Source: http://homedocbox.com/Environmental_Safety/96829003-University-of-houston-master-construction-specifications-insert-project-name-section-dry-pipe-fire-sprinkler-system-part-1-general.html
Timestamp: 2020-07-15 11:54:59
Document Index: 73994464

Matched Legal Cases: ['ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 2', 'ART 3', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'ART 1', 'art 5', 'ART 1', 'ART 1']

University of Houston Master Construction Specifications Insert Project Name SECTION DRY-PIPE FIRE SPRINKLER SYSTEM PART 1 - GENERAL - PDF Free Download
University of Houston Master Construction Specifications Insert Project Name SECTION DRY-PIPE FIRE SPRINKLER SYSTEM PART 1 - GENERAL
Download "University of Houston Master Construction Specifications Insert Project Name SECTION DRY-PIPE FIRE SPRINKLER SYSTEM PART 1 - GENERAL"
Duane Norton
1 SECTION DRY-PIPE FIRE SPRINKLER SYSTEM PART 1 - GENERAL 1.1 RELATED DOCUMENTS: A. The Conditions of the Contract and applicable requirements of Division 1, "General Requirements", and Section , "Mechanical General Provisions", govern this Section. 1.2 DESCRIPTION OF WORK: A. This Section of the Specification includes providing all labor and materials for the installation of a hydraulically calculated automatic, dry-pipe sprinkler system(s) in areas as specified herein and in Section , "Fire Protection Systems", and as shown on the Drawings, complete in all respects and ready for operation. The work includes the design of a dry-pipe automatic sprinkler system, complete and ready for operation. Design and installation of the sprinkler system shall be such that no parts interfere with general construction, doors, windows, heating, plumbing, air conditioning systems or electrical equipment. B. The Work shall be installed in accordance with the Drawings and Specifications. All devices and equipment shall be listed by Underwriters' Laboratories, Inc. or Factory Mutual-approved, individually and as a system, as applicable. C. Sprinkler heads shall be spaced, located, and positioned as shown on the Architectural reflected ceiling plans, where shown, as specified herein and as required to suit the building partition layout according to NFPA 13. Piping sizes and configurations shall be on the basis of hydraulic calculations. Where head layouts shown on the Drawings or requirements specified herein are more stringent than NFPA requirements, the more stringent requirements shall apply. Special consideration of locations or conditions shall conform to NFPA 13. D. The preference of the University is to connect to the campus Fire Water Distribution System (FWDS) provided Code compliant combination wet automatic fire sprinkler and where possible, automatic standpipe systems that do not contain alarm valves or local alarm devices, and a minimum 10 psig or 10% safety factor, whichever is greater, without requiring a building fire pump. E. Provide a complete automatic sprinkler system as defined by the latest edition of NFPA 13. All fire sprinkler systems installed on campus are required to be wet pipe systems unless the area being protected cannot be maintained above 40 degrees F, as required per NFPA 13. These areas will require a dry pipe system to be installed. Antifreeze systems of any size are not permitted on campus. Rooms or areas where it is not desirable to have water filled piping within the room, such as special collections, computer rooms, etc. may utilize double interlock pre-action systems. Use of pre-action systems must be approved by the University prior to system design. F. Zone the dry-pipe sprinkler system as shown on the Drawings. G. Coordinate the location of sprinkler heads and piping such that it does not interfere with the installed ceiling configuration or other building construction and equipment. 1.3 HYDRAULIC CALCULATIONS: A. Hydraulic calculations shall be prepared in accordance with Chapter 23 of NFPA 13 with the following exceptions: 1. Pipe friction losses may be calculated by using the nearest foot for all piping over one foot (1') in length. Horizontal lengths less than one foot (1') may be neglected. Vertical length less than one foot (1') shall be included for elevation purposes only. 2. Flows shall be calculated to the nearest whole gallon. Dry-Pipe Fire Sprinkler Systems
2 3. Velocity pressures may be neglected. 4. Velocities in underground piping shall not exceed 16 per second. Velocities in all other piping shall not exceed 20 per second. Velocities in standpipes must be calculated based on the combined sprinkler flow and hose flow. 5. Total sprinkler system flow shall not exceed 110% of the required flow. 6. The sprinkler/standpipe risers accommodate both the sprinkler and standpipe hose stream flows. Each riser shall accommodate 250 gallons per minute flow for standpipe hose stream. 7. Hydraulic calculations shall be performed by a State of Texas Licensed Responsible Managing Employee (RME) in the direct employ of the fire protection contractor. 8. Provide 10 psi safety factor for all sprinkler system hydraulic calculations. 9. No flexible drop sprinkler heads will be allowed. 1.4 QUALITY ASSURANCE: A. Contractor: The fire protection system shall be designed and installed by a fire protection contractor who is licensed by the State of Texas to perform fire protection work of the type specified for this project. The fire protection contractor shall have a minimum of 5 years of experience in the installation of fire protection work of the type specified for this project. B. Applicable Publications: The University, the International Building Code, National Fire Codes as published by the National Fire Protection Association (NFPA), State Fire Marshal, and the University of Houston Fire Marshal s requirements contain fire protection criteria and requirements for the design of all fire suppression systems. The publications listed below form a part of this Specification to the extent referenced. The publications are referred to in the text by basic designation only. 1. National Fire Protection Association (NFPA): a. NFPA 13- Standard for the Installation of Sprinkler Systems. b. NFPA 14- Standard for the Installation of Standpipe and Hose System. c. NFPA 20- Standard for the Installation of Centrifugal Fire Pumps. d. NFPA 24- Standard for the Installation of Private Fire Service Mains. e. NFPA 70- National Electrical Code. 2. Underwriters' Laboratories, Inc.: a. Fire Protection Equipment Directory (Latest Addition). 3. Factory Mutual Engineering Corporation (FM): a. Approval Guild (Latest Addition). 4. American National Standards Institute (ANSI): a. Z 53 Safety Color Code for Marking Physical Hazards. b. A 14 Safety Requirements for Fixed Ladders. 5. Materials shall be installed in accordance with NFPA 13. All valves, fittings, hose, sprinkler heads, and equipment shall be UL or FM-labeled. All necessary points of city connections shall be matched to city equipment. 6. Acceptable Manufacturers: The model numbers listed in the Specifications establish a level of quality and material. The following manufacturers are acceptable subject to compliance with the requirements of these Specifications. a. Sprinkler Equipment: 1) Viking Corporation. Dry-Pipe Fire Sprinkler Systems
