Source: http://docplayer.net/1618035-Section-16721-fire-alarm-and-smoke-detection-systems.html
Timestamp: 2017-01-20 08:29:04
Document Index: 228098130

Matched Legal Cases: ['ART 1', 'ART 2', 'ART 3', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1']

⭐SECTION FIRE ALARM AND SMOKE DETECTION SYSTEMS
Download "SECTION 16721 FIRE ALARM AND SMOKE DETECTION SYSTEMS"
1 SECTION PART 1 - GENERAL 1.1 SECTION INCLUDES A. Fire Alarm Control Panels B. Manual Fire Alarm Stations C. Automatic Smoke D. Fire Alarm Notification Appliances E. Auxiliary Fire Alarm Equipment 1.2 RELATED DOCUMENTS A. Drawings, general and special conditions, Division 1 - General Requirements and other applicable technical specifications apply to work of this Section. 1.3 RELATED SECTIONS A. Section Sprinkler Systems. B. Section Ductwork Accessories: Smoke dampers. C. Section Electrical Identification. 1.4 REFERENCES A. NFPA 70 - National Electrical Code. B. NFPA 72 - National Fire Code. C. NFPA Life Safety Code. D Florida Building and Fire Codes. E. UL-864 and other applicable standards. F. Complete Fire Protection System; UL listed. G. Conform to requirements of NFPA applicable sections. H. The American Disabilities Act (ADA). Tampa, Florida2 1.5 SYSTEM DESCRIPTION A. Fire Alarm System: NFPA 72, automatic fire alarm system with connections to central station. 1.6 SUBMITTALS A. Submit four (4) sets of fire Alarm shop drawings, product data, voltage drop calculations, and battery calculations to Intergroup Architects prior to installation. B. Shop Drawings: Provide annunciator layout and system wiring diagram showing each device and wiring connection required. C. Product Data: Provide electrical characteristics and connection requirements. D. Test Reports: Indicate satisfactory completion of required tests and inspections. E. Manufacturer's Installation Instructions: Indicate application conditions and limitations of use stipulated by Product testing agency. Include instructions for storage, handling, protection, examination, preparation, installation, and starting of products. 1.7 PROJECT RECORD DOCUMENTS A. Submit four (4) sets of record drawings (incorporate field changes) to Architect. B. Record actual locations of initiating devices, notificaiton appliances, and end-of-line devices. 1.8 OPERATION AND MAINTENANCE DATA A. Submit four (4) sets of ) O&M manuals. B. Operation Data: Operating instructions. C. Maintenance Data: Maintenance and repair procedures. 1.9 QUALIFICATIONS A. Manufacturer: Company specializing in manufacturing the products specified in this section with minimum three years experience, and with service facilities within 25 or 50 miles of Project. B. Installer: Company specializing in installing the products specified in this section with minimum three years documented experience, and certified by State of Florida as fire alarm installer. Tampa, Florida3 1.10 REGULATORY REQUIREMENTS A. Conform to requirements of NFPA 70, 72, and NFPA 101. B. Furnish products listed and classified by UL or agency acceptable to authority having jurisdiction as suitable for purpose specified and indicated MAINTENANCE SERVICE A. Furnish service and maintenance of fire alarm system for one year from Date of Substantial Completion EXTRA MATERIALS A. Notification 10% of each type of device, minimum three of each type. PART 2 - PRODUCTS 2.0 GENERAL A. All equipment and materials used shall be standard components, regularly manufactured, and regularly utilized in the manufacturer's system. B. All systems and components shall have been thoroughly tested and proven in actual use. C. All equipment shall be listed and labeled by Underwriters Laboratories. D. All sensors shall be of the intelligent type where possible. All sensors intelligent shall mount on a common base. E. Where equipment of different manufacturers is used, such equipment shall be included under the required overall UL system listing as a component of the integrated fire alarm system. F. The system shall be designed to operate with the unshielded wire, to the maximum practicable extent. 2.1 MANUFACTURERS A. Subject to compliance with specified requirements, products of the following manufacturers are acceptable: 1. Edwards (EST) Notifier Simplex or approved. 2.2 FIRE ALARM AND SMOKE DETECTION CONTROL PANEL A. Control Panel: Modular construction with surface wall-mounted enclosure. Tampa, Florida4 B. Power supply: Adequate to serve control panel modules, remote detectors, remote annunciators, relays, and alarm signaling devices. Include battery-operated emergency power supply with capacity for operating system in standby mode for 24 hours followed by alarm mode for 5 minutes. C. System Supervision: Component or power supply failure places system in trouble mode. D. Initiating Device Circuits: Supervised zone module with alarm and trouble indication; occurrence of single ground or open condition places circuit in trouble mode but does not disable that circuit from initiating an alarm. E. Notification Appliance Circuits: Supervised temperate three signal module, sufficient for notification appliances connected to system; occurrence of single ground or open condition places circuit in trouble mode. F. Remote Station Signal Transmitter: Electrically supervised digital alarm communicator transmitter, capable of transmitting alarm and trouble signals over telephone lines to central station receiver. G. Trouble Sequence of Operation: System or circuit trouble places system in trouble mode, which causes the following system operations: 1. Visual and audible trouble alarm indicated at fire alarm control panel. 