Source: http://docplayer.net/1617138-Tls-300c-ust-monitoring-and-leak-detection-system.html
Timestamp: 2017-01-21 20:50:10
Document Index: 374386261

Matched Legal Cases: ['art 1', 'art 2', 'art 2', 'art 3', 'art 68', 'art 15', 'art 4', 'art 5', 'art 6', 'ART 1', 'ART 1', 'ART 1', 'ART 2', 'ART 1', 'ART 1', 'ART 1', 'art 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 2', 'ART 1', 'ART 1']

⭐TLS-300C UST Monitoring and Leak Detection System
Download "TLS-300C UST Monitoring and Leak Detection System"
1 TLS-300C UST Monitoring and Leak Detection System Part 1 - General System Requirements 1.1 Description A. These specifications are intended to provide information by which prospective bidders may understand the requirements relative to furnishing and installing a monitoring system for underground or aboveground liquid storage tanks and associated product piping. B. These specifications shall describe specifically a continuous underground monitoring and leak detection system that shall perform in accordance with Subpart D of 40 CFR 280 and, as a standard of performance and quality, shall meet the performance specifications and functions of the Veeder-Root Company TLS-300C UST Monitoring system. C. The underground storage tank monitoring system shall meet all applicable standards and regulatory agency requirements including, but not limited to, the standards and requirements of the following: 1. American National Standards Institute (ANSI) 2. American Petroleum Institute (API) 3. American Society for Testing and Materials (ASTM) 4. Environmental Protection Agency (EPA) 5. National Bureau of Standards (NBS) 6. National Electrical Code (NEC) 7. National Fire Protection Agency (NFPA) 8. Underwriters Laboratories Inc. (UL) 9. Canadian Underwriters Laboratories Inc. (cul) 10. Underground Storage Tanks: Subpart D, 40 CFR Part Federal Communications Commission (FCC) 12. British Approval Service for Electrical Equipment in Flammable Atmospheres (BASEEFA) 13. Factory Mutual (FM) Part 2 - Operational Specifications 2.1 In-Tank Leak Detection A. The system shall utilize in-tank probes based on the magnetostrictive principle for liquid level measurement and in-tank leak detection. B. The tank gauge shall be capable of performing a static tank tightness test to an accuracy of 0.1 GPH with at least a 98% probability of detection [P(D)] and no more than 1% probability of false alarm [P(FA)]. C. The system shall have the ability to be programmed to run a static 0.2 GPH quick leak test. The static leak test will take one hour and commence 30 minutes after the last dispensing cycle, or five hours from the last delivery. whichever is greater. 2.2 Interstitial Leak Detection for Double Wall Tanks Wet Monitoring A. The system shall be able to perform automatic, continuous leak sensing by monitoring the liquid level in the reservoir of a brine-filled interstitial space (annulus) of a double wall tank, to detect a breach in the inner or outer shell. B. The system shall differentiate between a high liquid level and a low liquid level in the brine reservoir of a double-wall tank and provide a high-liquid alarm or a low-liquid alarm Dry Monitoring TLS-300C UST Monitoring and Leak Detection System Rev. B2 A. The system shall be able to perform automatic, continuous leak sensing in the dry interstitial space (annulus) of a double wall tank, to detect a breach in the inner or outer shell. B. The system shall have the ability to sense the presence of hydrocarbons and/or liquid, and provide an alarm for the worst case condition (fuel). C. The form factor of the sensor must provide for easy field installation and removal. D. The system shall have the ability to continuously monitor the integrity of the sensor for an open condition, alarm condition, or normal operating condition. 2.3 Containment Sump Monitoring A. The system shall be able to perform automatic, continuous leak sensing in the piping containment sump. B. The system shall have the ability to detect the presence of liquid (hydrocarbons and/or water) in the piping containment area and provide an alarm condition. C. The system shall have the ability to indicate when the sensing device has failed and is no longer providing environmental compliance. D. The system shall have the ability to continuously monitor the integrity of the sensor for an open condition, alarm condition, or normal operating condition. 2.4 Environmental Compliance Reports A. The system shall have the ability to provide a record of the last three occurrences of each type of alarm or warning condition detected by the system. B. The system shall provide the following types of reports related to environmental compliance matters: 1. System status messages 2. Liquid sensor warning and alarm messages 3. Normally-closed sensor warning and alarm conditions 4. Hydrostatic sensor warning and alarm conditions; high or low liquid level conditions 5. In-tank warning and alarm messages (optional) 6. In-tank tightness evaluation (optional) 7. External input messages 8. Software module alarm message 2.5 Product Inventory Control (Tank Gauging) A. The tank management system shall collect product height and temperature data from up to two magnetostrictive level probes and compute gross and temperature-compensated net gallons. The operator may choose from inventory or delivery information to generate a complete set of printed inventory or delivery reports. B. The system shall automatically generate an inventory increase report when a delivery of product to a tank has taken place. The report shall include the time and date of the delivery, the starting volume in the tank, the ending volume in the tank, the starting temperature of the fuel, the ending temperature of the fuel, and the inventory increase amount. C. The system shall have the ability to store up to ten of the most recent inventory increases in memory for business management purposes. D. The system shall provide the ability to monitor aboveground storage tanks, as well as underground storage tanks, for inventory management. 2.6 Inventory Management Reports TLS-300C UST Monitoring and Leak Detection System Rev. B3 A. The system shall monitor inventory in U.S. or Metric units for up to two tanks and produce a combination of automatic and manual reports for each tank, which include the following information: 1. Fuel volume 2. Fuel height 3. Water height 4. Fuel temperature 5. Ullage 6. Temperature-compensated fuel volume 7. Last inventory increase amount 8. Last in-tank leak test result 9. Time and date 10. Tank identification 11. Fuel type identification % ullage B. A printout of the inventory status report shall be generated any time the operator presses the print button while the system is in the normal operating mode, or generated automatically four times a day, with the information stored in memory. C. The system shall provide an automatic delivery report, programmed to print from 1 to 99 minutes after a bulk delivery to a tank is complete. The information shall include station header, product label, date, starting and ending time, starting and ending volumes, and temperature of the fuel, as well as the net volume increase. The information shall be available in U.S. or Metric units. D. The system shall be able to generate reports in a display/printer format as well as a computer format upon demand. 2.7 Communications A. The tank monitoring system shall provide the ability to communicate with locally attached electronic devices through an RS-232 port, or remote locations via an RS-232 port. The system shall provide data in a display or packed computer data format. B. The communications protocol shall be Veeder-Root standard serial communications protocol or compatible. C. The tank monitoring system shall provide all reports available on the integral printer through the communications port. These shall include all reports associated with inventory management, environmental compliance, and diagnostics/troubleshooting. D. The system shall provide for setup and configuration through the communications port using the Veeder-Root standard serial communications protocol or compatible Serial Communications A. The system shall provide an RS-232 communications interface for data transmission to a computer, point of sale terminal, printing device, or modem for remote communications. B. The system shall provide an auxiliary RS-232 communications interface for connection to a second tank monitoring system Wide Area Network Software (Remote Monitoring) A. The manufacturer shall provide a communications/database software package to poll remote tank monitoring sites from a central location. B. The communications/database