Source: http://docplayer.net/1352812-Summary-of-express-terms-of-new-york-nycrr-parts-711-712-713-715-and-716-set-forth-the-architectural.html
Timestamp: 2016-12-08 07:06:16
Document Index: 718962327

Matched Legal Cases: ['arts 711', 'arts 711', 'arts 711', 'arts 711', 'art 712', 'art 712', 'art 712', 'art 712', 'art 712', 'art 712', 'art 713', 'art 713', 'art 713', 'art 713', 'art 713', 'art 714', 'art 714', 'art 713', 'art 715', 'art 715', 'art 715', 'art 715', 'art 715', 'art6', 'art 716', 'art 716', 'art 716', 'art 716', 'art 716', 'art 712', 'art 716', 'arts 711', 'art 711', 'art 711', 'arts 35', 'arts 35', 'art 36', 'art 711', 'art 711', 'art 711', 'art 711', 'ART 1', 'art 1', 'art 1', 'art 1228', 'art 1228', 'art 1228', 'ART 713', 'ART 713', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 2']

⭐SUMMARY OF EXPRESS TERMS. of New York (NYCRR) Parts 711, 712, 713, 715 and 716 set forth the architectural,
SUMMARY OF EXPRESS TERMS. of New York (NYCRR) Parts 711, 712, 713, 715 and 716 set forth the architectural,
Download "SUMMARY OF EXPRESS TERMS. of New York (NYCRR) Parts 711, 712, 713, 715 and 716 set forth the architectural,"
1 Standards of Construction for Health Care Facilities Effective date: 12/29/10 SUMMARY OF EXPRESS TERMS Title 10 of the Official Compilation of Codes, Rules and Regulations of the State of New York (NYCRR) Parts 711, 712, 713, 715 and 716 set forth the architectural, engineering, equipment and construction and other physical environment standards for all health facilities subject to Department of Health oversight pursuant to Public Health Law (PHL) Article 28. Proposed Revisions to 10 NYCRR Part NYCRR Section would be revised to more clearly identify the facilities and the standards that are subject to regulation. In addition, language would be added to clearly identify construction related information that must be filed with construction applications. The proposal would clarify the process for submitting a construction application. 10 NYCRR Section would be revised to require health care facilities to comply with more current National Fire Protection Association ("NFPA") standards, including NFPA 101, Life Safety Code, 2000 edition, which is the life safety code currently mandated by the federal government for Medicare and Medicaid certification. In addition, 10 NYCRR Section would be revised to require that health care facilities comply with more current national codes addressing radiation protection, facility heating, cooling and ventilation (HVAC) and gas and vacuum systems. 102 NYCRR section would be revised to require that future health care facility construction conform to the 2010 edition of Guidelines for Design and Construction of Health Care Facilities. 10 NYCRR Section 711.3, which establishes general site requirements for health care facilities, would be revised to clarify language, add requirements for facility occupants other than patients and eliminate outdated site requirements. 10 NYCRR Sections 711.4, 711.5, 711.7, 711.8, and would be repealed. New 10 NYCRR Section would set forth specific requirements for obtaining waivers of construction standards. Proposed Revisions to 10 NYCRR Part 712 The regulatory proposal would repeal existing 10 NYCRR Part 712, which includes standards of construction for some hospitals, and replace it with a new Part 712 (Standards of Construction for General Hospital Facilities). The proposal would consolidate all requirements specific to general hospital construction into 10 NYCRR Part 712. New Part 712 would be divided into two Subparts based on the date when general hospital construction was or is to be undertaken. New Subpart would set forth minimum construction and physical environment standards applicable to general hospitals built and to portions of general hospitals altered or renovated pursuant to Department or commissioner approval granted prior to October 14, 1998 and to general hospital construction projects not requiring such approvals that were completed prior to October 14, New Subpart would 23 include requirements in existing 10 NYCRR Section and existing 10 NYCRR Part 712. New Subpart would set forth minimum construction and physical environment standards applicable to general hospitals built and to portions of general hospitals altered or renovated pursuant to Department or commissioner approval granted on or after October 14, 1998 and to general hospital construction projects not requiring such approvals that were or will be completed after October 14, New Subpart would require that construction projects comply with Guidelines for Design and Construction of Health Care Facilities and would include some additional regulatory requirements. Proposed Revisions to 10 NYCRR Part 713 The regulatory proposal would repeal existing Part 713, which sets forth construction standards for some nursing homes, and replace it with a new Part 713 (Standards of Construction for Nursing Home Facilities). The proposal would consolidate all requirements specific to nursing home construction into 10 NYCRR Part 713. Part 713 would be divided into four subparts based on the date when nursing home construction was or is to be undertaken. Subpart would set forth minimum construction and physical environment standards applicable to nursing home facilities built, to portions of nursing homes facilities renovated or altered prior to August 25, 1975 and to nursing home construction projects approved by the commissioner or Department prior to August 25, New Subpart would include requirements that are in existing 10 NYCRR Section4 Subpart would set forth minimum construction and physical environment standards applicable to nursing home facilities built, to portions of nursing homes facilities renovated or altered between August 25, 1975 and July 1, 1990 and to nursing home construction projects approved by the commissioner or Department between August 25, 1975 and July 1, Subpart would include requirements that are in existing 10 NYCRR Section Subpart would set forth minimum construction and physical environment standards applicable to nursing home facilities built, to portions of nursing homes facilities renovated or altered between July 1, 1990 and December 31, 2010 and to nursing home construction projects approved by the commissioner or Department between July 1, 1990 and December 31, Subpart would incorporate by reference Guidelines for Design and Construction of Health Care Facilities. Additional requirements not addressed in this document would be included in the proposed Subpart. Subpart would set forth minimum construction and physical environment standards applicable to nursing home facilities built, to portions of nursing homes facilities renovated or altered after December 31, 2010 and to nursing home construction projects approved by the commissioner or Department after December 31, Subpart would require that construction projects comply with the 2010 edition of the Guidelines for Design and Construction of Health Care Facilities as well as additional regulatory requirements. Proposed Revisions to 10 NYCRR Part 714 45 The regulatory proposal would consolidate all requirements specific to adult day health care program facility construction into 10 NYCRR Part 714, including requirements in existing 10 NYCRR Part 713. It would require future adult day health care program facility construction to comply with the 2010 edition of the Guidelines for Design and Construction of Health Care Facilities as well as additional regulatory requirements. Proposed Revisions to 10 NYCRR Part 715 The regulatory proposal would repeal existing 10 NYCRR Part 715 and replace it with a new Part 715 (Standards of Construction for Freestanding Ambulatory Care Facilities). The regulatory proposal would consolidate all requirements specific to freestanding ambulatory care facilities into 10 NYCRR Part 715. New Part 715 would be divided into two Subparts based on the date when ambulatory care facility construction was or is to be undertaken. New Subpart would set forth minimum construction and physical environment standards applicable to: (1) diagnostic center and treatment center facilities built and to portions of such facilities renovated or altered prior to January 1, 2011; (2) general hospital offsite outpatient facilities built and to portions of such facilities renovated or altered prior to January 1, 2011; and, (3) general