Source: https://www.law.cornell.edu/cfr/text/40/60.482-11a
Timestamp: 2016-09-30 03:30:41
Document Index: 446527395

Matched Legal Cases: ['art 60', '§ 60', '§ 60', '§ 60', '§ 60', '§ 60', '§ 60', '§ 60', '§ 60', '§ 63', '§ 60']

40 CFR 60.482-11a - Standards: Connectors in gas/vapor service and in light liquid service. | US Law | LII / Legal Information Institute
CFR › Title 40 › Chapter I › Subchapter C › Part 60 › Subpart VVa › Section 60.482-11a 40 CFR 60.482-11a - Standards: Connectors in gas/vapor service and in light liquid service.
§ 60.482-11a Standards: Connectors in gas/vapor service and in light liquid service.
(b) Except as allowed in § 60.482-1a(c), § 60.482-10a, or as specified in paragraph (e) of this section, the owner or operator shall monitor all connectors in gas and vapor and light liquid service as specified in paragraphs (a) and (b)(3) of this section.
(1) The connectors shall be monitored to detect leaks by the method specified in § 60.485a(b) and, as applicable, § 60.485a(c).
CL = Number of connectors measured at 500 ppm or greater, by the method specified in § 60.485a(b).
(d) When a leak is detected pursuant to paragraphs (a) and (b) of this section, it shall be repaired as soon as practicable, but not later than 15 calendar days after it is detected, except as provided in § 60.482-9a. A first attempt at repair as defined in this subpart shall be made no later than 5 calendar days after the leak is detected.
(e) Any connector that is designated, as described in § 60.486a(f)(1), as an unsafe-to-monitor connector is exempt from the requirements of paragraphs (a) and (b) of this section if:
Inaccessible, ceramic, or ceramic-lined connectors.
(1) Any connector that is inaccessible or that is ceramic or ceramic-lined (e.g., porcelain, glass, or glass-lined), is exempt from the monitoring requirements of paragraphs (a) and (b) of this section, from the leak repair requirements of paragraph (d) of this section, and from the recordkeeping and reporting requirements of §§ 63.1038 and 63.1039. An inaccessible connector is one that meets any of the provisions specified in paragraphs (f)(1)(i) through (vi) of this section, as applicable:
At 73 FR 31376, June 2, 2008, § 60.482-11a was stayed until further notice.