Source: https://www.scribd.com/document/374252658/info-iec62271-202-ed2-0-b
Timestamp: 2018-12-15 14:18:55
Document Index: 529648291

Matched Legal Cases: ['art 202', 'art 202', 'art 2', 'art 202', 'art 2', 'art 2', 'art 1', 'art 3', 'art 1', 'art 1', 'art 2', 'art 7', 'art 1', 'art 2', 'art 1', 'art 2', 'art 13', 'art 1', 'art 4', 'art 11', 'art 1', 'art 12', 'art 5', 'art 10', 'art 1', 'art 300', 'art 1', 'art 200', 'art 208', 'art 201', 'art 1']

info_iec62271-202{ed2.0}b | Electrical Substation | High Voltage
info_iec62271-202{ed2.0}b
Uploaded by Sila Silva
NORME INTERNATIONALE IEC 62271-202
Powerline 2007 Jan-feb
32-TMSS-07-R0
subdividedsystems.ppt
11-2-SecivbPreComm
10-7RW600E.pdf
PLANO DIRETOR. DOM 3332 16.01.2014 EEs.pdf
Manual_Bombas_de_Incendio.pdf
1424_14_Manual-Biodigestor_web.pdf
resolucao_51_apresentacao_de_projetos.pdf
sistemas de ventilação para estacionamento.pdf
lei_pro_aguas.pdf
N03Cap4.pdf
NBR13103_-_2006_-_Instalacao_de_aparelho_de_gas_para_uso_residencial.pdf
127160334-NBR-6925-Conexao-de-ferro-fundido-maleavel-de-classes-150-e.pdf
NBR-15.527-Aproveitamento-água-da-chuva.pdf
Criterios de Hidrometracao (Manual Empreendedor) v 18 07 13 (2)
ABNT-LUMINÁRIA.pdf
NBR_13714_Hidrantes_e_mangotinhos.pdf
IT-21-11
Edition 2.0 2014-03
INTERNATIONALE colour
Part 202: High-voltage/low-voltage prefabricated substation
Partie 202: Postes préfabriqués haute tension/basse tension
INTERNATIONALE PRICE CODE
CODE PRIX XD
ICS 29.130.10 ISBN 978-2-8322-1483-1
–2– IEC 62271-202:2014 © IEC 2014
FOREWORD ........................................................................................................................... 8
1 General ......................................................................................................................... 11
1.1 Scope .............................................................................................................. 11
1.2 Normative references ....................................................................................... 11
2 Normal and special service conditions ........................................................................... 13
2.1 Normal service conditions ................................................................................ 13
2.1.1 Indoor switchgear and controlgear .................................................. 13
2.1.1.101 Low-voltage switchgear and controlgear ......................................... 13
2.1.1.102 Transformer .................................................................................... 13
2.1.2 Outdoor switchgear and controlgear ............................................... 14
2.2 Special service conditions ................................................................................ 14
2.2.1 Altitude ........................................................................................... 14
2.2.2 Pollution ......................................................................................... 14
2.2.3 Temperature and humidity .............................................................. 15
2.2.4 Vibrations, shock or tilting............................................................... 15
2.2.5 Wind speed .................................................................................... 15
2.2.6 Other parameters ........................................................................... 15
3 Terms and definitions .................................................................................................... 15
4 Ratings .......................................................................................................................... 17
4.1 Rated voltage (U r ) ........................................................................................... 18
4.2 Rated insulation level ....................................................................................... 18
4.3 Rated frequency (f r ) ......................................................................................... 19
4.4 Rated normal current and temperature rise ...................................................... 19
4.4.1 Rated normal current (I r ) ................................................................ 19
4.4.2 Temperature rise ............................................................................ 19
4.4.3 Particular points of Table 3 ............................................................. 19
4.5 Rated short-time withstand current (I k ) ............................................................ 19
4.5.101 Rated short-time withstand current of high voltage switchgear
and controlgear and high voltage interconnection (I k ) ..................... 20
4.5.102 Rated short-time phase to earth withstand current (I ke ) .................. 20
4.5.103 Rated short-time withstand currents of low voltage switchgear
and controlgear and low voltage interconnection (I cw) .................... 20
4.6 Rated peak withstand current (I p ) .................................................................... 20
4.6.101 Rated peak withstand current (I p ) ................................................... 20
4.6.102 Rated peak phase to earth withstand current (I pe ) .......................... 20
4.6.103 Rated peak withstand currents of low voltage switchgear and
controlgear and low voltage interconnection (I pk ) ........................... 20
4.7 Rated durations of short circuit (t k ) .................................................................. 20
4.7.101 Rated duration of short circuit (t k ) ................................................... 21
4.7.102 Rated duration of phase to earth short circuit (t ke ) ......................... 21
4.7.103 Rated duration of short circuits for low voltage switchgear and
controlgear and low voltage interconnection ................................... 21
4.7.104 Rated duration of short circuits for transformers ............................. 21
4.8 Rated supply voltage of closing and opening devices and auxiliary and
control circuits (U a ) .......................................................................................... 21
4.9 Rated supply frequency of closing and opening devices and of auxiliary
circuits ............................................................................................................. 21
.........1 Provisions for dielectric tests on cables ....................................................................................................................104...................104.............................................................. AB) ..105.............1 Rated maximum power of the prefabricated substation .......................................................................................... 30 5........4 Labels .......... 26 5............ 25 5.105 Other provisions............. 23 5.......................................................................107 Electromagnetic fields .11 Rated filling levels for insulation and/or operation ...............................................................................................................................................104....................................................................................................... 22 4............ 25 5....102 Ratings of the internal arc classification ........................ 24 5..1 Requirements for liquids in switchgear and controlgear ...... 25 5..........18 Electromagnetic compatibility (EMC) ....................................................104......................................................15 Gas and vacuum tightness ....................................................2 Rated class of enclosure ................................17 Fire hazard (flammability) ......................... 28 5............................... 22 4...................................................................2 Requirements for gases in switchgear and controlgear ............. This is a preview ......................104 Enclosure ...........101. 25 5...............105...................16 Liquid tightness ....... 31 5.............................................................................................. 22 4................................7 Independent manual or power operation (independent unlatched operation) ......................... 26 5.... 25 5........ 31 ........................................... 25 5..................................................................................................4 Rated arc fault duration (t A .........11 Interlocking devices ................105..14 Creepage distances for outdoor insulators ................................................ 26 5........6 Stored energy operation ..........101 Protection of the prefabricated substation against mechanical stress .....3 Operation aisle ...............................5 Dependent power operation .............................................................................................. t Ae ) ..........................6 Partitions ..........................................................................102..................................................12 Position indication ..............................................2 Types of accessibility (A........................103 Internal arc fault .. 31 5......102................and high-pressure interlocking and monitoring devices ................1 General ..4 Covers and doors ......... 31 5............... 23 5.......... B...... 28 5....................... 31 5....................................... 26 5..................................................................................................... 26 5...................... 23 5....................................2 Fire behaviour .................... 23 5 Design and construction ......................................................... 21 4... 22 4... 22 4........................... 26 5............................................................. 25 5. 28 5..................10 Rated pressure of compressed gas supply for controlled pressure systems ................................. 30 5...5 Ventilation openings .................................13 Degree of protection provided by enclosures .............3 Earthing of switchgear and controlgear .......... 22 4. 31 5.................... 27 5.......................................................................................................................... 30 5....................................................8 Operation of releases ...... 29 5............10 Nameplates...... 26 5.....101 Rated maximum power and class of enclosure ...............................................................................................102....................................................................................3 Corrosion .................. 31 6 Type tests ........................ I Ae ) ..................... 26 5......102.........................9 Low...............................104...1 General .......................................................102 Protection of the environment due to internal defects ............................................................... 27 5... 25 5... 21 4....................................................................4 Auxiliary and control equipment ..........................3 Rated arc fault currents (I A .........................................................105....104......................106 Sound emission ...................................................... 22 4........................click here to buy the full publication IEC 62271-202:2014 © IEC 2014 –3– 4......2 Accessories .................... 31 5......................................................101........................