3 1.5 SUBMITTALS: 2) Grinnell Fire Protection Systems Co., Inc. 3) Automatic Sprinkler Corporation. 4) Firematic Sprinkler Devices, Inc. 5) Reliable Automatic Sprinkler Co. A. The University of Houston Project Manager shall review and distribute all submittals for approval by the University insurer, the U of H Fire Marshal, the Owner s representative, and others as appropriate. B. Refer to provisions established in the Project Specifications and in related section of Division 01 General Requirements. All product data shall be submitted under provisions of Division 01. C. Shop drawing submittals shall include, but not be limited to: 1. Cut sheets marked to clearly indicate all fire protection system materials, accessories and manufacturers to be used, including, but not limited to dry pipe valve assemblies, pipe and fittings, pipe hangers and supports, valves, sprinkler heads, specialties, waterflow switches, valve supervisory switches, and other required materials. This shall include cut sheets on all grooved piping system components and all manufacturers which will be used on the project. 2. Samples of sprinkler heads to be furnished. 3. Preliminary submittal drawings showing all proposed sprinkler head locations for Architect/Engineer approval and including a layout and details sufficient to indicate the coordination of the location of sprinkler heads with the installed ceiling configuration shall be provided. 4. The Contractor shall submit detailed and accurate shop drawings prepared in accordance with NFPA 13, NFPA 14 (if applicable), and NFPA 24 for approval of all equipment to be constructed and installed. Shop drawings shall identify all materials and list all equipment to be used. Shop drawings shall include ceiling grid or reflected ceiling layout and shall be coordinated with other trades prior to submittal. Final fire protection system shop drawings showing all piping sizes and elevations, sprinkler head types and hydraulic calculations. Piping shall be sized and elevation of mains shall be indicated. Drawings shall be approved by state and local authorities prior to being submitted. Drawings shall be in accordance with NFPA 13 and NFPA 20 shall be submitted to the Engineer for approval prior to fabrication of piping. Hydraulic calculations shall be a part of this submittal. A fire pump characteristic curve for the building fire pump shall be a part of this submittal. 5. Hydraulic calculations for sprinkler systems shall comply with NFPA 13 and shall include comprehensive hydraulic data sheets. Provide a 10 psi or 10% whichever is greater safety factor for all sprinkler system hydraulic calculations. 6. No work shall be performed until the University has approved the shop drawings, calculations, and data sheets. The Contractor is solely liable for any work performed prior to this approval. 7. The submittal shall include a statement from the sprinkler contractor certifying that the design meets the hydraulic design parameters stated in this Specification. 8. Additional items as specified in Section and Section PRODUCT DELIVERY, STORAGE AND HANDLING: A. Deliver sprinkler system components in factory-fabricated water resistant packaging. B. Handle sprinkler system components carefully to avoid damage to components, enclosures, and finish. C. Store sprinkler system components in a clean, dry space and protect from weather. Dry-Pipe Fire Sprinkler Systems
4 PART 2 - PRODUCTS 2.1 SYSTEM DESCRIPTION: A. The dry-pipe sprinkler system shall be a fixed water type fire protection sprinkler system of the air charged type which automatically controls the water supply to fusible sprinkler heads for control of fire. No flexible drop sprinkler heads will be allowed. B. Sprinklers shall be listed or FM approved and shall not include O-rings seals. Any sprinkler that incurs damage, is painted, or is sprayed with any obstructive material during construction shall be replaced at no cost to the University. Installation of sprinklers shall be coordinated with other work, including duct and electric fixture installation, to prevent sprinkler obstructions. C. Sprinklers located less than eight feet above finished floor or that may be subject to mechanical damage shall be provided with guards listed for use with the model of sprinkler installed. D. Quick-response sprinklers are required throughout all light-hazard occupancies, and may also be installed in ordinary-hazard occupancies for the quick-response hydraulic design area reduction per NFPA 13 for utilizing quick-response sprinklers. Extended coverage sprinklers may be utilized if proven in the hydraulic calculations. E. Where required by the project, sprinklers shall be centered in two directions in ceiling tiles. Pendent sprinklers required to be placed in the center of ceiling tiles, shall be supplied from a return bend that connects to an outlet at the top of the fire sprinkler branch line piping. F. Main electrical equipment rooms may have alternate protection such as a pre-action, dry sprinkler systems or chemical suppression system. Approval must be sought by appropriate department in cooperation with the UH Fire Marshal s Office. G. The sprinkler system shall be designed to meet the more stringent of the requirements of NFPA 13 or the following requirements: 1. Storage rooms and mechanical equipment room shall be hydraulically calculated and designed to provide 0.18 gpm/sf over the hydraulically most remote 3900 square foot area (Ordinary Hazard