Source: http://docplayer.net/21576097-Section-15105-ductile-iron-pipe-and-fittings.html
Timestamp: 2019-01-22 23:09:28
Document Index: 101698101

Matched Legal Cases: ['ART 1', 'ART 2', 'ART 3', 'art 2', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1']

SECTION DUCTILE IRON PIPE AND FITTINGS - PDF
SECTION DUCTILE IRON PIPE AND FITTINGS
Download "SECTION 15105 DUCTILE IRON PIPE AND FITTINGS"
Annabel Maude Holmes
1 SECTION DUCTILE IRON PIPE AND FITTINGS PART 1 GENERAL.01 COORDINATION OF WORK Connection to existing pipelines may require shutdown of Owner facilities. Closely coordinate construction work and connections with the Owner through the Engineer. The Engineer, in consultation with the Owner, may select the time for connection to existing pipelines, including Saturdays, Sundays, or holidays, which, in the opinion of the Engineer, will cause the least inconvenience to the Owner and/or its customers. Make such connections at such times as may be directed by the Owner, at the Contract prices, with no claim for premium time or additional costs..02 RELATED WORK Piping - General Provisions - Specification Section SUBMITTALS Submit shop drawings and manufacturer's literature for all Contractor supplied materials promptly to the Engineer for approval in accordance with Specification Section PART 2 PRODUCTS Research has documented that certain elastomers (such as those used in gasket material) may be subject to permeation by lower-molecular weight organic solvents or petroleum products. Products supplied under this Specification Section assume that petroleum products or organic solvents will not be encountered. If during the course of pipeline installation the Contractor identifies, or suspects the presence of petroleum products or any unknown chemical substance, notify AW immediately. Stop installing piping in the area of suspected contamination until direction is provided by AW..01 PIPE MATERIAL A. General Ductile iron pipe shall conform to the latest specifications as adopted by the American National Standards Institute, Inc., (ANSI) and the American Water
2 Works Association (AWWA). Specifically, ductile iron pipe shall conform to AWWA Standard C151. The pipe or fitting exterior shall be coated with a bituminous coating in accordance with AWWA Standard C151. The pipe or fitting interior shall be cement mortar lined and seal coated in compliance with the latest revision of AWWA Standard C104. B. Quality Pipe and fittings shall meet the following minimum quality requirements by conforming to the following: 1. AWWA C105 / ANSI A21.5 Cement-Mortar Lining for Ductile-Iron Pipe and Fittings for Water Polyethylene Encasement for Ductile- Iron Pipe Systems 2. AWWA C110 / ANSI A21.10 Ductile Iron and Gray Iron Fittings, 3 NPS through 48 NPS for Water AWWA C111 / ANSI A21.11 Rubber-Gasket Joints for Ductile-Iron Pressure Pipe and Fittings 3. AWWA C115 / ANSI A21.15 Flanged Ductile-Iron Pipe with Ductile- Iron or Gray-Iron Threaded Flanges 4. AWWA C116 / ANSI A21.16 Protective Fusion-Bonded Epoxy Coating for the Interior and Exterior Surfaces of Ductile-Iron and Gray-Iron Fittings for Water Supply Service 5. AWWA C150 / ANSI A21.50 Thickness Design of Ductile-Iron Pipe 6. AWWA C151 / ANSI A21.51 Ductile-Iron Pipe, Centrifugally Cast, for Water 7. AWWA C153 / ANSI A21.53 Ductile-Iron Compact Fittings, 3 NPS through 24 NPS and 54 NPS through 64 NPS, for Water Service Ductile iron water pipe and fittings will be accepted on the basis of the Manufacturer s certification that the material conforms to this specification. The certification for iron fittings shall list a fitting description, quantity, bare fitting weight and source, (AWWA Standard C110, C153 or Manufacturer, if fitting is not listed in either standard). The certification shall accompany the material delivered to the project site. The Owner reserves the right to sample and test this material subsequent to delivery at the project site. If foreign manufactured fittings are provided, then the Contractor is obligated to notify AW with a submittal and provide the necessary documentation to satisfy the AW that the materials provided meet the specified AWWA standards and, among other documentation that may be required, provide certificates of compliance on the component supplied
3 C. Pipe Class The pressure class of pipe to be furnished shall be in accordance with Table 1 and the notes listed below. D. Testing Table 1 MINIMUM RATED WORKING PRESSURE FOR DUCTILE IRON PIPE MANUFACTURED IN ACCORDANCE WITH AWWA Standard C151 Pressure Class Pipe Size (Inch) NOTES: 1. Larger pipe sizes up to 54-inch can be installed as pressure Class 200 with cover up to nine (9) feet and an operating pressure of 200 psi, where approved by the Engineer. When trench depths exceed fifteen (15) feet for pipe sizes of 16-inch or larger, AW shall direct the Contractor on the proper class pipe to use. 2. The noted pressure class is adequate to support 3/4 and 1-inch corporation stops. Use a full saddle for larger taps (e.g.., air relief valves or larger corporations) due to limited wall thickness. 3. There are special conditions where a larger wall thickness is required. AW shall direct the Contractor on the proper pressure class pipe to use in specific instances; e.g. at treatment plant or booster station sites where frequent excavation can be anticipated in the vicinity of pipe, where the pipeline is laid on a river channel bottom to prevent external damage to the pipe and minimize the potential for costly pipe replacement, etc. Perform a hydrostatic test of all pipe and appurtenances as required by AWWA Standard C151 and Specification Section