................ 36 6...............4 Measurement of the resistance of circuits .............102............. 32 6..................... 45 6...................................2......... 44 6..... 43 6............................................................................11 Voltage test as condition check ......2............................10...... 34 6...................................................2..................... 43 6....................................... 41 6......102........... 31 6.....................2...........2 Roof loads .. 46 ................................2 Information for identification of specimens ..........................2..........................101 Calculations and mechanical tests ....................................................... 37 6.................................................... 42 6..... 36 6...........................................................9 Electromagnetic compatibility tests (EMC) .....................2............................... 33 6.............................10 Dielectric tests on auxiliary and control circuits.......................... 33 6....................... 44 6................................................ 45 6........................................................5.10........1 General . 32 6.............. 35 6................................6 Short-time withstand current and peak withstand current tests ............................... 44 6........1 General ................10 Additional tests on auxiliary and control circuits ............................3 Arrangement of the equipment .... 38 6.................................6 Tests of switchgear and controlgear of U r ≤ 245 kV ....101...............3 Radio interference voltage (r....101 General ............................................................................................... 43 6..................1.........4 Verification of the operational characteristics of auxiliary contacts ................................................................i.................................................) test ...........................5.........10.............................. 33 6..................................1.................... 44 6.........................................................................102 Tests on low-voltage interconnection ...........................1 Wind pressure .................2 Test conditions ..............................................2 Dielectric tests ......................5 Application of the test voltage and test conditions ....................................7 Verification of the protection ..............7 Tests of switchgear and controlgear of U r > 245 kV ..... 43 6..............2.102..................... 45 6..10..............9 Partial discharge tests ...................................103 Test methods ......................6 Dielectric test ...............v.........................2............................... 33 6...102 Internal arc test ..101..............................2.................................5........ ...........................5.........................3 Electrical continuity of earthed metallic parts test .............................................2.............................8 Tightness tests ......... 44 6...................................... 34 6...................................................................5........... This is a preview ..............10....................... 33 6............... 36 6......................1 General ............................................................ 44 6. 33 6...................... 32 6................2.....102........ 45 6.. 33 6..1..................................................................5 Temperature-rise tests . 44 6... 46 6....3 Information to be included in type-test reports ..........8 Artificial pollution tests for outdoor insulators .............. 44 6..................3 Conditions of switchgear and controlgear during dielectric tests .............. 34 6.......2 Functional tests ......................................... 36 6......................................................................................... 44 6.2.........105 Acceptance criteria ...................3 Mechanical impacts .... 33 6......... 33 6..................................1 Grouping of tests ...........................5 Environmental tests ...104 Measurements ............................10.... 44 6...................... 45 6.................................................................101 Tests on the high-voltage interconnection ............click here to buy the full publication –4– IEC 62271-202:2014 © IEC 2014 6.......11 X-radiation test procedures for vacuum interrupters ............................................. 33 6......................................4 Test procedure .......102 Test conditions ...........................1 Ambient air conditions during tests ...................2..........2 Wet test procedure .......................................................101........................4 Criteria to pass the test ....................................
..............................2........ 49 7............2...... 49 8........................................................ maintenance ............................ 60 10.............................................1 Information with enquiries and orders ................................... 49 7.... storage...............................................................5 Final installation inspection ..................................7 Basic input data by the manufacturer ................................................2.......... 58 9.................................................................. recycling and disposal at the end-of-service life ......... 48 7 Routine tests ..............3 Operation ......................................105 Tests after assembly on site ............................... 59 10 Transport.103 Thermal aspects .........................101 Dielectric test on the high voltage interconnection........................................................................................ storage and installation . 50 8........................................6 Basic input data by the user ....102 Voltage withstand tests on auxiliary circuits ........ 49 8................................................................103 Measurement or calculation of electromagnetic fields ................ 61 10....................................................102................................. ratings and optional tests ........... 58 9.........4 Maintenance ...................................................................... 49 7.......................................................104 Internal arc aspects ............. 53 8.................... 61 10...................1 General ....................................................1 Conditions during transport......... 54 9 Information to be given with enquiries........................ 62 11.................................7 Transferability of tests results ......102 Selection of rated values ........................... 61 10.....4 Connections ..................... 63 Annex AA (normative) Internal arc fault – Method to verify the internal arc classification (IAC) .............................105 Summary of technical requirements.............................. 50 8............................101 Electrical aspects ...................................3 Supplementary protective measures ................................ This is a preview .... 61 10.............. 61 10..............2.... 50 8.........................................6 IAC classification .............................102..................................................................... 50 8.................. 49 7............ tenders and orders ................................................................................................. 62 11 Safety .......................................................................... 62 10................. 64 .... 61 10............................................................................... 51 8............ 61 10.................................................... 62 11................................................................................... 62 12 Influence of the product on the environment .............................................................................................................. 53 8.101 Dismantling......................104... 46 6..... 48 Replacement: ........................................................103 Functional tests ......................................................................................................................................................................................................102 Mechanical aspects .............................................4 Considerations for the selection and installation .......104 Internal arc fault .........................................................................................2 Information with tenders .....5 Internal arc test .....................104........... 62 11..........101 General ........................................104.....................3 Mounting ............................ 48 6.103 Selection of class of enclosure ..2 Assembly ...................................104....................................................................... operation. 51 8........ 60 10............................................ 49 8 Guide to the selection of prefabricated substation ...........................102...............5 Criteria to pass the test ................................................ 60 10................click here to buy the full publication IEC 62271-202:2014 © IEC 2014 –5– 6.........................................................................................................................................................................1 Unpacking and lifting ..........................................................104...................... 49 Replacement: ........2 Installation .. 53 8............. installation..... 61 10...2 Causes and preventive measures ..104.........................................................................2... 62 11.............................. 49 7...........................104 Verification of correct wiring ................2......................................... 47 6.........................................................2..................................6 Test report ..............................................
................ 37 Figure 103 – Diagram of the preferred temperature-rise test method .1 – Liquid-filled transformer load factor in an enclosure ...... 80 DD.......................................4 Tolerances for geometrical dimensions of test arrangements ..... 41 Figure AA.........................................2 – Dry-type transformer load factor outside of the enclosure ...................................2 – Horizontal indicators ............................................ 93 Figure 101 – Measurement of transformer temperature rise in ambient air: ∆t 1 ...2 Concrete ..........3 Indicators (for assessing the thermal effects of the gases) ... 40 Figure 105 – Diagram for open-circuit test ...... 81 ..2 Liquid-filled transformer ............................. 76 Annex CC (normative) Mechanical impact test ..................................................................................................2 Test specimen ......1 – Impact test apparatus ....2 Room simulation ......................................................................................................... 76 BB....... 91 Bibliography .......................1 Test for the verification of the resistance to mechanical impact ................. 74 Figure AA..........7 – Selection of tests on high voltage interconnections for class IAC-B ........2 Paints ..................................................................3........... 73 Figure AA....5 – Selection of tests on high voltage switchgear for class IAC-B ..............................................................................................3 – Arrangement of indicators ...................... 64 AA.......... 91 FF..................... 37 Figure 102 – Measurement of transformer temperature rise in an enclosure: ∆t 2 .................................................................................................................................................................... 78 CC........................................................... 71 Figure AA..................................................... 39 Figure 104 – Diagram of the alternative temperature-rise test method .....2 Apparatus for the verification of the protection against mechanical damage.......................4 Example............... 68 Figure AA....... 91 FF.....................................................................1 – Mounting frame for vertical indicators ...................................................4 Measurements ........ 64 AA..........................................................................1 Purpose ...................................... 78 Annex DD (informative) Rating of transformers in an enclosure ...............................................................................................................................................1 Metals .3................................................................................................................................................... 91 FF......................................................................................................................................................................................................................................................................4 – Selection of tests on high voltage switchgear for class IAC-A .1 Coatings ...... 79 Figure DD..1 General ................. 81 DD.............. 72 Figure AA..................................................................... 76 BB..1..............................3 Test method . 88 Annex FF (informative) Characteristics of enclosure materials ........................................................................................ 91 FF................................................. 76 BB........... 78 CC.............................. 80 DD.. 80 DD............................................. 85 Annex EE (informative) Examples of earthing circuits . 76 BB..........................................................................................................................2 Arrangement of indicators .................3 Dry-type transformer ....... 67 AA........................ 66 AA.........................1 General ........1 General ................................................click here to buy the full publication –6– IEC 62271-202:2014 © IEC 2014 AA......1..........................5 Presentation and calculation of the results ............................................ 81 Figure DD......................... 68 Figure AA........... This is a preview ....................................... 67 Annex BB (normative) Test to verify the sound level of a prefabricated substation ................................................ 64 AA.................................. 64 AA.................................................................................................6 – Selection of tests on high voltage interconnections for class IAC-A ............................ 65 AA..... 75 Figure CC.......................................5 Test parameters ..................6 Test procedure ............ 76 BB.....................................................................................................
