Source: https://www.ada.gov/loudounvaattf2.htm
Timestamp: 2018-08-17 21:36:10
Document Index: 112669848

Matched Legal Cases: ['§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 8', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 8', '§ 8', '§ 8', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4', '§ 4']

Settlement Agreement between the United States and Loudoun County, Virginia, Attachment (F)2
Attachment F (2): Program Access in Existing Facilities in Sterling
LITTLE LEAGUE LOWER FIELDS
a. Although the parking lot has a total of 38 parking spaces, access aisles and signage designated for spaces reserved for persons with disabilities are lacking. On the shortest accessible route to the accessible entrance, provide 1 van accessible space and 1 standard space designated as reserved for people with disabilities. Ensure that standard accessible spaces are a minimum of 96 inches wide and served by access aisles at least 60 inches wide. Ensure that van accessible spaces are a minimum of 96 inches wide and served by access aisles at least 96 inches wide. At all spaces designated as reserved for persons with disabilities, provide vertical signs with the International Symbol of Accessibility located such that they cannot be obstructed by parked vehicles. At van accessible spaces, provide an additional "Van-Accessible" sign located below the International Symbol of Accessibility. Ensure that all spaces and access aisles for persons with disabilities are flat and level, with slopes and cross-slopes not exceeding 1:50 in all directions, and that their surfaces are firm, stable, and slip-resistant. Standards §§ 4.1.2(5), 4.6, 4.30.7(1).
LANESVILLE HOUSE /CLAUDE MOORE PARK
4. ACCESSIBLE ROUTE
a. The route to the ramp is inaccessible because it is not firm, stable or slip resistant. Provide at least one accessible route within the boundary of the site connecting these elements that, to the maximum extent feasible, coincides with the route for the general public. The accessible route must have a minimum clear width of 36 inches, or a minimum clear width of 42 inches if there is a turn around an obstruction less than 48 inches wide; have passing spaces at least 60 inches by 60 inches at least every 200 feet; have a minimum clear headroom of 80 inches; have a surface that is firm, stable, and slip resistant; have, in the absence of a curb ramp ramp, elevator, or platform lift, no level changes in excess of ½ inch vertically; and have a running slope of less than 1:20 (5%) (or have been constructed as a fully accessible ramp) and a cross slope of less than 1:50 (2%). Standards §§ 4.3, 4.5, Fig. 7.
b. The ramp is inaccessible because it is too steep and the landings are grassy. Provide a ramp that is at least 36 inches wide with a slope not exceeding 1:12 and a cross slope not exceeding 1:50; with level landings at least as wide as the ramp and 60 inches long at the top and bottom of the ramp; with level landings measuring at least 60 inches by 60 inches when the ramp changes direction; and edge protection that is at least 2 inches high at the drop off sides. Provide handrails that are between 1¼ inches and 1½ inches in diameter such that the inside handrail is continuous and both handrails have a continuous gripping surface along both sides of the ramp extending at least 12 inches beyond the top and bottom of the ramp parallel with the ground surface; the handrails do not rotate within their fittings; and both handrails are mounted between 34 inches and 38 inches above the ramp surface, with ends rounded or returned smoothly to the floor, wall, or post. Ensure that the ramp and approaches are designed so that water will not accumulate on walking surfaces. Standards §§ 4.3.8, 4.8.
c. The entrance door is inaccessible because knob hardware is used. Provide a door with hardware that is easy to grasp with one hand and that does not require tight grasping, pinching, or twisting of the wrist to operate. Lever-operated mechanisms, push-type mechanisms, and U-shaped handles are acceptable designs. Standards § 4.13.9.
FROGSHACKLE COTTAGE/ CLAUDE MOORE PARK
a. The route through the entrance door into the house is inaccessible because there are only 73 inches of head room provided. Provide an accessible route at this location with a minimum of 80 inches of clear head room throughout. If the vertical clearance is reduced to less than 80 inches at any point, provide a barrier. Standards § 4.4.2, Fig. 8(c-1).
EASTERN LOUDOUN LIBRARY
21030 Whitfield Place Drive, Sterling
a. The ramp is inaccessible because the cross slope is 4 %, the mid-level landing slope is 3.3%, the handrails are mounted 29 inches above the finished surface of the ramp, the handrails lack 12 inch extensions, the ends are not rounded or returned smoothly to the ground or floor, and the handrails are 2 ½ inches in diameter and the space between the bar and the wall is measured 2 to 2 ½ inches. Provide a ramp that is at least 36 inches wide with a slope not exceeding 1:12 and a cross slope not exceeding 1:50; with level landings at least as wide as the ramp and 60 inches long at the top and bottom of the ramp; with level landings measuring at least 60 inches by 60 inches when the ramp changes direction; and edge protection that is at least 2 inches high at the drop off sides. Provide handrails that are between 1¼ inches and 1½ inches in diameter such that the inside handrail is continuous and both handrails have a continuous gripping surface along both sides of the ramp extending at least 12 inches beyond the top and bottom of the ramp parallel with the ground surface; the handrails do not rotate within their fittings; and both handrails are mounted between 34 inches and 38 inches above the ramp surface, with ends rounded or returned smoothly to the floor, wall, or post. Ensure that the ramp and approaches are designed so that water will not accumulate on walking surfaces. Standards §§ 4.3.8, 4.8.
a. Although there is one public telephones provided, and a TTY is provided, it lacks appropriate signage. Provide at least one accessible public TTY with appropriate signage. Standards §§ 4.30.7(3), 4.31.9.
