Source: http://www.ada.gov/humbolt_pca/humboldtattl.htm
Timestamp: 2015-04-27 04:08:11
Document Index: 770679909

Matched Legal Cases: ['§ 35', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 8', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4']

Attachment L to Settlement Agreement between the United States of America and Humboldt County, CA in DJ# 204-11-275
Attachment L: Access to Humboldt County Programs Housed in Others' Facilities
Please Note: Paragraph 50 of the Settlement Agreement requires that, within three months of the effective date of this Agreement, the County provide signage as necessary to comply with 28 C.F.R. § 35.163(b), after having surveyed all facilities that are the subject of this Agreement for the purpose of identifying those that have multiple entrances not all of which are accessible.
Within six months of the effective date of this Agreement, the County will implement and report to the Department its written plan regarding how the program, activity, or service at issue, when viewed in its entirety, will be made accessible to persons with disabilities.
Employment Development Department - Employment Training Center (State owned)
The wall-mounted drinking fountain is inaccessible because there is 26¾ inches of knee clearance between the bottom of the apron and the finished floor. Provide a drinking fountain with clear knee space between the bottom of the apron and the finished floor or ground of at least 27 inches high, 30 inches wide; and a minimum clear floor space of 30 inches by 48 inches to allow a person in a wheelchair to approach the unit facing forward. Standards § 4.15.5(1), Figs. 27(a), (b).
(1)The door, which is accessed from the hinge side of the door, is inaccessible because there is insufficient clear floor space on the latch side, push side of the door. On the push side of the door, provide a clear maneuvering space at least 54 inches wide, measured from the latch side, and at least 42 inches deep. Standards § 4.13.6, Fig. 25(b).
(2)The hand dryer protrudes into the walkway and would not be detectable to a blind person using a cane. Provide a circulation path at this location such that no objects with their bottom leading edges measuring between 27 inches and 80 inches above the finished floor protrude more than 4 inches into walks, halls, corridors, passageways, or aisles. Free-standing objects mounted on posts or pylons may overhang 12 inches maximum from 27 inches to 80 inches above the ground or finished floor. Providing a cane-detectable barrier is an acceptable solution. Standards § 4.4.
(3)The shelf under the mirror protrudes into the walkway and would not be detectable to a blind person using a cane. Provide a circulation path at this location such that no objects with their bottom leading edges measuring between 27 inches and 80 inches above the finished floor protrude more than 4 inches into walks, halls, corridors, passageways, or aisles. Free-standing objects mounted on posts or pylons may overhang 12 inches maximum from 27 inches to 80 inches above the ground or finished floor. Providing a cane-detectable barrier is an acceptable solution. Standards § 4.4.
(4)The toilet is inaccessible because its centerline measures 19.5 inches from the side wall. Provide a toilet with a centerline that measures 18 inches from the near side wall. Standards § 4.17.3, Fig. 30.
(5)No accessible coat hook has been provided. Provide a coat hook at a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.25.2, 4.25.3, 4.2.4, 4.2.5, 4.2.6.
(1)The rear grab bar at the toilet is inaccessible because the closer end it is mounted 7 inches from the side wall. Provide a rear grab bar that is at least 36 inches in overall length, with the closer end no more than 6 inches from the side wall; mounted 33 to 36 inches above the finished floor; with a diameter between 1¼ and 1½ inches; with 1½ inches between the grab bar and the wall; and at least 1½ inches between the grab bar and any other object, such as a toilet seat cover dispenser. Standards §§ 4.17.6, 4.26.2, Fig. 30.
Public Health MCAH (Altered)
Parking (owned by City)
There are no designated van accessible spaces provided. On the shortest accessible route to the accessible entrance, provide one van accessible space designated as reserved for people with disabilities. Ensure that van accessible spaces are a minimum of 96 inches wide and served by access aisles at least 96 inches wide. At all spaces designated as reserved for persons with disabilities, provide vertical signs with the International Symbol of Accessibility located such that they cannot be obstructed by parked vehicles. At van accessible spaces, provide an additional "Van-Accessible" sign located below the International Symbol of Accessibility. Ensure that all spaces and access aisles for persons with disabilities are flat and level, with slopes and cross-slopes not exceeding 1:50 in all directions, and that their surfaces are firm, stable, and slip-resistant. Standards §§ 4.1.2(5), 4.6, 4.30.7(1). Offices
The meeting room and office doors are inaccessible because knob hardware is used. Provide doors with hardware that is easy to grasp with one hand and that does not require tight grasping, pinching, or twisting of the wrist to operate. Lever-operated mechanisms, push-type mechanisms, and U-shaped handles are acceptable designs. Standards § 4.13.9.
Unisex Single User
The toilet room sign is not mounted on the latch side of the door. Provide a toilet room sign with raised and Braille characters mounted on the wall adjacent to the latch side of the door with the centerline of the sign 60 inches above the finished floor and situated such that a person can approach within 3 inches of the sign without encountering an obstruction or standing within a door swing. Standards §§ 4.1.2(7)(d), 4.30.1, 4.30.4, 4.30.5, 4.30.6.
The door to the toilet room, which is accessed through a front approach, is inaccessible because it has only 11 inches of clear floor space on the latch side, pull side of the door. On the pull side of the door, provide maneuvering clearance at least 60 inches deep and provide a minimum of 18 inches (24 inches is preferred) of maneuvering clearance on the latch side of the door. Standards § 4.13.6, Fig. 25(a).
No accessible mirror has been provided. Provide a mirror with the bottom edge of its reflecting surface no more than 40 inches above the finished floor. Standards § 4.19.6.
The toilet seat cover dispenser is inaccessible because the controls are mounted at 47 inches above the finished floor over an obstruction. Provide a (*identify amenity) such that the controls comply with Fig. 5 for a forward reach or with Fig. 6 for a side reach and such that it is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach, respectively, by a person using a wheelchair. Standards §§ 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
The toilet is inaccessible because there is insufficient clear floor space. Provide clear floor space at the toilet that complies with Fig. 28. Standards § 4.16.2, Fig. 28.
Social Services Branch (Altered)
Although the parking lot has a total of 22 parking spaces, an inadequate number are van accessible. On the shortest accessible route to the accessible entrance, provide one van accessible space a minimum of 96 inches wide, served by access aisles at least 96 inches wide, with vertical signs with the International Symbol of Accessibility located such that they cannot be obstructed by parked vehicles, and with an additional "Van-Accessible" sign located below the International Symbol of Accessibility. Standards §§ 4.1.2(5)(b), 4.6, 4.30.7(1).
The parking reserved for persons with disabilities is inaccessible because the shared access aisle is 52 inches wide. Provide designated accessible parking spaces that are a minimum of 96 inches wide and served by access aisles at least 60 inches wide. Provide van accessible spaces that are a minimum of 96 inches wide and served by access aisles at least 96 inches wide. Standards §§ 4.1.2(5), 4.6.3, Fig.9. Offices
The door to Meeting Room #34 is inaccessible because knob hardware is used. Provide a door with hardware that is easy to grasp with one hand and that does not require tight grasping, pinching, or twisting of the wrist to operate. Lever-operated mechanisms, push-type mechanisms, and U-shaped handles are acceptable designs. Standards § 4.13.9.
The door to Psych Counseling #14 is inaccessible because knob hardware is used. Provide a door with hardware that is easy to grasp with one hand and that does not require tight grasping, pinching, or twisting of the wrist to operate. Lever-operated mechanisms, push-type mechanisms, and U-shaped handles are acceptable designs. Standards § 4.13.9. Toilet Rooms
(1)The toilet room sign is mounted on the door. Provide a toilet room sign with raised and Braille characters mounted on the wall adjacent to the latch side of the door with the centerline of the sign 60 inches above the finished floor and situated such that a person can approach within 3 inches of the sign without encountering an obstruction or standing within a door swing. Standards §§ 4.1.2(7)(d), 4.30.1, 4.30.4, 4.30.5, 4.30.6.
(2)The entry door is inaccessible because the pressure required to open the door is 10 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards § 4.13.11(2)(b).
(3)The entry door, which is accessed through a front approach, is inaccessible because the trash can is obstructing the clear floor space at the latch side, pull side of the door. On the pull side of the door, provide maneuvering clearance at least 60 inches deep and provide a minimum of 18 inches (24 inches is preferred) of maneuvering clearance on the latch side of the door. Standards § 4.13.6, Fig. 25(a).
