Source: https://docplayer.fr/2966359-International-standard-norme-internationale.html
Timestamp: 2020-01-26 03:51:02
Document Index: 397554471

Matched Legal Cases: ['art 2', 'art 2', 'art 2', 'art 2', 'art 1', 'art 2', 'art 4', 'art 4', 'art 4', 'art 4', 'art 4', 'art 4', 'art 3', 'art 3']

INTERNATIONAL STANDARD NORME INTERNATIONALE - PDF Téléchargement Gratuit
1 IEC Edition INTERNATIONAL STANDARD NORME INTERNATIONALE Alarm systems Part 2: Electromagnetic compatibility Immunity requirements for components of fire and security alarm systems Systèmes d'alarme Partie 2: Compatibilité électromagnétique Exigences relatives à l immunité des composants des systèmes d alarme de détection d incendie et de sécurité INTERNATIONAL ELECTROTECHNICAL COMMISSION COMMISSION ELECTROTECHNIQUE INTERNATIONALE PRICE CODE CODE PRIX T ICS ISBN Registered trademark of the International Electrotechnical Commission Marque déposée de la Commission Electrotechnique Internationale
2 IEC:2010 CONTENTS FOREWORD Scope Normative references Terms, definitions and abbreviations Terms and definitions Abbreviations Application of tests Conditions during testing Configuration Environmental conditions Operating condition Functional test Mains supply voltage variations Object of the test Principle Test procedure General Initial examination State of specimen during conditioning Conditioning Measurements during conditioning Final measurements Criteria for compliance Mains supply voltage dips and short interruptions Object of the test Principle Test procedure General Initial examination State of specimen during conditioning Conditioning Measurements during conditioning Final measurements Criteria for compliance Electrostatic discharge Object of the test Principle Test procedure General Initial examination State of specimen during conditioning Conditioning Measurements during conditioning Final measurements Criteria for compliance Radiated electromagnetic fields...14
3 IEC: Object of the test Principle Test procedure General Initial examination State of specimen during conditioning Conditioning Measurements during conditioning Final measurements Criteria for compliance Conducted disturbances induced by electromagnetic fields Object of the test Principle Test procedure General Initial examination State of specimen during conditioning Conditioning Measurements during conditioning Final measurements Criteria for compliance Fast transient bursts Object of the test Principle Test procedure General Initial examination State of specimen during conditioning Conditioning Measurements during conditioning Final measurements Criteria for compliance Slow high energy voltage surge Object of the test Principle Test procedure General Initial examination State of specimen during conditioning Conditioning Measurements during conditioning Final measurements Criteria for compliance...23 Figure 1 Example of relative orientations of the EUT and the field vectors...15 Figure 2 Forms of the modulation types relative to the continuous wave...16 Figure 3 Typical arrangement for coupling onto screened signal lines...22
4 IEC:2010 Table Table Table Table Table Table Table
5 IEC: INTERNATIONAL ELECTROTECHNICAL COMMISSION ALARM SYSTEMS Part 2: Electromagnetic compatibility Immunity requirements for components of fire and security alarm systems FOREWORD 1) The International Electrotechnical Commission (IEC) is a worldwide organization for standardization comprising all national electrotechnical committees (IEC National Committees). The object of IEC is to promote international co-operation on all questions concerning standardization in the electrical and electronic fields. To this end and in addition to other activities, IEC publishes International Standards, Technical Specifications, Technical Reports, Publicly Available Specifications (PAS) and Guides (hereafter referred to as IEC Publication(s) ). Their preparation is entrusted to technical committees; any IEC National Committee interested in the subject dealt with may participate in this preparatory work. International, governmental and nongovernmental organizations liaising with the IEC also participate in this preparation. IEC collaborates closely with the International Organization for Standardization (ISO) in accordance with conditions determined by agreement between the two organizations. 2) The formal decisions or agreements of IEC on technical matters express, as nearly as possible, an international consensus of opinion on the relevant subjects since each technical committee has representation from all interested IEC National Committees. 