b. The exterior pay telephone is inaccessible because the highest operable part is 56 inches above the finished floor and no lower phone is provided. Provide an accessible telephone with a clear floor space of at least 30 inches by 48 inches that allows either a forward or parallel approach by a person using a wheelchair such that bases, enclosures, and fixed seats do not impede approaches to the telephone; with the highest operable part of the telephone mounted no more than 48 inches above the floor for a front approach or no more than 54 inches above the floor for a side approach; that are hearing aid compatible and have a volume control mechanism; with telephone books, if provided, located between 15 and 48 inches above the finished floor for a front approach or between 9 and 54 inches above the finished floor for a side approach; and with a cord of at least 29 inches long from the telephone to the handset. Standards § 4.31.
c. The route past the telephone is inaccessible because the phone protrudes into the walkway. Provide an accessible route at this location such that no objects with their bottom leading edges measuring between 27 inches and 80 inches above the finished floor protrude more than 4 inches into walks, halls, corridors, passageways, or aisles. Free-standing objects mounted on posts or pylons may overhang 12 inches maximum from 27 inches to 80 inches above the ground or finished floor. Standards § 4.4.
a. The building is inaccessible because the signage provided lacks the International Symbol of Accessibility at accessible and inaccessible entrances. Provide accessible directional signage with the International Symbol of Accessibility at inaccessible entrances directing users to the accessible entrance, and provide accessible signage with the International Symbol of Accessibility at all permanent accessible entrances. Standards §§ 4.1.3(8)(d), 4.13, 4.30.
b. The signage provided does not indicate that there is a designated accessible study room. Provide permanent room signage with upper case, sans serif or simple serif type letters and numerals, meeting the requirements of the Standards for character height, raised characters, finish and contrast, accompanied by Grade 2 Braille and the International Symbol of Accessibility; mounted on the wall adjacent to the latch side of the door or on the nearest adjacent wall at a height of 60 inches above the finished floor to the centerline of the sign; and located so that a person may approach within 3 inches of the signage without encountering protruding objects or standing within the swing of a door. Standards §§ 4.30.1, 4.30.4, 4.30.5, 4.30.6, 4.30.7.
c. The card catalog and magazine display are inaccessible because they are higher than 54 inches and the bottom of the card catalog is 7 ½ inches above the finished floor. Provide a card catalog and magazine display with a minimum of 36 inches of clear width between units and with reach ranges of between 18 inches and 54 inches (maximum height of 48 inches is preferred) above the finished floor. Standards § 8.4, Fig. 55.
a. Although the facility contains an emergency alarm system, the alarm system is inaccessible because visual alarms are lacking in some toilet rooms, hallways, corridors, meeting rooms, and auditoriums. Provide visual alarm devices in toilet rooms and any other general usage areas (e.g., meeting rooms), hallways, lobbies, and any other area for common use. Such devices shall be integrated into the facility alarm system and shall meet the requirements of the Standards for lamp type, color, pulse duration, intensity, and flash rate. Visual alarm appliances shall be placed 80 inches above the highest floor level within the space or 6 inches below the ceiling, whichever is lower. Visual alarm appliances shall be located such that no place in any room or space, including common corridors or hallways, required to have a visual alarm appliance shall be more than 50 feet from the signal. In large rooms and spaces exceeding 100 feet across, without obstructions 6 feet above the finished floor, devices may be placed around the perimeter, spaced a maximum of 100 feet apart, in lieu of suspending appliances from the ceiling. Standards § 4.28.3.
a. Although 2 drinking fountains are provided, there is no accessible drinking fountain because the spout is 37 ½ inches above the finished floor and the height of the water is 3 inches. Provide at least one drinking fountain with a spout height no higher than 36 inches, measured from the finished floor or ground surface to the spout outlet; and a spout located at the front of the unit that directs the water flow in a trajectory that is nearly parallel to the front of the unit and is positioned so the flow of water is within 3 inches of the front edge of the fountain and at least 4 inches high. Ensure that fountain controls are operable with one hand, require 5 lbf or less to operate without tight grasping, pinching, or twisting of the wrist; and are front mounted or side mounted near the front edge. For each accessible drinking fountain, provide a drinking fountain that is accessible to people who have difficulty bending or stooping. This can be accommodated by the use of a "hi-lo" fountain; by providing one fountain accessible to those who use wheelchairs and one fountain at a standard height convenient for those who have difficulty bending; by providing a fountain accessible to people who use wheelchairs and a cup dispenser; or by such other means as would achieve the required accessibility for each group of people. Standards §§ 4.15, 4.27.4, Fig. 27.
b. The wall-mounted drinking fountain is inaccessible because there is not adequate knee space or clear floor space. Provide a drinking fountain with clear knee space between the bottom of the apron and the finished floor or ground of at least 27 inches high, 30 inches wide, and 17 to 19 inches deep; and a minimum clear floor space of 30 inches by 48 inches to allow a person in a wheelchair to approach the unit facing forward. Standards § 4.15.5(1), Figs. 27(a), (b).