..................................................................................................................3 – Example within the framework serving as the main earthing conductor .6 – Insulation class 155 °C (F) dry-type transformers load factor in an enclosure .2 – Example of earthing circuits ......................................................................................................................................................................9 – Insulation class 220 °C (H) dry-type transformers load factor in an enclosure ......................................................... 84 Figure DD.......................................................................... 82 Figure DD. 90 Table 101 – Synthetic material characteristics ................................5 – Insulation class 130 °C (B) dry-type transformers load factor in an enclosure ............................................................................. 83 Figure DD.....................................................................1 – Treatment of coatings ........... 88 Figure EE....................................................................................................................................................... 82 Figure DD.............................4 – Insulation class 120 °C (E) dry-type transformers load factor in an enclosure ........................................................... 85 Figure EE............ 84 Figure DD................................................................................................3 – Test of concrete .............................2 – Tests of coatings ..click here to buy the full publication IEC 62271-202:2014 © IEC 2014 –7– Figure DD.......................... 92 ........................................................................................ 54 Table 104 – Summary of technical requirements and ratings for prefabricated substations (1 of 4) ...... causes and examples of measures decreasing the probability of internal arcs ...................................................... 91 Table FF.........3 – Insulation class 105 °C (A) dry-type transformers load factor in an enclosure ........................... 91 Table FF..................................................................................... 52 Table 103 – Single phase-to-earth arc fault current depending on the network neutral earthing .............................. 83 Figure DD............................................................................................................................................. This is a preview ................................................................. 29 Table 102 – Locations.........................................................................1 – Example of earthing circuits ................... 89 Figure EE............................................................................7 – Insulation class 180 °C (H) dry-type transformers load factor in an enclosure ........................................ 55 Table FF....................................8 – Insulation class 200 °C (H) dry-type transformers load factor in an enclosure .......
an international consensus of opinion on the relevant subjects since each technical committee has representation from all interested IEC National Committees. This is a preview . c) assessment of electromagnetic fields is considered including a type test (optional) according IEC/TR 62271-208:2009. International Standard IEC 62271-202 has been prepared by subcommittee 17C: High-voltage switchgear and controlgear assemblies. To this end and in addition to other activities. Their preparation is entrusted to technical committees. IEC cannot be held responsible for the way in which they are used or for any misinterpretation by any end user. 6) All users should ensure that they have the latest edition of this publication. This edition constitutes a technical revision. 5) IEC itself does not provide any attestation of conformity. . Independent certification bodies provide conformity assessment services and. The object of IEC is to promote international co-operation on all questions concerning standardization in the electrical and electronic fields. of IEC technical committee 17: Switchgear and controlgear. 8) Attention is drawn to the Normative references cited in this publication. access to IEC marks of conformity. employees. Publicly Available Specifications (PAS) and Guides (hereafter referred to as “IEC Publication(s)”). or reliance upon. This second edition cancels and replaces the first edition published in 2006. IEC is not responsible for any services carried out by independent certification bodies. use of. This edition includes the following significant technical changes with respect to the previous edition: a) regarding temperature-rise test an alternative method for liquid filled transformers is (re)introduced and the temperature-rise test method for dry-type transformers is specified more precisely. in some areas. IEC collaborates closely with the International Organization for Standardization (ISO) in accordance with conditions determined by agreement between the two organizations. 7) No liability shall attach to IEC or its directors. 4) In order to promote international uniformity. Technical Specifications. or for costs (including legal fees) and expenses arising out of the publication. Technical Reports. any IEC National Committee interested in the subject dealt with may participate in this preparatory work. this IEC Publication or any other IEC Publications. b) testing procedure for short time and peak withstand current tests are specified more precisely. IEC shall not be held responsible for identifying any or all such patent rights. IEC publishes International Standards. servants or agents including individual experts and members of its technical committees and IEC National Committees for any personal injury. 9) Attention is drawn to the possibility that some of the elements of this IEC Publication may be the subject of patent rights. property damage or other damage of any nature whatsoever.click here to buy the full publication –8– IEC 62271-202:2014 © IEC 2014 INTERNATIONAL ELECTROTECHNICAL COMMISSION _____________ HIGH-VOLTAGE SWITCHGEAR AND CONTROLGEAR – Part 202: High-voltage/low-voltage prefabricated substation FOREWORD 1) The International Electrotechnical Commission (IEC) is a worldwide organization for standardization comprising all national electrotechnical committees (IEC National Committees). While all reasonable efforts are made to ensure that the technical content of IEC Publications is accurate. whether direct or indirect. Use of the referenced publications is indispensable for the correct application of this publication. IEC National Committees undertake to apply IEC Publications transparently to the maximum extent possible in their national and regional publications. governmental and non- governmental organizations liaising with the IEC also participate in this preparation. 3) IEC Publications have the form of recommendations for international use and are accepted by IEC National Committees in that sense. Any divergence between any IEC Publication and the corresponding national or regional publication shall be clearly indicated in the latter. as nearly as possible. 2) The formal decisions or agreements of IEC on technical matters express. International.
The text of this standard is based on the following documents: FDIS Report on voting 17C/595/FDIS 17C/598/RVD Full information on the voting for the approval of this standard can be found in the report on voting indicated in the above table. . under the general title High-voltage switchgear and controlgear. unless otherwise specified. The committee has decided that the contents of this publication will remain unchanged until the stability date indicated on the IEC web site under "http://webstore.click here to buy the full publication IEC 62271-202:2014 © IEC 2014 –9– d) influence of the product on the environment is considered (Clause 12). the publication will be • reconfirmed.2 are worked out in detail. This publication has been drafted in accordance with the ISO/IEC Directives. In order to simplify the indication of corresponding requirements. This is a preview . Tables B. A list of all parts of the IEC 62271 series can be found.ch" in the data related to the specific publication. The contents of the corrigendum of April 2015 have been included in this copy. to which it refers and which is applicable. whilst additional subclauses are numbered from 101. on the IEC website. f) the method for defining the load factor in an enclosure for liquid filled transformers is extended with different temperature rises for the transformer outside the enclosure (Annex DD). Users should therefore print this document using a colour printer. Amendments to these clauses and subclauses are given under the same numbering.1 and B. • replaced by a revised edition. • withdrawn. IMPORTANT – The 'colour inside' logo on the cover page of this publication indicates that it contains colours which are considered to be useful for the correct understanding of its contents. or • amended. Part 2. g) for the calculation of the load factor of dry-type transformers in an enclosure the insulation systems according to IEC 60076-1:2011.iec. e) internal arc test requirements have been adapted to IEC 62271-200:2011 and requirements for the assessment of pressure relief volumes below the floor / ground has been assigned. This standard should be read in conjunction with IEC 62271-1:2007 and its Amendment 1:2011. At this date. the same numbering of clauses and subclauses is used as in IEC 62271-1.
click here to buy the full publication – 10 – IEC 62271-202:2014 © IEC 2014 INTRODUCTION Prefabricated substations are defined as a type-tested assembly comprising an enclosure containing in general transformers. This means that. low-voltage and high-voltage switchgear. The correct design and performance of the prefabricated substation are verified by means of relevant type tests described in this standard. This is a preview . Use of type-tested components and suitable design and construction of the enclosure ensure this protection. both operators and general public. ratings and relevant test procedures. including internal arc tests. . connections and auxiliary equipment to supply low-voltage energy from a high-voltage system or vice versa. particular attention has been paid to the specification concerning the protection of persons. in addition to the specified characteristics. These substations are in locations accessible to the public and should ensure protection to persons according to the specified service conditions.
