Source: https://de.scribd.com/doc/186250988/siprotec4-7ut6-catalog-sip-e6
Timestamp: 2019-11-17 09:34:29
Document Index: 72176215

Matched Legal Cases: ['art 15', 'art 15', 'art 303', 'art 303', 'art 303', 'art 303', 'art 1', 'art 2']

siprotec4 7ut6 catalog sip e6 | Relay | Transformer
speichernsiprotec4 7ut6 catalog sip e6 für später speichern
P12x_ent_f65
I7015E
Differential protection for 2- up to 5-winding transformers (3-/1-phase) Differential protection for motors and generators Differential protection for short 2 up to 5 terminal lines Differential protection for busbars up to 12 feeders (phase-segregated or with summation CT)
7UT613 Fig. 8/1 SIPROTEC 4 7UT6 differential protection relay for transformers, generators, motors and busbars 7UT612
Description The SIPROTEC 7UT6 differential protection relays are used for fast and selective fault clearing of short-circuits in transformers of all voltage levels and also in rotating electric machines like motors and generators, for short lines and busbars. The protection relay can be parameterized for use with three-phase and single-phase transformers. The specific application can be chosen by parameterization. In this way an optimal adaptation of the relay to the protected object can be achieved. In addition to the differential function, a backup overcurrent protection for 1 winding/star point is integrated in the relay. Optionally, a low or high-impedance restricted earth-fault protection, a negativesequence protection and a breaker failure protection can be used. 7UT613 and 7UT633 feature 4 voltage inputs. With this option an overvoltage and undervoltage protection is available as well as frequency protection, reverse / forward power protection, fuse failure monitor and overexcitation protection. With external temperature monitoring boxes (thermo-boxes) temperatures can be measured and monitored in the relay. Therefore, complete thermal monitoring of a transformer is possible, e.g. hot-spot calculation of the oil temperature. 7UT613 and 7UT63x only feature full coverage of applications without external relays by the option of multiple protection functions e.g. overcurrent protection is available for each winding or measurement location of a transformer. Other functions are available twice: earth-fault differential protection, breaker failure protection and overload protection. Furthermore, up to 12 user-defined (flexible) protection functions may be activated by the customer with the choice of measured voltages, currents, power and frequency as input variables. The relays provide easy-to-use local control and automation functions. The integrated programmable logic (CFC) allows the users to implement their own functions, e.g. for the automation of switchgear (interlocking). User-defined messages can be generated as well. The flexible communication interfaces are open for modem communication architectures with control system.
Protection functions Differential protection with phasesegregated measurement Sensitive measuring for low-fault currents Fast tripping for high-fault currents Restraint against inrush of transformer Phase /earth overcurrent protection Overload protection with or without temperature measurement Negative-sequence protection Breaker failure protection Low/high-impedance restricted earth fault (REF) Voltage protection functions (7UT613/633) Control functions Commands for control of circuitbreakers and isolators 7UT63x: Graphic display shows position of switching elements, local/remote switching by key-operated switch Control via keyboard, binary inputs, DIGSI 4 or SCADA system User-defined logic with CFC Monitoring functions Self-supervision of the relay Trip circuit supervision Oscillographic fault recording Permanent differential and restraint current measurement, extensive scope of operational values Communication interfaces PC front port for setting with DIGSI 4 System interface IEC 61850 Ethernet IEC 60870-5-103 protocol, PROFIBUS-FMS/-DP, MODBUS or DNP 3.0 Service interface for DIGSI 4 (modem)/ temperature monitoring (thermo-box) Time synchronization via IRIG-B/DCF 77
Application The numerical protection relays 7UT6 are primarily applied as differential protection on transformers 7UT612: 2 windings 7UT613/633: 2 up to 3 windings 7UT635: 2 up to 5 windings, generators motors short line sections small busbars parallel and series reactors. The user selects the type of object that is to be protected by setting during configuration of the relay. Subsequently, only those parameters that are relevant for this particular protected object need to be set. This concept, whereby only those parameters relevant to a particular protected object need to be set, substantially contributed to a simplification of the setting procedure. Only a few parameters must be set. Therefore the new 7UT6 relays also make use of and extend this concept. Apart from the protected plant objects defined in the 7UT6, a further differential protection function allows the protection of single busbars with up to 12 feeders. The well-proven differential measuring algorithm of the 7UT51 relay is also used in the new relays, so that a similar response with regard to short-circuit detection, tripping time saturation detection and inrush restraint is achieved.
7UT612 7UT635
Three-phase Single-phase Autotransformer transformer transformer
Busbar, 3-phase
Busbar, 1-phase
Differential protection Earth-fault differential protection Overcurrent-time protection 3I0 Overcurrent-time protection, earth Overcurrent-time protection, single-phase Negative-sequence protection Overload protection IEC 60255-8 Overload protection IEC 60354 Overexcitation protection *) V/Hz Overvoltage protection *) V> Undervoltage protection *) V< Frequency protection *) f>, f< Reverse power protection *) -P Fuse failure protection Breaker failure protection External temperature monitoring (thermo-box) Lockout Measured-value supervision Trip circuit supervision Direct coupling 1 Direct coupling 2 Operational measured values Flexible protection functions
87T/G/M/L 87 N 50/51N 50/51G
1 2 3 3 2 1 1 2 2 1 1 1 1 1 1 1 2 X X X X X X X 12
1 2 3 3 2 1 1 2 2 2 X X X X X X X 12
X X*) X X X X X X X X X X X X X X X X X X X X X X X
Overcurrent-time protection, phases 50/51
46 49 49 24 59 27 81 32R 60FL 50 BF 38 86 74 TC
Forward power protection*) P>, P< 32F
X Function applicable Function not applicable in this application *) Only 7UT613/63x
Construction The 7UT6 is available in three housing widths referred to a 19" module frame system. The height is 243 mm. 1/3 1/2 1/1 (7UT612), (7UT613), (7UT633/635) of 19
All cables can be connected with or without cable ring lugs. Plug-in terminals are available as an option, it is thus possible to employ prefabricated cable harnesses. In the case of surface mounting on a panel, the connection terminals are located above and below in the form of screw-type terminals. The communication interfaces are located on the same sides of the housing. For dimensions please refer to the dimension drawings (part 15).
Protection functions Differential protection for transformers (ANSI 87T) When the 7UT6 is employed as fast and selective short-circuit protection for transformers the following properties apply:
Tripping characteristic according to
Fig. 8/4 with normal sensitive IDIFF> and high-set trip stage IDIFF>> Vector group and ratio adaptation Depending on the treatment of the transformer neutral point, zero-sequence current conditioning can be set with or without consideration of the neutral current. With the 7UT6, the star-point current at the star-point CT can be measured and considered in the vector group treatment, which increases sensitivity by one third for single-phase faults. Fast clearance of heavy internal transformer faults with high-set differential element IDIFF>>. Restrain of inrush current with 2nd harmonic. Cross-block function that can be limited in time or switched off. Restrain against overfluxing with a choice of 3rd or 5th harmonic stabilization is only active up to a settable value for the fundamental component of the differential current. Additional restrain for an external fault with current transformer saturation (patented CT-saturation detector from 7UT51). Insensitivity to DC current and current transformer errors due to the freely programmable tripping characteristic and fundamental filtering. The differential protection function can be blocked externally by means of a binary input.
Protection functions Sensitive protection by measurement of star-point current (see Fig. 8/6) (ANSI 87N/87GD) Apart from the current inputs for detection of the phase currents on the sides of the protected object, the 7UT6 also contains normal sensitivity IE and high sensitivity IEE current measuring inputs. Measurement of the star-point current of an earthed winding via the normal sensitivity measuring input, and consideration of this current by the differential protection, increases the sensitivity during internal single-phase faults by 33 %. If the sum of the phase currents of a winding is compared with the star-point current measured with the normal sensitivity input IE, a sensitive earth current differential protection can be implemented (REF). This function is substantially more sensitive than the differential protection during faults to earth in a winding, detecting fault currents as small as 10 % of the transformer rated current. Furthermore, this relay contains a high-impedance differential protection input. The sum of the phase currents is compared with the star-point current. A voltage-dependent resistor (varistor) is applied in shunt (see Fig. 8/6). Via the sensitive current measuring input IEE, the voltage across the varistor is measured; in the milli-amp range via the external resistor. The varistor and the resistor are mounted externally. An earth fault results in a voltage across the varistor that is larger than the voltage resulting from normal current transformer errors. A prerequisite is the application of accurate current transformers of the class 5P (TPY) which exhibit a small measuring error in the operational and overcurrent range. These current transformers may not be the same as used for the differential protection, as the varistor may cause rapid saturation of this current transformers. Both high-impedance and low-impedance REF are each available twice (option) for transformers with two earthed windings. Thus separate REF relays are not required.
Differential protection for single-phase busbars (see Fig. 8/7) (ANSI 87L) The short-circuit protection is characterized by the large number of current measuring inputs. The scope of busbar protection ranges from a few bays e.g. in conjunction with one and a half circuit-breaker applications, to large stations having up to more than 50 feeders. In particular in smaller stations, the busbar protection arrangements are too expensive. With the 7UT6 relays the current inputs may also be used to achieve a cost-effective busbar protection system for up to 12 feeders (Fig. 8/7). This busbar protection functions as a phase-selective protection with 1 or 5 A current transformers, whereby the protected phase is connected. All three phases can therefore be protected by applying three relays. Furthermore a single-phase protection can be implemented by connecting the three-phase currents via a summation transformer. The summation transformer connection has a rated current of 100 mA. The selectivity of the protection can be improved by monitoring the current magnitude in all feeders, and only releasing the differential protection trip command when the overcurrent condition is also met. The security measures to prevent maloperation resulting from failures in the current transformer secondary circuits can be improved in this manner. This overcurrent release may also be used to implement a breaker failure protection. Should the release signal not reset within a settable time, this indicates that a breaker failure condition is present, as the short-circuit was not switched off by the bay circuit-breaker. After expiry of the time delay the circuitbreakers of the infeeds to the busbar may be tripped. Differential protection for generators and motors (see Fig. 8/8) (ANSI 87G/M) Equal conditions apply for generators, motors and series reactors. The protected zone is limited by the sets of current transfomers at each side of the protected object.