Group 3) or over the entire area, whichever is less. 2. Parking garage and ramps shall be hydraulically calculated and designed to provide 0.15 gpm/sf over the hydraulically most remote 2600 square foot area (Ordinary Hazard Group 1) or over the entire area, whichever is less. 3. Minimum design shall be hydraulically calculated and designed to provide 0.12 gpm/sf over the hydraulically most remote 3900 square foot area. H. All sprinkler heads in general shall be in a straight line, parallel to the lines of the building and shall be located in the approximate center of ceiling tiles. [Sprinkler heads in public finished areas shall be located exactly (double swing connection) where shown on the Architectural reflected ceiling plans.] Sprinkler head quantities, where shown, are the minimum which must be provided. If additional heads are required to meet NFPA 13, the location of additional heads must be approved by the Architect. The Contractor shall submit Sprinkler Head locations to the Architect and Engineer for location and type approval prior to completing the sprinkler system design, unless otherwise instructed, in writing, by the Architect. I. Sprinkler heads in rooms with electrical equipment shall be located as far as code requirements allow from electrical equipment. 2.2 SYSTEM COMPONENTS: A. System components for each zone shall include, but not be limited to: 1. Dry-pipe valves and trim. 2. Main drain valves. Dry-Pipe Fire Sprinkler Systems
5 3. Air supplies. 4. Pressure switch. 5. Alarm test valve. 6. Waterflow pressure switches. 7. Valve supervisory switches. 8. Piping. 9. Sprinkler heads. 2.3 DRY PIPE VALVES: A. Valve: Provide a 175 psi WWP rated, bronze fitted, cast iron body dry-pipe valve assembly with EPDM seats, spring-loaded latching clapper and required tapped trim connections. Valve shall be Viking Model E, Reliable Model D, or an approved equal. B. Trim: Provide valve with all required trim including, but not limited to, drip check valve, drain cup, reset bar, alarm test shutoff valve, drain check valve, accelerator, variable pressure retard, air pressure switch, and other required trim. 2.4 AIR SUPPLIES: A. Dry pipe systems shall be filled from a constant source of air (if shown on the drawings) or from a high capacity portable air compressor. The air pressure in the system shall be maintained by a selfcontained air pressure maintenance device which is set at design pressure. To automatically maintain the design air pressure a maintenance air compressor shall be provided and shall operate on 120 volt, 20 ampere, single phase power. A pressure switch shall be provided to turn the compressor off when the design air pressure is reached, and on when the pressure falls below the design air pressure. 2.5 PIPE AND FITTINGS: A. Refer to Section for pipe and fitting requirement. 2.6 PIPING FABRICATION/SHOP DRAWINGS: A. Piping fabrication/shop drawings shall be submitted for all fire protection and sprinkler piping. Refer to Section for additional requirements. 2.7 PIPE HANGERS AND SUPPORTS: A. Refer to Section for pipe hanger and support requirements. 2.8 SLEEVES AND ESCUTCHEONS: A. Refer to Section for pipe sleeve and escutcheon requirements. 2.9 VALVES: A. Refer to Section for fire protection valve requirements SPRINKLER HEADS/SPECIALTIES: A. Unless otherwise specified, sprinkler heads shall have 165³F ordinary degree rating. Heads located within the air streams of heat emitting equipment and located at the top of elevator shafts shall be selected for proper temperature rating. Corrosion-resistant sprinkler heads shall be installed where they are exposed to weather, moisture, or corrosive vapors. Heads installed where they might receive mechanical injury or are less than 7 above the floor level shall be protected with approved guards in accordance with NFPA 13. Sprinkler guards shall be provided for sprinklers in electrical Dry-Pipe Fire Sprinkler Systems
6 closets. Sprinklers in areas with suspended ceilings shall be pendant type, with pipe and fittings located above the suspended ceiling. No flexible drop sprinkler heads will be allowed. B. Sprinkler heads in finished areas shall be Reliable Model G semi-recessed chrome-plated heads with a [white] [polished chrome-plated] escutcheon or an approved equal. Sprinkler head shall be UL-listed and FM-approved with the provided escutcheon plate. C. Sprinkler heads in the unfinished areas shall be Reliable Model G or approved equal brass, upright pendant heads as required. D. Pendant sprinkler heads for dry pipe sprinkler systems shall be Reliable Model A, chrome plated dry pendant sprinkler heads with pendant length as required. E. Provide a metal cabinet containing a stock of spare sprinkler heads of all types and ratings installed. The cabinet shall be located where the temperature will not exceed 100 F; the location shall be approved by the Owner. The number of spare sprinklers shall conform to Section of NFPA PRESSURE SWITCH: A. An auxiliary pressure switch shall be provided to provide a loss of air flow alarm to the sprinkler control panel VALVE SUPERVISORY SWITCHES: A. All valves that affect the flow of fire protection water to any area shall be supervised. Switches shall be Potter Electric Signal Co. Model OSYS-U or and approved equal. B. Supervisory switches shall be furnished and installed by this Contractor and wired by Division 28. Coordinate wiring of all switches with Division WATERFLOW PRESSURE SWITCHES: A. Viking or equal waterflow pressure switches, with adjustable retard feature shall be provided in the supply pipe to each zone for remote alarm. Switch shall be double-pole single-throw type and shall be rated at least 7 amperes at 125/250 volts. B. Waterflow pressure switches shall be furnished and installed by this Contractor and wired by Division 16. Coordinate wiring of flow switches with Division BUILDING FIRE ALARM SYSTEM INTERFACE: A. Each dry-pipe system shall provide a trouble signal output to the Building Fire Alarm System (wiring by Division 28) whenever a loss of air condition exists in the dry-pipe system. B. Each dry-pipe system shall provide an alarm signal output to the Building Fire Alarm System (wiring by Division 28) whenever there is waterflow in the zone. C. Each valve which controls the flow of sprinkler system water shall be monitored by the Building Fire Alarm System (wiring by Division 28). PART 3 - EXECUTION 3.1 INSTALLATION: A. General: Refer to Section for installation of fire protection system piping and other general requirements. B. Dry-pipe System: Install and test the dry-pipe system in accordance with the system manufacturer's written installation instructions. Locate dry-pipe valves and trim in a heated space. C. Inspector's Test Valves: Test valves shall be provided in accordance with Section 22 of NFPA 13, supplied from the highest and most remote part of the system in relation to the riser assembly, and shall discharge to the outside of the building or to a building drain. Test valves shall be conveniently Dry-Pipe Fire Sprinkler Systems
