Source: https://www.scribd.com/document/154348428/PICS-VERIFICACI-N-DE-INSTALACIONES-pdf
Timestamp: 2019-06-18 12:54:15
Document Index: 631834647

Matched Legal Cases: ['art 4', 'art 1', 'art 2', 'art 3', 'art 4', 'art 5', 'arts 1', 'arts 4', 'art 1', 'art 2']

PICS VERIFICACI�N DE INSTALACIONES.pdf | Hvac (27 views)
Uploaded by Mario Vazquez B
saveSave PICS VERIFICACI�N DE INSTALACIONES.pdf For Later
Soft Wall Cleanromms
PI 009-3 25 September 2007
PIC/S September 2007 Reproduction prohibited for commercial purposes. Reproduction for internal use is authorised, provided that the source is acknowledged.
PIC/S Secretariat info@picscheme.org http://www.picscheme.org
PI 009-3
TABLE OF CONTENTS Page 1. 2. 3. 4. 5. 6. 1. Document History............................................................................................ 1 Introduction ..................................................................................................... 1 Purpose........................................................................................................... 1 Scope.............................................................................................................. 1 Aide Memoire .................................................................................................. 2 Revision History .............................................................................................. 9 DOCUMENT HISTORY 24 April 2002 1 July 2002
Adoption by Committee Entry into force 2. 2.1 INTRODUCTION
Technological and technical progress have increased in the pharmaceutical industry in the last decades. Progress has not only been made in the area of production equipment, technology and quality control but also in the area of auxiliary systems such as HVAC and media systems. PIC/S has paid due attention to these systems for the manufacture of medicinal products. In 2001, the annual PIC/S Seminar was devoted to the inspection of utilities used by the manufacturer of pharmaceuticals (Prague, Czech Republic). PURPOSE The purpose of this document is to provide guidance for GMP inspectors to use for training purposes and in preparation for inspections. The Aide-Memoire is the direct result of the 2001 PIC/S Seminar and was drafted with the aim of facilitating the effective planning and conduct of GMP inspections of utilities. The Aide-Memoire should enable the inspector to make both an optimal use of the inspection time and an optimal evaluation of GMP compliance. SCOPE The following Aide-Memoire describes different areas which could be evaluated during the GMP inspection of HVAC systems, pharmaceutical water, steam and medicinal gases. However, the Aide-Memoire should be considered as a nonexhaustive list of areas to be looked at during an inspection. At the time of issue, this document reflected the current state of the art. It is not intended to be a barrier to technical innovation or the pursuit of excellence. The advice in this Aide-Memoire is not mandatory for industry. However, industry should consider PIC/S recommendations and aide-memoires as appropriate.
Area of operation/Items HVAC for medicinal products Key design parameters
Notes Need for separate systems Level of filtration (Filter specifications) Recirculation or makeup air Location of filters Position of inlet and air return, dust extractors Temperature Humidity Air changes Pressure differentials Design of ducting Easy and effective cleaning Alarm system Air flow direction- LAF and/or turbulent
Crucial questions How do you prevent cross contamination by air?
Supporting documents PIC/S GMP Guide 3.10, 3.14, 5.10, 5.11, 5.18, 5.20. Annex 1- 29-31, Annex 2 -9,10,14,15, Annex 15- 9,10 ISO 14644-4: Clean rooms and associated controlled environments Part 4: Design and construction. International Organisation for Standardisation ISO, Geneva (April 2001) EN 1822: High efficiency particulate air filters (HEPA and ULPA): Part 1 Requirements, testing, marking; Part 2 Aerosol production, measuring equipment, particle counting statistics; Part 3 Testing the planar filter medium; Part 4 Testing the filter element for leaks (scan method); Part 5 Testing the efficiency of the filter element. European Committee for Standardisation, Brussels (parts 1-3 were ratified in March 1998, parts 4-5 in August 2000). EN 779: Particle air filters for general ventilation Requirements, testing, marking. European Committee for Standardisation, Brussels (July 1993). Guide - 4.26, 5.21, 5.22, 5.24, 5.37, Annex 1-30, Annex 15 2-18. EN ISO 14644-1: Clean rooms and associated controlled environments Part 1: Classification of air cleanliness. International Organisation for Standardisation ISO, Geneva and European
Qualification of HVAC 1 systems
DQ, IQ, OQ a PQ Average speed and uniformity of airflow Pressure differentials Air changes Integrity and tightness of terminal installed final filters
How have you implemented recommendations and correct deviations mentioned in qualification reports? Who is responsible for evaluating if requalification is necessary?