(4)The toilet room door swings into the required clear floor space at the paper towel dispenser and the sanitary napkin dispenser. Ensure that no door swings into the required clear floor space at any accessible fixture. Standards § 4.22.2.
(5)There is insufficient turning space within the toilet room. Provide an unobstructed turning space at least 60 inches in diameter or a T-shaped space complying with Fig. 3(b). Standards §§ 4.22.3, 4.2.3, Fig. 3.
(6)The stall door is inaccessible because it has an opening width of only 27 inches. Provide a door with a clear opening of 32 inches with the door open 90 degrees, measured between the face of the door and the opposite stop. Standards § 4.13.5, Fig. 24.
(7)The toilet is inaccessible because the toilet and the stall door are not adjacent to each other. Provide clear floor space that complies with Fig. 30 at the toilet. Standards § 4.17.3, Fig. 30.
(8)The toilet is inaccessible because its centerline measures 17 inches from the side wall. Provide a toilet with a centerline that measures 18 inches from the near side wall. Standards § 4.17.3, Fig. 30. (9)The toilet paper dispenser is inaccessible because is mounted 45 inches from the rear wall. Provide a toilet paper dispenser that is mounted with its top at least 1½ inches under the side grab bar and 36 inches or less from the rear wall and is centered at least 19 inches above the finished floor. Standards § 4.17.3, Fig. 30(d). (10)	The side grab bar at the toilet is inaccessible because the closer end is mounted 13 inches from the rear wall and the bar is mounted 32 inches high. Provide a side grab bar that is at least 40 inches in overall length, with the far end mounted at least 52 inches from the rear wall and the closer end 12 inches or less from the rear wall; mounted 33 to 36 inches above the finished floor; with a diameter between 1¼ and 1½ inches; with 1½ inches between the grab bar and the wall; and at least 1½ inches between the grab bar and any other object, such as the toilet paper dispenser. Standards §§ 4.17.6, 4.26.2, Figs. 30(a), (d).
(11)	The rear grab bar at the toilet is inaccessible because the closer end is mounted 10 inches from the side wall. Provide a rear grab bar that is at least 36 inches in overall length, with the closer end no more than 6 inches from the side wall; mounted 33 to 36 inches above the finished floor; with a diameter between 1¼ and 1½ inches; with 1½ inches between the grab bar and the wall; and at least 1½ inches between the grab bar and any other object, such as a toilet seat cover dispenser. Standards §§ 4.17.6, 4.26.2, Fig. 30.
(2)The entry door is inaccessible because the pressure required to open the door is 15 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards § 4.13.11(2)(b).
(3)The entry door, which is accessed through a front approach, is inaccessible because the trash can is obstructing the clear floor space on the latch side, pull side of the door. On the pull side of the door, provide maneuvering clearance at least 60 inches deep and provide a minimum of 18 inches (24 inches is preferred) of maneuvering clearance on the latch side of the door. Standards § 4.13.6, Fig. 25(a).
(4)The lavatory is inaccessible because the apron is mounted 28 inches above the finished floor. Provide a lavatory with the top of its rim or counter 34 inches or less above the finished floor; the bottom edge of the apron at least 29 inches above the finished floor; and knee and toe clearances that comply with Fig. 31. Standards § 4.19.2, Fig. 31.
(5)The urinal is inaccessible because the elongated rim is mounted higher than 17 inches above the finished floor and the flush control is 54 inches above the finished floor. Provide a urinal with an elongated rim mounted 17 inches or less above the finished floor, a clear floor space of at least 30 inches wide and 48 inches deep centered on the urinal, and a flush control height of 44 inches or less above the finished floor. Standards §§ 4.18.2, 4.18.3, 4.18.4. (6)The toilet is inaccessible because the toilet and the stall door are not adjacent to each other. Provide clear floor space that complies with Fig. 30 at the toilet. Standards § 4.17.3, Fig. 30.
(7)No accessible coat hook has been provided. Provide a coat hook at a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.25.2, 4.25.3, 4.2.4, 4.2.5, 4.2.6.
(8)The toilet paper dispenser is inaccessible because it is mounted above the grab bar. Provide a toilet paper dispenser that is mounted with its top at least 1½ inches under the side grab bar and 36 inches or less from the rear wall and is centered at least 19 inches above the finished floor. Standards § 4.17.3, Fig. 30(d).
(9)The side grab bar at the toilet is inaccessible because the closer end is mounted 13 inches from the rear wall. Provide a side grab bar that is at least 40 inches in overall length, with the far end mounted at least 52 inches from the rear wall and the closer end 12 inches or less from the rear wall; mounted 33 to 36 inches above the finished floor; with a diameter between 1¼ and 1½ inches; with 1½ inches between the grab bar and the wall; and at least 1½ inches between the grab bar and any other object, such as the toilet paper dispenser. Standards §§ 4.17.6, 4.26.2, Figs. 30(a), (d).
(10)	The rear grab bar at the toilet is inaccessible because the closer end is mounted at 9.5 inches from the side wall. Provide a rear grab bar that is at least 36 inches in overall length, with the closer end no more than 6 inches from the side wall; mounted 33 to 36 inches above the finished floor; with a diameter between 1¼ and 1½ inches; with 1½ inches between the grab bar and the wall; and at least 1½ inches between the grab bar and any other object, such as a toilet seat cover dispenser. Standards §§ 4.17.6, 4.26.2, Fig. 30. Newspaper Building (Employment Training Dept.)
The ramp is inaccessible because there is no level landing at the bottom of the ramp, the top of the handrail is 32 inches high, and there are no 12 inch extensions at the top or bottom of the ramp that are parallel to the ground. Provide a ramp that is at least 36 inches wide with a slope not exceeding 1:12 and a cross slope not exceeding 1:50; with level landings at least as wide as the ramp and 60 inches long at the top and bottom of the ramp; and with edge protection at least 2 inches high at the drop off sides. Provide handrails that are between 1¼ inches and 1½ inches in diameter with a continuous gripping surface along both sides of the ramp, extending at least 12 inches beyond the top and bottom of the ramp parallel with the ground surface. Ensure that handrails are mounted between 34 inches and 38 inches above the ramp surface and 1½ inches from the wall, with ends rounded or returned smoothly to the floor, wall, or post, and that they do not rotate within their fittings. Ensure that the ramp and approaches are designed so that water will not accumulate on walking surfaces. Standards §§ 4.3.8, 4.8.
The elevator is inaccessible because there is no hoist way signage. Provide signage at hoist way entrances with raised and Braille floor designations on both jambs such that the centerline of the characters is 60 inches above the finished floor and the characters are 2 inches high. Standards § 4.10.5, Fig. 20.
The elevator is inaccessible because the door re-opening device keeps the door open for less than 5 seconds. Provide doors that open and close automatically with a reopening device that will stop and reopen the car door and hoist way door automatically if the door becomes obstructed by an object or person. Ensure that the device is capable of completing these operations without requiring contact for obstructions passing through the opening at heights of 5 inches and 29 inches above the finished floor; that door reopening devices remain effective for at least 20 seconds, after which the doors may close; that the minimum time from notification that a car is answering a call until the doors of that car start to close is 5 seconds; and that the minimum time for elevator doors to remain fully open in response to a car call is 3 seconds. Standards §§ 4.10.6, 4.10.7, 4.10.8, Figs. 20, 21.
There is no accessible drinking fountain because the spout is 42 inches above the finished floor, the water height less than 4 inches, the water flow is not withing 3 inches of the front of the fountain, the controls are not front or side mounted, the controls require 10 pounds of force to operate and there is no second higher fountain for people who have trouble bending or stooping . Provide at least one (*or number equal to 50% of fountains) drinking fountain with a spout height no higher than 36 inches, measured from the finished floor or ground surface to the spout outlet; and a spout located at the front of the unit that directs the water flow in a trajectory that is nearly parallel to the front of the unit and is positioned so the flow of water is within 3 inches of the front edge of the fountain and at least 4 inches high. Ensure that fountain controls are operable with one hand, require 5 lbf or less to operate without tight grasping, pinching, or twisting of the wrist; and are front mounted or side mounted near the front edge. Additionally, provide a drinking fountain that is accessible to people who have difficulty bending or stooping. This can be accommodated by the use of a "hi-lo" fountain; by providing one fountain accessible to those who use wheelchairs and one fountain at a standard height convenient for those who have difficulty bending; by providing a fountain accessible to people who use wheelchairs and a cup dispenser; or by such other means as would achieve the required accessibility for each group of people. Standards §§ 4.15, 4.27.4, Fig. 27.
