Source: http://docplayer.fr/1743803-International-standard-norme-internationale.html
Timestamp: 2016-12-11 06:49:08
Document Index: 98397054

Matched Legal Cases: ['art 3', 'art 3', 'art 2', 'art 1', 'art 2', 'art 3', 'art 1', 'ART 2', 'ART 3', 'art 3', 'art 9', 'art 31', 'art 7', 'art 8', 'art 4', 'art 6', 'art 7', 'art 1', 'art 2', 'art 3', 'art 25', 'art 24', 'art 3', 'art 1', 'art 34', 'art 5', 'art 2', 'art 4', 'art 9', 'art 16', 'art 29', 'art 5', 'art 4', 'art 1', 'art 1', 'art 1', 'art 1', 'art 2', 'art 3', 'art 5', 'art 2', 'art 2', 'art 3', 'art 2', 'art 1', 'art 3', 'art 2']

⭐INTERNATIONAL STANDARD NORME INTERNATIONALE
Marie-Rose Raymond
1 INTERNATIONAL STANDARD NORME INTERNATIONALE IEC Edition Functional safety Safety instrumented systems for the process industry sector Part 3: Guidance for the determination of the required safety integrity levels Sécurité fonctionnelle Systèmes instrumentés de sécurité pour le secteur des industries de transformation Partie 3: Conseils pour la détermination des niveaux exigés d intégrité de sécurité INTERNATIONAL ELECTROTECHNICAL COMMISSION COMMISSION ELECTROTECHNIQUE INTERNATIONALE PRICE CODE CODE PRIX XA ICS ISBN Registered trademark of the International Electrotechnical Commission Marque déposée de la Commission Electrotechnique Internationale2 IEC:2003 CONTENTS FOREWORD...4 INTRODUCTION Scope Terms, definitions and abbreviations Risk and safety integrity general guidance General Necessary risk reduction Role of safety instrumented systems Safety integrity Risk and safety integrity Allocation of safety requirements Safety integrity levels Selection of the method for determining the required safety integrity level...15 Annex A (informative) As Low As Reasonably Practicable (ALARP) and tolerable risk concepts...16 Annex B (informative) Semi-quantitative method...20 Annex C (informative) The safety layer matrix method...28 Annex D (informative) Determination of the required safety integrity levels a semi-qualitative method: calibrated risk graph...34 Annex E (informative) Determination of the required safety integrity levels a qualitative method: risk graph...43 Annex F (informative) Layer of protection analysis (LOPA)...49 Figure 1 Overall framework of this standard...8 Figure 2 Typical risk reduction methods found in process plants...10 Figure 3 Risk reduction: general concepts...13 Figure 4 Risk and safety integrity concepts...14 Figure 5 Allocation of safety requirements to the Safety Instrumented Systems, non-sis prevention/mitigation protection layers and other protection layers...15 Figure A.1 Tolerable risk and ALARP...17 Figure B.1 Pressurized vessel with existing safety systems...21 Figure B.2 Fault tree for overpressure of the vessel...24 Figure B.3 Hazardous events with existing safety systems...25 Figure B.4 Hazardous events with redundant protection layer...26 Figure B.5 Hazardous events with SIL 2 SIS safety function...27 Figure C.1 Protection layers...28 Figure C.2 Example safety layer matrix...32 Figure D.1 Risk graph: general scheme...39 Figure D.2 Risk graph: environmental loss...42 Figure E.1 DIN V risk graph personnel protection (see Table E.1)...46 Figure E.2 Relationship between IEC series, DIN and VDI/VDE Figure F.1 Layer of Protection Analysis (LOPA) Report...503 IEC: Table A.1 Example of risk classification of incidents...19 Table A.2 Interpretation of risk classes...19 Table B.1 HAZOP study results...22 Table C.1 Frequency of hazardous event likelihood (without considering PLs)...31 Table C.2 Criteria for rating the severity of impact of hazardous events...31 Table D.1 Descriptions of process industry risk graph parameters...35 Table D.2 Example calibration of the general purpose risk graph...40 Table D.3 General environmental consequences...41 Table E.1 Data relating to risk graph (see Figure E.1)...47 Table F.1 HAZOP developed data for LOPA... 59H50 10HTable F.2 Impact event severity levels... 60H51 11HTable F.3 Initiation Likelihood... 61H51 12HTable F.4 Typical protection layer (prevention and mitigation) PFDs... 62H524 IEC:2003 INTERNATIONAL ELECTROTECHNICAL COMMISSION FUNCTIONAL SAFETY SAFETY INSTRUMENTED SYSTEMS FOR THE PROCESS INDUSTRY SECTOR Part 3: Guidance for the determination of the required safety integrity levels FOREWORD 1) The International Electrotechnical Commission (IEC) is a worldwide organization for standardization comprising all national electrotechnical committees (IEC National Committees). The object of IEC is to promote international co-operation on all questions concerning standardization in the electrical and electronic fields. To this end and in addition to other activities, IEC publishes International Standards, Technical Specifications, Technical Reports, Publicly Available Specifications (PAS) and Guides (hereafter referred to as IEC Publication(s) ). Their preparation is entrusted to technical committees; any IEC National Committee interested in the subject dealt with may participate in this preparatory work. International, governmental and nongovernmental organizations liaising with the IEC also participate in this preparation. IEC collaborates closely with the International Organization for Standardization (ISO) in accordance with conditions determined by agreement between the two organizations. 2) The formal decisions or agreements of IEC on technical matters express, as nearly as possible, an international consensus of opinion on the relevant subjects since each technical committee has representation from all interested IEC National Committees. 3) IEC Publications have the form of recommendations for international use and are accepted by IEC National Committees in that sense. While all reasonable efforts are made to ensure that the technical content of IEC Publications is accurate, IEC cannot be held responsible for the way in which they are used or for any misinterpretation by any end user. 4) In order to promote international uniformity, IEC National Committees undertake to apply IEC Publications transparently to the maximum extent possible in their national and regional publications. Any divergence between any IEC Publication and the corresponding national or regional publication shall be clearly indicated in the latter. 