Source: http://homedocbox.com/Environmental_Safety/77124863-International-standard.html
Timestamp: 2020-08-11 09:48:13
Document Index: 351534319

Matched Legal Cases: ['art 2', 'art 2', 'art 2', 'art 1', 'art 2', 'art 3', 'art 4', 'art 5', 'art 6', 'art 7', 'art 2', 'art 101', 'art 504', 'art 2', 'art 2', 'art 1', 'art 3', 'art 5', 'art 7', 'art 100']

1 INTERNATIONAL STANDARD IEC First edition Mobile and fixed offshore units Electrical installations Part 2: System design IEC 2005 Copyright - all rights reserved No part of this publication may be reproduced or utilized in any form or by any means, electronic or mechanical, including photocopying and microfilm, without permission in writing from the publisher. International Electrotechnical Commission, 3, rue de Varembé, PO Box 131, CH-1211 Geneva 20, Switzerland Telephone: Telefax: Web: Commission Electrotechnique Internationale International Electrotechnical Commission Международная Электротехническая Комиссия PRICE CODE For price, see current catalogue XB
2 IEC:2005(E) CONTENTS FOREWORD...5 INTRODUCTION Scope Normative references Terms and definitions Sources of electrical power General Main source of electrical power Emergency source of electrical power Additional requirements for periodically unattended machinery spaces General requirements for renewable sources of electrical power Arrangement and location Output Additional requirements for electrical emergency power systems Starting arrangements for emergency generators System earthing General General requirements Neutral earthing methods Neutral earthing for systems up to and including V Neutral earthing for systems above V Generators operated in parallel with source transformers Earthing resistors, connection to hull/structure Distribution systems DC distribution systems AC distribution systems Distribution system requirements Earthed distribution systems Methods of distribution Balance of loads Final circuits Control circuits Socket-outlets Shore connections for mobile units Motor circuits Diversity (demand) factors Final circuits Circuits other than final circuits Application of diversity (demand) factors Motive-power circuits - General System study and calculations General Electrical load study Load flow calculations...39
3 IEC:2005(E) Short-circuit calculations Protection and discrimination study Power system dynamic calculations Calculation of harmonic currents and voltages Protection General Characteristic and choice of protective devices with reference to short-circuit rating Choice of protective devices with reference to overload Choice of protective devices with regard to their application Undervoltage protection Overvoltage protection Lighting General General lighting system Emergency lighting system Escape lighting system Lighting circuits in machinery spaces, accommodation spaces, open deck spaces, etc Luminaires Discharge lamp luminaires of voltages above 250 V Searchlights Control and instrumentation Safeguarding Supply arrangement Dependability Safety Segregation Performance Integration Development activities Electromagnetic compatability Design Installation and ergonomics Specific installations Automatic control installations for electrical power supply Machinery control installations Public address and general alarm systems Computer based systems Software Tests Documentation Degrees of protection by enclosures General...67 Bibliography...69
4 IEC:2005(E) Figure 1 Continuity of supply/continuity of service...14 Figure 2 TN-S d.c. system...25 Figure 3 TN-C d.c. system...26 Figure 4 TN-C-S d.c. system...27 Figure 5 IT d.c. system...28 Figure 6 TN-S a.c. system...30 Figure 7 TN-C-S a.c. system...30 Figure 8 TN-C a.c. system...31 Figure 9 IT a.c. system...31 Table 1 Summary of principal features of the neutral earthing methods...23 Table 2 Voltages for d.c. systems...29 Table 3 AC systems having a nominal voltage between 100 V and V inclusive and related equipment...32 Table 4 AC three-phase systems having a nominal voltage above 1 kv and not exceeding 35 kv and related equipment*...33 Table 5 General lighting illumination levels...50 Table 6 Escape Lighting illumination levels...52 Table 7 Minimum requirements for the degree of protection for mobile and fixed offshore units...67
5 IEC:2005(E) 5 INTERNATIONAL ELECTROTECHNICAL COMMISSION MOBILE AND FIXED OFFSHORE UNITS ELECTRICAL INSTALLATIONS Part 2: System design FOREWORD 1) The International Electrotechnical Commission (IEC) is a worldwide organization for standardization comprising all national electrotechnical committees (IEC National Committees). The object of IEC is to promote international co-operation on all questions concerning standardization in the electrical and electronic fields. To this end and in addition to other activities, IEC publishes International Standards, Technical Specifications, Technical Reports, Publicly Available Specifications (PAS) and Guides (hereafter referred to as IEC Publication(s) ). Their preparation is entrusted to technical committees; any IEC National Committee interested in the subject dealt with may participate in this preparatory work. International, governmental and nongovernmental organizations liaising with the IEC also participate in this preparation. IEC collaborates closely with the International Organization for Standardization (ISO) in accordance with conditions determined by agreement between the two organizations. 2) The formal decisions or agreements of IEC on technical matters express, as nearly as possible, an international consensus of opinion on the relevant subjects since each technical committee has representation from all interested IEC National Committees. 3) IEC Publications have the form of recommendations for international use and are accepted by IEC National Committees in that sense. While all reasonable efforts are made to ensure that the technical content of IEC Publications is accurate, IEC cannot be held responsible for the way in which they are used or for any misinterpretation by any end user. 4) In order to promote international uniformity, IEC National Committees undertake to apply IEC Publications transparently to the maximum extent possible in their national and regional publications. Any divergence between any IEC Publication and the corresponding national or regional publication shall be clearly indicated in the latter. 5) IEC provides no marking procedure to indicate its approval and cannot be rendered responsible for any equipment declared to be in conformity with an IEC Publication. 6) All users should ensure that they have the latest edition of this publication. 7) No liability shall attach to IEC or its directors, employees, servants or agents including individual experts and members of its technical committees and IEC National Committees for any personal injury, property damage or other damage of any nature whatsoever, whether direct or indirect, or for costs (including legal fees) and expenses arising out of the publication, use of, or reliance upon, this IEC Publication or any other IEC Publications. 8) Attention is drawn to the Normative references cited in this publication. Use of the referenced publications is indispensable for the correct application of this publication. 9) Attention is drawn to the possibility that some of the elements of this IEC Publication may be the subject of patent rights. IEC shall not be held responsible for identifying any or all such patent rights. International Standard IEC has been prepared by IEC technical committee 18: Electrical installations of ships and of mobile and fixed offshore units. The text of this standard is based on the following documents: FDIS 18/965/FDIS Report on voting 18/995/RVD Full information on the voting for the approval of this standard can be found in the report on voting indicated in the above table. This publication has been drafted in accordance with the ISO/IEC Directives, Part 2.
