Source: https://www.ecfr.gov/cgi-bin/text-idx?mc=true&node=ap40.16.63_110042.1&rgn=div9
Timestamp: 2019-12-15 06:32:38
Document Index: 488479753

Matched Legal Cases: ['§63', 'art 60', 'art 63', 'art 60', 'art 60', '§63']

As stated in §63.9991, you must comply with the following applicable emission limits:
If your EGU is in this
subcategory . . .
You must meet the following emission limits and work
practice standards . . .
Using these requirements, as appropriate (e.g., specified sampling volume or test run duration) and limitations with the test
methods in Table 5 to this Subpart . . .
1. Coal-fired unit not low rank virgin coal a. Filterable particulate matter (PM) 9.0E-2 lb/MWh1 Collect a minimum of 4 dscm per run.
b. Hydrogen chloride (HCl) 1.0E-2 lb/MWh For Method 26A at appendix A-8 to part 60 of this chapter, collect a minimum of 3 dscm per run. For ASTM D6348-032 or Method 320 at appendix A to part 63 of this chapter, sample for a minimum of 1 hour.
Sulfur dioxide (SO2)3 1.0 lb/MWh SO2 CEMS.
2. Coal-fired units low rank virgin coal a. Filterable particulate matter (PM) 9.0E-2 lb/MWh1 Collect a minimum of 4 dscm per run.
b. Hydrogen chloride (HCl) 1.0E-2 lb/MWh For Method 26A, collect a minimum of 3 dscm per run For ASTM D6348-032 or Method 320, sample for a minimum of 1 hour.
3. IGCC unit a. Filterable particulate matter (PM) 7.0E-2 lb/MWh4 9.0E-2 lb/MWh5 Collect a minimum of 1 dscm per run.
b. Hydrogen chloride (HCl) 2.0E-3 lb/MWh For Method 26A, collect a minimum of 1 dscm per run; for Method 26 at appendix A-8 to part 60 of this chapter, collect a minimum of 120 liters per run. For ASTM D6348-032 or Method 320, sample for a minimum of 1 hour.
Sulfur dioxide (SO2)3 4.0E-1 lb/MWh SO2 CEMS.
4. Liquid oil-fired unit—continental (excluding limited-use liquid oil-fired subcategory units) a. Filterable particulate matter (PM) 3.0E-1 lb/MWh1 Collect a minimum of 1 dscm per run.
Mercury (Hg) 1.0E-4 lb/GWh For Method 30B at appendix A-8 to part 60 of this chapter sample volume determination (Section 8.2.4), the estimated Hg concentration should nominally be < 1⁄2 the standard.
b. Hydrogen chloride (HCl) 4.0E-4 lb/MWh For Method 26A, collect a minimum of 3 dscm per run. For ASTM D6348-032 or Method 320, sample for a minimum of 1 hour.
c. Hydrogen fluoride (HF) 4.0E-4 lb/MWh For Method 26A, collect a minimum of 3 dscm per run. For ASTM D6348-032 or Method 320, sample for a minimum of 1 hour.
5. Liquid oil-fired unit—non-continental (excluding limited-use liquid oil-fired subcategory units) a. Filterable particulate matter (PM) 2.0E-1 lb/MWh1 Collect a minimum of 1 dscm per run.
Mercury (Hg) 4.0E-4 lb/GWh For Method 30B sample volume determination (Section 8.2.4), the estimated Hg concentration should nominally be < 1⁄2 the standard.
b. Hydrogen chloride (HCl) 2.0E-3 lb/MWh For Method 26A, collect a minimum of 1 dscm per run;for Method 26, collect a minimum of 120 liters per run. For ASTM D6348-032 or Method 320, sample for a minimum of 1 hour.
c. Hydrogen fluoride (HF) 5.0E-4 lb/MWh For Method 26A, collect a minimum of 3 dscm per run.For ASTM D6348-032 or Method 320, sample for a minimum of 1 hour.
6. Solid oil-derived fuel-fired unit a. Filterable particulate matter (PM) 3.0E-2 lb/MWh1 Collect a minimum of 1 dscm per run.
1 Gross output.
2 Incorporated by reference, see §63.14.
3 You may not use the alternate SO2 limit if your EGU does not have some form of FGD system (or, in the case of IGCC EGUs, some other acid gas removal system either upstream or downstream of the combined cycle block) and SO2 CEMS installed.
4 Duct burners on syngas; gross output.
5 Duct burners on natural gas; gross output.
[81 FR 20190, Apr. 6, 2016]