Source: http://docplayer.fr/60013267-International-standard-norme-internationale.html
Timestamp: 2018-11-19 05:40:18
Document Index: 421641809

Matched Legal Cases: ['art 1', 'art 1', 'art 2', 'art 1', 'art 2', 'art 1', 'art 3']

1 INTERNATIONAL STANDARD NORME INTERNATIONALE IEC Edition Electrolyte and water for vented lead acid accumulators Part 1: Requirements for electrolyte Électrolyte et eau pour accumulateurs plomb-acide ouverts Partie 1: Exigences pour l'électrolyte INTERNATIONAL ELECTROTECHNICAL COMMISSION COMMISSION ELECTROTECHNIQUE INTERNATIONALE ICS ISBN Warning! Make sure that you obtained this publication from an authorized distributor. Attention! Veuillez vous assurer que vous avez obtenu cette publication via un distributeur agréé. Registered trademark of the International Electrotechnical Commission Marque déposée de la Commission Electrotechnique Internationale
2 2 IEC :2016 IEC 2016 CONTENTS FOREWORD Scope Normative references Terms and definitions Preparation of electrolyte for lead-acid accumulators Physical properties of diluted sulfuric acid as electrolyte Dependence of acid density on temperature Relationship of electrolyte density on the content of sulfuric acid at 25 C Electrolyte density compared to the state of discharge Requirements of sulfuric acid used as electrolyte Impurities of sulfuric acid of higher concentration degrees Impurities of filling acid Impurities of operating electrolyte Storage of electrolyte Remedy in the event of damage due to electrolyte Bibliography Table 1 Correction of density from measuring temperature to reference/specified temperature... 7 Table 2 Acid density versus percentage of sulphuric acid at 25 C... 8 Table 3 Maximum allowed impurities of diluted sulfuric acid as filling electrolyte for lead-acid batteries in the density range 1,30 kg/l... 9 Table 4 Maximum allowed impurity of diluted acid as operating electrolyte for lead-acid batteries in the density range 1,30 kg/l... 10
3 IEC :2016 IEC INTERNATIONAL ELECTROTECHNICAL COMMISSION ELECTROLYTE AND WATER FOR VENTED LEAD ACID ACCUMULATORS Part 1: Requirements for electrolyte FOREWORD 1) The International Electrotechnical Commission (IEC) is a worldwide organization for standardization comprising all national electrotechnical committees (IEC National Committees). The object of IEC is to promote international co-operation on all questions concerning standardization in the electrical and electronic fields. To this end and in addition to other activities, IEC publishes International Standards, Technical Specifications, Technical Reports, Publicly Available Specifications (PAS) and Guides (hereafter referred to as IEC Publication(s) ). Their preparation is entrusted to technical committees; any IEC National Committee interested in the subject dealt with may participate in this preparatory work. International, governmental and nongovernmental organizations liaising with the IEC also participate in this preparation. IEC collaborates closely with the International Organization for Standardization (ISO) in accordance with conditions determined by agreement between the two organizations. 2) The formal decisions or agreements of IEC on technical matters express, as nearly as possible, an international consensus of opinion on the relevant subjects since each technical committee has representation from all interested IEC National Committees. 3) IEC Publications have the form of recommendations for international use and are accepted by IEC National Committees in that sense. While all reasonable efforts are made to ensure that the technical content of IEC Publications is accurate, IEC cannot be held responsible for the way in which they are used or for any misinterpretation by any end user. 4) In order to promote international uniformity, IEC National Committees undertake to apply IEC Publications transparently to the maximum extent possible in their national and regional publications. Any divergence between any IEC Publication and the corresponding national or regional publication shall be clearly indicated in the latter. 5) IEC itself does not provide any attestation of conformity. Independent certification bodies provide conformity assessment services and, in some areas, access to IEC marks of conformity. IEC is not responsible for any services carried out by independent certification bodies. 6) All users should ensure that they have the latest edition of this publication. 7) No liability shall attach to IEC or its directors, employees, servants or agents including individual experts and members of its technical committees and IEC National Committees for any personal injury, property damage or other damage of any nature whatsoever, whether direct or indirect, or for costs (including legal fees) and expenses arising out of the publication, use of, or reliance upon, this IEC Publication or any other IEC Publications. 8) Attention is drawn to the Normative references cited in this publication. Use of the referenced publications is indispensable for the correct application of this publication. 9) Attention is drawn to the possibility that some of the elements of this IEC Publication may be the subject of patent rights. IEC shall not be held responsible for identifying any or all such patent rights. International Standard IEC has been prepared by IEC technical committee 21: Secondary cells and batteries. The text of this standard is based on the following documents: FDIS 21/874/FDIS Report on voting 21/881/RVD Full information on the voting for the approval of this standard can be found in the report on voting indicated in the above table. This publication has been drafted in accordance with the ISO/IEC Directives, Part 2.