Protection functions n Backup protection functions Overcurrent-time protection (ANSI 50, 50N, 51, 51N) Backup protection on the transformer is achieved with a two-stage overcurrent protection for the phase currents and 3I0 for the calculated neutral current. This function may be configured for one of the sides or measurement locations of the protected object. The high-set stage is implemented as a definite-time stage, whereas the normal stage may have a definite-time or inverse-time characteristic. Optionally, IEC or ANSI characteristics may be selected for the inverse stage. The overcurrent protection 3I0 uses the calculated zero-sequence current of the configured side or measurement location. Multiple availability: 3 times (option) Overcurrent-time protection for earth (ANSI 50/51G) The 7UT6 feature a separate 2-stage overcurrent-time protection for the earth. As an option, an inverse-time characteristic according to IEC or ANSI is available. In this way, it is possible to protect e.g. a resistor in the transformer star point against thermal overload, in the event of a single-phase short-circuit not being cleared within the time permitted by the thermal rating. Multiple availability: 3 times (option) Phase-balance current protection (ANSI 46) (Negative-sequence protection) Furthermore a negative-sequence protection may be defined for one of the sides or measurement locations. This provides sensitive overcurrent protection in the event of asymmetrical faults in the transformer. The set pickup threshold may be smaller than the rated current. Breaker failure protection (ANSI 50BF) If a faulted portion of the electrical circuit is not disconnected upon issuing of a trip command, another command can be initiated using the breaker failure protection which operates the circuit-breaker, e.g., of an upstream (higher-level) protection relay. Multiple availability: 2 times (option)
Overexcitation protection Volt/Hertz (ANSI 24) (7UT613/633 only) The overexcitation protection serves for detection of an unpermissible high induction (proportional to V/f) in generators or transformers, which leads to a thermal overloading. This may occur when starting up, shutting down under full load, with weak systems or under isolated operation. The inverse characteristic can be set via seven points derived from the manufacturer data. In addition, a definite-time alarm stage and an instantaneous stage can be used. Trip circuit supervision (ANSI 74TC) One or two binary inputs can be used for monitoring the circuit-breaker trip coil including its incoming cables. An alarm signal occurs whenever the circuit is interrupted. Lockout (ANSI 86) All binary outputs (alarm or trip relays) can be stored like LEDs and reset using the LED reset key. The lockout state is also stored in the event of supply voltage failure. Reclosure can only occur after the lockout state is reset. External trip coupling For recording and processing of external trip information via binary inputs. They are provided for information from the Buchholz relay or specific commands and act like a protective function. Each input initiates a fault event and can be individually delayed by a timer.
Undervoltage protection (ANSI 27) (7UT613/633 only) The undervoltage protection evaluates the positive-sequence components of the voltages and compares them with the threshold values. There are two stages available. The undervoltage function is used for asynchronous motors and pumped-storage stations and prevents the voltage-related instability of such machines. The function can also be used for monitoring purposes. Overvoltage protection (ANSI 59) (7UT613/633 only) This protection prevents insulation faults that result when the voltage is too high. Either the maximum line-to-line voltages or the phase-to-earth voltages (for low-voltage generators) can be evaluated. The measuring results of the line-to-line voltages are independent of the neutral point displacement caused by earth faults. This function is implemented in two stages. Frequency protection (ANSI 81) (7UT613/633 only) The frequency protection prevents impermissible stress of the equipment (e.g. turbine) in case of under or overfrequency. It also serves as a monitoring and control element. The function has four stages; the stages can be implemented either as underfrequency or overfrequency protection. Each stage can be delayed separately. Even in the event of voltage distortion, the frequency measuring algorithm reliably identifies the fundamental waves and determines the frequency extremely precisely. Frequency measurement can be blocked by using an undervoltage stage.
Protection functions Reverse-power protection (ANSI 32R) (7UT613/633 only) The reverse-power protection monitors the direction of active power flow and picks up when the mechanical energy fails. This function can be used for operational shutdown (sequential tripping) of the generator but also prevents damage to the steam turbines. The reverse power is calculated from the positive-sequence systems of current and voltage. Asymmetrical power system faults therefore do not cause reduced measuring accuracy. The position of the emergency trip valve is injected as binary information and is used to switch between two trip command delays. When applied for motor protection, the sign () of the active power can be reversed via parameters. Forward-power protection (ANSI 32F) (7UT613/633 only) Monitoring of the active power produced by a generator can be useful for starting up and shutting down generators. One stage monitors exceeding of a limit value, while another stage monitors falling below another limit value. The power is calculated using the positive-sequence component of current and voltage. The function can be used to shut down idling motors. Flexible protection functions (7UT613/63x only) For customer-specific solutions up to 12 flexible protection functions are available and can be parameterized. Voltages, currents, power and frequency from all measurement locations can be chosen as inputs. Each protection function has a settable threshold, delay time, blocking input and can be configured as a 1-phase or 3-phase unit. Monitoring functions The relay comprises high-performance monitoring for the hardware and software. The measuring circuits, analog-digital conversion, power supply voltages, battery, memories and software sequence (watch-dog) are all monitored. The fuse failure function detects failure of the measuring voltage due to short-circuit or open circuit of the wiring or VT and avoids overfunction of the undervoltage elements in the protection functions. (7UT613/633 only) Thermal monitoring of transformers The importance of reducing the costs of transmitting and distributing energy by optimizing the system load has resulted in the increased importance of monitoring the thermal condition of transformers. This monitoring is one of the tasks of the monitoring systems, designed for medium and large transformers. Overload protection based on a simple thermal model, and using only the measured current for evaluation, has been integrated in differential protection systems for a number of years. The ability of the 7UT6 to monitor the thermal condition can be improved by serial connection of a temperature monitoring box (also called thermo-box or RTDbox) (Fig. 8/9). The temperature of up to 12 measuring points (connection of 2 boxes) can be registered. The type of sensor (Pt100, Ni100, Ni120) can be selected individually for each measuring point. Two alarm stages are derived for each measuring point when the corresponding set threshold is exceeded. Alternatively to the conventional overload protection, the relay can also provide a hotspot calculation according to IEC 60345. The hot-spot calculation is carried out separately for each leg of the transformer and takes the different cooling modes of the transformer into consideration. The oil temperature must be registered via the thermo-box for the implementation of this function. An alarm warning stage and final alarm stage is issued when the maximum hot-spot temperature of the three legs exceeds the threshold value. For each transformer leg a relative rate of ageing, based on the ageing at 98 C is indicated as a measured value. This value can be used to determine the thermal condition and the current thermal reserve of each transformer leg. Based on this rate of ageing, a remaining thermal reserve is indicated in % for the hottest spot before the alarm warning and final alarm stage is reached.
Protection functions Measured values The operational measured values and statistic value registering in the 7UT6, apart from the registration of phase currents and voltages (7UT613/633 only) as primary and secondary values, comprises the following:
Currents 3-phase IL1, IL2, IL3, I1, I2, 3I0 for
each side and measurement location Currents 1-phase I1 to I12 for each feeder and further inputs Ix1 to Ix4 Voltages 3-phase VL1, VL2, VL3, VL1L2, VL2L3, VL3L1, V1, V2, V0 and 1-phase VEN, V4 Phase angles of all 3-phase/ 1-phase currents and voltages Power Watts, Vars, VA/P, Q, S (P, Q: total and phase selective) Power factor (cos ), Frequency Energy + kWh, + kVarh, forward and reverse power flow Min./max. and mean values of VPH-PH, VPHE, VE, V0, V1, V2, IPH, I1, I2, 3I0, IDIFF, IRESTRAINT, S, P, Q, cos , f Operating hours counter Registration of the interrupted currents and counter for protection trip commands Mean operating temperature of overload function Measured temperatures of external thermo-boxes differential protection and REF Metered values For internal metering, the unit can calculate an energy metered value from the measured current and voltage values. The 7UT6 relays may be integrated into monitoring systems by means of the diverse communication options available in the relays. An example for this is the connection to the SITRAM transformer monitoring system with PROFIBUS-DP interface. Commissioning and operating aids Commissioning could hardly be easier and is fully supported by DIGSI 4. The status of the binary inputs can be read individually and the state of the binary outputs can be set individually. The operation of switching elements (circuit-breakers, disconnect devices) can be checked using the switch8/10
Differential and restraint currents of
ing functions of the bay controller. The analog measured values are represented as wide-ranging operational measured values. To prevent transmission of information to the control center during maintenance, the bay controller communications can be disabled to prevent unnecessary data from being transmitted. During commissioning, all indications with test marking for test purposes can be connected to a control and protection system. All measured currents and voltages (7UT613/633 only) of the transformer can
be indicated as primary or secondary values. The differential protection bases its pickup thresholds on the rated currents of the transformer. The referred differential and stabilising (restraint) currents are available as measured values per phase. If a thermo-box is connected, registered temperature values may also be displayed. To check the connection of the relay to the primary current and voltage transformers, a commissioning measurement is provided.
Protection functions This measurement function works with only 5 to 10 % of the transformer rated current and indicates the current and the angle between the currents and voltages (if voltages applied). Termination errors between the primary current transfomers and input transformers of the relay are easily detected in this manner. The operating state of the protection may therefore be checked online at any time. The fault records of the relay contain the phase and earth currents as well as the calculated differential and restraint currents. The fault records of the 7UT613/633 relays also contain voltages. Browser-based commissioning aid The 7UT6 provides a commissioning and test program which runs under a standard internet browser and is therefore independent of the configuration software provided by the manufacturer. For example, the correct vector group of the transformer may be checked. These values may be displayed graphically as vector diagrams. The stability check in the operating characteristic is available as well as event log and trip log messages. Remote control can be used if the local front panel cannot be accessed. n Control and automation functions Control In addition to the protection functions, the SIPROTEC 4 units also support all control and monitoring functions that are required for operating medium-voltage or highvoltage substations. The main application is reliable control of switching and other processes. The status of primary equipment or auxiliary devices can be obtained from auxiliary contacts and communicated via binary inputs. Therefore it is possible to detect and indicate both the OPEN and CLOSED position or a fault or intermediate circuitbreaker or auxiliary contact position. The switchgear or circuit-breaker can be controlled via: integrated operator panel binary inputs substation control and protection system DIGSI 4
Command processing All the functionality of command processing is offered. This includes the processing of single and double commands with or without feedback, sophisticated monitoring of the control hardware and software, checking of the external process, control actions using functions such as runtime monitoring and automatic command termination after output. Here are some typical applications:
Chatter disable The chatter disable feature evaluates whether, in a configured period of time, the number of status changes of indication input exceeds a specified figure. If exceeded, the indication input is blocked for a certain period, so that the event list will not record excessive operations. Filter time All binary indications can be subjected to a filter time (indication suppression). Indication filtering and delay Indications can be filtered or delayed. Filtering serves to suppress brief changes in potential at the indication input. The indication is passed on only if the indication voltage is still present after a set period of time. In the event of indication delay, there is a wait for a preset time. The information is passed on only if the indication voltage is still present after this time. Indication derivation A further indication (or a command) can be derived from an existing indication. Group indications can also be formed. The volume of information to the system interface can thus be reduced and restricted to the most important signals. Transmission lockout A data transmission lockout can be activated, so as to prevent transfer of information to the control center during work on a circuit bay. Test operation During commissioning, all indications can be passed to an automatic control system for test purposes.
Single and double commands using 1, 1
plus 1 common or 2 trip contacts User-definable bay interlocks Operating sequences combining several switching operations such as control of circuit-breakers, disconnectors and earthing switches
Automation / user-defined logic With integrated logic, the user can set, via a graphic interface (CFC), specific functions for the automation of switchgear or substation. Functions are activated via function keys, binary input or via communication interface. Switching authority Switching authority is determined according to parameters, communication or by key-operated switch (when available). If a source is set to LOCAL, only local switching operations are possible. The following sequence of switching authority is laid down: LOCAL; DIGSI PC program, REMOTE Every switching operation and change of breaker position is kept in the status indication memory. The switch command source, switching device, cause (i.e. spontaneous change or command) and result of a switching operation are retained. Assignment of feedback to command The positions of the circuit- breaker or switching devices and transformer taps are acquired by feedback. These indication inputs are logically assigned to the corresponding command outputs. The unit can therefore distinguish whether the indication change is a consequence of switching operation or whether it is a spontaneous change of state (intermediate position).