11. WOMEN'S TOILET ROOM
b. Although an audible alarm is provided in this facility, there is no visual alarm appliance in the toilet room. Provide a visual alarm appliance in the toilet room. Standards §§ 4.28.1, 4.28.3.
c. The seat cover dispenser in the designated accessible stall is inaccessible because the controls are mounted at 55 ½ inches above the finished floor . Provide a seat cover dispenser with the controls a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
d. The toilet in the designated accessible stall is inaccessible because its centerline measures 19 ½ inches from the side wall. Provide a toilet with a centerline that measures 18 inches from the near side wall. Standards § 4.17.3, Fig. 30.
f. The rear grab bar at the toilet in the designated accessible stall is inaccessible because the closer end is mounted 12 inches from the side wall. Provide a rear grab bar that is at least 36 inches in overall length, with the closer end no more than 6 inches from the side wall; mounted 33 to 36 inches above the finished floor; with a diameter between 1¼ and 1½ inches; with 1½ inches between the grab bar and the wall; and at least 1½ inches between the grab bar and any other object, such as a toilet seat cover dispenser. Standards §§ 4.17.6, 4.26.2, Fig. 30.
c. The seat cover dispenser in the designated accessible stall is inaccessible because the controls are mounted at 56 inches above the finished floor. Provide a seat cover dispenser with the controls a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
d. The urinal is inaccessible because the clear floor space on which the urinal is centered is 27 inches. Provide a urinal with an elongated rim mounted 17 inches or less above the finished floor, a clear floor space of at least 30 inches wide and 48 inches deep centered on the urinal, and a flush control height of 44 inches or less above the finished floor. Standards §§ 4.18.2, 4.18.3, 4.18.4.
102 Enterprise Street, Sterling
a. Although the parking lot has a total of 98 parking spaces, an inadequate number are designated as reserved for people with disabilities. On the shortest accessible route to the accessible entrance, provide at least 1 van accessible space and 3 standard spaces designated as reserved for people with disabilities. Standard accessible spaces shall be a minimum of 96 inches wide and served by access aisles at least 60 inches wide. Van accessible spaces shall be a minimum of 96 inches wide and served by access aisles at least 96 inches wide. All spaces designated as reserved for people with disabilities shall have vertical signs with the International Symbol of Accessibility located such that they cannot be obstructed by parked vehicles. Van accessible spaces shall have an additional "Van-Accessible" sign located below the International Symbol of Accessibility. Standards §§ 4.1.2(5), 4.6, 4.30.7(1).
b. The parking reserved for persons with disabilities is inaccessible because the access aisles are 55 inches wide. Provide designated accessible parking spaces that are a minimum of 96 inches wide and served by access aisles at least 60 inches wide. Provide van accessible spaces that are a minimum of 96 inches wide and served by access aisles at least 96 inches wide. Standards §§ 4.1.2(5), 4.6.3, Fig.9.
14. ACCESSIBLE ROUTE
a. The route from the parking lot to the building is inaccessible because the curb ramp has lips on both sides, lacks smooth transitions, and is not firm, stable or slip resistant. Provide a curb ramp that is at least 36 inches wide, has a maximum slope of 1:12, is located so that it cannot be obstructed by parked vehicles, and has a stable, firm, and slip-resistant surface with a detectable warning extending the full width and depth of the ramp. If the curb ramp is located where pedestrians must walk across it, provide either flared sides (with a maximum slope of 1:10) or handrails or guardrails to protect against cross traffic. Standards § 4.3.8, 4.7, Fig. 12.
b. The route from the parking lot to the building is inaccessible because the curb ramps lack detectable warnings. Provide a curb ramp that is at least 36 inches wide, has a maximum slope of 1:12, is located so that it cannot be obstructed by parked vehicles, and has a stable, firm, and slip-resistant surface with a detectable warning extending the full width and depth of the ramp. If the curb ramp is located where pedestrians must walk across it, provide either flared sides (with a maximum slope of 1:10) or handrails or guardrails to protect against cross traffic. Standards § 4.3.8, 4.7, Fig. 12.
15. EXTERIOR ENTRANCE AND DOORS
a. The building is inaccessible because it lacks signage at the rear entrance to indicate where the accessible entrance is located. Provide accessible, directional signage with the International Symbol of Accessibility at inaccessible entrances directing users to the accessible entrance, and provide accessible signage with the International Symbol of Accessibility at all permanent accessible entrances. Standards §§ 4.1.3(8)(d), 4.13, 4.30.
b. There is no accessible route from the rear entrance to the playground/picnic tables. Provide at least one accessible route within the boundary of the site connecting these elements that, to the maximum extent feasible, coincides with the route for the general public. The accessible route must have a minimum clear width of 36 inches, or a minimum clear width of 42 inches if there is a turn around an obstruction less than 48 inches wide; have passing spaces at least 60 inches by 60 inches at least every 200 feet; have a minimum clear headroom of 80 inches; have a surface that is firm, stable, and slip resistant; have, in the absence of a curb ramp, ramp, elevator, or platform lift, no level changes in excess of ½ inch vertically; and have a running slope of less than 1:20 (5%) (or have been constructed as a fully accessible ramp) and a cross slope of less than 1:50 (2%). Standards §§ 4.3, 4.5, Fig. 7.
c. The rear entrance door is inaccessible because there is a 1 inch change in level at the threshold to the door. Provide an accessible door with a threshold that is no greater than ¼ inch, or is no greater than ½ inch and is beveled with a slope no greater than 1:2. Standards §§ 4.13.8, 4.5.2.
