Source: https://www.ecfr.gov/cgi-bin/retrieveECFR?gp=&mc=true&r=SUBPART&n=sp40.14.63.yyyy
Timestamp: 2020-01-19 20:18:40
Document Index: 226028082

Matched Legal Cases: ['§63', '§63', '§63', '§63', '§63', '§63', '§63', '§63', '§63', 'art 63', 'art 60', '§63', 'art 60', 'art 60', 'art 63', '§63', '§63', '§63', '§63', '§63', '§63', '§63', '§63', '§63', '§63', '§63', '§63', '§63', '§63', '§63']

(a) You must be in compliance with the emission limitations and operating limitations which apply to you at all times except during startup, shutdown, and malfunctions.
(b) If you must comply with emission and operating limitations, you must operate and maintain your stationary combustion turbine, oxidation catalyst emission control device or other air pollution control equipment, and monitoring equipment in a manner consistent with good air pollution control practices for minimizing emissions at all times including during startup, shutdown, and malfunction.
(b) Each performance test must be conducted according to the requirements of the General Provisions at §63.7(e)(1) and under the specific conditions in Table 2 of this subpart.
(c) Do not conduct performance tests or compliance evaluations during periods of startup, shutdown, or malfunction. Performance tests must be conducted at high load, defined as 100 percent plus or minus 10 percent.
(c) Consistent with §§63.6(e) and 63.7(e)(1), deviations that occur during a period of startup, shutdown, and malfunction are not violations if you have operated your stationary combustion turbine in accordance with §63.6(e)(1)(i).
[69 FR 10537, Mar. 5, 2004, as amended at 71 FR 20467, Apr. 20, 2006]
(a) Anyone who owns or operates a stationary combustion turbine which must meet the emission limitation for formaldehyde must submit a semiannual compliance report according to Table 6 of this subpart. The semiannual compliance report must contain the information described in paragraphs (a)(1) through (a)(4) of this section. The semiannual compliance report must be submitted by the dates specified in paragraphs (b)(1) through (b)(5) of this section, unless the Administrator has approved a different schedule.
(4) For each deviation from an emission limitation, the compliance report must contain the information in paragraphs (a)(4)(i) through (a)(4)(iii) of this section.
(c) If you are operating as a stationary combustion turbine which fires landfill gas or digester gas equivalent to 10 percent or more of the gross heat input on an annual basis, or a stationary combustion turbine where gasified MSW is used to generate 10 percent or more of the gross heat input on an annual basis, you must submit an annual report according to Table 6 of this subpart by the date specified unless the Administrator has approved a different schedule, according to the information described in paragraphs (d)(1) through (5) of this section. You must report the data specified in (c)(1) through (c)(3) of this section.
(e) If you are operating a lean premix gas-fired stationary combustion turbine or a diffusion flame gas-fired stationary combustion turbine as defined by this subpart, and you use any quantity of distillate oil to fire any new or existing stationary combustion turbine which is located at the same major source, you must submit an annual report according to Table 6 of this subpart by the date specified unless the Administrator has approved a different schedule, according to the information described in paragraphs (d)(1) through (5) of this section. You must report the data specified in (e)(1) through (e)(3) of this section.
(a) You must keep the records as described in paragraphs (a)(1) through (5).
(3) Records of the occurrence and duration of each startup, shutdown, or malfunction as required in §63.10(b)(2)(i).
(4) Records of the occurrence and duration of each malfunction of the air pollution control equipment, if applicable, as required in §63.10(b)(2)(ii).
(5) Records of all maintenance on the air pollution control equipment as required in §63.10(b)(iii).
(3) Fails to meet any emission limitation or operating limitation in this subpart during malfunction, regardless of whether or not such failure is permitted by this subpart; or
(4) Fails to satisfy the general duty to minimize emissions established by §63.6(e)(1)(i).
As stated in §63.6100, you must comply with the following emission limitations
4. a diffusion flame oil-fired stationary combustion turbine as defined in this subpart. limit the concentration of formaldehyde to 91 ppbvd or less at 15 percent O2.
As stated in §63.6120, you must comply with the following requirements for performance tests and initial compliance demonstrations
a. demonstrate formaldehyde emissions meet the emission limitations specified in Table 1 by a performance test initially and on an annual basis AND Test Method 320 of 40 CFR part 63, appendix A; ASTM D6348-03 provided that %R as determined in Annex A5 of ASTM D6348-03 is equal or greater than 70% and less than or equal to 130%; or other methods approved by the Administrator formaldehyde concentration must be corrected to 15 percent O2, dry basis. Results of this test consist of the average of the three 1 hour runs. Test must be conducted within 10 percent of 100 percent load.
b. select the sampling port location and the number of traverse points AND Method 1 or 1A of 40 CFR part 60, appendix A §63.7(d)(1)(i) if using an air pollution control device, the sampling site must be located at the outlet of the air pollution control device.
c. determine the O2 concentration at the sampling port location AND Method 3A or 3B of 40 CFR part 60, appendix A measurements to determine O2 concentration must be made at the same time as the performance test.
d. determine the moisture content at the sampling port location for the purposes of correcting the formaldehyde concentration to a dry basis Method 4 of 40 CFR part 60, appendix A or Test Method 320 of 40 CFR part 63, appendix A, or ASTM D6348-03 measurements to determine moisture content must be made at the same time as the performance test.
§63.6(e)(1) Operation and maintenance Yes
§63.6(e)(3) SSMP Yes
§63.6(f)(1) Applicability of standards except during startup, shutdown, or malfunction (SSM) Yes
§63.7(e)(1) Conditions for conducting performance tests Yes
§63.8(c)(1)(i) Routine and predictable SSM Yes
§63.8(c)(1)(iii) SSMP for CMS required Yes
§63.8(d) CMS quality control Yes
§63.9(g)(3) Notification that criterion for alternative to relative accuracy test audit (RATA) is exceeded Yes If alternative is in use.
§63.10(b)(2)(i)-(iii) Records related to SSM Yes
§63.10(b)(2)(iv)-(v) Records related to actions during SSM Yes
§63.10(b)(2)(xiii) Records when using alternative to RATA Yes For CO standard if using RATA alternative.
§63.10(c) Additional records for sources using CMS Yes Except that §63.10(c)(2)-(4) and (9) are reserved.
§63.10(d)(5) Startup, shutdown, and malfunction reports No Subpart YYYY does not require reporting of startup, shutdowns, or malfunctions.
§63.10(e)(3) Excess emissions and parameter exceedances reports Yes