Source: http://codeofchina.com/standard/GBT16895.18-2010.html
Timestamp: 2020-08-08 15:19:56
Document Index: 481270581

Matched Legal Cases: ['art 5', 'art 5', 'art 5', 'art 5', 'art 2', 'art 4', 'art 1', 'art 22', 'art 4', 'art 5', 'art 4', 'art 1', 'art 4', 'art 3', 'art 3', 'art 1', 'art 4', 'art 4', 'art 4', 'art 4', 'art 1', 'art 4', 'art 4', 'art 5', 'art 5']

GB/T 16895.18-2010 English Version, GB/T 16895.18-2010 Electrical installations of buildings—Part 5-51:Selection and erection of electrical equipment—Common rules (English Version) - Code of China
Position: Chinese Standard in English/GB/T 16895.18-2010
GB/T 16895.18-2010 Electrical installations of buildings—Part 5-51:Selection and erection of electrical equipment—Common rules (English Version)
Standard No.: GB/T 16895.18-2010 Status: valid remind me the status change
Add GB/T 16895.18-2010 to Cart
Detail of GB/T 16895.18-2010
Introduction of GB/T 16895.18-2010
Contents of GB/T 16895.18-2010
Standard No.: GB/T 16895.18-2010
English Name: Electrical installations of buildings—Part 5-51:Selection and erection of electrical equipment—Common rules
Chinese Name: 建筑物电气装置　第5-51部分：电气设备的选择和安装　通用规则
Superseding: GB/T 16895.18-2002 Electrical installations of buildings--Part 5:Selection and erection of electrical equipment--Chapter 51:Common rules
510 Introduction 510.1 Scope This part deals with the selection of equipment and its erection. It provides common rules for compliance with measures of protection for safety, requirements for proper functioning for intended use of the installation, and requirements appropriate to the external influences foreseen. 510.2 Normative References The following referenced documents are indispensable for the application of this document. For dated references, only the edition cited applies. For undated references, the latest edition of the referenced document (including any amendments) applies. GB/T 2423.17-2008	Environmental Testing - Part 2: Tests. Test Ka: Salt Mist (IEC 60068-2-11:1981) GB 3836 (All Parts)	Electrical Apparatus for Explosive Gas Atmospheres [IEC 60079 (All Parts)] GB/T 4025-2003	Basic and Safety Principles for Man-machine Interface, Marking and Identification - Coding Principles for Indication Devices and Actuators (IEC 60073:1996) GB/T 4205-2003	Man-machine Interface (MMI) - Actuating Principles (IEC 60447:1993) GB 4208-2008	Degrees of Protection Provided by Enclosures (IP Code) (IEC 60529:1989) GB/T 4728 (All Parts)	Graphical Symbols for Diagrams (IEC 60617) GB/T 4798.4-2007	Environmental Conditions Existing in the Application of Electric and Electronic Products - Part 4: Stationary Use at Non-weather-protected Locations (IEC 60721-3-4:1995, MOD) GB/T 5094.1-2002	Industrial Systems, Installations and Equipment and Industrial Products - Structuring Principles and Reference Designations - Part 1: Basic Rules (IEC 61346-1:1996, IDT) GB/T 6988 (All Parts)	Preparation of Documents Used in Electrotechnology (IEC 61082) GB 7947-2006	Basic and Safety Principles for Man-machine Interface, Marking and Identification - Identification of Conductors by Colors or Numerals(IEC 60446:1999) GB/T 11020-2005	Flammability of Solid Non-metallic Materials When Exposed to Flame Sources - List of Test Methods (IEC 60707:1999, IDT) GB/T 14598.13-2008	Electrical Relays - Part 22: Electrical Disturbance Tests for Measuring Relays and Protection Equipment - Section 1: 1Mhz Burst Disturbance Tests (IEC 60255-22-1:1988, eqv) GB 16895.2-2005	Electrical Installations of Buildings - Part 4-42: Protection for Safety - Protection against Thermal Effects (IEC 60364-4-42: 2001, IDT) GB 16895.3-2004	Electrical Installations of Buildings - Part 5-54: Selection and Erection of Electrical Equipment - Earthing Arrangements and Protective Conductors and Protective Bonding Conductors (IEC 60364-5-54: 2002, IDT) GB 16895.21-2004	Electrical Installations of Buildings - Part 4-41: Protection for Safety - Protection against Electric Shock (IEC 60364-4-41: 2001, IDT) GB/T 17045-2008	Protection against Electric Shock - Common Aspects for Installation and Equipment (IEC 61140: 2001+A1: 2004, IDT) GB/T 17626.3-2006	Electromagnetic Compatibility - Testing and Measurement Techniques - Radiated Radio-frequency Electromagnetic Field Immunity Test (IEC 61000-4-3: 2002) GB/T 17626.12-1998	Electromagnetic Compatibility - Testing and Measurement Techniques - Oscillatory Waves Immunity Test (IEC 61000-4-12:1995) GB 18039 (All Parts)	Electromagnetic Compatibility - Environment (IEC 61000-2) GB/Z 18039.1-2000	Electromagnetic Compatibility - Environment - Classification of Electromagnetic Environments (IEC 61000-2-5:1996) GB/T 18039.3-2003	Electromagnetic Compatibility - Environment - Compatibility Levels for Low-frequency