Source: http://www.law.cornell.edu/cfr/text/40/part-60/subpart-DDDD/appendix-Table7
Timestamp: 2014-09-23 19:19:02
Document Index: 669035057

Matched Legal Cases: ['art 60', 'art 60', 'art 60', 'art 60', 'art 60', 'art 60', '§ 60', 'art 60', 'art 60', 'art 60', 'art 60', 'art 60', 'art 60', 'art 60', 'art 60', 'art 60', 'art 60']

40 CFR Part 60, Subpart DDDD, Table 7 to Subpart DDDD of Part 60 - Model Rule-Emission Limitations That Apply to Energy Recovery Units After May 20, 2011 | LII / Legal Information Institute
CFR › Title 40 › Chapter I › Subchapter C › Part 60 › Subpart DDDD › Appendix Table7 40 CFR Part 60, Subpart DDDD, Table 7 to Subpart DDDD of Part 60 - Model Rule-Emission Limitations That Apply to Energy Recovery Units After May 20, 2011
Pt. 60, Subpt. DDDD, Table 7
Table 7 to Subpart DDDD of Part 60—Model Rule—Emission Limitations That Apply to Energy Recovery Units After May 20, 2011
You must meet this emissionlimitation a
Using thisaveraging time
And determiningcompliance using this method
a All emission limitations (except for opacity) are measured at 7 percent oxygen, dry basis at standard conditions. For dioxins/furans, you must meet either the total mass basis limit or the toxic equivalency basis limit.
b Incorporated by reference, see § 60.17.
0.023 milligrams per dry standard cubic meter
0.00051 milligrams per dry standard cubic meter
3-run average (collect a minimum volume of 2 dry standard cubic meters)
Performance test (Method 29 at 40 CFR part 60, appendix A-8). Use ICPMS for the analytical finish.
36 parts per million dry volume
Biomass—490 parts per million dry volumeCoal—59 parts per million dry volume
Performance test (Method 10 at 40 CFR part 60, appendix A-4). Use a span gas with a concentration of 100 ppm or less for liquid/gas boilers and coal-fed boilers. Use a span gas with a concentration of 1000 ppm or less for biomass-fed boilers.
Dioxins/furans (total mass basis)
2.9 nanograms per dry standard cubic meter
0.35 nanograms per dry standard cubic meter
3-run average (collect a minimum volume of 1 dry standard cubic meter)
Performance test (Method 23 at 40 CFR part 60, appendix A-7).
0.32 nanograms per dry standard cubic meter
0.059 nanograms per dry standard cubic meter
14 parts per million dry volume
0.45 parts per million dry volume
3-run average (collect a minimum volume of 1 dry standard cubic meters)
Performance test (Method 26 or 26A at 40 CFR part 60, appendix A-8).
0.096 milligrams per dry standard cubic meter
0.0036 milligrams per dry standard cubic meter
0.0013 milligrams per dry standard cubic meter
0.00033 milligrams per dry standard cubic meter
3-run average (For Method 29 and ASTM D6784-02 (Reapproved 2008),b collect a minimum volume of 2 dry standard cubic meters per run. For Method 30B, collect a minimum sample as specified in Method 30B at 40 CFR part 60, appendix A)
Performance test (Method 29 or 30B at 40 CFR part 60, appendix A-8) or ASTM D6784-02 (Reapproved 2008).b
76 parts per million dry volume
Biomass—290 parts per million dry volumeCoal—340 parts per million dry volume
Performance test (Method 7E at 40 CFR part 60, appendix A-4). Use a span gas with a concentration of 150 ppm or less for liquid/gas fuel boilers. Use a span gas with a concentration of 700 ppm or less for solid fuel boilers.
Particulate matter filterable
110 milligrams per dry standard cubic meter
250 milligrams per dry standard cubic meter or 30-day rolling average if PM CEMS is required or being used
Performance test (Method 5 or 29 at 40 CFR part 60, appendix A-3 or appendix A-8) if the unit has a design capacity less than or equal to 250 MMBtu/hr; or PM CEMS (performance specification 11 of appendix B of this part) if the unit has a design capacity greater than 250 MMBtu/hr. Use Method 5 or 5I of Appendix A of this part and collect a minimum sample volume of 1 dscm for the PM CEMS correlation testing.
720 parts per million dry volume
Biomass—6.2 parts per million dry volumeCoal—650 parts per million dry volume
Performance test (Method 6 or 6c at 40 CFR part 60, appendix A-4. Use a span gas with a concentration of 20 ppm or less for biomass-fed boilers. Use a span gas with a concentration of 1500 ppm or less for liquid/gas and coal-fed boilers.
Fugitive ash
Visible emissions for no more than 5 percent of the hourly observation period
Three 1-hour observation periods
Visible emission test (Method 22 at 40 CFR part 60, appendix A-7).
At 76 FR 15486, Mar. 21, 2011, table 7 to subpart DDDD is added, effective May 20, 2011. At 76 FR 28661, May 18, 2011, the amendment was delayed indefinitely. Title 40 published on 2014-07-01The following are only the Rules published in the Federal Register after the published date of Title 40.For a complete list of all Rules, Proposed Rules, and Notices view the Rulemaking tab.2014-08-15; vol. 79 # 158 - Friday, August 15, 201479 FR 48072 - NESHAP for Reciprocating Internal Combustion Engines; NSPS for Stationary Internal Combustion Engines