a. Although 1 drinking fountain is provided, there is no accessible drinking fountain because a person using a wheelchair could not use a front approach and it is not accessible for people who have trouble bending or stooping. Provide at least one drinking fountain with a spout height no higher than 36 inches, measured from the finished floor or ground surface to the spout outlet; and a spout located at the front of the unit that directs the water flow in a trajectory that is nearly parallel to the front of the unit and is positioned so the flow of water is within 3 inches of the front edge of the fountain and at least 4 inches high. Ensure that fountain controls are operable with one hand, require 5 lbf or less to operate without tight grasping, pinching, or twisting of the wrist; and are front mounted or side mounted near the front edge. For each accessible drinking fountain, provide a drinking fountain that is accessible to people who have difficulty bending or stooping. This can be accommodated by the use of a "hi-lo" fountain; by providing one fountain accessible to those who use wheelchairs and one fountain at a standard height convenient for those who have difficulty bending; by providing a fountain accessible to people who use wheelchairs and a cup dispenser; or by such other means as would achieve the required accessibility for each group of people. Standards §§ 4.15, 4.27.4, Fig. 27.
a. Although there are public telephones provided, a TTY is not provided. Provide at least one accessible public TTY with appropriate signage. Standards §§ 4.30.7(3), 4.31.9.
b. The telephone is inaccessible because the highest operable part is mounted 56 inches above the floor and there is not adequate knee space provided. Provide an accessible telephone with a clear floor space of at least 30 inches by 48 inches that allows either a forward or parallel approach by a person using a wheelchair such that bases, enclosures, and fixed seats do not impede approaches to the telephone; with the highest operable part of the telephone mounted no more than 48 inches above the floor for a front approach or no more than 54 inches above the floor for a side approach; that are hearing aid compatible and have a volume control mechanism; with telephone books, if provided, located between 15 and 48 inches above the finished floor for a front approach or between 9 and 54 inches above the finished floor for a side approach; and with a cord of at least 29 inches long from the telephone to the handset. Standards § 4.31.
18. MEN'S TOILET ROOM ACROSS FROM RECEPTIONIST DESK
a. The toilet room sign is inaccessible. Provide a toilet room sign with the International Symbol of Accessibility and raised and Braille characters. The sign shall be mounted on the wall adjacent to the latch side of the door with the centerline of the sign at 60 inches above the finished floor and situated such that a person can approach within 3 inches of the sign without encountering an obstruction or standing within a door swing. Standards §§ 4.1.2(7)(d), 4.30.1, 4.30.4, 4.30.5, 4.30.6, 4.30.7.
c. Although an audible alarm is provided in this facility, there is no visual alarm appliance in the toilet room. Provide a visual alarm appliance in the toilet room. Standards §§ 4.28.1, 4.28.3.
e. The urinal is inaccessible because it is not low or elongated. Provide a urinal with an elongated rim mounted 17 inches or less above the finished floor, a clear floor space of at least 30 inches wide and 48 inches deep centered on the urinal, and a flush control height of 44 inches or less above the finished floor. Standards §§ 4.18.2, 4.18.3, 4.18.4.
f. The lavatory is inaccessible. Provide a lavatory with the top of its rim or counter 34 inches or less above the finished floor; the bottom edge of the apron at least 29 inches above the finished floor; knee and toe clearances that comply with Fig. 31; hot water and drain pipes covered or otherwise configured to protect against contact; clear floor space at least 30 inches wide and 48 inches deep centered on the lavatory; and a faucet that can be operated with 5 pounds of force or less and can be used with one hand and without tight grasping, pinching, or twisting of the wrist (lever-operated, push-type, and electronically controlled mechanisms are examples of acceptable designs). Standards §§ 4.19.2, 4.19.3, 4.19.4, 4.19.5, 4.27.4, Figs. 31, 32.
g. There is no accessible stall provided. Provide a "standard" accessible toilet stall at least 60 inches wide and at least 59 inches deep (or at least 56 inches deep with a wall-mounted toilet) such that all of the stall's elements, including stall door, stall door hardware, water closet, size and arrangement, toe clearances, grab bars, controls, and dispensers, comply with the Standards. Standards §§ 4.13, 4.16, 4.17, 4.26, 4.27, Fig. 30.
b. The toilet room door is inaccessible because the pressure required to open the door is in excess of 5 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards § 4.13.11(2)(b).
c. The lavatory is inaccessible. Provide a lavatory with the top of its rim or counter 34 inches or less above the finished floor; the bottom edge of the apron at least 29 inches above the finished floor; knee and toe clearances that comply with Fig. 31; hot water and drain pipes covered or otherwise configured to protect against contact; clear floor space at least 30 inches wide and 48 inches deep centered on the lavatory; and a faucet that can be operated with 5 pounds of force or less and can be used with one hand and without tight grasping, pinching, or twisting of the wrist (lever-operated, push-type, and electronically controlled mechanisms are examples of acceptable designs). Standards §§ 4.19.2, 4.19.3, 4.19.4, 4.19.5, 4.27.4, Figs. 31, 32.
d. There is no accessible stall provided. Provide a "standard" accessible toilet stall at least 60 inches wide and at least 59 inches deep (or at least 56 inches deep with a wall-mounted toilet) such that all of the stall's elements, including stall door, stall door hardware, water closet, size and arrangement, toe clearances, grab bars, controls, and dispensers, comply with the Standards. Standards §§ 4.13, 4.16, 4.17, 4.26, 4.27, Fig. 30.
e. Although an audible alarm is provided in this facility, there is no visual alarm appliance in the toilet room. Provide a visual alarm appliance in the toilet room. Standards §§ 4.28.1, 4.28.3.
f. No accessible mirror has been provided. Provide a mirror with the bottom edge of its reflecting surface no more than 40 inches above the finished floor. Standards § 4.19.6.