software shall provide the ability to communicate directly with the tank monitoring system, via a 25-pin RS-232 serial interface, or remotely via a dial-up connection over the public telephone network. TLS-300C UST Monitoring and Leak Detection System Rev. B4 C. The software package shall provide the ability to remotely configure a system. D. The software shall provide a communications mode, in which it can automatically and continuously poll locations that have been designated for data retrieval, and store the data in a standard database format. E. The stored data shall be easily transferable to other software packages, such as spreadsheets, database packages, etc., for data manipulation. F. The software shall provide an immediate on-line mode to retrieve specific information from a tank monitoring system and to download setup and configuration information. G. The software shall be able to generate inventory and environmental compliance management reports on demand, for all of the data stored, or specific ranges of data. H. The software system shall provide the user the ability to retrieve all diagnostic data from the tank monitoring system. It shall also provide the ability to backup and recover data that has been stored. I. The software package shall permit the user to connect on-line with a location and enter serial communication protocol commands for information retrieval Reports A. The system shall be able to generate reports in a display/printer format as well as a computer format through the communication interface using the Veeder-Root serial communications protocol. All reports including inventory, delivery, environmental compliance (leak detect), alarm history, and status may be retrieved through remote or local communications. 2.8 Input/Output Capabilities Output Relay A. The system shall provide the ability to enable external audible/visual alarms, or control external devices through a relay contact closure. B. The system shall provide 2 Form C contact relays. C. The system shall provide the ability to program the relay in either a Normally Open or Normally Closed orientation. D. The system shall provide the ability to assign sensor or system alarm conditions to a selected relay. E. The system shall provide the ability to assign a 20 character label to a device connected to the output relay through system programming Input Interface A. The system shall provide the ability to accept an input from an external device and enable a relay to control an external device. B. The system shall have the ability to define the type of input connected to the system. C. The system shall have the ability to name, through system programming, each external device connected to an input position. 2.9 Alarms A. The tank monitoring system shall provide an audible and visual indication of all system in-tank leak, product line leak, and external sensor alarm conditions. TLS-300C UST Monitoring and Leak Detection System Rev. B5 B. The system alarm conditions shall include: 1. Maximum Product level 2. High level limit 3. Overfill alarm 4. High water alarm 5. Second high water alarm 6. Delivery needed alarm 7. Low limit 8. Sudden Loss C. The tank monitoring system shall provide an audible and visual alarm indication for external sensor leak failures (fuel, water, and sensor out). D. In conjunction with providing an audible and visual alarm, the system shall have the ability to print out all alarm conditions to the integral thermal printer. E. The system shall have the ability to send all alarm conditions to the RS-232 serial communications port for data transmission to a central computer. The system shall have the ability to transmit the alarm condition immediately, or program a delay time before sending. The system shall also have the ability to enter a repeat function in the programming to repeat sending the alarm condition. F. The system shall provide the operator with the ability to disable the audible portion of an alarm, but the visual alarm shall not be disabled until the alarm condition has been corrected. G. The system shall be equipped with an external audible and visual alarm with acknowledgement switch. The external alarm box and acknowledgement switch shall be contained in a watertight gasketed enclosure for installation in an outdoor environment. The external alarm box and acknowledgement switch shall interface to the tank monitoring system via an internal relay. H. The system shall have the ability to store up to three alarm occurrences in memory. The operator shall have the ability to print the alarm history and alarm status on the integral printer, as well as retrieve alarm history and alarm status through the communications interface (RS-232) Setup (Startup/Installation) A. The system shall contain parameter-driven software to adapt the tank monitor to site specifications. The parameters must be enterable in assigned fields at the time of system startup. In addition, the parameters must be field updatable so that changes in tank dimensions and site specifications can be made. B. The system shall provide the use of a security code to prohibit unauthorized entry to the system's set-up parameters. The system security code shall be a six-digit number entered through the front-panel keyboard or through the external communications interface. The security code shall have the capability of containing alpha or numeric characters. C. A four-line, 24-character custom location header to identify the site must be user-programmable. The header must appear automatically on inventory status reports, leak detection reports, and automatic delivery reports each time they are printed. D. Set-up parameters shall include the following: 1. System setup data 2. Communications setup data 3. In-tank setup data 4. Liquid sensor setup data 5. External sensor setup data 6. Output relay setup data 2.11 Diagnostics/Troubleshooting TLS-300C UST Monitoring and Leak Detection System Rev. B6 A. All diagnostic information shall be generated by the system itself. The system shall not allow the user to change or enter diagnostic information in any way. The following diagnostic information shall be included in the system: 2.12 Reports 1. Probe diagnostics a. Probe type b. Serial number c. Probe length d. Calibration values 2. System diagnostics a. Software revision level b. Software part number c. Software creation date 3. In-tank diagnostics 4. In-tank leak results (optional) 5. Liquid sensor diagnostics 6. Alarm history report A. All diagnostic information, listed in Part 2, section 2.11, paragraph A, subsections 1 through 6, shall be capable of being printed by the system's integral printer for hard-copy documentation and historical record keeping. Part 3 - Product Specifications/Capacities 3.1 Console A. The console shall be wall mounted using external mounting tabs. B. The console shall be equipped with a 2-line, 24-character liquid crystal display for on-site viewing of all inventory, leak detection, and alarm information. C. The console shall be equipped with a 24-key front-panel keypad with control and alphanumeric capability for programming, operating, and reporting functions. D. The console shall be equipped with three front-panel indicators to provide a visual indication of power on, warning, and alarm conditions. E. The console shall be equipped with an integral, 24-character, thermal report printer with built-in take-up spool for hard-copy documentation of inventory, leak detect, and alarm information. F. The console shall be equipped with a back-up battery to maintain all programming information, as well as inventory, leak detect, and alarm information in the event of a power outage. G. The console shall provide 2 form C contact relays to provide the ability to enable an external audible/visual alarm or control external devices. H. The console shall have a fixed feature set design to address business management, leak detection, and communications requirements. I. The console shall be equipped with three 1-3/4" conduit knockouts on the top and the bottom of the monitor for rigid conduit entry into the monitor. One conduit entry shall be designated for the intrinsically safe compartment, and two conduit entries (top and bottom) shall be designated for the high-power compartment. J. The console shall be separated into two compartments for: 1) intrinsically safe wiring and devices; 2) high-power wiring and devices. K. The console shall have an internal quick-disconnect connector for 120 VAC wiring to the console for ease of installation, TLS-300C UST Monitoring and Leak Detection System Rev. B7 service, and troubleshooting. L. The console shall be equipped with