hospital offsite outpatient facility construction projects and diagnostic center and treatment center facility construction projects approved by the commissioner or Department prior to January 1, New Subpart would include requirements that are in existing 10 NYCRR Section and existing 10 NYCRR Part6 New Subpart would set forth minimum construction and physical environment standards applicable to:(1) diagnostic center and treatment center facilities built and to portions of such facilities renovated or altered after January 1, 2011; (2) general hospital offsite outpatient facilities built and to portions of such facilities renovated or altered after January 1, 2011; and, (3) general hospital offsite outpatient facility construction projects and diagnostic center and treatment center facility construction projects approved by the commissioner or department after January 1, New Subpart would require future ambulatory care construction to comply with the 2010 edition of the Guidelines for Design and Construction of Health Care Facilities as well as additional regulatory requirements. Proposed Revisions to 10 NYCRR Part 716 The regulatory proposal would repeal existing 10 NYCRR Part 716 and replace it with a new Part 716 (Standards of Construction for Rehabilitation Facilities). The regulatory proposal would consolidate into New Part 716 all standards of construction specifically applicable to rehabilitation facilities. New Part 716 would include requirements that are in existing 10 NYCRR Section and existing 10 NYCRR Part 712. New Part 716 would also require that future rehabilitation facility construction comply with the 2010 edition of the Guidelines for Design and Construction of Health Care Facilities as well as additional regulatory requirements. 67 Pursuant to the authority vested in the State Hospital Review and Planning Council, and subject to the approval of the Commissioner of Health, by Sections 2802 and 2803 of the Public Health Law; Parts 711, 712, 713, 714, 715, and 716 of Title 10 (Health) of the Official Compilation of Codes Rules and Regulations of the State of New York are hereby amended to be effective upon publication of a Notice of Adoption in the New York State Register, to read as follows: Section of Part 711 is amended to read as follows: Section Applicability. (a) [The general construction standards set forth in this Part shall apply to all medical facilities and together with the construction standards set forth elsewhere in this Chapter shall constitute the minimum construction standards for medical facilities.] This Part sets forth minimum construction and physical environment standards applicable to all health facilities subject to Public Health Law Article 28, including but not limited to, general hospitals, nursing homes and ambulatory care facilities. [(b) For the purpose of hearings on the issue of compliance with the standards of this Subchapter, the determination of compliance or noncompliance shall be based upon those standards existent on the date of notice of a hearing.] [(c) If the application, project concept, of any new facility was approved prior to the effective date of this Subchapter, the facility, upon completion of construction, shall be required to comply only with those standards for new construction which were extant on the date of approval of the aforementioned application.] 78 [(d) If the application, program scope, for a nonsubstantial project, was approved prior to the effective date of this Subchapter, the facility, upon completion of construction, shall be required to comply only with those standards for new construction which were extant on the date of approval of the aforementioned application.] [(e) Upon initial submission of all projects for department review, the health care provider shall submit a functional program that defines the construction aspects of the project and describes the purpose of the project, departmental objectives, space requirements, and other basic information including, as applicable, the projected demand or utilization and staffing patterns, relating to fulfillment of the institution s objectives. Depending upon the scope of the project, this program may consist, all or in part, of drawings or narrative that describes each function or service; the operational space required for each function; the quantity of staff or other occupants for each space; the numbers, types and areas (in net square feet) of all spaces; special design features; systems of operation; and interrelationships of all spaces and functions. This program must include a description of those services necessary for complete operation of the facility. Any services available elsewhere in the community or institution must be indicated, and need not be duplicated.] (b) An applicant seeking approval to construct a new health facility or alter or renovate an existing health facility shall submit to the department a completed application and functional program. The applicant shall ensure that all terms and acronyms are clearly defined and consistently used in the application and functional program. The functional program, which is a detailed architectural and design plan for the health facility, shall include a description of the following: 89 (1) the scope and purpose of the proposed construction project and other basic information relating to fulfillment of the applicant s objectives; (2) the services necessary for the complete operation of the health facility, the size and function of each space, any special design features, the projected occupant load, and numbers and types of staff, patients, residents, visitors and vendors; (3) the types and projected numbers of procedures to be performed in each treatment area and circulation patterns for staff, patients or residents, and the public; (4) the projected demand or utilization, staffing patterns, departmental relationships, space requirements, and circulation patterns that are a function of infection control requirements and for clean and soiled materials; (5) equipment requirements, including building service equipment and fixed and moveable equipment; and, (6) potential future expansion that may be needed to accommodate increased demand. (c) Once approved by the department, [this] the functional program[,] and the approved plans and specifications developed from it[,] shall be used in the development, design and construction of the project and serve as the basis for all subsequent construction approvals regarding the specific project. The applicant or health facility operator shall retain and make available to the department, upon the department's request, the functional program, all government approved plans and specifications developed from it and any other design data to facilitate alterations, and program changes. 910 Section of Part 711 is amended to read as follows: Section Pertinent technical standards. [All medical facilities shall provide for proper, safe and efficient patient and resident care. Compliance with pertinent provisions of the following national codes and standards is required] All health facilities shall comply with the pertinent provisions of the standards and codes referred to in this section and with local laws relating to zoning, sanitation, fire safety and construction, where such local laws represent standards in addition to those required by this Part. Reference throughout this chapter to [national] codes and standards shall be those editions listed in this section. If a conflict occurs between the following codes and standards or between them and regulations elsewhere in this chapter then compliance with the more restrictive regulation is required. If federal regulatory requirements conflict with the codes and standards referred to in this section, the department may waive compliance with such standards and codes, provided that a health facility fully complies with said federal regulatory requirements. (a) The following National Fire Protection Association (NFPA) Codes and Standards are hereby incorporated by reference, with the same force and effect as if fully set forth at length herein. These codes and standards are available for public inspection and copying at the [Office of Regulatory Reform] Regulatory Affairs Unit, New York State Department of Health, Corning Tower, Empire State Plaza, Albany, NY The codes and standards are published by the National Fire