4 E. Joints.02 FITTINGS 1. Mechanical and Push-On Mechanical and push-on joints including accessories shall conform to AWWA Standard C Flanged Flanged joints shall conform to AWWA Standard C110 or ANSI B16.1 for fittings and AWWA Standard C115 for pipe. Do not use flanged joints in underground installations except within structures. Furnish all flanged joints with 1/8-inch thick, red rubber or styrene butadiene rubber gaskets. The bolts shall have American Standard heavy unfinished hexagonal head and nut dimensions all as specified in American Standard for Wrench Head Bolts and Nuts and Wrench Openings (ANSI B18.2). For bolts of 1-3/4-inches in diameter and larger, bolt studs with a nut on each end are recommended. The highstrength, low-alloy steel for bolts and nuts shall have the characteristics listed in Table 6 of AWWA Standard C Restrained Joint Pipe Restrained joints for pipes shall be of the boltless push-on type which provides joint restraint independent of the joint seal. Restrained pushon joints allowed for pipe only shall have accessories conforming to AWWA Standard C111. Restrained system shall be suitable for the following minimum working pressures: A. Ductile Iron Fittings Size (Inch) Pressure (psi) Less than " " - 64" 200 Standard fittings shall be ductile iron conforming to AWWA Standard C110. Compact ductile iron fittings shall meet the requirements of AWWA Standard C
5 1. Working Pressures Fittings shall be suitable for the following working pressures unless otherwise noted in AWWA Standard C110 or C153: Pressure (psi) Compact Fittings Standard Fittings Size Ductile Iron Ductile Iron 3" - 24" , 350 (with special gaskets) 30" - 48" N/A The use of standard ductile iron fittings having a 250 psi pressure rating with ductile iron pipe (having a rating of 350 psi) is not permitted except by the expressed written approval by AW. 2. Coating and Lining The fittings shall be coated on the outside with a petroleum asphaltic coating in accordance with AWWA Standard C110 or fusion coated epoxy in accordance with AWWA Standard C116 and lined inside with cement-mortar and seal coated in accordance with AWWA Standard C104 or fusion coated epoxy in accordance with AWWA Standard C116. B. Joints 1. Mechanical and Push-On Mechanical and push-on joints including accessories shall conform to AWWA Standard C111. Anti-Rotation l T-Bolts shall be used on mechanical joints shall be of domestic origin, high strength, low alloy steel bolts only, meeting the current provisions of American National Standard ANSI/AWWA C111/A for rubber gasket joints for cast iron or ductile iron pipe and fittings. Bolt manufacturer s certification of compliance must accompany each shipment. T-bolts shall corrosion resistant to handle corrosive conditions on any buried bolts. 2. Flanged Flanged joints shall meet the requirements of AWWA Standard C115 or ANSI B16.1. Do not use flanged joints in underground installations except within structures. Furnish all flanged joints with a minimum
6 PART 3 EXECUTION 1/8-inch, thick red rubber or styrene butadiene rubber gasket. The bolts shall have American Standard heavy unfinished hexagonal head and nut dimensions all as specified in ANSI B18.2. Xylan or FluoroKote #1 Hex Bolts (corrosion resistant) to handle corrosive conditions shall be used on any buried flanged bolts. Flange gaskets shall be rubber in composition; paper gaskets are not permitted. Bolts and nuts hall be threaded in accordance with ASME/ANSI B1.1, Unified Inch Screw Threads (UN and UNR Thread Form) class 2A external and class 2B internal. For bolts of 1-3/4-inches in diameter and larger, bolt studs with a nut on each end are recommended. Material for bolts and nuts shall conform to ASTM A307, 60,000 PSI Tensile Strength, Grade B, unless otherwise specified. Bolt manufacturer s certification of compliance must accompany each shipment. 3. Restrained.01 INSTALLATION Restrained joints for valves and fittings shall be of the boltless push-on type which provides joint restraint independent of the joint seal. Field Lok gaskets are not permitted on valves or fittings. Restrained pushon joints allowed for pipe only shall have accessories conforming to AWWA Standard C111. Restrained system shall be suitable for the following minimum working pressures: Size Pressure (psi) Less than " " - 64" 250 Where adjacent fittings are to be placed (as in a mechanical joint hydrant tee and a mechanical joint hydrant valve), the use of a suitably sized Foster adaptor is permitted to facilitate restraint between the fittings. Follow the provisions of Specification Section in addition to the following requirements:
7 A. Push-On Joints Clean the surfaces that the gasket will contact thoroughly, just prior to assembly using a bacteria free solution (bleach, potable water or NSF approved material). Insert the gasket into the groove in the bell. Apply a liberal coating of special lubricant to the gasket and the spigot end of the pipe before assembling the joint. Center the spigot end in the bell and push home the spigot end. B. Mechanical Joints Clean and lubricate all components with soapy water prior to assembly. Slip the follower gland and gasket over the pipe plain end making sure that the small side of the gasket and lip of the gland face the bell socket. Insert the plain end into socket. Push gasket into position with fingers. Seat gasket evenly. Slide gland into position, insert bolts, and tighten nuts by hand. Tighten bolts alternately (across from one another) to the recommended manufacturing rating or if not provided, to the following normal torques: Bolt Size Range of Torque In Foot-Pounds 5/8" /4" " /4" After field installation, all bolts shall receive petrolatum tape or petroleum wax protection or other approved coating material. Protection shall be applied before applying polywrap per specification C. Restrained Joints 1. Ball and Socket Assemble and install the ball and socket joint according to the manufacturer's recommendations. Thoroughly clean and lubricate the joint. Check the retainer ring fastener. 2. Push-On Assemble and install the push-on joint according to the manufacturer's recommendations. Thoroughly clean and lubricate the joint. Check the retainer ring fastener
8 D. Pipe Protection Protect pipe from damage from the jacking device (backhoe bucket, pipe jack, etc.) when pushing home any pipe by using wood or other suitable (non metallic) material. (3) Mechanical Joint Assemble and install the mechanical joint according to the manufacturer's recommendations. Thoroughly clean and lubricate the joint. Use approved restrained joint device on fittings and valves where required and approved for use by AW. Protect pipe from damage from the jacking device (backhoe bucket, pipe jack, etc.) when pushing home any pipe. Wood or other suitable material (non metallic) shall be used to push home the pipe. E. Gaskets Gaskets shall be as provided or recommended by the manufacturer and satisfy AWWA standard C111 in all respects. As noted in the products section of this specification, some gasket materials are prone to permeation of certain hydrocarbons which may exist in the soil (see part 2). Under these conditions and at AW S discretion require contractor to provide FKM (Viton, Flourel) gasket material in areas of concern. END OF SECTION
SECTION 15056 DUCTILE-IRON PIPE AND FITTINGS
SECTION 15056 PART 1 GENERAL 1.01 DESCRIPTION This section includes materials and installation of ductile-iron pipe and fittings for potable and recycled water systems. A written request to use Ductile
SECTION 33 11 00.11 POLYVINYL CHLORIDE (PVC) PIPE
SECTION 33 11 00.11 POLYVINYL CHLORIDE (PVC) PIPE PART 1: GENERAL 1.01 SECTION INCLUDES PVC pressure pipe and fabricated fittings in nominal sizes 4-inches through 12-inches with cast iron pipe equivalent
AMERICAN Mechanical Joint Pipe For Water, Sewage or Other Liquids
AMERICAN Mechanical Joint Pipe For Water, Sewage or Other Liquids The AMERICAN Mechanical Joint was developed by the American Cast Iron Pipe Company and first marketed in 1929. Since that time, millions
2014 Edition 3"-64" NSF. industrial Applications, water & Wastewater. Certified to ANSI/NSF 61
3"-64" Ductile Iron industrial Applications, water & Wastewater 866.DI.IE 2 Table of Contents Flanged ipe for Water and Other Liquids 3 Ductile Iron Flanged ipe With Threaded Flanges-Flanged Details 5
SECTION 8 AMERICAN. Flanged Pipe
SECTION 8 AMERICAN Flanged Pipe The principal standards covering Flanged Pipe are ANSI/AWWA C115/A21.15 and ANSI/AWWA C110/A21.10. These and other standards are referenced throughout this Section either
DESIGN AND CONSTRUCTION GUIDELINES AND STANDARDS DIVISION 33 UTILITIES 33 00 00 SITE UTILITIES
SECTION INCLUDES Domestic Water Fire Water Service Water Well Sanitary Sewer Storm Drains Foundation Drainage RELATED SECTIONS 03 30 00 Concrete 21 00 00 Fire Suppression - Sprinklers 22 00 00 Plumbing
FULL FACE FLANGE-TYTE Gasket FOR FLANGED JOINTS
4"-64" FULL FACE FLANGE-TYTE Gasket FOR FLANGED JOINTS NSF FOR WATER & WASTEWATER, FIRE PROTECTION & INDUSTRIAL APPLICATIONS NSF P 2 Table of Contents Introduction 3 Pressure Performance 3 Torque Performance
3. ASTM D Specification for Rigid Poly (Vinyl Chloride) (PVC) Compounds and Chlorinated Poly (Vinyl Chloride) (CPVC) Compounds.
SECTION 02623 PART 1 GENERAL 1.1 SCOPE OF WORK A. Furnish all labor, materials, equipment, and incidentals required, and install polyvinyl chloride (PVC) waterline, fittings, service connections and appurtenances
SECTION 15064 PVC PRESSURE PIPE AWWA C900
SECTION 15064 PVC PRESSURE PIPE (AWWA C900) PART 1 GENERAL 1.01 DESCRIPTION This section includes materials, installation, and testing of polyvinyl chloride (PVC) pressure pipe conforming to AWWA C900.