20. MEN'S TOILET ROOM IN AUDITORIUM
b. The toilet room door is inaccessible because the pressure required to open the door is 14 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards § 4.13.11(2)(b).
c. There is insufficient turning space within the toilet room. Provide an unobstructed turning space at least 60 inches in diameter or a T-shaped space complying with Fig. 3(b). Standards §§ 4.22.3, 4.2.3, Fig. 3.
d. Although an audible alarm is provided in this facility, there is no visual alarm appliance in the toilet room. Provide a visual alarm appliance in the toilet room. Standards §§ 4.28.1, 4.28.3.
e. The paper towel dispenser is inaccessible because the controls are mounted at 50 inches above the finished floor. Provide a paper towel dispenser with the controls a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
g. The lavatory is inaccessible because the faucet requires 10 pounds of force to operate. Provide a lavatory with a faucet that can be operated with 5 pounds of force or less and can be used with one hand and without tight grasping, pinching, or twisting of the wrist (lever-operated, push-type, and electronically controlled mechanisms are examples of acceptable designs). Standards §§ 4.19.5, 4.27.4.
h. There is no accessible stall provided. Provide a "standard" accessible toilet stall at least 60 inches wide and at least 59 inches deep (or at least 56 inches deep with a wall-mounted toilet) such that all of the stall's elements, including stall door, stall door hardware, water closet, size and arrangement, toe clearances, grab bars, controls, and dispensers, comply with the Standards. Standards §§ 4.13, 4.16, 4.17, 4.26, 4.27, Fig. 30.
21. WOMEN'S TOILET ROOM IN AUDITORIUM
b. The toilet room door is inaccessible because the pressure required to open the door is 8 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards § 4.13.11(2)(b).
d. The door to the toilet room, which is accessed from the latch side of the door, is inaccessible because it lacks maneuvering clearance. On the pull side of the door, provide a path of travel at least 48 inches wide for a side approach and at least 24 inches of clear maneuvering space adjacent to the latch side of the door. Standards § 4.13.6, Fig. 25(c).
e. The designated accessible toilet stall is inaccessible because there is not adequate space on the pull side of the door. Provide a toilet stall that is at least 60 inches wide and at least 56 inches deep for a wall-mounted toilet or at least 59 inches deep for a floor-mounted toilet, such that the centerline of the toilet is exactly 18 inches from the near side wall or partition, and there is at least 9 inches of toe clearance above the floor at the front partition if the stall is no more than 60 inches deep. Standards § 4.17, Fig. 30.
f. Although an audible alarm is provided in this facility, there is no visual alarm appliance in the toilet room. Provide a visual alarm appliance in the toilet room. Standards §§ 4.28.1, 4.28.3.
g. No accessible mirror has been provided. Provide a mirror with the bottom edge of its reflecting surface no more than 40 inches above the finished floor. Standards § 4.19.6.
h. The paper towel dispenser is inaccessible because the controls are mounted at 50 inches above the finished floor . Provide a paper towel dispenser with the controls a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
j. The lavatory is inaccessible because the faucet hardware requires turning. Provide a lavatory with a faucet that can be operated with 5 pounds of force or less and can be used with one hand and without tight grasping, pinching, or twisting of the wrist (lever-operated, push-type, and electronically controlled mechanisms are examples of acceptable designs). Standards §§ 4.19.5, 4.27.4.
k. There is no accessible stall provided. Provide a "standard" accessible toilet stall at least 60 inches wide and at least 59 inches deep (or at least 56 inches deep with a wall-mounted toilet) such that all of the stall's elements, including stall door, stall door hardware, water closet, size and arrangement, toe clearances, grab bars, controls, and dispensers, comply with the Standards. Standards §§ 4.13, 4.16, 4.17, 4.26, 4.27, Fig. 30.
22. WEIGHT ROOM
a. The weight room door is inaccessible because knob hardware is used. Provide a door with hardware that is easy to grasp with one hand and that does not require tight grasping, pinching, or twisting of the wrist to operate. Lever-operated mechanisms, push-type mechanisms, and U-shaped handles are acceptable designs. Standards § 4.13.9.
b. The weight room door is inaccessible because the pressure required to open the door is 10 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards § 4.13.11(2)(b).
c. There is no accessible route throughout the weight room. Provide at least one accessible route within the boundary of the site connecting these elements that, to the maximum extent feasible, coincides with the route for the general public. The accessible route must have a minimum clear width of 36 inches, or a minimum clear width of 42 inches if there is a turn around an obstruction less than 48 inches wide; have passing spaces at least 60 inches by 60 inches at least every 200 feet; have a minimum clear headroom of 80 inches; have a surface that is firm, stable, and slip resistant; have, in the absence of a curb ramp, ramp, elevator, or platform lift, no level changes in excess of ½ inch vertically; and have a running slope of less than 1:20 (5%) (or have been constructed as a fully accessible ramp) and a cross slope of less than 1:50 (2%). Standards §§ 4.3, 4.5, Fig. 7.
23. COMPUTER ROOM
a. The computer room door is inaccessible because the pressure required to open the door is 14 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards § 4.13.11(2)(b).
b. The computer tables are inaccessible because they lack clear floor space under the tables. Provide a computer on a table or counter that has clear floor space that is 30 inches wide and 48 inches deep, knee clearance at least 27 inches high, 30 inches wide, and 19 inches deep, and a writing surface between 28 and 34 inches above the finished floor. Standards §§ 4.2.4.1, 4.32.
c. There is no accessible signage provided. Provide permanent room signage with upper case, sans serif or simple serif type letters and numerals, meeting the requirements of the Standards for character height, raised characters, finish and contrast, accompanied by Grade 2 Braille and the International Symbol of Accessibility; mounted on the wall adjacent to the latch side of the door or on the nearest adjacent wall at a height of 60 inches above the finished floor to the centerline of the sign; and located so that a person may approach within 3 inches of the signage without encountering protruding objects or standing within the swing of a door. Standards §§ 4.30.1, 4.30.4, 4.30.5, 4.30.6, 4.30.7.