7 accessible within 7'of floor. Inspector's test connections must be provided for all zones, so that the waterflow switch for the zone can be tested. D. Protection During Construction: Provide necessary fire protection during construction in accordance with NFPA and applicable codes. 3.2 CLEANING: A. All fire protection piping shall thoroughly flushed out to remove any slag or debris prior to being tested or put into service. 3.3 SYSTEM PRESSURE REDUCTION: A. Where fire system pressures exceed 175 psi, provide of the pressure reducing valves to regulate the pressure at that point to 165 psi. 3.4 TESTS AND INSPECTIONS: A. Inspections, examinations and tests required by the authorities or agencies specified shall be arranged and paid for by the Fire Protection Subcontractor, as necessary, to obtain complete and final acceptance of the system as installed. The certificates of inspection shall be in quadruplicate, and shall be delivered to the Engineer for review and distribution. B. Sprinkler systems shall be hydrostatically tested by the Contractor upon completion of the installation as required by NFPA 13 in the presence of the UH Fire Marshal. When hydrostatic and alarm tests have been completed and all necessary corrections made, a material and test certification shall be provided in accordance with NFPA 13. Final inspection shall include full flow testing through the inspector's test connection. Actuation of the flow switch shall occur within one minute of opening of the inspector's test valve. The final tests may be witnessed by the Engineer and shall be witnessed by the UH Fire Marshal. C. Sprinkler system zone control assemblies shall be tested to demonstrate proper operation of the flow switch and valve supervisory switch. D. Dry-pipe sprinkler system shall be tested to demonstrate that system charge time is within the requirements of NFPA 13. E. Arrange and pay for all tests and inspections required by UH Fire Marshal. 3.5 PERIODIC INSPECTION SERVICE: A. Refer to Section for requirements. B. This agreement shall be executed at no cost to the Owner and shall include four inspections of the entire sprinkler system during the warranty period, each with a NASFCA "Report of Inspection to the Owner". The final inspection shall include operation and lubrication of all valves, cleaning of all alarm valves and operational testing of all system Electrical and alarm components. 3.6 TRAINING: A. The system installation contractor shall provide a minimum of 4 hours of training for the Owner in operation and maintenance of the dry-pipe sprinkler system. 3.7 IDENTIFICATION: A. Refer to Section , "Basic Materials and Methods", for applicable painting, nameplates and labeling requirements. All drain valves, test valves, and other system valves shall be clearly labeled as to use and the fact that they are fire protection system valves. END OF SECTION Dry-Pipe Fire Sprinkler Systems
A. Hydraulic calculations shall be prepared in accordance with Chapter 23 of NFPA 13 with the following exceptions:
SECTION DRY PIPE SPRINKLER SYSTEMS MODEL F SERIES DRY VALVE
SECTION 21 1316 DRY PIPE SPRINKLER SYSTEMS MODEL F SERIES DRY VALVE PART 1 GENERAL 1.01 SECTION INCLUDES A. Dry-pipe sprinkler system. B. System design, installation, and certification. C. Fire department
C. All components of the systems described shall meet the requirements as stated herein and shall be approved by the Architect and Consultant.
SECTION 218800 - FIRE PROTECTION 1. GENERAL A. Provisions of Division 1, GENERAL REQUIREMENTS, and Section 230000, MECHANICAL GENERAL CONDITIONS, and Section 230050, SEISMIC PROTECTION are a part of this
SECTION DRY PIPE SPRINKLER SYSTEMS MODEL G SERIES DRY VALVE
SECTION 21 1316 DRY PIPE SPRINKLER SYSTEMS MODEL G SERIES DRY VALVE PART 1 GENERAL 1.01 SECTION INCLUDES A. Dry-pipe sprinkler system. B. System design, installation, and certification. C. Fire department
SECTION WET-PIPE SPRINKLER SYSTEMS EASY RISER CHECK VALVE
SECTION 21 1313 WET-PIPE SPRINKLER SYSTEMS PART 1 GENERAL 1.01 SECTION INCLUDES A. Wet-pipe sprinkler system. B. System design, installation, and certification. C. Fire department connections. 1.02 RELATED
PART 1 GENERAL 1.01 DESCRIPTION A. The provisions of the General Requirements, Supplementary Requirements, and Division 1 apply to the plumbing work specified in this Division. B. The requirements of this
SECTION 213100 WET PIPE FIRE PROTECTION SPRINKLER SYSTEM PART 1 - GENERAL 1.01 GENERAL REQUIREMENTS A. The requirements of the General Conditions and Supplementary Conditions apply to all work herein.
B. Product Data: Provide manufacturers catalogue information. Indicate valve data and ratings.
DIVISION 21 21 05 00 COMMON WORK RESULTS FOR FIRE SUPPRESSION PART 1 GENERAL 1.1 SECTION INCLUDES A. Pipe, fittings, sleeves, escutcheons, seals, and connections for sprinkler systems. 1.2 RELATED REQUIREMENTS
Gas Station & C Store SECTION CWM Job No
SECTION 21 1300 - PART 1 - GENERAL 1.1 WORK INCLUDED A. Provide labor, materials, equipment and services to perform operations required for the complete installation and related Work as required in Contract
B. Section Identification for Fire Suppression Piping and Equipment.
SECTION 211300 - FIRE SUPPRESSION SPRINKLERS PART 1 GENERAL 1.1 SECTION INCLUDES A. Dry-pipe sprinkler system. B. System design, installation, and certification. C. Fire department connections. 1.2 RELATED
FIRE PROTECTION. 1. Vertical fire pumps shall not be used at the University.
15500 - FIRE PROTECTION PART I DESIGN GUIDELINES A. General 1. Vertical fire pumps shall not be used at the University. 2. coupling piping shall be permitted for sprinkler and standpipe systems only. B.