5) IEC provides no marking procedure to indicate its approval and cannot be rendered responsible for any equipment declared to be in conformity with an IEC Publication. 6) All users should ensure that they have the latest edition of this publication. 7) No liability shall attach to IEC or its directors, employees, servants or agents including individual experts and members of its technical committees and IEC National Committees for any personal injury, property damage or other damage of any nature whatsoever, whether direct or indirect, or for costs (including legal fees) and expenses arising out of the publication, use of, or reliance upon, this IEC Publication or any other IEC Publications. 8) Attention is drawn to the Normative references cited in this publication. Use of the referenced publications is indispensable for the correct application of this publication. 9) Attention is drawn to the possibility that some of the elements of this IEC Publication may be the subject of patent rights. IEC shall not be held responsible for identifying any or all such patent rights. International Standard IEC has been prepared by subcommittee 65A: System aspects, of IEC technical committee 65: Industrial-process measurement and control. This bilingual version, published in , corresponds to the English version. The text of this standard is based on the following documents: FDIS 65A/367/FDIS Report on voting 65A/370/RVD Full information on the voting for the approval of this standard can be found in the report on voting indicated in the above table.5 IEC: The French version of this standard has not been voted upon. This publication has been drafted in accordance with the ISO/IEC Directives, Part 2. IEC consists of the following parts, under the general title Functional safety Safety Instrumented Systems for the process industry sector (see Figure 1): Part 1: Framework, definitions, system, hardware and software requirements Part 2: Guidelines for the application of IEC Part 3: Guidance for the determination of the required safety integrity levels The committee has decided that the contents of this publication will remain unchanged until the maintenance result date indicated on the IEC web site under "http://webstore.iec.ch" in the data related to the specific publication. At this date, the publication will be reconfirmed; withdrawn; replaced by a revised edition, or amended.6 IEC:2003 INTRODUCTION Safety instrumented systems have been used for many years to perform safety instrumented functions in the process industries. If instrumentation is to be effectively used for safety instrumented functions, it is essential that this instrumentation achieves certain minimum standards and performance levels. This International Standard addresses the application of safety instrumented systems for the process industries. It also requires a process hazard and risk assessment to be carried out to enable the specification for safety instrumented systems to be derived. Other safety systems are only considered so that their contribution can be taken into account when considering the performance requirements for the safety instrumented systems. The safety instrumented system includes all components and subsystems necessary to carry out the safety instrumented function from sensor(s) to final element(s). This standard has two concepts which are fundamental to its application; safety lifecycle and safety integrity levels. This standard addresses safety instrumented systems which are based on the use of Electrical (E)/Electronic (E)/Programmable Electronic (PE) technology. Where other technologies are used for logic solvers, the basic principles of this standard should be applied. This standard also addresses the safety instrumented system sensors and final elements regardless of the technology used. This standard is process industry specific within the framework of IEC (see Annex A of IEC ). This standard sets out an approach for safety lifecycle activities to achieve these minimum standards. This approach has been adopted in order that a rational and consistent technical policy be used. In most situations, safety is best achieved by an inherently safe process design. If necessary, this may be combined with a protective system or systems to address any residual identified risk. Protective systems can rely on different technologies (chemical, mechanical, hydraulic, pneumatic, electrical, electronic, programmable electronic). Any safety strategy should consider each individual safety instrumented system in the context of the other protective systems. To facilitate this approach, this standard requires that a hazard and risk assessment is carried out to identify the overall safety requirements; requires that an allocation of the safety requirements to the safety instrumented system(s) is carried out; works within a framework which is applicable to all instrumented methods of achieving functional safety; details the use of certain activities, such as safety management, which may be applicable to all methods of achieving functional safety. This standard on safety instrumented systems for the process industry: addresses all safety life cycle phases from initial concept, design, implementation, operation and maintenance through to decommissioning; enables existing or new country specific process industry standards to be harmonized with this standard.7 IEC: This standard is intended to lead to a high level of consistency (for example, of underlying principles, terminology, information) within the process industries. This should have both safety and economic benefits. In jurisdictions where the governing authorities (for example national, federal, state, province, county, city) have established process safety design, process safety management, or other requirements, these take precedence over the requirements defined in this standard. This standard deals with guidance in the area of determining the required SIL in hazards and risk analysis (H & RA). The information