Important for the introductory inspection
Area of operation/Items HVAC for medicinal products
Notes Number of particles Recovery tests Air temperature Smoke tests Requalification (parameters for requalification) Change control
Crucial questions What are the requirements for regular requalification? Show me your deviations and change control reports for HVAC?
Supporting documents Committee for Standardisation CEN, Brussels (May 1999). EN ISO 14644-2: Clean rooms and associated controlled environments Part 2: Specifications for testing and monitoring to prove continued compliance with ISO 14644-1. International Organisation for Standardisation ISO, Geneva and European Committee for Standardisation (September 2000). Guide - 3.6, 3.7, 3.12, 4.27 Annex 1 -29, Annex 2-14
Walk round tour Confront differences between design specifications, drawings (in SMF) and reality, unplanned maintenance and change control and following items
Are rooms for the production of medicinal products equipped with HVAC in accordance with GMP 1 requirements ? Location of filters Position of inlets and air return Dust extractors, Pressure differences (across filters, between production and adjacent rooms) Logbooks-maintenance and calibration Monitoring of other process parameters HVAC alarm systems function
How do you challenge your alarm systems? Place and procedure for sampling? Where and how do you weigh and refill starting materials?
Environmental monitoring (particles, micro organ, humidity, temperature) Chemical residue testing
Guide 4.15, Annex 1 4-6,
Maintenance and calibration of HVAC systems
Maintenance program Calibration program SOPs Records Breakdown/Emergency including challenges of alarm systems
The interaction between unplanned maintenance and requalification
Guide 3.41
Area of operation/Items HVAC for medicinal products Documentation for HVAC systems
Notes Technical data SOP, recordsmaintenance, calibration, validation, monitoring, deviations, change control Validation protocols and reports Asbuilt engine drawing
Supporting documents Guide 4.1, 4.26, 4.28, 4.29
Area of operation/Items Pharmaceutical water system Key design parameters WFI
Crucial questions What are the design features that prevent entrainment? Who owns the system?
Supporting documents Guide 3.10 FDA- Guide to Inspection of Highly Purified Water Systems Annex 1-35 Annex 15 9,10
Weld quality Passivation of pipeworks Vent filters All kinds of pharmaceutical water Suitability of construction materials Slope of pipeworks Recirculation at adequate velocity and temperature Sanitary joints Capacity x daily demand Valves Draining /flushing Samplings ports 2.2 Qualification DQ, IQ, OQ, PQ AND COMPUTER VALIDATION IF NEEDED Drawing, with all sampling points Setting operation and cleaning parameters-I. Stage CONSISTENTLY PRODUCING WATER OF DESIRED QUALITY
All qualification completed? For existing systems, show me deviation and change control reports? Does staff understand what, how and why the work is performed? What do signatures mean?
3.3.4, 3.38, 5.22, 5.24 Annex 15 2-18.
Area of operation/Items Pharmaceutical water system Walk round inspection Is water for injection produced and used according to requirements of Note for Guidance on Quality of Water for Pharmaceutical Purposes and Ph Eur? Confront differences between drawings and reality, unplanned maintenance and change control. Follow the system from pre-treatment to user points: in each part, check leaks, sampling points (access), who does what, start up and shutdown, cleaning / disinfection / sterilisation), quantities produced.
Notes Water quality grade and purposes of its use feed water pre- treatment distillation sight glass storage tank-filter, break valve, Q-spray ball distribution loop-temp, conductivity, TOC heat exchangerintegrity user points-number, design and location control system-alarms, record of action, set points and demonstration monitoring print outs DISINFECTION? HOT WATER? STEAM? CONTINUOUS RECIRCULATION?
Crucial questions How is the system kept in a validated state? Let me have a look in the sight glass! Show me records of alarms that have occurred!
Supporting documents Ph. Eur. current edition CPMP - Note for Guidance on Quality of Water for Pharmaceutical Purposes Annex 1 35
PROGRAMME, INCLUDING TEST METHODS SCHEDULE? SAMPLING, WHO TAKES SAMPLES, TRAINING, VOLUME SAMPLED, HANDLING OF SAMPLES Limits (micro, chemical, endotoxin) Out of spec. results (OOS) Trending of results Check that all points are sampled over time, accessibility to sampling points
How do you perform sampling (handling, volume, done by, all points covered)? What are alert, action limits? Source water testing?