Protection Association, and [C]copies are also available from the National Fire Protection Association, 1 1011 Batterymarch Park, P.O. Box 9101, Quincy, MA , or The various codes and standards are available from the NFPA either as individual publications or as contained within the [1996] Compilation of NFPA National Fire Codes, 1999 edition. (1) NFPA 101[-1997], Life Safety Code[.], 2000 edition. (2) NFPA 101A [1995], Guide on Alternative Approaches to Life Safety[.], 1998 edition. (3) NFPA 10[-1994], Standard for Portable Fire Extinguishers[.], 1998 edition. [(4) NFPA Standard for Low Expansion Foam. (5) NFPA 11A Standard for Medium and High Expansion Foam Systems. (6) NFPA Standard on Carbon Dioxide Extinguishing Systems. (7) NFPA 12A Standard on Halon 1301 Fire Extinguishing Systems.] [(8)] (4) NFPA 13[-1996-], Standard for the Installation of Sprinkler Systems[.], 1999 edition. [(9)] (5) NFPA 14 [-1996], Standard for the Installation of Standpipe, Private Hydrants and Hose Systems[.], 2000 edition. [(10) NFPA Standard for Water Spray Fixed Systems for Fire Protection. (11) NFPA Standard for the Installation of Deluge Foam-Water Sprinkler Systems and Foam-Water Spray Systems. (12) NFPA Standard for Dry Chemical Extinguishing Systems. (13) NFPA Standard for the Installation of Centrifugal Fire Pumps.] (6) NFPA 25, Standard for the Inspection, Testing, and Maintenance of Water-Based Fire Protection Systems, 1998 edition. [(14)] (7) NFPA Flammable and Combustible Liquids Code. [(15)] (8) NFPA 31[-1992-], Standard for the Installation of Oil- Burning Equipment[.], 1997 edition. [(16)] (9) NFPA Standard on Fire Protection for Laboratories Using Chemicals. 1112 [(17)] (10) NFPA 54[-1996], National Fuel Gas Code[.], 1999 edition. [(18] (11) NFPA 58[-1995 Standard for the Storage and Handling of: Liquefied Petroleum Gases], Liquefied Petroleum Gases Code, 1998 edition. [(19)] (12) NFPA 70 [-1996], National Electrical Code, 1999 edition. [(20)] (13) NFPA 72 [ 1996], National Fire Alarm Code[.], 1999 edition. [(21)] (14) NFPA 80 [-1995], Standard for Fire Doors and Fire Windows[.], 1999 edition. [(22)] (15) NFPA 82 [-1994], Standard on Incinerators[,] and Waste and Linen Handling Systems and Equipment[.], 1999 edition. [(23)] (16) NFPA 90A [-1996], Standard for the Installation of Air Conditioning and Ventilating Systems[.], 1999 edition. (17) NFPA 90B, Standard for the Installation of Warm Air Heating and Air-Conditioning Systems, 1999 edition. [(24)] (18) NFPA 91[-1995], Standards for Exhaust Systems for Air Conveying of [Materials] Vapors, Gases, Mists and Noncombustible Particulate Solids, 1999 edition. [(25)] (19) NFPA 96 [-1994], Standard for Ventilation Control and Fire Protection of Commercial Cooking Operations, 1998 edition. [(26)] (20) NFPA 99 [-1996], Standard for Health Care Facilities, 1999 edition. [(27)] (21) NFPA 110 [-1996], Standard for Emergency and Standby Power Systems, 1999 edition. (22) NFPA 111, Standard on Stored Electrical Energy Emergency and Standby Power Systems, 1996 edition. (23) NFPA 211, Standard for Chimneys, Fireplaces, Vents, and Solid Fuel-Burning Appliances, 2000 edition. [(28)] (24) NFPA 220 [-1995], Standard on Types of Building Construction[.], 1999 edition. (25) NFPA 221, Standard for Fire Walls and Fire Barrier Walls, 1997 edition. [(29)] (26) NFPA Standard for Safeguarding Construction, Alteration, and Demolition Operations. 1213 [(30)] (27) NFPA 251[-1995], Standard Methods of Tests of Fire Endurance of Building Construction and Materials[.], 1999 edition. [(31)] (28) NFPA 252 [-1995], Standard Methods of Fire Tests of Door Assemblies[.], 1999 edition. [(32)] (29) NFPA 253[-1995], Standard Method of Test for Critical Radiant Flux of Floor Covering Systems Using a Radiant Heat Energy Source[.], 2000 edition. [(33)] (30) NFPA 255[-1996], Standard Method of Test of Surface Burning Characteristics of Building Materials[.], 2000 edition. [(34)] (31) NFPA 256[-1993], Standard Methods of Fire Tests of Roof Coverings[.], 1998 edition. [(35)] (32) NFPA 257[- 1996], Standard [for] on Fire [Tests] Test for Windows and Glass Block Assemblies[.], 2000 edition. (33) NFPA 260, Standard Methods of Tests and Classification System for Cigarette Ignition Resistance of Components of Upholstered Furniture, 1998 edition. (34) NFPA 261, Standard Method of Tests for Determining Resistance of Mock-Up Upholstered Furniture Material Assemblies to Ignition by Smoldering Cigarettes, 1998 edition. (35) NFPA 265, Standard Methods of Fire Tests for Evaluating Room Fire Growth Contribution of Textile Wall Coverings, 1998 edition. (36) NFPA 266, Standard Method of Test for Fire Characteristics of Upholstered Furniture Exposed to Flaming Ignition Source, 1998 edition. (37) NFPA 267, Standard Method of Test for Fire Characteristics of Mattresses and Bedding Assemblies Exposed to Flaming Ignition Source, 1998 edition. (38) NFPA 286, Standard Methods of Fire Tests for Evaluating Room Fire Contribution of Wall and Ceiling Interior Finish, 2000 edition. (39) NFPA 418, Standard for Heliports, 1995 edition. [(36)] (40) NFPA 701 [-1996], Standard Methods of Fire Tests for Flame[-Resistant] Propagation of Textiles and Films[.], 1999 edition. [(37)] (41) NFPA 703 [-1995-], Standard for Fire Retardant Impregnated Wood and Fire Retardant Coatings for Building Materials[.], 2000 edition. [(38) NFPA Standard for Public Fire Service Communication Systems.] 1314 (b) The following codes and standards are hereby incorporated by reference, with the same force and effect as if fully set forth at length herein. These codes and standards are available for public inspection and copying at the [Office of Regulatory Reform] Regulatory Affairs Unit, New York State Department of Health, Corning Tower, Empire State Plaza, Albany, NY Copies are also available from the publisher or issuing organization at the address listed. [(1) National Standard Plumbing Code-Illustrated, 1993, with supplement. National Association of Plumbing-Heating-Cooling Contractors, P.O. Box 6808, Falls Church, VA ] [(2) U.S. Department of Health, Education and Welfare (DHEW) Publication No. (FDA) Food Service Sanitation Manual. Superintendent of Documents, U.S. Government Printing Office, Washington, DC ] [(3) American Society of Heating, Refrigerating and Air-Conditioning Engineers, Inc. (ASHRAE) Standard No. [ ] Testing Air-Cleaning Devices Used in General Ventilation for Removing Particulate Matter](1) ANSI/ASHRAE Standard , Method of Testing Air-Cleaning Devices for Removal Efficiency by Particle Size, 1999 edition. American Society of Heating, Refrigerating and Air-Conditioning Engineers, Inc., 1791 Tullie Circle NE, Atlanta, GA [(4) American Society of Heating, Refrigerating and Air-Conditioning Engineers (ASHRAE). Table for Climatic Conditions for the United States in the 1993 Handbook of Fundamentals. American Society of Heating, Refrigerating and Air-Conditioning Engineers, 1741 Tullie Circle, NE, Atlanta GA ] 1415 [(5) Department of Defense (DOD) Penetration Test Method, Military Standard No. 282 (1956 edition with 1995 amendments) Filter Units, Protective Clothing, Gas Mask Components and Related Produces: Performance Test Methods. Naval Publications and Form Center, 5801 Tabor Avenue, Philadelphia, PA ] [(6)](2) Compressed Gas Association, Inc. (CGA) Pamphlet [P ] E-10, [Recommendations for] Maintenance of Medical[-Surgical-]Gas and Vacuum Systems in Health Care Facilities, third edition, Compressed Gas Association, Inc., 4221 Walney Road, Chantilly, VA, , [(7)] (3) National Council on Radiation Protection and Measurements (NCRP) Report No. [33] 102- Medical X-Ray, Electron Beam and Gamma-Ray Protection for Energies Up to 50MeV (1989). National Council on Radiation Protection and Measurements, 7910 Woodmont Avenue, Bethesda, MD , [(8)] (4) National Council on Radiation Protection and Measurements (NCRP) Report No. [49] 147- Structural Shielding Design [and Evaluation] for Medical [Use of X-Rays] X-Ray Imaging Facilities [and Gamma Rays of Energies Up to 10 MeV (1976)], 2004 edition. National Council on Radiation Protection and Measurements, [P.O. Box 30175, Washington, DC 20014] 7910 Woodmont Avenue, Bethesda, MD , [(9)] (5) National Council on Radiation Protection and Measurements (NCRP) Report No. [51] 144- Radiation Protection [Design Guidelines] for [ MeV] Particle Accelerator Facilities [(1977)], 2003 edition. National