Source: https://www.ada.gov/SpringhillattI.htm
Timestamp: 2018-02-20 19:31:40
Document Index: 455222835

Matched Legal Cases: ['§ 35', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 5', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4']

SETTLEMENT AGREEMENT BETWEEN THE UNITED STATES OF AMERICA AND THE CITY OF SPRINGHILL, LOUISIANA, Attachment I
Please Note: Paragraph 48 of the Settlement Agreement requires that within three months of the effective date of this Agreement, the City will provide signage as necessary to comply with 28 C.F.R. § 35.163(b), after having surveyed all facilities that are the subject of this Agreement for the purpose of identifying those that have multiple entrances not all of which are accessible.
1. Within 12 months of the effective date of this Agreement, the City will complete the following modifications to the Springhill Police Department, located at 025 Clinic Street, in Springhill:
a. Ramp: The ramp is inaccessible because it lacks handrails, edge protection, and a level landing where the route changes direction. Provide a ramp that is at least 36 inches wide with a slope not exceeding 1:12 and a cross slope not exceeding 1:50; with level landings at least as wide as the ramp and 60 inches long at the top and bottom of the ramp; with level landings measuring at least 60 inches by 60 inches when the ramp changes direction; and edge protection that is at least 2 inches high at the drop off sides. Provide handrails that are between 1¼ inches and 1½ inches in diameter such that the inside handrail is continuous and both handrails have a continuous gripping surface along both sides of the ramp extending at least 12 inches beyond the top and bottom of the ramp parallel with the ground surface; the handrails do not rotate within their fittings; and both handrails are mounted between 34 inches and 38 inches above the ramp surface and 1½ inches from the wall, with ends rounded or returned smoothly to the floor, wall, or post. Ensure that the ramp and approaches are designed so that water will not accumulate on walking surfaces. Standards §§ 4.1.2(1), 4.1.2(2), 4.3.8, 4.8.
b. Interior Signage: The permanent room signs do not have raised and Braille characters and are not consistently mounted with their centerline at 60 inches on the wall to the latch side of the door. Provide permanent room signage with upper case, sans serif or simple serif type letters and numerals, meeting the requirements of the Standards for character height, raised characters, finish and contrast, accompanied by Grade 2 Braille; mounted on the wall adjacent to the latch side of the door or on the nearest adjacent wall at a height of 60 inches above the finished floor to the centerline of the sign; and located so that a person may approach within 3 inches of the signage without encountering protruding objects or standing within the swing of a door. Standards §§ 4.1.2(7), 4.30.1, 4.30.4, 4.30.5, 4.30.6.
c. Laundry Room: The laundry room door is inaccessible because knob hardware is used. Provide a door with hardware that is easy to grasp with one hand and that does not require tight grasping, pinching, or twisting of the wrist to operate. Lever-operated mechanisms, push-type mechanisms, and U-shaped handles are acceptable designs. Standards §§ 4.1.3(7)(b), 4.13.9.
d. Men’s Single User Toilet Room
i. The toilet is inaccessible because the flush control is on the closed side, is too high. Provide a flush control mounted on the “open” side of the toilet’s clear floor space; 44 inches or less above the finished floor; and requiring a maximum of 5 pounds of force to operate; or provide an automatic flush device. Standards §§ 4.1.3(11), 4.22.4, 4.16.5, 4.17.2, 4.27.4.
ii. The toilet paper dispenser is inaccessible because it is 39 inches from the rear wall. Provide a toilet paper dispenser that is mounted within reach, with its top at least 1½ inches under the side grab bar, and centered at least 19 inches above the finished floor. Standards §§ 4.1.3(11), 4.22.4, 4.16.6, Fig. 29(b).
e. Women’s Single User Toilet Room
i. The door to the women’s toilet room is inaccessible because the pressure required to open the door is 9 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards §§ 4.1.3(7)(b), 4.13.11(2)(b).
