Source: http://docplayer.nl/96969983-Nederlandse-norm-nen-iec-en.html
Timestamp: 2018-10-18 21:07:08
Document Index: 478465093

Matched Legal Cases: ['art 1', 'art 1', 'art 1', 'art 1', 'art 2', 'art 1', 'art 3', 'art 3']

Nederlandse norm NEN-IEC (en) - PDF
Nederlandse norm NEN-IEC (en)
Download "Nederlandse norm NEN-IEC (en)"
1 Dit document mag slechts op een stand-alone PC worden geinstalleerd. Gebruik op een netwerk is alleen. toestaan als een aanvullende licentieovereenkomst voor netwerkgebruik met NEN is afgesloten. This document may only be used on a stand-alone PC. Use in a network is only permitted when a supplementary license agreement for us in a network with NEN has been concluded. Nederlandse norm NEN-IEC (en) Kabels voor sterkstroom - Berekening van de toelaatbare stroom - Deel 1-1: Berekeningsmethode voor de continu toelaatbare stroom en voor de verliezen - Algemeen (IEC :2006,IDT) Electric cables - Calculation of the current rating - Part 1: Current rating equations (100% load factor) and calculation of losses - General (IEC :2006,IDT) Vervangt NEN-IEC :1995/A2:2001; NEN :1995; NEN :1995/A1:1996 ICS januari 2007
2 NEN-IEC Als Nederlandse norm is aanvaard: - IEC :2006,IDT Nederlands Elektrotechnisch Comité (NEC) Normcommissie "Draad en kabel voor elektrische sterkstroominstallaties (NEC 20)" Apart from exceptions provided by the law, nothing from this publication may be duplicated and/or published by means of photocopy, microfilm, storage in computer files or otherwise, which also applies to full or partial processing, without the written consent of the Netherlands Standardization Institute. The Netherlands Standardization Institute shall, with the exclusion of any other beneficiary, collect payments owed by third parties for duplication and/or act in and out of law, where this authority is not transferred or falls by right to the Reproduction Rights Foundation. Auteursrecht voorbehouden. Behoudens uitzondering door de wet gesteld mag zonder schriftelijke toestemming van het Nederlands Normalisatie-instituut niets uit deze uitgave worden verveelvoudigd en/of openbaar gemaakt door middel van fotokopie, microfilm, opslag in computerbestanden of anderszins, hetgeen ook van toepassing is op gehele of gedeeltelijke bewerking. Het Nederlands Normalisatie-instituut is met uitsluiting van ieder ander gerechtigd de door derden verschuldigde vergoedingen voor verveelvoudiging te innen en/of daartoe in en buiten rechte op te treden, voor zover deze bevoegdheid niet is overgedragen c.q. rechtens toekomt aan de Stichting Reprorecht. Although the utmost care has been taken with this publication, errors and omissions cannot be entirely excluded. The Netherlands Standardization Institute and/or the members of the committees therefore accept no liability, not even for direct or indirect damage, occurring due to or in relation with the application of publications issued by the Netherlands Standardization Institute. Hoewel bij deze uitgave de uiterste zorg is nagestreefd, kunnen fouten en onvolledigheden niet geheel worden uitgesloten. Het Nederlands Normalisatie-instituut en/of de leden van de commissies aanvaarden derhalve geen enkele aansprakelijkheid, ook niet voor directe of indirecte schade, ontstaan door of verband houdend met toepassing van door het Nederlands Normalisatie-instituut gepubliceerde uitgaven Nederlands Normalisatie-instituut Postbus 5059, 2600 GB Delft Telefoon (015) , Fax (015)
3 INTERNATIONAL STANDARD IEC Second edition Electric cables Calculation of the current rating Part 1-1: Current rating equations (100 % load factor) and calculation of losses General This English-language version is derived from the original bilingual publication by leaving out all French-language pages. Missing page numbers correspond to the Frenchlanguage pages. Reference number IEC :2006(E)
4 Publication numbering As from 1 January 1997 all IEC publications are issued with a designation in the series. For example, IEC 34-1 is now referred to as IEC Consolidated editions The IEC is now publishing consolidated versions of its publications. For example, edition numbers 1.0, 1.1 and 1.2 refer, respectively, to the base publication, the base publication incorporating amendment 1 and the base publication incorporating amendments 1 and 2. Further information on IEC publications The technical content of IEC publications is kept under constant review by the IEC, thus ensuring that the content reflects current technology. Information relating to this publication, including its validity, is available in the IEC Catalogue of publications (see below) in addition to new editions, amendments and corrigenda. Information on the subjects under consideration and work in progress undertaken by the technical committee which has prepared this publication, as well as the list of publications issued, is also available from the following: IEC Web Site ( Catalogue of IEC publications The on-line catalogue on the IEC web site ( enables you to search by a variety of criteria including text searches, technical committees and date of publication. On-line information is also available on recently issued publications, withdrawn and replaced publications, as well as corrigenda. IEC Just Published This summary of recently issued publications ( justpub) is also available by . Please contact the Customer Service Centre (see below) for further information. Customer Service Centre If you have any questions regarding this publication or need further assistance, please contact the Customer Service Centre: Tel: Fax:
5 INTERNATIONAL STANDARD IEC Second edition Electric cables Calculation of the current rating Part 1-1: Current rating equations (100 % load factor) and calculation of losses General IEC 2006 Copyright - all rights reserved No part of this publication may be reproduced or utilized in any form or by any means, electronic or mechanical, including photocopying and microfilm, without permission in writing from the publisher. International Electrotechnical Commission, 3, rue de Varembé, PO Box 131, CH-1211 Geneva 20, Switzerland Telephone: Telefax: Web: Commission Electrotechnique Internationale International Electrotechnical Commission PRICE CODE For price, see current catalogue V
6 IEC: CONTENTS FOREWORD...5 INTRODUCTION General Scope Normative references Symbols Permissible current rating of cables Calculation of losses AC resistance of conductor Dielectric losses (applicable to a.c. cables only) Loss factor for sheath and screen (applicable to power frequency a.c. cables only) Loss factor for armour, reinforcement and steel pipes (applicable to power frequency a.c. cables only)...49 Table 1 Electrical resistivities and temperature coefficients of metals used...59 Table 2 Skin and proximity effects Experimental values for the coefficients ks and kp...61 Table 3 Values of relative permittivity and loss factors for the insulation of highvoltage and medium-voltage cables at power frequency...63 Table 4 Absorption coefficient of solar radiation for cable surfaces...65
7 IEC: INTERNATIONAL ELECTROTECHNICAL COMMISSION ELECTRIC CABLES CALCULATION OF THE CURRENT RATING Part 1-1: Current rating equations (100 % load factor) and calculation of losses General FOREWORD 1) The International Electrotechnical Commission (IEC) is a worldwide organization for standardization comprising all national electrotechnical committees (IEC National Committees). The object of IEC is to promote international co-operation on all questions concerning standardization in the electrical and electronic fields. To this end and in addition to other activities, IEC publishes International Standards, Technical Specifications, Technical Reports, Publicly Available Specifications (PAS) and Guides (hereafter referred to as IEC Publication(s) ). Their preparation is entrusted to technical committees; any IEC National Committee interested in the subject dealt with may participate in this preparatory work. International, governmental and nongovernmental organizations liaising with the IEC also participate in this preparation. IEC collaborates closely with the International Organization for Standardization (ISO) in accordance with conditions determined by agreement between the two organizations. 2) The formal decisions or agreements of IEC on technical matters express, as nearly as possible, an international consensus of opinion on the relevant subjects since each technical committee has representation from all interested IEC National Committees. 3) IEC Publications have the form of recommendations for international use and are accepted by IEC National Committees in that sense. While all reasonable efforts are made to ensure that the technical content of IEC Publications is accurate, IEC cannot be held responsible for the way in which they are used or for any misinterpretation by any end user. 4) In order to promote international uniformity, IEC National Committees undertake to apply IEC Publications transparently to the maximum extent possible in their national and regional publications. Any divergence between any IEC Publication and the corresponding national or regional publication shall be clearly indicated in the latter. 5) IEC provides no marking procedure to indicate its approval and cannot be rendered responsible for any equipment declared to be in conformity with an IEC Publication. 6) All users should ensure that they have the latest edition of this publication. 7) No liability shall attach to IEC or its directors, employees, servants or agents including individual experts and members of its technical committees and IEC National Committees for any personal injury, property damage or other damage of any nature whatsoever, whether direct or indirect, or for costs (including legal fees) and expenses arising out of the publication, use of, or reliance upon, this IEC Publication or any other IEC Publications. 8) Attention is drawn to the Normative references cited in this publication. Use of the referenced publications is indispensable for the correct application of this publication. 9) Attention is drawn to the possibility that some of the elements of this IEC Publication may be the subject of patent rights. IEC shall not be held responsible for identifying any or all such patent rights. International Standard IEC has been prepared by IEC technical committee 20: Electric cables. This second edition cancels and replaces the first edition published in 1994, Amendment 1 (1995) and Amendment 2 (2001) The document 20/780/FDIS, circulated to the National Committees as Amendment 3, led to the publication of this new edition.