A. Section includes wet-pipe sprinkler system, system design, installation, and certification.
SECTION 21 13 13 WET-PIPE SPRINKLER SYSTEMS PART 1 - GENERAL 1.1 SUMMARY A. Section includes wet-pipe sprinkler system, system design, installation, and certification. 1.2 REFERENCES A. General: Comply
THE JAMES RUSHTON EARLY LEARNING AND FAMILY SUCCESS CENTER #2616 ISSUE FOR CONSTRUCTION
SECTION 21 1301- FIRE-SUPPRESSION SYSTEMS PART 1 - GENERAL 1.1 SUMMARY: A. This Section includes fire-suppression piping and equipment for the following building systems: 1. Wet-pipe, fire-suppression
West District Library Section Campeau Drive, Ottawa SPRINKLER SYSTEMS City of Ottawa Project No. CR Page 1 of 8
City of Ottawa Project No. CR006230 Page 1 of 8 PART 1 - GENERAL 1.1 Reference Standards.1 Conform to the following:.1 Provincial and municipal building and fire regulations as approved by Provincial Fire
2. Welding Materials and Procedures shall conform to the ASME Code.
PART 1 GENERAL 1.01 Scope of Standard A. The design guidelines contained herein include the requirements for systems, materials, fittings and valves utilized for fire protection systems at Sam Houston
D. The work addressed in this section consists of a fire protection system, which may include coordination with one or more of the following:
PART 1 GENERAL 1.01 Scope of Standard A. This standard provides general requirements of Sam Houston State University for the design and construction of standpipe systems to include combination standpipe
CubeSmart Gulf Breeze Storage AUTOMATIC FIRE SPRINKLER SYSTEM
SECTION 21 0000 AUTOMATIC FIRE SPRINKLER SYSTEM PART 1 GENERAL 1.1 QUALITY ASSURANCE A. Codes and Standards: 1. FBC (Florida Building Code 2015) 2. FBC (Florida Fire Code 2015) 3. NFPA #13R (Standard for
1.1 Refer to Section for General Mechanical Requirements. 1.3 Refer to Section for Pipe and Equipment Identification Requirements.
FIRE PROTECTION GENERAL INFORMATION 1.1 Refer to Section 230000 for General Mechanical Requirements. 1.2 Refer to Section 230529 for Hangers and Supports. 1.3 Refer to Section 230553 for Pipe and Equipment
SECTION SPRINKLER SYSTEMS
SECTION 15325 SPRINKLER SYSTEMS PART 1 - GENERAL 1.1 SECTION INCLUDES A. Wet-pipe sprinkler systems. B. Preaction sprinkler systems. C. System design, installation, and certification. D. Fire department
SECTION DRY-PIPE SPRINKLER SYSTEMS
SECTION 21 1300 S PART 1 -GENERAL 1.01 RELATED DOCUMENTS A. Drawings and general provisions of the Contract, including General and Supplementary Conditions and Division 01 Specification Sections, apply
SECTION WET AUTOMATIC FIRE SPRINKLER SYSTEMS
SECTION 15501 WET AUTOMATIC FIRE SPRINKLER SYSTEMS PART 1 GENERAL 1.01 SUMMARY A. Section Includes: Wet automatic fire sprinkler systems including fire pump, fire pump controller, alarms, safety devices,
B. The sprinkler system shall be designed to meet the more stringent of the requirements of NFPA 13 and FM Global requirements.
SECTION 21 13 13 FIRE PROTECTION SPRINKLER SYSTEMS PART 1 - GENERAL 1.01 SUMMARY A. Section includes labor and materials for the installation of a hydraulically calculated automatic, wet-pipe sprinkler
SECTION WET FIRE SPRINKLER SYSTEMS
SUNY GENESEO 211310-1 PART 1 - GENERAL 1.1 WORK INCLUDED A. Provide labor, materials, equipment and services to perform operations required for the complete installation and related Work as required in
WET AUTOMATIC FIRE SPRINKLER SYSTEMS
COBB COUNTY SCHOOLS /S&A % BID DOCUMENTS 2/18/11 SECTION SPRINKLER SYSTEM
SECTION 21 10 00 PART 1 - GENERAL 1.1 CODES A. Work shall conform to NFPA 13 Sprinkler Systems, 2002 Edition and NFPA 24 Outside Protection, 2002 Edition. NFPA 14 Standpipe Systems, 2000 Edition and International
SECTION WET-PIPE SPRINKLER SYSTEMS
SECTION 21 13 13 WET-PIPE SPRINKLER SYSTEMS PART 1 - GENERAL 1.1 SCOPE OF WORK A. Design, installation and testing shall be in accordance with NFPA 13 except for specified exceptions. B. The demolition
SPRINKLERS TABLE OF CONTENTS
SPRINKLERS TABLE OF CONTENTS SECTION 21 13 13 WET PIPE SPRINKLER SYSTEMS SECTION 211313 - WET PIPE SPRINKLER SYSTEMS PART 1 GENERAL 1.1 RELATED DOCUMENTS A. Drawings and general provisions of the Contract,
SECTION FIRE-SUPPRESSION STANDPIPES
PART 1 - GENERAL 1.1 DESCRIPTION Fire-suppression wet and manual dry standpipes. 1.2 SCOPE OF WORK SECTION 21 12 00 A. Design, installation and testing shall be in accordance with NFPA 14 except for specified
SECTION FIRE PROTECTION. A. Examine all conditions as they exist at the project, prior to submitting a bid for the work of this section
PART 1 - GENERAL 1.00 GENERAL PROVISIONS A. Examine all conditions as they exist at the project, prior to submitting a bid for the work of this section 1.01 DESCRIPTION OF WORK A. Work Included: Provide
ADDENDUM NO. 3 March 19, 2018
ADDENDUM NO. 3 March 19, 2018 PROJECT: MT. VIEW ELEMENTARY CASSIA SCHOOL DISTRICT NO 151 BURLEY, IDAHO The following addenda apply to the Project Manual and / or Drawings for this project and shall be
Division 21: FIRE SUPRESSION WET-PIPE SPRINKLER PROTECTION SYSTEM. The Academy Sept Table of Contents 1 Division 21
Division 21: FIRE SUPRESSION 21 1313 WET-PIPE SPRINKLER PROTECTION SYSTEM Table of Contents 1 Division 21 SECTION 21 1313 WET-PIPE SPRINKLER PROTECTION SYSTEM PART 1 - GENERAL 1.1 RELATED DOCUMENTS A.