Council on Radiation Protection and Measurements, [P.O. Box 30175, Washington, DC 20014] 7910 Woodmont Avenue, Bethesda, MD , 1516 [(10)] (6) Guidelines for Design and Construction of Hospital and Health Care Facilities, 1996 edition. The American Institute of Architects Academy of Architecture for Health, with assistance from the U.S. Department of Health and Human Services, the American Institute of Architects Press, 1735 New York Avenue, N.W., Washington, D.C The standards set forth in this paragraph are applicable to construction projects completed pursuant to Subparts and and other applicable provisions in this Chapter. Such projects must, at minimum, maintain compliance with these standards. (7) Guidelines for Design and Construction of Health Care Facilities, 2010 edition. The American Society for Healthcare Engineering, with assistance from the U.S. Department of Health and Human Services, One North Franklin Street, Chicago, Illinois, 60606, and at (c) Design standards for the disabled. The Americans with Disabilities Act of 1990 (ADA) extends comprehensive civil rights protection to persons with disabilities. Health care facilities must comply with the ADA and the regulations, which implement it. [(28 CFR Parts 35 and 36)] Title 28 of the Code of Federal regulations, Public Health Parts 35, Non-Discrimination on the Basis of Disability in State and Local Government Services, and Part 36, Non-Discrimination on the Basis of Disability by Public Accommodations and in Commercial Facilities, including Appendix A, Standard for Accessible Design, 2004 edition. These regulations are published by the Office of the Federal Register National Archives and Records Administration. Copies may be obtained from the Superintendent of Documents, United States Government Printing Office, Washington D.C17 Section of Part 711 is amended to read as follows: Section Site requirements. (a) [The site of any medical] Each health facility shall be easily accessible to patients or residents, staff and visitors [the community] and to service vehicles such as fire protection apparatus. Health facility grounds shall have paved roads and walkways to provide access to all public and service entrances, including loading docks. Emergency department entrances shall be conspicuously marked to facilitate access from public roads and streets. Access to emergency entrances shall not conflict with other vehicular or pedestrian traffic. (b) Health[F]facilities [should] shall be located with due regard to the accessibility by public transportation for patients, staff and visitors and the availability of competent medical and surgical consultation. [(c) Paved roads shall be provided within the lot lines to provide access to the main entrance, emergency entrance, entrances serving community activities and to service entrances, including loading and unloading docks for delivery trucks. Hospitals having an organized emergency services department shall have the emergency entrance well marked to facilitate entry from the public roads or streets serving the site. Access to the emergency entrance shall not conflict with other vehicular traffic or pedestrian traffic. Paved walkways shall be provided for pedestrian traffic.] [(d)] (c) Off-street parking shall be made available for patients, staff and visitors. [It is recognized that in urban areas where alternate means of transportation, by public carrier, may exist, compliance with this provision may not be possible, or necessary for functional operation of the facility, and may constitute a hardship in compliance. Where 1718 such hardship exists, and where acceptable alternate means of transportation are available, the commissioner may grant a waiver to the requirements of this subdivision.] In urban areas where a health facility is accessible by public transportation, the commissioner may waive the requirement for off-street parking, if compliance with this requirement is burdensome or unnecessary because adequate parking exists to accommodate patients, staff and visitors. [(e) Special design features for the people with disabilities (patients, staff and visitors) shall be provided for all buildings in accordance with section (c).] [(f)] (d) [In regions where local experience shows that earthquakes have caused loss of life or extensive property damage, buildings and structures shall be designed to withstand the force assumptions specified in the latest issue of International Conference of Building Officials uniform building code, and where applicable, the local authority having jurisdiction. In buildings which] In earthquake prone regions, health facilities that are subdivided into separate structural units by seismic joints, each unit shall be provided with an exit stairway to permit evacuation from the building without traversing the seismic joints. Special care shall be taken to anchor fixed equipment, suspended ceilings, light fixtures and similar items to minimize hazard to occupants and damage to the equipment and building during an earthquake. Storage shelves and racks holding breakable or fragile supplies shall be designed to retain their contents when subject to the lateral forces of an earthquake. [(g)] (e) [The commissioner may require a facility located in an area which may be subject to flooding, to a degree which could impair normal operation of the facility, to] If 1819 a health facility is located in a flood plain, the commissioner may require that the health facility comply with any, or all, of the following: (1) [The] Health facility footings, foundations, and structural frame shall be designed to be stable under flood conditions. (2) [An area on the roof shall be accessible to, designated for, and structurally designed to allow the impact loads for landing of a helicopter. Access suitable for patient evacuation from the patient floors to the helicopter landing area shall be provided.] A helicopter landing pad shall be located on the facility roof and shall be structurally sound and suitable for safe helicopter evacuations of patients and staff. (3) [Provision shall be made to insure that the following services will be operable when and] The health facility shall be designed and capable of providing services necessary to maintain the life and safety of patients and staff if floodwaters reach the one-hundred year flood crest level and shall include the following: (i) electrical service, emergency power supply, heating, ventilating and sterilizers, [for those areas necessary to maintain the life safety of patients]; (ii) main internal communication [panels such as] capability, including nurses' call systems and the fire alarm system; (iii) [the capability of communicating outside the facility independent of telephone service] dietary service; (iv) an acceptable alternate to the normal water supply system; (v) an acceptable emergency means of storage and/or disposal of sewage, biological waste, and garbage; (vi) emergency department service; and, 1920 (vii) [X-ray] x-ray service[; and (viii) dietary service]. (4) No floor level or basement shall be located below the 100-year flood crest level, unless specifically approved by the commissioner. On those floor levels or basements that the commissioner approves to be below the 100-year flood crest level: (i) all new partitions shall be constructed without void such as solid concrete, solid concrete block, or other solid material; (ii) no new carpeting shall be installed; and (iii) the following services and equipment shall not be provided or located in such area: (a) medical records storage area; (b) medical records library; (c) surgical suite; and (d) such other services and fixed equipment that the commissioner may determine, taking into consideration patient safety and cost of replacement. (5) Storage of available building plans of the existing buildings shall be above the 100- year flood crest level. Section of Part 711 is REPEALED and RESERVED. Section of Part 711 is REPEALED and RESERVED. Section of Part 711 is REPEALED and RESERVED. 20 View more
Nurses Station & Resident Call System PRE 1975: NEW YORK Downloaded 01.15.11 713 1.3 Nursing units. Each nursing unit shall include the following service areas and shall meet the following minimum requirements: More information R432. Health, Health Systems Improvement, Licensing. R432-5. Nursing Facility Construction. R432-5-1. Legal Authority. R432-5-2. Purpose.
