Source: http://docplayer.fr/1178521-Final-draft-international-standard-projet-final-de-norme-internationale.html
Timestamp: 2018-04-26 21:33:53+00:00
Document Index: 139461400

Matched Legal Cases: ['art 4', 'art 4', 'art 4', 'art 4', 'art 2', 'art 1', 'art 2', 'art 3', 'art 4', 'art 5', 'art 6', 'art 9', 'art 4', 'art 2', "l'article 5"]

1 This is a preview - click here to buy the full publication IEC Edition FINAL DRAFT INTERNATIONAL STANDARD PROJET FINAL DE NORME INTERNATIONALE colour inside Electromagnetic compatibility (EMC) Part 4-24: Testing and measurement techniques Test methods for protective devices for HEMP conducted disturbance Compatibilité electromagnétique (CEM) Partie 4-24: Techniques d essai et de mesure Méthodes d essai pour les dispositifs de protection pour perturbations conduites IEMN-HA INTERNATIONAL ELECTROTECHNICAL COMMISSION COMMISSION ELECTROTECHNIQUE INTERNATIONALE ICS Warning! Make sure that you obtained this publication from an authorized distributor. Attention! Veuillez vous assurer que vous avez obtenu cette publication via un distributeur agréé. Registered trademark of the International Electrotechnical Commission Marque déposée de la Commission Electrotechnique Internationale
2 77C/245/FDIS FINAL DRAFT INTERNATIONAL STANDARD PROJET FINAL DE NORME INTERNATIONALE Project number IEC Ed 2.0 Numéro de projet Submitted for parallel voting in CENELEC Soumis au vote parallèle au CENELEC Also of interest to the following committees Intéresse également les comités suivants SC45A, ITU-T SG5, CIGRÉ C4 Horizontal standard Norme horizontale IEC/TC or SC CEI/CE ou SC SC 77C Distributed on / Diffusé le Supersedes document Remplace le document 77C/238/CDV & 77C/242/RVC Secretariat / Secrétariat United Kingdom Voting terminates on / Vote clos le Other TC/SCs are requested to indicate their interest, if any, in this FDIS to the TC/SC secretary Les autres CE/SC sont requis d indiquer leur intérêt, si nécessaire, dans ce FDIS à l intention du secrétaire du CE/SC Functions concerned Fonctions concernées Safety Sécurité EMC CEM Environment Environnement Quality assurance Assurance de la qualité CE DOCUMENT EST UN PROJET DIFFUSÉ POUR APPROBATION. IL NE PEUT ÊTRE CITÉ COMME NORME INTERNATIONALE AVANT SA PUBLICATION EN TANT QUE TELLE. OUTRE LE FAIT D'ÊTRE EXAMINÉS POUR ÉTABLIR S'ILS SONT ACCEPTABLES À DES FINS INDUSTRIELLES, TECHNOLOGIQUES ET COMMERCIALES, AINSI QUE DU POINT DE VUE DES UTILISATEURS, LES PROJETS FINAUX DE NORMES INTERNATIONALES DOIVENT PARFOIS ÊTRE EXAMINÉS EN VUE DE LEUR POSSIBILITÉ DE DEVENIR DES NORMES POUVANT SERVIR DE RÉFÉRENCE DANS LES RÈGLEMENTATIONS NATIONALES. LES RÉCIPIENDAIRES DU PRÉSENT DOCUMENT SONT INVITÉS À PRÉSENTER, AVEC LEURS OBSERVATIONS, LA NOTIFICATION DES DROITS DE PROPRIÉTÉ DONT ILS AURAIENT ÉVENTUELLEMENT CONNAISSANCE ET À FOURNIR UNE DOCUMENTATION EXPLICATIVE. THIS DOCUMENT IS A DRAFT DISTRIBUTED FOR APPROVAL. IT MAY NOT BE REFERRED TO AS AN INTERNATIONAL STANDARD UNTIL PUBLISHED AS SUCH. IN ADDITION TO THEIR EVALUATION AS BEING ACCEPTABLE FOR INDUSTRIAL, TECHNOLOGICAL, COMMERCIAL AND USER PURPOSES, FINAL DRAFT INTERNATIONAL STANDARDS MAY ON OCCASION HAVE TO BE CONSIDERED IN THE LIGHT OF THEIR POTENTIAL TO BECOME STANDARDS TO WHICH REFERENCE MAY BE MADE IN NATIONAL REGULATIONS. RECIPIENTS OF THIS DOCUMENT ARE INVITED TO SUBMIT, WITH THEIR COMMENTS, NOTIFICATION OF ANY RELEVANT PATENT RIGHTS OF WHICH THEY ARE AWARE AND TO PROVIDE SUPPORTING DOCUMENTATION. Titre IEC : Compatibilité Electromagnétique (CEM) Partie 4-24: Techniques d essai et de mesure Méthodes d essai pour les dispositifs de protection pour perturbations conduites IEMN-HA Title IEC : Electromagnetic Compatibility (EMC) Part 4-24: Testing and measurement techniques Test methods for protective devices for HEMP conducted disturbance Copyright 2015 International Electrotechnical Commission, IEC. All rights reserved. It is permitted to download this electronic file, to make a copy and to print out the content for the sole purpose of preparing National Committee positions. You may not copy or "mirror" the file or printed version of the document, or any part of it, for any other purpose without permission in writing from IEC. Registered trademark of the International Electrotechnical Commission FORM FDIS (IEC)/FORMULAIRE FDIS (CEI)