herein is intended to provide a broad overview of the wide range of global methods used to implement H & RA. The information provided is not of sufficient detail to implement any of these approaches. Before proceeding, the concept and determination of safety integrity level(s) (SIL) provided in IEC should be reviewed. The annexes in this standard address the following: Annex A Annex B Annex C Annex D Annex E Annex F provides an overview of the concepts of tolerable risk and ALARP. provides an overview of a semi-quantitative method used to determine the required SIL. provides an overview of a safety matrix method to determine the required SIL. provides an overview of a method using a semi-qualitative risk graph approach to determine the required SIL. provides an overview of a method using a qualitative risk graph approach to determine the required SIL. provides an overview of a method using a layer of protection analysis (LOPA) approach to select the required SIL.8 IEC:2003 Technical requirements Support Parts Development of the overall safety requirements (concept, scope definition, hazard and risk assessment) Allocation of the safety requirements to the safety instrumented functions and development of safety requirements Specification Design phase for safety instrumented systems Clause 11 Clause 8 Clauses 9 and 10 Design phase for safety instrumented system software Clause 12 Factory acceptance testing, installation and commissioning and safety validation of safety instrumented systems Clauses 13, 14, and 15 Operation and maintenance, modification and retrofit, decommissioning or disposal of safety instrumented systems Clauses 16, 17, and 18 References Clause 2 Definitions and abbreviations Clause 3 Conformance Clause 4 Management of functional safety Clause 5 Safety lifecycle requirements Clause 6 Verification Clause 7 Information requirements Clause 19 Differences Annex A Guidelines for the application of part 1 Clause 2 PART 2 Guidance for the determination of the required safety integrity levels PART 3 IEC 3008/02 Figure 1 Overall framework of this standard9 IEC: FUNCTIONAL SAFETY SAFETY INSTRUMENTED SYSTEMS FOR THE PROCESS INDUSTRY SECTOR Part 3: Guidance for the determination of the required safety integrity levels 1 Scope This part of IEC provides information on the underlying concepts of risk, the relationship of risk to safety integrity, see Clause 3; the determination of tolerable risk, see Annex A; a number of different methods that enable the safety integrity levels for the safety instrumented functions to be determined, see Annexes B, C, D, E, and F. In particular, this part a) applies when functional safety is achieved using one or more safety instrumented functions for the protection of either personnel, the general public, or the environment; b) may be applied in non-safety applications such as asset protection; c) illustrates typical hazard and risk assessment methods that may be carried out to define the safety functional requirements and safety integrity levels of each safety instrumented function; d) illustrates techniques/measures available for determining the required safety integrity levels; e) provides a framework for establishing safety integrity levels but does not specify the safety integrity levels required for specific applications; f) does not give examples of determining the requirements for other methods of risk reduction. Annexes B, C, D, E, and F illustrate quantitative and qualitative approaches and have been simplified in order to illustrate the underlying principles. These annexes have been included to illustrate the general principles of a number of methods but do not provide a definitive account. NOTE Those intending to apply the methods indicated in these annexes should consult the source material referenced in each annex. Figure 1 shows the overall framework for IEC , IEC and IEC and indicates the role that this standard plays in the achievement of functional safety for safety instrumented systems. Figure 2 gives an overview of risk reduction methods.10 IEC:2003 COMMUNITY EMERGENCY RESPONSE Emergency broadcasting PLANT EMERGENCY RESPONSE Evacuation procedures MITIGATION Mechanical mitigation systems Safety instrumented control systems Safety instrumented mitigation systems Operator supervision PREVENTION Mechanical protection system Process alarms with operator corrective action Safety instrumented control systems Safety instrumented prevention systems CONTROL and MONITORING Basic process control systems Monitoring systems (process alarms) Operator supervision PROCESS IEC 3009/02 Figure 2 Typical risk reduction methods found in process plants (for example, protection layer model) 2 Terms, definitions and abbreviations For the purposes of this document, the definitions and abbreviations given in Clause 3 of IEC apply. 3 Risk and safety integrity general guidance 3.1 General This clause provides information on the underlying concepts of risk and the relationship of risk to safety integrity. This information is common to each of the diverse hazard and risk analysis (H & RA) methods shown herein.11 CEI:2003 SOMMAIRE AVANT-PROPOS...60 INTRODUCTION Domaine d'application Termes, définitions et abréviations Risque et intégrité de sécurité informations générales Généralités Réduction nécessaire du risque Rôle des systèmes instrumentés de sécurité Intégrité de sécurité Risque et intégrité de sécurité Allocation des exigences de sécurité Niveaux d'intégrité de sécurité Choix de la méthode de détermination du niveau d'intégrité de sécurité requis...71 Annexe A (informative) Concepts d'alarp (aussi faible que raisonnablement possible) et de risque tolérable...72 Annexe B (informative) Méthode semi-quantitative...76 Annexe C (informative) Méthode de la matrice de couches de sécurité...84 Annexe D (informative) Détermination des niveaux d'intégrité de sécurité requis une méthode semi-qualitative: Graphe de risque étalonné...90 Annexe E (informative) Détermination des niveaux d'intégrité de sécurité requis une méthode qualitative: graphe de risque...99 Annexe F (informative) Analyse des couches de protection (LOPA) Figure 1 Structure générale de la présente norme...64 Figure 2 Méthodes types de réduction du risque utilisées dans les installations de transformation (par exemple, modèle de couches de protection)...66 Figure 3 Réduction du risque: concepts généraux...69 Figure 4 Concepts de risque et d'intégrité de sécurité...70 Figure 5 Allocation des exigences de sécurité aux systèmes instrumentés de sécurité, aux couches de protection de prévention/d'atténuation non SIS ainsi qu'à d'autres couches de protection...71 Figure A.1 Risque tolérable et ALARP...73 Figure B.1 Récipient sous pression avec ses systèmes de sécurité existants...77 Figure B.2 Arborescence des anomalies pour la surpression interne du récipient...80 Figure B.3 Evénements dangereux avec des systèmes de sécurité existants...81 Figure B.4 Evénements dangereux avec une couche de protection redondante...82 Figure B.5 Evénements dangereux avec une fonction de sécurité ayant un niveau d'intégrité de sécurité SIL2 et mise en oeuvre dans un système instrumenté de sécurité (SIS) 83 Figure C.1 Couches de protection...84 Figure C.2 Exemple de matrice de couches de sécurité...88 Figure D.1 Graphe de risque: plan général...95 Figure D.2 Graphe de risque: atteinte à l'environnement...98 Figure E.1 Graphe de risque selon DIN V protection du personnel Figure E.2 Relation entre la CEI 61511, DIN et VDI/VDE Figure F.1 Compte-rendu d'analyse de couches de protection (LOPA)...10612 CEI: Tableau A.1 Exemple de classification des risques d'accidents...75 Tableau A.2 Interprétation des classes de risques...75 Tableau B.1 Résultats d'une analyse HAZOP...78 Tableau C.1 Probabilité d'occurrence des événement dangereux (sans tenir compte des couches de protection)...87 Tableau C.2 Critères de classement de la gravité de l'impact des événements dangereux...87 Tableau D.1 Descriptions des paramètres du graphe des risques pour les industries de transformation...91 Tableau D.2 Exemple d'étalonnage du graphe de risque général...96 Tableau D.3 Conséquences générales sur l'environnement...97 Tableau E.1 Données relatives au graphe de risque (voir Figure E.1) Tableau F.1 Données élaborées au cours de l'étude HAZOP pour l'analyse LOPA Tableau F.2 Degrés de gravité des événements à impact Tableau F.3 Probabilité d'occurrence de causes initiatrices Tableau F.4 PFD types des couches de protection (prévention et atténuation)13 CEI:2003 COMMISSION ÉLECTROTECHNIQUE INTERNATIONALE SÉCURITÉ FONCTIONNELLE SYSTÈMES INSTRUMENTÉS DE SÉCURITÉ POUR LE SECTEUR DES INDUSTRIES DE TRANSFORMATION Partie 3: Conseils pour la détermination des niveaux exigés d'intégrité de sécurité AVANT-PROPOS 1) La Commission Electrotechnique Internationale (CEI) est une organisation mondiale de normalisation composée de l'ensemble des comités électrotechniques nationaux (Comités nationaux de la CEI). La CEI a pour objet de favoriser la coopération internationale pour toutes les questions de normalisation dans les domaines de l'électricité et de l'électronique. A cet effet, la CEI entre autres activités publie des Normes internationales, des Spécifications techniques, des Rapports techniques, des Spécifications accessibles au public (PAS) et des Guides (ci-après dénommés "Publication(s) de la CEI"). Leur élaboration est confiée à des comités d'études, aux travaux desquels tout Comité national intéressé par le sujet traité peut participer. Les organisations internationales, gouvernementales et non gouvernementales, en liaison avec la CEI, participent également aux travaux. La CEI collabore étroitement avec l'organisation Internationale de Normalisation (ISO), selon des conditions fixées par accord entre les deux organisations. 2) Les décisions ou accords officiels de la CEI concernant les questions techniques représentent, dans la mesure du possible, un accord international sur les sujets étudiés, étant donné que les Comités nationaux de la CEI intéressés sont représentés dans chaque comité d études. 3) Les Publications de la CEI se présentent sous la forme de recommandations internationales et sont agréées comme telles par les Comités nationaux de la CEI. Tous les efforts raisonnables sont entrepris afin que la CEI s'assure de l'exactitude du contenu technique de ses publications; la CEI ne peut pas être tenue responsable de l'éventuelle mauvaise utilisation ou interprétation qui en est faite par un quelconque utilisateur final. 4) Dans le but d'encourager l'uniformité internationale, les Comités nationaux de la CEI s'engagent, dans toute la mesure possible, à appliquer de façon transparente les Publications de la CEI dans leurs publications nationales et régionales. Toutes divergences entre toutes Publications de la CEI et toutes publications nationales ou régionales correspondantes doivent être indiquées en termes clairs dans ces dernières. 5) La CEI n a prévu aucune procédure de marquage valant indication d approbation et n'engage pas sa responsabilité pour les équipements déclarés conformes à une de ses Publications. 6) Tous les utilisateurs doivent s'assurer qu'ils sont en possession de la dernière édition de cette publication. 7) Aucune responsabilité ne doit être imputée à la CEI, à ses administrateurs, employés, auxiliaires ou mandataires, y compris ses experts particuliers et les membres de ses comités d'études et des Comités nationaux de la CEI, pour tout préjudice causé en cas de dommages corporels et matériels, ou de tout autre dommage de quelque nature que ce soit, directe ou indirecte, ou pour supporter les coûts (y compris les frais de justice) et les dépenses découlant de la publication ou de l'utilisation de cette Publication de la CEI ou de toute autre Publication de la CEI, ou au crédit qui lui est accordé. 8) L'attention est attirée sur les références normatives citées dans cette publication. L'utilisation de publications référencées est obligatoire pour une application correcte de la présente publication. 