Source: http://links.casemakerlegal.com/bDocView.aspx?statecd=us&codesec=60.756&sessionyr=&Title=40&version=&datatype=D&cvfilename=usadmincv2020Title40ChapterISubchapterCPart60SubpartWWW.htm&noheader=0&nojumpmsg=0&userid=REPLACE_LOGINID&categoryAlias=ADMIN&state=Federal&strdatatype=ADMIN&catcalled=Code%20of%20Federal%20Regulations&browseLevel=3&ci=25
Timestamp: 2020-08-03 17:03:55
Document Index: 571465505

Matched Legal Cases: ['§ 60', '§ 60', '§ 60', '§ 60', '§ 60', '§ 60', '§ 60', '§ 60', '§ 60', '§ 60', '§ 60', '§ 60', '§ 60', '§ 60', '§ 60', '§ 60', '§ 60', '§ 60', '§ 60']

§ 60.756. Monitoring of operations.
§ 60.756. Monitoring of operations
Except as provided in § 60.752(b)(2)(i)(B),
(a) Each owner or operator seeking to comply with § 60.752(b)(2)(ii)(A) for an active gas collection system shall install a sampling port and a thermometer, other temperature measuring device, or an access port for temperature measurements at each wellhead and:
(1) Measure the gauge pressure in the gas collection header on a monthly basis as provided in § 60.755(a)(3) ; and
(2) Monitor nitrogen or oxygen concentration in the landfill gas on a monthly basis as provided in § 60.755(a)(5) ; and
(3) Monitor temperature of the landfill gas on a monthly basis as provided in § 60.755(a)(5).
(b) Each owner or operator seeking to comply with § 60.752(b)(2) (iii) using an enclosed combustor shall calibrate, maintain, and operate according to the manufacturer's specifications, the following equipment.
(c) Each owner or operator seeking to comply with § 60.752(b)(2) (iii) using an open flare shall install, calibrate, maintain, and operate according to the manufacturer's specifications the following equipment:
(d) Each owner or operator seeking to demonstrate compliance with § 60.752(b)(2) (iii) using a device other than an open flare or an enclosed combustor shall provide information satisfactory to the Administrator as provided in § 60.752(b)(2)(i)(B) describing the operation of the control device, the operating parameters that would indicate proper performance, and appropriate monitoring procedures. The Administrator shall review the information and either approve it, or request that additional information be submitted. The Administrator may specify additional appropriate monitoring procedures.
(e) Each owner or operator seeking to install a collection system that does not meet the specifications in § 60.759 or seeking to monitor alternative parameters to those required by § 60.753 through § 60.756 shall provide information satisfactory to the Administrator as provided in § 60.752(b)(2)(i) (B) and (C) describing the design and operation of the collection system, the operating parameters that would indicate proper performance, and appropriate monitoring procedures. The Administrator may specify additional appropriate monitoring procedures.
(f) Each owner or operator seeking to demonstrate compliance with § 60.755(c), shall monitor surface concentrations of methane according to the instrument specifications and procedures provided in § 60.755(d). Any closed landfill that has no monitored exceedances of the operational standard in three consecutive quarterly monitoring periods may skip to annual monitoring. Any methane reading of 500 ppm or more above background detected during the annual monitoring returns the frequency for that landfill to quarterly monitoring.
Cite as 40 C.F.R. § 60.756
§ 60.756. Monitoring of operations. (You are viewing section)