3 2 IEC FDIS IEC 2015 CONTENTS FOREWORD... 5 INTRODUCTION Scope Normative references Terms, definitions and abbreviated terms Terms and definitions Abbreviated terms Test methods for protective devices (excluding filter) for conducted disturbance General Test setup Pulse generator Launching line Test fixtures General Type A fixtures Type B fixtures Termination Oscilloscope Test procedure Adjustment of the pulse generator Verification procedures Test Final examination of the DUT Referring to this standard Measurement method for HEMP combination filters Verification setup Measurement setup Measurement instrument Pulse generators Oscilloscope Current sensors Test loads Test modes required Measurement procedure General Verification of pulses Measurement procedure Evaluation of test results Test report Annex A (informative) Investigation for the establishment of a measurement setup A.1 General A.2 Variation of the cable connected for the measurement of short-circuit current A.3 Variation of the length of the cable L2 connected for the measurement of residual current A.4 Variation of load impedance and cable length for connection between load and ground... 31
4 IEC FDIS IEC A.5 Variation of the cable length between load and ground Annex B (informative) Test method for the quantitative determination of the direct response behaviours of a coaxial surge protector Bibliography Figure 1 Test setup for testing protective devices Figure 2 Example of a type B test fixture (universal) Figure 3 Typical setup for verification of the pulse test level Figure 4 Example of test setup using one or two shielded enclosures Figure 5 Example of test setup using a shielded enclosure Figure 6 Double exponential waveform Figure 7 Example of wiring setup of a single line DUT Figure 8 Example of wiring setup for a mutually coupled multi-line DUT Figure A.1 Setup for calibration Figure A.2 Peak current calibration results with 9 mm 2 cables: A ± 4 % Figure A.3 Rise time calibration results with 9 mm 2 cables Figure A.4 FWHM calibration results with 9 mm 2 cables Figure A.5 Peak current calibration results with 4 mm 2 cables: A ± 8 % Figure A.6 Rise time calibration results with 4 mm 2 cables Figure A.7 FWHM calibration results with 4 mm 2 cables Figure A.8 Measurement setup for residual current Figure A.9 Measurement result of peak current with variation of measurement cable L Figure A.10 Measurement result of peak rate of rise with variation of measurement cable L Figure A.11 Measurement result of root action with variation of measurement cable L Figure A.12 Variation of the position of current sensor 2 on the measurement cable L Figure A.13 Peak current with variation of cable L2 and at different positions Figure A.14 Peak rate of rise with variation of cable L2 and at different positions Figure A.15 Root action with variation of cable L2 and at different positions Figure A.16 Measurement result of peak current with variation of load impedance Figure A.17 Measurement result of peak rate of rise with variation of load impedance Figure A.18 Measurement result of root action with variation of load impedance Figure A.19 Variation of the length of cable L3 connected between load and ground plane Figure A.20 Measurement result of peak current with variation of measurement cable L Figure A.21 Measurement result of peak rate of rise with variation of measurement cable L Figure A.22 Measurement result of root action with variation of measurement cable L Figure B.1 Test setup with a power divider for testing protective devices Figure B.2 Waves propagating along the branches Figure B.3 Simplified test setup for testing protective devices Table 1 Overview of conducted early-time HEMP (CEP) test requirements defined in other specifications... 18
5 4 IEC FDIS IEC 2015 Table 2 Overview of conducted intermediate-time HEMP (CIP) test requirements defined in other specifications Table 3 Test mode and DUT wiring setup Table 4 Performance criteria of filter against early-time HEMP AC power port with nominal load 2 Ω Table 5 Performance criteria of filter against early-time HEMP DC power port with nominal load 2 Ω Table 6 Performance criteria of filter against early-time HEMP Signal, data and control port with nominal load 50 Ω Table A.1 Measurement results for the waveform calibration of short-circuit current Table A.2 Measurement results for variation of the cable length at the measurement points Table A.3 Measurement results for variation of the load impedance Table A.4 Measurement results for variation of the cable length between load and ground... 34