9) L attention est attirée sur le fait que certains des éléments de la présente Publication de la CEI peuvent faire l objet de droits de propriété intellectuelle ou de droits analogues. La CEI ne saurait être tenue pour responsable de ne pas avoir identifié de tels droits de propriété et de ne pas avoir signalé leur existence. La Norme internationale CEI a été préparée par le sous-comité 65A: Aspects systèmes, du comité technique 65 de la CEI: Mesure et commande dans les procédés industriels. Cette version bilingue, publiée en , correspond à la version anglaise. Le texte anglais de cette norme est issu des documents 65A/367/FDIS et 65A/370/RVD. Le rapport de vote 65A/370/RVD donne toute information sur le vote ayant abouti à l approbation de cette norme. La version française de cette norme n a pas été soumise au vote.14 CEI: La présente publication a été rédigée conformément aux Directives ISO/CEI, Partie 2. La CEI comprend les parties suivantes, présentées sous le titre général Sécurité fonctionnelle Systèmes instrumentés de sécurité pour le secteur des industries de transformation (voir Figure 1): Partie 1: Cadre, définitions, exigences pour le système, le matériel et le logiciel Partie 2: Lignes directrices pour l'application de la CEI Partie 3: Conseils pour la détermination des niveaux exigés d'intégrité de sécurité Le comité a décidé que le contenu de cette publication ne sera pas modifié avant la date de maintenance indiquée sur le site web de la CEI sous «http://webstore.iec.ch» dans les données relatives à la publication recherchée. A cette date, la publication sera reconduite; supprimée; remplacée par une édition révisée, ou amendée.15 CEI:2003 INTRODUCTION Les systèmes instrumentés de sécurité sont utilisés dans les industries de transformation depuis de nombreuses années pour remplir des fonctions instrumentées de sécurité. Si l'instrumentation doit réellement être utilisée pour réaliser des fonctions instrumentées de sécurité, il est indispensable qu'elle présente des niveaux minimums de qualité et de performance. La présente Norme internationale traite de l'utilisation des systèmes instrumentés de sécurité dans les industries de transformation. Elle prescrit également une évaluation du danger et du risque liés aux procédés pour permettre d'en déduire la spécification relative à des systèmes instrumentés de sécurité. D'autres systèmes de sécurité sont considérés uniquement pour que leur contribution puisse être prise en compte lors de l'étude des exigences relatives aux qualités de fonctionnement des systèmes instrumentés de sécurité. Le système instrumenté de sécurité inclut tous les composants et tous les sous-systèmes nécessaires à la réalisation des fonctions instrumentées de sécurité, depuis les capteurs jusqu'aux éléments terminaux. La présente norme offre deux concepts fondamentaux: le cycle de vie en sécurité et les niveaux d'intégrité de sécurité. La présente norme traite de systèmes instrumentés de sécurité fondés sur les technologies électrique/électronique/électronique programmable. Il convient d'appliquer les principes de base de la présente norme lorsque d'autres technologies sont utilisées pour l'unité de traitement. La présente norme traite également des capteurs et des éléments terminaux des systèmes instrumentés de sécurité, quelle que soit la technologie utilisée. La présente norme est propre aux industries de transformation, dans le cadre de la CEI (se reporter à l'annexe A de la CEI ). La présente norme propose des principes pour mener les actions de sécurité tout au long du cycle de vie, afin de mettre en oeuvre une politique technique cohérente et rationnelle et d'obtenir les niveaux de qualité requis. Dans la plupart des cas et lorsque cela est possible, le meilleur moyen d'assurer la sécurité est de concevoir un procédé intrinsèquement sûr, combiné si nécessaire à un certain nombre de systèmes de technologies différentes (chimique, mécanique, hydraulique, pneumatique, électrique, électronique, électronique programmable) assurant la protection contre tout risque résiduel identifié. Il convient que les stratégies de sécurité considèrent chaque système instrumenté de sécurité dans le contexte des autres systèmes de protection. Pour faciliter cette approche, la présente norme: requiert une évaluation du danger et du risque pour identifier l'ensemble des exigences de sécurité; requiert l'allocation des exigences de sécurité au(x) système(s) instrumenté(s) de sécurité; se place dans un cadre applicable à toutes les méthodes instrumentées d'obtention de la sécurité fonctionnelle; détaille certaines activités, telles que la gestion de la sécurité, qui peuvent s'appliquer à toutes les méthodes d'obtention de la sécurité fonctionnelle. La présente norme relative aux systèmes instrumentés de sécurité pour le secteur des industries de transformation: prend en compte toutes les phases du cycle de vie en sécurité, de la préparation du projet à la conception, la réalisation, l'exploitation, la maintenance et la mise hors service; permet l'harmonisation des normes existantes ou nouvelles concernant les industries de transformation et spécifiques à différents pays avec la présente norme.16 CEI: La présente norme vise à obtenir un haut niveau de cohérence (par exemple, des principes sous-jacents, de la terminologie, de la documentation) dans les industries de transformation. Ceci devrait présenter des avantages tant du point de vue de la sécurité que du point de vue économique. Lorsque des autorités compétentes (nationales, fédérales, provinciales, cantonales, municipales) ont défini des exigences relatives à la conception de la sécurité des procédés, à la gestion de la sécurité des procédés, ou d'autres exigences, celles-ci priment sur les exigences définies dans la présente norme. La présente norme donne des conseils pour déterminer le niveau d'intégrité de sécurité (SIL) dans le cadre de l'analyse du danger et du risque (H & RA). Les informations contenues dans le présent document ont pour but de donner un aperçu général de la grande variété de méthodes globales utilisées pour effectuer une analyse du danger et du risque (H & RA). Les informations fournies ne sont pas suffisamment détaillées pour permettre l'utilisation de l'une quelconque de ces méthodes. Avant d'aller plus loin, il convient de considérer le concept