Ph. Eur. current edition CPMP Note for Guidance on Quality of Water for Pharmaceutical Purposes Guide 3.43, 4.15, 4.22, 6.7
Temperature Speed Vent filters DI column regeneration pH UV light (PW) Conductivity Leakage TOC
By whom and how are corrective actions made?
Guide 4.15 Annex 1 44
Area of operation/Items Pharmaceutical water system Maintenance and calibration of water systems
Notes Maintenance program Calibration programme SOPs Records Breakdown/Emergency including challenges of alarm systems
Crucial questions The interaction between unplanned maintenance and requalification
Supporting documents Guide 3.41
Drawing up to date (SMF?) OOS evaluation Deviation reports Change control reports Operation of the system Cleaning / sanitation / sterilisation Logbook monitoring parameters- see 1.6, incidents, filter changes, shut down periods, cleaning/sanitation, maintenance
Guide 5.38 Guide 4.1, 4.26, 4.28, 4.29
Area of operation/Items Pharmaceutical steam systems Key design parameters
Notes entrainment prevention cross contaminationfactory/ clean steam non condensable gases reduction slope of pipeworks no dead legs
Supporting documents Guide 3.10 Annex 15 9-10
DQ, IQ, OQ, PQ AND COMPUTER VALIDATION IF NEEDED THE SCOPE OF VALIDATION
All qualification completed? For existing systems, show me deviation and change control reports
3.3.4, 3.38, 5.22, 5.24 Annex 15- 2-18
Walk round tour What kind of steam is used for manufacture of pharmaceutical products factory, clean steam generator)? What kind of source water is used for production of steam? Confront differences
FEED WATER-TYPE, LEVEL, TEMPERATURE Sample pointslocation, number, access System for removal of air loop
Area of operation/Items Pharmaceutical steam systems between drawings and reality, unplanned maintenance and change control. Follow the system in logical order. Pay attention to leaks, sampling points (access), who does what, start up and shutdown, cleaning / disinfection / sterilisation), quantities produced.
control of entrainment level control of feed water pressure control inside still temperature filters blown down frequency emergency shutdown and start up
methods (contains non condensable gases and additives) limits sampling OOS results Trending results
Guide 3.43, 4.15, 4.22, 6.7 Annex 1- 68
Maintenance and calibration of the system
Maintenance program Calibration programme SOPs Records Breakdown/Emergency including challenges of alarm systems
Drawing up to date (SMF?) OOS evaluation Deviation reports Change control reports Operation of the system Cleaning / sanitation / sterilisation Logbook - monitoring parameters - see 1.6, incidents, filter changes, shut down periods, cleaning / sanitation, maintenance
Area of operation/Items Pharmaceutical gases Key design criteria (compressed air)
Notes air inlet-source, contamination risks filters (pre final) suitability of materials welding prevention of contamination (receiver vessel) valves
Supporting documents Guide 3.10. Annex 15- 9-10
(DQ, IQ, OQ? PQ) solid contaminants, water, oil limits capacity, filter pressure drops, alarm operation
how do you assure that filters are replaced in time?
Guide 3.34, 3.38 ISO 8573 Compressed air 1-7 Annex 15- 2-18
Walk round inspection Identify all used gases with the risk for medicinal products. Confront differences between drawings and reality, unplanned maintenance and change control Follow the system in logical order
contact with the product or with the process equipment type of the product non sterile (terminally sterilised, aseptic procedures) labelling and identification of the system Connections-risk of mix up Identify all other used gases
Changing system for filters SIP system Back-up systems Capacity-consumption
Leakage tests Filter integrity tests Pressure control
Quality control Maintenance and calibration of the system
Pollution - oil, water, particles, bio burden Maintenance program Calibration programme SOPs Records Breakdown/Emergency including challenges of alarm systems The interaction between unplanned maintenance and requalification
Guide 3.43, 4.15, 4.22, 6.7 Guide 3.41
Area of operation/Items Pharmaceutical gases Documentation
Notes Line drawings (pipeline, flow, valves, filters, rooms) Deviation and corrective actions Cleaning / sanitation / sterilisation Logbook monitoring parameters see 1.6, incidents, filter changes, shut down periods, cleaning / sanitation, maintenance
REVISION HISTORY Date Version Number PI 009-2 PI 009-3 Reasons for revision Change in the Editors co-ordinates Change in the Editors co-ordinates
1 July 2004 25 September 2007
Documents Similar To PICS VERIFICACI�N DE INSTALACIONES.pdf
Cad Outsourcing Offer HVAC Enginering Services.doc
More From Mario Vazquez B