2. Visual and audible trouble alarm indicated at remote annunciator panel. 3. Trouble signal transmitted to central station. 4. Manual acknowledge function at fire alarm control panel silences audible trouble alarm; visual alarm is displayed until initiating failure or circuit trouble is cleared. H. Alarm Sequence of Operation: Actuation of initiating device places circuit in alarm mode, which causes the following system operations: 1. Sound and display local fire alarm notification appliances with temperate three signal. 2. Transmit signal to central station. 3. Indicate location of alarm on fire alarm control panel and on remote annunciator panel. 4. Shutdown the fans. 5. Transmit signal to release developed egress doors. I. Alarm Reset: System remains in alarm mode until manually reset with key-accessible Tampa, Florida5 reset function; system resets only if initiating circuits are out of alarm mode. 2.3 INITIATING DEVICES A. General: 1. Each device shall be assigned a unique address. Address selection by jumpers is not acceptable. 2. Devices shall receive power and communication from the same pair of wires. For fault-tolerant circuits, any separate power wiring shall also be made faulttolerant. 3. Each device shall contain screw terminals with rising plates for positive termination of up to #14 AWG wire. B. Manual Station: Surface mounted, non-coded type, double action manual station with break-glass rod. Provide manufacturer's standard backbox. C. Duct Mounted Smoke Detector: Photoelectric type with auxiliary SPDT relay contact, key-operated NORMAL-RESET-EST switch, duct sampling tubes extending width of duct, and visual indication of detector actuation, in duct-mounted housing. 2.4 NOTIFICATION APPLIANCES A. Visible Appliance: Stobe lamp and flasher with red & white lettered "FIRE" on bezel and clear. B. Audio Appliance: 1. Horn: Surface or flush alarm horn. Sound Rating: 87 Db at 10 feet. Provide integral strobe lamp and flasher with red lettered "FIRE" on clear lens. C. Remote Annunciator: Provide supervised remote annunciator including audible and visual indication of fire alarm by zone, and audible and visual indication of system trouble. Install in flush wall-mounted enclosure. 2.5 AUXILIARY DEVICES A. Monitor Modules: 1. The Monitor Mudule shall provide an addressable input for N.O. or N.C. contact devices such as manual stations, water flow switches, sprinkler supervisory devices, door contacts, intrusion detectors, etc. 2. The Monitor Module shall provide a supervised initiating circuit. An opencircuit fault shall be annunciated at the FACP. Tampa, Florida6 3. The Module shall mount in a standard electrical box. B. Controls Modules: 1. The Control Module shall provide an addressable output for a separatelypowered alarm-indicating circuit or for a control relay. 2. The Control Module shall provide a supervised indicating circuit where indicated on the drawings. An open-circuit fault shall be annunciated at the FACP. 3. The Control Module shall provide a control relay where indicated on the plans. The relay contacts shall be SPST (Form "C" rated at 2 amps at 28 VDC). 2.6 OTHER DEVICES 4. The module shall mount in a standard electrical box. A. Tamper Switches: Furnished by Sprinkler Contractor wired by Fire Alarm. B. Flow Switches: Furnished by Sprinkler Contractor wired by Fire Alarm. C. Provide addressable control and/or monitor module for each device indicated in paragraphs A & B above. Include wiring to the device and to the fire alarm loop as required. D. Provide control relays as required to accomplish functions such as fan shutdown, door release, etc. Relays shall have 24 VDC coils, with DPDT contacts rated at 10A, minimum, at 120 VAC, shall be provided with screw terminals, and shall be UL listed as fire alarm control accessories. Relay enclosures shall provide conduit knockouts at top and bottom, and shall have manufacturer's standard finish. Control relays shall be installed near the associated fire alarm system control modules. 2.7 FIRE ALARM WIRE AND CABLE A. Fire Alarm Power Branch Circuits: Building wire as specified in Section B. Initiating Device and Notification Appliance Circuits: As specified by the equipment manufacturer PART 3 - EXECUTION 3.1 INSTALLATION A. Install products in accordance with manufacturer's instructions. B. Mount end-of-line device box with last device or separate box adjacent to last device in Tampa, Florida7 circuit. C. Mount outlet box for electric door holder to withstand 80 pounds pulling force. D. Make conduit and wiring connections to door release devices, sprinkler flow switches, sprinkler valve tamper switches, duct smoke detectors. E. Automatic Detector Installation: Conform to NFPA FIELD QUALITY CONTROL A. Test in accordance with NFPA 72 and local fire department requirements. 