6 IEC FDIS IEC INTERNATIONAL ELECTROTECHNICAL COMMISSION ELECTROMAGNETIC COMPATIBILITY (EMC) Part 4-24: Testing and measurement techniques Test methods for protective devices for HEMP conducted disturbance FOREWORD 1) The International Electrotechnical Commission (IEC) is a worldwide organization for standardization comprising all national electrotechnical committees (IEC National Committees). The object of IEC is to promote international co-operation on all questions concerning standardization in the electrical and electronic fields. To this end and in addition to other activities, IEC publishes International Standards, Technical Specifications, Technical Reports, Publicly Available Specifications (PAS) and Guides (hereafter referred to as IEC Publication(s) ). Their preparation is entrusted to technical committees; any IEC National Committee interested in the subject dealt with may participate in this preparatory work. International, governmental and nongovernmental organizations liaising with the IEC also participate in this preparation. IEC collaborates closely with the International Organization for Standardization (ISO) in accordance with conditions determined by agreement between the two organizations. 2) The formal decisions or agreements of IEC on technical matters express, as nearly as possible, an international consensus of opinion on the relevant subjects since each technical committee has representation from all interested IEC National Committees. 3) IEC Publications have the form of recommendations for international use and are accepted by IEC National Committees in that sense. While all reasonable efforts are made to ensure that the technical content of IEC Publications is accurate, IEC cannot be held responsible for the way in which they are used or for any misinterpretation by any end user. 4) In order to promote international uniformity, IEC National Committees undertake to apply IEC Publications transparently to the maximum extent possible in their national and regional publications. Any divergence between any IEC Publication and the corresponding national or regional publication shall be clearly indicated in the latter. 5) IEC itself does not provide any attestation of conformity. Independent certification bodies provide conformity assessment services and, in some areas, access to IEC marks of conformity. IEC is not responsible for any services carried out by independent certification bodies. 6) All users should ensure that they have the latest edition of this publication. 7) No liability shall attach to IEC or its directors, employees, servants or agents including individual experts and members of its technical committees and IEC National Committees for any personal injury, property damage or other damage of any nature whatsoever, whether direct or indirect, or for costs (including legal fees) and expenses arising out of the publication, use of, or reliance upon, this IEC Publication or any other IEC Publications. 8) Attention is drawn to the Normative references cited in this publication. Use of the referenced publications is indispensable for the correct application of this publication. 9) Attention is drawn to the possibility that some of the elements of this IEC Publication may be the subject of patent rights. IEC shall not be held responsible for identifying any or all such patent rights. International Standard IEC has been prepared by subcommittee 77C: High power transient phenomena, of IEC technical committee 77: Electromagnetic compatibility. It forms Part 4-24 of IEC It has the status of a basic EMC publication in accordance with IEC Guide 107. This second edition cancels and replaces the first edition published in This edition constitutes a technical revision. This edition includes the following significant technical changes with respect to the previous edition: a) A new Clause 5: Measurement method for HEMP combination filters, which contains 5.1 Verification setup, 5.2 Measurement setup, 5.3 Measurement instrument, 5.4 Test modes,
7 6 IEC FDIS IEC Measurement procedures, 5.6 Evaluation of test results, which introduced performance criteria of filter, and 5.7 Test report. b) A new informative Annex A: Investigation for the establishment of a measurement setup, which was based on Clause 5. c) A new informative Annex B: Test method for the quantitative determination of the direct response behaviours of a coaxial surge protector. The text of this standard is based on the following documents: FDIS 77C/XX/FDIS Report on voting 77C/XX/RVD Full information on the voting for the approval of this standard can be found in the report on voting indicated in the above table. This publication has been drafted in accordance with the ISO/IEC