Communication With respect to communication, particular emphasis has been placed on high levels of flexibility, data integrity and utilization of standards common in energy automation. The design of the communication modules permits interchangeability on the one hand, and on the other hand provides openness for future standards (for example, Industrial Ethernet). Local PC interface The PC interface accessible from the front of the unit permits quick access to all parameters and fault event data. Of particular advantage is the use of the DIGSI 4 operating program during commissioning. Rear-mounted interfaces Two communication modules located on the rear of the unit incorporate optional equipment complements and readily permit retrofitting. They assure the ability to comply with the requirements of different communication interfaces. The interfaces make provision for the following applications:
Commissioning aid via a standard Web browser In the case of the 7UT6, a PC with a standard browser can be connected to the local PC interface or to the service interface (refer to Commissioning program). The relays include a small Web server and send their HTML-pages to the browser via an established dial-up network connection. Retrofitting: Modules for every type of communication Communication modules for retrofitting are available for the entire SIPROTEC 4 unit range. These ensure that, where different communication interfaces (electrical or optical) and protocols (IEC 61850 Ethernet, IEC 60870-5-103, PROFIBUS-FMS/-DP, MODBUS RTU, DNP 3.0, DIGSI, etc.) are required, such demands can be met. Safe bus architecture
With this data transmission via copper conductors electromagnetic fault influences are largely eliminated by the use of twisted-pair conductor. Upon failure of a unit, the remaining system continues to operate without any disturbances. Fiber-optic double ring circuit The fiber-optic double ring circuit is immune to electromagnetic interference. Upon failure of a section between two units, the communication system continues to operate without disturbance. It is generally impossible to communicate with a unit that has failed. If a unit were to fail, there is no effect on the communication with the rest of the system.
Service interface (Port C/Port D1))
In the RS485 version, several protection units can be centrally operated with DIGSI 4. On connection of a modem, remote control is possible. Via this interface communication with thermo-boxes is executed. System interface (Port B) This interface is used to carry out communication with a control or protection and control system and supports a variety of communication protocols and interface designs, depending on the module connected.
Fig. 8/13 Bus structure for station bus with Ethernet und IEC 61850, fiber-optic ring
Communication IEC 61850 Ethernet The Ethernet-based IEC 61850 protocol is the worldwide standard for protection and control systems used by power supply corporations. Siemens was the first manufacturer to support this standard. By means of this protocol, information can also be exchanged directly between bay units so as to set up simple masterless systems for bay and system interlocking. Access to the units via the Ethernet bus is also possible with DIGSI. IEC 60870-5-103 IEC 60870-5-103 is an internationally standardized protocol for the efficient communication in the protected area. IEC 60870-5-103 is supported by a number of protection device manufacturers and is used worldwide. PROFIBUS-DP PROFIBUS-DP is an industry-recognized standard for communications and is supported by a number of PLC and protection device manufacturers. MODBUS RTU MODBUS RTU is an industry-recognized standard for communications and is supported by a number of PLC and protection device manufacturers. DNP 3.0 DNP 3.0 (Distributed Network Protocol Version 3) is a messaging-based communication protocol. The SIPROTEC 4 units are fully Level 1 and Level 2 compliant with DNP 3.0. DNP 3.0 is supported by a number of protection device manufacturers.
Fig. 8/14 RS232/RS485 electrical communication module
Fig. 8/15 820 nm fiber-optic communication module
Fig. 8/16 PROFIBUS communication module, optical double-ring
Fig. 8/17 Optical Ethernet communication module for IEC 61850 with integrated Ethernet switch
Communication System solutions for protection and station control Together with the SICAM power automation system, SIPROTEC 4 can be used with PROFIBUS-FMS. Over the low-cost electrical RS485 bus, or interference-free via the optical double ring, the units exchange information with the control system. Units featuring IEC 60870-5-103 interfaces can be connected to SICAM in parallel via the RS485 bus or radially by fiber-optic link. Through this interface, the system is open for the connection of units of other manufacturers (see Fig. 8/12). Because of the standardized interfaces, SIPROTEC units can also be integrated into systems of other manufacturers or in SIMATIC. Electrical RS485 or optical interfaces are available. The optimum physical data transfer medium can be chosen thanks to opto-electrical converters. Thus, the RS485 bus allows low-cost wiring in the cubicles and an interference-free optical connection to the master can be established.
Fig. 8/18 System solution: Communications
For IEC 61850, an interoperable system solution is offered with SICAM PAS. Via the 100 Mbits/s Ethernet bus, the units are linked with PAS electrically or optically to the station PC. The interface is standardized, thus also enabling direct connection of units of other manufacturers to the Ethernet bus. With IEC 61850, however, the units can also be used in other manufacturers systems (see Fig. 8/13).
Fig. 8/19 Standard connection to a transformer without neutral current measurement
Fig. 8/20 Connection to a transformer with neutral current measurement
Fig. 8/21 Connection of transformer differential protection with high impedance REF (I8) and neutral current measurement at I7
Fig. 8/22 Connection example to a single-phase power transformer with current transformer between starpoint and earthing point
Fig. 8/23 Connection example to a single-phase power transformer with only one current transformer (right side)
Fig. 8/24 Connection to a three-phase auto-transformer with current transformer between starpoint and earthing point
Fig. 8/25 Generator or motor protection
Fig. 8/26 Connection 7UT612 as single-phase busbar protection for 7 feeders, illustrated for phase L1
Fig. 8/27 Connection 7UT612 as busbar protection for feeders, connected via external summation current transformers (SCT) partial illustration for feeders 1, 2 and 7
Fig. 8/28 Connection example 7UT613 for a three-winding power transformer
Fig. 8/29 Connection example 7UT613 for a three-winding power transformer with current transformers between starpoint and earthing point, additional connection for high-impedance protection; IX3 connected as high-sensitivity input
Fig. 8/30 Connection example 7UT613 for a three-phase auto-transformer with three-winding and current transformer between starpoint and earthing point
Fig. 8/31 Connection example 7UT635 for a three-winding power transformer with 5 measurement locations (3-phase) and neutral current measurement
Fig. 8/32 Voltage transformer connection to 3 star-connected voltage transformers (7UT613 and 7UT633 only)
Fig. 8/33 Voltage transformer connection to 3 star-connected voltage transformers with additional delta winding (e-n-winding) (7UT613 and 7UT633 only)
General unit data Analog inputs Rated frequency Rated current Power consumption In CT circuits with IN = 1 A; in VA approx. with IN = 5 A; in VA approx. with IN = 0.1 A; in VA approx. sensitive input; in VA approx. Overload capacity In CT circuits Thermal (r.m.s.) 50 or 60 Hz (selectable) 0.1 or 1 or 5 A (selectable by jumper, 0.1 A) 7UT 612 0.02 0.2 0.001 0.05 IN 100 IN for 1 s 30 IN for 10 s 4 IN continuous 250 IN (half cycle) 300 A for 1 s 100 A for 10 s 15 A continuous 750 A (half cycle) 80 to 125 V w 0.1 VA 613 0.05 0.3 0.001 0.05 633 0.05 0.3 0.001 0.05 635 0.05 0.3 0.001 0.05 Switching capacity Make Break Break (with resistive load) Break (with L/R w 50 ms) Switching voltage Permissible total current Operating time, approx. NO contact NO/NC contact (selectable) Fast NO contact High-speed*) NO trip outputs LEDs Quantity RUN (green) ERROR (red) LED (red), function can be assigned Unit design Housing 7XP20 Degree of protection acc. to IEC 60529 For the device in surface-mounting housing in flush-mounting housing front rear For personal safety Housing Size, referred to 19 frame Weight, in kg Flush-mounting housing Surface-mounting housing 613 6/12 12/19 633 635 6/12 6/12 20/28 20/28 Serial interfaces Operating interface 1 for DIGSI 4 or browser Connection W 50 ms Front side, non-isolated, RS232, 9-pin subminiature connector (SUB-D) 7UT612: 4.8 to 38.4 kbaud 7UT613/633/635: 4.8 to 115 kbaud 15 m Rear side, 9-pin subminiature connector (SUB-D) (terminals with surface-mounting housing) 5, 12 or 24 V (optional) 9-pin subminiature connector (SUB-D) 500 V / 50 Hz Max. 15 m / 49.2 ft Max. 1000 m / 3300 ft 1.5 km (1 mile) For dimensions please refer to dimension drawings part 15 7UT 612 1 1 7 613 1 1 14 633 1 1 14 635 1 1 14 1000 W / VA 30 VA 40 W 25 W 250 V 30 A for 0.5 seconds 5 A continuous 8 ms 8 ms 5 ms < 1 ms
Dynamic (peak value) In CT circuits for highly sensitive input IEE Thermal
Dynamic Rated voltage (7UT613/633 only) Power consumption per phase at 100 V Overload capacity Thermal (r.m.s.) Auxiliary voltage Rated voltage
230 V continuous 24 to 48 V DC 60 to 125 V DC 110 to 250 V DC and 115 V AC (50/60 Hz), 230 V AC -20 to +20 % w 15 % 7UT 612 5 7
IP 51 IP 51 IP 50 IP 2x with closed protection cover 7UT 612 1/3 5.1 9.6 613 1/2 8.7 13.5 633 1/1 13.8 22.0 635 1/1 14.5 22.7
Permissible tolerance Superimposed AC voltage (peak-to-peak) Power consumption (DC/AC) Quiescent; in W approx. Energized; in W approx. depending on design Bridging time during failure of the auxiliary voltage Vaux W 110 V Binary inputs Functions are freely assignable Quantity marshallable
Transmission rate in kbaud Setting as supplied: 38.4 kbaud, parity 8E1 Distance, max. 613 5 633 21 635 29 Connection
7UT 612 3
Rated voltage range Minimum pickup threshold Ranges are settable by means of jumpers for each binary input Maximum permissible voltage Current consumption, energized Output relay Command / indication / alarm relay Quantity each with 1 NO contact (marshallable) 1 alarm contact, with 1 NO or NC contact (not marshallable)
24 to 250 V, bipolar 19 or 88 V DC (bipolar)
Voltage levels 300 V DC Approx. 1.8 mA Isolated RS232/RS485/FO Dielectric test Distance for RS232 Distance for RS485 Distance for FO 613 8 633 24 635 24
7UT 612 4