3.3 MANUFACTURER'S FIELD SERVICES A. Prepare and start systems. B. Include services of certified technician to supervise installation, adjustments, final connections, and system testing. 3.4 DEMONSTRATION A. Demonstrate normal and abnormal modes of operation, and required responses to each. END OF SECTION Tampa, Florida8 NW-7938A!" # $ DATE FA NORTH 26TH STREET TAMPA, FLORIDA 2009 COLO, LLC, and its affiliates. All rights reserved. The drawings and structure depicted herein are proprietary to Furniture Row COLO, LLC and its affiliates. No part may be used or reproduced without prior written permission. Copyright % FURNITURE ROW9 FA-02 DATE FURNITURE ROW 815 NORTH 26TH STREET TAMPA, FLORIDA 2009 COLO, LLC, and its affiliates. All rights reserved. The drawings and structure depicted herein are proprietary to Furniture Row COLO, LLC and its affiliates. No part may be used or reproduced without prior written permission. Copyright %!"#$ NW-7938A Similar documents
FLORIDA ATLANTIC UNIVERSITY FIRE ALARM SYSTEM INSTALLATION MANUAL January, 2003 Environmental Health and Safety Florida Atlantic University 777 Glades Rd. Boca Raton, FL 33431 Phone: 561-297-3129 Fax: More information SECTION 16721 FIRE ALARM AND DETECTION SYSTEM
Polk School District Specifications for the New Fire Alarm in the Existing Building Eastside Elementary School FIRE ALARM SYSTEM 1.01 SUBMITTALS A. Shop drawings shall be submitted as follows: 1. Manufacturer's More information SECTION 16853 ZONED (DC LOOP) FIREALARM SYSTEM
SECTION 16853 ZONED (DC LOOP) FIRE-ALARM SYSTEM PART 1 - GENERAL 1.1 RELATED DOCUMENTS A. Drawings and general provisions of the Contract, including General and Supplementary Conditions and Division 1 More information Design and Construction Standards SECTION 16720 FIRE ALARM AND SMOKE DETECTION SYSTEMS
SECTION 16720 FIRE ALARM AND SMOKE DETECTION SYSTEMS PART 1 GENERAL 1.1 SECTION INCLUDES: A. Fire alarm and smoke detection systems. 1.2 REFERENCES 1.3 NFPA 72 1.4 NFPA 101 1.5 REGULATORY REQUIREMENTS More information C. Conform to requirements of Americans with Disabilities Act (ADA).
SECTION 16721 FIRE ALARM AND DETECTION SYSTEM PART 1 - GENERAL 1.1 RELATED DOCUMENTS: A. Drawings and general provisions of Contract, including General and Supplementary Conditions and Division-1 Specification More information FVSU-33201301 REPAIR & UPGRADE FIBER OPTIC 280000-1 SECTION 280000 FIRE ALARM SYSTEM CONNECTIVITY
FVSU-33201301 REPAIR & UPGRADE FIBER OPTIC 280000-1 SECTION 280000 FIRE ALARM SYSTEM CONNECTIVITY PART 1 - GENERAL 1.1 SUMMARY A. Section Includes: 1. Fire-alarm control unit. 2. Addressable interface More information Module 4, Lesson 12 Fire Alarm Systems
Student Manual Module 4, Lesson 12 Fire Alarm Systems Performance Objectives At the conclusion of this lesson, you will be able to: Identify the components and functions of a fire alarm system and determine More information FIRE ALARM SYSTEM RECORD OF COMPLETION
FUNDAMENTALS OF FIRE ALARM SYSTEMS 72 33 FIRE ALARM SYSTEM RECORD OF COMPLETION To be completed by the system installation contractor at the time of system acceptance and approval. 1. PROTECTED PROPERTY More information SECTION 28 31 11 FIRE ALARM AND DETECTION SYSTEM
KNOXVILLE, TENNESSEE SECTION 28 31 11 PAGE 1 PART 1 - GENERAL 1.01 DESCRIPTION OF WORK SECTION 28 31 11 A. Extent of fire alarm and detection system work shall be as described in this specification, as More information SECTION 16721 FIRE ALARM AND DETECTION SYSTEMS
NC State University Design and Construction Guidelines Division 26 Fire Alarm Systems 1.0 Purpose A. The following guideline provides the minimum standards and requirements for fire alarm systems. 2.0 More information FIRE ALARM SYSTEM RECORD OF COMPLETION
FIRE ALARM SYSTEM RECORD OF COMPLETION To be completed by the system installation contractor at the time of system acceptance and approval. 1. Protected Property Information Name of property: Description More information DELAWARE STATE FIRE MARSHAL FIRE ALARM SYSTEM CERTIFICATE OF INSTALLATION
Phone System Owner Phone System Engineered by: of Record Drawings: of System Manuals: of Test Reports: System Installer 1. GENERAL INFORMATION Phone Delaware License No: Certificate Holder No. System Supplier More information Fire Alarm System Plans Submittal Guidelines For New and Existing Systems
Fire Alarm System Plans Submittal Guidelines For New and Existing Systems SCOPE The Temecula Fire Prevention Bureau (TFPB) has established the following requirements for the submittal of all fire alarms, More information DTW Works Master Specification Version 2006
Issued 2006/08/01 Section 13852 Multiplex Fire Alarm System Page 1 of 10 PART 1 GENERAL 1.1 RELATED WORK.1 Section 01330 Submittal Procedures..2 Section 01780 Closeout Procedures..3 Section 01810 Commissioning..4 More information HERNANDO COUNTY FIRE ALARM GUIDELINES
