR č. 94/2004 Z.z. schodisk&aacute; tvoriace chr&aacute;nen&eacute; &uacute;nikov&eacute; cesty.
Pr&iacute;stupov&aacute; komunik&aacute;cia umožn&iacute; hasičsk&yacute;m vozidl&aacute;m pribl&iacute;žiť sa k v&yacute;chodom zo stavieb do vzdialenosti
30 m (&sect; 82 vyhl&aacute;šky MV SR č. 94/2004 Z.z.).
Vn&uacute;torn&eacute; z&aacute;sahov&eacute; cesty s&uacute; podľa požiadaviek &sect; 84 vyhl&aacute;šky MV SR č. 94/2004 Z.z. zriaden&eacute; a tvoria
ich chr&aacute;nen&eacute; &uacute;nikov&eacute; cesty typu B.
Voda pre hasenie požiarov
Potreba požiarnej vody pre hasenie požiaru bola stanoven&aacute; v zmysle &sect;6 (1) vyhl&aacute;šky MV SR č.
699/2004 Z.z. a podľa STN 92 0400 čl. 4.1 a tab. 2, pre najnepriaznivejš&iacute; požiarny &uacute;sek ktor&yacute; sa uvažuje do
max. plochy 1000 m2.
12 l/s pri r&yacute;chlosti v = 1,5 m/s (r&yacute;chlosť dosiahnut&aacute; pomocou požiarneho čerpadla).
Potreba požiarnej vody je zabezpečen&aacute; z rozvodu vody DN 100, na ktor&yacute;ch sa nach&aacute;dzaj&uacute; podzemn&eacute;
hydranty DN100 na ul. Gogoľova a ul. Jozefa Kronera.
V posudzovanom bytovom dome bud&uacute; podľa &sect;12 (1a) navrhnut&eacute; hadicov&eacute; navijaky s dĺžkou hadice 30 m,
s menovitou svetlosťou 25 mm, s minim&aacute;lnym priemerom hubice 10 mm s minim&aacute;lnym prietokom Q = 1,0 l/s pri
tlaku 0,2 MPa (čl.5.5.2 d1, STN 92 0400). Vodovodn&eacute; potrubie (ležat&eacute; i st&uacute;pacie) bude navrhnut&eacute; pre s&uacute;časn&eacute;
použitie najmenej dvoch hadicov&yacute;ch zariaden&iacute; (čl. 5.6.1 STN 92 0400).
Označenie zariaden&iacute; požiarneho vodovodu, tlakov&eacute; sk&uacute;šky a kontrola sa musia prev&aacute;dzať podľa
vyhl&aacute;šky MV SR č. 699/2004 Z.z. a STN 92 0400 pr&iacute;loha C. Jednotliv&eacute; časti požiarneho vodovodu musia mať
preuk&aacute;zan&uacute; zhodu vlastnost&iacute;. Jednotliv&eacute; časti vn&uacute;torn&eacute;ho i vonkajšieho požiarneho vodovodu musia mať
preuk&aacute;zan&uacute; zhodu vlastnost&iacute;.
Požiarnotechnick&eacute; zariadenia
V stavb&aacute;ch sa inštal&aacute;cia EPS, SHZ a ZODT nepožaduje.
Zhromažďovacie priestory a gar&aacute;že pre viac ako 50 motorov&yacute;mi vozidlami sa v priestoroch
posudzovan&yacute;ch stavieb nenach&aacute;dzaj&uacute;.
Z&aacute;ver – zhodnotenie riešenia stavby
stavby z hľadiska potrieb &uacute;zemn&eacute;ho konania
Pre potreby &uacute;zemn&eacute;ho konania je stavba posudzovan&aacute; a schvaľovan&eacute; z hľadiska t&yacute;chto aspektov PB:
- umožnenia &uacute;činn&eacute;ho hasebn&eacute;ho z&aacute;sahu,
- potreby zabezpečenia stavieb vodou pre hasenie požiarov,
- vz&aacute;jomn&eacute;ho vzťahu s jestvuj&uacute;cou z&aacute;stavbou v r&aacute;mci pos&uacute;denia odstupov&yacute;ch
vzdialenost&iacute;,
Z tohto pos&uacute;denia a koncepčn&eacute;ho riešenia PB vypl&yacute;va, že v rozsahu požadovanom pre &uacute;zemn&eacute; konanie
s&uacute; požiadavky protipožiarnej bezpečnosti v dokument&aacute;cii pre stavbu splnen&eacute;.
2.5.2 CIVILN&Aacute; OCHRANA
Pri n&aacute;vrhu ukrytia projektant v spolupr&aacute;ci s pracovn&iacute;kom CO vytypoval priestory stavby, ktor&eacute; by pri
čo najmenšej pracnosti, spotrebe materi&aacute;lu a nasadenosti pracovn&yacute;ch s&iacute;l zabezpečovali požadovyn&yacute; typ &uacute;krytu
a dosahovali požadovan&uacute; hodnotu ochrann&eacute;ho s&uacute;činiteľa stavby k0. &Uacute;kryt bude situovan&yacute; v suter&eacute;ne ( 1.PP ),
ktor&yacute; je cel&yacute; pod &uacute;rovňou ter&eacute;nu. S&uacute; navrhnut&eacute; dva jednoduch&eacute; &uacute;kryty budovan&eacute; svojpomocne ( spolu pre 20
os&ocirc;b ).
Norma na uvedenie &uacute;krytu do stavu technickej pripravenosti od vyhl&aacute;senia mimoriadnej situ&aacute;cie, alebo
brannej pohotovosti št&aacute;tu je v zmysle Vyhl.č.202/2002 Zb. z. 12 hod. pre pr&iacute;jem uk&yacute;van&yacute;ch a 24 hod pre
zv&yacute;šenie ochrann&yacute;ch vlastnost&iacute; stavby. Požadovan&aacute; hodnota k0 mus&iacute; byť minim. 50 – pre predmetn&yacute; typ &uacute;krytu.
Podrobn&eacute; riešenie ochrany bude spracovan&eacute; v ďalšom stupni PD..
3.1. Vecn&eacute; v&auml;zby stavby na okolie
Nadstavba a dostavba existuj&uacute;ceho objektu b&yacute;valej šk&ocirc;lky, toho času využ&iacute;van&yacute; na komerčn&eacute; &uacute;čely ako
napr. predajňa, či miestne pohostinstvo je m&aacute;lo využ&iacute;van&eacute; a ch&aacute;traj&uacute;ce. Vybavenosť v r&aacute;mci s&iacute;dliska Ľadoveň je
postačuj&uacute;ca a tak&eacute;to prev&aacute;dzky, ktor&eacute; s&uacute; v dnešnom objekte sa javia ako nadbytočn&eacute;, alebo m&aacute;lo využ&iacute;van&eacute;.
Avšak z&aacute;ujem o nov&eacute; b&yacute;vanie v tomto &uacute;zem&iacute; je veľk&yacute;, pr&aacute;ve pre spom&iacute;nan&eacute; existuj&uacute;ce z&aacute;zemie a existuj&uacute;cu
infraštrukt&uacute;ru a hlavne zeleň, ktor&aacute; je v r&aacute;mci &uacute;zemia už dostatočne vzrastl&aacute; a funkčn&aacute;.
Z toho d&ocirc;vodu investor prehodnotil svoju činnosť v &uacute;zem&iacute; a na z&aacute;klade t&yacute;chto faktorov sa rozhodol
prestavať tento objekt na bytov&yacute; dom z nadštandardn&yacute;mi bytmi.
Navrhovanou nadstavbou vznikne 5 nov&yacute;ch bytov&yacute;ch jednotiek, ktor&yacute;m bude treba zabezpečiť potrebn&yacute;
počet dlhodob&yacute;ch parkovac&iacute;ch st&aacute;t&iacute; /min. 11 miest z toho 1 pre telesne postihnut&eacute;ho/ a ostatn&uacute; vybavenosť
s&uacute;visiacu s touto stavbou.
3.2. Term&iacute;n začatia a dokončenia stavby
Predpokladan&yacute; term&iacute;n začatia stavebn&yacute;ch pr&aacute;c je
a dokončenia stavby je
Objekt je napojen&yacute; na existuj&uacute;ce inžinierske siete, ktor&eacute; ponech&aacute;vame v p&ocirc;vodn&yacute;ch koridoroch. Samotn&aacute;
v&yacute;stavba si nevyžiada preložky inžinierskych siet&iacute; a nijako neovplyvn&iacute; chod existuj&uacute;cich prev&aacute;dzok.
4.1.1. Zariadenie staveniska
Pre potreby zriadenia staveniska bud&uacute; k dispoz&iacute;cii iba plochy na vlastnej stavbe, t.j. na parcel&aacute;ch
investora. Pozemok je oploten&yacute; existuj&uacute;cim oploten&iacute;m. Pr&iacute;jazd na stavbu bude z ulice Gogoľova. Bližšie riešenie
n&aacute;rokov zriadenia staveniska bud&uacute; spracovan&eacute; v ďalšom stupni PD.