Section C-1 Pipes and Fittings
Section C-1 Pipes and Fittings C1.00 Work Included The work under this Division of the Specifications shall include all labor, materials, and equipment necessary to furnish and install all piping, pipelines,
Section 3510: Reclaimed water Pipes, Valves, and Appurtenances February 11, 2011
STANDARDS AND CONSTRUCTION MANUAL : Reclaimed water Pipes, Valves, and Appurtenances February 11, 2011 PART 1 - GENERAL 1.01 SCOPE OF WORK A. These specifications cover the pipes, fittings, and appurtenances
STANDARD SPECIFICATION SECTION 15292 POLYVINYL CHLORIDE (PVC) PRESSURE PIPE (AWWA C900)
STANDARD SPECIFICATION SECTION 15292 POLYVINYL CHLORIDE (PVC) PRESSURE PIPE (AWWA C900) PART 1 - GENERAL 1.01 DESCRIPTION This section includes materials, installation, and testing of PVC pressure pipe
SECTION 02720 SANITARY SEWER AND STORM DRAIN SYSTEMS
SECTION 02720 SANITARY SEWER AND STORM DRAIN SYSTEMS PART 1 GENERAL 1.01 SECTION INCLUDES A. The requirements for pipe material and installation in sewer and drainage collection systems. All materials
SECTION WATER MAINS. 1. Protection of the environment; Section Trench excavation, backfill, and compaction; Section
02551-1 of 13 SECTION 02551 WATER MAINS 02551.01 GENERAL A. Description Water main installation shall include, but not necessarily be limited to, furnishing and installing water pipe, fittings, and appurtenances
Technical Note PP 811-TN PE Flange Connections
Technical Note PP 811-TN PE Flange Connections Flange Connection Flanged joints are made using a DriscoPlex Flange Adapter that is fused to the pipe then joined to a mating flange adapter or a mating appurtenance
SECTION 15125 HIGH DENSITY POLYETHYLENE (HDPE) PIPE AND FITTINGS FOR WATER DISTRIBUTION AND TRANSMISSION
SECTION 15125 HIGH DENSITY POLYETHYLENE (HDPE) PIPE AND FITTINGS FOR WATER DISTRIBUTION AND TRANSMISSION PART 1 GENERAL.01 SECTION INCLUDES Furnishing and installing 4 inch through 16 inch high density
Strength and Durability for Life. FEATURES Ductile Iron Pipe Joints and Their Uses
Strength and Durability for Life FEATURES Ductile Iron Pipe Joints and Their Uses Last Revised: May 2016 Joints for Iron pipe have come a long way. About 550 years ago, the first Cast Iron pipes were made
SECTION 02401 - SANITARY SEWER PIPE
PART 1 - GENERAL 1.1 DESCRIPTION A. The WORK under this Section includes providing all labor, materials, tools and equipment necessary for furnishing and installing sanitary sewer pipe, in accordance with
San Antonio Water System Standard Specifications for Construction ITEM NO. 816 STEEL PIPE INSTALLATION
ITEM NO. 816 STEEL PIPE INSTALLATION 816.1 DESCRIPTION: This item shall consist of steel pipe installation in accordance with these specifications and as directed by the Engineer. 816.2 SUBMITTALS: Contractor
Mechanical Joint Restraints
-15 PVC Pipe Restrainer The PVC mechanical joint restrainer eliminates the need for thrust blocking, tie rodding, or harnessing mechanical joint fittings when they are used with PVC pipe. The key to the
SECTION 13 WATER MAIN TAPS General
SECTION 13 WATER MAIN TAPS 13-1.01 Scope 13-1 General This section describes the requirements for furnishing and installing water main taps using tapping saddles, couplings, and sleeves; including the
WATER MAIN CONSTRUCTION TECHNIQUES DEPARTMENT OF PUBLIC WORKS WATER & WASTEWATER DIVISION
WATER MAIN CONSTRUCTION TECHNIQUES Overview Water Main - Materials Specifications Installation Future? Water Main Materials Material Types There are various material types used for water mains, these include:
Mechanical joint fittings
30"-48" Mechanical joint fittings Ductile Iron - c110 For Water & Wastewater, Fire rotection & Industrial pplications 866.DI.IE 2 able of Contents Mechanical Joint Fittings 3 Standard Mechanical Joint
POLYETHYLENE ENCASEMENT
FOR DUCTILE IRON PIPE FOR WATER & WASTEWATER, FIRE PROTECTION & INDUSTRIAL APPLICATIONS P2 Table of Contents Polyethylene Encasement 3 Installation Instructions 4 Products for Water, Wastewater and Fire
University of Rhode Island. URI Water System Specifications
University of Rhode Island Water System Work Specifications 1. Water System Authorization a. Only authorized URI employees or approved contractors shall be allowed to make water service repairs, connections
INDEX. Sec. No. Items Page Nos.
