Source: http://lawfilesext.leg.wa.gov/Law/WSR/2007/03/07-03-043.htm
Timestamp: 2020-08-06 08:17:12
Document Index: 57889337

Matched Legal Cases: ['§ 51', '§ 51', '§ 51', '§ 51', '§ 51', '§ 51', '§ 51', '§ 51']

WSR 07-03-043
[ Filed January 11, 2007, 10:59 a.m. , effective July 1, 2007 ]
Purpose: To adopt and amend the 2006 Edition of the Uniform Plumbing Code Appendices, chapter 51-57 WAC.
OTS-8966.1
WAC 51-57-003 Uniform Plumbing Code Standards. The ((2003)) 2006 edition of the Uniform Plumbing Code Standards (Appendixes A, B and I), published by the International Association of Plumbing and Mechanical Officials are hereby adopted by reference.
[Statutory Authority: RCW 19.27.031 and 19.27.074. 04-01-110, § 51-57-003, filed 12/17/03, effective 7/1/04; 02-01-114, § 51-57-003, filed 12/18/01, effective 7/1/02.]
WAC 51-57-004 Conflicts between Appendix I and the manufacturer's installation instructions. Where a conflict exists between the provisions of Appendix I and the manufacturer's installation instructions, the conditions of the listing and the manufacturer's installation instructions shall apply.
WAC 51-57-007 Exceptions. The exceptions and amendments to the ((Uniform)) Model Codes contained in the provisions of chapter 19.27 RCW shall apply in cases of conflict with any of the provisions of these rules.
[Statutory Authority: RCW 19.27.031, 19.27.074. 02-01-114, § 51-57-007, filed 12/18/01, effective 7/1/02.]
WAC 51-57-008 Implementation. The Uniform Plumbing Code Standards adopted by chapter 19.27 RCW shall become effective in all counties and cities of this state on July 1, ((2004)) 2007, unless local government residential amendments have been approved by the state building code council.
[Statutory Authority: RCW 19.27.031 and 19.27.074. 04-01-110, § 51-57-008, filed 12/17/03, effective 7/1/04; 02-01-114, § 51-57-008, filed 12/18/01, effective 7/1/02.]
((301.1.1 Materials. Materials shall comply with the following:
((Materials ASTM Std
Raw Material - CPVC 23447-B D1784-95
Sch 40 (1/2 in., 3/4 in., and 1 in.) F 441-89e1
Sch 80 (1/2 in. - 2 in.) F 441-94
SDR 11 (1/2 in. - 2 in.) D2846-93
Sch 40 (1/2 in., 3/4 in., and 1 in.) F 438-93
Sch 80 (1/2 in. - 2 in.) F 439-93a
Tube Fittings (1/2 in. - 2 in.) D2846-93))
EXCEPTION: Listed solvent cements that do not require the use of primer shall be permitted for use with CPVC pipe and fittings, manufactured in accordance with ASTM D2845 (((1/2 in. - 2 in.))), 1/2 inch through 2 inches in diameter.
[Statutory Authority: RCW 19.27.031 and 19.27.074. 04-01-110, § 51-57-202000, filed 12/17/03, effective 7/1/04.]
WAC 51-57-790000 Installation Standard ((7-90)) 7-03 -- Polyethylene cold water building supply and yard piping.
((604.1)) 2.6.1 Location. Polyethylene piping may terminate within a building or structure. The connection to the potable water distribution system shall be accessible, except that it may be buried underground outside of the building or structure in an accessible location. Barbed insert fittings with hose clamps are prohibited within a building.
[Statutory Authority: RCW 19.27.031, 19.27.074. 02-01-114, § 51-57-790000, filed 12/18/01, effective 7/1/02.]
WAC 51-57-895000 Installation Standard ((8-95)) 8-03 -- PVC cold water building supply and yard piping.
((604.1)) 2.7.1 Location. PVC piping may terminate within a building or structure. The connection to the potable water distribution system shall be accessible, except that it may be buried underground outside of the building or structure in an accessible location.
[Statutory Authority: RCW 19.27.031, 19.27.074. 02-01-114, § 51-57-895000, filed 12/18/01, effective 7/1/02.]