4.1.2. Bezpečnostn&eacute; predpisy
Organiz&aacute;cie poveren&eacute; realiz&aacute;ciou stavby s&uacute; povinn&eacute; riadiť sa platn&yacute;mi bezpečnostn&yacute;mi smernicami
MPSVaR č. 718/2002 Z.z.
330/96 BOZP
374/1990 S&Uacute;BP
201/2001 Z.z.
Stavba bude realizovan&aacute; z vlastn&yacute;ch zdrojov investora a p&ocirc;žičky. Cel&aacute; invest&iacute;cia bude realizovan&aacute; na
pozemku investora, ktor&yacute; je pr&iacute;stupn&yacute; z verejnej komunik&aacute;cie a je napojen&yacute; na všetky inžinierske siete. Z toho
d&ocirc;vodu nebude nutn&eacute; investovať do t&yacute;chto oblast&iacute;.
4.2.1. Aproximat&iacute;vny odhad stavebn&yacute;ch n&aacute;kladov
Rozpočtov&eacute; n&aacute;klady na stavbu boli spracovan&eacute; na z&aacute;klade technicko-ekonomick&yacute;ch ukazovateľov
CENKROS 2009. Vypoč&iacute;tan&aacute; cena m&aacute; len orientačn&yacute; charakter, vych&aacute;dzaj&uacute;c z dan&eacute;ho stupňa PD.
• ASAN&Aacute;CIE EXISTUJ&Uacute;CICH KONŠTRUKCII A ODVOZ NA SKL&Aacute;DKU
(objem odpadov&yacute;ch konštrukcii cca 300
• NADSTAVBA A STAVEBN&Eacute; &Uacute;PRAVY OBJEKTU (obostavan&yacute; priestor BD=cca 2500 m3, jednotkov&aacute; cena podľa
2500 x 173 = 432 500.- Eur
tab. KS 1122, OS 803 5 Domy bytov&eacute; netypov&eacute;= 173 Eur/m3 )
• DROBN&Aacute; ARCHITEKT&Uacute;RA (obostavan&yacute; priestor 10 m3, jednotkov&aacute; cena podľa tab. KS 1230, OS 815 94
10 x 128 = 1 280,- Eur
Pr&iacute;strešky a kiosky a pod. = 128 Eur/m3 )
• SPEVNEN&Eacute; PLOCHY PARKOVISKA S VYBUDOVAN&Iacute;M ORL (rozloha 261 m , jednotkov&aacute; cena podľa tab. = 65,20
(261 x 65,20)+550+2800 = 20 367,- Eur
Eur/m2 + 550 Eur za zemne prace + 2800 Eur ORL)
• SPEVNEN&Eacute; PLOCHY NOV&Yacute;CH CHODN&Iacute;KOV (rozloha 22 m2, jednotkov&aacute; cena podľa tab. = 38,00 Eur/m2 + 65 Eur
za zemne prace)
22 x 38,00)+65 = 901,0- Eur
• NOV&Eacute; OPLOTENIE + automatick&aacute; br&aacute;na (dĺžka nov&yacute;ch oploten&iacute; cca 100 m, jednotkov&aacute; cena podľa tab. KS 2ex
OS 815 22 Oplotenia s podmur. = 240 Eur/m)
100x240= 24 000,- Eur
• SADOVN&Iacute;CKE &Uacute;PRAVY OKOLIA A VYBUDOVANIE osvetlenia + pr&iacute;pojky teplovodu
cca 10 000,- Eur
∑ 493 548,00 Eur
Projekt predpoklad&aacute; pripojenie na existuj&uacute;ce inžinierske siete. Existuj&uacute;ci objekt je napojen&yacute; na verejn&yacute;
vodovod, kanaliz&aacute;ciu, plyn, silnopr&uacute;d i slabopr&uacute;d a hor&uacute;covod. Pre určenie jednotliv&yacute;ch kapac&iacute;t, je poč&iacute;tan&eacute; s 20
4.3.1. Z&aacute;sobovanie Teplom
Projekt rieši n&aacute;vrh a koncepciu &uacute;stredn&eacute;ho vykurovania. Zdrojom tepla bude kompaktn&aacute; OST syst&eacute;mu
hor&uacute;ca voda/voda pripojen&aacute; na existuj&uacute;ce miestne rozvody CZT.
POTEBA TEPLA A TEPELN&Eacute;HO V&Yacute;KONU
Celkov&yacute; projektovan&yacute; tepeln&yacute; pr&iacute;kon objektu bol vypoč&iacute;tan&yacute; pre nasledovn&eacute; okrajov&eacute; podmienky:
• Vonkajšia v&yacute;počtov&aacute; teplota (Martin)
• Priemern&aacute; vn&uacute;torn&aacute; teplota obytn&yacute;ch priestorov
• Priemern&aacute; vn&uacute;torn&aacute; teplota technick&yacute;ch priestorov v 1.P.P. a 1.N.P.
• Priemern&aacute; vonkajšia teplota počas vykurovacieho obdobia
• Dĺžka vykurovacieho obdobia
+2,8&deg;C
235 dn&iacute;
Tepeln&eacute; straty boli vypoč&iacute;tan&eacute; zjednodušenou met&oacute;dou obalov&yacute;ch konštrukci&iacute; pre vyššie uveden&eacute; okrajov&eacute;
podmienky a s uvažovan&iacute;m tepelnotechnick&yacute;ch vlastnost&iacute; obalov&yacute;ch stavebn&yacute;ch konštrukci&iacute; v s&uacute;lade s
STN 73 0540:
• 1.P.P.
• 1.N.P.
• 2.N.P.
• 3.N.P.
• Celkov&aacute; tepeln&aacute; strata objektu
Pri uvažovan&iacute; tepeln&yacute;ch str&aacute;t v rozvodoch vo v&yacute;ške 5% bude požadovan&yacute; menovit&yacute; tepeln&yacute; v&yacute;kon
zdroja tepla QZDR = 50,0 + 0,05 x 50,0 = 52,5kW.
Predbežn&aacute; ročn&aacute; potreba tepla na vykurovanie objektu:
QR,VYK =
24 &times; 3,6 x 10-3&times; 0,8&times; 52,5&times; 235&times; (20− 2,8)
20− (−15)
= 419,074GJ/rok = 116,6 MWh/rok
Zdrojom tepla bude kompaktn&aacute; odovzd&aacute;vacia stanica tepla (OST) hor&uacute;ca voda/voda. Prim&aacute;rnym zdrojom
tepla bude hor&uacute;covodn&aacute; sieť CZT v spr&aacute;ve Martico, a.s. OST bude pripojen&aacute; na sieť CZT hor&uacute;covodnou pr&iacute;pojkou.
OST bude umiestnen&aacute; v samostatnej miestnosti v 1.N.P. objektu. Bude pozost&aacute;vať z dvojice doskov&yacute;ch
tepeln&yacute;ch v&yacute;menn&iacute;kov, s&uacute;stavy armat&uacute;r, fakturačn&eacute;ho merača tepla, riadiaceho syst&eacute;mu, sekund&aacute;rnych armat&uacute;r,
čerpadiel a zabezpečovacieho zariadenia.
Hor&uacute;covodn&aacute; pr&iacute;pojka bude na lok&aacute;lnu vetvu siete CZT pripojen&aacute; v mieste existuj&uacute;ceho vedenia
zo z&aacute;padnej strany objektu na potrubia DN65..
Pr&iacute;pojka vst&uacute;pi do objektu v priestore pod spojovacou chodbou, smerom do technickej miestnosti kde sa
nach&aacute;dza v&yacute;menn&iacute;kov&aacute; stanica. V pr&iacute;pade požiadavky bude vykurovac&iacute; syst&eacute;m rozčlenen&yacute; na niekoľko vetiev
v zmysle dispozičn&eacute;ho a funkčn&eacute;ho členenia objektu. Rozdelenie bude na kombinovanom rozdeľovači a zberači,
pripojenom na doskov&yacute; tepeln&yacute; v&yacute;menn&iacute;k vykurovania. Každ&aacute; vetva bude vybaven&aacute; vlastnou miešacou armat&uacute;rou
a obehov&yacute;m čerpadlom. Riadenie teploty vykurovacej vody každej vetvy bude ekvitermick&eacute;.
Druh&yacute; doskov&yacute; tepeln&yacute; v&yacute;menn&iacute;k bude sl&uacute;žiť na ohrev pitnej vody. Voda bude ohrievan&aacute; prietokov&yacute;m
sp&ocirc;sobom cez doskov&yacute; v&yacute;menn&iacute;k s menovit&yacute;m tepeln&yacute;m v&yacute;konom 80,0kW a n&aacute;sledne akumulovan&aacute; vo
vyrovn&aacute;vacom z&aacute;sobn&iacute;ku teplej vody s objemom 400 litrov. Rozvod teplej vody bude vybaven&yacute; cirkulačn&yacute;m
potrub&iacute;m a čerpadlom.