HERNANDO COUNTY FIRE ALARM GUIDELINES To be used for all commercial building fire alarm system plan review. The procedures set forth in this document are the minimum requirements necessary to ensure a More information CLARK COUNTY FIRE DEPARTMENT Fire Hazard & Prevention Services
CLARK COUNTY FIRE DEPARTMENT Fire Hazard & Prevention Services 575 E. Flamingo Road, Las Vegas, NV 89119 (702) 455-7316 FAX (702) 455-7347 105.8a-6.1 TITLE: FIRE ALARM SYSTEM REQUIREMENTS SCOPE: This guideline More information PLAN REVIEW GUIDE FOR FIRE ALARM
PLAN REVIEW GUIDE FOR FIRE ALARM PROJECT NAME: PERMIT # PROJECT ADDRESS: CONTACT PERSON: PHONE Fire alarm system installation information shall be provided on the appropriate architectural and electrical More information SECTION 16721 FIRE DETECTION AND ALARM SYSTEM PART 1 - GENERAL 1.01 DESCRIPTION
SECTION 16721 FIRE DETECTION AND ALARM SYSTEM PART 1 - GENERAL 1.01 DESCRIPTION A. This section of the specifications includes the furnishing, installation, and connection of the microprocessor-controlled More information Bold items are particular to the City of Euless
EULESS FIRE DEPARTMENT FIRE MARSHAL S OFFICE INFORMATION LINE: Revised 2/12 Fire Chief Wes Rhodes Fire Marshal Paul Smith EFD-FMO 3-2 2009 International Fire & Building Code as Amended NFPA Standards Adopted More information HONEYWELL COMMERCIAL FIRE/BURG PANEL UL LISTING REQUIREMENTS (Compiled from VistaFBPT Installation Instructions 800-09617V1 Rev A 11/12)
HONEYWELL COMMERCIAL FIRE/BURG PANEL UL LISTING REQUIREMENTS (Compiled from VistaFBPT Installation Instructions 800-09617V1 Rev A 11/12) UL864 (Commercial Fire) Compliance General Requirements The VISTA-128FBPT/VISTA250FBPT More information SECTION 28 31 00 FIRE DETECTION AND ALARM SYSTEM
SECTION 28 31 00 FIRE DETECTION AND ALARM SYSTEM PART 1 - GENERAL 1.01 SECTION INCLUDES A. Fire alarm system requirements B. Fire alarm equipment C. Fire alarm peripheral devices 1.02 RELATED SECTIONS More information FIRE ALARM SYSTEMS PERMIT APPLICATION, PLAN SUBMITTAL, DESIGN, INSTALLATION AND INSPECTION REQUIREMENTS Effective Date: January, 2011
Office of the Fire Marshal 1.0 PERMITS FIRE ALARM SYSTEMS PERMIT APPLICATION, PLAN SUBMITTAL, DESIGN, INSTALLATION AND INSPECTION REQUIREMENTS Effective Date: January, 2011 1.1 To acquire an installation More information SECTION 13850 (28 31 00) FIRE DETECTION AND ALARM SYSTEM
SECTION 13850 (28 31 00) FIRE DETECTION AND ALARM SYSTEM ENGINEERING SPECIFICATION INTELLIGENT REPORTING FIRE DETECTION SYSTEM PART 1 GENERAL 1.1 DESCRIPTION A. This specification includes the furnishing, More information JULY 2013 UCB STANDARDS 16720-1
SECTION 16720 FIRE ALARM AND DETECTION SYSTEMS PART 1 GENERAL 1.01 Reference A. Related Sections 1. Section 15300 Fire Protection 2. Section 15950 Controls 3. Division 16 Electrical 4. Division 14 - Conveying More information CITY OF PHILADELPHIA DEPARTMENT OF LICENSES AND INSPECTIONS ANNUAL CERTIFICATION FOR FIRE ALARM SYSTEMS
CITY OF PHILADELPHIA DEPARTMENT OF LICENSES AND INSPECTIONS ANNUAL CERTIFICATION FOR FIRE ALARM SYSTEMS PROPERTY ADDRESS (BRT Address Required) TESTING CONTRACTOR (Name and Address) License No. ANNUAL More information FireSeeker Fire Alarm Control Panel Model FS-250 Programming Manual
FireSeeker Fire Alarm Control Panel Model FS-250 Programming Manual P/N 315-049403-1 Siemens Building Technologies Fire Safety Table Of Contents Introduction...1 The Access levels...1 User Level...1 Maintenance More information Invitation to Bid FIRE ALARM & DETECTION SYSTEM
Invitation to Bid FIRE ALARM & DETECTION SYSTEM Responses to an Invitation to Bid will be received by the Purchasing Supervisor, Sumner County Board of Education, 1500 Airport Road, Gallatin, TN 37066 More information EXHIBIT A SCOPE OF WORK
FIRE ALARM APPLICATION ENUMCLAW FIRE DEPARTMENT 1330 Wells St, Enumclaw, WA 98022 Phone: 360-825-5544 Fax: 360-825-9442 COMMUNITY DEVELOPMENT, BUILDING DEPARTMENT 1309 Myrtle Ave Enumclaw WA 98022 Phone: More information ENGINEERING SPECIFICATIONS
ENGINEERING SPECIFICATIONS FM-200 CLEAN-AGENT FIRE SUPPRESSION SYSTEM with PYRO-CHEM DETECTION/RELEASE SYSTEM March 2001 SECTION 1 - GENERAL I. SCOPE This specification outlines the requirements for a More information Fire Alarm System Plans Review Checklist Property location Date of Review
Rancho Cucamonga Fire Protection District Prevention Bureau Standard Title: Fire Alarm and Monitoring Systems Standard # 9-3 Effective: May 2002 Number of Pages: 7 Revised: January 2014 INTENT The intent More information INSTRUCTIONS FOR BUILDINGS WITH FIRE PROTECTION EQUIPMENT
INSTRUCTIONS FOR BUILDINGS WITH FIRE PROTECTION EQUIPMENT FIRE EXTINGUISHERS,SPRINKLER SYSTEMS AND FIRE ALARMS Attachment #1 Inspection of Fire Extinguishers Fire Extinguishers must be tested according More information C. NICET: National Institute for Certification in Engineering Technologies. D. Definitions in NFPA 72 apply to fire alarm terms used in this Section.