The front office door is inaccessible because knob hardware is used. Provide a door with hardware that is easy to grasp with one hand and that does not require tight grasping, pinching, or twisting of the wrist to operate. Lever-operated mechanisms, push-type mechanisms, and U-shaped handles are acceptable designs. Standards § 4.13.9.
The training room door is inaccessible because knob hardware is used. Provide a door with hardware that is easy to grasp with one hand and that does not require tight grasping, pinching, or twisting of the wrist to operate. Lever-operated mechanisms, push-type mechanisms, and U-shaped handles are acceptable designs. Standards § 4.13.9.
The computers in the training room are inaccessible because they are on desks that are not wheelchair accessible. Provide a computer on a table or counter that has clear floor space that is 30 inches wide and 48 inches deep, knee clearance at least 27 inches high, 30 inches wide, and 19 inches deep, and a writing surface between 28 and 34 inches above the finished floor. Standards §§ 4.2.4.1, 4.32.
Women's in Main Hallway
(1)There is no accessible toilet room sign. Provide a toilet room sign with raised and Braille characters mounted on the wall adjacent to the latch side of the door with the centerline of the sign 60 inches above the finished floor and situated such that a person can approach within 3 inches of the sign without encountering an obstruction or standing within a door swing. Standards §§ 4.1.2(7)(d), 4.30.1, 4.30.4, 4.30.5, 4.30.6.
(2)The entry door is inaccessible because the pressure required to open the door is 16 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards § 4.13.11(2)(b).
(3)There is no adequate clearance on the latch side pull side of the door. On the pull side of the door, provide maneuvering clearance at least 60 inches deep and provide a minimum of 18 inches (24 inches is preferred) of maneuvering clearance on the latch side of the door. Standards § 4.13.6, Fig. 25(a).
(4)No accessible mirror has been provided. Provide a mirror with the bottom edge of its reflecting surface no more than 40 inches above the finished floor. Standards § 4.19.6.
(5)The lavatory is inaccessible because the apron is mounted 27 inches above the finished floor, there is no adequate knee toe clearance, the hot water pipes are not covered or configured to protect against contact, and the faucet hardware requires tight grasping, pinching, or twisting of the wrist. Provide a lavatory with the top of its rim or counter 34 inches or less above the finished floor; the bottom edge of the apron at least 29 inches above the finished floor; knee and toe clearances that comply with Fig. 31; hot water and drain pipes covered or otherwise configured to protect against contact; clear floor space at least 30 inches wide and 48 inches deep centered on the lavatory; and a faucet that can be operated with 5 pounds of force or less and can be used with one hand and without tight grasping, pinching, or twisting of the wrist (lever-operated, push-type, and electronically controlled mechanisms are examples of acceptable designs). Standards §§ 4.19.2, 4.19.3, 4.19.4, 4.19.5, 4.27.4, Figs. 31, 32.
(6)The toilet is inaccessible because there is insufficient clear floor space. Provide clear floor space that complies with Fig. 30 at the toilet. Standards § 4.17.3, Fig. 30.
(7)The toilet is inaccessible because the top of the seat is 15.5 inches above the finished floor. Provide a toilet with a seat that measures 17 to 19 inches above the finished floor. Standards §§ 4.16.3, 4.17.2, Fig. 30(d).
(8)The side grab bar at the toilet is inaccessible because the further end of the grab bar is 48¾ inches from the rear wall. Provide a side grab bar that is at least 40 inches in overall length, with the far end mounted at least 52 inches from the rear wall and the closer end 12 inches or less from the rear wall; mounted 33 to 36 inches above the finished floor; with a diameter between 1¼ and 1½ inches; with 1½ inches between the grab bar and the wall; and at least 1½ inches between the grab bar and any other object, such as the toilet paper dispenser. Standards §§ 4.17.6, 4.26.2, Figs. 30(a), (d).
(9)The rear grab bar at the toilet is inaccessible because grab bar is 30 inches long and closer end is mounted 11 inches from the side wall. Provide a rear grab bar that is at least 36 inches in overall length, with the closer end no more than 6 inches from the side wall; mounted 33 to 36 inches above the finished floor; with a diameter between 1¼ and 1½ inches; with 1½ inches between the grab bar and the wall; and at least 1½ inches between the grab bar and any other object, such as a toilet seat cover dispenser. Standards §§ 4.17.6, 4.26.2, Fig. 30.
Men's in Main Hallway
(1)There is no accessible toilet room sign. Provide a toilet room sign with raised and Braille characters mounted on the wall adjacent to the latch side of the door with the centerline of the sign 60 inches above the finished floor and situated such that a person can approach within 3 inches of the sign without encountering an obstruction or standing within a door swing. Standards §§ 4.1.2(7)(d), 4.30.1, 4.30.4, 4.30.5, 4.30.6
(3)No accessible mirror has been provided. Provide a mirror with the bottom edge of its reflecting surface no more than 40 inches above the finished floor. Standards § 4.19.6.
(4)The urinal is inaccessible. Provide a urinal with an elongated rim mounted 17 inches or less above the finished floor, a clear floor space of at least 30 inches wide and 48 inches deep centered on the urinal, and a flush control height of 44 inches or less above the finished floor. Standards §§ 4.18.2, 4.18.3, 4.18.4.
(5)The toilet is inaccessible because there is insufficient clear floor space. Provide clear floor space that complies with Fig. 30 at the toilet. Standards § 4.17.3, Fig. 30.
Men's in Newsroom
(2)The entry door, which is accessed through a front approach, is inaccessible because there is no space on the pull and push side of the door. On the pull side of the door, provide maneuvering clearance at least 60 inches deep and provide a minimum of 18 inches (24 inches is preferred) of maneuvering clearance on the latch side of the door. On the push side of the door, provide maneuvering clearance at least 48 inches deep and provide a minimum of 12 inches of maneuvering clearance on the latch side of the door, or remove the closer or the latch. Standards § 4.13.6, Fig. 25(a). (3)No accessible mirror has been provided. Provide a mirror with the bottom edge of its reflecting surface no more than 40 inches above the finished floor. Standards § 4.19.6.
(4)The paper towel dispenser is inaccessible because the controls are mounted at 55½ inches above the finished floor. Provide a paper towel dispenser with the controls a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
(5)The lavatory is inaccessible because the bottom of the apron is mounted 24 inches above the finished floor, the hot water drain and pipes are not covered or configured to protect against contact and the faucet hardware requires tight grasping, pinching, or twisting fo the wrist. Provide a lavatory with the top of its rim or counter 34 inches or less above the finished floor; the bottom edge of the apron at least 29 inches above the finished floor; knee and toe clearances that comply with Fig. 31; hot water and drain pipes covered or otherwise configured to protect against contact; clear floor space at least 30 inches wide and 48 inches deep centered on the lavatory; and a faucet that can be operated with 5 pounds of force or less and can be used with one hand and without tight grasping, pinching, or twisting of the wrist (lever-operated, push-type, and electronically controlled mechanisms are examples of acceptable designs). Standards §§ 4.19.2, 4.19.3, 4.19.4, 4.19.5, 4.27.4, Figs. 31, 32.
(6)The urinal is inaccessible because the elongated rim is 24.5 inches above the finished floor and the flush controls are 52 inches above the finished floor. Provide a urinal with an elongated rim mounted 17 inches or less above the finished floor, a clear floor space of at least 30 inches wide and 48 inches deep centered on the urinal, and a flush control height of 44 inches or less above the finished floor. Standards §§ 4.18.2, 4.18.3, 4.18.4.
(7)There is no accessible stall provided. Provide a "standard" accessible toilet stall at least 60 inches wide and at least 59 inches deep (or at least 56 inches deep with a wall-mounted toilet) such that all of the stall's elements, including stall door, stall door hardware, water closet, size and arrangement, toe clearances, grab bars, controls, and dispensers, comply with the Standards. Standards §§ 4.13, 4.16, 4.17, 4.26, 4.27, Fig. 30.