Directives, Part 2. A list of all parts in the IEC series, published under the general title Electromagnetic compatibility (EMC), can be found on the IEC website. The committee has decided that the contents of this publication will remain unchanged until the stability date indicated on the IEC website under "http://webstore.iec.ch" in the data related to the specific publication. At this date, the publication will be reconfirmed, withdrawn, replaced by a revised edition, or amended. The National Committees are requested to note that for this publication the stability date is THIS TEXT IS INCLUDED FOR THE INFORMATION OF THE NATIONAL COMMITTEES AND WILL BE DELETED AT THE PUBLICATION STAGE. IMPORTANT The 'colour inside' logo on the cover page of this publication indicates that it contains colours which are considered to be useful for the correct understanding of its contents. Users should therefore print this document using a colour printer.
8 IEC FDIS IEC INTRODUCTION This standard is part of the IEC series of standards, according to the following structure: Part 1: General General considerations (introduction, fundamental principles) Definitions, terminology Part 2: Environment Description of the environment Classification of the environment Compatibility levels Part 3: Limits Emission limits Immunity limits Part 4: Testing and measurement techniques Measurement techniques Testing techniques Part 5: Installation and mitigation guidelines Installation guidelines Mitigation methods and devices Part 6: Generic standards Part 9: Miscellaneous Each part is further subdivided into several parts, published either as international standards, as technical specifications or technical reports, some of which have already been published as sections. Others will be published with the part number followed by a dash and a second number identifying the subdivision (example: IEC ). The IEC has initiated the preparation of standardized methods to protect civilian society from the effects of high power electromagnetic (HPEM) environments. Such effects could disrupt systems for communications, electric power, information technology, etc. This part of IEC is an international standard that establishes the required test procedures for protective devices for HEMP conducted disturbance, such as gas discharge tubes, varistors, two-port SPDs and HEMP combination filters. The application of this standard is, however, not dependent on access to other sections and parts of the IEC 61000, except for those specifically referred to.
9 8 IEC FDIS IEC 2015 ELECTROMAGNETIC COMPATIBILITY (EMC) Part 4-24: Testing and measurement techniques Test methods for protective devices for HEMP conducted disturbance 1 Scope This part of IEC deals with methods for testing protective devices for HEMP conducted disturbance. It includes two-terminal elements, such as gas discharge tubes, varistors, and two-port SPDs, such as HEMP combination filters. It covers testing of voltage breakdown and voltage-limiting characteristics but also methods to measure the residual voltage and/or the residual current, peak rate of rise and root action for the case of very fast changes of voltage and current as a function of time. This standard does not cover insertion loss measurement methods. 2 Normative references The following documents, in whole or in part, are normatively referenced in this document and are indispensable for its application. For dated references, only the edition cited applies. For undated references, the latest edition of the referenced document (including any amendments) applies. IEC , Electromagnetic compatibility (EMC) Part 2-10: Environment Description of HEMP environment Conducted disturbance 3 Terms, definitions and abbreviated terms For the purposes of this document, the following terms, definitions and abbreviated terms apply. 3.1 Terms and definitions feed-through device two-port device, which is designed to feed a signal through an electromagnetic barrier (shield) Note 1 to entry: Typically it is in good electrical contact with the barrier and has one port on each side of the barrier, thus maintaining the isolation of the barrier gas discharge tube device with two or three metal electrodes hermetically sealed so that gas mixture and pressure are under control, and designed to protect apparatus or personnel from high transient voltages HEMP high-altitude electromagnetic pulse electromagnetic pulse produced by a nuclear explosion outside the earth s atmosphere Note 1 to entry: Typically above an altitude of 30 km.