4 4 IEC :2016 IEC 2016 A list of all parts of the IEC series can be found, under the general title Electrolyte and water for vented lead acid accumulators, on the IEC website. The committee has decided that the contents of this publication will remain unchanged until the stability date indicated on the IEC web site under " in the data related to the specific publication. At this date, the publication will be reconfirmed, withdrawn, replaced by a revised edition, or amended. The contents of the corrigendum of May 2017 have been included in this copy.
5 IEC :2016 IEC ELECTROLYTE AND WATER FOR VENTED LEAD ACID ACCUMULATORS Part 1: Requirements for electrolyte 1 Scope This part of IEC applies to electrolyte and their components used for filling vented lead-acid batteries, for example dry charged cells or batteries, and for electrolyte replacement or electrolyte density adjustment of batteries in operation. This international standard defines the composition, purity and properties of electrolyte to be applied where specific instructions from the battery manufacturer are not available. 2 Normative references The following documents, in whole or in part, are normatively referenced in this document and are indispensable for its application. For dated references, only the edition cited applies. For undated references, the latest edition of the referenced document (including any amendments) applies. IEC , Electrolyte and water for vented lead acid accumulators Part 2: Requirements for water
6 14 IEC :2016 IEC 2016 SOMMAIRE AVANT-PROPOS Domaine d application Références normatives Termes et définitions Préparation de l'électrolyte pour les accumulateurs plomb-acide Propriétés physiques de l'acide sulfurique dilué utilisé comme électrolyte Rapport entre la densité de l'acide et la température Relation entre la densité de l électrolyte et la concentration en acide sulfurique à 25 C Densité de l'électrolyte comparée à l'état de décharge Exigences pour l'acide sulfurique utilisé comme électrolyte Impuretés de l'acide sulfurique à des degrés de concentration élevés Impuretés de l'acide de remplissage Impuretés de l'électrolyte de fonctionnement Stockage de l électrolyte Mesures à prendre en cas de dommages dus à l'électrolyte Bibliographie Tableau 1 Correction de la densité entre la température de mesure et la température de référence/spécifiée Tableau 2 Densité d'acide par rapport au pourcentage d'acide sulfurique à 25 C Tableau 3 Impuretés maximales admises dans l'acide sulfurique dilué utilisé comme électrolyte pour le remplissage des batteries plomb-acide dans la plage de densités 1,30 kg/l Tableau 4 Impuretés maximales admises dans l'acide dilué utilisé comme électrolyte de fonctionnement des batteries plomb-acide dans la plage de densités 1,30 kg/l... 22
7 IEC :2016 IEC COMMISSION ÉLECTROTECHNIQUE INTERNATIONALE ÉLECTROLYTE ET EAU POUR ACCUMULATEURS PLOMB-ACIDE OUVERTS Partie 1: Exigences pour l'électrolyte AVANT-PROPOS 1) La Commission Electrotechnique Internationale (IEC) est une organisation mondiale de normalisation composée de l'ensemble des comités électrotechniques nationaux (Comités nationaux de l IEC). L IEC a pour objet de favoriser la coopération internationale pour toutes les questions de normalisation dans les domaines de l'électricité et de l'électronique. A cet effet, l IEC entre autres activités publie des Normes internationales, des Spécifications techniques, des Rapports techniques, des Spécifications accessibles au public (PAS) et des Guides (ci-après dénommés "Publication(s) de l IEC"). Leur élaboration est confiée à des comités d'études, aux travaux desquels tout Comité national intéressé par le sujet traité peut participer. Les organisations internationales, gouvernementales et non gouvernementales, en liaison avec l IEC, participent également aux travaux. L IEC collabore étroitement avec l'organisation Internationale de Normalisation (ISO), selon des conditions fixées par accord entre les deux organisations. 2) Les décisions ou accords officiels de l IEC concernant les questions techniques représentent, dans la mesure du possible, un accord international sur les sujets étudiés, étant donné que les Comités nationaux de l IEC intéressés sont représentés dans chaque comité d études. 3) Les Publications de l IEC se présentent sous la forme de recommandations internationales et sont agréées comme telles par les Comités nationaux de l IEC. Tous les efforts raisonnables sont entrepris afin que l IEC s'assure de l'exactitude du contenu technique de ses publications; l IEC ne peut pas être tenue responsable de l'éventuelle mauvaise utilisation ou interprétation qui en est faite par un quelconque utilisateur final. 