INDEX Sec. No. Items Page Nos. 1. Types of Pipe............... MSSP- 2 2. Concrete Pipe............... MSSP- 2 thru MSSP-3 3. ABS and PVC Truss Pipe............... MSSP- 3 4. ABS and PVC Solid Wall Pipe...............
SECTION DIP AND PVC PIPE, FITTINGS, VALVES, AND APPURTENANCES
SECTION 02600 DIP AND PVC PIPE, FITTINGS, VALVES, AND APPURTENANCES PART 1 GENERAL 1.01 DESCRIPTION OF WORK: A. This section includes the material and installation standards for pipe, fittings, valves,
Suggested Specifications: Steel Pipe for Water Transmission
Suggested Specifications: Steel Pipe for Water Transmission. Suggested Specifications - Steel Pipe for Water Transmisssion Cement-mortar Lined and Tape Coated PART 1 - GENERAL 1.01 Description Scope of
SECTION 15062 POLYVINYL CHLORIDE GRAVITY SEWER PIPE AND FITTINGS
SECTION 15062 POLYVINYL CHLORIDE (PVC) GRAVITY SEWER PIPE AND FITTINGS PART 1 GENERAL 1.01 DESCRIPTION This section designates the requirements for the manufacture and installation of polyvinyl chloride,
DUCTILE IRON PIPE JOINTS AND THEIR USES
DUCTILE IRON PIPE JOINTS AND THEIR USES Ductile Iron Pipe Joints and Their Uses By Richard W. Bonds, P.E. DIPRA Research and Technical Director Introduction Joints for Iron pipe have come a long way. About
ONTARIO P.O. Box 2849 1757 Burlington Street East Hamilton, ON L8N 3R5 Tel: (905) 547-3251 Fax: (905) 547-7369
ONTARIO P.O. Box 2849 1757 Burlington Street East Hamilton, ON L8N 3R5 Tel: (905) 547-3251 Fax: (905) 547-7369 WESTERN #1100-1200 West 73 rd Avenue Vancouver, BC V6P 6G5 Tel: (604) 737-1279 Fax: (604)
SECTION 02110 - ASBESTOS CEMENT PIPE REPAIRS, DEMOLITION, AND DISPOSAL
SECTION 02110 - ASBESTOS CEMENT PIPE REPAIRS, DEMOLITION, AND DISPOSAL PART 1 - GENERAL 1.1 WORK INCLUDED IN THIS SECTION A. The WORK of this Section includes the repair, demolition, and disposal of asbestos
866.DIP.PIPE Edition. pipe and fittings mm
2005 Edition 2008 EDITION 100-1600 mm INTERNATIONAL Restrained joint ductile iron pipe and fittings Water & Wastewater 2 Table of Contents Introduction 3 General Specifications Dimensions 5 Mechanical
field cutting and welding
Restrained Joint Ductile Iron Pipe and Fittings For FIRE PROTECTION, Water & Wastewater P 2 Table of Contents Field Cutting and Welding Procedure 3 Materials and Equipment 4 8 Field Cutting and Welding
08003-1 WATER SERVICE 2
08003_Mar08_2011.pdf Page 1 of 7 INDEX Page 08003-1 WATER SERVICE 2 1.1 Pipe 2 1.1.1 Copper 2 1.1.2 Polyethylene 2 1.2 Valves and Fittings 2 1.2.1 Main Stops 3 1.2.2 Curb Stops 3 1.2.3 Curb Box 3 1.2.4
SECTION 6 SANITARY SEWER MAIN 6.01 SCOPE
6.01 SCOPE The work covered by this section of the specifications consists of the furnishing of all plant, labor, materials, equipment and supervision and performing all operations involved in the construction
MS-3/2009 HDPE (High Density Polyethylene) Pipe and Fittings Specification for Buried Potable Water
MS-3/2009 HDPE (High Density Polyethylene) Pipe and Fittings Specification for Buried Potable Water 105 Decker Court, Suite 825, Irving, TX 75062 P: 469-499-1044 F: 469-499-1063 www.plasticpipe.org HDPE
SECTION 15 AIR RELEASE VALVE ASSEMBLIES. 15-1 General
SECTION 15 AIR RELEASE VALVE ASSEMBLIES 15-1.01 Scope 15-1 General This section describes the requirements for furnishing and installing Air Release Valve Assemblies of the size and type shown on the plans,
SECTION 603 SANITARY SEWER FORCE MAINS
SECTION 603 SANITARY SEWER FORCE MAINS 1. GENERAL Pipelines for sanitary sewer force main systems shall conform to the following specifications and shall be installed at the locations indicated on the
SECTION 06000 WATER DISTRIBUTION SYSTEMS TABLE OF CONTENTS
SECTION 06000 WATER DISTRIBUTION SYSTEMS TABLE OF CONTENTS 06010 WATER DISTRIBUTION PIPE A. Design B. Materials C. Installation 06020 FIRE PROTECTION A. Fire Hydrants B. Automatic Fire Sprinkler Systems
SECTION 02563 SANITARY SEWER FORCE MAINS
SECTION 02563 SANITARY SEWER FORCE MAINS 1.0 GENERAL A. Description Sanitary sewer force main installation shall include, but not necessarily be limited to, furnishing and installing pressure rated pipe,
SECTION 33 11 00.13 HIGH DENSITY POLYETHYLENE (HDPE) PIPE AND FITTINGS
SECTION 33 11 00.13 HIGH DENSITY POLYETHYLENE (HDPE) PIPE AND FITTINGS PART 1: GENERAL 1.01 SECTION INCLUDES Furnishing and installing up to 16-inch high density polyethylene (HDPE) pipe and fittings for
American- Darling 5¼" B-84-B-5.