the ability to communicate directly with an external POS terminal, printing device, or PC. The system shall also have the ability to communicate with a remote device via the telephone lines. M. The console shall be capable of selectively communicating in English, French, German, Polish, Portuguese, Spanish, and Swedish. N. The console shall he equipped with internal audible and visual warning and alarm indicators. O. The console shall provide an intrinsically safe electrical barrier, for connection to devices mounted in hazardous areas, with Underwriters Laboratories (UL) and Canadian Underwriters Laboratories (cul) approval. P. The console shall comply with the FCC's RF emissions and susceptibility restrictions and be tested to be in compliance with FCC Part 68, Subpart 15. Q. The console shall be mounted and wired according to the manufacturer supplied installation manuals, with all underground intrinsically safe field wiring enclosed in dedicated conduit and separate from all other wiring. The system's high-voltage wiring may share existing conduit with other high-voltage devices in accordance with the applicable guidelines published in the National Electrical Code (NEC). R. The console shall continuously monitor all probes and sensors, reporting not only normal operating conditions, but also system malfunctions or failures. 3.2 Probes A. The probe shall be capable of utilizing standard non-shielded gas- and oil-resistant wire between 14 AWG and 18 AWG for field connections. B. There shall be no more than two conductors between each probe and the control console. C. The probe shall be capable of performing a leak detect test to 0.1 GPM or higher. D. Third-Party Certification is required in accordance with the U.S. EPA's "Standard Test Procedure for Evaluating Leak Detection Methods: Automatic Tank Gauging Systems" (0.2 GPH monthly monitoring). E. Third-Party Certification is required in accordance with the U.S. EPA's "Standard Test Procedure for Evaluating Leak Detection Methods: Volumetric Tank Tightness Testing Method" (0.1 GPH annual tank tightness test). F. The probe shall be compatible for aboveground tank installations as well as underground tank installations. G. A cap and ring kit, available from the manufacturer, shall be supplied with each probe for easy installation and removal. H. The probe shall use a digital communications protocol format for maximum RF/EMF immunity. 3.3 Sensors A. The system shall provide the ability to monitor up to 8 interstitial areas and/or containment areas, utilizing a standard float style sensor Piping Sump Sensor A. The piping sump sensor shall be of PVC construction, utilizing a float and reed switch technology to sense the presence of liquid. The sensor shall also be supplied with a mounting bracket for installation of the sensor in a containment area. B. The piping sump sensor shall be 12" long to address monitoring in piping containment sumps, as well as dispenser pan/sump areas. TLS-300C UST Monitoring and Leak Detection System Rev. B8 C. The sump sensor shall be designed with a five-foot leader cable to connect the sensor to field wiring in the sensor junction box. The sensor shall be supplied with watertight cord grip assemblies to install in the sensor junction box. 1. Power Requirements: Intrinsically safe power supplied by tank monitor. 2. Sensor Type: Hermetically sealed magnetic reed switch. 3. Contact Rating: 15 watts. 4. Switch Travel: 7/8 inch to contact. 5. Operating temperature: Hydrocarbons: -25 C to +60 C. Freezing Liquids: 0 C to +60 C Hydrostatic Sensor A. The hydrostatic sensor shall be supplied by the manufacturer in a single-float or a dual-float configuration. B. The dual-float hydrostatic sensor shall be 19" long with a clear Lexan tubular housing for visible confirmation of sensor operation. The sensor shall be 2.5" in diameter to install in the riser pipe assembly of a double-wall tank brine reservoir. C. The single-float hydrostatic sensor shall be 6.0" long with a clear Lexan tubular housing for visible confirmation of sensor operation. The sensor shall be 2.5" in diameter to install in the riser pipe assembly of a double-wall tank brine reservoir. D. The single- and dual-float hydrostatic sensor shall be supplied with a 12-foot leader cable to connect the sensor to field wiring in the sensor junction box. E. The single- and dual-float hydrostatic sensor shall be supplied with a lockable, watertight riser cap to prevent accidental spills into the tank reservoir. The cap shall be equipped with a vent tube to vent air out of the reservoir area and prevent liquids from entering into the reservoir. F. The single-float hydrostatic sensor shall indicate only a low-liquid level in the tank reservoir. G. The single-float hydrostatic sensor shall utilize a float and reed switch assembly for sensing the presence and change in liquid level. The contact shall be a Normally Closed dry contact. H. The dual-float hydrostatic sensor shall indicate a high liquid level and a low liquid level in the tank reservoir. I. The dual-float hydrostatic sensor shall utilize a dual float and reed switch assembly for sensing the presence and change in liquid level. The contact shall be a Normally Closed dry contact. 1. Operating temperature: -25 C to +70 C. 2. Installed in a brine solution of up to 30% calcium chloride. 3. Clear plastic housing for visual inspection. 4. Cable length: 12 Feet. 5. Available in both a single-float and a dual-float configuration Interstitial Sensor for Double-Wall Steel tank A. The interstitial sensor for a double-wall steel tank shall be 2.5" high and 1.5" in diameter to fit into a riser pipe for a double-wall steel tank of 1.5" I.D. or greater. B. The steel tank interstitial sensor shall be equipped with a 25-foot leader cable to connect the sensor to field wiring in the sensor junction box. C. The sensor shall utilize a float and reed switch technology to sense and alarm for the presence of liquid. 1. Operating temperature: Hydrocarbons: -25 C to +70 C. Freezing Liquids: 0 C to +70 C. 2. Cable length: 25 Feet. 3. Dimensions: 2.5" high, 1.50" dia. 4. Can be used in the annulus of steel tanks with a sensor riser pipe of 1.5" I.D. or greater. TLS-300C UST Monitoring and Leak Detection System Rev. B9 5. Two-wire connection to the monitor Interstitial Sensor for Double-Wall Fiberglass tank A. The interstitial sensor for a double-wall fiberglass tank shall be 2.13" long, 1.27" wide, and 0.58" high. The sensor shall be designed to fit in the interstitial area of any size double-wall fiberglass tank from 4' in diameter to 12' in diameter. B. The sensor shall utilize a float and reed switch technology to sense and alarm for the presence of liquid. C. The sensor shall be designed with a pull cord hole where a pull cord may be attached to install the sensor in the interstitial area of the tank. D. The sensor shall be designed with a protective braid covering the switch assembly and cable to provide mechanical protection. 1. Operating temperature: Hydrocabons: -25 C to +70 C. Freezing Liquids: 0 C to +70 C. 2. Can be used in the annulus of fiberglass tanks with a sensor riser pipe of 4". 3. Two-wire connection to the monitor. 3.4 Communications RS-232 Serial Communications Interface A. The system shall have the capability of communicating directly with a computer, teletype, or printer. B. The system shall provide direct interface via a 25-pin D connector using standard RS-232 serial communications hand-shaking signals Auxiliary RS-232 Serial Communications Interface A. The system shall provide an auxiliary 25-pin D connector for multiple console communications connections. B. The system shall have the capacity for two 25-pin D connectors to interface a second tank monitor, as well as connect directly to a PC, teletype, or remote communications device. Part 4 - Manufacturer's Support/Field Service 4.1 Technical Support A. The manufacturer shall provide technical phone support available to customers from 8:00 AM to 7:00 PM EST B. The manufacturer shall provide technical phone support available to authorized distributors and service contractors for on-site troubleshooting of UST system problems. Phone support shall be available from 8:00 AM to 7:00 PM EST. 4.2 Field Service A. The manufacturer shall maintain a nation-wide field service staff to provide on-site customer support and training, as well as over seeing installation of tank monitoring system by installation contractor. B. The distributor/contractor field service representative shall be available for on-site training of company maintenance personnel on installation, programming and troubleshooting of tank monitoring system. C. The manufacturer shall have a territorial field service staff to support the distributor/contractor field service network. 