R432. Health, Health Systems Improvement, Licensing. R432-5. Nursing Facility Construction. R432-5-1. Legal Authority. This rule is promulgated pursuant to Title 26, Chapter 21. R432-5-2. Purpose. The More information Page 1 of 6 COMPLIANCE CHECKLIST. > Long Term Care Facility - Nursing Unit
COMPLIANCE CHECKLIST Page 1 of 6 > Long Term Care Facility - Nursing Unit The following checklist is for plan review of new long-term care facilities and new additions to existing long-term care facilities. More information Page 1 of 5 COMPLIANCE CHECKLIST. > Hospice Inpatient Facility Nursing Care Unit
COMPLIANCE CHECKLIST Page 1 of 5 > Hospice Inpatient Facility Nursing Care Unit The following checklist is for plan review of hospice inpatient facilities. This checklist is derived from Section 105 CMR More information GUIDELINES IN THE PLANNING AND DESIGN OF A HOSPITAL AND OTHER HEALTH FACILITIES
A hospital and other health facilities shall be planned and designed to observe appropriate architectural practices, to meet prescribed functional programs, and to conform to applicable codes as part of More information Element D Services Plumbing
Medical Vacuum and Gas PART 1 - GENERAL 1.01 OVERVIEW A. This section addresses medical vacuum, waste anesthetic gas disposal, compressed air, oxygen, nitrous oxide, nitrogen and carbon dioxide systems. More information SECTION.3400 - MECHANICAL: ELECTRICAL: PLUMBING
SECTION.3400 - MECHANICAL: ELECTRICAL: PLUMBING 10A NCAC 13D.3401 HEATING AND AIR CONDITIONING Heating and cooling systems shall meet the American Society of Heating, Refrigerating, and Air Conditioning More information HEALTH FACILITY CHECKLIST SECTION 1226 [OSHPD 3] CLINICS 1226.6 PRIMARY CARE CLINICS
Compliance Checklist: [OSHPD 3] Primary Care Clinics Page 1 of 7 HEALTH FACILITY CHECKLIST SECTION 1226 [OSHPD 3] CLINICS 1226.6 PRIMARY CARE CLINICS Primary Care Clinics are Health Facilities licensed More information CHAPTER 4675 DEPARTMENT OF HEALTH OUTPATIENT SURGICAL CENTERS
1 4675.0100 DEFINITIONS. 4675.0200 LEGAL AUTHORITY. 4675.0300 LICENSURE. 4675.0400 ADMINISTRATION. 4675.0500 MEDICAL STAFF. 4675.0600 ADMINISTRATIVE AREAS. CHAPTER 4675 DEPARTMENT OF HEALTH OUTPATIENT More information Subpart 1. Installation. All plumbing systems must be. installed and tested according to this chapter and chapter 4715,
4658.4500 PLUMBING SYSTEMS; NEW CONSTRUCTION. Subpart 1. Installation. All plumbing systems must be installed and tested according to this chapter and chapter 4715, the Minnesota Plumbing Code. Subp. 2. More information Ch. 205 PLANT & EQUIPMENT STANDARDS 28 CHAPTER 205. PHYSICAL PLANT AND EQUIPMENT STANDARDS FOR LONG-TERM CARE NURSING FACILITIES
Ch. 205 PLANT & EQUIPMENT STANDARDS 28 CHAPTER 205. PHYSICAL PLANT AND EQUIPMENT STANDARDS FOR LONG-TERM CARE NURSING FACILITIES Sec. 205.1. Location or site. 205.2. Grounds. 205.3. [Reserved]. 205.4. More information TEXT (CO Detection Commercial Buildings Final) Part 1228 of Title 19 NYCRR is amended by adding a new section 1228.4, to read as follows:
TEXT (CO Detection Commercial Buildings Final) Part 1228 of Title 19 NYCRR is amended by adding a new section 1228.4, to read as follows: Section 1228.4. Carbon Monoxide Detection in Commercial Buildings More information Effective June 27, 2015. TEXT (CO Detection Commercial Buildings)
TEXT (CO Detection Commercial Buildings) Part 1228 of Title 19 NYCRR is amended by adding a new section 1228.4, to read as follows: Section 1228.4. Carbon Monoxide Detection in Commercial Buildings (a) More information General Fire Code Requirements Within Commercial Tenant Spaces
FIRE DEPARTMENT in cooperation with Scope: General Fire Code Requirements Within Commercial Tenant Spaces This handout is designed to assist owners, architects, contractors and others in understanding More information FIRE AND LIFE SAFETY REQUIREMENTS FOR CONVENTIONS, TRADE SHOWS AND EXHIBITS November 2011
FIRE AND LIFE SAFETY REQUIREMENTS FOR CONVENTIONS, TRADE SHOWS AND EXHIBITS November 2011 COLORADO SPRINGS FIRE DEPARTMENT Division of the Fire Marshal If you have any questions or comments regarding the More information Operating Room Requirements for 2014 and Beyond
2014 FGI Guidelines Update Series FGI Guidelines Update #3 September 15, 2014 Operating Room Requirements for 2014 and Beyond Byron Burlingame, MS, RN, CNOR A comparison of the inpatient surgery section More information 527 CMR: BOARD OF FIRE PREVENTION REGULATIONS
527 CMR 31.00: CARBON MONOXIDE ALARMS Section 31.01: Purpose and Scope 31.02: Definitions 31.03: General Installation Provisions 31.04: Specific Installation Provisions 31.05: Carbon Monoxide Protection: More information Georgia State Amendments to the International Mechanical Code (2012 Edition)
Georgia State Amendments to the International Mechanical Code (2012 Edition) Georgia Department of Community Affairs Community Development Division 60 Executive Park South, N.E. Atlanta, Georgia 30329-2231 More information FIRE AND LIFE SAFETY REQUIREMENTS FOR CONVENTIONS, TRADE SHOWS AND EXHIBITS
FIRE AND LIFE SAFETY REQUIREMENTS FOR CONVENTIONS, TRADE SHOWS AND EXHIBITS November 2011, Updated March 2012 COLORADO SPRINGS FIRE DEPARTMENT Division of the Fire Marshal If you have any questions or More information NEW YORK. Downloaded 01.15.11. Title: Section 713 1.6 Nutrition and dining services 713 1.6 Nutrition and dining services.
NEW YORK Downloaded 01.15.11 Dining/Lounge Area PRE 1975: Title: Section 713 1.6 Nutrition and dining services 713 1.6 Nutrition and dining services. (a) A nursing home shall have at least one room of More information SECTION THREE CONSTRUCTION CODES
SECTION THREE CONSTRUCTION CODES CHAPTER 36: Construction Codes in Michigan Purpose and Applicability of Regulations Manufacturing facilities and other businesses must be designed according to code in More information BY-LAW CONCERNING THE SANITATION AND MAINTENANCE OF DWELLING UNITS
A/E REVIEW CHECKLIST ARCHITECTURAL Reviewers should - Use Checklists when reviewing any type of VA construction project for the following disciplines: Architectural, Boiler Safety Devices Operation Checklist, More information SUBPART 713-1 STANDARDS OF CONSTRUCTION FOR NEW EXISTING NURSING HOMES (Statutory authority: Public Health Law, Section 2803)
NEW YORK SUBPART 713-1 STANDARDS OF CONSTRUCTION FOR NEW EXISTING NURSING HOMES (Statutory authority: Public Health Law, Section 2803) Effective Date: 12/29/2010 Title: Section 713-1.1 - Applicability More information FIRE SAFETY SELF-INSPECTION FORM FOR CULTURAL INSTITUTIONS. 1. All Floors (inspect from top floor to basement): Yes No
General Inspection FIRE SAFETY SELF-INSPECTION FORM FOR CULTURAL INSTITUTIONS 1. All Floors (inspect from top floor to basement): Yes are fire exits and directional signs properly illuminated? is the emergency More information BUILDING INSPECTORS INSPECTION FORM FOR CHILD CARE CENTERS
DCD-0304 Identification # Rev. 9/08 County Date of Inspection NAME OF OPERATION BUILDING INSPECTORS INSPECTION FORM FOR CHILD CARE CENTERS ADDRESS TELEPHONE: CITY STATE ZIP BUILDING INSPECTORS CERTIFICATE More information CHAPTER HALFWAY HOUSES, HOSTELS, GROUP HOMES
CHAPTER 33-14-05 HALFWAY HOUSES, HOSTELS, GROUP HOMES Section 33-14-05-01 Standards for Administration 33-14-05-02 Staff 33-14-05-03 Recreational Activities 33-14-05-04 Maintenance 33-14-05-05 Resident More information Safety, Health and Accessibility Design Guidelines For Architects, Engineers and Design Firms
Safety, Health and Accessibility Design Guidelines For Architects, Engineers and Design Firms U.S. Department of the Interior Bureau of Indian Affairs Division of Safety and Risk Management Introduction More information Health Chapter 420-5-22 ALABAMA STATE BOARD OF HEALTH ALABAMA DEPARTMENT OF PUBLIC HEALTH ADMINISTRATIVE CODE
Health Chapter 420-5-22 ALABAMA STATE BOARD OF HEALTH ALABAMA DEPARTMENT OF PUBLIC HEALTH ADMINISTRATIVE CODE CHAPTER 420-5-22 SUBMISSION OF PLANS AND SPECIFICATIONS FOR HEALTH CARE FACILITIES TABLE OF More information NEW YORK. Downloaded 01.15.11
Housekeeping/Laundry/Maintenance PRE 1975: NEW YORK Downloaded 01.15.11 (d) At least one janitor's closet shall be provided in each facility. 1975 1990: (a) If linen is to be processed on the site, the More information Upper Southampton Township Department of Licenses and Inspections 939 Street Rd. Southampton, Pa. 18966 Phone: 215-322-9700 Fax: 215-322-5842