Meranie spotreby tepla bude priamo v OST. Nainštalovan&eacute; bud&uacute; dva fakturačn&eacute; merače tepla
umožňuj&uacute;ce osobitn&eacute; meranie spotreby tepla pre vykurovanie objektu a osobitn&eacute; meranie spotreby tepla pre
ohrev pitnej vody.
VYKUROVAC&Iacute; SYST&Eacute;M
Vykurovac&iacute; syst&eacute;m bude dvojr&uacute;rkov&yacute;, uzatvoren&yacute;, s n&uacute;ten&yacute;m obehom teplonosn&eacute;ho m&eacute;dia. Teplonosn&yacute;m
m&eacute;diom bude chemicky upraven&aacute; vykurovacia voda, napusten&aacute; a dop&uacute;šťan&aacute; do vykurovacieho syst&eacute;mu
z prim&aacute;rneho okruhu zdroja tepla – kompaktnej CZT.
Hlavn&yacute; ležat&yacute; rozvod bude veden&yacute; pod stropom 1.N.P. a bude tepelne izolovan&yacute;. Zvisl&eacute; rozvody
(st&uacute;pačky) bud&uacute; veden&eacute; na vhodn&yacute;ch miestach tak, aby ich počet bol čo možno najmenš&iacute; a bud&uacute; tepelne
izolovan&eacute;. Na p&auml;te každej st&uacute;pačky bud&uacute; osaden&eacute; uzatv&aacute;racie, regulačn&eacute; a vyp&uacute;šťacie armat&uacute;ry.
Vykurovac&iacute; syst&eacute;m bude na 1 N.P. konvekčn&yacute;, s vykurovac&iacute;mi telesami, v k&uacute;peľniach doplnen&yacute;
teplovodn&yacute;m podlahov&yacute;m vykurovan&iacute;m pripojen&yacute;m na spiatočku pr&iacute;slušn&eacute;ho vykurovacieho telesa a na 2 -3 N.P.
bude teplovodn&eacute; podlahov&eacute; vykurovanie. Na všetk&yacute;ch vykurovac&iacute;ch teles&aacute;ch bud&uacute; osaden&eacute; termostatick&eacute; ventily
ovl&aacute;dan&eacute; termostatick&yacute;mi hlavicami a regulačn&eacute; spiatočkov&eacute; ventily. Každ&eacute; vykurovacie teleso bude vybaven&eacute;
odvzdušňovacou z&aacute;tkou. Všetky bytov&eacute; rozvody vykurovacieho syst&eacute;mu bud&uacute; veden&eacute; v podlahe pr&iacute;slušn&eacute;ho
bytu. Na p&auml;te bytu bud&uacute; rozvody ukončen&eacute; v plechovej skrinke uzatv&aacute;rac&iacute;mi a regulačn&yacute;mi armat&uacute;rami,
prietokomerom a meračom tepla. Skrinky bud&uacute; osaden&eacute; tak, aby boli pr&iacute;stupn&eacute; zo schodiskov&eacute;ho priestoru resp.
z chodieb.
Schodiskov&yacute; priestor ako aj spoločn&eacute; priestory v 1.P.P. a 1.N.P. objektu nebud&uacute; vykurovan&eacute;. Vykurovan&yacute;
bude len spoločn&yacute; priestor na 2.N.P. a priestor dieln&iacute; na 1.N.P., kde bude na p&auml;te vykurovacieho syst&eacute;mu
osaden&eacute; samostatn&eacute; meranie spotreby tepla.
V&yacute;počtov&yacute; teplotn&yacute; sp&aacute;d vykurovacieho syst&eacute;mu bude 60/45&deg;C s ekvitermickou regul&aacute;ciou teploty
vykurovacej vody (požiadavka na MaR zdroja tepla).
4.3.2. Zdravotechnika
V projekte je riešen&eacute; napojenie nov&yacute;ch zariaďovac&iacute;ch predmetov na existuj&uacute;ce rozvody vodovodu
Nov&eacute; rozvody vodovodu bud&uacute; napojen&eacute; na existuj&uacute;cu pr&iacute;pojku vodovodu. Vn&uacute;torn&eacute; rozvody vody bud&uacute;
vyhotoven&eacute; z plasthlin&iacute;kov&yacute;ch r&uacute;r. V objekte bud&uacute; na každom podlaž&iacute; osaden&eacute; stabiln&eacute; hadicov&eacute; navijaky s
tvarovo st&aacute;lou hadicou.
Ohrev teplej vody je riešen&yacute; cez v&yacute;menikov&uacute; stanicu, t.j. cez doskov&yacute; tepeln&yacute; v&yacute;menn&iacute;k, dohrievan&aacute;
elektricky v pr&iacute;pade potreby.
Nov&aacute; splaškov&aacute; kanaliz&aacute;cia v objekte bude napojen&aacute; na existuj&uacute;cu pr&iacute;pojku splaškovej kanaliz&aacute;cie.
Potrubia veden&eacute; v zemi bud&uacute; vyhotoven&eacute; z PVC-U r&uacute;r. Potrubia veden&eacute; nad zemou v objekte bud&uacute; vyhotoven&eacute;
z HT odpadn&eacute;ho syst&eacute;mu z polypropyl&eacute;nov&yacute;ch r&uacute;r. Dažďov&eacute; odpadov&eacute; vody zo striech bud&uacute; odv&aacute;dzan&eacute; do
spoločnej kanaliz&aacute;cie.
VODOVODN&Aacute; PR&Iacute;POJKA
Objekt m&aacute; existuj&uacute;cu vodovodn&uacute; pr&iacute;pojku DN 32 s menovit&yacute;m prietokom 10,0 m3/h a maxim&aacute;lnym
prietokom 20,0 m3/h. Od vodomernej šachty je potrubie veden&eacute; do bytov&eacute;ho domu z južnej strany, kde cez 1 P.P.
bude zveden&eacute; do miestnosti v&yacute;menn&iacute;kovej stanice, tu bude umiestnen&yacute; hlavn&yacute; uz&aacute;ver vodovodu.
SPLAŠKOV&Aacute; KANALIZ&Aacute;CIA
Splaškov&eacute; odpadov&eacute; vody s&uacute; odv&aacute;dzan&eacute; kanalizačnou pr&iacute;pojkou do verejnej kanaliz&aacute;cie vedenej v pešej
komunik&aacute;cii v bl&iacute;zkosti riešenej stavby. Kanalizačn&aacute; pr&iacute;pojka je vyhotoven&aacute; z r&uacute;r PVC-U DN 200.
DAŽĎOV&Aacute; KANALIZ&Aacute;CIA
Dažďov&eacute; odpadov&eacute; vody zo striech s&uacute; odv&aacute;dzan&eacute; do spoločnej kanaliz&aacute;cie. Časť dažďovej vody
z navrhovan&yacute;ch vn&uacute;tro blokov&yacute;ch spevnen&yacute;ch pl&ocirc;ch bude odveden&aacute; do vsaku, dažďov&aacute; voda z navrhovan&yacute;ch
parkovac&iacute;ch pl&ocirc;ch priľahl&yacute;ch k miestnej komunik&aacute;cii bude odveden&aacute; do existuj&uacute;cich cestn&yacute;ch vpustov, cez novo
navrhovan&uacute; dažďov&uacute; kanaliz&aacute;ciu s ORL. Potrubia bud&uacute; vyhotoven&eacute; z r&uacute;r PVC-U DN 150. Na zmenu tr&aacute;s a zmenu
sp&aacute;du potrubia bud&uacute; vyhotoven&eacute; na potrub&iacute; prefabrikovan&eacute; kruhov&eacute; šachty.