8 IEC: The text of this standard is based on the first edition, its Amendments 1 and 2, and the following documents: FDIS Report on voting 20/851/FDIS 20/867/RVD Full information on the voting for the approval of this standard can be found in the report on voting indicated in the above table. This publication has been drafted in accordance with the ISO/IEC Directives, Part 2. A list of all parts of the IEC series, published under the general title: Electric cables Calculation of the current rating, can be found on the IEC website. The committee has decided that the contents of this publication will remain unchanged until the maintenance result date indicated on the IEC web site under " in the data related to the specific publication. At this date, the publication will be reconfirmed, withdrawn, replaced by a revised edition, or amended.
9 IEC: INTRODUCTION This Part 1-1 contains formulae for the quantities R, W d, λ 1 and λ 2. It contains methods for calculating the permissible current rating of cables from details of the permissible temperature rise, conductor resistance, losses and thermal resistivities. Formulae for the calculation of losses are also given. The formulae in this standard contain quantities which vary with cable design and materials used. The values given in the tables are either internationally agreed, for example, electrical resistivities and resistance temperature coefficients, or are those which are generally accepted in practice, for example, thermal resistivities and permittivities of materials. In this latter category, some of the values given are not characteristic of the quality of new cables but are considered to apply to cables after a long period of use. In order that uniform and comparable results may be obtained, the current ratings should be calculated with the values given in this standard. However, where it is known with certainty that other values are more appropriate to the materials and design, then these may be used, and the corresponding current rating declared in addition, provided that the different values are quoted. Quantities related to the operating conditions of cables are liable to vary considerably from one country to another. For instance, with respect to the ambient temperature and soil thermal resistivity, the values are governed in various countries by different considerations. Superficial comparisons between the values used in the various countries may lead to erroneous conclusions if they are not based on common criteria: for example, there may be different expectations for the life of the cables, and in some countries design is based on maximum values of soil thermal resistivity, whereas in others average values are used. Particularly, in the case of soil thermal resistivity, it is well known that this quantity is very sensitive to soil moisture content and may vary significantly with time, depending on the soil type, the topographical and meteorological conditions, and the cable loading. The following procedure for choosing the values for the various parameters should, therefore, be adopted. Numerical values should preferably be based on results of suitable measurements. Often such results are already included in national specifications as recommended values, so that the calculation may be based on these values generally used in the country in question; a survey of such values is given in Part 3-1. A suggested list of the information required to select the appropriate type of cable is given in Part 3-1.
10 Bestelformulier Stuur naar: NEN Standards Products & Services t.a.v. afdeling Klantenservice Antwoordnummer WB Delft NEN Standards Products & Services Postbus GB Delft Vlinderweg AX Delft Ja, ik bestel ex. NEN-IEC :2007 en Kabels voor sterkstroom - Berekening van de toelaatbare stroom - Deel 1-1: Berekeningsmethode voor de continu toelaatbare stroom en voor de verliezen - Algemeen T (015) F (015) Wilt u deze norm in PDF-formaat? Deze bestelt u eenvoudig via Gratis nieuwsbrieven Wilt u op de hoogte blijven van de laatste ontwikkelingen op het gebied van normen, normalisatie en regelgeving? Neem dan een gratis abonnement op een van onze nieuwsbrieven. Gegevens Bedrijf / Instelling T.a.v. O M O V Klantnummer NEN Uw ordernummer BTW nummer Postbus / Adres Postcode Plaats Telefoon Fax Factuuradres (indien dit afwijkt van bovenstaand adres) Postbus / Adres Postcode Plaats Datum Handtekening Retourneren Fax: Post: NEN Standards Products & Services, t.a.v. afdeling Klantenservice Antwoordnummer 10214, 2600 WB Delft (geen postzegel nodig). Voorwaarden De prijzen zijn geldig tot 31 december 2018, tenzij anders aangegeven. Alle prijzen zijn excl. btw, verzend- en handelingskosten en onder voorbehoud bij o.m. ISO- en IEC-normen. Bestelt u via de normshop een pdf, dan betaalt u geen handeling en verzendkosten. Meer informatie: telefoon , dagelijks van 8.30 tot uur. Wijzigingen en typefouten in teksten en prijsinformatie voorbehouden. U kunt onze algemene voorwaarden terugvinden op: LEREN, WERKEN EN GROEIEN MET NEN preview