Within 12 months of the effective date of this Agreement, the County will complete the following modifications to Child Support Services, located at 2420 Sixth Street.
There is no designated van accessible parking space. On the shortest accessible route to the accessible entrance, provide at least 1 van accessible space a minimum of 96 inches wide, served by an access aisle at least 96 inches wide, with a vertical sign with the International Symbol of Accessibility located such that it cannot be obstructed by parked vehicles, and with an additional "Van-Accessible" sign located below the International Symbol of Accessibility. Standards §§ 4.1.2(5)(b), 4.6, 4.30.7(1).
The signage designating parking reserved for persons with disabilities is not mounted at each accessible space, and the existing sign is mounted so that it can not be seen above a car parked in the space. At all spaces designated as reserved for persons with disabilities, provide vertical signs with the International Symbol of Accessibility located such that they cannot be obstructed by parked vehicles. Standards §§ 4.1.2(5), 4.6.4, 4.30.7(1).
The reception counter protrudes into the walkway and would not be detectable to a blind person using a cane. Provide a circulation path at this location such that no objects with their bottom leading edges measuring between 27 inches and 80 inches above the finished floor protrude more than 4 inches into walks, halls, corridors, passageways, or aisles. Free-standing objects mounted on posts or pylons may overhang 12 inches maximum from 27 inches to 80 inches above the ground or finished floor. Providing a cane-detectable barrier is an acceptable solution. Standards §§ 4.1.2(3), 4.4.
Secured meeting room - The door is inaccessible because the pressure required to open the door is 10 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards §§ 4.1.3(7)(b), 4.13.11(2)(b).
Non-secured meeting room - The door is inaccessible because the pressure required to open the door is 10 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards §§ 4.1.3(7)(b), 4.13.11(2)(b).
The drinking fountain has a spout that is 37 inches above the finished floor. Provide a fountain that has a spout height no higher than 36 inches, measured from the finished floor or ground surface to the spout outlet, and that otherwise complies with the Standards. Standards §§ 4.1.3(10), 4.15, 4.27.4, Fig. 27.
Within 12 months, unless otherwise noted, of the effective date of this Agreement, the County will complete the following modifications to the McKinleyville Sheriff's Substation, located at 1608 Pickett Street in McKinleyville.
The signage designating parking as reserved for persons with disabilities is too low. At each space designated as reserved for persons with disabilities, provide a vertical sign with the International Symbol of Accessibility located such that it cannot be obstructed by vehicles parked in the space. Standards §§ 4.1.2(5), 4.6.4, 4.30.7(1).
The van accessible parking reserved for persons with disabilities lacks the appropriate signage. At van accessible spaces, provide a "Van-Accessible" sign located below the International Symbol of Accessibility such that the sign cannot be obstructed by vehicles parked in the space. Standards §§ 4.1.2(5), 4.6.4, 4.30.7(1).
The built-up curb ramp impermissibly extends into the required parking space's access aisle. Within 24 months of the effective date of this Agreement, the County shall provide a curb ramp located so that it does not project into this element and all aspects of the ramp or curb cut comply with the Standards. Standards §§ 4.1.2(1), 4.1.2(2), 4.3.8, 4.7.6.
Counter - The counter is inaccessible because it is 43 inches high. Provide a counter on an accessible route such that a portion of the counter is at least 36 inches wide and no more than 36 inches above the finished floor, or provide an auxiliary counter with a maximum height of 36 inches in close proximity to the main counter, or provide equivalent facilitation. Equivalent facilitation may be provided in the form of a folding shelf attached to the main counter, an auxiliary table nearby, a clip board made available to the public, or other means. Standards §§ 4.1.1(2), 7.2(2), 4.1.3(1), 4.3.
Within 12 months of the effective date of this Agreement, the County will complete the following modifications to the McKinleyville Library located at 1606 Pickett Road.
(1)The toilet room sign is mounted on the door more than 60 inches above the finished floor. Provide a toilet room sign with raised and Braille characters mounted on the wall adjacent to the latch side of the door with the centerline of the sign 60 inches above the finished floor and situated such that a person can approach within 3 inches of the sign without encountering an obstruction or standing within a door swing. Standards §§ 4.1.2(7)(d), 4.30.1, 4.30.4, 4.30.5, 4.30.6.
(2)The door is inaccessible because the pressure required to open the door is 11 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards §§ 4.1.3(7)(b), 4.13.11(2)(b).
(3)The toilet is inaccessible because its centerline measures 19 inches from the side wall. Provide a toilet with a centerline that measures 18 inches from the near side wall. Standards §§ 4.1.3(11), 4.22.4, 4.17.3, Fig. 30.
(4)No accessible coat hook has been provided. Provide a coat hook at a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.1.3(12)(a), 4.25.2, 4.25.3, 4.2.4, 4.2.5, 4.2.6.
(5)The toilet paper dispenser is inaccessible because it is mounted 42 inches from the rear wall. Provide a toilet paper dispenser that is mounted with its top at least 1½ inches under the side grab bar and 36 inches or less from the rear wall and is centered at least 19 inches above the finished floor. Standards §§ 4.1.3(11), 4.22.4, 4.17.3, Fig. 30(d).
(2)The toilet is inaccessible because its centerline measures 20 inches from the side wall. Provide a toilet with a centerline that measures 18 inches from the near side wall. Standards §§ 4.1.3(11), 4.22.4, 4.17.3, Fig. 30.
(3)No accessible coat hook has been provided. Provide a coat hook at a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.1.3(12)(a), 4.25.2, 4.25.3, 4.2.4, 4.2.5, 4.2.6.
(4)The toilet paper dispenser is inaccessible because it is mounted 41 inches from the rear wall. Provide a toilet paper dispenser that is mounted with its top at least 1½ inches under the side grab bar and 36 inches or less from the rear wall and is centered at least 19 inches above the finished floor. Standards §§ 4.1.3(11), 4.22.4, 4.17.3, Fig. 30(d).
Within 12 months of the effective date of this Agreement, the County will complete the following modifications to Redwood Regional Development, 520 E. Street in Eureka.
The toilet room sign is not mounted on the latch side of the door. Provide a toilet room sign with the International Symbol of Accessibility and raised and Braille characters mounted on the wall adjacent to the latch side of the door with the centerline of the sign 60 inches above the finished floor and situated such that a person can approach within 3 inches of the sign without encountering an obstruction or standing within a door swing. Standards §§ 4.1.2(7)(d), 4.1.6(1)(b), 4.30.1, 4.30.4, 4.30.5, 4.30.6, 4.30.7.
The door is inaccessible because the pressure required to open the door is 7 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards §§ 4.1.3(7)(b), 4.1.6(1)(b), 4.13.11(2)(b).
No accessible mirror has been provided. Provide a mirror with the bottom edge of its reflecting surface no more than 40 inches above the finished floor. Standards §§ 4.1.3(11), 4.1.6(1)(b), 4.22.6, 4.19.6.
The toilet is inaccessible because the flush control is on the closed side. Provide a flush control mounted on the "open" side of the toilet's clear floor space; 44 inches or less above the finished floor; and requiring a maximum of 5 pounds of force to operate; or provide an automatic flush device. Standards §§ 4.1.3(11), 4.1.6(1)(b), 4.22.4, 4.16.5, 4.17.2, 4.27.4.
No accessible coat hook has been provided. Provide a coat hook at a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.1.3(12)(a), 4.1.6(1)(b), 4.25.2, 4.25.3, 4.2.4, 4.2.5, 4.2.6.
The toilet paper dispenser is inaccessible because it is mounted 43 inches from the rear wall. Provide a toilet paper dispenser that is mounted with its top at least 1½ inches under the side grab bar and 36 inches or less from the rear wall and is centered at least 19 inches above the finished floor. Standards §§ 4.1.3(11), 4.1.6(1)(b), 4.22.4, 4.17.3, Fig. 30(d).
