Source: https://www.govregs.com/regulations/40/60.482-4a
Timestamp: 2020-07-06 17:45:02
Document Index: 224818716

Matched Legal Cases: ['§ 60', '§ 60', '§ 60', '§ 60', '§ 60', '§ 60', '§ 60']

40 CFR 60.482-4a - Standards: Pressure relief devices in gas/vapor service. § 60.482-4a - Standards: Pressure relief devices in gas/vapor service.
§ 60.482-4a - Standards: Pressure relief devices in gas/vapor service.
(a) Except during pressure releases, each pressure relief device in gas/vapor service shall be operated with no detectable emissions, as indicated by an instrument reading of less than 500 ppm above background, as determined by the methods specified in § 60.485a(c).
(b)(1) After each pressure release, the pressure relief device shall be returned to a condition of no detectable emissions, as indicated by an instrument reading of less than 500 ppm above background, as soon as practicable, but no later than 5 calendar days after the pressure release, except as provided in § 60.482-9a.
(2) No later than 5 calendar days after the pressure release, the pressure relief device shall be monitored to confirm the conditions of no detectable emissions, as indicated by an instrument reading of less than 500 ppm above background, by the methods specified in § 60.485a(c).
(c) Any pressure relief device that is routed to a process or fuel gas system or equipped with a closed vent system capable of capturing and transporting leakage through the pressure relief device to a control device as described in § 60.482-10a is exempted from the requirements of paragraphs (a) and (b) of this section.
(2) After each pressure release, a new rupture disk shall be installed upstream of the pressure relief device as soon as practicable, but no later than 5 calendar days after each pressure release, except as provided in § 60.482-9a.