ainsi que la détermination du ou des niveaux d'intégrité de sécurité (SIL) décrits dans la CEI Les annexes de la présente norme traitent des sujets suivants: Annexe A Annexe B Annexe C Annexe D Annexe E Annexe F cette annexe donne un aperçu général des concepts de risque tolérable et d'alarp (aussi faible que raisonnablement possible). cette annexe donne un aperçu général d'une méthode semi-quantitative utilisée pour déterminer le niveau d'intégrité de sécurité (SIL) requis. cette annexe donne un aperçu général d'une méthode utilisant une matrice de sécurité pour déterminer le niveau d'intégrité de sécurité (SIL) requis. cette annexe donne un aperçu général d'une méthode utilisant un graphe de risque semi-qualitatif pour déterminer le niveau d'intégrité de sécurité (SIL) requis. cette annexe donne un aperçu général d'une méthode utilisant un graphe de risque qualitatif pour déterminer le niveau d'intégrité de sécurité (SIL) requis. cette annexe donne un aperçu général d'une méthode d'analyse des couches de protection (LOPA) pour sélectionner le niveau SIL requis.17 CEI:2003 Exigences techniques Autres Parties Développement des Exigences globales de sécurité (concept, définition du domaine d application, analyse de danger et de risque) Allocation des Exigences de sécurité aux fonctions instrumentées de sécurité et développement de la spécification des Exigences de sécurité Phase de conception pour les systèmes instrumentés de sécurité Article 11 Article 8 Articles 9 et 10 Phase de conception pour les logiciels des systèmes instrumentés de sécurité Article 12 Essais de recette en usine, installation et mise en service, et validation de la sécurité des systèmes instrumentés de sécurité Articles 13, 14, et 15 Exploitation et maintenance, modification et remise à niveau, mise hors service ou au rebut des systèmes instrumentés de sécurité Articles 16, 17, et 18 Références Article 2 Définitions et abréviations Article 3 Conformité Article 4 Gestion de la sécurité fonctionnelle Article 5 Exigences de cycle de vie de sécurité Article 6 Vérification Article 7 Exigences d'informations Article 19 Différences Annexe A Indications pour l'application de la partie 1 PARTIE 2 Indications pour la détermination des niveaux d'intégrité de sécurité requis PARTIE 3 IEC 3008/02 Figure 1 Structure générale de la présente norme18 CEI: SÉCURITÉ FONCTIONNELLE SYSTÈMES INSTRUMENTÉS DE SÉCURITÉ POUR LE SECTEUR DES INDUSTRIES DE TRANSFORMATION Partie 3: Conseils pour la détermination des niveaux exigés d'intégrité de sécurité 1 Domaine d'application La présente partie de la CEI fournit des informations sur: les concepts sous-jacents de risque et la relation entre risque et intégrité, se reporter à l'article 3; la détermination du risque tolérable, se reporter à l'annexe A; différentes méthodes permettant de déterminer les niveaux d'intégrité de sécurité des fonctions instrumentées de sécurité, se reporter aux Annexes B, C, D, E et F. En particulier, la présente partie: a) s'applique lorsque la sécurité fonctionnelle est obtenue à l'aide d'une ou plusieurs fonctions instrumentées de sécurité pour la protection du personnel, du public ou de l'environnement; b) peut être utilisée dans des applications qui ne sont pas liées à la sécurité, comme la protection des biens; c) décrit des méthodes types d'analyse de danger et de risque, qui peuvent être utilisées pour établir les exigences fonctionnelles de sécurité et les niveaux d'intégrité de sécurité de chaque fonction instrumentée de sécurité; d) identifie des techniques et mesures disponibles pour déterminer les niveaux d'intégrité de sécurité spécifiés; e) fournit un cadre pour l'établissement des niveaux d'intégrité de sécurité, mais ne spécifie pas les niveaux d'intégrité de sécurité requis pour des applications spécifiques; f) ne donne pas d'exemples de détermination des exigences relatives à d'autres méthodes de réduction du risque. Les Annexes B, C, D, E et F décrivent des méthodes quantitatives et qualitatives sous forme simplifiée, afin d'en illustrer les principes sous-jacents. Ces annexes ont été incorporées pour illustrer les principes généraux d'un certain nombre de méthodes, mais ne constituent pas une description exhaustive. NOTE Il est souhaitable que ceux qui envisagent d'utiliser les méthodes indiquées dans ces annexes consultent le document source mentionné dans chaque annexe. La Figure 1 illustre la structure générale des parties 1 à 3 de la présente norme et indique le rôle joué par la partie 3 dans l'obtention de la sécurité fonctionnelle des systèmes instrumentés de sécurité. La Figure 2 donne un aperçu général des méthodes de réduction du risque.19 CEI:2003 RÉACTION DU PUBLIC À UNE SITUATION CRITIQUE Radiodiffusion d'urgence MESURES PRISES PAR L'INSTALLATION DANS UNE SITUATION CRITIQUE Procédures d'évacuation ATTÉNUATION DES CONSÉQUENCES Systèmes mécaniques d'atténuation Systèmes instrumentés de sécurité de commande Systèmes instrumentés de sécurité d'atténuation Surveillance par opérateur PRÉVENTION Système de protection mécanique Alarmes du procédé avec action corrective de l'opérateur Systèmes instrumentés de sécurité de commande Systèmes instrumentés de sécurité de prévention CONTRÔLE ET SURVEILLANCE Systèmes de commande de procédé de base Systèmes de surveillance (alarmes du procédé) Surveillance par opérateur PROCÉDÉ IEC 3009/02 Figure 2 Méthodes types de réduction du risque utilisées dans les installations de transformation (par exemple, modèle de couches de protection) 2 Termes, définitions et abréviations Pour les besoins du présent document, les définitions et abréviations de l'article 3 de la CEI s'appliquent. 3 Risque et intégrité de sécurité informations générales 3.1 Généralités Le présent article fournit des informations sur les concepts sous-jacents de risque et de relation entre risque et intégrité de sécurité. Ces informations sont communes à toutes les méthodes d'analyse de danger et de risque (H & RA) décrites dans le présent document. Montrer encore