SECTION (13900) - FIRE SUPPRESSION SYSTEMS
PART 1 GENERAL 1.01 SUMMARY SECTION 21 10 00 (13900) - FIRE SUPPRESSION SYSTEMS A. Section Includes: 1. Pipe and Fittings. 2. Sprinklers. B. Related Documents: 1. Marriott s Fire Protection and Life Safety
PART 1 GENERAL 1.01 Scope of Standard A. This standard provides general requirements of The University of Texas at Austin for fire-extinguishing systems other than water-based fire suppression systems.
A. This section includes design and performance information for fire protection and suppression systems.
SECTION 21 00 10: FIRE PROTECTION SYSTEM DESIGN 1. SUMMARY A. This section includes design and performance information for fire protection and suppression systems. 2. GENERAL A. All fire protection materials
Port of St Helens SIA Aircraft Hanger Scappoose, OR
Port of St Helens SIA Aircraft Hanger Scappoose, OR AUTOMATIC FIRE SPRINKLER SYSTEM REVISION 2 MARCH 12, 2018 Scope: Furnish and install foam and water fire protection system including underground entrance
DIVISION 21 FIRE SUPPRESSION SECTION FIRE PROTECTION SPECIALTIES
DIVISION 21 FIRE SUPPRESSION PART 1 GENERAL 1.01 DESCRIPTION A. Provide UL listed, FM approved listed fire protection specialties or accessories as required by either the equipment manufacturer or the
MLA Architects Pierz Public Schools ISD #484 Healy High School Multi-Purpose & Choir Additions Pioneer Elementary School Class Room Addition Pierz, MN
DIVISION 21 - FIRE SUPPRESSION (REFER TO SECTION 23 05 00 FOR BASIC FIRE SUPPRESSION REQUIREMENTS) 21 05 00 Common Work Results for Fire Suppression 21 13 13 Wet-Pipe Sprinkler Systems END OF SECTION FIRE
SECTION 13900 SPRINKLER SYSTEMS PART 1 - GENERAL 1.1 RELATED DOCUMENTS A. Drawings and general provisions of the Contract, including General and Supplementary Conditions and Division 1 Specification Sections,
TABLE OF CONTENTS DIVISION 21- FIRE SUPPRESSION PAGES SECTION WATER BASED FIRE PROTECTION SYSTEMS... 5
DOC Cremer Heating and Hot Water Plant Project Number: M 1411-04 TABLE OF CONTENTS DIVISION 21- FIRE SUPPRESSION PAGES SECTION 21 30 00- WATER BASED FIRE PROTECTION SYSTEMS... 5 SECTION 22 40 00 -PLUMBING
1.2 CODES AND REGULATIONS A. Sprinkler system design, equipment, materials, devices, and installation shall conform to the following:
SECTION 21 10 00 - WATER-BASED FIRE-SUPPRESSION PART I - GENERAL 1.1 SUMMARY A. Inclusion of sprinkler and standpipe systems shall be as determined by NFPA National Fire Code pamphlet 101 and program statement.
SECTION 211313 - WET-PIPE SPRINKLER SYSTEMS PART 1 - GENERAL 1.1 SUMMARY A. Section Includes: 1. Pipes, fittings, and specialties. 2. Fire-protection valves. 3. Fire-department connections. 4. Sprinklers.
SECTION 21 30 00 FIRE PUMPS GENERAL This standard provides general requirements of The University of South Alabama in Mobile Alabama for fire pumps. This document is not intended to serve as a guide specification.
DIVISION 21 FIRE SUPPRESSION FIRE SUPRESSION
DIVISION 21 FIRE SUPPRESSION 21 00 00 FIRE SUPRESSION 21 01 00 Operation and Maintenance of Fire Suppression 21 01 10 Operation and Maintenance of Water Based Fire Suppression Systems 21 01 20 Operation
SECTION 21 13 13 WET-PIPE SPRINKLER SYSTEMS PART 1 - GENERAL 1.1 RELATED DOCUMENTS A. Drawings and general provisions of the Contract, including General and Supplementary Conditions and Division 01 Specification
SECTION WATER BASED FIRE SUPPRESSION SYSTEMS
PART 1: GENERAL 1.01 Scope of Standard A. This standard provides general guidance concerning the specific preferences of Texas State University-San Marcos for automatic fire sprinkler and standpipe systems.
SECTION 21 13 13 PART 1 - GENERAL 1.1 SCOPE OF WORK A. Design, installation and testing shall be in accordance with NFPA 13 except for specified exceptions. B. The design and installation of a hydraulically
Ul611-0l SECTION 211316- DRY-PIPE SPRINKLER SYSTEMS PARTl-GENERAL 1.1 RELATED DOCUMENTS Drawings and general provisions of the Contract, including General and Supplementary Conditions, and Division 1 Specification
SECTION 21 1314D - AUTOMATIC SPRINKLER SYSTEMS (DRY-PIPE) PART 1 - GENERAL 1.1 RELATED DOCUMENTS A. Drawings and general provisions of the Contract, including General and Supplementary Conditions and Division
DARTMOUTH COLLEGE DESIGN November 15, 2007 & CONSTRUCTION GUIDELINES
SECTION 15300 FIRE PROTECTION PART 1 DESIGN DIRECTIVES 1.1 DESIGN CRITERIA A. Dartmouth College is currently insured by Factory Mutual. References to the owner s insurance company in this specification
UC Santa Cruz Campus Design Guide. Includes the following sections: None DESIGN REQUIREMENTS
DIVISION 21 - FIRE SUPPRESSION Includes the following sections: None DESIGN REQUIREMENTS It is the policy of City of Santa Cruz to install fire sprinkler systems in all new construction/facilities. If
ADDENDUM #3 DATE: August 8, 2018 Page 1 of 1. The Curators of the University of Missouri
ADDENDUM #3 DATE: August 8, 2018 Page 1 of 1 TO CONTRACT DOCUMENTS ENTITLED: PROJECT MANUAL FOR: Women s and Children s Hospital New Water Service Main PROJECT NUMBER: CP172631 ADVERTISEMENT DATE: July