SECTION 283100 - FIRE DETECTION AND ALARM PART 1 - GENERAL 1.1 RELATED DOCUMENTS A. Drawings and general provisions of the Contract, including General and Supplementary Conditions and Division 01 Specification More information New and Existing Fire Alarm & Signaling Systems
ORANGE COUNTY FIRE AUTHORITY Planning & Development Services Section 1 Fire Authority Road, Building A, Irvine, CA 92602 714-573-6100 www.ocfa.org New and Existing Fire Alarm & Signaling Systems Guideline More information Module 5. Fire and Emergency Alarm System Part I- Basics
Module 5 Fire and Emergency Alarm System Part I- Basics 1 This module will describe: 1. Components and the arrangements of components in fire and emergency alarm systems. 2. How these systems work. 3. More information FIREFINDER XLS ADDRESSABLE FIRE ALARM SYSTEM SECTION 13851
FIREFINDER XLS ADDRESSABLE FIRE ALARM SYSTEM SECTION 13851 PART 1 - GENERAL 1.1 RELATED DOCUMENTS A. Drawings and general provisions of the Contract, including General and Supplementary Conditions and More information TAMARAC FIRE RESCUE INSTRUCTIONS FOR FIRE ALARM PRE-SUBMITTAL CHECKLIST
TAMARAC FIRE RESCUE INSTRUCTIONS FOR FIRE ALARM PRE-SUBMITTAL CHECKLIST In order to provide a comprehensive plan review in a timely manner, and to insure the design and installation of fire alarm systems More information SECTION 16610 FIRE DETECTION AND ALARM SYSTEM
SECTION 16610 FIRE DETECTION AND ALARM SYSTEM PART 1 - GENERAL 1.01 REQUIREMENTS A. The general provisions of the Contract, including General and Supplementary Conditions and General Requirements, apply More information SPECIFICATION MICROMIST FIRE SUPPRESSION SYSTEM WITH CHEETAH Xi CONTROL PANEL
SECTION 1 - GENERAL CONDITIONS I. SCOPE: This specification outlines the requirements for a Fike Micromist Water Mist Fire Suppression System with a Cheetah Xi addressable detection and control system. More information A. This Standard outlines the requirements for an addressable fire detection and alarm system.
1.00 GENERAL 1.01 Scope: A. This Standard outlines the requirements for an addressable fire detection and alarm system. B. This Standard consists of all materials, equipment and services necessary and More information Fire Pump Controllers Remote Alarm Panels
Fire Pump Controllers Remote Alarm Panels Remote Alarm Panels 1.8 Remote Alarm Panels FDAP-M Electric... DFDAP-M Diesel... Product Specifications... 2 6 9 Features 1-1 DFDAP-M / FDAP-M Remote Alarm Panel More information Life Alarm Fire Alarm Controls
FIRE SUPERVISORY SUPV SILENCED SILENCE AC POWER RESET UL, ULC Listed FM Approved MEA Approved* Life Alarm Fire Alarm Controls Fire Alarm Controls 4005 Series Fire Alarm Control Panels Eight through Thirty-Six More information Fire Alarm and Detection Systems And Central Station Monitoring Plan Submittal Guidelines
Fire Alarm and Detection Systems And Central Station Monitoring Plan Submittal Guidelines Red Oak Fire Rescue Office of the Fire Marshal 547 N. Methodist Red Oak, TX 75154 Phone: 469-218-7713 Fax: 468-218-7719 More information Security Systems Intrusion Alarm
Dufferin-Peel Catholic District School Board STANDARD TEXT GUIDELINE FOR Security Systems for SECONDARY AND ELEMENTARY SCHOOLS Prepared by the Plant Department With Assistance from Vision Dynamics Formatted More information SECTION 16700 FIRE ALARM SYSTEM
SECTION 16700 FIRE ALARM SYSTEM PART ONE: GENERAL 1.1 GENERAL REQUIREMENTS A. Definition of Work : This section of the specification includes the furnishing, installation, connection and testing of the More information D287/D288/D292/D293A/D293E
D87/D88/D9/D9A/D9E EN Installation Guide Smoke Detector Bases D87/D88/D9/D9A/D9E Installation Guide.0 Overview.0 Overview The D87/D88/D9/D9A/D9E Smoke Detector Bases are designed for use with the D8 Ionization More information Fire Alarm FAQs. Q: How many zone/circuit fire alarm panel do I need? Q: What candela strobes do I need?