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 747-6-3 QC 750113 Première édition First edition 1993-11 Dispositifs à semiconducteurs Dispositifs discrets Partie 6: Thyristors Section trois Spécification Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
IEC 60512-9-3 Edition 2.0 2011-06 INTERNATIONAL STANDARD NORME INTERNATIONALE Connectors for electronic equipment Tests and measurements Part 9-3: Endurance tests Test 9c: Mechanical operation (engaging Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
INTERNATIONAL STANDARD NORME INTERNATIONALE IEC 62058-31 Edition 1.0 2008-09 Electricity metering equipment (AC) Acceptance inspection Part 31: Particular requirements for static meters for active energy Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
INTERNATIONAL STANDARD NORME INTERNATIONALE IEC 60839-7-6 Edition 1.0 2001-03 Alarm systems Part 7-6: Message formats and protocols for serial data interfaces in alarm transmission systems Alarm system Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
IEC 60512-8-3 Edition 1.0 2011-04 INTERNATIONAL STANDARD NORME INTERNATIONALE Connectors for electronic equipment Tests and measurements Part 8-3: Static load tests (fixed connectors) Test 8c: Robustness Plus en détail NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 60839-7-11 Première édition First edition 2001-03 Systèmes d'alarme Partie 7-11: Formats de message et protocoles pour les interfaces de données série Plus en détail NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 81714-3 Deuxième édition Second edition 2004-10 Création de symboles graphiques utilisables dans la documentation technique de produits Partie 3: Classification Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
IEC 61850-4 Edition 2.0 2011-04 INTERNATIONAL STANDARD NORME INTERNATIONALE Communication networks and systems for power utility automation Part 4: System and project management Réseaux et systèmes de Plus en détail COPYRIGHT Danish Standards. NOT FOR COMMERCIAL USE OR REPRODUCTION. DS/EN 62053-61:1998
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 62053-61 Première édition First edition 1998-02 COPYRIGHT Danish Standards. NOT FOR COMMERCIAL USE OR REPRODUCTION. DS/EN 62053-61:1998 Equipement de Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
IEC 60191-6-2 Edition 1.0 2001-12 INTERNATIONAL STANDARD NORME INTERNATIONALE Mechanical standardization of semiconductor devices Part 6-2: General rules for the preparation of outline drawings of surface Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 62301 Première édition First edition 2005-06 Appareils électrodomestiques Mesure de la consommation en veille Household electrical appliances Measurement Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 61554 Première édition First edition 1999-10 Appareils montés en tableaux Instruments de mesure électriques Dimensions pour le montage en tableaux Panel Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
IEC 60749-7 Edition 2.0 2011-06 INTERNATIONAL STANDARD NORME INTERNATIONALE Semiconductor devices Mechanical and climatic test methods Part 7: Internal moisture content measurement and the analysis of Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
IEC 62670-1 Edition 1.0 2013-09 INTERNATIONAL STANDARD NORME INTERNATIONALE Photovoltaic concentrators (CPV) Performance testing Part 1: Standard conditions Concentrateurs photovoltaïques (CPV) Essai de Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
IEC 62297-2 Edition 1.0 2005-05 INTERNATIONAL STANDARD NORME INTERNATIONALE Triggering messages for broadcast applications Part 2: Transport methods Messages de déclenchement pour les applications de radiodiffusion Plus en détail NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 60839-7-2 Première édition First edition 2001-03 Systèmes d'alarme Partie 7-2: Formats de message et protocoles pour les interfaces de données série Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
INTERNATIONAL STANDARD NORME INTERNATIONALE IEC 61249-3-4 Edition 1.0 1999-02 Materials for printed boards and other interconnecting structures Part 3-4: Sectional specification set for unreinforced base Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 62148-4 Première édition First edition 2003-06 Composants et dispositifs actifs en fibres optiques Normes de boîtier et d'interface Partie 4: Emetteurs-récepteurs Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
INTERNATIONAL STANDARD NORME INTERNATIONALE IEC 61754-25 Edition 1.0 2008-11 Fibre optic connector interfaces Part 25: Type RAO connector family Interfaces de connecteurs pour fibres optiques Partie 25: Plus en détail NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 60424-3 Première édition First edition 1999-06 Noyaux ferrites Guide relatif aux limites des irrégularités de surface Partie 3: Noyaux ETD et E Ferrite Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 61386-23 Première édition First edition 2002-02 Systèmes de conduits pour installations électriques Partie 23: Règles particulières Systèmes de conduits Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
IEC 61851-24 Edition 1.0 2014-03 INTERNATIONAL STANDARD NORME INTERNATIONALE Electric vehicle conductive charging system Part 24: Digital communication between a d.c. EV charging station and an electric Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
IEC 62496-3-1 Edition 1.0 2009-08 INTERNATIONAL STANDARD NORME INTERNATIONALE Optical circuit boards Part 3-1: Performance standards Flexible optical circuit boards using unconnectorized optical glass Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
INTERNATIONAL STANDARD NORME INTERNATIONALE IEC 62137-1-1 Edition 1.0 2007-07 Surface mounting technology Environmental and endurance test methods for surface mount solder joint Part 1-1: Pull strength Plus en détail NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 60839-7-4 Première édition First edition 2001-03 Systèmes d'alarme Partie 7-4: Formats de message et protocoles pour les interfaces de données série Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
ISO/IEC 80079-34 INTERNATIONAL STANDARD NORME INTERNATIONALE Edition 1.0 2011-04 Explosive atmospheres Part 34: Application of quality systems for equipment manufacture Atmosphères explosives Partie 34: Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD. Essai d'environnement. Environmental testing