System interface IEC 61850 Ethernet, electrical (EN 100) for IEC 61850 and DIGSI Connection for flush-mounting case Rear panel, mounting location "B", two RJ45 connector, 100 Mbit acc. to IEEE802.3 At bottom part of the housing 500 V; 50 Hz 100 Mbits/s 20 m/66 ft Electrical tests Specifications Standards IEC 60255 (Product standards) ANSI/IEEE C37.90.0/.1/.2 UL 508 IEC 60255-5 and 60870-2-1 2.5 kV (r.m.s.), 50 Hz / 60 Hz
Insulation tests Standards Voltage test (100 % test) All circuits except for auxiliary supply, binary inputs and communication interfaces Auxiliary voltage and binary inputs (100 % test) RS485/RS232 rear side communication interfaces and time synchronization interface (100 % test) Impulse voltage test (type test) All circuits except for communication interfaces and time synchronization interface, class III EMC tests for interference immunity Standards IEC 60255-6, 60255-22 (product standards) EN 6100-6-2 (generic standard) DIN 57435 / Part 303 2.5 kV (peak); 1 MHz; = 15 ms; 400 surges per s; test duration 2 s; Ri = 200 8 kV contact discharge; 15 kV air discharge; both polarities; 150 pF; Ri = 330 10 V/m; 80 to 1000 MHz; 80 % AM; 1 kHZ
for surface-mounting case Test voltage Transmission Speed Distance Connection for flush-mounting case for surface-mounting case Optical wavelength Transmission Speed Laser class 1 acc. to EN 60825-1/-2 Permissible path attenuation Distance IEC 60870-5-103 Isolated RS232/RS485/FO Baud rate Dielectric test Distance for RS232 Distance for RS485
Ethernet, optical (EN 100) for IEC 61850 and DIGSI Rear panel, mounting location "B", LC connector receiver/transmitter Not available = 1350 nm 100 Mbits/s glass fiber 50/125 m or glass fiber 62/125m Max. 5 dB for glass fiber 62.5/125m Max. 800 m/0.5 mile 9-pin subminiature connector (SUB-D) 4800 to 19200 baud 500 V/50 Hz Max. 15 m Max. 1000 m ST connector = 820 nm Max. 8 dB, for glass-fiber 62.5/125 m Max. 1.5 km 9-pin subminiature connector (SUB-D) Max. 1.5 Mbaud 500 V / 50 Hz Max. 1000 m (3300 ft) at w 93.75 kbaud ST connector Optical interface with OLM1) Max. 1.5 Mbaud = 820 nm Max. 8 dB, for glass-fiber 62.5/125 m 500 kbaud 1.6 km (0.99 miles) 1500 kbaud 530 m (0.33 miles)
3.5 kV DC 500 V (r.m.s.), 50 Hz / 60 Hz
5 kV (peak); 1.2/50 s; 0.5 J 3 positive and 3 negative impulses at intervals of 5 s
For fiber-optic cable Connector type Optical wavelength Permissible attenuation Distance PROFIBUS RS485 (-FMS/-DP) Connector type Baud rate Dielectric test Distance PROFIBUS fiber optic (-FMS/-DP) Only for flush-mounting housing For surface-mounting housing Baud rate Optical wavelength Permissible attenuation Distance DNP 3.0 RS485 / MODBUS RS485 Connector type Baud rate Dielectric test Distance DNP 3.0 Optical/MODBUS FO Connector type Optical wavelength Permissible attenuation Distance
High frequency test IEC 60255-22-1, class III and DIN 57435 / Part 303, class III Electrostatic discharge IEC 60255-22-2 class IV EN 61000-4-2, class IV Irradiation with RF field, frequency sweep, IEC 60255-22-3, IEC 61000-4-3 class III
Irradiation with RF field, amplitude- 10 V/m; 80, 160, 450, 900 MHz, 80 % AM; modulated, single frequencies, duration > 10 s IEC 60255-22-3, IEC 61000-4-3, class III Irradiation with RF field, pulsemodulated, single frequencies, IEC 60255-22-3, IEC 61000-4-3/ ENV 50204, class III Fast transients interference, bursts IEC 60255-22-4 and IEC 61000-4-4, class IV 10 V/m; 900 MHz; repetition frequency 200 Hz; duty cycle 50 % PM 4 kV; 5/50 ns; 5 kHz; burst length = 15 ms; repetition rate 300 ms; both polarities; Ri = 50; test duration 1 min Impulse: 1.2/50 s Common (longitudinal) mode: 2kV; 12 , 9 F Differential (transversal) mode: 1kV; 2 , 18 F Common (longitude) mode: 2kV; 42 , 0.5 F Differential (transversal) mode: 1kV; 42 , 0.5 F 10 V; 150 kHz to 80 MHz; 80 % AM; 1 kHz
9-pin subminiatur connector (SUB-D) Max. 19200 baud 500 V / 50 Hz Max. 1000 m (3300 ft) ST connector = 820 nm Max. 8 dB, for glass-fiber 62.5/125 m 1.5 km (1 mile)
High-energy surge voltages (SURGE), IEC 61000-4-5, installation class III Auxiliary supply
1) Conversion with external OLM For fiber-optic interface please complete Order No. at 11th position with 4 (FMS RS485) or 9 (DP RS485) and Order code L0A and additionally order: For single ring: SIEMENS OLM 6GK1502-3AB10 For double ring: SIEMENS OLM 6GK1502-4AB10
Line-conducted HF, amplitudemodulated IEC 61000-4-6, class III
Electrical tests (contd) EMC tests for interference immunity (contd) Magnetic field with power frequency 30 A/m continuous; 300 A/m for 3 s; IEC 61000-4-8, IEC 60255-6 class IV 50 Hz, 0.5 mT; 50 Hz Oscillatory surge withstand capability, ANSI/IEEE C37.90.1 Fast transient surge withstand capability, ANSI/IEEE C37.90.1 2.5 kV (peak); 1 MHz; = 15 s; Damped wave; 400 surges per second; duration 2 s; Ri = 200 4 kV; 5/50 ns; 5 kHz; burst 15 ms; repetition rate 300 ms; both polarities; duration 1 min.; Ri = 80 2.5 kV (peak value), polarity alternating 100 kHz, 1 MHz, 10 MHz and 50 MHz, Ri = 200 EN 50081-* (generic standard) 150 kHz to 30 MHz Limit class B 30 to 1000 MHz Limit class B Climatic stress tests Temperatures Type-tested acc. to IEC 60068-2-1 and -2, test Bd, for 16 h Temporarily permissible operating temperature, tested for 96 h -25 C to +85 C / -13 F to +185 F -20 C to +70 C / -4 F to +158 F
Recommended permanent operating -5 C to +55 C / +25 F to +131 F temperature acc. to IEC 60255-6 (Legibility of display may be impaired above +55 C / +131 F) Limiting temperature during -25 C to +55 C / -13 F to +131 F permanent storage Limiting temperature during -25 C to +70 C / -13 F to +158 F transport Humidity Permissible humidity stress It is recommended to arrange the units in such a way that they are not exposed to direct sunlight or pronounced temperature changes that could cause condensation. CE conformity Yearly average w 75 % relative humidity; on 56 days in the year up to 93 % relative humidity; condensation not permitted
EMC tests for interference emission (type test) Standard Conducted interference, only auxiliary supply IEC-CISPR 22 Radio interference field strenght IEC-CISPR 22 Mechanical stress tests Vibration, shock stress and seismic vibration During operation Standards Vibration IEC 60255-21-1, class 2 IEC 60068-2-6 IEC 60255-21 and IEC 60068 Sinusoidal 10 to 60 Hz: 0.075 mm amplitude; 60 to 150 Hz: 1 g acceleration frequency sweep 1 octave/min. 20 cycles in 3 orthogonal axes Half-sinusoidal acceleration 5 g, duration 11 ms, 3 shocks each in both directions of the 3 axes Sinusoidal 1 to 8 Hz: 3.5 mm amplitude (horizontal axis) 1 to 8 Hz: 1.5 mm amplitude (vertical axis) 8 to 35 Hz: 1 g acceleration (horizontal axis) 8 to 35 Hz: 0.5 g acceleration (vertical axis) frequency sweep 1 octave/min 1 cycle in 3 orthogonal axes IEC 60255-21 and IEC 60068 Sinusoidal 5 to 8 Hz: 7.5 mm amplitude; 8 to 150 Hz: 2 g acceleration frequency sweep 1 octave/min 20 cycles in 3 orthogonal axes Half-sinusoidal acceleration 15 g, duration 11 ms, 3 shocks each in both directions of the 3 axes Half-sinusoidal acceleration 10 g, duration 16 ms, 1000 shocks on each of the 3 axes in both directions
This product is in conformity with the Directives of the European Communities on the harmonization of the laws of the Member States relating to electromagnetic compatibility (EMC Council Directive 89/336/EEC) and electrical equipment designed for use within certain voltage limits (Low voltage Council Directive 73/23/EEC). This unit conforms to the international standard IEC 60255, and the German standard DIN 57435/Part 303 (corresponding to VDE 0435/ Part 303). Further applicable standards: ANSI/IEEE C37.90.0 and C37.90.1. This conformity is the result of a test that was performed by Siemens AG in accordance with Article 10 of the Council Directive complying with the generic standards EN 50081-2 and EN 50082-2 for the EMC Directive and standard EN 60255-6 for the low-voltage Directive.
Shock IEC 60255-21-2, class 1 IEC 60068-2-27 Seismic vibration IEC 60255-21-2, class 1 IEC 60068-3-3
During transport Standards Vibration IEC 60255-21-1, class 2 IEC 60255-2-6
Functions Differential protection General Pickup values Differential current IDIFF > /INobj High-current stage Pickup on switch-on (factor of IDIFF >) 0.05 to 2.00 (steps 0.01) IDIFF >> /INobj 0.5 to 35.0 (steps 0.1) or deactivated (stage ineffective) 1.0 to 2.0 (steps 0.1) Generators, motors, reactors Operating times Pickup time/dropout time with single-side infeed Pickup time (in ms) at frequency 7UT 612 IDIFF >, min. IDIFF >>, min. Dropout time (in ms), approx. 7UT 613/63x IDIFF >, min. IDIFF >>, min. Dropout time (in ms), approx. 5 % of set value 5 % of set value 0.00 to 60.00 s (steps 0.01 s) or deactivated (no trip) Dropout ratio, approx. Busbars, short lines Differential current monitor TI-DIFF> Steady-state differential current monitoring IDIFF mon/INobj Delay of blocking with differential current monitoring TDIFF mon Feeder current guard 10 to 80 % 10 to 80 % (steps 1 %) (steps 1 %) Trip release Iguard/INobj by feeder current guard Operating times Pickup time/dropout time with single-side infeed Pickup time (in ms) at frequency Can be activated / deactivated 2 to 1000 AC cycles (steps 1 cycle) or 0 (crossblock deactivated) or deactivated (active until dropout) 7UT 612 IDIFF >, min. IDIFF >>, min. Dropout time (in ms), approx. 7UT 613/63x IDIFF >, min. IDIFF >>, min. 50 Hz 38 19 35 30 11 54 0.7 0 to 11 (x 30 ) (steps 1) Earthed or non-earthed (for each winding) 60 Hz 35 17 30 27 11 46 Dropout time (in ms), approx. Dropout ratio, approx. 25 19 30 11 11 54 0.7 25 17 30 11 11 46 50 Hz 60 Hz 0.20 to 2.00 (steps 0.01) or 0 (always released) 0.15 to 0.80 (steps 0.01) 50 Hz 38 19 35 30 11 54 0.7 60 Hz 35 17 30 27 11 46
Add-on stabilization on external fault 2.00 to 15.00 (steps 0.01) (ISTAB > set value) Iadd-on /INobj 2 to 250 cycles (steps 1 cycle) action time or deactivated (effective until dropoff) Tolerances (at preset parameters) IDIFF > stage and characteristic IDIFF >> stage Time delays Delay of IDIFF > stage Delay of IDIFF >> stage Time tolerance The set times are pure delay times Transformers Harmonic stabilization Inrush restraint ratio I2fN/IfN (2nd harmonic)
TI-DIFF >> 0.00 to 60.00 s (steps 0.01 s) or deactivated (no trip) 1 % of set value or 10 ms
Stabilization ratio further (n-th) harmonic (optional 3rd or 5th) InfN/IfN Crossblock function max. action time for crossblock
Operating times Pickup time/dropout time with single-side infeed Pickup time (in ms) at frequency 7UT 612 IDIFF >, min. IDIFF >>, min. Dropout time (in ms), approx. 7UT 613/63x IDIFF >, min. IDIFF >>, min. Dropout time (in ms), approx. Dropout ratio, approx. Current matching for transformers Vector group adaptation Star-point conditioning