24. MULTIPURPOSE ROOM
a. The multi purpose room door is inaccessible because knob hardware is used. Provide a door with hardware that is easy to grasp with one hand and that does not require tight grasping, pinching, or twisting of the wrist to operate. Lever-operated mechanisms, push-type mechanisms, and U-shaped handles are acceptable designs. Standards § 4.13.9.
b. The multi purpose room door is inaccessible because the pressure required to open the door is 15 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards § 4.13.11(2)(b).
c. The light switch is inaccessible because the controls are mounted 58 inches above the finished floor. Provide a light switch with the controls a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
d. The room is inaccessible because it lacks signage to the accessible entrance. Provide accessible, directional signage with the International Symbol of Accessibility at inaccessible entrances directing users to the accessible entrance, and provide accessible signage with the International Symbol of Accessibility at all permanent accessible entrances. Standards §§ 4.1.3(8)(d), 4.13, 4.30.
25. VENDING MACHINES/FIXED TABLES AND SEATING
a. The vending machine area is inaccessible because the quantity of accessible tables provided is fewer than 5% of the total number available to the general public. Provide at least one accessible table. Standards §§ 4.2.4.1, 4.32, 5.1.
a. The library door is inaccessible because the pressure required to open the door is 6 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards § 4.13.11(2)(b).
b. The signage provided is inaccessible. Provide permanent room signage with upper case, sans serif or simple serif type letters and numerals, meeting the requirements of the Standards for character height, raised characters, finish and contrast, accompanied by Grade 2 Braille; mounted on the wall adjacent to the latch side of the door or on the nearest adjacent wall at a height of 60 inches above the finished floor to the centerline of the sign; and located so that a person may approach within 3 inches of the signage without encountering protruding objects or standing within the swing of a door. Standards §§ 4.30.1, 4.30.4, 4.30.5, 4.30.6.
c. The check-out area is inaccessible because it is not at least 36 inches wide. Provide at least one accessible lane at each check out area such that the counter is on an accessible route at least 36 inches wide and it has a section at least 36 inches wide and no more than 36 inches above the finished floor. Standards §§ 8.3, 7.2(1).
d. The card catalog and magazine display is inaccessible. Provide a card catalog and magazine display with a minimum of 36 inches of clear width between units and with reach ranges of between 18 inches and 54 inches (maximum height of 48 inches is preferred) above the finished floor. Standards § 8.4, Fig. 55.
e. The book stacks are inaccessible because the space between stacks is not 36 inches. Provide at least 36 inches of clear width between all stacks and provide a clear width of 42 inches between stacks where possible. Standards § 8.5, Fig. 56.
f. The computer tables are inaccessible because they can not be used by a person in a wheelchair. Provide a computer on a table or counter that has clear floor space that is 30 inches wide and 48 inches deep, knee clearance at least 27 inches high, 30 inches wide, and 19 inches deep, and a writing surface between 28 and 34 inches above the finished floor. Standards §§ 4.2.4.1, 4.32.
g. Although the facility contains an emergency alarm system, the alarm system is inaccessible because it lacks visual alarms. Provide visual alarm devices in toilet rooms and any other general usage areas (e.g., meeting rooms), hallways, lobbies, and any other area for common use. Such devices shall be integrated into the facility alarm system and shall meet the requirements of the Standards for lamp type, color, pulse duration, intensity, and flash rate. Visual alarm appliances shall be placed 80 inches above the highest floor level within the space or 6 inches below the ceiling, whichever is lower. Visual alarm appliances shall be located such that no place in any room or space, including common corridors or hallways, required to have a visual alarm appliance shall be more than 50 feet from the signal. In large rooms and spaces exceeding 100 feet across, without obstructions 6 feet above the finished floor, devices may be placed around the perimeter, spaced a maximum of 100 feet apart, in lieu of suspending appliances from the ceiling. Standards § 4.28.3.
1115 West Church Road, Sterling
a. The parking reserved for persons with disabilities is inaccessible because the surface is gravel and unmarked. Provide designated accessible parking spaces and access aisles that are flat and level, with slopes and cross-slopes not exceeding 1:50 in all directions, with surfaces that are firm, stable, and slip-resistant. Standards §§ 4.3.6, 4.5.1, 4.6.3.
b. The parking lot is inaccessible because there are no access aisles. At each standard accessible space, provide an access aisle at least 60 inches wide. At each van accessible space, provide an access aisles at least 96 inches wide. Ensure that all access aisles are flat and level, with slopes and cross-slopes not exceeding 1:50 in all directions, and that their surfaces are firm, stable, and slip-resistant. Standards §§ 4.1.2(5), 4.6.3, Fig. 9.
c. The building is inaccessible because there is no signage directing persons with disabilities to the accessible entrance in the rear. Provide accessible, directional signage with the International Symbol of Accessibility at inaccessible entrances directing users to the accessible entrance, and provide accessible signage with the International Symbol of Accessibility at all permanent accessible entrances. Standards §§ 4.1.3(8)(d), 4.13, 4.30.