10 2 IEC FDIS IEC 2015 SOMMAIRE AVANT-PROPOS... 5 INTRODUCTION Domaine d'application Références normatives Termes, définitions et abréviations Termes et définitions Abréviations Méthodes d'essai des dispositifs de protection (à l'exception d'un filtre) pour perturbations conduites Généralités Montage d'essai Générateur d'impulsions Ligne d'émission Dispositifs/supports d'essai Généralités Dispositifs de type A Dispositifs de type B Charge Oscilloscope Procédure d'essai Réglage du générateur d impulsions Procédures de vérification Essai Dernier examen du DUT Référence à la présente Norme Méthode de mesure pour les filtres combinés IEMN-HA Montage de vérification Montage de mesure Appareil de mesure Générateurs d'impulsions Oscilloscope Capteurs de courant Charges d'essai Modes d essai exigés Procédure de mesure Généralités Vérification des impulsions Procédure de mesure Évaluation des résultats d'essais Rapport d'essai Annexe A (informative) Investigation relative à l'établissement du montage de mesure A.1 Généralités A.2 Variation du câble connecté pour la mesure du courant de court-circuit A.3 Variation de la longueur du câble L2 connecté pour la mesure du courant résiduel... 29
11 IEC FDIS IEC A.4 Variation de l'impédance de charge et de la longueur de câble pour une connexion entre la charge et le sol A.5 Variation de la longueur de câble entre la charge et le sol Annexe B (informative) Méthode d'essai pour la détermination quantitative des comportements de réponse directs d'un dispositif coaxial de protection contre les surtensions Bibliographie Figure 1 Montage d'essai pour dispositifs de protection Figure 2 Exemple d'un dispositif/support d'essai de type B (universel) Figure 3 Montage type de vérification du niveau d'essai d'impulsion Figure 4 Exemple de montage d'essai à l'aide d'une ou de deux enceintes blindées Figure 5 Exemple de montage d'essai à l'aide d'une enceinte blindée Figure 6 Forme d'onde biexponentielle Figure 7 Exemple de montage de câblage d'un DUT à lignes uniques Figure 8 Exemple de montage de câblage d'un DUT multiligne couplé mutuellement Figure A.1 Montage en vue de l'étalonnage Figure A.2 Résultats d'étalonnage du courant de crête avec des câbles de 9 mm 2 : A ± 4 % Figure A.3 Résultats d'étalonnage du temps de montée avec des câbles de 9 mm Figure A.4 Résultats d'étalonnage FWHM avec des câbles de 9 mm Figure A.5 Résultats d'étalonnage du courant de crête avec des câbles de 4 mm 2 : A ± 8 % Figure A.6 Résultats d'étalonnage du temps de montée avec des câbles de 4 mm Figure A.7 Résultats d'étalonnage FWHM avec des câbles de 4 mm Figure A.8 Montage de mesure du courant résiduel Figure A.9 Résultat de mesure du courant de crête avec variation du câble de mesure L Figure A.10 Résultat de mesure de la valeur de crête du temps de montée avec variation du câble de mesure L Figure A.11 Résultat de mesure de l'action racine avec variation du câble de mesure L Figure A.12 Variation de la position du capteur de courant 2 sur le câble de mesure L Figure A.13 Courant de crête avec variation du câble L2 et aux différentes positions Figure A.14 Valeur de crête du temps de montée avec variation du câble L2 et aux différentes positions Figure A.15 Action racine avec variation du câble L2 et aux différentes positions Figure A.16 Résultat de mesure du courant de crête avec variation de l'impédance de charge Figure A.17 Résultat de mesure de la valeur de crête du temps de montée avec variation de l'impédance de charge Figure A.18 Résultat de mesure de l'action racine avec variation de l'impédance de charge Figure A.19 Variation de la longueur du câble L3 connecté entre la charge et le plan de masse Figure A.20 Résultat de mesure du courant de crête avec variation du câble de mesure L