For dated references. 1.click here to buy the full publication IEC 62271-202:2014 © IEC 2014 – 11 – HIGH-VOLTAGE SWITCHGEAR AND CONTROLGEAR – Part 202: High-voltage/low-voltage prefabricated substation 1 General 1. Non-prefabricated substations should comply with the applicable requirements of IEC 61936- 1:2010. – auxiliary equipment and circuits. IEC 60050-461 (all parts). Power transformers – Part 2: Temperature rise for liquid-immersed transformers IEC 60076-3:2013. This is a preview . For undated references. which are cable-connected.1 Scope This part of IEC 62271 specifies the service conditions. Environmental testing – Part 2-75: Tests – Test Eh: Hammer tests IEC 60076-1:2011. to be operated from inside (walk-in type) or outside (non-walk-in type) for alternating current of rated voltages above 1 kV and up to and including 52 kV on the high voltage side. – high voltage and low voltage interconnections. – high voltage and low voltage switchgear and controlgear. rated characteristics. Power transformers – Part 1: General IEC 60076-2:2011. are normatively referenced in this document and are indispensable for its application.2 Normative references The following documents. and for one or more transformers for service frequencies up to and including 60 Hz for outdoor installation at locations with public accessibility and where protection of personnel is provided. an installation consisting of power transformer and low voltage switchgear).org) IEC 60068-2-75. in whole or in part. Power transformers – Part 3: Insulation levels. However. general structural requirements and test methods of high voltage/low voltage or low voltage/high voltage prefabricated substations. In general a prefabricated substation comprises an enclosure containing the following electrical components: – power transformers. only the edition cited applies.electropedia. dielectric tests and external clearances in air . Prefabricated substations can be situated at ground level or partially or completely below ground level. International Electrotechnical Vocabulary (available at www. the latest edition of the referenced document (including any amendments) applies. relevant provisions of this standard are applicable to designs where not all these electrical components exist (for example.
High-voltage switchgear and controlgear – Part 1: Common specifications Amendment 1:2011 . Low-voltage switchgear and controlgear – Part 1: General rules IEC 61180-1:1992. Low-voltage switchgear and controlgear assemblies – Part 2: Power switchgear and controlgear assemblies IEC 62262:2002. This is a preview . Power transformers – Part 7: Loading guide for oil-immersed power transformers IEC 60076-10:2001. Classification of environmental conditions – Part 1: Environmental parameters and their severities Amendment 1:1992 Amendment 2:1995 IEC 60721-2-2:2012. Classification of environmental conditions – Part 2-2: Environmental conditions appearing in nature – Precipitation and wind IEC 60721-2-4:1987. Low-voltage switchgear and controlgear assemblies – Part 1: General rules IEC 61439-2:2011. Classification of environmental conditions – Part 2: Environmental conditions appearing in nature – Solar radiation and temperature Amendment 1:1988 IEC/TS 60815-1:2008. Power transformers – Part 13: Self-protected liquid-filled transformers IEC 60364-4-41:2005. High-voltage test techniques for low-voltage equipment – Part 1: Definitions. Low-voltage electrical installations – Part 4-41: Protection for safety – Protection against electric shock IEC 60529:1989. Power transformers – Part 11: Dry-type transformers IEC 60076-12:2008.click here to buy the full publication – 12 – IEC 62271-202:2014 © IEC 2014 IEC 60076-5:2006. Insulation coordination for equipment within low-voltage systems – Part 1: Principles. Degrees of protection provided by enclosures (IP Code) Amendment 1:1999 Amendment 2:2013 IEC 60664-1:2007. information and general principles IEC 60947-1:2007. Degrees of protection provided by enclosures for electrical equipment against external mechanical impacts (IK code) IEC 62271-1:2007. Power transformers – Part 12: Loading guide for dry-type power transformers IEC 60076-13:2006. Power transformers – Part 5: Ability to withstand short circuit IEC 60076-7:2005. Power transformers – Part 10: Determination of sound levels IEC 60076-11:2004. Selection and dimensioning of high-voltage insulators intended for use in polluted conditions – Part 1: Definitions. requirements and tests IEC 60721-1:1990. test and procedure requirements IEC 61439-1:2011.
High-voltage switchgear and controlgear – Part 300: Seismic qualification of alternating current circuit-breakers ISO/IEC Guide 51:1999.1. Steels for general engineering purposes ISO 1182:2010. H. 2. G. However. C.1.102 Transformer IEC 60076-1:2011 is applicable.1 of IEC 61439-1:2011 is applicable.1. power-frequency electromagnetic fields generated by HV switchgear assemblies and HV/LV prefabricated substations IEC/TR 62271-300:2006. 2.1 Normal service conditions Unless otherwise specified in this standard. If the ambient temperature inside the substation is higher than the limits fixed for the components in their respective product standards. Safety aspects – Guidelines for their inclusion in standards ISO 1052:1982.111.1 Indoor switchgear and controlgear Subclause 2. This is a preview . de-rating may be necessary. Additional subclauses: 2. N. E. Reaction to fire tests for products – Non-combustibility tests ISO 1716:2010.1. the prefabricated substation is designed to be used under normal service conditions for outdoor switchgear and controlgear according to IEC 62271-1:2007. Metallic materials – Rockwell hardness test – Part 1: Test method (scales A. K. B. High-voltage switchgear and controlgear – Part 200: AC metal-enclosed switchgear and controlgear for rated voltages above 1 kV and up to and including 52 kV IEC 62271-201:2006. . the ambient temperature inside the enclosure of the prefabricated substation will be different from the ambient temperature as defined in 3. except as follows. T) 2 Normal and special service conditions Clause 2 of IEC 62271-1:2007 is applicable. Reaction to fire tests for products – Determination of the gross heat of combustion (calorific value) ISO 6508-1:2005.click here to buy the full publication IEC 62271-202:2014 © IEC 2014 – 13 – IEC 62271-200:2011.1. 2. Inside the enclosure it is assumed that normal indoor conditions prevail according to IEC 62271-1:2007. F.1 of IEC 62271-1:2007 is applicable. High-voltage switchgear and controlgear – Part 208: Methods to quantify the steady state. D. High-voltage switchgear and controlgear – Part 201: AC insulation enclosed switchgear and controlgear for rated voltages above 1 kV and up to and including 52 kV IEC/TR 62271-208:2009.101 Low-voltage switchgear and controlgear Subclause 7.1.
........................ 113 4...................................................................................................................7............................................................................................................ 102 INTRODUCTION ..................7 Durées de court-circuit assignée (t k ) ...2................103 Valeurs de crête du courant admissible assigné de l'appareillage basse tension et de l'interconnexion basse tension (I pk ) ..........................1.2.............4 Vibrations...................................1..................1 Tension assignée (U r ) ....101 Courant de crête admissible assigné (I p ) ....... 107 2................................................ 108 2...7.................6 Autres paramètres .......2 Appareillage pour l'extérieur ..... 115 4........ 105 2 Conditions normales et spéciales de service .......... 108 2............... 115 4.........................102 Transformateur .................................6.............................4...2......................................................................2.................................. 113 4..................2 Niveau d'isolement assigné .........................5 Vitesse du vent .5 Courant de courte durée admissible assigné (I k ) ..1 Courant assigné en service continu (I r ) ...................2.................................103 Durée de court-circuit assignée de l'appareillage basse tension et de l'interconnexion basse tension .................... 114 4........................ 115 4........... 114 4.....................................5.............7.........................................102 Courant phase-terre de crête admissible assigné (I pe ) .......................... 115 4...............6........1................2 Échauffement ....................4 Courant assigné en service continu et échauffement .1........................................... 114 4........101 Appareillage basse tension . 105 1.................................................................. 108 2..................................................... 113 4........................ 112 4............................102 Courant de courte durée admissible assigné phase-terre (I ke ) .................................1 Appareillage d'intérieur ............................6.................................2 Références normatives ....................... 104 1 Généralités .......................................... 108 2......................................... 108 2............................. 110 2................................................... This is a preview .... 112 4.............................................. 109 2........................... 116 .............................................................2 Conditions spéciales de service ..............101 Durée de court-circuit assignée (t k ) ............................102 Durée de court-circuit phase-terre assignée (t ke ) ............................ 105 1...1 Altitude .............................. 110 2................2 Pollution ........... 107 2............ 108 2......3 Points particuliers du Tableau 3 .....................104 Durée de court-circuit assignée des transformateurs ............................ 109 2......... 113 4............ 115 4...101 Courant de courte durée admissible assigné de l'appareillage haute tension et de l'interconnexion haute tension (I k ) ............................................................................................... 115 4..7............ 114 4...............................4.......5................................................................................2........................... 110 3 Termes et définitions .........................5.....................4.............................................................................1..................................... chocs ou basculements ................3 Température et humidité ........... 115 4.3 Fréquence assignée (f r ) ....................................1 Conditions normales de service .click here to buy the full publication – 96 – IEC 62271-202:2014 © IEC 2014 SOMMAIRE AVANT-PROPOS ..................103 Courants de courte durée admissibles assignés de l'appareillage basse tension et de l'interconnexion basse tension (I cw) ............................. 115 4...........................6 Valeur de crête du courant admissible assigné (I p ) ...............1...................................... 114 4........................................ 113 4.......................................1 Domaine d'application ................................... 110 4 Caractéristiques assignées .