B. Related Sections: The following Sections contain requirements that relate to this Section.
SECTION 211313- FIRE-SUPPRESSION PIPING PART1 -GENERAL 1.1 RELATED DOCUMENTS A. Drawings and general prov1s1ons of the Contract, including General and Supplementary Conditions and Division 1 Specification
A. Standard-Pressure Piping System Component: Listed for 175-psig minimum working pressure.
B. Galvanized-Steel-Sheet Sleeves: inch minimum thickness; round tube closed with welded longitudinal joint.
(816) 373-4878 U1208-01/FAI29-029 (573) 751-2624 SECTION 2 105 17 - SLEEVES AND SLEEVE SEALS FOR FIRE-SUPPRESSION PIPING PART 1 - GENERAL 1.1 RELATED DOCUMENTS A. Drawings and general provisions of the
SECTION FIRE PROTECTION SYSTEMS
PART 1 - GENERAL 1.1 RELATED DOCUMENTS: SECTION 21 12 00 FIRE PROTECTION SYSTEMS A. The Conditions of the Contract and applicable requirements of Division 1, "General Requirements", and Section 23
SECTION 21 1314W - AUTOMATIC SPRINKLER SYSTEMS (WET PIPE SYSTEMS) PART 1 - GENERAL 1.1 RELATED DOCUMENTS A. Drawings and general provisions of the Contract, including General and Supplementary Conditions
SECTION ADDENDUM NO. 1 FIRE SPRINKLER SYSTEM
PART 1 - GENERAL 1.01 GENERAL DESCRIPTION A. Furnish all materials and labor for the detailed design and installation for new fire sprinkler wet pipe systems for Buildings A through R hereafter referred
DIVISION 21: FIRE SUPPRESSION WATER BASED FIRE SUPRESSION SYSTEMS
DIVISION 21: FIRE SUPPRESSION 21 1000 WATER BASED FIRE SUPRESSION SYSTEMS 21 1200 FIRE-SUPPRESSION DRY STANDPIPES 21 1313 WET PIPE SPRINKLER PROTECTION SYSTEM 21 1314 WET-PIPE AUTOMATIC SPRINKLER SYSTEM
Table of Contents 21 00 00 FIRE SUPPRESSION...2 A. REFERENCE ABBREVIATIONS... 2 B. GENERAL... 2 C. DESIGN REQUIREMENTS... 2 D. DOCUMENTATION... 2 21 08 00 FIRE SUPPRESSION COMMISSIONING...2 A. PIPE CLEANING...
SECTION 15300 - FIRE PROTECTION PART 1 - GENERAL 1.01 RELATED DOCUMENTS A. Basic Requirements: Provisions of Section 15010, BASIC MECHANICAL REQUIREMENTS, and Section 15030, ELECTRICAL REQUIREMENTS FOR
Western Michigan University Facilities Management Engineering Division
Western Michigan University Facilities Management Engineering Division Design Guidelines for Facilities Construction: DESIGN GUIDELINE DG21-1 Fire Suppression Systems & Equipment I. GENERAL... 1 A. General
SECTION Fire Pumps
SECTION 21 30 00 Fire Pumps PART 1 GENERAL 1.1 WORK INCLUDED A. Furnish, install and test a motor-driven fire pump, jockey pump, and controllers in the space provided and as shown in the contract drawings.
SECTION AUTOMATIC SPRINKLER PIPING
SECTION 15330 AUTOMATIC SPRINKLER PIPING ****** ***** **** *** ** * ** *** **** ***** ****** NOTE TO SPECIFIER: This section contains several types of automatic sprinkler piping. Some piping is allowed
UBC Technical Guidelines Section Edition Fire Protection General Requirements Page 1 of 6
Page 1 of 6 1.0 GENERAL 1.1 Related UBC Guidelines.1 Section 20 00 05 Mechanical - General Requirements.2 Section 22 05 00 Plumbing - General Requirements.3 UBC Standard Fire Hydrant Drawings.4 Section
Environmental Health & Safety Oklahoma State University FIRE SPRINKLER SYSTEM STANDARD Environmental Health and Safety University Health Services Suite 002 Stillwater, OK 74078 (405) 744-7241 www.ehs.okstate.edu
A. All Fire Suppression System design and installation shall comply with the most current and adopted version of NFPA 13.