5/2/2014 Fire Alarm FAQs Question Answer Q: How many zone/circuit fire alarm panel do I need? Q: What candela strobes do I need? A: The size of a fire alarm panel is determined by a number of factors, More information SECTION 16721 MULTI-FIRE ALARM SYSTEM
PART 1. GENERAL 1.1 RELATED DOCUMENTS: A. Drawings and general provisions of the Contract, including General and Supplementary Conditions and Divisions 1 Specification Sections, apply to this Section. More information SPECIFICATIONS FOR THE INSTALLATION OF FIRE ALARM SYSTEMS, SPRINKLER SYSTEMS, AND MASTER BOXES IN THE POQUONNOCK BRIDGE FIRE DISTRICT
SPECIFICATIONS FOR THE INSTALLATION OF FIRE ALARM SYSTEMS, SPRINKLER SYSTEMS, AND MASTER BOXES IN THE POQUONNOCK BRIDGE FIRE DISTRICT The purpose of these specifications is to insure that there are minimum More information A. Product Data: For each type of product, including furnished options and accessories.
SECTION 283111 - DIGITAL, ADDRESSABLE FIRE-ALARM SYSTEM PART 1 - GENERAL 1.1 SUMMARY A. Section Includes: 1. Fire-alarm control unit. 2. Manual fire-alarm boxes. 3. System smoke detectors. 4. Non-system More information NATIONAL FIRE ALARM AND SIGNALING CODE
GAP.11.1.1.0 A Publication of Global Asset Protection Services LLC NATIONAL FIRE ALARM AND SIGNALING CODE INTRODUCTION National Fire Protection Association (NFPA) documents describe a level of fire protection More information Finance and Administration Department 907 Billy Mitchell Blvd. P: (210) 228-1022 Fire Alarm Permit Application
PERMIT FEE: $ Finance and Administration Department 907 Billy Mitchell Blvd. P: (210) 228-1022 Fire Alarm Permit Application PAYMENT TYPE: Check Credit Card Charge to Job #: (Please complete all of the More information FIRE ALARM SYSTEM CHECKLIST For Addressable Systems PRIOR TO INSPECTION
Building Name/Location: Installing Company: Observation By: Date: Time: 1 Building Occupants, Authorities and Alarm Monitoring Co Have Been Notified 2 FACP Manufacturer and Panel is Approved for NCSU Campus More information BELMONT FIRE DEPARTMENT FIRE ALARM SYSTEM REQUIREMENTS BFD-OFM-10-011
Fire Alarm System plan(s) MUST be reviewed and approved by the Belmont Fire Department prior to the start of construction. The design and any changes must be fully compliant with NFPA 1, NFPA 101, NFPA More information B. NICET: National Institute for Certification in Engineering Technologies.
PART 1 - GENERAL 1.01 RELATED DOCUMENTS A. Drawings and general provisions of the Contract, including General and Supplementary Conditions and Division 01 Specification Sections, apply to this Section. More information SPECIFICATION FOR A TOTAL FLOOD HFC-227ea CLEAN AGENT FIRE SUPPRESSION SYSTEM FOR USE WITH THE Cheetah Xi CONTROL PANEL SYSTEM
SECTION 1 - GENERAL CONDITIONS I. SCOPE: This specification outlines the requirements for a Total Flood Clean Agent Fire Suppression System with automatic detection and control. The work described in this More information SECTION 13850 (28 31 00) FIRE DETECTION AND ALARM SYSTEM
SECTION 13850 (28 31 00) FIRE DETECTION AND ALARM SYSTEM ENGINEERING SPECIFICATION 25-POINT INTELLIGENT COMMUNICATING FIRE DETECTION SYSTEM PART 1 GENERAL 1.1. DESCRIPTION: A. This section of the specification More information DORMA MODEL PS-406BB POWER SUPPLY INSTALLATION INSTRUCTIONS
Features: INSTALLATION Install in accordance with NFPA 70. DORMA MODEL PS-406BB POWER SUPPLY INSTALLATION INSTRUCTIONS Up to 1.95 Amps Load Capacity Class 2 Rated Outputs Overload, Over Voltage, and Short More information 16720S01 - FIRE ALARM SYSTEM (HARDWIRED), MANUAL AND AUTOMATIC
FIRE DETECTION AND ALARM GENERAL INFORMATION 1.1 In general, follow the guidelines below when designing and specifying addressable fire alarm systems. Unless specifically indicated otherwise, these guidelines More information FIRE ALARM SYSTEM TECHNICAL SPECIFICATIONS Page 1 of 10