-5 Sealed Lubrication Chamber Seals operating threads from water and debris which greatly reduces routine maintenance. Top Travel Stop Nut Helps prevent stem buckling and damage to bronze components which
JCM TAPPING SLEEVES MORE SELECTION, BENEFITS, OPTIONS
JCM TAPPING SLEEVES MORE SELECTION, BENEFITS, OPTIONS Specifying the right tapping sleeve for the condition of the job is the best way to assure a successful tap. JCM s are readily available in a wide
Wastewater Capital Projects Management Standard Construction Specification
CITY AND COUNTY OF DENVER ENGINEERING DIVISION Wastewater Capital Projects Management Standard Construction Specification 10.1 Precast Concrete Pipe 10.1.1 General This section covers material requirements,
SAN ANTONIO WATER SYSTEM SPECIFICATIONS FOR DRY-BARREL FIRE HYDRANTS ANSI/AWWA C502-05 Revised February 2013
21-30 SAN ANTONIO WATER SYSTEM SPECIFICATIONS FOR DRY-BARREL FIRE HYDRANTS ANSI/AWWA C502-05 Revised February 2013 1. SCOPE This product specification covers post-type, dry-barrel fire hydrants with compression
Model Specification 509 DRISCOPLEX 4200 and DRISCOPLEX 4300 Gravity Flow Sanitary Sewer
Model Specification 509 DRISCOPLEX 4200 and DRISCOPLEX 4300 Gravity Flow Sanitary Sewer The user may choose to adopt part or all of this Model Specification; however, the user should ensure that all parts
AIR RELEASE, CLEANOUT, AND SEWER MANHOLES
AIR RELEASE, CLEANOUT, AND SEWER MANHOLES **From Hartford IM BLDG(10) DESCRIPTION. This work shall consist of the construction of air release, cleanout, and sanitary sewer manholes; and the furnishing
City of Marshall Water Main Specifications
PART ONE - GENERAL 1.01 Description A. The CONTRACTOR shall furnish all labor, materials, and equipment required to construct water main, and all necessary appurtenant work as herein specified. The water
SECTION VALVE BOXES AND METER VAULTS
SECTION 03 48 20 VALVE BOXES AND METER VAULTS PART 1: GENERAL 1.01 SECTION INCLUDES A. Valve boxes for water and cleanout boxes for wastewater service. B. Meter boxes for water service. C. Meter vaults
12.1 MUELLER TAPPING MATERIALS AND SPECIALTY VALVES. MUELLER Tapping Valves. MUELLER Tapping Sleeves and Crosses
MUELLER TAPPING MATERIALS AND SPECIALTY VALVES 12.1 MUELLER Tapping Sleeves and Crosses Full range of Tapping Sleeves and Crosses to fit most types of pipe including cast iron, ductile iron, A-C, and cast
SECTION 51 PIPE INSTALLATION FOR WATER MAINS
SECTION 51 PIPE INSTALLATION FOR WATER MAINS 51. 1 GENERAL Pipe shall be installed in accordance with the manufacturer's specifications and instructions for the type of pipe used and applicable AWWA standards,
DIVISION 2 - SEWERAGE AND DRAINAGE SECTION 02720 - STORM DRAIN SYSTEMS PART 1 - GENERAL
DIVISION 2 - SEWERAGE AND DRAINAGE SECTION 02720 - STORM DRAIN SYSTEMS PART 1 - GENERAL 1.01 DESCRIPTION A. Furnish and install all storm drains, including manholes, inlets, service lines and other appurtenant
SECTION 33 41 13 PUBLIC STORM UTILITY DRAINAGE PIPING
SECTION 33 41 13 PUBLIC STORM PART 1 - GENERAL 1.01 SECTION INCLUDES A. Storm drainage piping, fittings, and accessories at proposed station areas and locations other than under and immediately adjacent
PWGSC Ontario STEAM AND CONDENSATE Section Region Project HEATING PIPING Page 1 Number R
Region Project HEATING PIPING Page 1 PART 1 - GENERAL 1.1 SECTION.1 Materials and installation of steel piping INCLUDES valves, fittings for steam and condensate building services piping. 1.2 RELATED.1
SANITARY SEWER SPECIFICATIONS
SANITARY SEWER SPECIFICATIONS OCTOBER 2003 HARVEST-MONROVIA WATER, SEWER, AND FIRE PROTECTION AUTHORITY SECTION 1.00 1.10 Purpose The purpose of this document is to assemble the sewer specifications, policies,
PVC Installation and Tapping For Potable Water and Sanitary Sewer. Handling and Installation Practices Manual
PVC Installation and Tapping For Potable Water and Sanitary Sewer Handling and Installation Practices Manual Table of Contents Introduction...1 Shipping and Handling...1 Handling and storage of pipe and