4) Dans le but d'encourager l'uniformité internationale, les Comités nationaux de l IEC s'engagent, dans toute la mesure possible, à appliquer de façon transparente les Publications de l IEC dans leurs publications nationales et régionales. Toutes divergences entre toutes Publications de l IEC et toutes publications nationales ou régionales correspondantes doivent être indiquées en termes clairs dans ces dernières. 5) L IEC elle-même ne fournit aucune attestation de conformité. Des organismes de certification indépendants fournissent des services d'évaluation de conformité et, dans certains secteurs, accèdent aux marques de conformité de l IEC. L IEC n'est responsable d'aucun des services effectués par les organismes de certification indépendants. 6) Tous les utilisateurs doivent s'assurer qu'ils sont en possession de la dernière édition de cette publication. 7) Aucune responsabilité ne doit être imputée à l IEC, à ses administrateurs, employés, auxiliaires ou mandataires, y compris ses experts particuliers et les membres de ses comités d'études et des Comités nationaux de l IEC, pour tout préjudice causé en cas de dommages corporels et matériels, ou de tout autre dommage de quelque nature que ce soit, directe ou indirecte, ou pour supporter les coûts (y compris les frais de justice) et les dépenses découlant de la publication ou de l'utilisation de cette Publication de l IEC ou de toute autre Publication de l IEC, ou au crédit qui lui est accordé. 8) L'attention est attirée sur les références normatives citées dans cette publication. L'utilisation de publications référencées est obligatoire pour une application correcte de la présente publication. 9) L attention est attirée sur le fait que certains des éléments de la présente Publication de l IEC peuvent faire l objet de droits de brevet. L IEC ne saurait être tenue pour responsable de ne pas avoir identifié de tels droits de brevets et de ne pas avoir signalé leur existence. La Norme internationale IEC a été établie par le comité d'études 21 de l'iec: Accumulateurs. Le texte de cette norme est issu des documents suivants: FDIS 21/874/FDIS Rapport de vote 21/881/RVD Le rapport de vote indiqué dans le tableau ci-dessus donne toute information sur le vote ayant abouti à l'approbation de cette norme. Cette publication a été rédigée selon les Directives ISO/IEC, Partie 2.
8 16 IEC :2016 IEC 2016 Une liste de toutes les parties de la série IEC 62877, publiées sous le titre général Electrolyte et eau pour accumulateurs plomb-acide ouverts, peut être consultée sur le site de l'iec. Le comité a décidé que le contenu de cette publication ne sera pas modifié avant la date de stabilité indiquée sur le site web de l IEC sous " dans les données relatives à la publication recherchée. A cette date, la publication sera reconduite, supprimée, remplacée par une édition révisée, ou amendée. Le contenu du corrigendum de mai 2017 a été pris en considération dans cet exemplaire.
9 IEC :2016 IEC ÉLECTROLYTE ET EAU POUR ACCUMULATEURS PLOMB-ACIDE OUVERTS Partie 1: Exigences pour l'électrolyte 1 Domaine d application Cette partie de l'iec s'applique à l'électrolyte et à ses composants utilisés pour le remplissage des batteries plomb-acide ouvertes, par exemple les éléments chargés secs ou les batteries chargées sèches et pour le remplacement de l'électrolyte ou l'ajustement de la densité de l'électrolyte des batteries en fonctionnement. La présente norme internationale définit la composition, la pureté et les propriétés de l'électrolyte qui doivent être appliquées en l'absence d'instructions spécifiques du fabricant de batteries. 2 Références normatives Les documents suivants sont cités en référence de manière normative, en intégralité ou en partie, dans le présent document et sont indispensables pour son application. Pour les références datées, seule l édition citée s applique. Pour les références non datées, la dernière édition du document de référence s applique (y compris les éventuels amendements). IEC , Electrolyte et eau pour accumulateurs plomb-acide ouverts Partie 2: Exigences pour l'eau
IEC 61190-1-2 Edition 3.0 2014-02 INTERNATIONAL STANDARD NORME INTERNATIONALE colour inside Attachment materials for electronic assembly Part 1-2: Requirements for soldering pastes for high-quality interconnects
IEC 62676-3 Edition 1.0 2013-07 INTERNATIONAL STANDARD NORME INTERNATIONALE Video surveillance systems for use in security applications Part 3: Analog and digital video interfaces Systèmes de vidéosurveillance