Source: http://www.ecfr.gov/cgi-bin/text-idx?c=ecfr&rgn=div8&view=text&node=46:2.0.1.2.15.6.1.2&idno=46
Timestamp: 2014-10-22 06:32:59
Document Index: 37553985

Matched Legal Cases: ['art 58', 'art 58', '§58', 'ART 58', 'art 58', '§58', 'art 54', '§147']

Title 46 → Chapter I → Subchapter F → Part 58 → Subpart 58.20 → §58.20-5
PART 58—MAIN AND AUXILIARY MACHINERY AND RELATED SYSTEMS Subpart 58.20—Refrigeration Machinery
§58.20-5 Design.(a) Refrigeration machinery may be accepted for installation provided the design, material, and fabrication comply with the applicable requirements of the ABS Steel Vessel Rules (incorporated by reference, see 46 CFR 58.03-1). The minimum pressures for design of all components must be those listed for piping in Table 501.2.4 of ANSI B31.5 (incorporated by reference; see 46 CFR 58.03-1). In no case may pressure components be designed for a pressure less than that for which the safety devices of the system are set. Pressure vessels must be designed in accordance with part 54 of this subchapter. (b) For refrigeration systems other than those for reliquefaction of cargo, only those refrigerants under §147.90 of this chapter are allowed.
[CGFR 68-82, 33 FR 18878, Dec. 18, 1968, as amended by CGFR 69-127, 35 FR 9980, June 17, 1970; CGD 84-044, 53 FR 7748, Mar. 10, 1988; USCG-2003-16630, 73 FR 65187, Oct. 31, 2008]