...........9 Fréquence assignée d'alimentation des dispositifs de fermeture et d'ouverture et des circuits auxiliaires .......101..................104..... 126 5................................ 123 5........... 121 5........................................................1 Dispositions pour les essais diélectriques des câbles .................. 119 5............................................................. 117 4..................................11 Dispositifs de verrouillages ..................7 Manœuvre indépendante manuelle ou manœuvre indépendante à source d’énergie extérieure (manœuvre indépendante sans accrochage mécanique) ............................... t Ae ) ....................................................2 Classe d'enveloppe assignée ........................ 120 5..................................................................................... 121 5....10 Pression assignée d'alimentation en gaz comprimé pour les systèmes à pression entretenue .......... 120 5.........................2 Types d'accessibilité (A.............102 Caractéristiques assignées de la classe de tenue à l'arc interne . 121 5............................................................... AB) ............105....1 Exigences pour les liquides utilisés dans l'appareillage ..................................105 Autres dispositions ...5 Manœuvre dépendante à source d'énergie extérieure ............................................6 Manœuvre à accumulation d'énergie ..9 Dispositifs de verrouillage et de surveillance basse et haute pression ..........................1 Généralités ........ 126 ..14 Lignes de fuite pour les isolateurs d’extérieur ............ 120 5................. 121 5...................104................3 Corrosion .............. 116 4.......................... This is a preview ............................................................................................. 118 5 Conception et construction ................................5 Ouvertures de ventilation .......................... 116 4..................................................................................... 118 5.............................103 Défaut d'arc interne ........................... 118 5.................... 116 4.................104........... 117 4.............. 118 5.............................. 121 5............102................................. B................................8 Fonctionnement des déclencheurs .................104...................10 Plaques signalétiques ...... 117 4..............102 Protection de l'environnement contre les conséquences des défauts internes .......................... 116 4........................................................................................... 120 5.......................1 Puissance assignée maximale du poste préfabriqué ..............................................................................17 Risque de feu (Inflammabilité) ............... 120 5.....15 Étanchéité au gaz et au vide ...8 Tension assignée d'alimentation des dispositifs de fermeture et d'ouverture et des circuits auxiliaires et de commande (U a ) ................................105. 120 5....... 121 5....................................2 Équipements auxiliaires .......................................................101 Puissance maximale et classe d'enveloppe assignées .....2 Tenue au feu ................................................................... 116 4..................104.....102...... 116 4.................................................... 116 4.. 122 5..... 125 5.................... 118 5.............................click here to buy the full publication IEC 62271-202:2014 © IEC 2014 – 97 – 4........................104 Enveloppe ........1 Généralités ......................................................................6 Cloisons ....... 124 5........................................ 122 5..............................16 Étanchéité au liquide .........................................................................3 Raccordement à la terre de l'appareillage ..................2 Exigences pour les gaz utilisés dans l'appareillage ............................................. 120 5....................................................... 122 5...3 Courants de défaut d'arc assignés (I A ............................104..................................... 123 5..........11 Niveaux assignés de remplissage pour l'isolement et/ou la manœuvre ....102........18 Compatibilité électromagnétique (CEM) ...............................................................................4 Capots et portes ............4 Équipements auxiliaires et de commande ..................4 Durée de défaut d’arc assignée (t A ................................ 117 4.................101 Protection du poste préfabriqué contre les contraintes mécaniques ..13 Degré de protection procuré par les enveloppes .................101... 121 5........... 126 5.......12 Indicateur de position ............ 126 5... 126 5........102.................. I Ae ) ......................................................... 124 5.........................................
.....1 Conditions de l'air ambiant pendant les essais ............................................................. 140 6.... 133 6..................2................................................... 132 6...........2 Information pour l'identification des spécimens d'essai ....2......... 138 6.................................................. 128 6............................................. 140 .......................6 Essais au courant de courte durée admissible et à la valeur de crête du courant admissible ............................. 128 6................9 Essais de décharges partielles ........... 139 6....................................................................... 140 6....... 126 5.10.........10 Essais supplémentaires sur les circuits auxiliaires et de commande ..............................................5.....................5................1........ 139 6................. 129 6...........5 Essais d’environnement ..............102 Essais de l'interconnexion basse tension .....2.......2....................... 133 6...........................10........105 Critères d'acceptation .4 Étiquettes .........................5................... 128 6......................................... 139 6................................click here to buy the full publication – 98 – IEC 62271-202:2014 © IEC 2014 5.............................................................................2 Modalités des essais sous pluie ...........................................2 Essais diélectriques ..6 Essai diélectrique ...... 132 6...5 Essais d'échauffement ............................2............. 132 6..................................................................10... 127 6 Essais de type ...............................................5 Application de la tension d'essai et conditions d'essai ..........11 Procédures d’essai des rayonnements X pour les ampoules à vide ..............3 Couloir de manœuvre ...............105...............................2 Charges sur toiture ................4 Critères de réussite des essais ...........1...................................................................................................... 129 6......................................11 Essai de tension comme essai de vérification d’état .................................................................3 Essais de tension de perturbation radioélectrique ................1 Pression du vent .........................103 Méthodes d'essai ............................................2........10................................ 128 6.....101..........................3 État de l'appareillage pendant les essais diélectriques ...... 128 6.......2...................................................... 132 6...................................................... 140 6........ 139 6....9 Essais de compatibilité électromagnétique (CEM) ...................4 Mesurage de la résistance des circuits................................................ 128 6.....8 Essais de pollution artificielle pour les isolateurs d’extérieur .................... 129 6............. 140 6..............7 Essais de l’appareillage de U r > 245 kV ........1 Généralités ...4 Vérification des caractéristiques de fonctionnement des contacts auxiliaires ............................ 137 6................................. 126 5....................106 Emission de bruit ............................................101..........................................................8 Essais d’étanchéité . 129 6.......................................................... 139 6......101 Généralités ....5................. This is a preview ..................................................2..................................................2................ 126 5..................................................3 Essais de continuité électrique des parties métalliques reliées à la terre ... 129 6.. 129 6.. 139 6.2................................ 128 6......................................................102 Conditions d’essai ....................5..................................... 138 6.......3 Information à inclure dans les rapports d’essai de type ...104 Mesures .......... 129 6.....2 Essais fonctionnels ............................................................2........10................... 140 6...................... 127 6..........101 Calculs et essais mécaniques .............10........................2.............6 Essais de l’appareillage de U r ≤ 245 kV .................10 Essais diélectriques sur les circuits auxiliaires et de commande ....................105......107 Champs électromagnétiques ......... 127 6....................................................... 128 6.......7 Vérification de la protection...........................101 Essais de l'interconnexion haute tension ......................1 Groupement des essais ...........1 Généralités ........ 140 6..........2.......................... 131 6............. 139 6......................................1............................. 129 6........
