Source: https://shop.standards.govt.nz/default.htm?action=legislation&legid=162&mod=catalog
Timestamp: 2019-05-19 17:28:40
Document Index: 767831153

Matched Legal Cases: ['art 2', 'art 1', 'art 2', 'art 3', 'art 1', 'art 1', 'art 3', 'art 1', 'art 2', 'art 1', 'art 2', 'art 3', 'art 1', 'art 2', 'art 2']

Standards New Zealand :: Citations by Gas (Safety And Measurement) Regulations 2010
AS/NZS 5601.2:2013 Gas installations - Part 2: LP Gas installations in caravans and boats for non-propulsive purposes
NZS AS 4553.1&.2(Int):2013 Gas space heating appliances - Part 1: Essential safety and Part 2: Efficiency and emissions
Schedule 2A4
AS/NZS 4645.1:2008 AA Gas distribution networks - Network management: Amendment A
25 Operators of distribution systems must keep records and plans (2) Compliance with either Part 3 of NZS 5258 (to the extent that that Part relates to records or plans of distribution systems), or Part 1 of AS/NZS 4645, in relation to that system or part of a system, is deemed to be compliance with subclause (1)
26 Owners and operators of distribution systems must ensure continuity of supply and safety (2) Compliance with Part 1 (network management) of AS/NZS 4645, or compliance with Part 3 of NZS 5258, is deemed to be compliance with subclause (1).
NZS 5259:2004 Gas measurement
21 Gas measurement (1) Every person who sells gas must do so in accordance with the requirements of Part 1 of NZS 5259 unless there is an agreement in writing to the contrary between the seller and the purchaser.
21 Gas measurement (4) Compliance with NZS 5259 is deemed to be compliance with subclauses (2) and (3).
22 Testing and installation of gas measurement systems (3) Compliance with Part 2 of NZS 5259 is deemed to be compliance with subclause (2).
Measurement of CNG (5) Compliance with NZS 5259 is deemed to be compliance with subclause (4).A
NZS 5259 is the New Zealand Standard known as NZS 5259:2004 (Gas measurement)
New Zealand Standard known as NZS/AS 3645:2012 (Essential requirements for gas equipment Part 1 and Part 2)
Schedule 2(A)(2)(2)(d)
(d) a cabinet heater must be fitted with a label and notice that complies with Appendices 1 and 2 (sic) of NZS/AS 3645.
NZS 5255:2014 Safety verification of existing gas installations
If the period since the last disconnection or isolation of the gas installation or part installation is more than 6 months, the person proposing to reconnect or restore supply must, before doing so, give or sight a certificate issued in accordance with NZS 5255 that...
5A(1)(f)
In these regulations, low-risk gasfitting means gasfitting that comprises any of the following:... ...(f) gasfitting for the purpose of testing in accordance with NZS 5255 or NZS 5256.
(2) For the purpose of subclause (1)(a),... ...(b) a gas appliance, fittings, or gas installation contained in property or premises for hire or lease is deemed safe for the purposes of hire or lease at the commencement of the hire or lease if it is assessed as not unsafe under NZS 5255.
(3) For the purposes of subclauses (1) and (2), a gas appliance, fittings, or gas installation is deemed safe for the purposes of the residential tenancy at the commencement of the tenancy if it is assessed as not unsafe under NZS 5255.
New Zealand Standard known as NZS 5255:2014 (Safety verification of existing gas installations)
25 Operators of distribution systems must keep records and plans (2) Compliance with either Part 3 of NZS 5258 (to the extent that that Part relates to records or plans of distribution systems), or ...
33 Substantive requirements of safety management systems Every safety management system must provide for the following:... ...(f) how the safety management system operator proposes to enhance continuously the safety performance of the gas supply system, including performance measurement through key performance indicators as specified in NZS 5258, internal audits, management reviews, and incident reviews; and...
NZS 5258 is the New Zealand Standard known as NZS 5258:2003 (Gas distribution networks) subject to the variation that references in this standard to AS/NZS 1596:2002 (Storage and handling of LP gas) must be read as references to AS/NZS 1596:2008 (Storage
(2) For the purpose of subclause (1)(a), - (a) a gas appliance, fittings, or gas installation is deemed safe for the purposes of hire or lease at the commencement of its hire or lease if it is assessed as not unsafe under NZS 5256
NZS 5256: New Zealand Standard known as NZS 5256:2014 (Verification of safety of gas appliances)
41 Quality of gas (3) Liquefied petroleum gas must comply with NZS 5435.
NZS 5435 is the New Zealand Standard known as NZS 5435:1996 (Specification for liquefied petroleum gas (LPG))
Quality of gas (2) Reticulated natural gas must comply with NZS 5442.
NZS 5442 is the New Zealand Standard known as NZS 5442:2008 (Specification for reticulated natural gas)
NZS 5266(Int):2012 Safety of gas appliances
(4) An endorsement must include the following:... ...(d) a statement that, in the opinion of the approved practitioner, the appliance or fittings comply with these regulations and NZS 5266; and...