PODMIEŇUJ&Uacute;CE PREDPOKLADY
bilancia potrieb vody
Pre stanovenie potreby vody sme vych&aacute;dzali zo Z.z. č. 684/2006, pr&iacute;loha č. 1 časť A – bytov&yacute; fond,
kde je špecifick&aacute; potreba vody pre byty &uacute;stredne vykurovan&yacute;mi s &uacute;strednou pr&iacute;pravou teplej vody a vaňov&yacute;m
k&uacute;peľom nasledovn&aacute;:
obyvateľ........................................................................................................145 dm 3/osoba.deň
Denn&aacute; potreba vody Qd
20 obyvateľov.........................&aacute; 145 dm3/osoba.deň...........................2900 dm3/deň
Spolu................................................................................................................2900 dm 3/deň
Ročn&aacute; potreba vody Qr
Qr = 365 x Qd
Qr = 365 x 2,90 = 1058,5 m3/rok
Maxim&aacute;lna denn&aacute; potreba vody
Qm = Qd x kd
Qm = 2,90 x 1,3 = 3,77 m3/deň
Maxim&aacute;lna hodinov&aacute; potreba vody
Qh = 1/24 x Qm x kh
Qh = 1/24 x 3,77 x 2,1 = 0,3299 m3/hod
V&yacute;počtov&yacute; prietok
Qp = √∑ (qi2 x ni)
Qp = √ (0,12 x 7) + (0,22 x 30) + (0,32 x 5)
Qp = 1,91 dm3/s
Pr&iacute;pojka vodovodu je navrhnut&aacute; na v&yacute;počtov&yacute; prietok vody potrebnej pre bytov&yacute; dom. Pre maxim&aacute;lnu r&yacute;chlosť
pr&uacute;denia vody v plastovom potrub&iacute; w = 2 m/s, bude minim&aacute;lny potrebn&yacute; priemer pr&iacute;pojky:
dmin = √( 4 x Qp / (π x w)) = √( 4 x 0,00191 / (π x 2,0))
dmin = 0,03488 m ⇒ DN 65
Splaškov&eacute; odpadov&eacute; vody
splaškov&yacute;ch odpadov&yacute;ch v&ocirc;d je totožn&aacute; s bilanciou potrieb pitnej vody a bude nasledovn&aacute;:
Ročn&eacute; množstvo splaškov&yacute;ch odpadov&yacute;ch v&ocirc;d
Qr = 1058,5 m3/rok
Denn&eacute; množstvo splaškov&yacute;ch odpadov&yacute;ch v&ocirc;d
Qd = 2900 dm3/deň
V&yacute;počtov&yacute; prietok splaškov v zmysle STN EN 12056-2
Qw = K √ Σ DU
Qw = 0,5 √ (0,5 x 10) + (1,5 x 5) + (0,8 x 25) + (2,5 x 6) = 3,446 dm3/s
Dažďov&eacute; odpadov&eacute; vody z parkoviska
Pri v&yacute;počte dažďov&yacute;ch odpadov&yacute;ch v&ocirc;d sa vych&aacute;dzalo z rovnice uvedenej vo vyhl&aacute;ške č. 397/2003 Z.z.
Plocha spevnen&yacute;ch pl&ocirc;ch (S)
s&uacute;činiteľ odtoku ψ - 0,9
ročn&yacute; priemer z dlhodob&eacute;ho zr&aacute;žkov&eacute;ho &uacute;hrnu pri 15 min&uacute;tovom daždi s periodicitou 0,5 pre okolie mesta Martin
je Hz – 152 dm3/s.ha
Parkovisko a spevnen&eacute; plochy
Qp = Hz x S x ψ = 152 x 0,0347 x 0,9 = 4,746 dm3/s
Odpadov&eacute; vody spolu
Qww = Qw + Qp
Qww = 3,446 + 4,746 = 8,192 dm3/s
Dažďov&eacute; odpadov&eacute; vody
V&yacute;počet množstva dažďov&yacute;ch odpadov&yacute;ch v&ocirc;d zo strechy
Strecha ploch&aacute;
Qs = Hz x S x ψ = 152 x 0,0355 x 0,9 = 4,856 dm3/s
N&aacute;vrh veľkosti ORL :
Q d=
x ss x qs
je s&uacute;činiteľ odtoku = 0,8 spev. plocha
ss je plocha odvodnenia = spev. plocha parkovisko
qs je v&yacute;datnosť dažďa = 0,0152 l/s.ha
Pre parkovacie plochy sa navrhol odlučovač ropn&yacute;ch l&aacute;tok , firmy PURATOR, s kvalitou čistenia na p=0,1
PARKOVISKO 261 m2
Qd= 3,17 l.s-1
Navrhnut&yacute; je ORL s prietokom Q=3,2 l.s-1
Odlučovač ropn&yacute;ch l&aacute;tok z parkov&iacute;sk:
Odlučovač sa osad&iacute; do vodorovnej polohy na vopred pripraven&uacute; železobet&oacute;nov&uacute; dosku s rovinnosťou +
5mm a v pr&iacute;pade zv&yacute;šenej hladiny spodnej vody mus&iacute; byť riadne ukotven&yacute;. &Uacute;činnosť odlučovača ropn&yacute;ch l&aacute;tok
s koalescenčn&yacute;m filtrom je podľa &uacute;dajov v&yacute;robcu tak&aacute;, že zbytkov&yacute; obsah uhlovod&iacute;kov&yacute;ch l&aacute;tok je v odpadovej
vode menš&iacute; ako 0,10 mg/l pri kontamin&aacute;cii vody.
Kaly s obsahom ropn&yacute;ch l&aacute;tok a ropn&eacute; produkty bud&uacute; likvidovan&eacute; tou organiz&aacute;ciu, ktor&aacute; je zmluvne
určen&aacute; investorom alebo prev&aacute;dzkovateľom. Na prev&aacute;dzku kanaliz&aacute;cie a odlučovača ropn&yacute;ch l&aacute;tok je potrebn&eacute;
vypracovať prev&aacute;dzkov&yacute; poriadok.
Vetranie soci&aacute;lnych priestorov a upratovacej komory bude n&uacute;tene podtlakovo odvetran&eacute; axi&aacute;lnymi ventil&aacute;tormi
pre jednotliv&eacute; miestnosti samostatne. Ovl&aacute;dan&eacute; bud&uacute; vyp&iacute;načom s časov&yacute;m dobehom z každej miestnosti
samostatne. V&yacute;mena vzduchu bude pre všetky priestory minim&aacute;lne 10 – n&aacute;sobn&aacute;. Potrubie bude kruhov&eacute;, od
ventil&aacute;tora veden&eacute; pod stropom a n&aacute;sledne bude potrubie za&uacute;sten&eacute; do st&uacute;pačky v šachte, ktor&aacute; bude vyveden&aacute;
nad strechu s ukončen&iacute;m kruhovou strieškou. Potrubie veden&eacute; nad strechu bude taktiež z kruhov&eacute;ho potrubia
Všetky ventil&aacute;tory pripojen&eacute; na rozvod vzt. musia mať pretlakov&eacute; klapky.
Na odvetranie kuch&yacute;ň a odvod p&aacute;r zo spor&aacute;ka bud&uacute; navrhnut&eacute; kuchynsk&eacute; digestory. Ovl&aacute;danie digestora bude
umiestnen&eacute; priamo na telese digestora. Digestor bude obsahovať lapače tukov a osvetlenie. V kuchyniach bud&uacute;
použit&eacute; kuchynsk&eacute; recirkulačn&eacute; digestory.
Vetranie skladov&yacute;ch priestorov v suter&eacute;ne a technick&aacute; miestnosť bude cez vetracie mriežky umiestnen&eacute; na
fas&aacute;dach objektu alebo cez anglick&eacute; dvorčeky v pr&iacute;pade pivn&iacute;c na 1.P.P.
&Uacute;tlm hluku a chvenia
Zariadenie nebude vykazovať v&auml;čšie zaťaženie hlukom ako je povolen&eacute; hygienickou normou, pre uveden&eacute;
Vzduchotechnick&eacute; zariadenia rešpektuj&uacute; požiarnu ochranu a normu STN 91 0201.
Vzt potrubie a distribučn&eacute; elementy
Pre distrib&uacute;ciu vzduchu z mal&yacute;ch axi&aacute;lnych ventil&aacute;torov bude navrhovan&eacute; kruhov&eacute; potrubie pr&iacute;slušn&eacute;ho priemeru
s veden&iacute;m v podhľade alebo pod stropom a n&aacute;sledne za&uacute;sten&eacute; do st&uacute;pačky VZT, ktor&aacute; bude veden&aacute; nad strechu
a bude z potrubia SPIRO s ukončen&iacute;m kruhovou strieškou.
NAPOJENIE OBJEKTU ELEKTRICKOU ENERGIOU:
Objekt bytov&eacute;ho domu je napojen&yacute; elektrickou energiou zo s&uacute;stavy nap&auml;tia:
- 3L PEN, 400/230V, str.50Hz, TN-C
- Stupeň d&ocirc;ležitosti : 3. stupeň
- Inštalovan&yacute; pr&iacute;kon: 160kW
- Predpokladan&yacute; max. s&uacute;časn&yacute; pr&iacute;kon: 103,5kW
Elektr&aacute;rensk&eacute; meranie spotreby elektrickej energie je umiestnen&eacute; v 1.N.P. navrhovan&eacute;ho bytov&eacute;ho objektu.
Skupina el. zariaden&iacute;
Podľa Vyhl&aacute;šky č. 718/2002 Zb.- časť III, je objekt investora zaraden&yacute; do skupiny „B“
Vn&uacute;torn&eacute; silnopr&uacute;dov&eacute; rozvody, rozvodn&eacute; zariadenia a umel&eacute; osvetlenie
- Bytov&eacute; jednotky a ich komunikačn&eacute; priestory
- Priestory komunitn&yacute;ch miestnost&iacute; a vybavenosti domu
- Centr&aacute;lna v&yacute;menn&iacute;kov&aacute; stanica objektu
Vn&uacute;torn&eacute; slabopr&uacute;dov&eacute; rozvody
Bilancia v&yacute;konov vych&aacute;dza z STN 332130 z 2.