4.3 Certification Training A. The manufacturer shall require and provide mandatory certification training for all of its authorized distributors and TLS-300C UST Monitoring and Leak Detection System Rev. B10 service contractors/installers. B. The certification program shall consist of three certification levels covering installation, setup/operation, and service/troubleshooting of the manufacturer's UST monitoring systems. C. The manufacturer shall provide certification information on contractor/installer to regulatory agencies that require certification documentation. D. The manufacturer shall offer recertification training to keep contractors/installers current with updated information. E. The manufacturer shall conduct regional training seminars throughout North America. F. The manufacturer shall provide a home study certification program for installing contractors. 4.4 Warranty Registration and Checkout Form (WRACO) A. The manufacturer shall require that all UST/AST monitoring systems be started up by an authorized distributor. B. The startup shall consist of installation checkout, operation checkout, and customer training on use of the equipment. C. The manufacturer shall supply a Warranty Registration and Checkout Form to properly document the site information to include: 1. Installation location 2. Installer 3. Equipment identification 4. Tank information 5. Leak detector information 6. Start up distributor information 7. Customer approval D. The manufacturer shall compensate the authorized distributor for the start up procedure when a properly completed Warranty Registration and Checkout Form is submitted to the manufacturer. E. Upon receipt of the Warranty Registration and Checkout Form, the manufacturer will initiate the system warranty and input the data into a site database. 4.5 Replacement and Service Parts A. The manufacturer shall offer Authorized Distributors preselected parts kits to service UST monitoring systems. 8. The manufacturer shall offer a preselected Parts kits designed for service truck and shop. C. The manufacturer shall offer a quick ship service for parts that shall ensure that a parts shipment is sent within 24 hours of request/order. 4.6 Delivery A. The manufacturer shall have the ability to ship tank monitoring systems in three (3) working days from the time that an order is entered into the computerized system to the ship date. 4.7 ISO-9001 A. The manufacturer shall maintain an ISO-9001 rating, ensuring quality management of design, manufacturing, training and technical documentation. Part 5 - Documentation TLS-300C UST Monitoring and Leak Detection System Rev. B11 5.1 Manuals A. The manufacturer shall supply product documentation that addresses the following categories as additional support: 1. Site preparation and installation instructions. 2. System setup instructions. 3. System operating instructions. 4. Individual sensor installation instructions. 5. Probe installation instructions. 6. Individual module installation instructions. 7. Product data sheets. 8. Troubleshooting and repair manuals. 9. Wiring diagrams which include the following: a. Identification of all devices and equipment terminals, and all external connection terminal blocks. b. All external wiring connections with approved wire colors and circuit designations. 10. Serial communications manuals. 5.2 Third-Party Certification A. The manufacturer shall supply third-party documentation for all products, certifying that performance meets or exceeds EPA requirements. 5.3 Authorized Service Personnel Listing A. The manufacturer shall supply a formal list of all Authorized Distributors and Service Contractors for sales, installation, training, and support. Part 6 - Warranty 6.1 System Warranty A. The tank monitoring system shall be warranted for a period of one year from date of installation or 15 months from date of invoice. B. The warranty is to include parts and labor, with all warranty work performed on site by an authorized manufacturer's representative. TLS-300C UST Monitoring and Leak Detection System Rev. B Similar documents
Note To Consultants and Designers: Use this document as a guide when writing specifications for Storage Tank Liquid Level Management Systems requiring 0.1 GPH or 0.2 GPH In-Tank leak detection, and/or More information OPW EDGE Double-Wall Spill Containers
www.opwglobal.com OPW EDGE Double-Wall Spill Containers Designed in collaboration with contractors and end-users, the OPW EDGE Double- Wall Spill Container installs in the same space as single-wall buckets. More information TLS-350R Monitoring Systems. Business Inventory Management.
TLS-350R Monitoring Systems Add value to automated tank gauging with the advanced capabilities of Business Inventory Management. Fuel Dispensing and Control Site and Retail Management Support Services More information AUTOMATIC TANK GAUGING SYSTEMS Achieving Compliance. John D. Sieger, Tanknology
AUTOMATIC TANK GAUGING SYSTEMS Achieving Compliance John D. Sieger, Tanknology The Objective: Monitor the Tanks & Piping Systems for leaks TANK GAUGING SYSTEM BRANDS DOUBLE WALL STEEL TANK MONITORING DOUBLE More information UST RULES CHANGES. Heather Peters, Environmental Specialist
UST RULES CHANGES Heather Peters, Environmental Specialist Today s Topic 2011 Rule package- what s left? Upcoming rule changes Federal Regulation Changes & Testing Protocols How are you doing? 2011 Rule More information LTR Series Uninterruptible Power Systems 700 VA - 2.1 KVA. General Specification
08/17/12 Rev2 LTR Series General Specification 700 VA to 2.1 KVA 1.0 General LTR Series Uninterruptible Power Systems 700 VA - 2.1 KVA General Specification This specification describes the features and More information Northern Region. Underground Storage Tank
California CUPA Northern Region Presents Underground Storage Tank Designated Operators Workshop Workshop Agenda Definitions Tank Construction Corrosion Protection Spill Prevention Overfill Prevention Piping More information Compliance and Fuel Management Service. Service Catalog
TM Compliance and Fuel Management Service Service Catalog We Have Received Orders To Comply With The EPA. Over. R o g e r. W i l c o. Introduction By taking on the job of monitoring tanks rather than just More information Alabama Air and Waste Regulatory Update
Alabama Air and Waste Regulatory Update September 24, 2015 RSA Activity Center Montgomery, AL New Federal UST Regulations (Effective Date October 13, 2015) What Does This Mean To Me? The Current ADEM Regulations More information SECTION 13850 DETECTION AND ALARM
SECTION 13850 DETECTION AND ALARM PART 1 GENERAL 1.01 SUMMARY A. Section Includes 1. Control Panel 2 Associated Equipment B. Products Installed But Not Supplied Under This Section 1. Section 16140 - Wiring More information Line Leak Detection Systems, UST Leak Detection Equipment, Mag Sump Sensor, and Other Sensors
Manual No: 577013-814 Revision: E Line Leak Detection Systems, UST Leak Detection Equipment, Mag Sump Sensor, and Other Sensors Operability Testing Guide Notice Veeder-Root makes no warranty of any kind More information Application for the Construction or Installation of Aboveground Storage Tank (AST) Systems or Associated Underground or Over-water Piping Systems
Page 1 of 5 Application for the Construction or Installation of Aboveground Storage Tank (AST) Systems or Associated Underground or Over-water Piping Systems New Hampshire Department of Environmental Services More information Recommended Product Specifications Fuel Day Tank System Tramont UTRS Fuel Day Tank
Recommended Product Specifications Fuel Day Tank System Tramont UTRS Fuel Day Tank This specification describes requirements for a Diesel Fuel Day Tank System consisting of one or more fuel tanks, an Electronic More information NC State University Design and Construction Guidelines Division 26 Fire Alarm Systems
NC State University Design and Construction Guidelines Division 26 Fire Alarm Systems 1.0 Purpose A. The following guideline provides the minimum standards and requirements for fire alarm systems. 2.0 More information Straight Talk On Tanks Leak Detection Methods For Petroleum Underground Storage Tanks And Piping
Straight Talk On Tanks Leak Detection Methods For Petroleum Underground Storage Tanks And Piping Printed on Recycled Paper Contents Do You Have Questions About Leak Detection?...1 An Overview Of Leak Detection More information Nortrax 23 52 23 190 David Manchester Road, Ottawa FAN ASSISTED COPPER TUBE BOILERS 21 May 2014 Project: 13-104-070 PART 1 - GENERAL...