12 4 IEC FDIS IEC 2015 Figure A.21 Résultat de mesure de la valeur de crête du temps de montée avec variation du câble de mesure L Figure A.22 Résultat de mesure de l'action racine avec variation du câble de mesure L Figure B.1 Montage d'essai avec un répartiteur de puissance en vue de soumettre des dispositifs de protection à essai Figure B.2 Ondes se propageant le long des branches Figure B.3 Montage d'essai simplifié pour l'essai de dispositifs de protection Tableau 1 Vue d'ensemble des exigences d'essai IEMN-HA initiale conduite (CEP) définies dans d'autres spécifications Tableau 2 Vue d'ensemble des exigences d'essai IEMN-HA intermédiaire conduite (CIP) définies dans d'autres spécifications Tableau 3 Mode d'essai et montage de câblage du DUT Tableau 4 Critères de performance du filtre par rapport à l'iemn-ha initiale Accès d'alimentation en courant alternatif avec charge nominale 2 Ω Tableau 5 Critères de performance du filtre par rapport à l'iemn-ha initiale Accès d'alimentation en courant continu avec charge nominale 2 Ω Tableau 6 Critères de performance du filtre par rapport à l'iemn-ha initiale Accès signal, données et contrôle avec charge nominale 50 Ω Tableau A.1 Résultats de mesure pour l'étalonnage de la forme d'onde du courant de court-circuit Tableau A.2 Résultats de mesure de la variation de la longueur du câble aux points de mesure Tableau A.3 Résultats de mesure de la variation de l'impédance de charge Tableau A.4 Résultats de mesure de la variation de la longueur du câble entre la charge et la masse... 37
13 IEC FDIS IEC COMMISSION ÉLECTROTECHNIQUE INTERNATIONALE COMPATIBILITÉ ÉLECTROMAGNÉTIQUE (CEM) Partie 4-24: Techniques d essai et de mesure Méthodes d essai pour les dispositifs de protection pour perturbations conduites IEMN-HA AVANT-PROPOS 1) La Commission Électrotechnique Internationale (IEC) est une organisation mondiale de normalisation composée de l'ensemble des comités électrotechniques nationaux (Comités nationaux de l IEC). L IEC a pour objet de favoriser la coopération internationale pour toutes les questions de normalisation dans les domaines de l'électricité et de l'électronique. À cet effet, l IEC entre autres activités publie des Normes internationales, des Spécifications techniques, des Rapports techniques, des Spécifications accessibles au public (PAS) et des Guides (ci-après dénommés "Publication(s) de l IEC"). Leur élaboration est confiée à des comités d'études, aux travaux desquels tout Comité national intéressé par le sujet traité peut participer. Les organisations internationales, gouvernementales et non gouvernementales, en liaison avec l IEC, participent également aux travaux. L IEC collabore étroitement avec l'organisation Internationale de Normalisation (ISO), selon des conditions fixées par accord entre les deux organisations. 2) Les décisions ou accords officiels de l IEC concernant les questions techniques représentent, dans la mesure du possible, un accord international sur les sujets étudiés, étant donné que les Comités nationaux de l IEC intéressés sont représentés dans chaque comité d études. 3) Les Publications de l IEC se présentent sous la forme de recommandations internationales et sont agréées comme telles par les Comités nationaux de l IEC. Tous les efforts raisonnables sont entrepris afin que l IEC s'assure de l'exactitude du contenu technique de ses publications; l IEC ne peut pas être tenue responsable de l'éventuelle mauvaise utilisation ou interprétation qui en est faite par un quelconque utilisateur final. 4) Dans le but d'encourager l'uniformité internationale, les Comités nationaux de l IEC s'engagent, dans toute la mesure possible, à appliquer de façon transparente les Publications de l IEC dans leurs publications nationales et régionales. Toutes divergences entre toutes Publications de l IEC et toutes publications nationales ou régionales correspondantes doivent être indiquées en termes clairs dans ces dernières. 