3) IEC Publications have the form of recommendations for international use and are accepted by IEC National Committees in that sense. While all reasonable efforts are made to ensure that the technical content of IEC Publications is accurate, IEC cannot be held responsible for the way in which they are used or for any misinterpretation by any end user. 4) In order to promote international uniformity, IEC National Committees undertake to apply IEC Publications transparently to the maximum extent possible in their national and regional publications. Any divergence between any IEC Publication and the corresponding national or regional publication shall be clearly indicated in the latter. 5) IEC itself does not provide any attestation of conformity. Independent certification bodies provide conformity assessment services and, in some areas, access to IEC marks of conformity. IEC is not responsible for any services carried out by independent certification bodies. 6) All users should ensure that they have the latest edition of this publication. 7) No liability shall attach to IEC or its directors, employees, servants or agents including individual experts and members of its technical committees and IEC National Committees for any personal injury, property damage or other damage of any nature whatsoever, whether direct or indirect, or for costs (including legal fees) and expenses arising out of the publication, use of, or reliance upon, this IEC Publication or any other IEC Publications. 8) Attention is drawn to the Normative references cited in this publication. Use of the referenced publications is indispensable for the correct application of this publication. 9) Attention is drawn to the possibility that some of the elements of this IEC Publication may be the subject of patent rights. IEC shall not be held responsible for identifying any or all such patent rights. International Standard IEC has been prepared by IEC technical committee 79: Alarm and electronic security systems. This standard is based on EN (1995) and its amendments 1 (1998) and 2 (2003), and integrates the most recent ACEC recommendations 1. 1 ACEC: Advisory Committee on Electromagnetic Compatibility is an IEC committee.
6 IEC:2010 The text of this standard is based on the following documents: FDIS 79/277/FDIS Report on voting 79/293/RVD Full information on the voting for the approval of this standard can be found in the report on voting indicated in the above table. This publication has been drafted in accordance with the ISO/IEC Directives, Part 2. A list of all parts in the IEC series, under the general title Alarm systems, can be found on the IEC website. The committee has decided that the contents of this publication will remain unchanged until the stability date indicated on the IEC web site under " in the data related to the specific publication. At this date, the publication will be reconfirmed, withdrawn, replaced by a revised edition, or amended.
7 IEC: ALARM SYSTEMS Part 2: Electromagnetic compatibility Immunity requirements for components of fire and security alarm systems 1 Scope This part of IEC for immunity requirements applies to the components of the following alarm systems, intended for use in and around buildings in residential, commercial, light industrial and industrial environments: access control systems, for security applications; alarm transmission systems 2 ; CCTV systems, for security applications; fire detection and fire alarm systems; intruder and hold-up alarm systems; social alarm systems. The tests and severities that should be used are the same for indoor and outdoor applications of fixed, movable and portable equipment. The levels do not cover extreme cases, which may occur in any location, but with an extremely low probability of occurrence, or in special locations close to powerful emitters (e.g. radar transmitters). Equipment within the scope of this standard should be designed in order to operate satisfactorily in the environmental electromagnetic conditions of residential, commercial, light industrial and industrial environments. This implies particularly that it should be able to operate correctly within the conditions fixed by the electromagnetic compatibility levels for the various disturbances on the low voltage public supply system as defined by IEC The immunity tests in this standard only concern the most critical disturbance phenomena. For equipment using radio signalling, mains signalling or with connections to the public telephone system, additional requirements, from other standards specific to these signalling media, may apply. This standard does not specify basic safety requirements, such as protection against electrical shocks, unsafe operation, insulation coordination and related dielectric tests. This standard does not cover EMC emission requirements. These are covered by other appropriate standards. 2 Normative references The following referenced documents are indispensable for the application of this document. For dated references, only the edition cited applies. For undated references, the latest edition of the referenced document (including any amendments) applies. 2 Apart from equipment which is part of a public telecommunication network.