21 May 2014 PART 1 - GENERAL... 1 1.1. WORK INCLUDED... 1 1.2. QUALITY ASSURANCE... 1 1.3. APPROVALS... 1 PART 2 - PRODUCTS... 1 2.1. HEATING BOILERS... 1 2.2. BOILER SEQUENCE CONTROL... Error! Bookmark More information Manual No: 576013-939 Rev.: F. Operator's Quick Help. TLS-3XX Series Consoles
Manual No: 576013-939 Rev.: F Operator's Quick Help TLS-3XX Series Consoles Notice Veeder-Root makes no warranty of any kind with regard to this publication, including, but not limited to, the implied More information NDEP Bureau of Corrective Actions Secondary Containment Regulations Guidance Document April 7, 2010 (Revision)
NDEP Bureau of Corrective Actions Secondary Containment Regulations Guidance Document April 7, 2010 (Revision) ADOPTED REGULATION OF THE STATE ENVIRONMENTAL COMMISSION LCB File No. R005-08 (Codified in More information Shop-Fabricated Secondary Containment Steel Storage Tanks
Shop-Fabricated Secondary Containment Steel Storage Tanks Technology corner Posted / Last update: 01-01-2004 Publication: Petroleum Equipment & Technology Archive Issued: January 2004 Author: Geyer Wayne More information SAMPLE REPORTS. Contents
Contents Types of Reports... 3 Sample Reports:... 4 Typical Information Shown On Reports... 4 Product Inventory Detail Reports... 5 Tank Inventory Summary Report... 5 Product Inventory Summary Report... More information ETC TWO STAGE ELECTRONIC TEMPERATURE CONTROL
RANCO INSTALLATION INSTRUCTIONS ETC TWO STAGE ELECTRONIC TEMPERATURE CONTROL Relay Electrical Ratings PRODUCT DESCRIPTION The Ranco ETC is a microprocessor-based family of electronic temperature controls, More information FIRE ALARM AND DETECTION SYSTEMS SECTION 16721
PART 1 - GENERAL 1.01 WORK INCLUDED FIRE ALARM AND DETECTION SYSTEMS SECTION 16721 A. Provide a complete fully addressable, power limited, fire detection and evacuation system. The system shall be connected More information DIVISION 28 ELECTRONIC SAFETY AND SECURITY SECTION 28 13 00 SECURITY AND ACCESS CONTROL SYSTEM
DIVISION 28 ELECTRONIC SAFETY AND SECURITY PART 1 GENERAL 1.01 DESCRIPTION A. Division 28 Contractor shall extend a complete Matrix Systems Access Control System as shown on the Drawings and as specified More information Advantium 2 Plus Alarm
ADI 9510-B Advantium 2 Plus Alarm INSTALLATION AND OPERATING INSTRUCTIONS Carefully Read These Instructions Before Operating Carefully Read These Controls Corporation of America 1501 Harpers Road Virginia More information CalMod Design-Build Electrification Services
SECTION 28 16 00 INTRUSION DETECTION SYSTEM PART 1 - GENERAL 1.1 DESCRIPTION A. This section describes the detailed technical requirements for the Intrusion Detection System (IDS), where the Contractor More information DORMA MODEL PS-406BB POWER SUPPLY INSTALLATION INSTRUCTIONS
Features: INSTALLATION Install in accordance with NFPA 70. DORMA MODEL PS-406BB POWER SUPPLY INSTALLATION INSTRUCTIONS Up to 1.95 Amps Load Capacity Class 2 Rated Outputs Overload, Over Voltage, and Short More information Maryland Containment System Testing Protocol. The individual performing the inspection and testing as outlined in this protocol must be either:
MARYLAND DEPARTMENT OF THE ENVIRONMENT Oil Control Program, Suite 620, 1800 Washington Blvd., Baltimore MD 21230-1719 4 410-537-3442 410-537-3092 (fax) 1-800-633-6101 http://www.mde.state.md.us Maryland More information Morrison Bros. Co. General Product Specifications
Morrison Bros. Co. General Product Specifications Tank Mounted Spillbox The spill containment device is manufactured to contain spills and drips that may occur at the fill point on aboveground storage More information O C M III. Open Channel Flow Monitor
O C M III Open Channel Flow Monitor Part 1. General 1.1 Scope A. This section describes the requirements for an ultrasonic flow transmitter with sensor and temperature compensation probe. B. Under this More information HONEYWELL COMMERCIAL FIRE/BURG PANEL UL LISTING REQUIREMENTS (Compiled from VistaFBPT Installation Instructions 800-09617V1 Rev A 11/12)
HONEYWELL COMMERCIAL FIRE/BURG PANEL UL LISTING REQUIREMENTS (Compiled from VistaFBPT Installation Instructions 800-09617V1 Rev A 11/12) UL864 (Commercial Fire) Compliance General Requirements The VISTA-128FBPT/VISTA250FBPT More information SECTION 16721 FIRE ALARM AND SMOKE DETECTION SYSTEMS
SECTION 16721 PART 1 - GENERAL 1.1 SECTION INCLUDES A. Fire Alarm Control Panels B. Manual Fire Alarm Stations C. Automatic Smoke D. Fire Alarm Notification Appliances E. Auxiliary Fire Alarm Equipment More information ENGINEERING SPECIFICATIONS FOR CO2 EXTINGUISHING AGENT PRE-ENGINEERED FIRE SUPPRESSION SYSTEMS
ENGINEERING SPECIFICATIONS FOR CO2 EXTINGUISHING AGENT PRE-ENGINEERED FIRE SUPPRESSION SYSTEMS SECTION 1 GENERAL SPECIFICATIONS I. SCOPE This specification outlines the requirements for a pre-engineered More information UFGS-28 33 00.00 40 (February 2011) UNIFIED FACILITIES GUIDE SPECIFICATIONS
USACE / NAVFAC / AFCEC / NASA UFGS-28 33 00.00 40 (February 2014) ----------------------------------- Preparing Activity: NASA Superseding UFGS-28 33 00.00 40 (February 2011) UNIFIED FACILITIES GUIDE SPECIFICATIONS More information Underground Storage Tank Operational Compliance Field Guide
Underground Storage Tank Operational Compliance Field Guide Created April 2012, Reaffirmed April 2015 Bureau of Underground Storage Tank Regulations http://www.com.state.oh.us/fire/default.aspx Department More information Introduction. Safety Guidelines. Part Numbers. Operation and Maintenance Manual. Operation and Maintenance Manual
Operation and Maintenance Manual Introduction Read all instructions thoroughly. Installation of the OilTector must comply with all Federal, State and Local Codes, Regulations and Practices. The OilTector More information Manual for Fire Suppression & Methane Detection System
Manual for Fire Suppression & Methane Detection System Fogmaker North America Post address: 150 Gordon Dr Exton, PA 19341 Delivery address: 150 Gordon Dr Exton, PA 19341 Tel: 610-265-3610 Fax: 610-265-8327 More information Utility Distribution Systems
Utility Distribution Systems 6/2012 A0011037 1 WARRANTY This equipment is warranted to be free from defects in materials and workmanship, under normal use and service, for a period of 12 months from date More information Security Systems Intrusion Alarm