28. WALKWAY
a. The route from the sloped walkway to the building is inaccessible because there is a 3/4 inch lip at the bottom of the walkway. Provide at least one accessible route within the boundary of the site connecting these elements that, to the maximum extent feasible, coincides with the route for the general public. The accessible route must have a minimum clear width of 36 inches, or a minimum clear width of 42 inches if there is a turn around an obstruction less than 48 inches wide; have passing spaces at least 60 inches by 60 inches at least every 200 feet; have a minimum clear headroom of 80 inches; have a surface that is firm, stable, and slip resistant; have, in the absence of a curb ramp, ramp, elevator, or platform lift, no level changes in excess of ½ inch vertically; and have a running slope of less than 1:20 (5%) (or have been constructed as a fully accessible ramp) and a cross slope of less than 1:50 (2%). Standards §§ 4.3, 4.5, Fig. 7.
29. EXTERIOR ENTRANCE AND DOORS
a. The building is inaccessible because the doors lack signage indicating the accessible entrances. Provide accessible, directional signage with the International Symbol of Accessibility at inaccessible entrances directing users to the accessible entrance, and provide accessible signage with the International Symbol of Accessibility at all permanent accessible entrances. Standards §§ 4.1.3(8)(d), 4.13, 4.30.
30. INTERIOR DOORS AND ROUTE
a. The interior room doors are inaccessible because knob hardware is used. Provide a door with hardware that is easy to grasp with one hand and that does not require tight grasping, pinching, or twisting of the wrist to operate. Lever-operated mechanisms, push-type mechanisms, and U-shaped handles are acceptable designs. Standards § 4.13.9.
31. OUTDOOR AREAS
a. There is no accessible route from the sidewalk to the play area and picnic tables. Provide at least one accessible route within the boundary of the site connecting these elements that, to the maximum extent feasible, coincides with the route for the general public. The accessible route must have a minimum clear width of 36 inches, or a minimum clear width of 42 inches if there is a turn around an obstruction less than 48 inches wide; have passing spaces at least 60 inches by 60 inches at least every 200 feet; have a minimum clear headroom of 80 inches; have a surface that is firm, stable, and slip resistant; have, in the absence of a curb ramp, ramp, elevator, or platform lift, no level changes in excess of ½ inch vertically; and have a running slope of less than 1:20 (5%) (or have been constructed as a fully accessible ramp) and a cross slope of less than 1:50 (2%). Standards §§ 4.3, 4.5, Fig. 7.
b. There is no accessible route from parking to baseball fields or spectator seating. Provide at least one accessible route within the boundary of the site connecting these elements that, to the maximum extent feasible, coincides with the route for the general public. The accessible route must have a minimum clear width of 36 inches, or a minimum clear width of 42 inches if there is a turn around an obstruction less than 48 inches wide; have passing spaces at least 60 inches by 60 inches at least every 200 feet; have a minimum clear headroom of 80 inches; have a surface that is firm, stable, and slip resistant; have, in the absence of a curb ramp, ramp, elevator, or platform lift, no level changes in excess of ½ inch vertically; and have a running slope of less than 1:20 (5%) (or have been constructed as a fully accessible ramp) and a cross slope of less than 1:50 (2%). Standards §§ 4.3, 4.5, Fig. 7.
c. The building is inaccessible because there is inadequate maneuvering space at the side entrance and no signage signage directing persons with disabilities to the accessible entrance. Provide accessible directional signage with the International Symbol of Accessibility at inaccessible entrances directing users to the accessible entrance, and provide accessible signage with the International Symbol of Accessibility at all permanent accessible entrances. Standards §§ 4.1.3(8)(d), 4.13, 4.30.
d. Although the parking lot has a total of 98 parking spaces, there is no accessible parking provided adjacent to the baseball field. On the shortest accessible route to the accessible entrance, provide at least 1 van accessible spaces and 3 standard spaces designated as reserved for people with disabilities. Ensure that standard accessible spaces are a minimum of 96 inches wide and served by access aisles at least 60 inches wide. Ensure that van accessible spaces are a minimum of 96 inches wide and served by access aisles at least 96 inches wide. At all spaces designated as reserved for persons with disabilities, provide vertical signs with the International Symbol of Accessibility located such that they cannot be obstructed by parked vehicles. At van accessible spaces, provide an additional "Van-Accessible" sign located below the International Symbol of Accessibility. Ensure that all spaces and access aisles for persons with disabilities are flat and level, with slopes and cross-slopes not exceeding 1:50 in all directions, and that their surfaces are firm, stable, and slip-resistant. Standards §§ 4.1.2(5), 4.6, 4.30.7(1).
e. The outdoor bleacher seating area is inaccessible because there is no wheelchair seating provided. Provide at least 1 wheelchair seating area, each with a minimum clear ground or floor space of 66 inches wide by 48 inches deep for forward or rear access, or 66 inches wide by 60 inches deep for side access. Ensure that the ground or floor at all wheelchair locations is level, firm, stable, and slip resistant; that wheelchair seating areas are an integral part of the fixed seating plan and are located so as to provide people with physical disabilities a choice of admission prices and lines of sight comparable to those available for members of the general public; that wheelchair seating areas adjoin an accessible route that also serves as a means of egress in case of emergency; and that at least one fixed companion seat is provided next to each wheelchair seating area. Standards §§ 4.1.3(19)(a), 4.5, 4.33.
a. The auditorium is inaccessible to people with hearing impairments because it lacks signage indicating the availability of an assisted listening system. Provide a permanently installed assistive listening system (ALS) or a portable ALS with an adequate number of electrical outlets or other supplementary wiring necessary to support a portable assistive listening system. Also provide (*number: 4% of total seats or a minimum of 2) receivers for use by the general public and signage indicating their availability. Standards §§ 4.30, 4.33.