8 IEC:2010 IEC :1988, Environmental testing Part 1: General and guidance Amendment 1 (1992) IEC :2002, Electromagnetic compatibility (EMC) Part 2-2: Environment Compatibility levels for low-frequency conducted disturbances and signalling in public lowvoltage power supply systems IEC :2008, Electromagnetic compatibility (EMC) Part 4-2: Testing and measurement techniques Electrostatic discharge immunity test IEC :2006, Electromagnetic compatibility (EMC) Part 4-3: Testing and measurement techniques Radiated, radio-frequency, electromagnetic field immunity test IEC :2004, Electromagnetic compatibility (EMC) Part 4-4: Testing and measurement techniques Electrical fast transient/burst immunity test IEC :2005, Electromagnetic compatibility (EMC) Part 4-5: Testing and measurement techniques Surge immunity test IEC :2008, Electromagnetic compatibility (EMC) Part 4-6: Testing and measurement techniques Immunity to conducted disturbances, induced by radio-frequency fields IEC :2004, Electromagnetic compatibility (EMC) Part 4-11: Testing and measurement techniques Voltage dips, short interruptions and voltage variations immunity tests ETSI EN (all parts), Electromagnetic compatibility and radio spectrum matters (ERM) Electromagnetic compatibility (EMC) standard for radio equipment and services ETSI EN , Electromagnetic compatibility and radio spectrum matters (ERM) General Electromagnetic compatibility (EMC) for radio communications equipment 3 Terms, definitions and abbreviations For the purposes of this document, the following terms, definitions and abbreviations apply. 3.1 Terms and definitions regional product performance standard regional standard which specifies the product performance requirements NOTE Such a standard may include EMC requirements but is not limited to EMC requirements. (e.g. series for fire alarm systems, series for intruder alarm systems) basic EMC standard standards giving the description of, and test and measurement methods for an EMC phenomenon, along with details of the test apparatus and test set-up NOTE Although a basic EMC standard may give guidance on the choice of severity, it does not give the prescribed limits or criteria for compliance intruder alarm system alarm system to detect and indicate the presence, entry or attempted entry of an intruder into supervised premises
9 CEI:2010 SOMMAIRE AVANT-PROPOS Domaine d'application Références normatives Termes, définitions et abréviations Termes et définitions Abréviations Application des essais Conditions pendant l'essai Configuration Conditions d'environnement Condition de fonctionnement Essai fonctionnel Variations de la tension d'alimentation secteur Objet de l'essai Principe Procédure d essais Généralités Vérification initiale Etat de l'échantillon pendant l'épreuve Epreuve Mesures pendant l'épreuve Mesures finales Critères d'acceptation Chutes de tension et interruptions de courte durée de l'alimentation secteur Objet de l'essai Principe Procédure d'essai Généralités Vérification initiale Etat de l'échantillon pendant l'épreuve Epreuve Mesures pendant l'épreuve Mesures finales Critères d'acceptation Décharge électrostatique Objet de l'essai Principe Procédure d'essai Généralités Vérification initiale Etat du spécimen pendant l'épreuve Epreuve Mesures pendant l'épreuve Mesures finales Critères d'acceptation Champs électromagnétiques rayonnés...36
10 CEI: Objet de l'essai Principe Procédure d'essai Généralités Vérification initiale Etat du spécimen pendant l'épreuve Epreuve Mesures pendant l'épreuve Mesures finales Critères d'acceptation Perturbations conduites induites par les champs électromagnétiques Objet de l'essai Principe Procédure d'essai Généralités Vérification initiale Etat du spécimen pendant l'épreuve Epreuve Mesures pendant l'épreuve Mesures finales Critères d'acceptation Transitoires rapides en salves Objet de l'essai Principe Procédures d'essai Généralités Vérification initiale Etat de l échantillon pendant l'épreuve Epreuve Mesures pendant l'épreuve Mesures finales Critères d'acceptation Surtensions lentes à haute énergie Objet de l'essai Principe Procédures d'essai Généralités Vérification initiale Etat du spécimen pendant l'épreuve Epreuve Mesures pendant l'épreuve Mesures finales Critères d'acceptation...46 Figure 1 Exemple d'orientations relatives entre l'est et les vecteurs champs...38 Figure 2 Formes de types de modulation pour l'onde continue...39 Figure 3 Montage typique pour le couplage sur des câbles de signaux blindés...45