Dufferin-Peel Catholic District School Board STANDARD TEXT GUIDELINE FOR Security Systems for SECONDARY AND ELEMENTARY SCHOOLS Prepared by the Plant Department With Assistance from Vision Dynamics Formatted More information Technical Requirements for Aboveground Storage Tanks (ASTs) Storing Class IIIB Liquids (other than used oil)
Technical Requirements for Aboveground Storage Tanks (ASTs) Storing Class IIIB Liquids (other than used oil) References: Comm 10 2009 EDITION / NFPA 30 2008 EDITION ITEM DESCRIPTION Comm 10 / NFPA General More information FVSU-33201301 REPAIR & UPGRADE FIBER OPTIC 280000-1 SECTION 280000 FIRE ALARM SYSTEM CONNECTIVITY
FVSU-33201301 REPAIR & UPGRADE FIBER OPTIC 280000-1 SECTION 280000 FIRE ALARM SYSTEM CONNECTIVITY PART 1 - GENERAL 1.1 SUMMARY A. Section Includes: 1. Fire-alarm control unit. 2. Addressable interface More information DRAFT REVISED 2015. Musts For USTs DRAFT. Printed on Recycled Paper. Updated June 2015
DRAFT REVISED 2015 Musts For USTs DRAFT Printed on Recycled Paper EPA wrote this booklet for owners and operators of underground storage tanks (USTs). This booklet describes the 2015 revised federal UST More information SECTION 13850 (28 31 00) FIRE DETECTION AND ALARM SYSTEM
SECTION 13850 (28 31 00) FIRE DETECTION AND ALARM SYSTEM ENGINEERING SPECIFICATION INTELLIGENT REPORTING FIRE DETECTION SYSTEM PART 1 GENERAL 1.1 DESCRIPTION A. This specification includes the furnishing, More information SECTION 16721 FIRE ALARM AND DETECTION SYSTEM
1. GENERAL 1.1. Related Documents: 1.2. Scope: 1.1.1. The general provisions of the Contract, including General and Supplementary Conditions and General Requirements apply to the work specified in this More information SP4-LOC SAFEPATH4 REMOTE MICROPHONE AND LOCAL OPERATOR CONSOLE
SP4LOC SAFEPATH4 REMOTE MICROPHONE AND LOCAL OPERATOR CONSOLE INSTALLATION AND OPERATION MANUAL MASS NOTIFICATION SYSTEM Part Number: P84767 Rev. A Copyright 2006 Cooper Wheelock, Inc. All rights reserved. More information ENGINEERED DRAWINGS FOR PETROLEUM STORAGE TANKS
Facility Name: ENGINEERED DRAWINGS FOR PETROLEUM STORAGE TANKS The following is intended to be used as a guideline for information required to appear on engineered drawings involving petroleum storage More information MOBILE FIRE - RESCUE DEPARTMENT FIRE CODE ADMINISTRATION
MOBILE FIRE - RESCUE DEPARTMENT FIRE CODE ADMINISTRATION Fire Pump Plan Review 2009 International Fire Code and NFPA 20 Date of Review / / BLD201 - Project Address: Project Name: Contractor s Business More information MEASURE AND CONTROL INVENTORY MANAGEMENT CONSOLE (IMC) 381190 Console for stand alone use. 381191 Console with PC interface, software & USB cable
INVENTORY MANAGEMENT CONSOLE (IMC) This powerful console is designed for the shop that wants simple control of their fluids. The IMC offers ease of operation, great value, and several features not previously More information INTRUSION DETECTION SYSTEM Section 281600
PART 1 - GENERAL 1.1 RELATED DOCUMENTS A. Drawings and general provisions of the Contract, including General and Supplementary Conditions and Division 01 Specification Sections, apply to this Section. More information SECTION 16721 FIRE ALARM AND DETECTION SYSTEMS
SECTION 16721 FIRE ALARM AND DETECTION SYSTEMS The equipment requirements of this section apply to the IUB Campus. The IUPUI Campus has a preferred vendor agreement for fire alarm systems. Contact Pat More information OREGON FIRE CODE Interpretations and Technical Advisories
OREGON FIRE CODE Interpretations and Technical Advisories A collaborative service by local and state fire professionals, along with our stakeholders and customers, to provide consistent and concise application More information Industrial Strength Leak Detection
Industrial Strength Leak Detection Don t let an undetected leak or spill ruin the environment or your reputation... TraceTek Technology: Find leaks before major damage is done... TraceTek Technology: Sensors More information Petroleum Storage Tank Compliance 101
Petroleum Storage Tank Compliance 101 Palm Beach County Board of County Commissioners Department of Environmental Resources Management Petroleum Storage Tank Compliance Section www.pbcgov.com/erm 561-233-2400 More information RI-215A Operator s Manual. Part Number: 71-0045RK Revision 0 Released: 10/3/05
RI-215A Operator s Manual Part Number: 71-0045RK Revision 0 Released: 10/3/05 Warranty RKI Instruments, Inc., warrants gas alarm equipment sold by us to be free from defects in materials and workmanship, More information FIBERGLASS UNDERGROUND STORAGE TANKS Special Installation Instructions for New York City Gasoline and Diesel Motor Fuels
INTRODUCTION The purpose of this manual is to provide speci c, detailed supplemental instruction regarding the installation of special Fiberglass Double-Wall Underground Storage Tanks (including compartment More information Invitation to Bid FIRE ALARM & DETECTION SYSTEM
Invitation to Bid FIRE ALARM & DETECTION SYSTEM Responses to an Invitation to Bid will be received by the Purchasing Supervisor, Sumner County Board of Education, 1500 Airport Road, Gallatin, TN 37066 More information Alliance System Ordering Guide
Alliance System Ordering Guide Multiple Technologies Versatile Hardware Powerful Software One family of parts and accessories Version 12-Nov-03 Alliance System Ordering Guide Table of Contents Controllers More information Fire Pump Controllers Remote Alarm Panels
Fire Pump Controllers Remote Alarm Panels Remote Alarm Panels 1.8 Remote Alarm Panels FDAP-M Electric... DFDAP-M Diesel... Product Specifications... 2 6 9 Features 1-1 DFDAP-M / FDAP-M Remote Alarm Panel More information SECTION 16720 - FIRE AND SMOKE ALARM SYSTEM. City of San Diego, CWP Guidelines
PART 1 -- GENERAL 1.1 WORK OF THIS SECTION SECTION 16720 - City of San Diego, CWP Guidelines A. The WORK of this Section includes providing manual and automatic fire alarm and smoke detection systems meeting More information Underground Storage Tanks
Underground Storage Tanks An Informational and Guidance Document for the University Community. Please contact Yale Environmental Health and Safety for latest Regulatory Requirements. A typical UST installation More information Architectural and Engineering Specification for a Perimeter Intrusion Detection System. FiberPatrol-ZR