f. Conference Room: The computer table is inaccessible because the knee clearance is only 24 inches high. Provide a computer on a table or counter that has clear floor space that is 30 inches wide and 48 inches deep, knee clearance at least 27 inches high, 30 inches wide, and 19 inches deep, and a writing surface between 28 and 34 inches above the finished floor. Standards §§ 4.1.3(18), 4.2.4.1, 4.32.
g. Jail
i. The unisex shower in the jail is inaccessible because the size and clear floor space do not comply with roll-in shower or transfer shower types, the controls are not mounted correctly, and it is lacking a seat. Provide a shower in this room that is exactly 36 inches wide and 36 inches deep with a 48 inch long and 36 inch wide clear floor space alongside the shower opening, and an L-shaped shower seat mounted on the wall opposite the controls and extending the full depth of the stall; OR a shower that is at least 30 inches deep and 60 inches wide with no curb or threshold and with a 36 inch deep and 60 inch wide clear floor space at the shower opening. Ensure that the shower has grab bars, controls, a shower spray unit, and a seat, curb, and enclosure, if provided, that comply fully with the Standards and with Figs. 35, 36, and 37, as applicable. Standards §§ 4.1.3(11), 4.21, Figs. 35, 36, 37.
ii. The counter at the visitor’s booth is inaccessible because it is blocked by a fixed stool and because the height of the window would render it difficult for a person with a disability to see through it. For at least one visitation booth, provide clear floor space in front of the counter on both the visitor and inmate sides and provide a window at a height that can be used by persons who use wheelchairs. Standards §§ 4.1.1(2), 7.2(1), 4.1.3(1), 4.3.
h. Conference Room: The conference room table is inaccessible because the table does not provide 27 inches of knee space. Provide a computer on a table or counter that has clear floor space that is 30 inches wide and 48 inches deep, knee clearance at least 27 inches high, 30 inches wide, and 19 inches deep, and a writing surface between 28 and 34 inches above the finished floor. Standards §§ 4.1.3(18), 4.2.4.1, 4.32.
i. Kitchen: The kitchen counter is inaccessible because the counter is 36 inches high and the sink faucet and controls are out of reach. Provide a portion of the main counter on an accessible route such that the counter is 60 inches minimum in length and between 28 and 34 inches in height, or provide service at accessible tables within the same area of the facility. Standards § 5.2.
2. Within 12 months of the effective date of this Agreement, the City will complete the following modifications to the Frank Anthony Community Activity Center located at 301 West Church Street, Springhill:
i. Women’s Toilet Rooms with Stalls (Lobby)
(1) No accessible coat hook is provided in the toilet stall for persons who use wheelchairs or in the toilet stall for ambulatory persons with disabilities. For each, provide a coat hook at a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.1.3(12)(a), 4.25.2, 4.25.3, 4.2.4, 4.2.5, 4.2.6.
ii. Men’s Toilet Room with Stall (Lobby)
(1) The men’s toilet room is inaccessible because the pressure required to open the door is 9 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards §§ 4.1.3(7)(b), 4.13.11(2)(b).
(2) The flush control on the lower urinal is too high. Provide a urinal with an elongated rim mounted 17 inches or less above the finished floor, a clear floor space of at least 30 inches wide and 48 inches deep centered on the urinal, and a flush control height of 44 inches or less above the finished floor. Standards §§ 4.1.3(11), 4.22.5, 4.18.2, 4.18.3, 4.18.4.
(a) The toilet is inaccessible because the flush control is mounted on the closed side. Provide a flush control mounted on the “open” side of the toilet’s clear floor space; 44 inches or less above the finished floor; and requiring a maximum of 5 pounds of force to operate; or provide an automatic flush device. Standards §§ 4.1.3(11), 4.22.4, 4.16.5, 4.17.2, 4.27.4.
(b) No accessible coat hook has been provided. Provide a coat hook at a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.1.3(12)(a), 4.25.2, 4.25.3, 4.2.4, 4.2.5, 4.2.6.
(1) All auditorium area doors are inaccessible because the pressure required to open each door is 10 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards §§ 4.1.3(7)(b), 4.13.11(2)(b).