There is no accessible urinal provided. Provide a urinal with an elongated rim mounted 17 inches or less above the finished floor, a clear floor space of at least 30 inches wide and 48 inches deep centered on the urinal, and a flush control height of 44 inches or less above the finished floor. Standards §§ 4.1.3(11), 4.1.6(1)(b), 4.22.5, 4.18.2, 4.18.3, 4.18.4.
Within 12 months, unless otherwise noted, of the effective date of this Agreement, the County will complete the following modifications to Social Services Building C, 600 W. Clark in Eureka.
The parking reserved for persons with disabilities is inaccessible because the designated van accessible space and access aisle are not level. Provide designated accessible parking spaces and access aisles that are flat and level, with slopes and cross-slopes not exceeding 1:50 in all directions, with surfaces that are firm, stable, and slip-resistant. Standards §§ 4.1.2(5), 4.1.6(1)(b), 4.3.6, 4.5.1, 4.6.3.
The entrance door, which is accessed from the latch side of the door, is inaccessible because a planter is obstructing the clear floor space on the latch side, pull side of the door. On the pull side of the door, provide a path of travel at least 48 inches wide for a side approach and at least 24 inches of clear maneuvering space adjacent to the latch side of the door. Standards §§ 4.1.3(7)(b), 4.1.6(1)(b), 4.13.6, Fig. 25(c).
The door to the conference room is inaccessible because it has an opening width of only 29 inches. Within 24 months of the effective date of this Agreement, the County shall provide a door with a clear opening of 32 inches with the door open 90 degrees, measured between the face of the door and the opposite stop. Standards §§ 4.1.3(7)(b), 4.1.6(1)(b), 4.13.5, Fig. 24.
Although an accessible drinking fountain is provided, there is no drinking fountain provided for people who have difficulty bending or stooping. Provide a drinking fountain that is accessible to people who have difficulty bending or stooping. This can be accommodated by the use of a "hi-lo" fountain; by providing one fountain accessible to those who use wheelchairs and one fountain at a standard height convenient for those who have difficulty bending; by providing a fountain accessible to people who use wheelchairs and a cup dispenser, or by such other means as would achieve the required accessibility for each group of people. Standards §§ 4.1.3(10)(a), 4.1.6(1)(b).
(1)The paper towel dispenser is inaccessible because the controls are mounted 54 inches above the finished floor with a forward reach required. Provide a paper towel dispenser with the controls a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.1.3(13), 4.1.6(1)(b), 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
(2)The sanitary napkin dispenser is inaccessible because the controls are mounted 58 inches above the finished floor. Provide a sanitary napkin dispenser with the controls a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.1.3(13), 4.1.6(1)(b), 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
(3)The toilet stall is not configured so as to be accessible. Provide a toilet stall complies with Figure 30(a). Standards §§ 4.1.3(11), 4.1.6(1)(b), 4.22.4, 4.17.3, Fig. 30.
(4)The toilet is inaccessible because the flush control is on the closed side. Provide a flush control mounted on the "open" side of the toilet's clear floor space; 44 inches or less above the finished floor; and requiring a maximum of 5 pounds of force to operate; or provide an automatic flush device. Standards §§ 4.1.3(11), 4.1.6(1)(b), 4.22.4, 4.16.5, 4.17.2, 4.27.4.
(5)The toilet paper dispenser is inaccessible because it is mounted 40 inches from the rear wall. Provide a toilet paper dispenser that is mounted with its top at least 1½ inches under the side grab bar and 36 inches or less from the rear wall and is centered at least 19 inches above the finished floor. Standards §§ 4.1.3(11), 4.1.6(1)(b), 4.22.4, 4.17.3, Fig. 30(d).
(1)The toilet paper dispenser is inaccessible because it is mounted 43 inches from the rear wall. Provide a toilet paper dispenser that is mounted with its top at least 1½ inches under the side grab bar and 36 inches or less from the rear wall and is centered at least 19 inches above the finished floor. Standards §§ 4.1.3(11), 4.1.6(1)(b), 4.22.4, 4.17.3, Fig. 30(d).
Within 30 months of the effective date of this Agreement, the County will complete the following modifications to the Mental Health - Child Youth and Family Services, located at 1711 3rd Street.
There is no designated van accessible space with an access aisle, and the pavement markings are not clear. On the shortest accessible route to the accessible entrance, provide 1 van accessible space a minimum of 96 inches wide, served by access aisles at least 96 inches wide, with vertical signs with the International Symbol of Accessibility located such that they cannot be obstructed by parked vehicles, and with an additional "Van-Accessible" sign located below the International Symbol of Accessibility. Standards §§ 4.1.2(5)(b), 4.6, 4.30.7(1).
The route from the parking lot into the building is inaccessible because the surface is not stable, firm or slip resistant and the surface is not level. Provide at least one accessible route within the boundary of the site connecting these elements that, to the maximum extent feasible, coincides with the route for the general public. The accessible route must have a minimum clear width of 36 inches, or a minimum clear width of 42 inches if there is a turn around an obstruction less than 48 inches wide; have passing spaces at least 60 inches by 60 inches at least every 200 feet; have a minimum clear headroom of 80 inches; have a surface that is firm, stable, and slip resistant; have, in the absence of a curb ramp, ramp, elevator, or platform lift, no level changes in excess of ½ inch vertically; and have a running slope of less than 1:20 (5%) (or have been constructed as a fully accessible ramp) and a cross slope of less than 1:50 (2%). Standards §§ 4.3, 4.5, Fig. 7.
The entrance is inaccessible because there is no level approach at the front entrance within the door's required maneuvering clearance. Provide a door so that the floor or ground area within the required clearances is level and clear. Standards § 4.13.6, Fig. 25.
There is no signage directing people with disabilities to the accessible toilet rooms. Provide accessible directional signage with the International Symbol of Accessibility at inaccessible toilet rooms indicating the location of the nearest accessible toilet room, and provide accessible signage with the International Symbol of Accessibility at all accessible toilet rooms. Standards §§ 4.1.2(7)(d), 4.1.6(3)(e)(iii), 4.30.1, 4.30.2, 4.30.3, 4.30.5, 4.30.7.
Toilet Room - "Accessible"
There is no toilet room sign. Provide a toilet room sign with raised and Braille characters mounted on the wall adjacent to the latch side of the door with the centerline of the sign 60 inches above the finished floor and situated such that a person can approach within 3 inches of the sign without encountering an obstruction or standing within a door swing. Standards §§ 4.1.2(7)(d), 4.30.1, 4.30.4, 4.30.5, 4.30.6.
The toilet seat cover dispenser is inaccessible because the controls are mounted at 41 inches above the finished floor over a 28 inch obstruction. Provide a toilet seat cover dispenser such that the controls comply with Fig. 5 for a forward reach or with Fig. 6 for a side reach and such that it is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach, respectively, by a person using a wheelchair. Standards §§ 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
The lavatory is inaccessible because the hot water pipes are not insulated or otherwise configured to protect against contact. Provide hot water and drain pipes that are insulated or otherwise configured to protect against contact. Standards § 4.19.4.
The toilet is inaccessible because the seat is 16 inches above the finished floor and the centerline is 16 inches from the side wall. Provide a toilet with a centerline that is 18 inches from the near side wall; a seat that is between17 and 19 inches above the finished floor; and clear floor space at the toilet that complies with Fig. 28. Standards §§ 4.16.2, 4.16.3, Figs. 28, 29.
There are no grab bars provided. Provide a rear grab bar that is at least 36 inches in overall length, with the closer end no more than 6 inches from the side wall, and a side grab bar that is at least 42 inches in overall length, with the far end mounted at least 54 inches from the rear wall and the closer end 12 inches or less from the rear wall. Ensure that the grab bars are mounted 33 to 36 inches above the finished floor; with a diameter between 1¼ and 1½ inches; with 1½ inches between the grab bars and the wall; and at least 1½ inches between the grab bars and any object beside or below it and at least 18 inches between the grab bar and any object above it. Standards §§ 4.16.4, 4.26.2, Figs. 29, 39.
Within 24 months of the effective date of this Agreement, the County will complete the following modifications to Family Visitation Center, located at 231 D Street.