Architectural and Engineering Specification for a Perimeter Intrusion Detection System FiberPatrol-ZR Sept 3, 2014 Page 1 of 13 FLR1DA0315-001 Rev A This document is intended to provide performance specifications More information site monitoring Kit Site Monitoring Kit User Manual we prove it.
site monitoring Kit 1 User Manual Site Monitoring Kit User Manual we prove it. 2 site monitoring Kit Content 1. Introduction 3 2. Content of the Site Monitoring Kit 4 3. Preparation 6 1. Positioning of More information EXHIBIT A SCOPE OF WORK
EXHIBIT A SCOPE OF WORK 1. (Contractor) shall provide fire alarm system maintenance/repair/testing services as described herein to the California Department of Veterans Affairs (hereinafter CDVA, CalVet, More information Metering Pumps Manufactured Since 1957. PCM Series. Pump Control Module INSTALLATION AND MAINTENANCE MANUAL
Metering Pumps Manufactured Since 1957 PCM Series Pump Control Module INSTALLATION AND MAINTENANCE MANUAL Table of Contents WarrantyandServicePolicy...3 Safety Information............................................... More information The following definitions apply with regard to requirements specified in this document:
Fire Pump Plan Review March 2010 Date of Review: / / Permit Number: Business/Building Name: Address of Project: Designer Name: Designer s Phone: Contractor: Contractor s Phone: Occupancy Classification: More information Product Description. Model VM 500 series [ VM508/VM508E ] Water Alarm. Telephone/Pager Alert Calls. Power Alarm. Maximum Number of Sensors
Product Description You need to protect the equipment in your data center, computer room, or equipment room from the damaging effects of high temperature and high humidity. The best way to protect sensitive More information LNG Monitoring. Fiber-Optic Leakage Detection System. Pipeline leakage detection. Regasification and liquefaction monitoring
LNG Monitoring Fiber-Optic Leakage Detection System Pipeline leakage detection Regasification and liquefaction monitoring Tank annulus and base slab monitoring Spill containment control Intelligent Solutions More information UST Site Inspection Guidance Document
UST Site Inspection Guidance Document September 2004 Publication No. 04-09-089 UST Site Inspection Guidance Document Prepared by: Washington State Department of Ecology Toxics Cleanup Program September More information MAINE DEPARTMENT OF ENVIRONMENTAL PROTECTION
Oxford Hills Bus Garage 36 Brown St, Norway, ME Oil Storage Inspection 2/20/14 CONDITIONS OBSERVED Underground Oil Storage: 12,000 gallon underground oil storage tank (split 10,000 gallon diesel/2,000 More information MAKING MODERN LIVING POSSIBLE. AK-SC255 On-Site Installation Guide DANFOSS ELECTRONIC CONTROLS & SENSORS
MAKING MODERN LIVING POSSIBLE AK-SC255 On-Site Installation Guide DANFOSS ELECTRONIC CONTROLS & SENSORS How to Use This Guide Read this Guide completely as you install and start up your new AK-SC 255 controller. More information C. Conform to requirements of Americans with Disabilities Act (ADA).
SECTION 28 31 00 - FIRE ALARM AND DETECTION SYSTEMS PART 1 - GENERAL 1.1 SECTION INCLUDES A. Fire alarm and detection systems 1.2 REFERENCES A. NFPA 70 - National Electrical Code B. NFPA 72 - National More information Y7230A CO 2 Alarm System
Y7230A CO 2 Alarm System FOR CO 2 GAS DETECTION PRODUCT DATA FEATURES APPLICATION Y7230A CO 2 alarm system is used to detect gas leaking from CO 2 beverage dispensing systems and posts an alarm to occupants More information The following definitions apply with regard to requirements specified in this document:
GUIDELINES FOR INSTALLATION OF TEMPORARY AND PERMANENT ABOVEGROUND DIESEL FUEL TANKS FOR EMERGENCY AND STANDBY POWER SYSTEMS LOCATED OUTSIDE OF BUILDINGS For Use by Unidocs Member Agencies or where approved More information Secondary Containment Options for Aboveground and Underground Tanks. Wayne Geyer Steel Tank Institute
Secondary Containment Options for Aboveground and Underground Tanks Wayne Geyer Steel Tank Institute Secondary containment tanks first appeared in the United States in the early 1980's, when several local More information Fire Alarm System Plans Submittal Guidelines For New and Existing Systems
Fire Alarm System Plans Submittal Guidelines For New and Existing Systems SCOPE The Temecula Fire Prevention Bureau (TFPB) has established the following requirements for the submittal of all fire alarms, More information UNIFIED FACILITIES GUIDE SPECIFICATIONS
USACE / NAVFAC / AFCEC / NASA UFGS-28 31 75.00 10 (November 2008) ----------------------------------- Preparing Activity: USACE Superseding UFGS-28 31 75.00 10 (April 2006) UNIFIED FACILITIES GUIDE SPECIFICATIONS More information Standard Test Procedures For Evaluating Leak Detection Methods. Volumetric Tank Tightness Testing Methods. Printed on Recycled Paper
United States Environmental Protection Agency Solid Waste And Emergency Response/ Research And Development (OS-420) WF EPA/530/UST-90-004 March 1990 Standard Test Procedures For Evaluating Leak Detection More information Commercial Semi-Instantaneous Water Heaters
FEATURES HWI Models A. O. Smith s HWI models are available for operation with steam or boiler water as the energy source. They are factory assembled with components sized, piped and checked at the factory More information A SUPERIOR SOLUTION TO DRUM AND STEEL TANK USAGE
A SUPERIOR SOLUTION TO DRUM AND STEEL TANK USAGE The U.L.C. Listed C142.14-03 Cubet container provides a unique solution to storage and dispensing fluids. The Cubet s logical and integrated design allows More information JNIOR. Overview. Get Connected. Get Results. JNIOR Model 310. JNIOR Model 312. JNIOR Model 314. JNIOR Model 410
The INTEG is an Ethernet I/O (digital, analog) device that monitors and controls a small set of process signals. functions as both basic I/O for integration with another application or system AND as a More information Waste Oil Collection / Storage
ENVIRONMENTAL & REGULATORY SERVICES Storage Tank Regulation Section P. O. Box 7837 Madison, Wisconsin 53707-7837 TDD #: (608) 264-8777 http://www.commerce.state.wi.us http://www.wisconsin.gov Jim Doyle, More information Tanks: What's in store?