11 CEI:2010 Tableau Tableau Tableau Tableau Tableau Tableau Tableau
12 CEI: COMMISSION ÉLECTROTECHNIQUE INTERNATIONALE SYSTÈMES D'ALARME Partie 2: Compatibilité électromagnétique Exigences relatives à l immunité des composants des systèmes d alarme de détection d incendie et de sécurité AVANT-PROPOS 1) La Commission Electrotechnique Internationale (CEI) est une organisation mondiale de normalisation composée de l'ensemble des comités électrotechniques nationaux (Comités nationaux de la CEI). La CEI a pour objet de favoriser la coopération internationale pour toutes les questions de normalisation dans les domaines de l'électricité et de l'électronique. A cet effet, la CEI entre autres activités publie des Normes internationales, des Spécifications techniques, des Rapports techniques, des Spécifications accessibles au public (PAS) et des Guides (ci-après dénommés "Publication(s) de la CEI"). Leur élaboration est confiée à des comités d'études, aux travaux desquels tout Comité national intéressé par le sujet traité peut participer. Les organisations internationales, gouvernementales et non gouvernementales, en liaison avec la CEI, participent également aux travaux. La CEI collabore étroitement avec l'organisation Internationale de Normalisation (ISO), selon des conditions fixées par accord entre les deux organisations. 2) Les décisions ou accords officiels de la CEI concernant les questions techniques représentent, dans la mesure du possible, un accord international sur les sujets étudiés, étant donné que les Comités nationaux de la CEI intéressés sont représentés dans chaque comité d études. 3) Les Publications de la CEI se présentent sous la forme de recommandations internationales et sont agréées comme telles par les Comités nationaux de la CEI. Tous les efforts raisonnables sont entrepris afin que la CEI s'assure de l'exactitude du contenu technique de ses publications; la CEI ne peut pas être tenue responsable de l'éventuelle mauvaise utilisation ou interprétation qui en est faite par un quelconque utilisateur final. 4) Dans le but d'encourager l'uniformité internationale, les Comités nationaux de la CEI s'engagent, dans toute la mesure possible, à appliquer de façon transparente les Publications de la CEI dans leurs publications nationales et régionales. Toutes divergences entre toutes Publications de la CEI et toutes publications nationales ou régionales correspondantes doivent être indiquées en termes clairs dans ces dernières. 5) La CEI elle-même ne fournit aucune attestation de conformité. Des organismes de certification indépendants fournissent des services d'évaluation de conformité et, dans certains secteurs, accèdent aux marques de conformité de la CEI. La CEI n'est responsable d'aucun des services effectués par les organismes de certification indépendants. 6) Tous les utilisateurs doivent s'assurer qu'ils sont en possession de la dernière édition de cette publication. 7) Aucune responsabilité ne doit être imputée à la CEI, à ses administrateurs, employés, auxiliaires ou mandataires, y compris ses experts particuliers et les membres de ses comités d'études et des Comités nationaux de la CEI, pour tout préjudice causé en cas de dommages corporels et matériels, ou de tout autre dommage de quelque nature que ce soit, directe ou indirecte, ou pour supporter les coûts (y compris les frais de justice) et les dépenses découlant de la publication ou de l'utilisation de cette Publication de la CEI ou de toute autre Publication de la CEI, ou au crédit qui lui est accordé. 8) L'attention est attirée sur les références normatives citées dans cette publication. L'utilisation de publications référencées est obligatoire pour une application correcte de la présente publication. 9) L attention est attirée sur le fait que certains des éléments de la présente Publication de la CEI peuvent faire l objet de droits de propriété intellectuelle ou de droits analogues. La CEI ne saurait être tenue pour responsable de ne pas avoir identifié de tels droits de propriété et de ne pas avoir signalé leur existence. La Norme internationale CEI a été établie par le comité d'études 79 de la CEI: Systèmes d alarme et de sécurité électronique. La présente norme est basée sur l EN (1995) et ses Amendements 1 (1998) et 2 (2003), et prend en compte les plus récentes recommandations de l ACEC 1. 1 ACEC: Advisory Committee on Electromagnetic Compatibility est un comité de la CEI.