The designated accessible parking space is not van accessible. On the shortest accessible route to the accessible entrance, provide a van accessible space designated as reserved for people with disabilities. Ensure that van accessible spaces are a minimum of 96 inches wide and served by access aisles at least 96 inches wide. At all spaces designated as reserved for persons with disabilities, provide vertical signs with the International Symbol of Accessibility located such that they cannot be obstructed by parked vehicles. At van accessible spaces, provide an additional "Van-Accessible" sign located below the International Symbol of Accessibility. Ensure that all spaces and access aisles for persons with disabilities are flat and level, with slopes and cross-slopes not exceeding 1:50 in all directions, and that their surfaces are firm, stable, and slip-resistant. Standards §§ 4.1.2(5), 4.6, 4.30.7(1).
(1)The toilet room sign is not mounted on the latch side of the door. Provide a toilet room sign with raised and Braille characters mounted on the wall adjacent to the latch side of the door with the centerline of the sign 60 inches above the finished floor and situated such that a person can approach within 3 inches of the sign without encountering an obstruction or standing within a door swing. Standards §§ 4.1.2(7)(d), 4.30.1, 4.30.4, 4.30.5, 4.30.6. (2)The entry door is inaccessible because the pressure required to open the door is 10 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards § 4.13.11(2)(b).
(3)The entry door, which is accessed through a front approach, is inaccessible because there is insufficient clear floor space on the latch side, pull side of the door. On the pull side of the door, provide maneuvering clearance at least 60 inches deep and provide a minimum of 18 inches (24 inches is preferred) of maneuvering clearance on the latch side of the door. Standards § 4.13.6, Fig. 25(a).
(4)The toilet room door swings into the required clear floor space at the toilet. Ensure that no door swings into the required clear floor space at any accessible fixture. Standards § 4.22.2.
(6)The toilet is inaccessible because its centerline measures 19 inches from the side wall. Provide a toilet with a centerline that measures 18 inches from the near side wall. Standards § 4.16.2, Fig. 28.
(7)The rear grab bar at the toilet is inaccessible because the toilet tank interferes with its use. Provide a rear grab bar that has at least 1½ inches between the grab bar and any other object, such as a toilet seat cover dispenser. Standards §§ 4.16.4, 4.26.2, Fig. 39.
(1)The toilet room sign is not mounted on the latch side of the door. Provide a toilet room sign with raised and Braille characters mounted on the wall adjacent to the latch side of the door with the centerline of the sign 60 inches above the finished floor and situated such that a person can approach within 3 inches of the sign without encountering an obstruction or standing within a door swing. Standards §§ 4.1.2(7)(d), 4.30.1, 4.30.4, 4.30.5, 4.30.6.
(2)The entry door, which is accessed through a front approach, is inaccessible because there is insufficient clear floor space on the latch side, pull side of the door. On the pull side of the door, provide maneuvering clearance at least 60 inches deep and provide a minimum of 18 inches (24 inches is preferred) of maneuvering clearance on the latch side of the door. Standards § 4.13.6, Fig. 25(a).
(3)There is insufficient turning space within the toilet room. Provide an unobstructed turning space at least 60 inches in diameter or a T-shaped space complying with Fig. 3(b). Standards §§ 4.22.3, 4.2.3, Fig. 3.
(4)The toilet is inaccessible because its centerline measures 19 inches from the side wall. Provide a toilet with a centerline that measures 18 inches from the near side wall. Standards § 4.16.2, Fig. 28.
(5)The toilet is inaccessible because the flush control is on the closed side. Provide a flush control mounted on the "open" side of the toilet's clear floor space; 44 inches or less above the finished floor; and requiring a maximum of 5 pounds of force to operate; or provide an automatic flush device. Standards §§ 4.16.5, 4.27.4.
(6)The rear grab bar at the toilet is inaccessible because the toilet tank interferes with its use. Provide a rear grab bar that has at least 1½ inches between the grab bar and any other object, such as a toilet seat cover dispenser. Standards §§ 4.16.4, 4.26.2, Fig. 39.
Within 30 months of the effective date of this Agreement, the County will complete the following modifications to the Pace Program, located at 2501 Cypress in Eureka.
Probation office #1
(1)The door to the office is inaccessible because it has an opening width of only 28 inches. Provide a door with a clear opening of 32 inches with the door open 90 degrees, measured between the face of the door and the opposite stop. Standards § 4.13.5, Fig. 24.
(2)The door is inaccessible because knob hardware is used. Provide a door with hardware that is easy to grasp with one hand and that does not require tight grasping, pinching, or twisting of the wrist to operate. Lever-operated mechanisms, push-type mechanisms, and U-shaped handles are acceptable designs. Standards § 4.13.9.
(3)The door, which is accessed through a front approach, is inaccessible because it has only 8 inches of clear floor space on the latch side, pull side of the door. On the pull side of the door, provide maneuvering clearance at least 60 inches deep and provide a minimum of 18 inches (24 inches is preferred) of maneuvering clearance on the latch side of the door. Standards § 4.13.6, Fig. 25(a).
Probation office #2
(1)The door is inaccessible because knob hardware is used. Provide a door with hardware that is easy to grasp with one hand and that does not require tight grasping, pinching, or twisting of the wrist to operate. Lever-operated mechanisms, push-type mechanisms, and U-shaped handles are acceptable designs. Standards § 4.13.9.
(2)The door, which is accessed through a front approach, is inaccessible because it has only 5 inches of clear floor space on the latch side, pull side of the door. On the pull side of the door, provide maneuvering clearance at least 60 inches deep and provide a minimum of 18 inches (24 inches is preferred) of maneuvering clearance on the latch side of the door. Standards § 4.13.6, Fig. 25(a).
Class room 18 - Men's
(1)The toilet room sign is not mounted on the latch side of the door with Braille and raised characters. Provide a toilet room sign with raised and Braille characters mounted on the wall adjacent to the latch side of the door with the centerline of the sign 60 inches above the finished floor and situated such that a person can approach within 3 inches of the sign without encountering an obstruction or standing within a door swing. Standards §§ 4.1.2(7)(d), 4.30.1, 4.30.4, 4.30.5, 4.30.6.
(2)The door is inaccessible because it has an opening width of only 26 inches. Provide a door with a clear opening of 32 inches with the door open 90 degrees, measured between the face of the door and the opposite stop. Standards § 4.13.5, Fig. 24.
(3)The door is inaccessible because the pressure required to open the door is 17 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards § 4.13.11(2)(b).
(4)The toilet room door swings into the required clear floor space at the lavatory. Ensure that no door swings into the required clear floor space at any accessible fixture. Standards § 4.22.2.
(6)The paper towel dispenser is inaccessible because the controls are mounted at 52 inches above the finished floor over an obstruction. Provide a paper towel dispenser such that the controls comply with Fig. 5 for a forward reach or with Fig. 6 for a side reach and such that it is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach, respectively, by a person using a wheelchair. Standards §§ 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
(7)The lavatory is inaccessible because the apron is 27 inches above the finished floor; the hot water pipes and drain are not covered or otherwise configured to protect against contact; and the faucet has hardware that requires tight grasping, pinching, or twisting of the wrist. Provide a lavatory with the top of its rim or counter 34 inches or less above the finished floor; the bottom edge of the apron at least 29 inches above the finished floor; knee and toe clearances that comply with Fig. 31; hot water and drain pipes covered or otherwise configured to protect against contact; clear floor space at least 30 inches wide and 48 inches deep centered on the lavatory; and a faucet that can be operated with 5 pounds of force or less and can be used with one hand and without tight grasping, pinching, or twisting of the wrist (lever-operated, push-type, and electronically controlled mechanisms are examples of acceptable designs). Standards §§ 4.19.2, 4.19.3, 4.19.4, 4.19.5, 4.27.4, Figs. 31, 32.
(8)The urinal is inaccessible because the rim is mounted 24 inches above the finished floor, the controls are mounted 54 inches above the finished floor, and there is insufficient clear floor space around the urinal. Provide a urinal with an elongated rim mounted 17 inches or less above the finished floor, a clear floor space of at least 30 inches wide and 48 inches deep centered on the urinal, and a flush control height of 44 inches or less above the finished floor. Standards §§ 4.18.2, 4.18.3, 4.18.4.
(9)There is no accessible stall provided. Provide a "standard" accessible toilet stall at least 60 inches wide and at least 59 inches deep (or at least 56 inches deep with a wall-mounted toilet) such that all of the stall's elements, including stall door, stall door hardware, water closet, size and arrangement, toe clearances, grab bars, controls, and dispensers, comply with the Standards. Standards §§ 4.13, 4.16, 4.17, 4.26, 4.27, Fig. 30.