Upper Southampton Township Department of Licenses and Inspections 939 Street Rd. Southampton, Pa. 18966 Phone: 215-322-9700 Fax: 215-322-5842 APPLICATION for ZONING and BUILDING PERMIT APPLICATION INSTRUCTIONS: More information ALBERTA FIRE CODE SAFETY EQUIPMENT MAINTENANCE REQUIREMENTS
ALBERTA FIRE CODE SAFETY EQUIPMENT MAINTENANCE REQUIREMENTS In this document are the fire safety equipment maintenance requirements that are found in Division B of the Alberta Fire Code (AFC 2006) for More information FINAL EXPRESS TERMS FOR PROPOSED BUILDING STANDARDS OF THE OFFICE OF STATEWIDE HEALTH PLANNING AND DEVELOPMENT
FINAL EXPRESS TERMS FOR PROPOSED BUILDING STANDARDS OF THE OFFICE OF STATEWIDE HEALTH PLANNING AND DEVELOPMENT REGARDING PROPOSED CHANGES TO CALIFORNIA PLUMBING CODE CALIFORNIA CODE OF REGULATIONS, TITLE More information NEW YORK CITY FIRE DEPARTMENT. Notice of Public Hearing and Opportunity to Comment on Proposed Rules
NEW YORK CITY FIRE DEPARTMENT Notice of Public Hearing and Opportunity to Comment on Proposed Rules What are we proposing? The Fire Department is proposing to amend two rules. One relates to Fire Department More information FIRE SAFETY SELF-INSPECTION FORM FOR CULTURAL INSTITUTIONS
FIRE SAFETY SELF-INSPECTION FORM FOR CULTURAL INSTITUTIONS The attached self-inspection form is intended for staff use at regular, frequent intervals. It should not take the place of two other vital measures More information Inspection Item COMMENTS
APPENDIX 9 AFFORDABLE HOUSING PROGRAM INSPECTION CHECKLIST Participating Jurisdiction: Homeowner Name: Assisted Property Address: Date of Physical Inspection of Property: Total Square Footage of Property: More information Ethanol Vehicle and Infrastructure Codes and Standards Citations
Ethanol Vehicle and Infrastructure Codes and Standards Citations This document lists codes and standards typically used for U.S. ethanol vehicle and infrastructure projects. To determine which codes and More information RULES OF DEPARTMENT OF COMMUNITY HEALTH HEALTHCARE FACILITY REGULATION DIVISION REVISE CHAPTER 111-8-40 RULES AND REGULATIONS FOR HOSPITALS
RULES OF DEPARTMENT OF COMMUNITY HEALTH HEALTHCARE FACILITY REGULATION DIVISION REVISE CHAPTER 111-8-40 RULES AND REGULATIONS FOR HOSPITALS SYNOPSIS OF PROPOSED RULE CHANGES STATEMENT OF PURPOSE: The Department More information 2. What building projects are exempted? (permit not required)
BUILDING AND SAFETY DEPARTMENT 1. What building projects require a permit? Following is a list of projects that require building permits based on Appendix chapter 1 of the California Building Code and More information Minimum Housing and Health Standards
APPENDIX M.O. 57/2012 Minimum Housing and Health Standards Original version July 20, 1999. Revisions to Part lll, Housing Premises, sections 3 and 4, June 30, 2012 (all revisions are bolded and underlined). More information General Safety & Health Standards Published by the Division of Building Safety In Cooperation with the Idaho Industrial Commission
General Safety & Health Standards Published by the Division of Building Safety In Cooperation with the Idaho Industrial Commission Local Fire Alarm 064. FIRE ALARM SYSTEMS 01. Scope 02. Definitions 03. More information Ontario Fire Code SECTION 5.13 DIP TANKS. Illustrated Commentary. Office of the Ontario Fire Marshal
Ontario Fire Code SECTION 5.13 DIP TANKS Illustrated Commentary Office of the Ontario Fire Marshal Dip Tanks Illustrated Commentary 1 5.13.1. Location 5.13.1.1. Dip tank operations involving flammable More information ZONE STANDARDS RV PARKS RV
ZONE STANDARDS RV PARKS RV Chapter 13 Recreational Vehicle Parks 13.1 PURPOSE 13.2 DESIGN STANDARDS 13.3 ESTABLISHMENT OF RV PARK 13.4 APPLICATION REQUIREMENTS AND PROCEDURES 13.5 LANDSCAPING AND OPEN More information The Johns Hopkins Hospital and The Johns Hopkins University Health, Safety and Environment Manual Fire Safety:
Page 1 of 10 Keywords: Emergency Room, Evacuation, Evacuation Plans, Fire, Fire Incident Responsibilities, Fire Safety, Gas Shutoff, Inpatient Area, Intensive Care, JHH Fire Incident Responsibilities, More information The Commonwealth of Massachusetts Executive Office of Public Safety Department of Fire Services
MITT ROMNEY GOVERNOR KERRY HEALEY LT. GOVERNOR EDWARD A. FLYNN SECRETARY The Commonwealth of Massachusetts Executive Office of Public Safety Department of Fire Services P.O. Box 1025 State Road Stow, Massachusetts More information CHAPTER 150: BUILDING REGULATIONS. Adoption of Regulatory Codes by Reference
CHAPTER 150: BUILDING REGULATIONS Section Adoption of Regulatory Codes by Reference 150.01 Scope 150.02 Commercial Construction Code 150.03 Commercial Plumbing Code 150.04 Heating, Air Conditioning, Refrigeration More information City of Elk River BASEMENT Office Use Only
City of Elk River BASEMENT Office Use Only Fire and Building Safety Division (FABS) Building Permit Application Notes Scan Permit Total Date Permit # PID # $ Site Address Suite/Unit Structure Type Single More information CONSTRUCTION FIRE SAFETY PLANNING GUIDELINES
CONSTRUCTION FIRE SAFETY PLANNING GUIDELINES Review the following information pertaining to Construction Fire Safety Planning: B.C. Building Code Sections 8.1 up to and including Subsection 8.2.3 B.C. More information State of Arizona Administrative Code TITLE 9. HEALTH SERVICES CHAPTER 10. DEPARTMENT OF HEALTH SERVICES HEALTH CARE INSTITUTIONS: LICENSING
State of Arizona Administrative Code TITLE 9. HEALTH SERVICES CHAPTER 10. DEPARTMENT OF HEALTH SERVICES HEALTH CARE INSTITUTIONS: LICENSING Supp. 05-2 Editor's Note: The heading for 9 A.A.C. 10 changed More information RHODE ISLAND. Downloaded 01.15.11
Housekeeping/Laundry/Maintenance Section 35.0 Housekeeping RHODE ISLAND Downloaded 01.15.11 35.1 A full time employee of the facility shall be designated responsible for housekeeping services, supervision More information Arizona Health Care Association DISASTER PLANNING AND EMERGENCY MANAGEMENT GUIDE POST INCIDENT DAMAGE ASSESSMENT CHECKLIST
It is essential to perform a Basic Damage Assessment (BDA) following an adverse event to help ensure the safety of building occupants as well as prevent additional losses from occurring. This checklist More information PLAN REVIEW AND APPROVAL FOR FOOD ESTABLISHMENTS PLUMBING REQUIREMENTS FOR FOOD ESTABLISHMENT PREMISES
PLAN REVIEW AND APPROVAL FOR FOOD ESTABLISHMENTS PLUMBING REQUIREMENTS FOR FOOD ESTABLISHMENT PREMISES Health Systems Protection Rev. 07/2006 35-05-20/06/07/18 OFFICE OF FOOD PROTECTION 417 FEDERAL ST More information SOUTH CAROLINA. Downloaded January 2011
SOUTH CAROLINA Downloaded January 2011 1401. General (II) B. When meals are catered to a facility, such meals shall be obtained from a meal service establishment graded by the Department, pursuant to R.61 More information TYPICAL FIRE SAFETY INSPECTION VIOLATIONS
TYPICAL FIRE SAFETY INSPECTION VIOLATIONS The following is a list of typical violations often found by inspectors and a generic solution. You can use this list to improve the safety of your facility, to More information What to Expect From the Examination. How to Study the Plumbing Codes
Texas State Board of Plumbing Examiners Plumbing Inspector Examination Review Course The following Examination Review Course is designed to assist an applicant in preparing for the Plumbing Inspector examination. More information RULES AND REGULATIONS FOR LICENSURE OF RENAL DIALYSIS CENTERS
RULES AND REGULATIONS FOR LICENSURE OF RENAL DIALYSIS CENTERS CHAPTER 18 Section 1. Authority. These rules are promulgated by the Department of Health pursuant to the Health Facilities Licensure Act at More information Winnipeg Fire Department Fire Prevention Branch
Winnipeg Fire Department Fire Prevention Branch Manitoba Fire Code Life-Safety Equipment Maintenance Requirements The Fire Prevention Branch of the Winnipeg Fire Department has prepared this document of More information Control filling, grading, dredging, and other development which may increase erosion or flood damage; and
ARTICLE 16. FLOOD DAMAGE PREVENTION Section 16-1: Findings of Fact The flood hazard areas of the Town of Lillington are subject to periodic inundation which results in loss of life and property, health More information PUBLIC RESTROOMS, DESIGN INTENT
PUBLIC RESTROOMS, DESIGN INTENT 1.01 STRUCTURAL A. Where feasible, metal stud partitions will be constructed on a 6 high concrete curb. 1.02 MECHANICAL A. Restrooms will have a minimum of 15 air changes More information Applications for building permits will not be reviewed until all of the required information has been submitted.
