Source: https://www.townhall.virginia.gov/l/ViewXML.cfm?textid=8904
Timestamp: 2019-11-19 02:46:47
Document Index: 686557327

Matched Legal Cases: ['art 1910', 'art 1926', 'art 1910', '§1910', '§1910', '§1910', '§1910', '§1910', '§1910', '§1910', '§1910', '§1910', 'art\n16', 'art 1926']

Electric Power Generation, Transmission, and Distribution and ...
7/14/14 10:58 AM [latest] 7/1/14 4:29 PM
At end, move this text up to the Title of Regulation section, and delete everything else, including Chapter 155 since the entire chapter is repealed.
Titles of Regulations: 16VAC25-90. Federal Identical General Industry Standards (amending 16VAC25-90-1910.136, 16VAC25-90-1910.137, Appendix B to Subpart I of Part 1910, 16VAC25-90-1910.269, Appendices A through D to 16VAC25-90-1910.269, 16VAC25-90-1910.331, 16VAC25-90-1910.339; adding Appendices E through G to 16VAC25-90-1910.269).
16VAC25-155. Virginia Construction Industry General Requirements for Clearances, Construction of Electric Transmission and Distribution Lines and Equipment (repealing 16VAC25-155-10).
16VAC25-175. Federal Identical Construction Industry Standards (amending 16VAC25-175-1926.500, 16VAC25-175-1926.950, 16VAC25-175-1926.951, 16VAC25-175-1926.952, 16VAC25-175-1926.953, 16VAC25-175-1926.954, 16VAC25-175-1926.955, 16VAC25-175-1926.956, 16VAC25-175-1926.957, 16VAC25-175-1926.958, 16VAC25-175-1926.959, 16VAC25-175-1926.960, 16VAC25-175-1926.961, 16VAC25-175-1926.962, 16VAC25-175-1926.963, 16VAC25-175-1926.964, 16VAC25-175-1926.965, 16VAC25-175-1926.966, 16VAC25-175-1926.967, 16VAC25-175-1926.968, 16VAC25-175-1926.1053, 16VAC25-175-1926.1400, 16VAC25-175-1926.1410; adding 16VAC25-175-1926.97, Appendices A through G to Subpart V of Part 1926).
amend 16VAC25-90-1910.136, Foot Protection
amend 16VAC25-90-1910.137, Electrical Protective Equipment
amend Appendix B to Subpart I of Part 1910  Nonmandatory Compliance Guidelines for Hazard Assessment and Personal Protective Equipment Selection
Subpart R  Special Industries
amend 16VAC25-90-1910.269, Electric Power Generation, Transmission, and Distribution
amend the following appendices to §1910.269:
Appendix A - Flow Charts
Appendix A-1 - Application of §1910.269 and Subpart S of this Part to the Design of Electrical Installations
Appendix A-2 - Application of §1910.269 and Subpart S of this Part to Electrical Safety-Related Work Practices
Appendix A-3 - Application of §1910.269 and Subpart S of this Part to Tree-Trimming Operations
Appendix A-4 to §1910.269  Application of §§1910.147, 1910.269 and 1910.333
Appendix A-5 to §1910.269  Application of §§1910.146 and 1910.269 to Permit-Required Confined Spaces
Appendix B  Working on Exposed Energized Parts
Appendix C  Protection From Hazardous Differences in Electric Potential
Appendix D  Methods of Inspecting and Testing Wood Poles
add the following appendices to §1910.269:
Appendix E  Protection From Flames and Electric Arcs
Appendix F  Work-Positioning Equipment Inspection Guidelines
Appendix G  Reference Documents
Subpart S  Electrical
amend 16VAC25-90-1910.331(c)(1), Scope
amend 16VAC25-90-1910.339, Definitions Applicable to this Subpart
16VAC25-155
VIRGINIA CONSTRUCTION INDUSTRY GENERAL REQUIREMENTS FOR CLEARANCES, CONSTRUCTION OF ELECTRIC TRANSMISSION AND DISTRIBUTION LINES AND EQUIPMENT (REPEALED)
16VAC25-155-10
16VAC25-155-10. General requirements. (Repealed.)
A. No employee shall be permitted to approach or take any conductive object without an approved insulating handle closer to exposed energized parts than shown in subsection B of this section (Table V-1) unless:
1. The employee is insulated or guarded from the energized part (insulating gloves or insulating gloves and sleeves worn in accordance with 16VAC25-90-1910.269 (l)(3) are considered insulation of the employee only with regard to the energized part upon which work is being performed);
3. The employee is isolated, insulated, or guarded from any other exposed conductive object(s), as during live-line bare-hand work.
B. Alternating current -- minimum distance.
ALTERNATING CURRENT -- MINIMUM DISTANCES
(1) 7 ft. 0 in.
500 to 552
(1) 11 ft. 0 in.
700 to 765
(1) 15 ft. 0 in.
(1) NOTE: For 345-362 kv., 500-552 kv., and 700-765 kv., minimum clear hot stick distance may be reduced provided that such distances are not less than the shortest distance between the energized part and the grounded surface.
16VAC25-175
Subpart E- Personal Protective and Life Saving Equipment
add 16VAC25-175-1926.97, Electrical Protective Equipment
amend 16VAC25-175-1926.500, Scope, Application, and Definitions Applicable to this Subpart
Subpart V  Electric Power Transmission and Distribution
amend 16VAC25-175-1926.950, General
amend 16VAC25-175-1926.951, Medical Services and First Aid
amend 16VAC25-175-1926.952, Job Briefing
amend 16VAC25-175-1926.953, Enclosed Spaces
amend 16VAC25-175-1926.954, Personal Protective Equipment
amend 16VAC25-175-1926.955, Portable Ladders and Platforms
amend 16VAC25-175-1926.956, Hand and Portable Power Equipment
amend 16VAC25-175-1926.957, Live-line tools
amend 16VAC25-175-1926.958, Materials Handling and Storage
amend 16VAC25-175-1926.959, Mechanical Equipment
amend 16VAC25-175-1926.960, Working on or near Exposed Energized Parts
amend 16VAC25-175-1926.961, Deenergizing lines and Equipment for Employee Protection
amend 16VAC25-175-1926.962, Grounding for the Protection of Employees
amend 16VAC25-175-1926.963, Testing and Test Facilities
amend 16VAC25-175-1926.964, Overhead Lines and Live-line Barehand Work
amend 16VAC25-175-1926.965, Underground Electrical Installations
amend 16VAC25-175-1926.966, Substations
amend 16VAC25-175-1926.967, Special Conditions
amend 16VAC25-175-1926.968, Definitions
add Appendices to Subpart V of Part 1926:
Appendix A -Reserved
Appendix B -Working on Exposed Energized Parts
Appendix C -Protection From Hazardous Differences in Electric Potential
Appendix D -Methods of Inspecting and Testing Wood Poles
Appendix E - Protection From Flames and Electric Arcs
Appendix F Work-Positioning Equipment Inspection Guidelines
Subpart X  Stairways and Ladders
amend 16VAC25-175-1926.1053(b)(12), Ladders
Subpart CC  Cranes and Derricks in Construction
amend 16VAC25-175-1926.1400(g), Scope
amend 16VAC25-175-1926.1410, Power Line Safety (All Voltages) Equipment Operations Closer than the Table A Zone