V navrhovan&yacute;ch bytov&yacute;ch jednotk&aacute;ch sa uvažuje, že na varenie a pečenie sa bud&uacute; použ&iacute;vať elektrick&eacute; spotrebiče
s v&yacute;konom nad 3,5 kVA. V zmysle citovanej normy s&uacute; tieto byty zaraden&eacute; do stupňa elektriz&aacute;cie B
s predpokladan&yacute;m maxim&aacute;lnym s&uacute;časn&yacute;m v&yacute;konom 11 kW pre jeden byt.
Pre s&uacute;streden&uacute; bytov&uacute; z&aacute;stavbu sa koeficient s&uacute;časnosti pre odoberan&yacute; v&yacute;kon celej skupiny vypoč&iacute;ta
zo vzorca:
k = kn + (1- kn).1/n1/2 , kde n je celkov&yacute; počet bytov v skupine a kn je koeficient s&uacute;časnosti pre 5 bytov,
s prihliadnut&iacute;m na predpokladan&uacute; vybavenosť
t.j. 0,35.
V navrhovanej bytovej z&aacute;stavbe je celkov&yacute; počet bytov 5. Pre tento počet zvol&iacute;me kn = 0,35.
Potom: k = 0,35 + ((1-0,35) x 1/51/2 ) = 0,35+( 0,65 x 1/2,2) = 0,35 + 0,295 = 0,645
Celkov&yacute; vypoč&iacute;tan&yacute; s&uacute;časn&yacute; v&yacute;kon v bytov&yacute;ch priestoroch
( v 5 bytoch) :
Pcv = 11 kW x 5 x 0,645 = 35,475 kW
Predpokladan&yacute; max. s&uacute;časn&yacute; pr&iacute;kon zdrojov umel&eacute;ho osvetlenia (okrem bytov)
Predpokladan&yacute; max s&uacute;č. pr&iacute;kon v z&aacute;suvkov&yacute;ch okruhoch objektu ( okrem bytov )
Predpokladan&yacute; max. s&uacute;č. pr&iacute;kon pre VZT
Predpokladan&yacute; max. s&uacute;č. pr&iacute;kon pre technol&oacute;giu kotolne
Predpokladan&yacute; inšt. pr&iacute;kon pre slabopr. zariadenia, poč. techniku, PPZ a pod.
S&uacute;čet predpokladan&yacute;ch max. odoberan&yacute;ch pr&iacute;konov v objekte investora
103,475 kW
Predpokladan&yacute; koeficient s&uacute;časnosti 0,75
Predpokladan&yacute; max s&uacute;č. odber el. energie v celom objekte
Predpokladan&aacute; denn&aacute; spotreba el. energie v celom objekte
Predpokladan&aacute; ročn&aacute; spotreba el. energie v celom objekte
103,475 x 0,75 = 77,61 kW
103,475 kW x 5 hod/deň = 0,517 MWh/deň
0,517 MWh/deň x 365 dn&iacute; x 0,8 = 150,96 MWh/rok
Vypoč&iacute;tan&eacute; predpokladan&eacute; hodnoty spotreby el. energie bud&uacute; upresnen&eacute; po vypracovan&iacute; realizačn&eacute;ho projektu
v spolupr&aacute;ci s projektantmi technologick&yacute;ch zariaden&iacute; a z&aacute;stupcom investora.
Nap&aacute;jac&iacute; rozvod NN :
Dod&aacute;vka maxim&aacute;lneho s&uacute;časn&eacute;ho pr&iacute;konu elektrickej energie - odoberan&eacute;ho navrhovan&yacute;mi spotrebičmi
a zariadeniami predmetn&eacute;ho objektu bude zabezpečovan&aacute; existuj&uacute;cou trafostanicou.
Počet pr&iacute;pojkov&yacute;ch k&aacute;blov bude určen&yacute; realizačn&yacute;m projektom na z&aacute;klade v&yacute;počtu &uacute;bytku nap&auml;tia a selektivity
vedenia v&yacute;počtov&yacute;m programom SICHR 6. Pr&iacute;pojkov&eacute; k&aacute;ble z trafostanice s&uacute; veden&eacute; cez poistkov&uacute; pr&iacute;pojkov&uacute;
skriňu PRIS do priestoru so skupinov&yacute;mi elektromerov&yacute;mi rozv&aacute;dzačmi objektu. Z nich navrhujeme viesť st&uacute;pacie
k&aacute;blov&eacute; vedenia do jednotliv&yacute;ch podlaž&iacute; schodiskov&yacute;m priestorom domu. Istenie okruhov spoločnej spotreby
navrhujeme s&uacute;strediť do pr&iacute;strojov&eacute;ho rozv&aacute;dzača, umiestnen&eacute;ho v 1.N.P. – v bl&iacute;zkosti ktor&eacute;ho bude umiestnen&aacute;
hlavn&aacute; ochrann&aacute; zbernica prepojen&aacute; na hlavn&yacute; zemnič objektu. V objekte nevznikne nutnosť použitia
kompenzačn&eacute;ho rozv&aacute;dzača.
Elektr&aacute;rensk&eacute; meranie spotreby el. energie navrhujeme rozdeliť do nasledovn&yacute;ch skup&iacute;n:
• samostatn&eacute; meranie všetk&yacute;ch bytov&yacute;ch jednotiek
• spoločn&eacute; meranie vonkajšieho osvetlenia a automatickej br&aacute;ny
• samostatn&eacute; meranie komunitn&yacute;ch miestnost&iacute; na 1.N.P i 2 N.P.
• spoločn&eacute; meranie spoločn&yacute;ch komunikačn&yacute;ch priestorov, kotolne,
• technol&oacute;gie VZT, vonkajšieho osvetlenia, n&uacute;dzov&eacute;ho osvetlenia, spotreby zariaden&iacute; pre slabopr&uacute;d
Vn&uacute;torn&eacute; silnopr&uacute;dov&eacute; rozvody:
Rozvodn&aacute; s&uacute;stava:
Od trafostanice po skupinov&eacute; elektromerov&eacute; rozv&aacute;dzače Rm:
3+PEN str. 50Hz, 400/230 V / TN-C
Za skupinov&yacute;mi elektromerov&yacute;mi rozv&aacute;dzačmi:
3+N+PE str. 50Hz, 400/230 V / TN-C-S
II nap&auml;ťov&eacute; p&aacute;smo pre striedav&eacute; nap&auml;tie podľa STN 33 0110 : 2000
Ochrana proti skratu, preťaženiu a &uacute;razu elektrick&yacute;m pr&uacute;dom:
Silov&eacute; rozvody elektroinštal&aacute;cie objektu navrhujeme chr&aacute;niť proti skratu a preťaženiu jednop&oacute;lov&yacute;mi a
trojp&oacute;lov&yacute;mi istiacimi pr&iacute;strojmi so skratovou odolnosťou 10 až 25 kA, umiestnen&yacute;mi v hlavn&yacute;ch a pr&iacute;strojov&yacute;ch
rozv&aacute;dzačoch jednotliv&yacute;ch podlaž&iacute; objektu. Skratov&aacute; odolnosť nožov&yacute;ch poistiek v pr&iacute;pojkovej skrini PRIS bude
nad hranicou 80kA, čo je dostatočnou ochranou pred &uacute;činkami maxim&aacute;lnych skratov&yacute;ch pr&uacute;dov. V rozvodniach
objektu navrhne realizačn&yacute; projekt inštal&aacute;ciu spoločn&yacute;ch zvodičov prep&auml;tia triedy B+C s pr&iacute;slušn&yacute;m isten&iacute;m.
Živ&eacute;, vodiv&eacute; časti el. silov&yacute;ch rozvodov a zariaden&iacute; navrhujeme chr&aacute;niť pred &uacute;razom elektrick&yacute;m pr&uacute;dom
v zmysle STN 33 2000-4-41:
v norm&aacute;lnej prev&aacute;dzke
ochranou izolovan&iacute;m živ&yacute;ch čast&iacute;
ochranou krytmi, alebo prep&aacute;žkami
ochrana z&aacute;branou
doplnkovou ochranou pr&uacute;dov&yacute;mi chr&aacute;ničmi
ochranou mal&yacute;m nap&auml;t&iacute;m
ochranou samočinn&yacute;m odpojen&iacute;m nap&aacute;jania
ochranou použit&iacute;m zariaden&iacute; triedy ochrany II
ochranou uzemnen&yacute;m miestnym posp&aacute;jan&iacute;m
ochrana el. oddelen&iacute;m
Ochrana pred vz&aacute;jomn&yacute;mi vplyvmi:
pri kryt&iacute; pr&iacute;strojov, zodpovedaj&uacute;com dan&eacute;mu prostrediu sa nepredpokladaj&uacute; vz&aacute;jomn&eacute; škodliv&eacute; &uacute;činky elektrick&yacute;ch
a neelektrick&yacute;ch inštal&aacute;cii
Druh prostredia:
Viď protokol o určen&iacute; prostredia v realizačnom projekte.