STANDARD SPECIFICATIONS SECTION 02512 CLEANING AND LINING WATER MAINS
STANDARD SPECIFICATIONS SECTION 02512 CLEANING AND LINING WATER MAINS PART 1 GENERAL 1.1 DESCRIPTION A. Section includes requirements for cleaning and lining existing cast iron and ductile iron water mains
Department of Utilities General Specifications
Department of Utilities General Specifications City of Lima Utility Field Services 1405 Reservoir Rd. Lima, Ohio 45804 Ph: (419) 221-5175 Revised 10/25/2010 UTILITY FIELD SERVICES GENERAL SPECIFICATIONS
Section 002345 FIRE HYDRANTS
CCU STANDARD SPECIFICATIONS Section 002345 FIRE HYDRANTS Effective Date: Nov. 1st, 2011 Page 1 of 7 PART 1 - GENERAL The following specification is intended for use for the design, selection of materials,
Anatomy of a Grooved Pipe Joint ANATOMY OF A GROOVED PIPE JOINT
The grooved piping system has been around for over 85 years, providing fast, easy, reliable piping assembly. While technology has changed application parameters cut grooving to roll grooving, standard
SECTION 11 WATER MAINS
SECTION 11 WATER MAINS 11.01 SCOPE: These general and detailed Specifications form a part of the Contract Documents and shall govern the handling and installation of water piping, valves, hydrants and
STANDARD SPECIFICATIONS SECTION MANUAL VALVES. This section includes materials, testing, and installation of manually operated valves.
STANDARD SPECIFICATIONS SECTION 15100 MANUAL VALVES PART 1 - GENERAL A. Description This section includes materials, testing, and installation of manually operated valves. Manual valves to be supplied
CITY OF NEWTON, KANSAS DESIGN STANDARDS FOR SANITARY SEWER IMPROVEMENTS
CITY OF NEWTON, KANSAS DESIGN STANDARDS FOR SANITARY SEWER IMPROVEMENTS APRIL 2005 THE CITY OF NEWTON, KANSAS STANDARD ENGINEERING DESIGN CRITERIA AND GENERAL IMPROVEMENT POLICY TABLE OF CONTENTS Page
DUCTILE IRON PIPE DESIGN
2 0 13 EDITION 3"-64" FOR FIRE ROTECTION, WATER & WASTEWATER 866.DI.IE 2 Table of Contents Ductile Iron ipe Laying Conditions Design Method and Examples of Selection Method ressure Class Thickness Class
September 2012 Brunswick County Engineering Department Revision 1.0. Technical Specification 020.01 GRAVITY SANITARY SEWER SYSTEM
1.0 General Technical Specification 020.01 GRAVITY SANITARY SEWER SYSTEM a) It is the intent of this specification to ensure that all gravity sewer system infrastructure constructed within the service
1.3.2 Method of construction and restoration of existing water service connections. This shall include:
1.0 GENERAL 1.1 DESCRIPTION: This specification shall cover the rehabilitation of existing water lines using the GRUNDOCRACK PIPE BURSTING SYSTEM. Pipe bursting is a system by which the pneumatic bursting
60.12. Depend-O-Lok FxE Expansion Coupling. System No. Submitted By Spec Sect Para Location Date Approved Date. DEPEND-O-LOK FxE EXPANSION COUPLING
60.1 D-O-L FxE expansion couplings are a bolted, split-sleeve design that provides for expansion and contraction at the coupled joint. These couplings are furnished with restraint rings that, when affixed
Section 02702 SEWER PIPE INSTALLATION AND TESTING
PART 1 - GENERAL Section 02702 SEWER PIPE INSTALLATION AND TESTING 1-1. SCOPE. This section covers the installation and testing of all sewer pipe furnished under the following specification sections: Concrete
A. Contractor shall furnish, to the Engineer, all materials certifications available from the manufacturer for all required materials.
PART 1 GENERAL 1.1 SCOPE A. This item shall include the work necessary for the installation of storm sewer line construction. B. Reference Section 3800 Trenching and Backfill and the General Conditions,
The work of this Section includes furnishing and installing Reinforced Concrete Pressure Pipe as shown on the Drawings and as specified.
Section 33 0200- Page 1 of 4 PART 1 - GENERAL 1.1 DESCRIPTION OF WORK The work of this Section includes furnishing and installing Reinforced Concrete Pressure Pipe as shown on the Drawings and as specified.
