Source: https://www.federalregister.gov/documents/2003/02/19/03-3936/nuclear-management-company-llc-monticello-nuclear-generating-plant-environmental-assessment-and
Timestamp: 2018-04-26 20:21:25
Document Index: 607266286

Matched Legal Cases: ['art 50', 'art 50', 'art 50', 'art 50', 'art 50', 'art 50', 'art 50', 'art 50', 'art 50']

Federal Register :: Nuclear Management Company, LLC; Monticello Nuclear Generating Plant; Environmental Assessment and Finding of No Significant Impact
68 FR 8052
03-3936
https://www.federalregister.gov/d/03-3936 https://www.federalregister.gov/d/03-3936
The U.S. Nuclear Regulatory Commission (NRC) is considering issuance of an exemption from Title 10 of the Code of Federal Regulations (10 CFR) Part 50, Section 50.60, “Acceptance criteria for fracture prevention measures for light-water nuclear power reactors for normal operation,” and 10 CFR Part 50, Appendix G, “Fracture Toughness Requirements,” for Facility Operating License No. DPR-22, issued to the Nuclear Management Company, LLC (the licensee), for operation of the Monticello Nuclear Generating Plant, located in Wright County, Minnesota. Therefore, as required by 10 CFR 51.21, the NRC is issuing this environmental assessment and finding of no significant impact.
The proposed action would exempt the licensee from the requirements of 10 CFR Part 50, Section 50.60(a) and Appendix G, which would allow the use of American Society of Mechanical Engineers Boiler and Pressure Vessel Code (ASME Code) Code Case N-640 as the basis for revised reactor vessel pressure and temperature (P/T) limit curves in the Monticello Technical Specifications (TSs).
The regulation at 10 CFR Part 50, Section 50.60(a), requires, in part, that except where an exemption is granted by the Commission, all light-water nuclear power reactors must meet the fracture toughness requirements for the reactor coolant pressure boundary set forth in Appendices G and H to 10 CFR Part 50. Appendix G to 10 CFR Part 50 requires that P/T limits be established for reactor pressure vessels (RPVs) during normal operating and hydrostatic or leak-rate testing conditions. Specifically, 10 CFR Part 50, Appendix G, states, “The appropriate requirements on both the pressure-temperature limits and the minimum permissible temperature must be met for all conditions.” Appendix G of 10 CFR Part 50 specifies that the requirements for these limits are the ASME Code, Section XI, Appendix G, limits.
ASME Code Case N-640 permits the use of alternate reference fracture toughness (i.e., use of “KIC fracture toughness curve” instead of “KIA fracture toughness curve,” where KIC and KIA are “Reference Stress Intensity Factors,” as defined in ASME Code, Section XI, Appendices A and G, respectively) for reactor vessel materials in determining the P/T limits. Since the KIC fracture toughness curve shown in ASME Code, Section XI, Appendix A, Figure A-2200-1, provides greater allowable fracture toughness than the corresponding KIA fracture toughness curve of ASME Code, Section XI, Appendix G, Figure G-2210-1, using ASME Code Case N-640 to establish the P/T limits would be less conservative than the methodology currently endorsed by 10 CFR Part 50, Appendix G. Therefore, an exemption to apply ASME Code Case N-640 is required.
The proposed action is in accordance with the licensee's application dated April 22, 2002, as supplemented by letter dated September 16, 2002.
The proposed exemption is needed to allow the licensee to implement ASME Code Case N-640 in order to revise the method used to determine the P/T limits because continued use of the present curves unnecessarily restricts the P/T operating window. Since the P/T operating window is defined by the ­ P/T operating and test limit curves developed in accordance with the ASME Code, Section XI, Appendix G, procedure, continued operation of Monticello with these P/T curves without the relief provided by ASME Code Case N-640 would unnecessarily require the RPV to maintain a temperature exceeding 212 °F in a limited operating window during the Start Printed Page 8053pressure test. Consequently, steam vapor hazards would continue to be one of the safety concerns for personnel conducting inspections in primary containment. Implementation of the proposed P/T curves, as allowed by ASME Code Case N-640, would not significantly reduce the margin of safety and would eliminate steam vapor hazards by allowing inspections in primary containment to be conducted at a lower coolant temperature.
The action does not involve the use of any different resource than those previously considered in the Final Environmental Statement for Monticello.
On February 11, 2003, the staff consulted with the Minnesota State official, Nancy Campbell of the Department of Commerce, regarding the environmental impact of the proposed action. The State official had no comments.
For further details with respect to the proposed action, see the licensee's application dated April 22, 2002, as supplemented by letter dated September 16, 2002. Documents may be examined, and/or copied for a fee, at the NRC's Public Document Room (PDR), located at One White Flint North, 11555 Rockville Pike (first floor), Rockville, Maryland. Publicly available records will be accessible electronically from the Agencywide Documents Access and Management System (ADAMS) Public Electronic Reading Room on the Internet at the NRC Web site, http://www.nrc.gov/​reading-rm/​adams.html. Persons who do not have access to ADAMS or who encounter problems in accessing the documents located in ADAMS, should contact the NRC PDR Reference staff by telephone at 1-800-397-4209 or 301-415-4737, or by e-mail to pdr@nrc.gov.
Dated at Rockville, Maryland, this 12th day of February 2003.
[FR Doc. 03-3936 Filed 2-18-03; 8:45 am]