Pri n&aacute;vrhu uloženia veden&iacute;, pr&iacute;strojov a spotrebičov na a do horľav&yacute;ch podkladov a hm&ocirc;t bude nevyhnutn&eacute;
dodržanie pr&iacute;slušn&yacute;ch platn&yacute;ch STN 332312, 061008 a pod.
Podľa STN 33 2000-5-54 bud&uacute; v budove zrealizovan&eacute; posp&aacute;jania hlavn&yacute;ch energetick&yacute;ch potrub&iacute; vodovodu,
kanaliz&aacute;cie,
potrub&iacute; VZT, &uacute;stredn&eacute;ho k&uacute;renia, ochrann&yacute;ch pr&iacute;pojn&iacute;c pr&iacute;strojov&yacute;ch rozv&aacute;dzačov, zvody
bleskozvodu a ochrann&yacute;ch zbern&iacute;c poistkov&yacute;ch pr&iacute;pojkov&yacute;ch skr&iacute;ň NN a pr&iacute;pojkov&yacute;ch skr&iacute;ň slabopr&uacute;du
Rozvody ochrann&eacute;ho pospojovania:
Hlavn&aacute; ochrann&aacute; zbernica ekvipotenci&aacute;lneho pospojovania vodiv&yacute;ch predmetov a krytov el. zariaden&iacute; bytov&eacute;ho
domu „EP“ bude umiestnen&aacute; v bl&iacute;zkosti hlavn&eacute;ho rozv&aacute;dzača 1.N.P.
Ekvipotenci&aacute;lnu zbernicu EP pripojiť pomocou vodiča FeZn 30/4mm, uložen&eacute;ho pod omietkou ku hlavn&eacute;mu zemniču
objektu a zemniacemu vodiču pr&iacute;pojky NN.
Ku zbernici EP pripojiť vodičmi CY 25mm2 v zmysle podmienok STN 33 2000-5-54
- vodiv&eacute; pr&iacute;pojkov&eacute; potrubie vodovodu
- vodiv&eacute; pr&iacute;pojkov&eacute; potrubie kanaliz&aacute;cie
- vodiv&eacute; potrubie &uacute;stredn&eacute;ho k&uacute;renia
- zvod bleskozvodu
- ochrann&uacute; svorku pr&iacute;pojkovej skrine NN
- hlavn&uacute; ochrann&uacute; zbernicu rozv&aacute;dzača Rm
- vodičmi CY 6mm2 pr&iacute;strojov&eacute; rozvodnice bytov&yacute;ch jednotiek Rb, pospojovanie vo v&yacute;menn&iacute;kovej stanici
- vodičom CY 4mm2 ochrann&eacute; pospojovanie k&uacute;peľn&iacute; bytov cez zbernice PE v bytov&yacute;ch rozvodniciach Rb.
Skratov&aacute; bezpečnosť : bude navrhnut&aacute; podľa STN IEC 60909 : 2000
Ochrana pred prep&auml;t&iacute;m : bude navrhnut&aacute; podľa STN 33 2000-1 : 2000
Merania spotreby el. energie: Pre všetk&yacute;ch odberateľov bud&uacute; podľa STN 33 3320 : 2002 na verejne pr&iacute;stupnom
Podmienky prostredia : STN 33 2000-3 : 2000
Vonkajšie vplyvy bud&uacute; určen&eacute; podľa podmienok STN 33 0300:2001 určen&eacute; protokol&aacute;rne.
Rozvody: Druhy el. rozvodov, sp&ocirc;sob inštal&aacute;cie, prierezy veden&iacute;, ochrann&eacute; a sp&iacute;nacie pr&iacute;stroje bud&uacute; volen&eacute;
podľa STN33 2000:2000,STN 33 2130 v n&aacute;v&auml;znosti a v s&uacute;vislosti s STN 33 0300.
Rozv&aacute;dzače: Bud&uacute; vyhotoven&eacute; podľa STN EN 60 439-1:2000
Určenie vonkajš&iacute;ch vplyvov podľa STN 33 2000 – 3 :
Prostredie – vlastnosti okolia : v miestnostiach objektu investora:
norm&aacute;lne : AA5, AB5, AC1, AD1, AE1, AF1, AG1, AH1, AK1, AL1, AM1, AN1, P1, AQ1, AR1, AS1.
Vn&uacute;torn&eacute; rozvody elektro :
Vo vchode do bytov&yacute;ch priestorov bude zriaden&eacute; hlavn&eacute; domov&eacute; vedenie, ktor&eacute; bude nap&aacute;jať pr&iacute;strojov&eacute;
rozvodnice bytov.
Sveteln&eacute;, z&aacute;suvkov&eacute; a ostatn&eacute; silov&eacute; rozvody každ&eacute;ho bytu bud&uacute; nap&aacute;jan&eacute; z bytov&yacute;ch rozvodn&iacute;c umiestnen&yacute;ch
v predsienkach bytov. Vn&uacute;torn&eacute; rozvody elektro s&uacute; navrhnut&eacute; vodičmi CYKYL a k&aacute;blami CYKY, ktor&eacute; bud&uacute;
uložen&eacute; pod omietkami. Vyp&iacute;nače a z&aacute;suvky sa osadia do pracovn&yacute;ch v&yacute;šok podľa podmienok STN 332130.
Z&aacute;suvkov&eacute; rozvody k&uacute;peľn&iacute; bytov bud&uacute; chr&aacute;nen&eacute; pr&uacute;dov&yacute;mi chr&aacute;ničmi.
Nap&aacute;janie osvetlenia spoločn&yacute;ch priestorov, ako aj nap&aacute;janie dom&aacute;cich telef&oacute;nov a elektrick&eacute;ho videovr&aacute;tnika
bytov bude z pr&iacute;strojov&eacute;ho rozv&aacute;dzača spoločnej spotreby objektu.
Intenzita osvetlenia v jednotliv&yacute;ch priestoroch objektu bude navrhnut&aacute; v zmysle STN 36 0450 s ohľadom na
zrakov&uacute; n&aacute;ročnosť. Krytie svietidiel, pr&iacute;strojov a elektroinštalačn&eacute;ho materi&aacute;lu bude podľa STN 332310 pre dan&yacute;
druh prostredia priestoru.
V objekte sa zriadi hlavn&eacute; posp&aacute;janie v zmysle STN 33 2000-4-41.
Nap&auml;ťov&aacute; s&uacute;stava 3/PEN AC 400/230V 50Hz TN-C-S.
Ochrana pred &uacute;razom elektrick&yacute;m pr&uacute;dom pri poruche v zmysle STN 33 2000-4-41- samočinn&yacute;m odpojen&iacute;m
nap&aacute;jania a pr&uacute;dov&yacute;mi chr&aacute;ničmi. Inštal&aacute;cia v k&uacute;peľniach a um&yacute;vac&iacute;ch priestoroch bytov bude podľa STN 33 20007-701. Doplnkov&eacute; posp&aacute;janie v k&uacute;peľniach bude navrhnut&eacute; vodičmi CY 4 zelenožltej farby.
Silov&eacute; rozvody v &uacute;nikov&yacute;ch priestoroch navrhn&uacute;ť k&aacute;blami 1-CHKE-R
Slabopr&uacute;dov&eacute; rozvody riešia rozvod pre inštal&aacute;ciu telef&oacute;nov.
Nap&auml;ťov&aacute; s&uacute;stava 2 DC 48V/ IT obvod PELV
Ochrana pred &uacute;razom el. pr&uacute;dom pri poruche bezpečn&yacute;m nap&auml;t&iacute;m PELV.
Rovnako bude v inštal&aacute;ci&iacute; zabezpečen&yacute; rozvod k&aacute;blovej telev&iacute;zie s riešen&iacute;m prepojovacieho bodu na vonkajš&iacute;
rozvod TV sign&aacute;lu. Vonkajš&iacute; rozvod bude riešen&yacute; provajderom.
Slabopr&uacute;dov&eacute; rozvody: -Vn&uacute;torn&eacute; slabopr&uacute;dov&eacute; rozvody:
V navrhovanom objekte bud&uacute; zriaden&eacute; tieto slabopr&uacute;dov&eacute; zariadenia:
Bytov&aacute; časť:
Telekom. Rozvody 100% n&eacute; osadenie
Audio resp. video dorozumievacie zariadenia
SKT, terestri&aacute;ln&eacute; resp. satelitn&eacute; rozvody
Podľa požiadavky – EPS,EZS
Vn&uacute;torn&eacute; telef&oacute;nne rozvody:
Pr&iacute;pojkov&yacute; k&aacute;bel pevnej telef&oacute;nnej siete bude ukončen&yacute; tlf. z&aacute;verom na vonkajšej strane obvodov&eacute;ho m&uacute;ru.