NOTICE: Applications for building permits will not be reviewed until all of the required information has been submitted. Once all items are submitted a minimum of ten (10) working days are required to More information Chapter 20 TRAILER COACHES AND TRAILER COACH PARKS* ARTICLE I. IN GENERAL
Chapter 20 TRAILER COACHES AND TRAILER COACH PARKS* Art. Art. I. In General II. Trailer Coach Parks Div. 1. Generally Div. 2. Facilities Requirements Generally Div. 3. Facilities for Transient Trailer More information COMMERCIAL PLAN SUBMISSION FOR NEW CONSTRUCTION AND/OR RENOVATIONS
COMMERCIAL PLAN SUBMISSION FOR NEW CONSTRUCTION AND/OR RENOVATIONS Permit applicants shall submit three (3) COMPLETE SETS of plans and specifications with each application for a permit. Plans and specifications More information APPLICATION FOR NEW CONSTRUCTION
CITY OF ELKINS 401 DAVIS AVE ELKINS WV 26241 Date Pd: Receipt #: Session #: PHIL ISNER BLDG INSPECTOR / CODE ENFORCEMENT OFFICER 304-636-1414 Ext 1431 APP. DATE APPLICATION FOR NEW CONSTRUCTION APPLICANT More information Electrical Contractors. and the. New Jersey. Rehabilitation Code
Electrical Contractors and the New Jersey Rehabilitation Code Alan Chech Electrical Seminars 609-890-7072 www.alanchech.com Information is based on the presently adopted electrical subcode NEC 2005. Current More information PLAN SUBMITTAL REQUIREMENTS FOR SPRAY BOOTHS AND SPRAYING ROOMS EXTINGUISHING SYSTEMS
January 1997 PLAN SUBMITTAL REQUIREMENTS FOR SPRAY BOOTHS AND SPRAYING ROOMS EXTINGUISHING SYSTEMS 1.0 PERMIT 1.1 After receipt of a Building Permit from the City of San Jose Building Department, submit More information Ch. 151 FIRE, SAFETY, DISASTER SERVICES 28 CHAPTER 151. FIRE, SAFETY AND DISASTER SERVICES GENERAL PROVISIONS INTERNAL DISASTER PLAN
Ch. 151 FIRE, SAFETY, DISASTER SERVICES 28 CHAPTER 151. FIRE, SAFETY AND DISASTER SERVICES Sec. 151.1. Principle. 151.2. Policies and procedures. GENERAL PROVISIONS 151.11. Fire fighting service. 151.12. More information MP 5.7 RESIDENTIAL SERVICES BUILDING STANDARD
MP 5.7 RESIDENTIAL SERVICES BUILDING STANDARD Index Purpose... 3 Commencement.3 Application...3 Compliance..3 Associated Requirements... 3 Definitions... 4 Kitchen Facilities... 6 Laundry Facilities... More information Vestibule Case Study. Vestibule Requirement Intent [2003 IECC, 2006 IECC, 2003 IBC, 2006 IBC, 90.1-2001, 90.1-2004]
Vestibule Case Study [2003 IECC, 2006 IECC, 2003 IBC, 2006 IBC, 90.1-2001, 90.1-2004] Vestibule Requirement Intent Page 1 of 14 The primary intent behind the requirement for a vestibule is to reduce infiltration More information Element D Services Plumbing
Laboratory Vacuum and Gas PART 1 - GENERAL 1.01 OVERVIEW A. This section addresses laboratory vacuum, compressed air, gaseous nitrogen, and carbon dioxide systems within and to five feet beyond building More information Standards Revisions Related to the Centers for Medicare & Medicaid Services CoPs
Standards Revisions Related to the Centers for Medicare & Medicaid Services CoPs EC.003.01 The hospital manages fire risks. 9. 10. Elements of Performance for EC.003.01 The hospital minimizes the potential More information Rhode Island State Fire Marshal Fire Protection Systems Narrative Reports. What is a Narrative Report?
RHODE ISLAND DIVISION OF STATE FIRE MARSHAL 1951 Smith Street, North Providence, RI 02911 Telephone: (401) 383-7717 Fax: (401) 383-8879 John E. Chartier, EFO, CFI State Fire Marshal Rhode Island State More information Land Use and Environmental Service Agency (Code Enforcement) NC Plumbing Code. Table of Contents
Chapter 1 Administration Chapter 3 General Regulations Chapter 5 Water Heaters Chapter 7 Sanitary Drainage Chapter 9 Vents Chapter 11 Storm Drainage Policy Statements Table of Contents Chapter 2 Definitions More information SPECIFICATIONS FOR APPROVED OFFSITE RECORDS STORAGE FACILITIES
1. Bonding and Insurance 2. Facilities (including equipment and materiel e.g., shelving, pallets, containers and other internal fixtures and contents) The storage facility company must be bonded and insured. More information Decree of the Ministry of the Environment. on fire safety of garages
E4 THE NATIONAL BUILDING CODE OF FINLAND Fire safety of garages Guidelines 2005 Decree of the Ministry of the Environment on fire safety of garages Adopted in Helsinki, 22 March 2005 Pursuant to the Decision More information TITLE 16 HEALTH & SOCIAL SERVICES DELAWARE ADMINISTRATIVE CODE 4400 Health Systems Protection. 4404 Free Standing Emergency Centers
4400 Health Systems Protection 1 4404 Free Standing Emergency Centers 1.0 Definitions "Free Standing Emergency Center" means a facility physically separate from a hospital, which uses in it's title or More information SECTION FC 2706 NON-PRODUCTION CHEMICAL LABORATORIES
New York City Administrative Code - Title 29 New York City Fire Code SECTION FC 2706 NON-PRODUCTION CHEMICAL LABORATORIES 2706.1 Scope. This section shall govern the storage, handling and use of laboratory More information Appendix B. 2010 Florida Building Code Building Section 423.25 Public Shelter Design Criteria
Appendix B 2010 Florida Building Code Building Section 423.25 Public Shelter Design Criteria 423.25 Public shelter design criteria. 423.25.1 New facilities. New educational facilities for school boards More information WHITE PLAINS PLUMBING CODE PART 1. GENERAL REQUIREMENTS
WHITE PLAINS PLUMBING CODE PART 1. GENERAL REQUIREMENTS a. New Plumbing and Gas Piping Systems. This code in conjunction with the Plumbing and Fuel Gas Codes of the State of New York shall apply to plumbing More information Water should be removed as soon as possible once the safety of the structure has been verified.