TECHNICAL SPECIFICATIONS Page 1 of 10 FIRE DETECTION AND ALARM SYSTEM Scope Furnish a complete 24V DC conventional, electrically supervised, zone annunciated, fire detection and alarm system as specified More information University Design Standard. Fire Alarm Systems
University Design Standard Fire Alarm Systems 1.0 Overview This document provides Virginia Tech s standards for the design and installation of fire alarm systems and equipment in new construction, retrofit More information SP4-LOC SAFEPATH4 REMOTE MICROPHONE AND LOCAL OPERATOR CONSOLE
SP4LOC SAFEPATH4 REMOTE MICROPHONE AND LOCAL OPERATOR CONSOLE INSTALLATION AND OPERATION MANUAL MASS NOTIFICATION SYSTEM Part Number: P84767 Rev. A Copyright 2006 Cooper Wheelock, Inc. All rights reserved. More information Original Document 10/16/07 Revised 01/30/09 2 nd Revision 01-23-12 3 rd Revision- 12/18/14
North Collier Fire Control & Rescue District Greater Naples Fire Rescue District Immokalee Fire Control & Rescue District 2800 North Horseshoe Drive Naples, Florida 34104 SYSTEM REHABILITATION PLAN CHECKLIST More information FIRE ALARM AND EMERGENCY COMMUNICATION SYSTEM RECORD OF COMPLETION
FIRE ALARM AND EMERGENCY COMMUNICATION SYSTEM RECORD OF COMPLETION To be completed by the system installation contractor at the time of system acceptance and approval. It shall be permitted to modify this More information Small Building Life Safety Solutions. GE Security. Affordable FireShield Conventional Fire Alarm Control Panels. imagination at work
GE Security Small Building Life Safety Solutions Affordable FireShield Conventional Fire Alarm Control Panels imagination at work cost Location: Environment: Solution: Flower shop Finely decorated, gentle More information CAN/ULC-S524-06 Installation of Fire Alarm Systems Amendment 1. Canadian Fire Alarm Association (CFAA) D. GOODYEAR FIRE CONSULTING
CAN/ULC-S524-06 Installation of Fire Alarm Systems Amendment 1 Canadian Fire Alarm Association (CFAA) CAN/ULC-S524 AMENDMENT 1 PUBLISHED February 2011 WHY Clarifications New requirements (Technology changes) More information PROJECT TITLE PROJECT NO: 0000000 CONTRACT TITLE GRANT NO: 0000000 UNIVERSITY OF CALIFORNIA, DAVIS CITY, CALIFORNIA
Fire alarm--all types of occupancies. The following standard specification is intended to be edited according to the specifics of the project. Brackets [ ] and areas shaded in gray [e.g. format] indicate More information SECTION 13850 DETECTION AND ALARM
SECTION 13850 DETECTION AND ALARM PART 1 GENERAL 1.01 SUMMARY A. Section Includes 1. Control Panel 2 Associated Equipment B. Products Installed But Not Supplied Under This Section 1. Section 16140 - Wiring More information PC4020CF v3.0 and higher Commercial Fire Installation Guide DLS-3 v1.3
PC4020CF v3.0 and higher Commercial Fire Installation Guide DLS-3 v1.3 Table of Contents Section 1: Introduction 1 1.1 Introduction...1 1.2 Hardware Description and Specifications...1 Section 2: Fire Zone More information Conventional Fire Detection and Extinguishant Control System Specification
Conventional Fire Detection and Extinguishant Control System Specification Page 1 of 9 Scope Furnish a complete 24VDC Conventional, electrically supervised, combined fire detection and extinguishant release More information FIRE ALARM SYSTEM Section 16750 Page 1
FIRE ALARM SYSTEM Section 16750 Page 1 PART 1 - GENERAL 1.1 REQUIREMENTS A. Provide a complete operational, stand-alone local protective signaling system in each defined building as indicated on the contract More information B. All Fire Detection and Alarm design and installation shall comply with the most current and adopted version of NFPA 72.