Tanks: What's in store? Technical and regulatory developments in tank construction prompt changes; operations and maintenance receive greater emphasis. Chemical Processing magazine By Wayne Geyer Tanks More information This page left intentionally blank
1 This page left intentionally blank 2 STATE OF TENNESSEE DEPARTMENT OF ENVIRONMENT AND CONSERVATION DIVISION OF UNDERGROUND STORAGE TANKS TECHNICAL CHAPTER 4.2 SPILL AND OVERFILL PREVENTION EFFECTIVE More information Fuel Management Systems
Fuel Management Systems Global Product Catalogue Effective June 1, 2012 Table of Contents Overview 5 The Total System Solution 6 Fuel Management System Consoles 9 TS-550 evo Fuel Management System 9 TS-5 More information The L&J Engineering Model MCG 1500SFI Servo Gauge
PRODUCT DATA SHEET The is the most compact and lightest servo available today. Accuracy / repeatability of 1/32 inch (0.8mm) Product and Interface, custody transfer Wireless Infrared Calibration Advanced More information Tank Gauging & Inventory Management Solutions
& Inventory Management Solutions Automation solutions for oil & gas, defense and aviation applications FuelsManager, Varec s industry-leading software is available in four editions: Standard, Professional, More information OPL BASIC. Dosing System for Professional Laundry machines. Contents
OPL BASIC Dosing System for Professional Laundry machines Contents 1 Getting Started. Page 2 2 Installation. Page 4 3 Set Up & Operation. Page 8 4 Maintenance & Accessories. Page 10 5 Troubleshooting Page More information HERNANDO COUNTY FIRE ALARM GUIDELINES
HERNANDO COUNTY FIRE ALARM GUIDELINES To be used for all commercial building fire alarm system plan review. The procedures set forth in this document are the minimum requirements necessary to ensure a More information INSTALLATION INSTRUCTIONS
LIGHTING CONTROL PANELS 4 AND 8 RELAYS INSTALLATION INSTRUCTIONS INSTALLATION OVERVIEW The installation instructions contained in this document are provided as a guide for proper and reliable installation. More information InHome Water Leak Detection Package
InHome Water Leak Detection Package For Model Numbers ILD10A-L and ILD10A-B Installation Guide / Wiring Diagram For Creating Water Leak Detection-based Events with Line-Powered or Battery-Powered Sensors More information Fluid Monitoring and Inventory Management
SECTION FOUR Fluid Monitoring and Inventory Management Introduction Alemite meets your fluid monitoring and inventory management needs with its Accu-Guard systems and its Bigview Tank Monitor. These systems More information INSTALLATION GUIDE. Card Reader & Controller with KIM Swipe Reader for Solitaire 850 / 950 / 850L Learnlok PK2930
INSTALLATION GUIDE Card Reader & Controller with KIM Swipe Reader for Solitaire 850 / 950 / 850L Learnlok PK2930 Card Reader and Controller Model 3.5 with KIM Swipe Reader Table of Contents 1. Features.................................. More information Water Leak Detection System
Water Leak Detection System Installation and Operating Manual 505-334-5865 ph 505-334-5867 fax www.rodisystems.com email:info@rodisystems.com 936 Highway 516 Aztec, NM 87410-2828 Manual Revisions and Copyright More information BACnet Automation Interface Module (Network Version)
Sense +V Tx Rx LAN LINK Over ARCNET KBaud BACnet Rx BACnet Tx Archive Valid Port S Tx Port S Rx Low Battery Network- Enhanced Access Default MSTP PTP = Download Required on Rnet and Port S IP Address IP More information INSTALLATION DATA ETC Single Stage Temperature Control Nema Type 4X
PRODUCT DESCRIPTION The Ranco ETC is a microprocessor-based electronic temperature control designed to provide on/off control for commercial heating, ventilating, air conditioning, and refrigeration. The More information Automated Time & Attendance System BIG EFFICIENCY FOR BUSINESS
Automated Time & Attendance System BIG EFFICIENCY FOR BUSINESS PAYROLL BECOMES A UTOMATIC Business owners used to have little choice when it came to processing time and attendance data either spend a lot More information CHAPTER 62-740 PETROLEUM CONTACT WATER
CHAPTER 62-740 PETROLEUM CONTACT WATER 62-740.010 Declaration of Intent (Repealed) 62-740.020 Applicability 62-740.030 Definitions 62-740.040 General 62-740.100 Management Practices for Producers of PCW More information Spill Containment Manholes
Spill Containment Manholes 1-2100 Series OPW and Pomeco Spill Containment Manholes are designed to prevent spilled product from entering the soil near the fill and vapor return riser connections on underground More information E-Version SECTION 15318 - CHLORINATION SYSTEM PART 1 - GENERAL PART 2 - PRODUCT
SECTION 15318 - CHLORINATION SYSTEM PART 1 - GENERAL 1.1. SCOPE OF WORK A. Under this item the Contractor shall furnish and install a sodium hypochlorite solution metering system complete with all accessories More information University of Houston Master Construction Specifications Insert Project Name
SECTION 21 22 13 - SAPPHIRE CLEAN-AGENT FIRE SUPPRESSION SYSTEM PART 1 GENERAL 1.1 RELATED DOCUMENTS A. The Conditions of the Contract and applicable requirements of Divisions 0 and 1 and this Section More information 2017 © DocPlayer.net Privacy Policy | Terms of Service | Feedback