Z neho bud&uacute; veden&eacute; vn&uacute;torn&eacute; rozvody pevnej telef&oacute;nnej siete k&aacute;blami SYKFY, vtiahnut&yacute;mi do r&uacute;rok PVC pod
omietkami do st&uacute;pačkov&yacute;ch odbočn&yacute;ch krab&iacute;c priestorom schodiska budovy.
Rozvody z odbočn&yacute;ch st&uacute;pačkov&yacute;ch krab&iacute;c schod&iacute;sk do priestorov jednotliv&yacute;ch bytov&yacute;ch jednotiek bud&uacute;
navrhnut&eacute; k&aacute;blami SYKY v r&uacute;rkach PVC pod omietkami.
Vn&uacute;torn&yacute; rozvod k&aacute;blovej telev&iacute;zie navrhn&uacute;ť z pr&iacute;pojkovej skrine vonkajš&iacute;ch rozvodov k&aacute;blovej telev&iacute;zie
koaxi&aacute;lnymi k&aacute;blami VCCEOY v t. PVC pod omietkami do miestnost&iacute; ob&yacute;vac&iacute;ch izieb všetk&yacute;ch bytov objektu
AUDIO KOMUNIKAČN&Eacute; ZARIADENIE DHZ :
Pri vstupn&yacute;ch dver&aacute;ch do jednotliv&yacute;ch vchodov bytov&yacute;ch podlaž&iacute; umiestniť tablo s dom&aacute;cim hovorov&yacute;m
zariaden&iacute;m (video vr&aacute;tnikmi). Ich st&uacute;pačkov&eacute; vedenia viesť priestormi schod&iacute;sk na jednotliv&eacute; podlažia
s ukončen&iacute;m rozvodn&yacute;ch k&aacute;blov v jednotliv&yacute;ch bytoch. Nap&aacute;jacie zdroje DHZ (video vr&aacute;tnikov) bud&uacute; umiestnen&eacute;
v rozv&aacute;dzači spoločnej spotreby tejto časti budovy.
Telekomunikačn&eacute; rozvody
N&aacute;vrh a prevedenie zariadenia bude podľa STN 34 2300,STN 34 2305,STN 34 2710
Kapacita telef&oacute;nnej pr&iacute;pojky: 6 p&aacute;rov
&Uacute;roveň tel. zab.: 100%
Telev&iacute;zia: telev&iacute;zny sign&aacute;l k&aacute;blovej telev&iacute;zie
El. vr&aacute;tnik: ovl&aacute;danie el. z&aacute;mku a dorozumievanie
Majitelia bytov sami požiadaj&uacute; o pripojenie do JTS
OCHRANA PRED &Uacute;ČINKAMI ATMOSF&Eacute;RICK&Yacute;CH V&Yacute;BOJOV
Bude riešen&aacute; bleskozvodovou s&uacute;stavou podľa STN 34 1390. Vzhľadom na tvar navrhovanej strešnej
konštrukcie a krytiny navrhujeme použiť mrežov&uacute; bleskozvodn&uacute; s&uacute;stavu, doplnen&uacute; 3 až 5 kusmi pomocn&yacute;ch
bleskozvodn&yacute;ch zberačov, umiestnen&yacute;mi na pomocn&yacute;ch nosn&yacute;ch konštrukci&aacute;ch. Ku bleskozvodnej s&uacute;stave bud&uacute;
typov&yacute;mi bleskozvodn&yacute;mi svorkami pripojen&eacute; trvalo vodiv&yacute;mi spojmi všetky pevne zabudovan&eacute; vodiv&eacute; predmety
a konštrukcie nad strešnou krytinou. S&uacute;časne bud&uacute; pred z&aacute;sahom atmosf&eacute;rick&yacute;ch prep&auml;t&iacute; chr&aacute;nen&eacute; vodiv&eacute;
konštrukcie a z&aacute;bradlia na obvodov&yacute;ch sten&aacute;ch stavby. Hlavn&yacute; zemnič objektu navrhujeme uložiť do z&aacute;kladov&eacute;ho
p&aacute;su objektu s jeho prepojen&iacute;m na zemnič pr&iacute;pojkov&eacute;ho vedenia NN a stožiarov okolit&eacute;ho vonkajšieho osvetlenia
parkovac&iacute;ch pl&ocirc;ch. Pri n&aacute;vrhu zemniacej s&uacute;stavy dodržať podmienky STN 341390, 33 2000-5-52, 341050 a 736005.
Okolie predmetn&eacute;ho objektu hlavne jeho parkovac&iacute;ch pl&ocirc;ch navrhujeme osvetliť dvoma stožiarov&yacute;mi
parkov&yacute;mi v&yacute;bojkov&yacute;mi svietidlami (umiestnenie viď. Vo v&yacute;kresovej časti – 1 situ&aacute;cia). Sveteln&eacute; zdroje vonkajšieho
osvetlenia bud&uacute; sp&iacute;nan&eacute; skupinovo pomocou s&uacute;mrakov&yacute;ch fotorel&eacute; a ich spotreba bude meran&aacute; v rozv&aacute;dzači
spoločnej spotreby na 1. podzemnom podlaž&iacute; každ&eacute;ho objektu. Možnosť pripojenia parkov&yacute;ch svietidiel na rozvody
verejn&eacute;ho osvetlenia je nutn&eacute; prekonzultovať so spr&aacute;vcom predmetnej siete.
Nap&auml;ťov&aacute; s&uacute;stava sveteln&yacute;ch zdrojov vonkajšieho osvetlenia parkov&yacute;mi svietidlami. 3L + PEN, str. 50Hz,
230/400V, TN-C.
Predpokladan&yacute; inštalovan&yacute; pr&iacute;kon vonkajšieho osvetlenia okolia objektu je do hodnoty 5kW.
Použit&eacute; normy:
STN trieda 33 Elektrotechnika – Elektrotechnick&eacute; predpisy
STN trieda 34 Elektrotechnika – STN 345141 Elektrotechnick&eacute; n&aacute;zvoslovie
STN trieda 36 Elektrotechnika
STN trieda 38 Energetika
4.4.1. Vybavenosť &uacute;zemia
Vzhľadom na veľkosť uvažovanej v&yacute;stavby (bytov&yacute; dom s 5-timi bytov&yacute;mi jednotkami, t.j.
obyvateľov) sa nepredpoklad&aacute; s v&yacute;razn&yacute;m vplyvom na okolit&uacute; občiansku vybavenosť v širšom &uacute;zem&iacute;.
existuj&uacute;ca verejn&aacute; a občianska vybavenosť v &uacute;zem&iacute; je plne zastupiteľn&aacute; bez nutnosti navršovania
kapac&iacute;t, t.j. počtu miest v matersk&yacute;ch a z&aacute;kladn&yacute;ch škol&aacute;ch, zdravotn&yacute;ch stred&iacute;sk a pod. Obsluha
verejnou dopravou je na uspokojivej &uacute;rovni.
Vypracoval: Ing. arch. Martin Pavl&iacute;k, v Tvrdoš&iacute;ne, dňa 31.1.2014
T0tO fQ~RJUtje
nUobudlopr'vop.
.!:f.:6:.~
avykonaJ'&quot; d&quot;a
ŽP 20174/2014/ 3 14 Hz
Mesto Martin ako pr&iacute;slušn&yacute; org&aacute;n št&aacute;tnej spr&aacute;vy v prvom stupni vo veciach ochrany pr&iacute;rody a krajiny
podľa &sect; 69 ods. l p&iacute;sm. a), d) a - h) z&aacute;kona Č. 543/2002 Z. z. o ochrane pr&iacute;rody a krajiny v znen&iacute;
neskorš&iacute;ch predpisov (ďalej len z&aacute;kon) a &sect; 2 p&iacute;sm. f) ods.1.z&aacute;kona Č. 416/2001 Z. z. o prechode
niektor&yacute;ch p&ocirc;sobnost&iacute; z org&aacute;nov št&aacute;tnej spr&aacute;vy na obce a na vyššie &uacute;zemn&eacute; celky v znen&iacute; neskorš&iacute;ch
predpisov ana z&aacute;klade žiadosti spoločnosti Pe Pplus, s.r.o., Ulica Gogoľova 3, 036 Ol Martin (ďalej
len žiadateľ) zo dňa 9.1.2014 podľa &sect; 47 ods.3, &sect; 48 ods. l a &sect; 82 ods.12 z&aacute;kona v znen&iacute; neskorš&iacute;ch
predpisova v s&uacute;lade &sect; 46 a &sect; 47 z&aacute;kona Č. 71/1967 Zb. o spr&aacute;vnom konan&iacute;
(spr&aacute;vny poriadok )
v znen&iacute; neskorš&iacute;ch predpisov vyd&aacute;va
žiadateľovi na v&yacute;rub 7 ks stromov rast&uacute;cich na pozemku parc.č.KN 1930/46 v k.&uacute;. Martin. Obvody
kmeňov stromov meran&yacute;ch vo v&yacute;ške 130 cm nad zemou a druhov&aacute; skladba drev&iacute;n, ktor&yacute;ch v&yacute;rub sa
~-~--~'-~----povoluje; je nasiecioVňa:;-šrii'feKovec opa &aacute;v&yacute; (Lanx decidua) - 5 ks -84,126,115,125,110
cm, javor
mliečny (Acer platanoides) - 2 ks - 165,172 cm
I. V s&uacute;lade s ustanoven&iacute;m &sect; 82 ods.12 z&aacute;kona mesto Martin určuje nasledovn&eacute;
činnosti zabezpečuj&uacute;ce ochranu pr&iacute;rody a krajiny.