5) L IEC elle-même ne fournit aucune attestation de conformité. Des organismes de certification indépendants fournissent des services d'évaluation de conformité et, dans certains secteurs, accèdent aux marques de conformité de l IEC. L IEC n'est responsable d'aucun des services effectués par les organismes de certification indépendants. 6) Tous les utilisateurs doivent s'assurer qu'ils sont en possession de la dernière édition de cette publication. 7) Aucune responsabilité ne doit être imputée à l IEC, à ses administrateurs, employés, auxiliaires ou mandataires, y compris ses experts particuliers et les membres de ses comités d'études et des Comités nationaux de l IEC, pour tout préjudice causé en cas de dommages corporels et matériels, ou de tout autre dommage de quelque nature que ce soit, directe ou indirecte, ou pour supporter les coûts (y compris les frais de justice) et les dépenses découlant de la publication ou de l'utilisation de cette Publication de l IEC ou de toute autre Publication de l IEC, ou au crédit qui lui est accordé. 8) L'attention est attirée sur les références normatives citées dans cette publication. L'utilisation de publications référencées est obligatoire pour une application correcte de la présente publication. 9) L attention est attirée sur le fait que certains des éléments de la présente Publication de l IEC peuvent faire l objet de droits de brevet. L IEC ne saurait être tenue pour responsable de ne pas avoir identifié de tels droits de brevets et de ne pas avoir signalé leur existence. La Norme internationale IEC a été établie par le sous-comité 77C: Phénomènes transitoires de forte intensité, du comité d études 77 de l'iec: Compatibilité électromagnétique. Elle constitue la Partie 4-24 de l'iec Elle a le statut de publication CEM de base conformément au Guide 107 de l'iec. Cette deuxième édition annule et remplace la première édition parue en Cette édition constitue une révision technique. Cette édition inclut les modifications techniques majeures suivantes par rapport à l'édition précédente:
14 6 IEC FDIS IEC 2015 a) Un nouvel Article 5: Méthode de mesure pour filtres combinés IEMN-HA, qui est divisé comme suit: 5.1 Montage de vérification, 5.2 Montage de mesure, 5.3 Appareil de mesure, 5.4 Modes d'essai, 5.5 Procédures de mesure, 5.6 Evaluation des résultats d'essai avec introduction d'un critère de performance de filtre, 5.7 Rapport d'essai. b) Une nouvelle Annexe A informative: Etude de l'établissement d'un montage de mesure qui était basé sur l'article 5. c) Une nouvelle Annexe B informative: Méthode d'essai pour la détermination quantitative des comportements de réponse directs d'un dispositif coaxial de protection contre les surtensions. Le texte de la présente Norme est issu des documents suivants: FDIS 77C/XX/FDIS Rapport de vote 77C/XX/RVD Le rapport de vote indiqué dans le tableau ci-dessus donne toute information sur le vote ayant abouti à l'approbation de cette norme. Cette publication a été rédigée selon les Directives ISO/IEC, Partie 2. Une liste de toutes les parties de la série IEC 61000, publiées sous le titre général Compatibilité électromagnétique (CEM), peut être consultée sur le site web de l'iec. Le comité a décidé que le contenu de cette publication ne sera pas modifié avant la date de stabilité indiquée sur le site web de l'iec sous "http://webstore.iec.ch" dans les données relatives à la publication recherchée. A cette date, la publication sera reconduite, supprimée, remplacée par une édition révisée, ou amendée. Pour la présente publication, les Comités nationaux sont priés de noter que la date de stabilité est CE TEXTE EST INCLUS A TITRE D'INFORMATION POUR LES COMITES NATIONAUX. IL SERA SUPPRIME AU STADE PUBLICATION. IMPORTANT Le logo "colour inside" qui se trouve sur la page de couverture de cette publication indique qu'elle contient des couleurs qui sont considérées comme utiles à une bonne compréhension de son contenu. Les utilisateurs devraient, par conséquent, imprimer cette publication en utilisant une imprimante couleur.