Restricted earth-fault protection Multiple availability Settings Differential current IREF >/INobj Limit angle Time delay REF TREF 0.05 to 2.00 110 (fixed) 0.00 to 60.00 s (steps 0.01 s) or deactivated (no trip) (steps 0.01) 2 times (option) Current stages (contd) Tolerances Definite time Inverse time Acc. to IEC Currents Times Currents Times 3 % of set value or 1 % of rated current 1 % of set value or 10 ms Pickup at 1.05 w I/IP w 1.15; or 1.05 w I/3IOP w 1.15
The set times are pure delay times Operating times Pickup time (in ms) at frequency 50 Hz 60 Hz Acc. to ANSI 38 32 40 30 29 23 Times 7UT 612 At 1.5 setting value IREF >, approx. 40 At 2.5 setting value IREF >, approx. 37 40 Dropout time (in ms), approx. 7UT 613/63x At 1.5 setting value IREF >, approx. 35 At 2.5 setting value IREF >, approx. 33 26 Dropout time (in ms), approx. Dropout ratio, approx. Multiple availability Characteristics Definite-time stages (DT) Inverse-time stages (IT) Acc. to IEC Acc. to ANSI IPh >>, 3I0 >>, IPh >, 3I0 > IP, 3I0P Inverse, very inverse, extremely inverse, long-time inverse Inverse, moderately inverse, very inverse, extremely inverse, definite inverse, short inverse, long inverse Alternatively, user-specified trip and reset characteristics Reset characteristics (IT) Current stages High-current stages IPh >> TIPh >> 3I0 >> T3I0 >> Definite-time stages IPh > TIPh 3I0 > T3I0 > Inverse-time stages Acc. to IEC IP TIP 3I0P T3I0P Inverse-time stages Acc. to ANSI IP DIP 3I0P D3I0P Acc. to ANSI with disk emulation 0.10 to 35.00 A 1) (steps 0.01 A) or deactivated (stage ineffective) 0.00 to 60.00 s (steps 0.01 s) or deactivated (no trip) 0.05 to 35.00 A 1) (steps 0.01 A) or deactivated (stage ineffective) 0.00 to 60.00 s (steps 0.01 s) or deactivated (no trip) 0.10 to 35.00 A 1) (steps 0.01 A) or deactivated (stage ineffective) 0.00 to 60.00 s (steps 0.01 s) or deactivated (no trip) 0.05 to 35.00 A 1) (steps 0.01 A) or deactivated (stage ineffective) 0.00 to 60.00 s (steps 0.01 s) or deactivated (no trip) 0.10 to 4.00 A 1) (steps 0.01 A) 0.05 to 3.20 s (steps 0.01 s) or deactivated (no trip) 0.05 to 4.00 A 1) (steps 0.01 A) 0.05 to 3.20 s (steps 0.01 s) or deactivated (no trip) 0.10 to 4.00 A 1) (steps 0.01 A) 0.50 to 15.00 s (steps 0.01 s) or deactivated (no trip) 0.05 to 4.00 A 1) (steps 0.01 A) 0.50 to 15.00 s (steps 0.01 s) or deactivated (no trip) 0.7 3 times (option)
5 % 15 ms at fN = 50/60 Hz for 2 w I/IP w 20 and TIP/s W 1; or 2 w I/3I0P w 20 and T3I0P/s W 1 5 % 15 ms at fN = 50/60 Hz for 2 w I/IP w 20 and DIP/s W 1; or 2 w I/3I0P w 20 and D3I0P/s W 1
The set definite times are pure delay times. Operating times of the definite-time stages Pickup time/dropout time phase current stages Pickup time (in ms) at frequency 50 Hz 7UT612 Without inrush restraint, min. With inrush restraint, min. Dropout time (in ms), approx. 7UT613/6x Without inrush restraint, min. With inrush restraint, min. Dropout time (in ms), approx. Pickup time (in ms) at frequency 7UT 612 Without inrush restraint, min. With inrush restraint, min. Dropout time (in ms), approx. 7UT613/6x Without inrush restraint, min. With inrush restraint, min. Dropout time (in ms), approx. Dropout ratios Current stages Inrush blocking Inrush blocking ratio I2fN/IfN (2nd harmonic) Lower operation limit Max. current for blocking 10 to 45 % I > 0.2 A 1) 0.30 to 25.00 A 1) (steps 0.01 A) (steps 1 %) Approx. 0.95 for I/IN W 0.5 21 31 45 19 29 43 40 40 30 35 35 30 11 33 35 50 Hz 11 29 35 60 Hz 20 40 30 18 35 30 60 Hz
Overcurrent-time protection for phase and residual currents
Pickup time/dropout time residual current stages
Crossblock function between phases Can be activated/deactivated 0.00 to 180 s (steps 0.01 A) max. action time for crossblock
1) Secondary values based on IN = 1 A; for IN = 5 A they must be multiplied by 5.
Overcurrent-time protection for earth current Multiple availability Characteristics Definite-time stages (DT) Inverse-time stages (IT) Acc. to IEC Acc. to ANSI IE >>, IE > IEP Inverse, very inverse, extremely inverse, long-time inverse Inverse, moderately inverse, very inverse, extremely inverse, definite inverse, short inverse, long inverse Alternatively, user-specified trip and reset characteristics Reset characteristics (IT) Current stages High-current stage IE >> TIE >> Definite-time stage IE > TIE > Inverse-time stages Acc. to IEC Inverse-time stages IEP TIEP IEP DIEP 0.05 to 35.00 A 1) (steps 0.01 A) or deactivated (stage ineffective) 0.00 to 60.00 s (steps 0.01 s) or deactivated (no trip) 0.05 to 35.00 A 1) (steps 0.01 A) or deactivated (stage ineffective) 0.00 to 60.00 s (steps 0.01 s) or deactivated (no trip) 0.05 to 4.00 A 1) (steps 0.01 A) 0.05 to 3.20 s (steps 0.01 s) or deactivated (no trip) 0.05 to 4.00 A 1) (steps 0.01 A) Tolerances 0.50 to 15.00 s (steps 0.01 s) or deactivated (no trip) 3 % of set value or 1 % of rated current 1 % of set value or 10 ms Pickup at 1.05 w I/IEP w 1.15 5 % 15 ms at fN = 50/60 Hz for 2 w I/IEP w 20 and TIEP/s W 1 5 % 15 ms at fN = 50/60 Hz for 2 w I/IEP w 20 and DIEP/s W 1 TT >> Definite-time stage I > Acc. to ANSI with disk emulation CB open time Active time TCB open TActive time 3 times (option) Dynamic cold-load pickup for overcurrent-time protection Time control Start criterion Binary input from circuit-breaker auxiliary contact or current criterion (of the assigned side) 0 to 21600 s (= 6 h) 1 to 21600 s (= 6 h) (steps 1 s) (steps 1 s)
Accelerated dropout time TStop time
1 to 600 s (= 10 min) (steps 1 s) or deactivated (no accelerated dropout) Setting ranges and steps are the same as for the functions to be influenced
Setting ranges and changeover values Dynamic parameters of current pickup and delay times or time multipliers Current stages High-current stage I >> 0.05 to 35.00 A 1) (steps 0.01 A) 0.003 to 1.500 A 2) (steps 0.001 A) or deactivated (stage ineffective) 0.00 to 60.00 s (steps 0.01 s) or deactivated (no trip) 0.05 to 35.00 A 1) (steps 0.01 A) 0.003 to 1.500 A 2) (steps 0.001 A) or deactivated (stage ineffective) 0.00 to 60.00 s (steps 0.01 s) or deactivated (no trip) 3 % of set value or 1 % of rated current at IN = 1 A or 5 A; 5 % of set value or 3 % of rated current at IN = 0.1 A 1 % of set value or 10 ms
Single-phase overcurrent-time protection
TI > Currents
Acc. to ANSI Tolerances Definite time
Currents Times
Times Operating times Pickup time/dropout time Pickup time (in ms) at frequency 7UT612 Minimum Dropout time (in ms), approx.
Inverse time Acc. to IEC Acc. to ANSI
Currents Times Times
The set definite times are pure delay times.
50 Hz 20 30 14 25
60 Hz 18 27 13 22
The set definite times are pure delay times. Operating times of the definite-time stages Pickup time/dropout time Pickup time (in ms) at frequency 7UT 612 Without inrush restraint, min. With inrush restraint, min. Dropout time (in ms), approx. 7UT613/63x Without inrush restraint, min. With inrush restraint, min. Dropout time (in ms), approx. Dropout ratios Current stages Inrush blocking Inrush blocking ratio I2fN/IfN (2nd harmonic) Lower operation limit Max. current for blocking 10 to 45 % I > 0.2 A 1) 0.30 to 25.00 A 1) (steps 0.01 A) (steps 1 %) Approx. 0.95 for I/IN W 0.5 11 33 35 11 29 35 20 40 30 18 35 30 50 Hz 60 Hz
7UT613/63x Minimum Dropout time (in ms), approx. Dropout ratios Current stages Approx. 0.95 for I/IN W 0.5
2) Secondary values for high-sensitivity current input I8, independent of rated current.
Unbalanced load protection (Negative-sequence protection) Characteristics Definite-time stages Inverse-time stages Acc. to IEC Acc. to ANSI Reset characteristics Operating range Current stages High-current stage I2 >> TI2 >> I2 > TI2 > I2P TI2P I2P DI2P 0.10 to 3.00 A 1) (steps 0.01 A) 0.00 to 60.00 s (steps 0.01 s) or deactivated (no trip) (steps 0.01 A) 0.10 to 3.00 A 0.00 to 60.00 s (steps 0.01 s) or deactivated (no trip) (steps 0.01 A) 0.10 to 2.00 A 1) 0.05 to 3.20 s (steps 0.01 s) or deactivated (no trip) (steps 0.01 A) 0.10 to 2.00 A 1) 0.50 to 15.00 s (steps 0.01 s) or deactivated (no trip) 3 % of set value or 1 % of rated current 1 % of set value or 10 ms Pickup at 1.05 w I/IEP w 1.15 5 % 15 ms at fN = 50/60 Hz for 2 w I/IEP w 20 and TIEP/s W 1 5 % 15 ms at fN = 50/60 Hz for 2 w I/IEP w 20 and DIEP/s W 1
Overload protection using a thermal replica (contd) Tripping characteristics Tripping characteristic for I/(k IN) w 8
I k IN
(DT) (IT)
I2 >>, I2 > I2P Inverse, very inverse, extremely inverse Inverse, moderately inverse, very inverse, extremely inverse
Ipre k IN
Acc. to ANSI with disk emulation 0.1 to 4 A 1)
t I Ipre k IN Dropout ratios /trip /alarm I/Ialarm
Tripping time Heating-up time constant Actual load current Preload current Setting factor IEC 60255-8 Rated current of the protected object
Definite-time stage
Dropout at alarm Approx. 0.99 Approx. 0.97
Inverse-time stages Acc. to IEC Inverse-time stages Acc. to ANSI Tolerances Definite-time Inverse time Acc. to IEC Acc. to ANSI
Tolerances (with one 3-phase measuring location) Referring to k IN Referring to tripping time Frequency influence referring to k IN In the range 0.9 w f/fN w 1.1 Thermo-box (temperature monitoring box) Number of measuring points From 1 thermo-box (up to 6 temperature sensors) or from 2 thermo-boxes (up to 12 temperature sensors) 1 % at fN = 50/60 Hz Hot-spot calculation and determination of the ageing rate 3 % or 10 mA 1); class 3 % acc. IEC 60255-8 3 % or 1 s at fN = 50/60 Hz for I/(k IN) > 1.25
Currents Times Currents Times Times
The set definite times are pure delay times. Operating times of the definite-time stages Pickup time/dropout time Pickup time (in ms) at frequency 7UT612 Minimum Dropout time (in ms), approx. 7UT613/63x Minimum Dropout time (in ms), approx. Dropout ratios Current stages Thermal overload protection Overload protection using a thermal replica Multiple availability Setting ranges Factor k acc. IEC 60255-8 Time constant Cooling down factor at motor stand-still (for motors)K-factor Thermal alarm stage alarm/trip Current-based alarm stage Ialarm Start-up recognition (for motors) Istart-up Emergency start run-on time (for motors) Trun-on 0.10 to 4.00 1.0 to 999.9 min 1.0 to 10.0 (steps 0.01) (steps 0.1 min) (steps 0.1) 2 times (option) Warning ageing rate Alarm ageing rate Approx. 0.95 for I2/IN W 0.5 41 23 34 20 50 30 45 30 50 Hz 60 Hz For hot spot calculation one temperature sensor must be connected. Cooling Cooling method
ON (oil natural) OF (oil forced) OD (oil directed) Y 1.6 to 2.0 22 to 29 98 to 140 C 208 to 284 F 98 to 140 C 208 to 284 F 0.125 to 128.000 0.125 to 128.000 (steps 0.1) (steps 1) (steps 1 C) (steps 1 F) (steps 1 C) (steps 1 F) (steps 0.001) (steps 0.001)
Oil exponent
Hot spot to top-oil gradient Hgr Annunciation thresholds Warning temperature hot spot Alarm temperature hot spot
50 to 100 % referred to trip temperature rise (steps 1 %) 0.10 to 4.00 A 1) (steps 0.01 A)
(steps 0.01 A) 0.60 to 10.00 A 1) or deactivated (no start-up recognition) 10 to 15000 s (steps 1 s) 1) Secondary values based on IN = 1 A; for IN = 5 A they must be multiplied by 5.
