Source: http://docplayer.net/20992009-Preview-indian-standard-common-specification-for-high-voltage-switchgear-and-controlgear-standards.html
Timestamp: 2018-05-25 21:03:15
Document Index: 396829750

Matched Legal Cases: ['art 1', 'art 351', 'art 2', 'art 4', 'art 5', 'art 1', 'art 2', 'art 2', 'art 2', 'art 2', 'art 2', 'art 2', 'art 2', 'art 1', 'art 2', 'art 4', 'art 5', 'art 8', 'art 21', 'art 21', 'art 23', 'art 1', 'art 2', 'art 2', 'art 1', 'art 2', 'art 1', 'art 1', 'art 2', 'art 1', 'art 2', 'art 2', 'art 2', 'art 3', 'art 4', 'art 5', 'art 7', 'art 7', 'art 4', 'art 4', 'art 4', 'art 4', 'art 4', 'art 5', 'art 5', 'art 5', 'art 6', 'art 4', 'art1', 'art 1', 'art 7', 'art 1', 'art 2', 'art 1', 'art 1']

(PREVIEW) Indian Standard COMMON SPECIFICATION FOR HIGH-VOLTAGE SWITCHGEAR AND CONTROLGEAR STANDARDS - PDF
Download "(PREVIEW) Indian Standard COMMON SPECIFICATION FOR HIGH-VOLTAGE SWITCHGEAR AND CONTROLGEAR STANDARDS"
1 (PREVIEW) Indian Standard COMMON SPECIFICATION FOR HIGH-VOLTAGE SWITCHGEAR AND CONTROLGEAR STANDARDS IS 12729:2004 IEC 60694(2002) 1.1 Scope This International Standard applies to a.c. switchgear and controlgear, designed for indoor and outdoor installation and for operation at service frequencies up to and including 60.Hz on systems having voltages above V. This standard applies to all high-voltage switchgear and controlgear except as otherwise specified in the relevant IEC standards for the particular type of switchgear and controlgear. 1.2 Normative references The following normative documents contain provisions which, through reference in this text, constitute provisions of this International Standard. At the time of publication, the editions indicated were valid. All normative documents are subject to revision, and parties to agreements based on this International Standard are encouraged to investigate the possibility of applying the most recent editions of the normative documents indicated below. Members of IEC and ISO maintain registers of currently valid International Standards. IEC :1996, Rotating electrical machines Part 1: Rating and performance 1 IEC 60038:1983, IEC standard voltages IEC 60050(131):1978, International Electrotechnical Vocabulary (IEV) Chapter 131: Electric and magnetic circuits IEC 60050( 151):1978, International Electrotechnical Vocabulary (IEV) Chapter 151: Electrical and magnetic devices IEC 60050(191):1990, International Electrotechnical Vocabulary (IEV) - Chapter 191: Dependability and quality of service IEC 60050(301):1983, International Electrotechnica Vocabulary (IEV) Chapter 301: General terms on measurements in electricity IEC :1998, International Electrotechnical Vocabulary (IEV) Part 351: Automatic control IEC 60050(44 1):1984,International Electrotechnical Vocabulary (IEV) Chapter 441: Switchgear, controlgear and fuses IEC 60050(446):1983, International Electrotechnical Vocabulary (IEV) Chapter 446: Electrical relays IEC 60050(581):1978, International Electrotechnical Vocabulary (IEV) Chapter 581: Electromechanical
2 components for electronic equipment IEC 60050(604): 1987, International Electrotechnical Vocabulary (IEV) Chapter 604: Generation, transmission and distribution of electricity Operation IEC 60050(811):1991, International Electrotechnical Vocabulary.(IEV) Chapter 811:.Electric traction IEC (826):1982, International Electrotechnical Vocabulary (IEV) Chapter 826: Electrical installations of buildings IEC :1984, Direct acting indicating analogue electrical measuring instruments and their accessories Part 2 : Special for ammeters and voltmeters IEC :1984, Direct acting indicating analogue electrical measuring instruments and their accessories Part 4 : Special for frequency meters IEC :1985, Direct acting indicating analogue electrical measuring instruments and their accessories Part 5: Special for phase meters, power factor meters and synchroscopes IEC 60056:1987, High-voltage alternating-current circuit-breakers IEC 60059:1938, IEC standard current ratings IEC :1989, High-voltage test techniques Part 1: General definitions and test IEC 60064:1993, Tungsten filament lamps for domestic and similar general lighting purposes Performance IEC (all parts), Environmental testing Part 2: Tests IEC :1990, Environmental testing Part 2: Tests. Tests A: Cold