Classroom 19 - Women's
(3)The door is inaccessible because the pressure required to open the door is 20 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards § 4.13.11(2)(b). (4)The toilet room door swings into the required clear floor space at the lavatory. Ensure that no door swings into the required clear floor space at any accessible fixture. Standards § 4.22.2.
(5)No accessible mirror has been provided. Provide a mirror with the bottom edge of its reflecting surface no more than 40 inches above the finished floor. Standards § 4.19.6.
(6)There is insufficient turning space within the toilet room. Provide an unobstructed turning space at least 60 inches in diameter or a T-shaped space complying with Fig. 3(b). Standards §§ 4.22.3, 4.2.3, Fig. 3.
(7)The toilet seat cover dispenser is inaccessible because the controls are mounted at 57 inches above the finished floor over the toilet. Provide a toilet seat cover dispenser such that the controls comply with Fig. 5 for a forward reach or with Fig. 6 for a side reach and such that it is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach, respectively, by a person using a wheelchair. Standards §§ 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
(8)The lavatory is inaccessible because the apron is mounted 28 inches above the finished floor; the hot water pipes and drain are not covered or otherwise configured to protect against contact; the faucet hardware requires tight grasping, pinching, or twisting of the wrist; and there is insufficient clear floor space at the lavatory. Provide a lavatory with the top of its rim or counter 34 inches or less above the finished floor; the bottom edge of the apron at least 29 inches above the finished floor; knee and toe clearances that comply with Fig. 31; hot water and drain pipes covered or otherwise configured to protect against contact; clear floor space at least 30 inches wide and 48 inches deep centered on the lavatory; and a faucet that can be operated with 5 pounds of force or less and can be used with one hand and without tight grasping, pinching, or twisting of the wrist (lever-operated, push-type, and electronically controlled mechanisms are examples of acceptable designs). Standards §§ 4.19.2, 4.19.3, 4.19.4, 4.19.5, 4.27.4, Figs. 31, 32.
Within 12 months of the effective date of this Agreement, the County will complete the following modifications to the Probation Department, located at 1105 Sixth Street.
Parking. The parking reserved for persons with disabilities lacks appropriate signage. At all spaces designated as reserved for persons with disabilities, provide vertical signs with the International Symbol of Accessibility located such that they cannot be obstructed by parked vehicles. At van accessible spaces, provide an additional "Van-Accessible" sign located below the International Symbol of Accessibility. Standards §§ 4.6.4, 4.30.7(1).
The entrance into the building is inaccessible because there is a 3 inch change in level at the threshold to the door. Provide an accessible door with a threshold that is no greater than ¼ inch, or is no greater than ½ inch and is beveled with a slope no greater than 1:2. Standards §§ 4.13.8, 4.5.2.
The hallway entrance to the program is not accessible because knob hardware is used. Provide a door with hardware that is easy to grasp with one hand and that does not require tight grasping, pinching, or twisting of the wrist to operate. Lever-operated mechanisms, push-type mechanisms, and U-shaped handles are acceptable designs. Standards § 4.13.9.
The toilet room sign is not mounted on the latch side of the door with Braille and raised characters. Provide a toilet room sign with raised and Braille characters mounted on the wall adjacent to the latch side of the door with the centerline of the sign 60 inches above the finished floor and situated such that a person can approach within 3 inches of the sign without encountering an obstruction or standing within a door swing. Standards §§ 4.1.2(7)(d), 4.30.1, 4.30.4, 4.30.5, 4.30.6.
The toilet is inaccessible because its centerline measures 28 inches from the side wall. Provide a toilet with a centerline that measures 18 inches from the near side wall. Standards § 4.16.2, Fig. 28.
The toilet is inaccessible because the flush control is on the closed side. Provide a flush control mounted on the "open" side of the toilet's clear floor space; 44 inches or less above the finished floor; and requiring a maximum of 5 pounds of force to operate; or provide an automatic flush device. Standards §§ 4.16.5, 4.27.4.
The toilet paper dispenser is inaccessible because it is mounted above the grab bar. Provide a toilet paper dispenser that is mounted within reach, with its top at least 1½ inches under the side grab bar, and centered at least 19 inches above the finished floor. Standards § 4.16.6, Fig. 29(b).
Within 30 months of the effective date of this Agreement, the County will complete the following modifications to the Rio Dell Library.
Parking. The parking has no designated accessible parking. On the shortest accessible route to the accessible entrance, provide one van accessible space designated as reserved for people with disabilities. Ensure that van accessible spaces are a minimum of 96 inches wide and served by access aisles at least 96 inches wide. Provide a vertical sign with the International Symbol of Accessibility located such that it cannot be obstructed by parked vehicles. Provide an additional "Van-Accessible" sign located below the International Symbol of Accessibility. Ensure that the space and access aisle for persons with disabilities are flat and level, with slopes and cross-slopes not exceeding 1:50 in all directions, and that their surfaces are firm, stable, and slip-resistant. Standards §§ 4.1.2(5), 4.6, 4.30.7(1).
The route from the parking lot to the building is inaccessible because the surface is not stable, firm, or slip resistant. Provide at least one accessible route within the boundary of the site connecting these elements that, to the maximum extent feasible, coincides with the route for the general public. The accessible route must have a minimum clear width of 36 inches, or a minimum clear width of 42 inches if there is a turn around an obstruction less than 48 inches wide; have passing spaces at least 60 inches by 60 inches at least every 200 feet; have a minimum clear headroom of 80 inches; have a surface that is firm, stable, and slip resistant; have, in the absence of a curb ramp, ramp, elevator, or platform lift, no level changes in excess of ½ inch vertically; and have a running slope of less than 1:20 (5%) (or have been constructed as a fully accessible ramp) and a cross slope of less than 1:50 (2%). Standards §§ 4.3, 4.5, Fig. 7.
Ramp. The ramp is inaccessible because the surface of the bottom of the ramp is not stable, firm, or slip resistant; the landing where there is a change in direction is 53 inches by 40 inches; and the handrails are mounted at 41 inches above the finished floor. Provide a ramp that with level landings measuring at least 60 inches by 60 inches when the ramp changes direction. Provide handrails that are between 1¼ inches and 1½ inches in diameter such that the inside handrail is continuous and both handrails have a continuous gripping surface along both sides of the ramp extending at least 12 inches beyond the top and bottom of the ramp parallel with the ground surface; the handrails do not rotate within their fittings; and both handrails are mounted between 34 inches and 38 inches above the ramp surface and 1½ inches from the wall, with ends rounded or returned smoothly to the floor, wall, or post. Ensure that the ramp and approaches are designed so that water will not accumulate on walking surfaces. Standards §§ 4.3.8, 4.8.
Within 30 months of the effective date of this Agreement, the County will complete the following modifications to the Trinidad Library.
The route is inaccessible because it has a slope of 8.4% and has no ramp features. Provide a ramp that is at least 36 inches wide with a slope not exceeding 8.33% and a cross slope not exceeding 2%; with level landings at least as wide as the ramp and 60 inches long at the top and bottom of the ramp; with level landings measuring at least 60 inches by 60 inches when the ramp changes direction; and edge protection that is at least 2 inches high at the drop off sides. Provide handrails that are between 1¼ inches and 1½ inches in diameter such that the inside handrail is continuous and both handrails have a continuous gripping surface along both sides of the ramp extending at least 12 inches beyond the top and bottom of the ramp parallel with the ground surface; the handrails do not rotate within their fittings; and both handrails are mounted between 34 inches and 38 inches above the ramp surface and 1½ inches from the wall, with ends rounded or returned smoothly to the floor, wall, or post. Ensure that the ramp and approaches are designed so that water will not accumulate on walking surfaces. Standards §§ 4.3.8, 4.8.
The building is inaccessible because there are no signs indicating the accessible route to the accessible entrance. Provide accessible directional signage with the International Symbol of Accessibility at inaccessible entrances directing users to the accessible entrance, and provide accessible signage with the International Symbol of Accessibility at all permanent accessible entrances. Standards §§ 4.1.3(8)(d), 4.13, 4.30.