8 8/31 /31
Thermo-boxes for overload protection Thermo-boxes (connectable) Number of temperature sensors per thermo-box Measuring type Annuciation thresholds For each measuring point: Warning temperature (stage 1) -50 to 250 C (steps 1 C) -58 to 482 F (steps 1 F) or deactivated (no warning) -50 to 250 C (steps 1 C) -58 to 482 F (steps 1 F) or deactivated (no alarm) 2 times (option) (steps 0.01 A) 0.04 to 1.00 A 1) for the respective side Approx. 0.9 for I W 0.25 A 1) 5 % of set value or 0.01 A 1) Binary input for CB auxiliary contact Internal trip External trip (via binary input) Approx. 2 ms (7UT613/63x) and approx. 3 ms (7UT612) with measured quantities present; Approx. 20 ms after switch-on of measured quantities, fN = 50/60 Hz 50 Hz 30 ms 25 ms 60 Hz Undervoltage blocking V1< 30 ms 25 ms Times Pickup times f>, f< Drop-off times f>, f< Drop-off difference f Drop-off ratio V1< Tolerances Frequency Undervoltage blocking Time delays T Reverse-power protection (ANSI 32R) Setting ranges Reverse power PRev.>/SN Time delays T Times Pickup time Drop-off time Drop-off ratio PRev.> Tolerances Reverse power PRev.> Time delays T - 0.5 to - 30 % (steps 0.01 %) 0 to 60 s (steps 0.01 s) or indefinite Approx. 360 ms (50 Hz); Approx. 300 ms (60 Hz) Approx. 360 ms (50 Hz); Approx. 300 ms (60 Hz) Approx. 0.6 0.25 % SN 3 % set value 1 % or 10 ms (steps 0.01 s) 10 to 125 V (steps 0.1 V) Approx. 100 ms Approx. 100 ms Approx. 20 mHz Approx. 1.05 10 mHz (at V> 0.5 VN) 1 % of set value or 0.5 V 1 % or 10 ms 1 or 2 Max. 6 Pt 100 or Ni 100 or Ni 120 Undervoltage protection (definite-time and inverse-time function) (ANSI 27) Setting range Undervoltage pickup V<, V<<, Vp< (positive sequence as phaseto-phase values) Time delays T Time multiplier TM Times Pickup time V<, V<< Drop-off time V<, V<< Drop-off ratio V<, V<<, Vp< Tolerances Voltage limit values Time delays T Inverse-time characteristic Overvoltage protection (ANSI 59) Setting ranges Overvoltage pickup V>, V>> 30 to 170 V (steps 0.1 V) (maximum phase-to-phase voltage or phase-to-earth-voltage) Time delays T 0 to 60 s (steps 0.01 s) or indefinite Times Pickup times V>, V>> Drop-off times V>, V>> Drop-off ratio V>, V>> Tolerances Voltage limit value Time delays T Frequency protection (ANSI 81) Setting ranges Steps; selectable f>, f< Pickup values f>, f< Time delays T 4 40 to 65 Hz (steps 0.01 Hz) 3 stages 0 to 100 s, 1 stage up to 600 s Approx. 50 ms Approx. 50 ms 0.9 to 0.99 (steps 0.01) 1 % of set value 0.5 V 1 % or 10 ms 10 to 125 V (steps 0.1 V)
0 to 60 s (steps 0.01 s) or indefinite 0.1 to 5 s (steps 0.01 s) Approx. 50 ms Approx. 50 ms 1.01 or 0.5 V 1 % of set value or 0.5 V 1 % or 10 ms 1 % of measured value of voltage
Alarm temperature (stage 2)
Breaker failure protection Multiple availability Setting ranges Current flow monitoring Dropoff to pickup ratio Pickup tolerance Breaker status monitoring Starting conditions For breaker failure protection Times Pickup time
Reset time (incl. output relay), approx. 7UT612 7UT613/63x Delay times for all stages Time tolerance Setting ranges Pickup threshold alarm stage Pickup threshold V/f>>-stage Time delays T Characteristic values of V/f and assigned times t (V/f) Cooling down time TCooling
0.00 to 60.00 s; deactivated (steps 0.01 s) 1 % of setting value or 10 ms
Overexitation protection (Volt / Hertz) (7UT613 / 633 only) 1 to 1.2 (steps 0.01) 1 to 1.4 (steps 0.01) 0 to 60 s (steps 0.01 s) or deactivated 1.05/1.1/1.15/1.2/1.25/1.3/1.35/1.4 0 to 20000 s (steps 1 s) 0 to 20000 s (steps 1 s) 60 Hz 31 23
Times (in ms) (alarm and V/f>>-stage) 50 Hz Pickup times at 1.1 of set value, approx. 36 Drop-off times, approx. 28 Drop-off ratio (alarm, trip) Tolerances V/f-Pickup Time delays T Thermal characteristic (time) 0.95
3 % of set value 1 % or 10 ms 5 % rated to V/f or 600 ms
Forward-power protection (ANSI 32F) Setting ranges Forward power PForw.</SN Forward power PForw.>/SN Time delays T Times Pickup time (accurate measuring) Pickup time (fast measuring) Drop-off time (accurate measuring) Drop-off time (fast measuring) Drop-off ratio PForw.< Drop-off ratio PForw.> Tolerances Active power PForw.<, PForw.> 0.5 to 120 % (steps 0.1 %) 1 to 120 % (steps 0.1 %) 0 to 60 s (steps 0.01 s) or indefinite Approx. 360 ms (50 Hz); Approx. 300 ms (60 Hz) Approx. 60 ms (50 Hz); Approx. 50 ms (60 Hz) Approx. 360 ms (50 Hz); Approx. 300 ms (60 Hz) Approx. 60 ms (50 Hz); Approx. 50 ms (60 Hz) 1.1 or 0.5 % of SN Approx. 0.9 or 0.5 % of SN 0.25 % SN 3 % of set value at Q < 0.5 SN at accurate measuring 0.5 % SN 3 % of set value at Q < 0.5 SN at fast measuring 1 % or 10 ms Trip circuit supervision Trip circuits Number of supervised trip circuits Operation of each trip circuit 1 With 1 binary input or with 2 binary inputs 12 Measurement location or side selectable I, I1, I2, 3I0, V, V1, V2, V0, P, Q, cos I, IE, IE sens., V, P, Q, cos f, binary input Exceeding or falling below threshold value 0.05 to 35 A (steps of 0.01 A) 0.001 to 1.5 A (steps of 0.001 A) 1 to 170 V (steps of 0.1 V) 1 to 200 V (steps of 0.1 V) 1.6 to 3000 W (steps of 0.1 W) 0.01 to 17 P/SN, Q/SN, (steps of 0.01) - 0.99 to + 0.99 (steps of 0.01) 10 to 66 Hz (steps of 0.01 Hz) 0 to 60 s (steps of 0.01 s) 0 to 3600 s (steps of 0.01 s) 0 to 60 s (steps of 0.01 s) On request (see Manual) On request (see Manual) On request (see Manual)
Flexible protection functions (ANSI 27, 32, 47, 50, 55, 59,81) N. of selectable stages Operating modes / measuring quantities 3-phase 1-phase Without fixed phase relation Pickup when Setting ranges Current I, I1, I2, 3I0, IE Sens. earth curr. IE sens. Voltages V, V1, V2, V0 Displacement voltage VE Power P, Q Power P, Q (side) Power factor (cos ) Frequency fN = 50/60 Hz Pickup delay time Trip delay time Dropout delay time Times Dropout times Tolerances Additional functions Operational measured values Operational measured values of currents, 3-phase for each side and measurement location Tolerance at IN = 1 or 5 A Tolerance at IN = 0.1 A Operational measured values of currents, 3-phase for each side and measurement location Tolerance Operational measured values of currents 1-phase for each measurement location Tolerance at IN = 1 or 5 A Tolerance at IN = 0.1 A For high-sensitivity inputs Tolerance Feeder 7UT612 7UT613 7UT633 7UT635 I1 to I7 I1 to I9 I1 to I9 I1 to I12 Further I7 to I8 Ix1 to Ix3 Ix1 to Ix3 Ix1 to Ix4 IL1; IL2; IL3 in A primary and secondary and % of IN 1 % of measured value or 1 % of IN 2 % of measured value or 2 % of IN 3I0; I1; I2 in A primary and secondary and % of IN 2 % of measured value or 2 % of IN
Time delays T External trip commands Binary inputs Number of binary inputs for direct tripping Operating time Dropout time Delay time Expiration tolerance Transformer annunciations External annunciations
2 Approx. 12.5 ms min. Approx. 25 ms typical Approx. 25 ms 0.00 to 60.00 s (steps 0.01 s) 1 % of set value or 10 ms
The set definite times are pure delay times. Buchholz warning Buchholz tank Buchholz tripping |Imin| / |Imax| < BAL. FAKT. I if Imax / IN > BAL. I LIMIT / IN 0.10 to 0.90 (steps 0.01) (steps 0.01 A) 0.10 to 1.00 A 1) |Vmin| / |Vmax| < BAL. FAKT. if |Vmax| > BALANCE V-LIMIT |VL1+ VL2+ VL3- kV VEN| > 25 V IL1 before IL2 before IL3 (clockwise) or IL1 before IL3 before IL2 (counter-clockwise) if |IL1|, |IL2|, |IL3| > 0.5 IN VL1 before VL2 before VL3 (clockwise) or VL1 before VL3 before VL2 (counter-clock) if |VL1|, |VL2|, |VL3| > 40 V/H3 Unexpected instantaneous current value and current interruption or missing zero crossing detects failure of the measured voltage
Measured quantities supervision Current symmetry (for each measurement location) BAL. FAKT. I BAL. I LIMIT Voltage symmetry (if voltages applied) Voltage sum (if voltages applied) Current phase sequence
in A primary and secondary and % of IN 1 % of measured value or 1 % of IN 2 % of measured value or 2 % of IN in A primary and secondary 1 % of measured value or 2 mA High-sensitivity I8 Ix3 Ix3 Ix3, Ix4 (IL1); (IL2); (IL3) in , referred to (IL1) 1 at rated current
Voltage phase sequence (if voltages applied)
Phase angles of currents, 3-phase for each measurement location Tolerance