28 31 00 PART 1 - GENERAL 1.01 SCOPE A. Background: Washington State University has agreements with Simplex- Grinnell and Siemens Industry, Inc. to provide Fire Detection and Alarm (FDA) systems for the More information INTELLIGENT FIRE ALARM CONTROL PANELS. MR-2100/MR-2200 Intelligent Fire Alarm Control Panels MEA. Features. Description
INTELLIGENT FIRE ALARM CONTROL PANELS MR-2100/MR-2200 Intelligent Fire Alarm Control Panels Description MR-2100/MR-2200 Intelligent Fire Alarm Control Panel (shown with optional LED modules) Secutron's More information SECTION SECURITY INTRUSION SYSTEM
SECTION 16620 SECURITY INTRUSION SYSTEM PART 1 - GENERAL 1.01 REQUIREMENTS A. The general provisions of the Contract, including General and Supplementary Conditions and General Requirements, apply to the More information SECTION 16620 FIRE ALARM SYSTEM
SECTION 16620 PART 1 GENERAL FIRE ALARM SYSTEM 1.01 SUMMARY A. Work included: Labor, materials and equipment necessary to complete the installation required for the item specified under this Division, More information 1.0 General. Inspection, Testing, and Maintenance 1 of 8
1.0 General 1.1 Scope This specifications covers the minimum requirements for the inspection, testing, and maintenance of the existing Notifier fire alarm systems at Bergen Community College (BCC) campus More information FIRE ALARM SYSTEM SUBMITTAL CHECKLIST AND APPLICATION
PERMITS AND INSPECTIONS FIRE ALARM SYSTEM SUBMITTAL CHECKLIST AND APPLICATION 911 Assigned PROJECT LOCATION Subdivision: Lot: Blk: Sec: PROJECT New Construction Addition/Remodel Demolition Other: Number More information Engineer s Project Number: 298-1062 Section 28 31 00 Page 1 FIRE ALARM AND DETECTION SYSTEMS
Engineer s Project Number: 298-1062 Section 28 31 00 Page 1 SECTION 28 31 00 PART 1 GENERAL 01 SUMMARY A. This Section covers fire alarm systems, including initiating devices, notification appliances, More information Release Control Fire Alarm Systems
SYSTEM ABORT PUSH AND HOLD COIL SUPERVISION MODULE (2 AMP) 2081-9046 RED INSTALLATION INSTRUCTIONS 574-437 REV YEL NAC+ MAINTAIN 1/4" SEPARATION BETWEEN POW ER LIMITED (RED/) AND NONPOWER S LIMITED (YEL/) More information OFPC Standard Specification
OFPC Standard Specification DIVISION 28 FIRE ALARM AND SMOKE DETECTION SYSTEM This Standard Specification Section is controlled by the Office of Facilities Planning and Construction, UT System. It is to More information City of Bettendorf Fire Alarm System Requirements
City of Bettendorf Fire Alarm System Requirements Section 907 of the 2009 Edition of the International Fire Code (IFC) and Section 10-7-3 of the Municipal Code provide fire alarm requirements. IFC Section More information SFC-200 SERIES FIRE ALARM CONTROL PANELS. SFC-200 Series Fire Alarm Control Panels. Features. Description
SFC-200 SERIES FIRE ALARM CONTROL PANELS SFC-200 Series Fire Alarm Control Panels Description Summit s SFC-200 Series fire alarm control panels consist of six and twelve zone models which are equipped More information D7050/D7050TH. Installation Instructions. Multiplex Photoelectric Smoke Detectors
D7050/D7050TH EN Installation Instructions Multiplex Photoelectric Smoke Detectors D7050/D7050TH Installation Instructions.0 Description Notices These instructions cover the installation of the D7050/D7050TH More information Brown University New August 8, 2012 Facilities Design & Construction Standards SECTION 28 31 10 - FIRE ALARM SYSTEMS, SMOKE ALARMS, CARBON MONOXIDE
SECTION 28 31 10 - FIRE ALARM SYSTEMS, SMOKE ALARMS, CARBON MONOXIDE PART 1 - GENERAL 1.1 SUMMARY: A. Section Includes: 1. Fire Alarm and Detection Systems 2. Single Station Smoke Alarms 3. Single Station More information 5. Central Control and Monitoring System. 6. Gas Detection Systems (future) 7. Mass Notification Systems (future) 8. Smoke Control Systems.
Scope Provide a fire alarm system, or expand the existing system, as required by Code, the requirements in the Special Instructions to Designers (SID) of the Design Guidelines, and/or as noted in the Program More information INTELLIGENT FIRE ALARM CONTROL UNITS. MMX-2017-12NDS Intelligent Network Fire Alarm Control Unit. Features. Description
INTELLIGENT FIRE ALARM CONTROL UNITS MMX-2017-12NDS Intelligent Network Fire Alarm Control Unit Description Secutron s MMX-2017-12NDS Network Fire Alarm Control Unit offers modular components to meet a More information A. This Section covers addressable fire alarm systems for wet and dry sprinkler systems, clean agent systems, and building fire alarms.
SECTION 283111 - PART 1 - GENERAL 1.1 SUMMARY A. This Section covers addressable fire alarm systems for wet and dry sprinkler systems, clean agent systems, and building fire alarms. 1.2 GENERAL REQUIREMENTS More information 283100 FIRE ALARM AND DETECTION SYSTEMS
283100 FIRE ALARM AND DETECTION SYSTEMS PART 1: GENERAL 1.01 QUALITY ASSURANCE A. The integrated fire alarm system including all equipment, components, and accessories shall be UL listed for the purpose More information COMMISSIONING OF FIRE ALARM SYSTEMS
COMMISSIONING OF FIRE ALARM SYSTEMS OWNER FURNISHED The owner directly contracts an independent third party commissioning agent for this project. This Commissioning Plan has been included for reference More information 2017 © DocPlayer.net Privacy Policy | Terms of Service | Feedback