Conducted Disturbances and Signaling in Public Low-voltage Power Supply Systems (IEC 61000-2-2:1990) IEC 60364-1: 2001	Electrical Installations of Buildings - Part 1: Fundamental Principles IEC 60364-4-44: 2001	Electrical Installations of Buildings - Part 4-44: Protection for Safety - Protection against Voltage Disturbances and Electromagnetic Disturbances IEC 60364-5-52: 2001	Electrical Installations of Buildings Selection and Erection of Electrical Equipment - Wiring Systems IEC 60721-3-0:1984	Classification of Environmental Conditions - Part 3: Classification of Groups of Environmental Parameters and Their Severities - Introduction IEC 60721-3-3:1994	Classification of Environmental Conditions - Part 3: Classification of Groups of Environmental Parameters and Their Severities - Section 3: Stationary Use at Weather-protected Locations IEC 60884-1 2002	Plugs and Socket - Outlets for Household and Similar Purposes - Part 1: General Requirements IEC 61000-4-2:1995	Electromagnetic Compatibility (EMC) - Part 4: Testing and Measurement Techniques - Section 2: Electrostatic Discharge Immunity Test. IEC 61000-4-4:1995	Electromagnetic Compatibility (EMC) - Part 4: Testing and Measurement Techniques - Section 4: Electrical Fast Transient/Burst Immunity Test. IEC 61000-4-6:1996	Electromagnetic Compatibility (EMC) - Part 4: Testing and Measurement Techniques - Section 6: Immunity to Conducted Disturbances, Induced by Radio-frequency Fields IEC 61000-4-8:1993	Electromagnetic Compatibility (EMC) - Part 4: Testing and Measurement Techniques - Section 8: Power Frequency Magnetic Field Immunity Test. IEC 61024-1:1990	Protection of Structures Against Lightning - Part 1: General Principles 510.3 General Every item of equipment shall be selected and erected so as to allow compliance with the rules stated in the following clauses of this part and the relevant rules in other parts. 511 Compliance with Standards 511.1 Every item of equipment shall comply with such standards as are appropriate and, in addition, with any applicable standards of the ISO. 511.2 Where there are no applicable or ISO standards, the item of equipment concerned shall be selected by special agreement between the person specifying the installation and the installer.
Foreword	I 510 Introduction 510.1 Scope 510.2 Normative References 510.3 General 511 Compliance with Standards 512 Operational Conditions and External Influences 512.1 Operational Conditions 512.2 External influences 513 Accessibility 513.1 General 514 Identification 514.1 General 514.2 Wiring Systems 514.3 Identification of Neutral and Protective Conductors 514.4 Protective Devices 514.5 Diagrams 515 Prevention of Mutual Detrimental Influence 516 Measures Related to Protective Conductor Currents 516.1 Transformer 516.2 Signaling systems Appendix A (Informative) Concise List of External Influences Appendix B (Informative) Interdependence of Air Temperature, Relative Air Humidity and Absolute Air Humidity Appendix C (Normative) Classification of Mechanical Conditions Appendix D (Normative) Classification of Macro-environments Appendix E (Informative) Permissible Protective Conductor Currents for Equipment Bibliography
* GB/T 4025-2003 Basic and safety principles for man-machine interface,marking and identification--Coding principles for indicatoin Devices and actuators
* GB/T 4205-2003
* GB/T 4798.4-2007 Environmental conditions existing in the application of electric and electronic products—Part 4:Stationary use at non-weather-protected locations
* GB 7947-2006 Basic and safety principles for man-machine interface marking and identification - Identification of conductors by colours or numerals
* GB/T 11020-2005 Flammability of solid non-metallic meterials when exposed to flame sources - List of test methods
* GB 16895.2-2005 Electrical installations of buildings - Part 4-42: Protection for safety - Protection against - Thermal effects
* GB/Z 18039.1-2000 Electromagnetic compatibility--Environment--Classification of electromagnetic environments
* GB/T 18039.3-2003 Electromagnetic compatibility--Environment--Compatibility levels for low-frequency conducted disturbances and signalling in public low-voltage power supply systems
Referred in GB/T 16895.18-2010:
Standard No. GB/T 16895.18-2010
Electrical installations of buildings—Part 5-51:Selection and erection of electrical equipment—Common rules
建筑物电气装置　第5-51部分：电气设备的选择和安装　通用规则
GB/T 16895.18-2002 Electrical installations of buildings--Part 5:Selection and erection of electrical equipment--Chapter 51:Common rules
GB/T 16895.18-2010, GB 16895.18-2010, GBT 16895.18-2010, GB/T16895.18-2010, GB/T 16895.18, GB/T16895.18, GB16895.18-2010, GB 16895.18, GB16895.18, GBT16895.18-2010, GBT 16895.18, GBT16895.18