.................. 156 10........ recyclage et enlèvement en fin de vie .............1 Conditions à respecter pendant le transport....... 145 8......................... 150 9 Renseignements à donner dans les appels d'offres..2.......................4 Maintenance ..........................102......................................................... le stockage et l'installation .. 147 8....... 146 8....2...........................2 Renseignements pour les soumissions................................... stockage..102..................................................................101 Démontage.... 154 9....... 156 10...............................105 Essais après assemblage sur le site ......104.....2 Assemblage .................................................... 142 6......102 Essais de tenue à la tension des circuits auxiliaires ....... 145 7................................................................................................6 Rapport d'essai .......102 Choix des caractéristiques assignées .....................................................2..... 145 7...........2....104...102..................................4 Considérations relatives au choix et à l’installation ...............2 Conditions d’essai ....................................7 Données d'entrée de base fournies par le constructeur ...................................................... 157 10..... 140 6............................ 158 10......104 Défaut d'arc interne .................... 140 6..................2 Installation ...................................2............... 145 8 Guide pour le choix des postes préfabriqués .......101....1 Renseignements dans les appels d'offres et les commandes ..............103 Essais fonctionnels ... des caractéristiques assignées et des essais optionnels...........................................3 Impacts mécaniques .................... les soumissions et les commandes ......................3 Montage de l’équipement ................................................................................................. 143 6.............................3 Mesures de protection supplémentaires ...105 Résumé des exigences techniques...................................... 142 6.......102 Essai d'arc interne ... 147 8.............102.... 146 8..........................................................104.... 149 8........................................................ 157 10............ 145 7.......................1 Généralités ...103 Mesures ou calcul des champs électromagnétiques ..................................................................... 144 6......................................... 144 7 Essais individuels de série ......................... 142 6........click here to buy the full publication IEC 62271-202:2014 © IEC 2014 – 99 – 6........ 145 8........................... 145 Remplacement: ............................ 157 10..101 Généralités ........ manœuvre et maintenance .......................................................................................................................7 Extension des résultats d’essais ...........................................................................................................................................................................................................................2................................................. 154 9................................................................104 Vérification de l'exactitude de la filerie ........................................ 140 6.............................104............................................... 145 8..............1 Déballage et manutention .................................................................................................................... 158 11 Sécurité .................... This is a preview ............................. 157 10.....................104.........................4 Procédure d'essai .. 158 ................................. 157 10............ 158 10...............................................102.............................................. installation.............. 144 Remplacement: ........................................................................2 Causes et mesures préventives . 157 10..5 Inspection finale de l'installation ............................ 145 7........................................................... 157 10........2....................................5 Critères de réussite des essais ...102............6 Données d'entrée de base fournies par l’utilisateur ...................................3 Fonctionnement ....................................... 145 7........................4 Raccordements.....................1 Généralités ...5 Essai d'arc interne .. 146 8.................................................................103 Choix de la classe d'enveloppe ......6 Classification IAC ........................ 149 8.................102......................................................3 Montage ............................ 141 6................... 148 8.104...........................101 Essai diélectrique de l’interconnexion haute tension ......................................................................................... 158 10..................................... 155 10 Transport.......
.............103 Aspects thermiques .......... 177 DD.....................................................................................................................4 Tolérances pour les dimensions géométriques des montages d’essai ................................ 187 FF........................2 Appareil de contrôle de la protection contre les dommages mécaniques .........................................................1 Essai de contrôle de la résistance aux impacts mécaniques.................. 135 Figure 104 – Schéma de la méthode alternative pour l’essai d’échauffement ............................................ 174 CC... 174 CC.. 164 Figure AA................2 Echantillon d'essai .......4 Mesures ....................................................................................................................................................................................................................102 Aspects mécaniques ..... 187 Bibliographie .......................................................................................... 187 FF................................... 159 11.......... 163 Annexe BB (normative) Essai de vérification du niveau de bruit d'un poste préfabriqué .................................................................................... 133 Figure 103 – Schéma de la méthode préférentielle pour l’essai d’échauffement ..2 Local d'essai .................................. This is a preview ......... 163 AA................................1 Généralités .........................2 – Indicateurs horizontaux ........2 Disposition des indicateurs ....................................................................................................... 181 Annexe EE (informative) Exemples de circuits de mise à la terre ....................................3........................................................................................................... 159 11..................................................................... 160 AA............. 136 Figure 105 – Schéma pour l'essai en circuit ouvert .................................................................................... 176 DD......................................................4 Exemple.. 172 BB.................. 187 FF....1 Revêtements ......3 Transformateur de type sec ..........................3 Méthode d'essai ... 160 AA.................1................................. 189 Figure 101 – Mesure de l'échauffement du transformateur à l'air ambiant: ∆t 1 ........................................5 Paramètres d’essai ..................... 159 12 Influence du produit sur l’environnement ............................................................................................. 172 BB............1 – Cadre de montage pour les indicateurs verticaux ............1 Objet .................... 176 DD.................................................................. 132 Figure 102 – Mesure de l'échauffement du transformateur dans une enveloppe: ∆t 2 ....................................................... 167 ............................................................................................. 172 BB.. 172 BB........ 163 AA.........5 Présentation et calcul des résultats ................................... 176 DD.... 187 FF.......3.......................... 160 AA...........................................104 Aspects liés à un arc dû à un défaut interne ........ 160 AA........................................................................................................................................................ 159 11................................3 Indicateurs (pour évaluer l'effet thermique des gaz) .............1 Généralités .............. 172 BB....................1 Généralités .. 164 Figure AA..................................................................................................................2 Béton ....................................................................................................... 136 Figure AA.....2 Transformateur immergé ............................3 – Disposition des indicateurs ........................................101 Aspects électriques .......................................click here to buy the full publication – 100 – IEC 62271-202:2014 © IEC 2014 11........................................ 161 AA................................... 174 Annexe DD (informative) Caractéristique assignée des transformateurs dans les enveloppes ................2 Peintures ................ 160 AA..................................................................1 Métaux ................ 184 Annexe FF (informative) Caractéristiques des matériaux de l'enveloppe ...........................................................................6 Procédure d'essai ....................... 159 Annexe AA (normative) Défaut d’arc interne – Méthode de vérification de la classification arc interne (IAC) ...............................................................................1...................................................... 172 Annexe CC (normative) Essai d'impact mécanique ...
..................................................4 – Sélection des essais sur l'appareillage haute tension pour la classe IAC-A ............2 – Facteur de charge d'un transformateur de type sec à l’extérieur de l’enveloppe .............. 185 Figure EE................................................................. 187 Tableau FF................. 180 Figure DD............................ This is a preview ................................................................ 184 Figure EE.................... 177 Figure DD.........1 – Appareil d'essai d'impact ....................................................................8 – Facteur de charge de transformateur de type sec de classe d’isolation de 200 °C (H) dans une enveloppe ...............................................................................7 – Facteur de charge de transformateur de type sec de classe d’isolation de 180 °C (H) dans une enveloppe ...................................................................................................................3 – Facteur de charge de transformateur de type sec de classe d’isolation de 105 °C (A) dans une enveloppe ............................................................................................ 186 Tableau 101 – Caractéristiques des matériaux synthétiques ........................... 179 Figure DD.............................. 187 Tableau FF...............................................................................................5 – Sélection des essais sur l'appareillage haute tension pour la classe IAC- B ..2 – Essais des revêtements .....3 – Exemple de circuit de mise à la terre avec le châssis servant de conducteur principal de terre ............................................... 124 Tableau 102 – Emplacements....................................................................................................................... 171 Figure CC...........................................................................3 – Essai du béton ....... 168 Figure AA. 151 Tableau FF............................................................................................. 170 Figure AA..............................................................................................................................................................................1 – Facteur de charge d'un transformateur immergé dans une enveloppe ............................... 175 Figure DD............................................................................6 – Facteur de charge de transformateur de type sec de classe d’isolation de 155 °C (F) dans une enveloppe ......4 – Facteur de charge de transformateur de type sec de classe d’isolation de 120 °C (E) dans une enveloppe ........................................................ 177 Figure DD...........................................................5 – Facteur de charge de transformateur de type sec de classe d’isolation de 130 °C (B) dans une enveloppe ........ 179 Figure DD..............9 – Facteur de charge de transformateur de type sec de classe d’isolation de 220 °C (H) dans une enveloppe ............................. 188 .............2 – Exemple de circuits de mise à la terre .......................1 – Traitement des revêtements .............................................................. causes et exemples de mesures de diminution de la probabilité d'arcs internes ..1 – Exemple de circuits de terre ...........................................................................................click here to buy the full publication IEC 62271-202:2014 © IEC 2014 – 101 – Figure AA........................................................................................................... 178 Figure DD............................................. 169 Figure AA.......................................... 147 Tableau 103 – Courant de défaut d’arc monophasé phase-terre en fonction de la mise à la terre du neutre du réseau ........... 178 Figure DD....................... 150 Tableau 104 – Résumé des exigences techniques et des caractéristiques assignées pour les postes préfabriqués (1 de 4) .........................6 – Sélection des essais sur les interconnexions haute tension pour la classe IAC-A ........ 181 Figure EE..................... 180 Figure DD.........................................7 – Sélection des essais sur les interconnexions haute tension pour la classe IAC-B ............