b. The auditorium door is inaccessible because the pressure required to open the door is 6 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards § 4.13.11(2)(b).
c. The stage is inaccessible because it has steps to the performing area. Install a ramp or platform lift in compliance with the Standards or establish a procedure for providing access to this area. Any procedure shall not require lifting or carrying persons with mobility impairments or require them to traverse unnecessary or extreme distances. Standards §§ 4.3, 4.33.5.
d. The route through the auditorium is inaccessible because the counter protrudes 5 inches into the walkway. Provide an accessible route at this location such that no objects with their bottom leading edges measuring between 27 inches and 80 inches above the finished floor protrude more than 4 inches into walks, halls, corridors, passageways, or aisles. Free-standing objects mounted on posts or pylons may overhang 12 inches maximum from 27 inches to 80 inches above the ground or finished floor. Standards § 4.4.
33. DRINKING FOUNTAINS NEAR WOMEN'S TOILET ROOM
a. Although drinking fountains are provided, there is no accessible drinking fountain because the water flow is 5 inches back from the edge. Provide at least one drinking fountain with a spout height no higher than 36 inches, measured from the finished floor or ground surface to the spout outlet; and a spout located at the front of the unit that directs the water flow in a trajectory that is nearly parallel to the front of the unit and is positioned so the flow of water is within 3 inches of the front edge of the fountain and at least 4 inches high. Ensure that fountain controls are operable with one hand, require 5 lbf or less to operate without tight grasping, pinching, or twisting of the wrist; and are front mounted or side mounted near the front edge. For each accessible drinking fountain, provide a drinking fountain that is accessible to people who have difficulty bending or stooping. This can be accommodated by the use of a "hi-lo" fountain; by providing one fountain accessible to those who use wheelchairs and one fountain at a standard height convenient for those who have difficulty bending; by providing a fountain accessible to people who use wheelchairs and a cup dispenser; or by such other means as would achieve the required accessibility for each group of people. Standards §§ 4.15, 4.27.4, Fig. 27.
b. The wall-mounted drinking fountain at is inaccessible because the knee clearance is 10 inches and a person using a wheelchair could not approach from the front. Provide a drinking fountain with clear knee space between the bottom of the apron and the finished floor or ground of at least 27 inches high, 30 inches wide, and 17 to 19 inches deep; and a minimum clear floor space of 30 inches by 48 inches to allow a person in a wheelchair to approach the unit facing forward. Standards § 4.15.5(1), Figs. 27(a), (b).
a. The telephone is inaccessible because the coin slot is mounted 55 inches above the finished floor. Provide an accessible telephone with a clear floor space of at least 30 inches by 48 inches that allows either a forward or parallel approach by a person using a wheelchair such that bases, enclosures, and fixed seats do not impede approaches to the telephone; with the highest operable part of the telephone mounted no more than 48 inches above the floor for a front approach or no more than 54 inches above the floor for a side approach; that are hearing aid compatible and have a volume control mechanism; with telephone books, if provided, located between 15 and 48 inches above the finished floor for a front approach or between 9 and 54 inches above the finished floor for a side approach; and with a cord of at least 29 inches long from the telephone to the handset. Standards § 4.31.
b. Although there are public telephones provided, a TTY is not provided. Provide at least one accessible public TTY with appropriate signage. Standards §§ 4.30.7(3), 4.31.9.
35. WOMEN'S TOILET ROOM
a. The toilet room sign is not mounted on the latch side of the door or centered 60 inches above the finished floor. Provide a toilet room sign with the International Symbol of Accessibility and raised and Braille characters. The sign shall be mounted on the wall adjacent to the latch side of the door with the centerline of the sign 60 inches above the finished floor and situated such that a person can approach within 3 inches of the sign without encountering an obstruction or standing within a door swing. Standards §§ 4.1.2(7)(d), 4.30.1, 4.30.4, 4.30.5, 4.30.6, 4.30.7.
b. There is no accessible stall provided. Provide a "standard" accessible toilet stall at least 60 inches wide and at least 59 inches deep (or at least 56 inches deep with a wall-mounted toilet) such that all of the stall's elements, including stall door, stall door hardware, water closet, size and arrangement, toe clearances, grab bars, controls, and dispensers, comply with the Standards. Standards §§ 4.13, 4.16, 4.17, 4.26, 4.27, Fig. 30.
c. The lavatory is inaccessible because there are support posts in front of the lavatory. Provide a lavatory with the top of its rim or counter 34 inches or less above the finished floor; the bottom edge of the apron at least 29 inches above the finished floor; and knee and toe clearances that comply with Fig. 31. Standards § 4.19.2, Fig. 31.
36. MEN'S TOILET ROOM
a. The light switch is inaccessible because the controls are mounted more than 54 inches above the finished floor. Provide a light switch with the controls a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
b. The lavatory is inaccessible because the faucet hardware requires twisting. Provide a lavatory with a faucet that can be operated with 5 pounds of force or less and can be used with one hand and without tight grasping, pinching, or twisting of the wrist (lever-operated, push-type, and electronically controlled mechanisms are examples of acceptable designs). Standards §§ 4.19.5, 4.27.4.
c. The urinal is inaccessible because the flush control is mounted more than 44 inches above the finished floor. Provide a urinal with an elongated rim mounted 17 inches or less above the finished floor, a clear floor space of at least 30 inches wide and 48 inches deep centered on the urinal, and a flush control height of 44 inches or less above the finished floor. Standards §§ 4.18.2, 4.18.3, 4.18.4.