V&yacute;rub drev&iacute;n bude zrealizovan&yacute; v čase do 30.3.2014.
V&yacute;rub bude vykonan&yacute; tak, aby nedošlo k poškodeniu okolit&yacute;ch drev&iacute;n.
Drevn&aacute; hmota patr&iacute; vlastn&iacute;kovi pozemku a zlikviduje ju žiadateľ na vlastn&eacute; n&aacute;klady cez spoločnosť na
to opr&aacute;vnen&uacute;.
II. V s&uacute;lade s &sect; 48 ods. 1 z&aacute;kona uklad&aacute; n&aacute;hradn&uacute; v&yacute;sadbu:
Žiadateľ uskutočn&iacute;
na svoje n&aacute;klady v term&iacute;ne do 30.11.2016 na pozemku parc. č. KN 1930/46
v k.&uacute;. Martin na pozemku v&yacute;rubu n&aacute;hradn&uacute; v&yacute;sadbu 20 ks okrasn&yacute;ch drev&iacute;n druhov&eacute;ho zloženia:
Tuja riasnat&aacute; (Thuja plicata).
Žiadate l'doruč&iacute; na konaj&uacute;ci spr&aacute;vny org&aacute;n doklad o vykonan&iacute; n&aacute;hradnej v&yacute;sadby do 31.12.2016.
Vlastn&iacute;k pozemku s&uacute;hlas&iacute; s umiestnen&iacute;m n&aacute;hradnej v&yacute;sadby na uvedenom pozemku.
V zmysle ustanovenia položky 160 ods.2, Z&aacute;kona NR SR č.145/1995 Z. z. o spr&aacute;vnych poplatkoch
a v znen&iacute; neskorš&iacute;ch predpisov žiadateľ uhradil spr&aacute;vny poplatok dňa 8.1.2014 do pokladne mesta
Martin vo v&yacute;ške l OO. - €.
Z d&ocirc;vodov uveden&yacute;ch v &sect; 89 ods. 1 p&iacute;sm. a) a p&iacute;sm. b) z&aacute;kona m&ocirc;že konaj&uacute;ci spr&aacute;vny org&aacute;n na n&aacute;vrh
alebo z vlastn&eacute;ho podnetu tento s&uacute;hlas zmeniť alebo zrušiť.
Certifik&aacute;t E&Uacute; za najlepšiu prax v kateg&oacute;rii:
Otv&aacute;ranie verejn&eacute;ho sektoru prostredn&iacute;ctvom
spolupr&aacute;ce na jeho riaden&iacute;
Mesto Martin, N&aacute;m. S.H.Vajansk&eacute;ho 1, 036 01, Martin
tel.+42143 4204175, fax+42143 4132 483
IČO:00316792
Prest&iacute;žne ocenenie OSN
l. miesto v kateg&oacute;rii:
Prevencia a boj proti korupcii
www.transparentnemesto.sk
Osobitn&eacute; predpisy / napr. vlastn&iacute;cke pr&aacute;vo / ako aj ostatn&eacute; ustanovenia
rozhodnutia nedotknut&eacute;.
z&aacute;kona ost&aacute;vaj&uacute; vydan&iacute;m tohto
Žiadateľ podal dňa 9 .1.2014 na tunajš&iacute; &uacute;rad žiadosť o ut1eleJiJ.ies&uacute;IlHrsu&quot; na v&yacute;rub 7 ks stromov
rast&uacute;cich na pozemkoch parc. č&iacute;slo KN 1930/43 v k. &Uacute;. Martin. Ako d&ocirc;vod v&yacute;rubu žiadateľ v žiadosti
uv&aacute;dza: v&yacute;stavba parkovac&iacute;ch pl&ocirc;ch pre bytov&uacute; jednotku.
Dňa 15.1.2014 bolo uskutočnen&eacute; v predmetnej veci &uacute;stne konanie spojen&eacute; s miestnou obhliadkou,
kde bol zisten&yacute; presne a &uacute;plne skutočn&yacute; stav veci.
Na konan&iacute; bol pr&iacute;tomn&yacute; z&aacute;stupca KOP Veľk&aacute; Fatra, Miroslav Blahušiak.
Stanovisko OOP mesta Martin: v&yacute;stavba parkovacej plochy pre bytov&uacute; jednotku je situovan&aacute; do
priestoru b&yacute;valej materskej šk&ocirc;lky. Stromy na ktor&eacute; bolo vydan&eacute; s&uacute;hlasn&eacute; stanovisko na v&yacute;rub rast&uacute;
v priestore vybudovania parkoviska. V priestore sa nach&aacute;dzaj&uacute; aj ďalšie dreviny, ktor&eacute; zostan&uacute; pri
stavbe parkovac&iacute;ch pl&ocirc;ch zachoval&eacute;.
Nakoľko p&ocirc;vodn&yacute; majiteľ po zrušen&iacute; prev&aacute;dzky školsk&eacute;ho
objekt ďalej neprev&aacute;dzkoval,
priestor hlavne vonkajš&iacute;
sa zmenil na skl&aacute;dku
nekontrolovan&eacute;ho odpadu s postupn&yacute;m mechanick&yacute;m poškodzovan&iacute;m a odumieran&iacute;m drev&iacute;n.
Na z&aacute;klade vypracovanej PD stromy, ktor&eacute; žiadateľ požaduje zo stanovišťa odstr&aacute;niť sa povoľuj&uacute;.
Stanovisko KOP Veľk&aacute; Fatra: mimovl&aacute;dna organiz&aacute;cia s&uacute;hlas&iacute; s v&yacute;rubom stromov.
Spr&aacute;vny org&aacute;n dal &uacute;častn&iacute;kom konania pred vydan&iacute;m rozhodnutia možnosť
vyjadriť sa k jeho
podkladu i sp&ocirc;sobu jeho zistenia, pr&iacute;padne navrhn&uacute;ť jeho doplnenie. &Uacute;častn&iacute;ci konania nemali žiadne
doplňuj&uacute;ce n&aacute;vrhy k rozhodnutiu a s&uacute;hlasia s jeho vydan&iacute;m v plnom znen&iacute;.
--Na z&aacute;klade uveden&eacute;ho
111(,stOľv1arttrr-dl~0-pri~1~išR~-crg&aacute;n ~t&oacute;.t!J::.:j c.ť,:i&quot;.'Y ~,r pr~.'('&middot;m stupn: vn veciach
ochrany drev&iacute;n rozhodol tak, ako je uveden&eacute; vo v&yacute;rokovej časti tohto rozhodnutia.
Proti tomuto rozhodnutiu je možn&eacute; podať v zmysle ustanovenia
&sect; 54 z&aacute;kona č.7111967 Zb.
o spr&aacute;vnom konan&iacute; v znen&iacute; neskorš&iacute;ch predpisov odvolanie do 15 dn&iacute; od jeho doručenia na spr&aacute;vny
org&aacute;n, ktor&yacute; napadnut&eacute; rozhodnutie vydal. Odvolac&iacute;m org&aacute;nom je Okresn&yacute; &uacute;rad Martin, Odbor
o životn&eacute; prostredie. Toto rozhodnutie, ktor&eacute; po vyčerpan&iacute; riadnych opravn&yacute;ch
prostriedkov nadobudne pr&aacute;voplatnosť, je možn&eacute; presk&uacute;mať s&uacute;dom v zmysle pr&iacute;slušn&yacute;ch ustanoven&iacute;
občianskeho s&uacute;dneho poriadku.
\\(\\ \i \ \~
Mgr. art.l~~~v
Rozhodnutie obdržia
: Pe Pplus, s.r.o., Ulica Gogoľova 3, 036 Ol Martin
: KOP Vel'k&aacute; Fatra, Švermoval, 03861 Vr&uacute;tky
: SIŽP, Inšpektor&aacute;t ochrany pr&iacute;rody, Legion&aacute;rska 5,01205
: Mesto Martin.
: Ing. Emil Hanzel
Univerzita Komenského v Bratislave Školenie ubytovaných
Lysus™ Catheter System
stiahni - Fajnorka
Školenie ubytovaných o ochrane pred požiarmi a
LIPTOVSKÉ MUZEUM V RUŽOMBERKU Nám.Š.N.Hýroša 10 034
ŠkVP Ochrana osôb pred požiarom.pdf
3 Deň mesta snina
Návod k montáži a obsluze krbových vložek
Frekvenčné meniče, ich využitie na pohony