Source: https://www.law.cornell.edu/cfr/text/47/15.611
Timestamp: 2017-06-27 19:26:15
Document Index: 383279910

Matched Legal Cases: ['art 15', '§ 15', '§ 15', '§ 15', '§ 15', '§ 15']

47 CFR 15.611 - General technical requirements. | US Law | LII / Legal Information Institute
CFR › Title 47 › Chapter I › Subchapter A › Part 15 › Subpart G › Section 15.611 47 CFR 15.611 - General technical requirements.
§ 15.611 General technical requirements.
(a)Conducted emission limits. Access BPL is not subject to the conducted emission limits of § 15.107.
(b)Radiated emission limits - (1)Medium voltage power lines.
(i) Access BPL systems that operate in the frequency range of 1.705 kHz to 30 MHz over medium voltage power lines shall comply with the radiated emission limits for intentional radiators provided in § 15.209.
(ii) Access BPL systems that operate in the frequency range above 30 MHz over medium voltage power lines shall comply with the radiated emission limits provided in § 15.109(b).
(2)Low voltage power lines. Access BPL systems that operate over low-voltage power lines, including those that operate over low-voltage lines that are connected to the in-building wiring, shall comply with the radiated emission limits provided in § 15.109(a) and (e).
(c)Interference Mitigation and Avoidance.
(1) Access BPL systems shall incorporate adaptive interference mitigation techniques to remotely reduce power and adjust operating frequencies, in order to avoid site-specific, local use of the same spectrum by licensed services. These techniques may include adaptive or “notch” filtering, or complete avoidance of frequencies, or bands of frequencies, locally used by licensed radio operations.
[ 70 FR 1374, Jan. 7, 2005, as amended at 71 FR 49379, Aug. 23, 2006; 76 FR 71908, Nov. 21, 2011]