IEC :1974, Environmental testing Part 2: Tests. Tests B: Dry heat IEC :1969, Environments/ testing Part 2: Tests. Test Ca: Damp heat, steady state IEC :1994, Environments/ testing Part 2: Tests Test Q: Sealing IEC :1980, Environmental testing Part 2: Tests. Test Db and guidance: Damp heat, cyclic ( hour cycle) IEC :1991, Environmental testing Part 2: Tests Test Eg: Impact, spring hammer IEC :1993, Insulation co-ordination Part 1: Definitions, principles and rules IEC :1996, Insulation co-ordination Part 2: Application guide IEC 60073:1996, Basic and safety principles for man-machine interface, marking and identification Coding Identification principles for indication devices and actuators IEC 60081:1997, Double-capped fluorescent lamps Performance specifications IEC 60083:1997, Plugs and socket-outlets for domestic and similar general use standardized in member countries of IEC
3 IEC 60085:1984, Thermal evaluation and classification of electrical insulation IEC :1982, Fixed resistors for use in electronic equipment Part 4: Sectional specification: Fixed power resistors IEC (all parts), Connectors for frequencies below 3 MHz IEC (all parts), Polyvinyl chloride insulated cables of rated voltages up to and including 450/750V IEC 60228:1978, Conductors of insulated cables IEC (all parts), Rubber insulated cables Rated voltages up to and including 450/750 V IEC :1977, Electrical relays Part 5: Insulation tests for electrical relays IEC :1990, Electrical relays Part 8: Thermal electrical relays IEC :1988, Electrical relays Part 21: Vibration, shock, bump and seismic tests on measuring relays and protection equipment - Section One: Vibration tests (sinusoidal) IEC :1993, Electrical relays Part 21: Vibration, shock, bump and seismic tests on measuring relays and protection equipment Section 3: Seismic tests IEC :1994, Electrical relays Part 23: Contact performance IEC :1998, Low-voltage fuses Part 1: General IEC :1986, Low-voltage fuses Part 2: Supplementary for fuses for use by authorized persons (fuses mainly for industrial application) IEC :1998, Low-voltage fuses Part 2-1: Supplementary for fuses for use by authorized persons (fuses mainly for industrial application) Sections I to V: Examples of types of standardized fuses IEC 60270:1981, Partial discharge measurements IEC 60296:1982, Specification for unused mineral insulating oils for transformers and switchgear IEC :1999, Plugs, socket-outlets and couplers for industrial purposes Part 1: General IEC :1999, Plugs, socket-outlets and couplers for industrial purposes Part 2: Dimensional interchangeability - for pin and contact-tube accessories IEC (all parts), Printed boards IEC 60376:1971, Specification and acceptance of new sulphur hexafluoride IEC :1989, Potentiometers for use in electronic equipment Part 1: Generic specification IEC (all parts), Graphical symbols for use on equipment IEC 60445: 1999, Basic and safety principles for man-machine interface, marking and identification Identification of equipment terminals and of terminations of certain designated conductors, including general rules for an alphanumeric system
4 IEC 60480:1974, Guide to the checking of sulphur hexafluoride (SF 6 ) taken from electrical equipment IEC 60485:1974, Digital electronic d.c. voltmeters and d.c. electronic analogue-to-digital converters IEC :1997, Power cables with extruded insulation and their accessories for rated voltages from 1 kv (Um = 1,2 kv) up to 30 kv (Um = 36 kv) - Part 1: Cables for rated voltages of 1 kv(um = 1,2 kv) and 3 W(Um = 3,6kV) IEC 60507:1991, Artificial pollution tests on high-voltage insulators to be used on a. c. systems IEC :1985, Electromechanical components for electronic equipment; basic testing procedures and measuring methods Part 2: General examination, electrical continuity and contact resistance tests, insulation tests and voltage -stress tests IEC 60529:1989, Degrees of protection provided by enclosures (IP code) IEC 60617, Graphical symbols for diagrams IEC :1998, Switches for household and similar fixed-electrical installations Part 1: General IEC 60721, Classification of environmental conditions IEC :1992, Automatic electrical controls for household and similar use Part 2:Particular for temperature sensing controls IEC :1995, Automatic electrical