13 CEI:2010 Le texte de cette norme est issu des documents suivants: FDIS 79/277/FDIS Rapport de vote 79/293/RVD Le rapport de vote indiqué dans le tableau ci-dessus donne toute information sur le vote ayant abouti à l'approbation de cette norme. Cette publication a été rédigée selon les Directives ISO/CEI, Partie 2. Une liste de toutes les parties de la série CEI 62599, présentées sous le titre général Systèmes d alarme, peut être consultée sur le site web de la CEI. Le comité a décidé que le contenu de cette publication ne sera pas modifié avant la date de stabilité indiquée sur le site web de la CEI sous " dans les données relatives à la publication recherchée. A cette date, la publication sera reconduite, supprimée, remplacée par une édition révisée, ou amendée.
14 CEI: SYSTÈMES D'ALARME Partie 2: Compatibilité électromagnétique Exigences relatives à l immunité des composants des systèmes d alarme de détection d incendie et de sécurité 1 Domaine d'application La présente partie de la CEI traitant des exigences d'immunité s'applique aux composants ci-après des systèmes d'alarme, comme ceux conçus pour être utilisés dans et autour des immeubles et qui sont situés dans des environnements tels que les résidences, les commerces, l'industrie légère et les environnements industriels: système de contrôle d'accès pour des applications de sécurité; systèmes de transmission d'alarmes 2 ; système CCTV pour des applications de sécurité; système de détection incendie et d'alarme incendie; système d'alarme d intrusion et de hold-up; système d'alarme sociale. Les essais et les sévérités qu il convient d utiliser sont les mêmes pour des applications intérieures et extérieures, et sont relatifs à des matériels fixes, mobiles et portatifs. Les niveaux ne couvrent pas les cas extrêmes pouvant exister en certains endroits, mais avec une très faible probabilité d'apparition, ou en des lieux particuliers situés à proximité d'émetteurs de forte puissance (par exemple les émetteurs radar). Il convient que les matériels du domaine d'application de la présente norme soient conçus pour fonctionner de manière satisfaisante dans des conditions d'environnement électromagnétique correspondant à des environnements comme les résidences, les commerces, les industries légères et les environnements industriels. Cela implique en particulier qu'il convient que ceux-ci soient capables de fonctionner correctement dans les conditions fixées par les niveaux de compatibilité électromagnétique, avec des perturbations diverses sur le réseau public basse tension comme cela est défini dans la CEI Les essais d'immunité relatifs à la présente norme concernent uniquement le phénomène perturbateur le plus critique. Pour les matériels utilisant des communications par radio, courants porteurs, ou ayant des liaisons avec le réseau téléphonique public, d'autres exigences provenant d'autres normes spécifiques à ces supports de transmission peuvent s appliquer. La présente norme ne spécifie pas les exigences relatives à la sécurité, telles que la protection contre les chocs électriques, l'utilisation dangereuse, la coordination de l'isolement, ni les essais relatifs au diélectrique. Cette norme ne couvre pas les exigences de compatibilité électromagnétique relatives aux émissions. Celles-ci sont couvertes par d'autres normes spécifiques. 2 A l'exception des équipements qui font partie du réseau de télécommunication public.