(2) The auditorium is inaccessible to people with hearing impairments because no assistive listening system (ALS) is provided. Provide a permanently installed ALS or a portable ALS with an adequate number of electrical outlets or other supplementary wiring necessary to support a portable assistive listening system. Also provide two receivers for use by the general public and signage indicating their availability. Standards §§ 4.1.3(19)(b), 4.30, 4.33.
(3) The route to the sound stage is inaccessible because the only routes to the stage have steps with no means of vertical access and the opening at the top of each set of steps is very narrow. Provide at least one accessible route within the boundary of the site connecting these elements that, to the maximum extent feasible, coincides with the route for the general public. The accessible route must have a minimum clear width of 36 inches, or a minimum clear width of 42 inches if there is a turn around an obstruction less than 48 inches wide; have passing spaces at least 60 inches by 60 inches at least every 200 feet; have a minimum clear headroom of 80 inches; have a surface that is firm, stable, and slip resistant; have, in the absence of a curb ramp, ramp, elevator, or platform lift, no level changes in excess of ½ inch vertically; and have a running slope of less than 1:20 (5%) (or have been constructed as a fully accessible ramp) and a cross slope of less than 1:50 (2%). Standards §§ 4.1.3(1), 4.3, 4.5, Fig. 7.
iv. Interior Entrance to Prep Area of Stage: The door to the prep are is inaccessible because the pressure required to open the door is 10 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards §§ 4.1.3(7)(b), 4.13.11(2)(b).
v. Prep Area Ramp: The ramp is inaccessible because the inside edges of the handrails are 2 ¼ inches from the walls and the handrails do not return smoothly. Provide handrails that are between 1¼ inches and 1½ inches in diameter such that the inside handrail is continuous and both handrails have a continuous gripping surface along both sides of the ramp extending at least 12 inches beyond the top and bottom of the ramp parallel with the ground surface; the handrails do not rotate within their fittings; and both handrails are mounted between 34 inches and 38 inches above the ramp surface and 1½ inches from the wall, with ends rounded or returned smoothly to the floor, wall, or post. Standards §§ 4.1.2(1), 4.1.2(2), 4.3.8, 4.8.5.
vi. Unisex Toilet Room: Single-User with Shower
(1) No accessible coat hook has been provided. Provide a coat hook at a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.1.3(12)(a), 4.25.2, 4.25.3, 4.2.4, 4.2.5, 4.2.6.
(2) The shower in unisex toilet room is inaccessible because there is a 6½ inch curb at the entrance to the shower, there are no grab bars, the shower unit is inaccessible, and there is no transfer bench. Provide a shower in this room that is exactly 36 inches wide and 36 inches deep with a 48 inch long and 36 inch wide clear floor space alongside the shower opening, and an L-shaped shower seat mounted on the wall opposite the controls and extending the full depth of the stall; OR a shower that is at least 30 inches deep and 60 inches wide with no curb or threshold and with a 36 inch deep and 60 inch wide clear floor space at the shower opening. Ensure that the shower has grab bars, controls, a shower spray unit, and a seat, curb, and enclosure, if provided, that comply fully with the Standards and with Figs. 35, 36, and 37, as applicable. Standards §§ 4.1.3(11), 4.21, Figs. 35, 36, 37.
vii. Unisex Toilet Room: Single-User without Shower
(1) The toilet is inaccessible because its centerline measures 16 inches from the side wall. Provide a toilet with a centerline that measures 18 inches from the near side wall. Standards §§ 4.1.3(11), 4.22.4, 4.16.2, Fig. 28.
b. Council on Aging
i. Women’s Toilet Room: Single-User: The women’s toilet room door is inaccessible because the pressure required to open the door is 12 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards §§ 4.1.3(7)(b), 4.13.11(2)(b).
ii. Men’s Toilet Room: Single-User
(1) The men’s toilet room door is inaccessible because the pressure required to open the door is 12 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards §§ 4.1.3(7)(b), 4.13.11(2)(b).