J-9 Pipe 1 2 Straight and Transition Ductile offer an easy and economical way of joining whether the is of the same nominal and/or type or different at each coupling. couplings will handle most of your
Specification for Pipe Bursting Gravity Sewer Mains with HDPE Pipe
Specification for Pipe Bursting Gravity Sewer Mains with HDPE Pipe 1. GENERAL The following supplemental sewer main specifications are intended to address the installation of high-density polyethylene
USACE / NAVFAC / AFCEC / NASA UFGS-33 30 00 (April 2008) Change 3-11/14 -------------------------- Preparing Activity: USACE Superseding UFGS-33 30 00 (July 2006) UNIFIED FACILITIES GUIDE SPECIFICATIONS
DESCRIPTION. Stud Bolts for Pressure-Temperature Piping 2-1. General Purpose End-to-End Studs 2-2. Tap End Stud Bolts 2-3. Double End Stud Bolts 2-4
DESCRIPTION PAGE B7 Studs and Nuts Stud Bolts for Pressure-Temperature Piping 2-1 General Purpose End-to-End Studs 2-2 Tap End Stud Bolts 2-3 Double End Stud Bolts 2-4 Sigma Fasteners, Inc. Section 2 STUD
MOBILE AREA WATER AND SEWER SYSTEM. Section 12. Sanitary Sewer Standard Specifications
MOBILE AREA WATER AND SEWER SYSTEM Section 12 Sanitary Sewer Standard Specifications May 31, 2012 TABLE OF CONTENTS 12.01 SCOPE:... 5 12.02 WORK INCLUDED:... 5 12.03 PIPELINE SYSTEM MATERIALS:... 5 A.
SECTION WATER MAINS AND ACCESSORIES. PART 1 - H.D.P.E. Pipe Specifications for Transmission of Potable Water
SECTION 331100 WATER MAINS AND ACCESSORIES Scope: This specification covers all aspects of requirements for new water mains, taps, and related accessories including submittals, products, and implementation.
CONSTRUCTION MATERIALS DIVISION 15 Construction Materials - Water Mains Section _Jan12_2016.pdf Page 1 of 18 INDEX
15001_Jan12_2016.pdf Page 1 of 18 INDEX Page 15001-1 WATER MAIN PRESSURE PIPE 3 1.1 Polyvinyl Chloride (PVC) Water Pipe (150mm 300mm) 3 1.2 Polyvinyl Chloride (PVC) Large Diameter Water Pipe (350mm - 1200mm)
SECTION LS 2530 SANITARY SEWERS. A. General: Submit the following in accordance with The General Conditions.
SECTION LS 2530 SANITARY SEWERS PART 1 GENERAL 1.1 SUBMITTALS A. General: Submit the following in accordance with The General Conditions. 1. Product data for drainage piping specialties. 2. Shop drawings
TECHNICAL SPECIFICATIONS GRAVITY AND PRESSURE SEWER LINE AND MATERIALS
TECHNICAL SPECIFICATIONS GRAVITY AND PRESSURE SEWER LINE AND MATERIALS Scope of Work Work performed under this contract shall consist of furnishing and installing, complete and ready for service, the sewer
Part VII - Water Mains and Service Laterals
ARTICLE 701 - GENERAL... 1 701.1 Definition.... 1 701.2 Description.... 1 701.3 Equipment.... 1 701.4 Tests.... 2 701.5 Finishing Work and Maintenance.... 2 701.6 Repairs and Replacement.... 2 701.7 Emergency
Ductile-Iron Pipe and Fittings AWWA MANUAL M41 Third Edition Manual of Water Supply Practices M41, Third Edition Ductile-Iron Pipe and Fittings Copyright 1996, 2003, 2009, American Water Works Association
EXHIBIT "A. Technical Specifications for Water and Sewer Service Lines
EXHIBIT "A Technical Specifications for Water and Sewer Service Lines Water and Sewer Line Bedding and Backfill: Drawings show cross-section of trench, pipe laid on top of 6" min. bedding material, bedding
SECTION 02601 WATER PIPE
SECTION 02601 PART 1 GENERAL 1.1 DESCRIPTION A. The WORK under this Section includes providing all labor, materials, tools and equipment necessary for furnishing and installing buried water pipe and fittings,
Section 3. AMERICAN Ductile Iron Pipe
Section 3 AMERICAN Ductile Iron Pipe AMERICAN Ductile Iron Pipe Centrifugally Cast in Metal Molds or Sand-Lined Molds For Water or Other Liquids. What is AMERICAN Ductile Iron? The ideal of cast iron with
Manufacturing, Supply & Quality Plan for Tower Bolts. SL Tower Bolt Market Penetration
Manufacturing, Supply & Quality Plan for Tower Bolts Project: SL Tower Bolt Market Penetration Document History Version Date Original Document First Submission Feb 9, 2013 Rev1 Requested Revisions Comments
Standard Specification K105 Water Reticulation
Standard Specification K105 Water Reticulation INDEX K105.1 SCOPE OF WORK 3 K105.2 STANDARDS 3 K105.3 MATERIALS 3 K105.3.1 Pipes and Fittings 3 K105.3.2 Storage and Handling 4 K105.3.3 Bedding and Haunching