15 2 Références normatives This is a preview - click here to buy the full publication CEI:2010 Les documents de référence suivants sont indispensables pour l'application du présent document. Pour les références datées, seule l'édition citée s'applique. Pour les références non datées, la dernière édition du document de référence s'applique (y compris les éventuels amendements). CEI :1988, Essais d'environnement Partie 1: Généralités et guide Amendement 1 (1992) CEI :2002, Compatibilité électromagnétique (CEM) Partie 2-2: Environnement Niveaux de compatibilité pour les perturbations conduites basse fréquence et la transmission de signaux sur les réseaux publics d'alimentation basse tension CEI :2008, Compatibilité électromagnétique (CEM) Partie 4-2: Techniques d'essai et de mesure Essai d'immunité aux décharges électrostatiques CEI :2006, Compatibilité électromagnétique (CEM) Partie 4-3: Techniques d'essai et de mesure Essai d'immunité aux champs électromagnétiques rayonnés aux fréquences radioélectriques CEI :2004, Compatibilité électromagnétique (CEM) Partie 4-4: Techniques d'essai et de mesure Essais d'immunité aux transitoires électriques rapides en salves CEI :2005, Compatibilité électromagnétique (CEM) Partie 4-5: Techniques d'essai et de mesure Essai d'immunité aux ondes de choc CEI :2008, Compatibilité électromagnétique (CEM) Partie 4-6: Techniques d'essai et de mesure Immunité aux perturbations conduites, induites par les champs radioélectriques CEI :2004, Compatibilité électromagnétique (CEM) Partie 4-11: Techniques d'essai et de mesure Essais d'immunité aux creux de tension, coupures brèves et variations de tension ETSI EN (toutes les parties), Compatibilité électromagnétique et spectre radioélectrique (ERM) Norme de compatibilité électromagnétique pour les équipements et les services radio ETSI EN , Compatibilité électromagnétique et spectre radioélectrique (ERM) Compatibilité électromagnétique (CEM) générale pour les appareils de radiocommunications 3 Termes, définitions et abréviations Pour les besoins du présent document, les termes, définitions et abréviations suivants s appliquent. 3.1 Termes et définitions norme régionale sur le fonctionnement des produits norme régionale spécifiant les caractéristiques du produit NOTE Une telle norme peut contenir les exigences de compatibilité électromagnétique (CEM), mais elle n'est pas limitée à celles-ci (par exemples: la série pour les systèmes d'alarme incendie, la série pour les systèmes d'alarme contre l'intrusion).
IEC 62682 Edition 1.0 2014-10 INTERNATIONAL STANDARD NORME INTERNATIONALE Management of alarms systems for the process industries Gestion de systèmes d'alarme dans les industries de transformation INTERNATIONAL
PROJECT IEC 62321-3-2 Edition 1.0 2013-03 FINAL DRAFT INTERNATIONAL STANDARD PROJET FINAL DE NORME INTERNATIONALE Determination of certain substances in electrotechnical products Part 3-2: Screening test
IEC 62645 Edition 1.0 2014-08 INTERNATIONAL STANDARD NORME INTERNATIONALE colour inside Nuclear power plants Instrumentation and control systems Requirements for security programmes for computer-based
IEC 61375-3-3 Edition 1.0 2012-06 INTERNATIONAL STANDARD NORME INTERNATIONALE Electronic railway equipment Train communication network (TCN) Part 3-3: CANopen Consist Network (CCN) Matériel électronique
INTERNATIONAL STANDARD NORME INTERNATIONALE IEC 62279 Edition 2.0 2015-06 Railway applications Communication, signalling and processing systems Software for railway control and protection systems Applications