Source: https://www.ecfr.gov/cgi-bin/text-idx?mc=true&node=se40.17.65_1103&rgn=div8
Timestamp: 2020-05-28 15:28:34
Document Index: 543534701

Matched Legal Cases: ['art 65', '§65', '§65', '§65', '§65', '§65', '§65', '§65', '§65', '§65', '§65', '§65', '§65', '§65', '§65', '§65', '§65', '§65', '§65', '§65', '§65', '§65', '§65', '§63', '§65']

Title 40 → Chapter I → Subchapter C → Part 65 → Subpart F → §65.103
§65.103 Equipment identification.
(a) General equipment identification. Equipment subject to this subpart shall be identified. Identification of the equipment does not require physical tagging of the equipment. For example, the equipment may be identified on a plant site plan, in log entries, by designation of process unit boundaries, by some form of weatherproof identification, or by other appropriate methods.
(b) Additional equipment identification. In addition to the general identification required by paragraph (a) of this section, equipment subject to any of the provisions in §§65.106 through 65.115 shall be specifically identified as required in paragraphs (b)(1) through (6) of this section, as applicable. Paragraph (b) of this section does not apply to an owner or operator of a batch product-process who elects to pressure test the batch product-process equipment train pursuant to §65.117.
(1) Connectors. Except for inaccessible, ceramic, or ceramic-lined connectors meeting the provisions of §65.108(e)(2), and instrumentation systems identified pursuant to paragraph (b)(5) of this section, identify the connectors subject to the requirements of this subpart. Connectors subject to §65.108(e)(3) shall be distinguished from other connectors. Connectors need not be individually identified if all connectors in a designated area or length of pipe subject to the provisions of this subpart are identified as a group, and the number of connectors subject is indicated. With respect to connectors, the identification shall be complete no later than the completion of the initial survey required by §65.108(a).
(3) Routed to a process or fuel gas system or equipped with a closed vent system and control device. Identify the equipment that the owner or operator elects to route to a process or fuel gas system or equip with a closed vent system and control device under the provisions of §65.107(e)(3) (pumps in light liquid service), §65.109(e)(3) (agitators), §65.111(d) (pressure relief devices in gas/vapor service), §65.112(e) (compressors), or §65.118 (alternative means of emission limitation for enclosed-vented process units).
(4) Pressure relief devices. Identify the pressure relief devices equipped with rupture disks under the provisions of §65.111(e).
(5) Instrumentation systems. Identify instrumentation systems subject to the provisions of this subpart. Individual components in an instrumentation system need not be identified.
(6) Equipment in service less than 300 hours per calendar year. Identify either by list, location (area or group), or other method, equipment in regulated material service less than 300 hours per calendar year within a process unit subject to the provisions of this subpart.
(c) Special equipment designations: Equipment that is unsafe or difficult-to-monitor—(1) Designation and criteria for unsafe-to-monitor. Valves meeting the provisions of §65.106(e)(1), pumps meeting the provisions of §65.107(e)(6), connectors meeting the provisions of §65.108(e)(1), and agitators meeting the provisions of §65.109(e)(7) may be designated unsafe-to-monitor if the owner or operator determines that monitoring personnel would be exposed to an immediate danger as a consequence of complying with the monitoring requirements of this subpart.
(2) Designation and criteria for difficult-to-monitor. Valves meeting the provisions of §65.106(e)(2) may be designated difficult-to-monitor if the provisions of paragraph (c)(2)(i) of this section apply. Agitators meeting the provisions of §65.109(e)(5) may be designated difficult-to-monitor if the provisions of paragraph (c)(2)(ii) of this section apply.
(i) Valves. The owner or operator of the valve:
(A) Determines that the valve cannot be monitored without elevating the monitoring personnel more than 2 meters (7 feet) above a support surface, or it is not accessible in a safe manner when it is in regulated material service, and the process unit within which the valve is located is a regulated source for which the owner or operator commenced construction, reconstruction, or modification prior to the compliance date of the referencing subpart; or
(B) Designates less than 3 percent of the total number of valves within the process unit as difficult-to-monitor.
(ii) Agitators. The owner or operator determines that the agitator cannot be monitored without elevating the monitoring personnel more than 2 meters (7 feet) above a support surface, or it is not accessible in a safe manner when it is in regulated material service.
(3) Identification of unsafe or difficult-to-monitor equipment. The owner or operator shall record the identity of equipment designated as unsafe-to-monitor according to the provisions of paragraph (c)(1) of this section and the planned schedule for monitoring this equipment. The owner or operator shall record the identity of equipment designated as difficult-to-monitor according to the provisions of paragraph (c)(2) of this section, the planned schedule for monitoring this equipment, and an explanation why the equipment is difficult-to-monitor.
(4) Written plan requirements. (i) The owner or operator of equipment designated as unsafe-to-monitor according to the provisions of paragraph (c)(1) of this section shall have a written plan that requires monitoring of the equipment as frequently as practical during safe-to-monitor times, but not more frequently than the periodic monitoring schedule otherwise applicable, and repair of the equipment according to the procedures in §65.105 if a leak is detected.
(ii) The owner or operator of equipment designated as difficult-to-monitor according to the provisions of paragraph (c)(2) of this section shall have a written plan that requires monitoring of the equipment at least once per calendar year and repair of the equipment according to the procedures in §65.105 if a leak is detected.
(d) Special equipment designations: Equipment that is unsafe to repair—(1) Designation and criteria. Connectors subject to the provisions of §65.105(e) may be designated unsafe to repair if the owner or operator determines that repair personnel would be exposed to an immediate danger as a consequence of complying with the repair requirements of this subpart, and if the connector will be repaired before the end of the next process unit shutdown as specified in §63.105(e).
(2) Identification of equipment. The identity of connectors designated as unsafe to repair and an explanation why the connector is unsafe to repair shall be recorded.
(e) Special equipment designations: Compressors operating with an instrument reading of less than 500 parts per million. Identify the compressors that the owner or operator elects to designate as operating with an instrument reading of less than 500 parts per million under the provisions of §65.112(f).
(f) Special equipment designations: Equipment in heavy liquid service. The owner or operator of equipment in heavy liquid service shall comply with the requirements of either paragraph (f)(1) or (2) of this section as provided in paragraph (f)(3) of this section.
(1) Retain information, data, and analyses used to determine that a piece of equipment is in heavy liquid service.
(2) When requested by the Administrator, demonstrate that the piece of equipment or process is in heavy liquid service.
(3) A determination or demonstration that a piece of equipment or process is in heavy liquid service shall include an analysis or demonstration that the process fluids do not meet the definition of “in light liquid service.” Examples of information that could document this include, but are not limited to, records of chemicals purchased for the process, analyses of process stream composition, engineering calculations, or process knowledge.