9) L’attention est attirée sur le fait que certains des éléments de la présente Publication de l'IEC peuvent faire l’objet de droits de brevet. employés. gouvernementales et non gouvernementales. L'IEC collabore étroitement avec l'Organisation Internationale de Normalisation (ISO). Tous les efforts raisonnables sont entrepris afin que l'IEC s'assure de l'exactitude du contenu technique de ses publications. dans la mesure du possible. 7) Aucune responsabilité ne doit être imputée à l'IEC. 4) Dans le but d'encourager l'uniformité internationale. Leur élaboration est confiée à des comités d'études. 6) Tous les utilisateurs doivent s'assurer qu'ils sont en possession de la dernière édition de cette publication. à appliquer de façon transparente les Publications de l'IEC dans leurs publications nationales et régionales. en liaison avec l'IEC. Toutes divergences entre toutes Publications de l'IEC et toutes publications nationales ou régionales correspondantes doivent être indiquées en termes clairs dans ces dernières. 3) Les Publications de l'IEC se présentent sous la forme de recommandations internationales et sont agréées comme telles par les Comités nationaux de l'IEC. l'IEC ne peut pas être tenue responsable de l'éventuelle mauvaise utilisation ou interprétation qui en est faite par un quelconque utilisateur final. L'utilisation de publications référencées est obligatoire pour une application correcte de la présente publication. parue en 2006. pour tout préjudice causé en cas de dommages corporels et matériels. L'IEC a pour objet de favoriser la coopération internationale pour toutes les questions de normalisation dans les domaines de l'électricité et de l'électronique. dans certains secteurs. selon des conditions fixées par accord entre les deux organisations. aux travaux desquels tout Comité national intéressé par le sujet traité peut participer. L'IEC ne saurait être tenue pour responsable de ne pas avoir identifié de tels droits de brevets et de ne pas avoir signalé leur existence. Cette édition constitue une révision technique. Les organisations internationales. La Norme internationale IEC 62271-202 a été établie par le sous-comité 17C: Ensembles d'appareillages à haute tension. . directe ou indirecte. les Comités nationaux de l'IEC s'engagent. des Spécifications accessibles au public (PAS) et des Guides (ci-après dénommés "Publication(s) de l'IEC"). du comité d'études 17 de l'IEC: Appareillage. dans toute la mesure possible. étant donné que les Comités nationaux de l'IEC intéressés sont représentés dans chaque comité d’études. 5) L'IEC elle-même ne fournit aucune attestation de conformité. 2) Les décisions ou accords officiels de l'IEC concernant les questions techniques représentent. ou au crédit qui lui est accordé. à ses administrateurs. des Spécifications techniques. accèdent aux marques de conformité de l'IEC.click here to buy the full publication – 102 – IEC 62271-202:2014 © IEC 2014 COMMISSION ÉLECTROTECHNIQUE INTERNATIONALE _____________ APPAREILLAGE À HAUTE TENSION – Partie 202: Postes préfabriqués haute tension/basse tension AVANT-PROPOS 1) La Commission Electrotechnique Internationale (IEC) est une organisation mondiale de normalisation composée de l'ensemble des comités électrotechniques nationaux (Comités nationaux de l'IEC). Des organismes de certification indépendants fournissent des services d'évaluation de conformité et. un accord international sur les sujets étudiés. l'IEC – entre autres activités – publie des Normes internationales. des Rapports techniques. et la méthode d’essai d’échauffement des transformateurs de type sec est spécifiée plus en détails. ou de tout autre dommage de quelque nature que ce soit. participent également aux travaux. b) la procédure d’essai au courant de courte durée et à la valeur de crête du courant admissible est spécifiée plus en détails. une autre méthode pour les transformateurs immergés est (ré)introduite. ou pour supporter les coûts (y compris les frais de justice) et les dépenses découlant de la publication ou de l'utilisation de cette Publication de l'IEC ou de toute autre Publication de l'IEC. auxiliaires ou mandataires. Cette édition inclut les modifications techniques majeures suivantes par rapport à l’édition précédente: a) eu égard à l’essai d’échauffement. 8) L'attention est attirée sur les références normatives citées dans cette publication. Cette deuxième édition annule et remplace la première édition. y compris ses experts particuliers et les membres de ses comités d'études et des Comités nationaux de l'IEC. À cet effet. L'IEC n'est responsable d'aucun des services effectués par les organismes de certification indépendants. This is a preview .
publiées sous le titre général Appareillage à haute tension. Les amendements à ces articles et paragraphes reprennent la même numérotation. y compris un essai de type (facultatif) conforme à l'IEC/TR 62271-208:2009. la numérotation des articles et paragraphes utilisée est la même que celle de l'IEC 62271-1.iec. et les paragraphes supplémentaires sont numérotés à partir de 101. Le contenu du corrigendum d'avril 2015 a été pris en considération dans cet exemplaire. Cette publication a été rédigée selon les Directives ISO/IEC. Afin de simplifier l’indication des exigences correspondantes. les systèmes d’isolation conformes au Tableaux B. par conséquent. peut être consultée sur le site web de l'IEC. IMPORTANT – Le logo "colour inside" qui se trouve sur la page de couverture de cette publication indique qu'elle contient des couleurs qui sont considérées comme utiles à une bonne compréhension de son contenu.click here to buy the full publication IEC 62271-202:2014 © IEC 2014 – 103 – c) l’évaluation des champs électromagnétiques est prise en compte. la publication sera • reconduite. Une liste de toutes les parties de la série IEC 62271. et les exigences d’évaluation des volumes de décharge de pression sous le sol ont été attribuées. Le texte de cette norme est issu des documents suivants: FDIS Rapport de vote 17C/595/FDIS 17C/598/RVD Le rapport de vote indiqué dans le tableau ci-dessus donne toute information sur le vote ayant abouti à l'approbation de cette norme. imprimer cette publication en utilisant une imprimante couleur. Partie 2. Le comité a décidé que le contenu de cette publication ne sera pas modifié avant la date de stabilité indiquée sur le site web de l'IEC sous «http://webstore. f) la méthode de définition du facteur de charge dans une enveloppe pour transformateurs immergés a été étendue aux différents échauffements. ou • amendée. g) pour le calcul du facteur de charge des transformateurs de type sec dans une enveloppe. e) les exigences d’essai d’arc interne ont été adaptées à l'IEC 62271-200:2011. .2 de l'IEC 60076-1:2011 ont été approfondis. • remplacée par une édition révisée.1 et B.ch» dans les données relatives à la publication recherchée. Il convient de lire cette norme en conjonction avec l'IEC 62271-1:2007 et son Amendement 1:2011 à laquelle elle se réfère et qui est applicable sauf indication contraire. pour le transformateur placé à l’extérieur de l’enveloppe (Annexe DD). A cette date. • supprimée. This is a preview . d) l’influence du produit sur l’environnement est prise en compte (Article 12). Les utilisateurs devraient.