21 10 00 PART 1 - GENERAL 1.01 SCOPE A. The following standards and procedures apply to the design and installation of all wet pipe and dry pipe sprinkler systems. The design of fire suppression systems
Montgomery County Government Building and Codes Department 350 Pageant Lane, Suite 309 Clarksville, TN 37040
Montgomery County Government Building and Codes Department 350 Pageant Lane, Suite 309 Clarksville, TN 37040 SPRINKLER SHOP DRAWINGS 2007 NFPA 13 and 2007 NFPA 24 Project: Listed items require sprinkler
DIVISION 21: FIRE SUPPRESSION SYSTEMS SECTION Fire Protection Systems Protecting Cold Storage and Unheated Warehouses
PART 1 - GENERAL 1.1 SCOPE A. Through Class III Commodity Classification, up to 12.2m of single, double or multiple row rack storage, up to 14.6m building height (VanQuish Fire Sprinkler System). Cartoned
SECTION FIRE SUPPRESSION SYSTEMS
PART 1 - GENERAL 1.1 RELATED DOCUMENTS A. Drawings and general provisions of the Contract, including General and Supplementary Conditions and Division 1 Specification Sections, apply to this Section. 1.2
ADMINISTRATIVE SERVICES 4202 E. FOWLER AVENUE, FPC110 PHONE: (813) 974-2625 FACILITIES PLANNING & CONSTRUCTION TAMPA, FLORIDA 33620-7550 WEBSITE: USF.EDU/FPC DESIGN & CONSTRUCTION GUIDELINES DIVISION 21
SECTION 211313 - WET-PIPE SPRINKLER SYSTEMS PART 1 - GENERAL 1.1 RELATED DOCUMENTS A. Drawings and general provisions of the Contract, including General and Supplementary Conditions and Division 01 Specification
SECTION 211000 - PART 1 - GENERAL 1.1 RELATED DOCUMENTS A. Related Documents: Drawings, Notice to Bidders, General Conditions, Project Coordination, RFP Format, Requested RFP Alternatives, Cutting and
SECTION PREACTION SPRINKLER SYSTEMS
PART 1 GENERAL SECTION 211316 - PREACTION SPRINKLER SYSTEMS 1.1 RELATED DOCUMENTS A. Drawings and general provisions of the Contract, including General and Supplementary Conditions and Division 01 Specification
University of Houston Master Construction Specifications Insert Project Name SECTION FIRE PROTECTION SYSTEMS PART 1 - GENERAL
SECTION 21 12 00 FIRE PROTECTION SYSTEMS PART 1 - GENERAL 1.1 RELATED DOCUMENTS: A. The Conditions of the Contract and applicable requirements of Division 1, "General Requirements", and Section 23 01 00,
SECTION : FIRE PROTECTION SYSTEMS
SECTION 21 00 10: FIRE PROTECTION SYSTEMS 1. GENERAL A. This section applies to the design and performance information for fire protection and suppression systems. B. All fire protection materials and
SECTION DRY-PIPE FIRE-SUPPRESSION SPRINKLERS
SECTION 13935 DRY-PIPE FIRE-SUPPRESSION SPRINKLERS PART 1 GENERAL 1.1 SUMMARY A. Includes But Not Limited To 1. Furnish and install complete fire sprinkler system as specified in Contract Documents. B.
APPENDIX H (DESIGN SUBMISSION CRITERIA)
APPENDIX H (DESIGN SUBMISSION CRITERIA) FIRE ALARM SYSTEM As per ACCORD standard Part 5, section 5.7 Fire Alarm System Design to be verified by ACCORD Chief Safety Inspector. Testing of the installation
2016 CDM Smith All Rights Reserved July 2016 SECTION FIRE PROTECTION - SPRINKLER AND STANDPIPE SYSTEMS
PART 1 GENERAL 1.01 SCOPE OF WORK SECTION 21 13 13 FIRE PROTECTION - SPRINKLER AND STANDPIPE SYSTEMS A. Furnish all labor, materials, equipment services and incidentals required to design and install properly
Revision May All designs must be submitted to FM Global for review and approval prior to issuing such for bids.
SECTION 211300 FIRE SUPPRESSION SYSTEMS 1.0 All new and renovated buildings shall be provided with automatic sprinklers throughout and fire standpipe systems. The design and installation of these systems
False Sense of Security???
IS YOUR SPRINKLER SYSTEM GIVING YOU A FALSE SENSE OF SECURITY? Best Practices in Fire Safety An ASSE Virtual Symposium March 1 & 2, 2011 Walter S. Beattie CSP, CFPS, CSHM False Sense of Security??? Fire
SECTION 15300 PART I - GENERAL 1.01 WORK INCLUDED A. Furnish all labor, materials, tools, and equipment to complete the automatic fire sprinkler system as hereinafter described, ready for service to the
CONSTRUCTION REQUIREMENTS Note: The buildings on the UCCS campus are divided into two categories: General Fund and Auxiliaries. General Fund Buildings include academic and administrative functions. Auxiliary
USACE / NAVFAC / AFCEC / NASA UFGS-21 21 03.00 10 February 2009) ---------------------------------- Preparing Activity: USACE Superseding UFGS-21 21 03.00 10 (April 2006) UNIFIED FACILITIES GUIDE SPECIFICATIONS
USACE / NAVFAC / AFCEC / NASA UFGS-21 13 17.00 10 (May 2009) Change 1-02/13 ------------------------------ Preparing Activity: USACE Superseding UFGS-21 13 17.00 10 (November 2008) UNIFIED FACILITIES GUIDE
Design and Construction Standards SECTION FIRE SUPPRESSION
SECTION 13900 FIRE SUPPRESSION PART 1 GENERAL 1.1 SCOPE A. The work under this section of the specifications consists of furnishing all materials, equipment, labor, testing, appurtenances, engineering
Page 1 of 8 CITY OF PASADENA FIRE DEPARTMENT INSTALLATION OF COMMERCIAL SPRINKLERS (Revised 12/10/2014) SCOPE: This standard applies to the design and installation of automatic fire sprinkler systems in
Public School Facilities Authority State of New Mexico 2019 Galisteo, Suite B Santa Fe, New Mexico 87505
Public School Facilities Authority State of New Mexico 2019 Galisteo, Suite B Santa Fe, New Mexico 87505 SPECIFICATIONS FOR FIRE PROTECTION SYSTEMS NEW MEXICO PUBLIC SCHOOLS November 7, 2005 . TABLE OF
PHYSICAL FACILITIES. 1 General. 2 Related Requirements. 5 Quality Assurance. 3 Wiring. 4 Submittals
1 General 1.1 Provide all material, labor, engineering and operations for the installation of complete and operable fire suppression systems as shown in the job scope and as specified herein. 1.2 Provide
AUTOMATIC FIRE SPRINKLER SYSTEM STANDARDS Development Standard #4.1 (Commercial Installations)
AUTOMATIC FIRE SPRINKLER SYSTEM STANDARDS Development Standard #4.1 (Commercial Installations) This standard applies to the design and installation of automatic fire sprinkler systems in conjunction with