FACT SHEET Posted October 18 2005 Check List for Infection Control Concerns when Reopening Healthcare Facilities Closed due to Extensive Water and Wind Damage Prior to opening a healthcare facility that More information Orange County Residential Code Compliance Significant Changes to the 5th Edition 2014 Florida Building Code
1 RESIDENTIAL Screen Enclosures Orange County Residential Code Compliance Alternative design method for screen enclosures R301.2.1.1.3 PLAN REVIEW Engineered plans must state that the Alternative Design More information ADA Scoping: New Construction
U. S. A CCESS B O A R D T E C H N I C A L G U I D E ADA Scoping: This guide provides an introduction to the scoping requirements that form the basis for the Department of Justice s 2010 ADA Standards and More information CHAPTER 7 BUILDING ARTICLE 7-1 UNIFORM CODES 1. 7-1-1 Adoption. Board of Appeals. Annual Review
CHAPTER 7 BUILDING ARTICLE 7-1 UNIFORM CODES 1 7-1-1 Adoption 7-1-2 Board of Appeals 7-1-3 Annual Review Section 7-1-1 Adoption A. Those certain documents known as the 1997 Uniform Building Code, Volumes More information Article 11 Laundry and Dry Cleaning
Article 11 Laundry and Dry Cleaning 41101. General Provisions. 41102. Construction Permit. 41103. Sanitary Permit. 41104. Materials and Construction of Physical Facilities. 41105. Sanitary Facilities Plumbing. More information Educational. Educational-Existing 1/28/2014. OCCUPANT LOADS [no change] Application. Application
February 2014 Code Requirements and Inspections in Educational Occupancies Presented By: Barry W. Rickert Douglas M. Schanne Fire Marshal Training Program Supervisor Office of Education & Data Management More information ALVERNIA UNIVERSITY OSHA REGULATION: 29 CFR 1910.252 WELDING, CUTTING, AND BRAZING ( HOT WORK ) SECTION: 3600
OSHA REGULATION: 9 CFR 90.5 WELDING, CUTTING, AND BRAZING ( HOT WORK ) A. POLICY. This procedure follows requirements set forth in 9 CFR 90.5.. This policy applies to all Hot Work operations being done More information Element D Services Plumbing
PART 1 - GENERAL 1.01 OVERVIEW A. This section addresses domestic cold, hot and hot water return distribution systems within and to five feet beyond building perimeter. PART 2 - DESIGN CRITERIA 2.01 GENERAL More information Ventilation Standard For Health Care Facilities
The following article was published in ASHRAE Journal, October 2008. Copyright 2008 American Society of Heating, Refrigerating and Air- Conditioning Engineers, Inc. It is presented for educational purposes More information FACILITY FIRE PREVENTION AND EMERGENCY PREPAREDNESS INSPECTION CHECKLIST
FACILITY FIRE PREVENTION AND EMERGENCY PREPAREDNESS INSPECTION CHECKLIST Date of Inspection: Conducted by: Location: Reviewed by: Date of Review: Comments or additional corrective action taken as a result More information Errata NFPA 1. Fire Code. 2015 Edition
Errata NFPA 1 Fire Code 2015 Edition Reference: 2.2, Table 6.1.14.4.1(a) and (b), 13.3.1.6, 13.7.2.13.2.1, 14.11.3.3, 18.5.2, 18.5.3, 20.1.2, 20.1.5.12, 25.1.1, 25.3, 25.4, A.3.3.164.2, and A.13.3.2.9.1 More information STATUTORY AUTHORITY: KRS 216B.042, 216B.105, 216B.455, 216B.457 (21)
902 KAR 20:330. Psychiatric residential treatment facilities. RELATES TO: KRS 216B.105, 216B.450-216B.457 STATUTORY AUTHORITY: KRS 216B.042, 216B.105, 216B.455, 216B.457 (21) NECESSITY, FUNCTION, AND CONFORMITY: More information c. As mandated by law, facilities must obtain and maintain valid zoning permits as well as permits for intended use.
Walmart Standards for Suppliers Section 7. Health and Safety 7. Health and Safety Suppliers must provide workers with a safe and healthy work environment. Suppliers must take proactive measures to prevent More information FLOOD DAMAGE PREVENTION ORDINANCE
FLOOD DAMAGE PREVENTION ORDINANCE SECTION 1.0 STATUTORY AUTHORIZATION, FINDINGS FO FACT, PURPOSE, AND OBJECTIVES 1.1 STATUTORY AUTHORIZATION The Legislature of the State of Washington has in RCW delegated More information DESIGN GUIDELINES FOR SUBSTANTIAL REHABILITATION.
1 DESIGN GUIDELINES FOR SUBSTANTIAL REHABILITATION. I. APPLICABILITY OF GUIDELINES. The design guidelines apply to the rehabilitation of multi-family buildings, subject to H.P.D. review and approval. The More information MP 5.5 PRIVATE HEALTH FACILITIES
MP 5.5 PRIVATE HEALTH FACILITIES Index Purpose... 3 Commencement.3 Application... 3 Referral Agency... 3 Associated Requirements... 4 Referenced Stards... 4 Definitions... 4 General Requirements... 7 Functionality... More information MINNESOTA HEALTH CARE ENGINEERS IN ASSISTED LIVING FACILITIES
MINNESOTA HEALTH CARE ENGINEERS FIRE/LIFE SAFETY IN ASSISTED LIVING FACILITIES September 13, 2012 MINNESOTA HEALTH CARE ENGINEERS FIRE/LIFE SAFETY IN ASSISTED LIVING FACILITIES WELCOME Exits Restrooms More information Georgia State Amendments to the International Plumbing Code
Georgia State Amendments to the International Plumbing Code (2006 Edition) Georgia Department of Community Affairs Local Government Assistance Division 60 Executive Park South, N.E. Atlanta, Georgia 30329-2231 More information NEBRASKA HEALTH AND HUMAN SERVICES REGULATION AND LICENSURE 175 HEALTH CARE FACILITIES AND SERVICES LICENSURE
NEBRASKA HEALTH AND HUMAN SERVICES REGULATION AND LICENSURE 175 HEALTH CARE FACILITIES AND SERVICES LICENSURE CHAPTER 12 SKILLED NURSING FACILITIES, NURSING FACILITIES, AND INTERMEDIATE CARE FACILITIES More information FLAMMABLE AND COMBUSTIBLE LIQUIDS. n OSHA Changes
FLAMMABLE AND COMBUSTIBLE LIQUIDS OSHA Changes Introduction This module covers the two primary hazards associated with flammable and combustible liquids: explosion and fire. In order to prevent these hazards, More information We hope these Frequently Asked Questions will be of use both to municipal officials and fire inspectors.
September 14, 2012 Dear AMM Member: Please see the attached Fire Code Frequently Asked Questions. This document was compiled by the Office of the Fire Commissioner at the AMM s request to help clarify More information CHAPTER 4 VENTILATION
CHAPTER 4 VENTILATION SECTION 401 GENERAL 401.1 Scope. This chapter, in conjunction with the building code, shall govern the ventilation of spaces within a building intended to be occupied. Mechanical More information 2016 © DocPlayer.net Privacy Policy | Terms of Service | Feedback