6 IEC:2005(E) IEC consists of the following parts, under the general title: Mobile and fixed offshore units Electrical installations: Part 1: General requirements and conditions Part 2: System design Part 3: Equipment Part 4: Cables 1) Part 5: Mobile units Part 6: Installation Part 7: Hazardous areas The committee has decided that the contents of this publication will remain unchanged until the maintenance result date indicated on the IEC web site under " in the data related to the specific publication. At this date, the publication will be reconfirmed; withdrawn; replaced by a revised edition, or amended. A bilingual version of this publication may be issued at a later date. 1) Under consideration. Before IEC is published, reference is made to the IEC X series.
7 IEC:2005(E) 7 INTRODUCTION IEC forms a series of International Standards intended to enable safety in the design, selection, installation, maintenance and use of electrical equipment for the generation, storage, distribution and utilisation of electrical energy for all purposes in offshore units, which are being used for the purpose of exploration or exploitation of petroleum resources. This part of IEC also incorporates and co-ordinates, as far as possible, existing rules and forms a code of interpretation, where applicable, of the requirements of the International Maritime Organisation, a guide for future regulations which may be prepared and a statement of practice for offshore unit owners, constructors and appropriate organisations. This standard is based on equipment and practices, which are in current use, but it is not intended in any way to impede development of new or improved techniques. The ultimate aim has been to produce a set of International standards exclusively for the offshore petroleum industry.
8 IEC:2005(E) MOBILE AND FIXED OFFSHORE UNITS ELECTRICAL INSTALLATIONS Part 2: System design 1 Scope This part of IEC contains provisions for system design of electrical installations in mobile and fixed units used in the offshore petroleum industry for drilling, production, processing and for storage purposes, including pipeline, pumping or 'pigging' stations, compressor stations and exposed location single buoy moorings. It applies to all installations, whether permanent, temporary, transportable or hand-held, to a.c. installations up to and including V and d.c. installations up to and including 750 V.(a.c. and d.c. voltages are nominal values) This standard does not apply either to fixed equipment used for medical purposes or to the electrical installations of tankers. 2 Normative references The following referenced documents are indispensable for the application of this document. For dated references, only the edition cited applies. For undated references, the latest edition of the referenced document (including any amendments) applies. IEC 60038:2002, IEC standard voltages IEC :2002, Electrical installations in ships Part 101: Definitions and general requirements IEC :2001, Electrical installations in ships Part 504: Special features Control and instrumentation IEC 60447, Basic and safety principles for man-machine interface, marking and identification Actuating principles IEC 60533, Electrical and electronic installations in ships Electromagnetic compatibility IEC DB:2001 2) Graphical symbols for diagrams Architectural and topographical installation plans and diagrams IEC :2003, Low voltage switchgear and controlgear Part 2: Circuit-breakers IEC , Electromagnetic compatibility (EMC) Part 2-4: Environment Compatibility levels in industrial plants for low-frequency conducted disturbances IEC (all parts), Functional safety of electrical/electronic/programmable electronic safety-related systems 2) DB refers to the on-line IEC database.
9 IEC:2005(E) 9 IEC 61511, (all parts), Functional safety Safety instrumented systems for the process industry sector IEC :2001, Mobile and fixed offshore units Electrical installations Part 1: General requirements and conditions IEC , Mobile and fixed offshore units Electrical installations Part 3: Equipment IEC :2000, Mobile and fixed offshore units Electrical installations Part 5: Mobile units IEC :1997, Mobile and fixed offshore units Electrical installations Part 7: Hazardous areas IEC , High-voltage switchgear and controlgear Part 100: High-voltage alternatingcurrent circuit-breakers SOLAS, International Convention for the Safety of Life at Sea IMO MODU Code:1990, Code for the Construction and Equipment of Mobile Offshore Drilling Units,