controls for household and similar use Part 2: Particular for humidity sensing controls IEC 60815:1986, Guide for the selection of insulators in respect of polluted conditions IEC 60816:1984, Guide on methods of measurement of short-duration transients on low-voltage power and signal lines IEC :1995, Low-voltage switchgear and controlgear - Part 2: Circuit-breakers IEC :1999, Low-voltage switchgear and controlgear Part 3: Switches, disconnectors, switchdisconnectors and fuse-combination units IEC :1990, Lo w-voltage switchgear and controtgear Part 4: Contractors and motor-starters -Section One: Electromechanical contractors and -motor-starters IEC :1997, Low-voltage switchgear and controlgear Part 5: Control circuit devices and switching elements Section One: Electromechanical control circuit devices IEC :1989, Low-voltage switchgear and controlgear Part 7: Ancillary equipment Section One: Terminal blocks for copper conductors IEC :1995, Low-voltage switchgear and controlgear Part 7: Ancillary equipment Section 2: Protective conductor terminal blocks for copper conductors IEC :1992, Electromagnetic compatibility (EMC) Part 4: Testing and measurement techniques Section 1: Overview of immunity tests Basic EMC publication IEC :1995, Electromagnetic compatibility (EMC) - Part 4: Testing and measurement techniques Section 4: Electrical fast transient/burst immunity test Basic EMC Publication
5 IEC :-1995, Electromagnetic compatibility (EMC) Part 4: Testing and measurement techniques Section 12: Oscillatory waves immunity test Basic EMC Publication IE.C :1999, Electromagnetic compatibility (EMC) Part 4-17: Testing and measurement techniques Ripple on d. c. input power port immunity test IEC :, Electromagnetic compatibility (EMC) Part 4-29: Testing and measurement techniques - Voltage dips, short interruptions and voltage variations on d. c.input power ports, immunity tests IEC (all parts), Electromagnetic compatibility (EMC) Part 5 Installation and mitigation guidelines IEC :1996, Electromagnetic compatibility (EMC) Part 5: Installation and mitigation guidelines Section 1: Genera/ considerations Basic EMC publication IEC :1997, Electromagnetic compatibility (EMC) Part 5: Installation and mitigation guidelines Section 2: Earthing and cabling IEC :, Electromagnetic compatibility (EMC) Part 6-5: Generic standards Immunity for power station and substation environments 1) IEC :1991, Electromechanical switches for use in electronic equipment - Part 4: I Sectional specification for lever (toggle) switches IEC 61166:1993, High-voltage alternating current circuit-breakers - Guide for seismic qualification of high-voltage alternating current circuit-breakers IEC :1992, High-voltage test techniques for low-voltage equipment Part1: Definitions, test and procedure IEC 61634:1995, High-voltage switchgear and controlgear Use and handling of sulphur hexafluoride (SF 6 ) in high-voltage switchgear and controlgear IEC (all parts), Electronechanical non-specified time all-or nothing relays IEC :1998, Electrornechanical non-specified time all-or-nothing relays Part 1: General IEC :1997, Electromechanical all-or-nothing relays - Part 7: Tests procedures CISPR 11:1990, Limits and methods of measurement of electromagnetic disturbance Characteristics of industrial, scientific and medical (ISM) radio-frequency equipment CISPR 16-1:1993, Specification for radio disturbance and immunity measuring apparatus and methods Part 1.-Radio disturbance and immunity measuring apparatus CISPR 18-2:1986, Radio interference characteristics of overhead power lines and high-voltage equipment - Part 2: Methods of measurement and procedure for determining limits Amendment 1 (1993) Other International Standards are referred to for information in this standard. They are listed in annex G.
(PREVIEW) NATIONAL ELECTRICAL CODE 2011 SECTION 1 SCOPE OF THE NATIONAL ELECTRICAL CODE
(PREVIEW) NATIONAL ELECTRICAL CODE 2011 SECTION OF THE NATIONAL ELECTRICAL CODE This Part 1/Section 1 of the Code describes the scope of the National Electrical Code. The National Electrical Code takes
BRITISH STANDARD BS EN 60204-1:2006 Safety of machinery Electrical equipment of machines Part 1: General requirements The European Standard EN 60204-1:2006 has the status of a British Standard ICS 29.020