Operational measured values (cont'd) Phase angles of currents, 7UT612 7UT613 7UT633 7UT635 1-phase for each measurement location Tolerance Operational measured values of voltages (7UT613/633 only) 3-phase (if voltage applied) Tolerance Tolerance 1-phase (if voltage applied) Tolerance Phase angles of voltages (7UT613/633 only, if voltages applied) Tolerance Operational measured values of frequency Range Tolerance Operational measured values of power (I1) to (I8) (I1) to (I9), (Ix1) to (Ix3) (I1) to (I9), (Ix1) to (Ix4) (I1) to (I12), (Ix1) to (Ix4) in , referred to (I1) 1 at rated current in kV primary and V secondary and % of VN VL1-E, VL2-E, VL3-E, VL1-L2, VL2-L3, VL3-L1, 0.2 % of measured value or + 0.2 V V1, V2, V0, 0.4 % of measured value or + 0.4 V VEN or V4 0.2 % of measured value or + 0.2 V (VL1-E)), (VL2-E), (VL3-E)), (V4), (VEN) 1 at rated voltage f in Hz and % of fN 10 to 75 Hz 1 % within range fN 10 % and I W IN S 7UT612 7UT613 7UT633 7UT635 S (apparent power) P (active power) Q (reactive power) x x x x P x x Q x x Max. / Min. / Mean report Report of measured values Reset, automatic With date and time from all sides and measurement locations Time of day adjustable (in minutes, 0 to 1439 min) Time frame and starting time adjustable (in days, 1 to 365 days, and ) Using binary input, using keypad, via communication IL1, IL2, IL3, I1 (positive-sequence component) I2 (negative-sequence component), 3I0, IDIFF L1, IDIFF L2, IDIFF L3, IRESTR.L1, IRESTR.L2, IRESTR.L3 VL1-E, VL2-E, VL3-E V1 (positive-sequence component) V2 (negative-sequence component) V0, VE, VL1-L2, VL2-L3, VL3-L1 S, P, Q, cos , frequency see above With a total of max. 200 messages
Min./max./mean values for current
Min./max./mean values for voltages
Min./max./mean values for power Min./max. for mean values Fault event log Storage of the messages of the last 8 faults Fault recording Number of stored fault records Storage period (start with pickup or trip)
Max. 8 Max. 5 s for each fault, Approx. 5 s in total 7UT 612 613 633 635
Applied or rated voltage Only if voltage applied, 7UT613/633 only Only if voltage applied, 7UT613/633 only, in kVA; MVA; GVA primary cos (p.f.) Only if voltage applied, 7UT613/633 only V/f Only if voltage applied, 7UT613/633 only 2 % of measured value L1; L2; L3; res, referred to tripping temperature rise trip thermo-box1 to thermo-box12 in C or F relative aging rate, load reserve IDIFF L1; IDIFF L2; IDIFF L3; IREST L1; IREST L2; IREST L3 in % of operational rated current 2 % of measured value or 2 % of IN (50/60 Hz) 3 % of measured value or 3 % of IN (16.7 Hz) IDIFFREF; IRestREF in % of operational rated current 2 % of measured value or 2 % of IN (50/60 Hz) 3 % of measured value or 3 % of IN (16.7 Hz)
Sampling rate at fN = 50 Hz Sampling rate at fN = 60 Hz Switching statistics Number of trip events caused by 7UT6
600 Hz 800 Hz 800 Hz 800 Hz 720 Hz 960 Hz 960 Hz 960 Hz
Operational measured value of power factor Overexcitation
Total of interrupted currents caused Segregated for each pole, each side by 7UT6 and each measurement location Operating hours Criterion Real-time clock and buffer battery Resolution for operational messages 1 ms Resolution for fault messages Buffer battery 1 ms 3 V/1 Ah, type CR 1/2 AA Self-discharging time approx. 10 years Up to 7 decimal digits Excess of current threshold
Tolerance Operational measured values for thermal value Operational measured values (Overload protection acc. to IEC 60354) Measured values of differential protection Tolerance (with preset values)
Time synchronization Operating modes: Internal IEC 60870-5-103 Time signal IRIG B Time signal DCF77 Time signal synchro-box Pulse via binary input Internal via RTC External via system interface (IEC 60870-5-103) External via IRIG B External, via time signal DCF77 External, via synchro-box External with pulse via binary input
Measured values of restricted earth-fault protection Tolerance (with preset values)
7UT612 differential protection relay for transformers, generators, motors and busbars Housing 1/3 x 19; 3 BI, 4 BO, 1 live status contact, 7 I, IEE1)
Rated current IN = 1 A IN = 5 A Rated auxiliary voltage (power supply, binary inputs) 24 to 48 V DC, binary input threshold 17 V 2) 60 to 125 V DC 3), binary input threshold 17 V 2) 110 to 250 V DC, 115/230 V AC, binary input threshold 73 V 2) Unit design For panel surface mounting, two-tier terminals on top and bottom
7UT612o-o - o A0
For panel flush mounting, plug-in terminals (2/3-pole AMP connector) For panel flush mounting, screw-type terminals, (direct wiring/ring lugs) Region-specific default settings/function and language settings Region DE, 50/60 Hz, IEC/ANSI, language German; selectable Region World, 50/60 Hz, IEC/ANSI, language English (GB); selectable Region US, 60/50 Hz, ANSI/IEC, language English (US); selectable Region World, 50/60 Hz, IEC/ANSI, language Spanish; selectable System interface (Port B ) on rear No system interface IEC 60870-5-103 protocol, electrical RS232 IEC 60870-5-103 protocol, electrical RS485 IEC 60870-5-103 protocol, optical 820 nm, ST connector PROFIBUS-FMS Slave, electrical RS485 PROFIBUS-FMS Slave, optical, single loop, ST connector4) PROFIBUS-FMS Slave, optical, double loop, ST connector4) PROFIBUS-DP Slave, electrical RS485 PROFIBUS-DP Slave, optical 820 nm, double loop, ST connector4) MODBUS, electrical RS485 MODBUS, optical 820 nm, ST connector4) DNP 3.0, electrical RS485 DNP 3.0, optical 820 nm, ST connector4) IEC 61850, 100 Mbit Ethernet, electrical, double, RJ45 connector (EN 100) IEC 61850, 100 Mbit Etherent, optical, double, LC connector (EN 100)5)
A B C E 0 1 2 3 4 5 6 9 9 9 9 9 9 9 9
0A 0B 0D 0 E 0G 0H 0R 0S
1) Sensitivity selectable normal/high. 2) The binary input thresholds are selectable in two stages by means of jumpers. 3) Transition between the two auxiliary voltage ranges can be selected by means of jumpers. 4) With surface-mounting housing: only RS485 interface available. 5) If position 9 = B (surface-mounting housing), please order relay with electrical Ethernet interface and use a separate FO switch. See next page
7UT612 differential protection relay for transformers, generators, motors and busbars
7UT612o - o- o A0
DIGSI 4/browser/modem interface (Port C) on rear/temperature monitoring box connection No DIGSI 4 port DIGSI 4/browser, electrical RS232 DIGSI 4/browser or temperature monitoring box1), electrical RS485 DIGSI 4/browser or temperature monitoring box1), 820 nm fiber optic, ST connector Functions Measured values/monitoring functions Basic measured values Basic measured values, transformer monitoring functions (connection to thermo-box/hot spot acc. to IEC, overload factor) Differential protection + basic functions Differential protection for transformer, generator, motor, busbar (87) Overload protection for one winding (49), Lockout (86) Overcurrent-time protection (50/51): I>, I>>, IP (inrush stabilization) Overcurrent-time protection (50N/51N): 3I0>, 3I0>>, 3I0P (inrush stabilization) Overcurrent-time protection earth (50G/51G): IE>, IE>>, IEP (inrush stabilization) Differential protection + basic functions + additional functions Restricted earth fault protection, low impedance (87N) Restricted earth fault protection, high impedance (87N without resistor and varistor), O/C 1-phase Trip circuit supervision (74TC), breaker failure protection (50BF), unbalanced load protection (46)
1) External temperature monitoring box required.
7UT613 differential protection relay 7UT613o-o - ooo for transformers, generators, motors and busbars Housing 1/2 x 19; 5 BI, 8 BO, 1 live status contact, 11 I, IEE1)
Rated current IN = 1 A IN = 5 A Rated auxiliary voltage (power supply, binary inputs) 24 to 48 V DC, binary input threshold 17 V2) 60 to 125 V DC3), binary input threshold 17 V2) 110 to 250 V DC1), 115/230 V AC, binary input threshold 73 V2) 110 to 250 V DC1), 115/230 V AC, binary input threshold 154 V2) Unit design Surface-mounting housing with two-tier terminals Flush-mounting housing with plug-in terminals Flush-mounting housing with screw-type terminals Region-specific default settings/language settings Region DE, 50/60 Hz, IEC/ANSI, language German; selectable Region World, 50/60 Hz, IEC/ANSI, language English (GB); selectable Region US, 60/50 Hz, ANSI/IEC, language English (US); selectable Region World, 50/60 Hz, IEC/ANSI, language French; selectable Region World, 50/60 Hz, IEC/ANSI, language Spanish; selectable System interface (Port B ) on rear No system interface IEC 60870-5-103 protocol, electrical RS232 IEC 60870-5-103 protocol, electrical RS485 IEC 60870-5-103 protocol, optical 820 nm, ST connector PROFIBUS-FMS Slave, electrical RS485 PROFIBUS-FMS Slave, optical, single ring, ST connector4) PROFIBUS-FMS Slave, optical, double ring, ST connector4) PROFIBUS-DP Slave, electrical RS485 PROFIBUS-DP Slave, optical 820 nm, double ring, ST connector4) MODBUS, electrical RS485 MODBUS, optical 820 nm, ST connector4) DNP 3.0, electrical RS485 DNP 3.0, optical 820 nm, ST connector4) IEC 61850, 100 Mbit Ethernet, electrical, double, RJ45 connector (EN 100) IEC 61850, 100 Mbit Etherent, optical, double, LC connector (EN 100)5)
B D E A B C D E 0 1 2 3 4 5 6 9 9 9 9 9 9 9 9
A B D E G H R S
1) Sensitivity selectable normal/high. 2) The binary input thresholds are selectable in two stages by means of jumpers. 3) Transition between the two auxiliary voltage ranges can be selected by means of jumpers. 4) With surface-mounting housing: only RS485 interface available. 5) If position 9 = B (surface-mounting housing), please order relay with electrical Ethernet interface and use a separate FO switch.