Within 24 months of the effective date of this Agreement, the County will complete the following modifications to the SCOP Office in Willow Creek.
Although the parking lot has a total of 8 parking spaces, there are no parking spaces designated as reserved for people with disabilities. On the shortest accessible route to the accessible entrance, provide 1 van accessible space designated as reserved for people with disabilities. Van accessible spaces shall be a minimum of 96 inches wide and served by access aisles at least 96 inches wide. The space shall have a vertical sign with the International Symbol of Accessibility located such that they cannot be obstructed by parked vehicles. Van accessible spaces shall have an additional "Van-Accessible" sign located below the International Symbol of Accessibility. Standards §§ 4.1.2(5), 4.6, 4.30.7(1).
The ramp at the side of the building is inaccessible because there is no edge protection; no level landing at the top of the ramp; the handrails are not at an adequate height, and there are no 12 inch extensions at the top or bottom of the ramp that are parallel to the ground. Provide a ramp that is at least 36 inches wide with a slope not exceeding 1:12 and a cross slope not exceeding 1:50; with level landings at least as wide as the ramp and 60 inches long at the top and bottom of the ramp; and with edge protection at least 2 inches high at the drop off sides. Provide handrails that are between 1¼ inches and 1½ inches in diameter with a continuous gripping surface along both sides of the ramp, extending at least 12 inches beyond the top and bottom of the ramp parallel with the ground surface. Ensure that handrails are mounted between 34 inches and 38 inches above the ramp surface and 1½ inches from the wall, with ends rounded or returned smoothly to the floor, wall, or post, and that they do not rotate within their fittings. Ensure that the ramp and approaches are designed so that water will not accumulate on walking surfaces. Standards §§ 4.3.8, 4.8.
Within 24 months of the effective date of this Agreement, the County will complete the following modifications to the Willow Creek Library.
Accessible Route. The route from the parking lot to the entrance is inaccessible because the surface is not stable, firm, and slip resistant. Provide at least one accessible route within the boundary of the site connecting these elements that, to the maximum extent feasible, coincides with the route for the general public. The accessible route must have a minimum clear width of 36 inches, or a minimum clear width of 42 inches if there is a turn around an obstruction less than 48 inches wide; have passing spaces at least 60 inches by 60 inches at least every 200 feet; have a minimum clear headroom of 80 inches; have a surface that is firm, stable, and slip resistant; have, in the absence of a curb ramp, ramp, elevator, or platform lift, no level changes in excess of ½ inch vertically; and have a running slope of less than 1:20 (5%) (or have been constructed as a fully accessible ramp) and a cross slope of less than 1:50 (2%). Standards §§ 4.3, 4.5, Fig. 7. The entry door is inaccessible because knob hardware is used. Provide a door with hardware that is easy to grasp with one hand and that does not require tight grasping, pinching, or twisting of the wrist to operate. Lever-operated mechanisms, push-type mechanisms, and U-shaped handles are acceptable designs. Standards § 4.13.9.
The free standing drinking fountain is inaccessible because there is no knee space. Provide a drinking fountain with a clear floor space of at least 30 inches by 48 inches that allows a person in a wheelchair to make a parallel approach to the unit. Standards §§ 4.15.5(2), 4.2.4, Figs. 27(c), (d).
The single user toilet room contains a number of inaccessible elements and is not accessible to people with disabilities. Provide an accessible toilet room such that all of the room's elements, including signage, door, door hardware, clear floor space, water closet, urinal (if provided), grab bars, lavatory, mirror, controls, and dispensers, comply with the Standards. Standards §§ 4.13, 4.16, 4.18, 4.19, 4.26, 4.27, 4.30, Figs. 28, 29.
Within 30 months of the effective date of this Agreement, the County will complete the following modifications to the Blue Lake Library.
The tables in the library are inaccessible because none provide adequate knee space. Provide accessible tables on an accessible route at least 36 inches wide. Ensure that the tables have clear floor space of 30 inches wide by 48 inches deep, knee clearance of at least 27 inches high by 30 inches wide by 19 inches deep, and a writing surface between 28 and 34 inches above the finished floor. Standards §§ 8.2, 4.2.4.1, 4.32.
The lavatory is inaccessible because the faucet hardware requires tight grasping, pinching, or twisting of the wrist. Provide a lavatory with a faucet that can be operated with 5 pounds of force or less and can be used with one hand and without tight grasping, pinching, or twisting of the wrist (lever-operated, push-type, and electronically controlled mechanisms are examples of acceptable designs). Standards §§ 4.19.5, 4.27.4.
The side grab bar at the toilet is inaccessible because the closest end to the rear wall is mounted 14.5 inches from the rear wall. Provide a side grab bar that is at least 42 inches in overall length, with the far end mounted at least 54 inches from the rear wall and the closer end 12 inches or less from the rear wall; mounted 33 to 36 inches above the finished floor; with a diameter between 1¼ and 1½ inches; with 1½ inches between the grab bar and the wall; and at least 1½ inches between the grab bar and any other object, such as the toilet paper dispenser. Standards §§ 4.16.4, 4.26.2, Fig. 29.
The rear grab bar at the toilet is inaccessible because toilet tank is 1.25 inches below the grab bar. Provide a rear grab bar that has at least 1½ inches between the grab bar and any other object, such as a toilet seat cover dispenser. Standards §§ 4.16.4, 4.26.2, Fig. 39.
The toilet is inaccessible because there is insufficient clear floor space because of a trash can obstructing the space. Provide clear floor space at the toilet that complies with Fig. 28. Standards § 4.16.2, Fig. 28.
The lavatory is inaccessible because the clear floor space is obstructed by boxes. Provide a lavatory with clear floor space at least 30 inches wide and 48 inches deep centered on the lavatory. Standards § 4.19.3, Fig. 32. Ramp. The ramp is inaccessible because the slope at the top of the ramp is 14.2%; the cross-slope ranges from .6% to 2.5%; handrails are not on both sides of the ramp; and the handrail that is provided is not mounted at an adequate height, there are no 12 inches extensions at the top or bottom of the ramp, and it does not return smoothly to the wall or post. Provide a ramp that is at least 36 inches wide with a slope not exceeding 1:12 and a cross slope not exceeding 1:50; with level landings at least as wide as the ramp and 60 inches long at the top and bottom of the ramp; and with edge protection at least 2 inches high at the drop off sides. Provide handrails that are between 1¼ inches and 1½ inches in diameter with a continuous gripping surface along both sides of the ramp, extending at least 12 inches beyond the top and bottom of the ramp parallel with the ground surface. Ensure that handrails are mounted between 34 inches and 38 inches above the ramp surface and 1½ inches from the wall, with ends rounded or returned smoothly to the floor, wall, or post, and that they do not rotate within their fittings. Ensure that the ramp and approaches are designed so that water will not accumulate on walking surfaces. Standards §§ 4.3.8, 4.8. Parking
There is no designated van accessible space. On the shortest accessible route to the accessible entrance, provide 1 van accessible space a minimum of 96 inches wide, served by access aisles at least 96 inches wide, with vertical signs with the International Symbol of Accessibility located such that they cannot be obstructed by parked vehicles, and with an additional "Van-Accessible" sign located below the International Symbol of Accessibility. Standards §§ 4.1.2(5)(b), 4.6, 4.30.7(1).
The parking reserved for persons with disabilities lacks appropriate signage. At all spaces designated as reserved for persons with disabilities, provide vertical signs with the International Symbol of Accessibility located such that they cannot be obstructed by parked vehicles. Standards §§ 4.6.4, 4.30.7(1).
One of the designated accessible parking spaces is not located on the shortest accessible route to the accessible facility entrance. Provide fully accessible parking that is located on the shortest accessible route to an accessible pedestrian entrance to the facility. Standards § 4.6.2.
Within 24 months of the effective date of this Agreement, the County will complete the following modifications to the Public Health (WIC) Office in Fortuna.
Accessible Route. The door into the building, which is accessed through a front approach, is inaccessible because there is no clear floor space on the pull side. On the pull side of the door, provide maneuvering clearance at least 60 inches deep and provide a minimum of 18 inches (24 inches is preferred) of maneuvering clearance on the latch side of the door. Standards § 4.13.6, Fig. 25(a).