15 IEC FDIS IEC INTRODUCTION La présente Norme fait partie de la série de normes IEC 61000, conformément à la structure suivante: Partie 1: Généralités Considérations générales (introduction, principes fondamentaux) Définitions, terminologie Partie 2: Environnement Description de l environnement Classification de l environnement Niveaux de compatibilité Partie 3: Limites Limites d émission Limites d'immunité Partie 4: Techniques d essai et de mesure Techniques de mesure Techniques d essai Partie 5: Guide d installation et d atténuation Guide d installation Méthodes et dispositifs d atténuation Partie 6: Normes génériques Partie 9: Divers Chaque partie est à son tour subdivisée en plusieurs parties, publiées soit comme normes internationales, soit comme spécifications techniques ou rapports techniques, dont certaines ont déjà été publiées en tant que sections. D autres seront publiées avec le numéro de la partie suivi d un tiret et d un second chiffre identifiant la subdivision (exemple: IEC ). L'IEC a lancé la préparation de méthodes normalisées de protection de la population civile contre les effets des environnements électromagnétiques haute puissance (HPEM). Ces effets peuvent entraîner la rupture de réseaux de communication, de réseaux d'alimentation électrique et de systèmes informatiques, etc. La présente partie de l'iec est une Norme internationale établissant les procédures d'essai exigées pour les dispositifs de protection pour perturbations conduites IEMN-HA, tels que les tubes à décharge, les varistances, les parafoudres à deux accès et les filtres combinés IEMN-HA. L'utilisation de la présente Norme est cependant indépendante des autres parties et sections de l'iec 61000, excepté pour les normes spécifiquement nommées en référence.
16 8 IEC FDIS IEC 2015 COMPATIBILITÉ ÉLECTROMAGNÉTIQUE (CEM) Partie 4-24: Techniques d essai et de mesure Méthodes d essai pour les dispositifs de protection pour perturbations conduites IEMN-HA 1 Domaine d'application La présente partie de l'iec définit les méthodes d'essai concernant les dispositifs de protection IEMN-HA contre les perturbations conduites. Elle inclut les éléments à deux bornes, tels que les tubes à décharge, varistances et les parafoudres à deux accès, tels que les filtres combinés IEMN-HA. Elle couvre les essais de caractéristiques de tension de claquage et de limitation de la tension résiduelle incluant les méthodes de mesure de tension résiduelle et/ou de courant résiduel, de la valeur de crête du temps de montée et de l'action racine dans le cas de variations très rapides de tension et de courant en fonction du temps. La présente Norme ne couvre pas les méthodes de mesure de l'affaiblissement d insertion. 2 Références normatives Les documents suivants sont cités en référence de manière normative, en intégralité ou en partie, dans le présent document et sont indispensables pour son application. Pour les références datées, seule l édition citée s applique. Pour les références non datées, la dernière édition du document de référence s applique (y compris les éventuels amendements). IEC , Compatibilité électromagnétique (CEM) Partie 2-10: Environnement Description de l environnement IEMN-HA Perturbations conduites 3 Termes, définitions et abréviations Pour les besoins du présent document, les termes, définitions et abréviations suivants s'appliquent. 3.1 Termes et définitions dispositif en traversée dispositif à deux accès, conçu pour envoyer un signal à travers une barrière électromagnétique (blindage) Note 1 à l'article: Il est généralement en bon contact électrique avec la barrière et possède un accès de chaque côté de cette dernière, maintenant ainsi son isolation tube à décharge dispositif comprenant deux ou trois électrodes métalliques hermétiquement protégées de façon à contrôler le mélange de gaz et sa pression et destiné à protéger un appareil ou le personnel contre des tensions transitoires élevées IEMN-HA impulsion électromagnétique à haute altitude impulsion électromagnétique produite par une explosion nucléaire en dehors de l'atmosphère de la Terre