(1) Every person who repairs, modifies, or makes adjustments to a gas appliance or fittings must take all practicable steps to ensure that... ...(b) the appliance complies with the technical requirements of NZS 5266. (1A) For the purpose of subclause (1)(b), the technical requirements of section 4 of NZS 5266 apply to all appliances, despite anything to the contrary in NZS 5266.
A person may, without contravening these regulations, repair and use a gas appliance that was made and installed before 1 January 1985, provided that the repairs, modifications, and adjustments of the gas appliance meet the technical requirements in NZS 5266.
NZS 5266: New Zealand Standard known as NZS 5266 (Int):2012 (Safety of gas appliances)
AS/NZS 5601.1:2013 Gas installations - Part 1: General installations
Listed as an applicable standard for exterior gas lights, gas log fires, and indoor gas lights.
AS/NZS 4645.3:2008 A1 Gas distribution networks - Plastics pipe systems: Amendment 1
Schedule 2A(1)
1 Bodies that may certify gas appliances and specified fittings The following bodies may certify gas appliances and specified fittings for the purposes of regulation 54(3):... ...(g) a body accredited by the Joint Accreditation System of Australia and New Zealand (JAS-ANZ) and with a scope that includes NZS/AS 3645:2010 Part 2.
What safety management systems must do (1) Every safety management system must comply with either— (a) NZS 7901; or (b) regulations 33 and 34. (2) Nothing in regulations 33 and 34 applies to safety management systems that comply with NZS 7901.
Audit of safety management systems (1) Every safety management system must be regularly audited to confirm whether— (a) the safety management system complies with NZS 7901 or regulations 33 and 34, as appropriate; and...
NZS 7901 is the New Zealand Standard known as NZS 7901:2008 (Electricity and gas industries - safety management systems for public safety)
AS/NZS 4645.3:2008 Gas distribution networks - Plastics pipe systems
AS/NZS 4645.1:2008 Gas distribution networks - Network management
AS/NZS 4645.2:2008 Gas distribution networks - Steel pipe systems
General requirement about what gas must be odorised and to what level (2) Compliance with Part 2 of NZS 5263 is deemed to be compliance with subclause (1).
NZS 5263 is the New Zealand Standard known as NZS 5263:2003) (Gas detection and odorisation)
Schedule 2A(2)(2)(d)
Particular requirements for CNG stations (5) Compliance with NZS 5425.1 is deemed to be compliance with this regulation in relation to a fast-fill CNG station.
NZS 5425.1 is the New Zealand Standard known as NZS 5425.1:1994 (Code of practice for CNG compressor and refuelling stations - on site storage and location of equipment)
Particular requirements for CNG stations... ...(4) Compliance with NZS 5425.2 is deemed to be compliance with this regulation in relation to a CNG compressor.
NZS 5425.2 is the New Zealand Standard known as NZS 5425.2:1996 (Code of practice for CNG compressor and refuelling stations - compressor equipment)
NZS 5425.3.1P:1985 Code of practice for CNG compressor and refuelling stations - Metering devices - Division 3.1P Metering method using tables and calculator programme
NZS 5425.3 is the New Zealand Standard known as NZS 5425.3 (Code of practice for CNG compressor and refuelling stations - metering devices)
NZS 5425.3.2:1984 Code of practice for CNG compressor and refuelling stations - Metering devices - Division 3.2 Installation and operation of on-line metering devices
Measurement of CNG (3) Compliance with Division 3.3 of NZS 5425.3 is deemed to be compliance with subclause (2).
NZS 5425.3 si the New Zealand Standard known as NZS 5425.3 (Code of practice for CNG compressor and refuelling stations - metering devices)
Particular requirements for CNG stations (6) Compliance with NZS 5425.4 is deemed to be compliance with this regulation in relation to a trickle-fill CNG station.
NZS 5425.4 is the New Zealand Standard known as NZS 5425.4:1994 (Code of practice for CNG compressor and refuelling stations - CNG trickle-fill stations on commercial and industrial premises)
5A(2)(b)(viii)
...is within 20 metres of a hazardous area (as determined in accordance with AS/NZS 60079.10.1 or AS/NZS 60079.10.2, as appropriate...
AS/NZS 60079.10.1:2009: New Zealand Standard known as AS/NZS 60079.10.1:2009 (Explosive atmospheres—Classification of areas—Explosive gas atmospheres)
AS/NZS 4645.3:2008 A2 Gas distribution networks - Plastics pipe systems: Amendment 2
AS/NZS 60079.10.2:2011: New Zealand Standard known as AS/NZS 60079.10.2:2011 (Explosive atmospheres—Classification of areas—Combustible dust atmospheres)
NZS AS 4558(Int):2013 Decorative gas log and other fuel effect appliances