Ces postes se trouvent dans des emplacements accessibles au public et il convient que la sécurité des personnes soit assurée dans les conditions de service spécifiées. . les opérateurs et le public. une attention particulière a été portée aux spécifications relatives à la protection des personnes. La conception et les performances du poste préfabriqué sont vérifiées au moyen d'essais de type décrits dans la présente norme. outre les caractéristiques spécifiées. des connexions et des équipements auxiliaires. les valeurs assignées et les procédures d'essai applicables. incluant les essais d'arc dû à un défaut interne. Cela signifie que. This is a preview .click here to buy the full publication – 104 – IEC 62271-202:2014 © IEC 2014 INTRODUCTION Les postes préfabriqués sont définis comme un ensemble soumis à des essais de type et comprenant une enveloppe incluant en général des transformateurs. destinés à fournir de l'énergie basse tension à partir d'un réseau haute tension ou inversement. des appareillages basse tension et haute tension. L'utilisation de matériels soumis à des essais de type ainsi que la conception et la construction adéquates de l'enveloppe assurent cette protection.
En règle générale. un poste préfabriqué est composé d’une enveloppe comprenant les composants électriques suivants: – transformateurs de puissance. seule l’édition citée s’applique.org) IEC 60068-2-75:1997. This is a preview . Toutefois. pour des fréquences de service inférieures ou égales à 60 Hz et pour installation extérieure. Les postes préfabriqués peuvent être situés au niveau du sol ou partiellement ou complètement au-dessous du niveau du sol. Transformateurs de puissance – Partie 1: Généralités .1 Domaine d'application La présente partie de l'IEC 62271 spécifie les conditions de service. dans le présent document et sont indispensables pour son application.2 Références normatives Les documents suivants sont cités en référence de manière normative. Pour les références non datées. – appareillage haute tension et basse tension. par exemple). les dispositions pertinentes de la présente norme sont également applicables aux conceptions pour lesquelles tous ces composants électriques ne sont pas présents (une installation comprenant un transformateur de puissance et un appareillage basse tension. les caractéristiques assignées. 1. dans des endroits accessibles au public et où la protection des personnes est assurée. pour courant alternatif de tensions assignées supérieures à 1 kV et inférieures ou égales à 52 kV côté haute tension. – interconnexions haute tension et basse tension. – des équipements et circuits auxiliaires. Pour les références datées. les exigences structurelles générales et les méthodes d'essai applicables aux postes préfabriqués haute tension/basse tension ou basse tension/haute tension qui sont connectés par câble. Il convient que les postes non préfabriqués satisfassent aux exigences de l'IEC 61936- 1:2010. en intégralité ou en partie. la dernière édition du document de référence s’applique (y compris les éventuels amendements). pour un ou plusieurs transformateurs. IEC 60050 (toutes les parties). pour être manœuvrés de l'intérieur (à aire de manœuvre) ou de l'extérieur (sans aire de manœuvre).electropedia.click here to buy the full publication IEC 62271-202:2014 © IEC 2014 – 105 – APPAREILLAGE À HAUTE TENSION – Partie 202: Postes préfabriqués haute tension/basse tension 1 Généralités 1. Vocabulaire électrotechnique international (disponible sous www. Essais d'environnement – Partie 2-75: Essais – Essai Eh: Essais aux marteaux IEC 60076-1:2011.
Transformateurs de puissance – Partie 12: Guide de charge pour transformateurs de puissance de type sec IEC 60076-13:2006. Coordination de l'isolement des matériels dans les systèmes (réseaux) à basse tension – Partie 1: Principes. Techniques des essais à haute tension pour matériels à basse tension – Partie 1: Définitions. Transformateurs de puissance – Partie 7: Guide de charge pour transformateurs immergés dans l'huile IEC 60076-10:2001. information and general principles (disponible en anglais seulement) IEC 60947-1:2007. Transformateurs de puissance – Partie 10: Détermination des niveaux de bruit IEC 60076-11:2004. Transformateurs de puissance – Partie 3: Niveaux d'isolement. Transformateurs de puissance – Partie 11: Transformateurs de type sec IEC 60076-12:2008. Ensembles d’appareillage de basse tension – Partie 1: Règles générales . prescriptions et modalités relatives aux essais IEC 61439-1:2011. This is a preview . Transformateurs de puissance – Partie 2: Échauffement des transformateurs immergés dans le liquide IEC 60076-3:2013.click here to buy the full publication – 106 – IEC 62271-202:2014 © IEC 2014 IEC 60076-2:2011. Classification des conditions d'environnement – Partie 2-2: Conditions d'environnement présentes dans la nature – Précipitations et vent IEC 60721-2-4:1987. Classification des conditions d'environnement – Deuxième partie: Conditions d'environnement présentes dans la nature – Rayonnement solaire et température Amendement 1:1988 IEC/TS 60815-1:2008. Installations électriques à basse tension – Partie 4-41: Protection pour assurer la sécurité – Protection contre les chocs électriques IEC 60529:1989. Selection and dimensioning of high-voltage insulators intended for use in polluted conditions – Part 1: Definitions. Transformateurs de puissance – Partie 5: Tenue au court-circuit IEC 60076-7:2005. Appareillage à basse tension – Partie 1: Règles générales IEC 61180-1:1992. essais diélectriques et distances d'isolement dans l'air IEC 60076-5:2006. Transformateurs de puissance – Partie 13: Transformateurs auto- protégés immergés dans un liquide diélectrique IEC 60364-4-41:2005. Classification des conditions d'environnement – Partie 1: Agents d'environnement et leurs sévérités Amendement 1:1992 Amendement 2:1995 IEC 60721-2-2:2012. Degrés de protection procurés par les enveloppes (Code IP) Amendement 1:1999 Amendement 2:2013 IEC 60664-1:2007. exigences et essais IEC 60721-1:1990.
N. Aciers de construction mécanique d'usage général ISO 1182:2010. on peut supposer que les conditions normales de service pour l'intérieur prévalent conformément à l'IEC 62271-1:2007. conformément à l'IEC 62271-1:2007. B. Cependant. This is a preview .111. Si la température ambiante à l'intérieur du poste est supérieure aux limites fixées pour les composants par leurs normes de produits respectives. À l'intérieur de l'enveloppe.click here to buy the full publication IEC 62271-202:2014 © IEC 2014 – 107 – IEC 61439-2:2011. G. Appareillage à haute tension – Partie 300: Qualification sismique des disjoncteurs à courant alternatif Guide ISO/IEC 51:1999. Appareillage à haute tension – Partie 1: Spécifications communes Amendement 1:2011 IEC 62271-200:2011.1 Conditions normales de service Sauf spécification contraire dans la présente norme. Essais de réaction au feu de produits – Essai d'incombustibilité ISO 1716:2010. F. Ensembles d’appareillage à basse tension – Partie 2: Ensembles d’appareillage de puissance IEC 62262:2002. 2. Appareillage à haute tension – Partie 208: Méthodes de quantification des champs électromagnétiques à fréquence industrielle en régime établi générés par les ensembles d'appareillages HT et les postes préfabriqués HT/BT IEC/TR 62271-300:2006. E. Matériaux métalliques – Essai de dureté Rockwell – Partie 1: Méthodes d'essais (Échelles A. Essais de réaction au feu de produits — Détermination du pouvoir calorifique supérieur (valeur calorifique) ISO 6508-1:2005. C. D. K. Appareillage à haute tension – Partie 200: Appareillage sous enveloppe métallique pour courant alternatif de tensions assignées supérieures à 1 kV et inférieures ou égales à 52 kV IEC 62271-201:2006. à l'exception de qui suit. H. Appareillage à haute tension – Partie 201: Appareillage sous enveloppe isolante pour courant alternatif de tensions assignées supérieures à 1 kV et inférieures ou égales à 52 kV IEC/TR 62271-208:2009. Degrés de protection procurés par les enveloppes de matériels électriques contre les impacts mécaniques externes (Code IK) IEC 62271-1:2007. . Aspects liés à la sécurité – Principes directeurs pour les inclure dans les normes ISO 1052:1982. un déclassement peut être nécessaire. la température ambiante à l'intérieur de l'enveloppe du poste préfabriqué sera différente de la température ambiante définie en 3. le poste préfabriqué est conçu pour être utilisé dans les conditions normales de service pour les appareillages d'extérieur. T) 2 Conditions normales et spéciales de service L’Article 2 de l'IEC 62271-1:2007 est applicable.
Documents Similar To info_iec62271-202{ed2.0}b
More From Sila Silva