7UT613 differential protection relay for transformers, generators, motors and busbars
Port C and Port D Port C: DIGSI 4/modem, electrical RS232; Port D: empty
7UT613o-o - ooo
Port C: DIGSI 4/modem/thermo-box, electrical RS485; Port D: empty Port C and Port D installed Port C (service interface) DIGSI 4/modem, electrical RS232 DIGSI 4/modem/thermo-box, electrical RS485 Port D (additional interface) Thermo-box, optical 820 nm, ST connector Thermo-box, electrical RS485 Measured values/monitoring functions Basic measured values Extended measured values, min./max. values, mean values Extended measured values, min./max., mean values, transformer monitoring functions (connection to thermo-box/hot spot, overload factor) Differential protection + basic functions Differential protection for transformer, generator, motor, busbar (87) Overload protection according to IEC for one side (49) Lock out (86) Overcurrent-time protection phases (50/51): I>, I>>, IP (inrush stabilization) Overcurrent-time protection 3 I0 (50N/51N): 3 I0>, 3 I0>>, 3 I0P (inrush stabilization) Overcurrent-time protection earth (50G/51G): IE>, IE>>, IEP (inrush stabilization)
M oo 1 2 A F 1 2 4
Differential protection + basic functions + additional current functions Restricted earth-fault protection, low impedance (87N) Restricted earth-fault protection, high impedance (87N without resistor and varistor), O/C 1-phase Trip circuit supervision (74TC) Unbalanced load protection (46) Breaker failure protection (50BF) High-sensitivity overcurrent-time protection/tank leakage protection (64), O/C 1-phase Additional voltage functions Without voltage functions With overexcitation protection and voltage/power/energy/measurement With overexcitation protection and voltage/power/energy measurement + Over/undervoltage protection (59/27) + Frequency protection (81) + Directional power protection (32R/F) + Fuse failure monitor (60FL) Additional functions (general) Without Multiple protection functions (50, 51, 50N/G, 87N, 50BF, 49)1) Flexible protection functions Multiple + flexible protection functions
C 0 1 2 3
1) Available if selected on position 14.
7UT63o differential protection relay for transformers, generators, motors and busbars, graphic display
Housing, inputs and outputs Housing 1/1 x 19, 21 BI, 24 BO, 1 live status contact 12 current inputs (11 I, IEE1)); 4 voltage inputs (1 x 3-phase + 1 x 1-phase) Housing 1/1 x 19, 29 BI, 24 BO, 1 live status contact 16 current inputs (14 I, 2 IEE1)) Rated current IN = 1 A IN = 5 A Rated auxiliary voltage (power supply, binary inputs) 24 to 48 V DC, binary input threshold 17 V2) 60 to 125 V DC3), binary input threshold 17 V2) 110 to 250 V DC1), 115/230 V AC, binary input threshold 73 V2)
7UT63- -
110 to 250 V DC1), 115/230 V AC, binary input threshold 154 V2) Unit design Surface-mounting with two-tier terminals Flush-mounting with plug-in terminals Flush-mounting with screw-type terminals Surface mounting with two-tier terminals, with 5 high-speed trip contacts Flush-mounting with plug-in terminals, with 5 high-speed trip contacts Flush-mounting with screw-type terminals, with 5 high-speed trip contacts Region-specific default settings/language settings Region DE, 50/60 Hz, IEC/ANSI language German; selectable Region World, 50/60 Hz, IEC/ANSI language English (GB); selectable Region US, 60/50 Hz, ANSI/IEC language English (US); selectable Region World, 50/60 Hz, IEC/ANSI, language French; selectable Region World, 50/60 Hz, IEC/ANSI language Spanish; selectable System interface (Port B ) on rear No system interface IEC 60870-5-103 protocol, electrical RS232 IEC 60870-5-103 protocol, electrical RS485 IEC 60870-5-103 protocol, optical 820 nm, ST connector PROFIBUS-FMS Slave, electrical RS485 PROFIBUS-FMS Slave, optical, single ring, ST connector4) PROFIBUS-FMS Slave, optical, double ring, ST connector4) PROFIBUS-DP Slave, electrical RS485 PROFIBUS-DP Slave, optical 820, double ring, ST connector4) MODBUS, electrical RS485 MODBUS, optical 820 nm, ST connector4) DNP 3.0, electrical RS485 1) Sensitivity selectable normal/high. 2) The binary input thresholds are selectable in two stages by means of jumpers. DNP 3.0, optical 820 nm, ST connector4) IEC 61850, 100 Mbit Ethernet, electrical, double, RJ45 connector (EN 100) IEC 61850, 100 Mbit Ethernet, optical, double, LC connector (EN 100)5)
B D E N P Q
A B C D E 0 1 2 3 4 5 6 9 9 9 9 9 9 9 9
3) Transition between the two auxiliary voltage ranges can be selected by means of jumpers. 4) With surface-mounting housing: only RS485 interface available. 5) If position 9 = B (surface-mounting housing), please order relay with electrical Ethernet interface and use a separate FO switch.
7UT63-o -
Port C: DIGSI 4/modem/thermo-box, electrical RS485; Port D: empty Port C and Port D installed Port C (service interface) DIGSI 4/modem, electrical RS232 DIGSI 4/modem/thermo-box, electrical RS485 Port D (additional interface) Thermo-box, optical 820 nm, ST connector Thermo-box, electrical RS485 Measured values/monitoring functions Basic measured values Extended measured values, min./max. values, mean values
Extended measured values, min./max. values, mean values, transformer monitoring functions (connection to thermo-box/hot spot, overload factor) Differential protection + basic functions Differential protection for transformer, generator, motor, busbar (87) Overload protection according to IEC for one side (49) Lock out (86) Overcurrent-time protection phases (50/51): I>, I>>, IP (inrush stabilization) Overcurrent-time protection 3 I0 (50N/51N): 3 I0>, 3 I0>>, 3 I0P (inrush stabilization) Overcurrent-time protection earth (50G/51G): IE>, IE>>, IEP (inrush stabilization) Differential protection + basic functions + additional current functions Restricted earth-fault protection, low impedance (87N) Restricted earth-fault protection, high impedance (87N without resistor and varistor), O/C 1-phase Trip circuit supervision (74TC) Unbalanced load protection (46) Breaker failure protection (50BF) High-sensitivity overcurrent-time protection/tank leakage protection (64), O/C 1-phase Additional voltage functions (only with 7UT633) Without voltage functions With overexcitation protection and voltage/power/energy/measurement With overexcitation protection and voltage/power/energy measurement + Over/undervoltage protection (59/27) + Frequency protection (81) + Directional power protection (32R/F) + Fuse failure monitor (6FL) Additional functions (general) Without Multiple protection functions (50, 51, 50N/G, 87N, 50BF, 49)1) Flexible protection functions Multiple + flexible protection functions
1) Available if selected on position 14
Description DIGSI 4 Software for configuration and operation of Siemens protection relays running under MS Windows (Windows 2000/XP Professional Edition), device templates, Comtrade Viewer, electronic manual included as well as Getting started manual on paper, connecting cables (copper) Basis Full version with license for 10 computers, on CD-ROM (authorization by serial number) Professional DIGSI 4 Basis and additionally SIGRA (fault record analysis), CFC Editor (logic editor), Display Editor (editor for default and control displays) and DIGSI 4 Remote (remote operation) Professional + IEC 61850 DIGSI 4 Basis and additionally SIGRA (fault record analysis), CFC Editor (logic editor), Display Editor (editor for default and control displays) and DIGSI 4 Remote (remote operation) + IEC 61850 system configurator IEC 61850 System configurator Software for configuration of stations with IEC 61850 communication under DIGSI, running under MS Windows 2000 or XP Professional Edition Optional package for DIGSI 4 Basis or Professional License for 10 PCs. Authorization by serial number. On CD-ROM SIGRA 4 (generally contained in DIGSI Professional, but can be ordered additionally) Software for graphic visualization, analysis and evaluation of fault records. Can also be used for fault records of devices of other manufacturers (Comtrade format) running under MS Windows 2000/XP Professional Edition. Incl. templates, electronic manual with license for 10 PCs. Authorization by serial number. On CD-ROM. Connecting cable Cable between PC/notebook (9-pin connector) and protection relay (9-pin connector) (contained in DIGSI 4, but can be ordered additionally) Cable between thermo-box and relay - length 5 m / 16.4 ft - length 25 m / 82 ft - length 50 m / 164 ft Voltage transformer miniature circuit-breaker Rated current 1.6 A; Thermal overload release 1.6 A; Overcurrent trip 6 A Temperature monitoring box with 6 thermal inputs For SIPROTEC units With 6 temperature sensors and 24 to 60 V AC/DC 90 to 240 V AC/DC RS485 interface Manual for 7UT612 English Manual for 7UT6 English V4.0 English V4.6
C53000-G1176-C148-1
C53000-G1176-C160-1 C53000-G1176-C160-2
Description Connector Crimp connector 2-pin 3-pin CI2 0.5 to 1 mm2 CI2 1 to 2.5 mm2
LSP2091-afpen.eps
Order No. C73334-A1-C35-1 C73334-A1-C36-1 0-827039-1 0-827396-1 0-827040-1 0-827397-1 0-163083-7 0-163084-2 0-539635-1 0-539668-2 0-734372-1 1-734387-1 C73165-A63-D200-1 For current contacts For voltage contacts large small C73334-A1-C33-1 C73334-A1-C34-1 C73334-A1-C31-1 C73334-A1-C32-1
Fig. 8/35 8/36
Fig. 8/34 Mounting rail for 19" rack
LSP2090-afpen.eps
Type III+ 0.75 to 1.5 mm2 Crimping tool For Type III+ and matching female For CI2 and matching female
Fig. 8/35 2-pin connector
Fig. 8/36 3-pin connector
19" mounting rail
8/34 8/37 8/38
Short-circuit links Safety cover for terminals
Fig. 8/37 Short-circuit link for current contacts
Fig. 8/38 Short-circuit link for voltage contacts
Fig. 8/39
Fig. 8/40a Additional setting by jumpers: Separation of common circuit of fast BO1 to BO5 with jumpers X80, X81, X82. Switching of fast BO7, BO8 as NO contact or NC contact with jumpers X41, X42, X43.
Fig. 8/40
Connection diagram 7UT613
1) Configuration of binary outputs up to hardware-version .../CC For advanced flexibility see Fig. 8/40a.
Fig. 8/41a Additional setting by jumpers: Separation of common circuit of fast BO1 to BO5 with jumpers X80, X81, X82. Switching of fast BO7, BO8 as NO contact or NC contact with jumpers X41, X42, X43.
1) Configuration of binary outputs up to hardware-version .../CC For advanced flexibility see Fig. 8/41a. 2) High-speed contacts (option), NO only 3) High-speed contacts (option)
Fig. 8/41
Connection diagram 7UT63
Fig. 8/42
Connection diagram 7UT635 part 1; continued on following page
1) High-speed contacts (option), NO only 2) High-speed contacts (option)
Fig. 8/43
Connection diagram 7UT635 part 2
Dokumente ähnlich wie siprotec4 7ut6 catalog sip e6
1MRK511230-UEN_en_Application_manual__REC670_1.2.pdf
V265M en M A005 Motor Diff Prot
INSTRUCTION MANUAL SMPR
Sympatetic Trip
RifqiRobuzaRohman
11ADA10CE001 Ph.A
Mehr von api-241473079
Beliebt in Electrical Substation
Lec 20, Protection 1
Jmrc,Jaipur Report
CV MIDHUN
ARR Order
T155 420 - 550 kV Gas-Insulated Substations Brochure GB
muneeswaran14