NORME INTERNATIONALE INTERNATIONAL STANDARD C E I IEC 68-2-69 Première édition First edition 1995-12 Essai d'environnement Partie 2: Essais Essai Te: Essai de brasabilité des composants électroniques pour Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
IEC 62851-5 Edition 1.0 2014-04 INTERNATIONAL STANDARD NORME INTERNATIONALE Alarm and electronic security systems Social alarm systems Part 5: Interconnections and communications Systèmes d'alarme et de Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
IEC 62430 Edition 1.0 2009-02 INTERNATIONAL STANDARD NORME INTERNATIONALE Environmentally conscious design for electrical and electronic products Eco-conception pour les produits électriques et électroniques Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
IEC 60068-2-5 Edition 2.0 2010-04 INTERNATIONAL STANDARD NORME INTERNATIONALE Environmental testing Part 2-5: Tests Test Sa: Simulated solar radiation at ground level and guidance for solar radiation testing Plus en détail This document is a preview generated by EVS
IEC 60974-4 Edition 2.0 2010-08 INTERNATIONAL STANDARD NORME INTERNATIONALE Arc welding equipment Part 4: Periodic inspection and testing Matériel de soudage à l arc Partie 4: Inspection et essais périodiques Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
IEC 60115-9-1 Edition 1.0 2003-10 INTERNATIONAL STANDARD NORME INTERNATIONALE Fixed resistors for use in electronic equipment Part 9-1: Blank detail specification: Fixed surface mount resistor networks Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
IEC 62148-16 Edition 1.0 2009-08 INTERNATIONAL STANDARD NORME INTERNATIONALE Fiber optic active components and devices Package and interface standards Part 16: Transmitter and receiver components for use Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
IEC 60034-29 INTERNATIONAL STANDARD NORME INTERNATIONALE Edition 1.0 2008-03 Rotating electrical machines Part 29: Equivalent loading and superposition techniques Indirect testing to determine temperature Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 60793-1-30 Première édition First edition 2001-07 Fibres optiques Partie 1-30: Méthodes de mesure et procédures d'essai Essais de sélection Optical fibres Plus en détail This document is a preview generated by EVS
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 60512-2-6 Première édition First edition 2002-02 Connecteurs pour équipements électroniques Essais et mesures Partie 2-6: Essais de continuité électrique Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 60068-2-10 Sixième édition Sixth edition 2005-06 BASIC SAFETY PUBLICATION PUBLICATION FONDAMENTALE DE SÉCURITÉ Essais d environnement Partie 2-10: Essais Plus en détail NORME INTERNATIONALE INTERNATIONAL STANDARD
This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 61619 Première édition First edition 1997-04 Isolants liquides Contamination par les polychlorobiphényles Plus en détail NORME CEI INTERNATIONALE IEC INTERNATIONAL 60839-2-7. Systèmes d'alarme
NORME CEI INTERNATIONALE IEC INTERNATIONAL 60839-2-7 STANDARD Première édition First edition 1994-12 Systèmes d'alarme Partie 2: Prescriptions pour les systèmes d'alarme anti-intrusion Section 7 Détecteurs Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 60512-23-4 Première édition First edition 2001-06 Connecteurs pour équipements électroniques Essais et mesures Partie 23-4: Essais de blindage et de Plus en détail NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 60317-0-2 1997 AMENDEMENT 2 AMENDMENT 2 2005-01 Amendement 2 Spécifications pour types particuliers de fils de bobinage Partie 0-2: Prescriptions générales Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
IEC 62642-5-3 Edition 1.0 2010-10 INTERNATIONAL STANDARD NORME INTERNATIONALE Alarm systems Intrusion and hold-up systems Part 5-3: Interconnections Requirements for equipment using radio frequency techniques Plus en détail This is a preview - click here to buy the full publication NORME CEI INTERNATIONALE IEC INTERNATIONAL 61194 STAN DARD
NORME CEI INTERNATIONALE IEC INTERNATIONAL 61194 STAN DARD Première édition First edition 1992-12 Paramètres descriptifs des systèmes photovoltaïques autonomes Characteristic parameters of stand-alone Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
IEC 62481-4 Edition 1.0 2014-03 INTERNATIONAL STANDARD NORME INTERNATIONALE Digital living network alliance (DLNA) home networked device interoperability guidelines Part 4: DRM interoperability solutions Plus en détail ISO 12353-1 INTERNATIONAL STANDARD NORME INTERNATIONALE. Road vehicles Traffic accident analysis Part 1: Vocabulary
INTERNATIONAL STANDARD NORME INTERNATIONALE ISO 12353-1 First edition Première édition 2002-03-01 Road vehicles Traffic accident analysis Part 1: Vocabulary Véhicules routiers Analyse des accidents de Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 61069-8 Première édition First edition 1999-04 Mesure et commande dans les processus industriels Appréciation des propriétés d un système en vue de son Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 60068-2-17 Quatrième édition Fourth edition 1994-07 BASIC SAFETY PUBLICATION PUBLICATION FONDAMENTALE DE SÉCURITÉ Essais fondamentaux climatiques et Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
INTERNATIONAL STANDARD NORME INTERNATIONALE IEC 61511-1 Edition 1.0 2003-01 Functional safety Safety instrumented systems for the process industry sector Part 1: Framework, definitions, system, hardware Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD. Interfaces de connecteurs pour fibres optiques
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 61754-13 Deuxième édition Second edition 2006-02 Interfaces de connecteurs pour fibres optiques Partie 13: Connecteurs de type FC-PC Fibre optic connector Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD C.E IEC 746-5 Première édition First edition 1992-12 Expression des qualités de fonctionnement des analyseurs électrochimiques Partie 5: Potentiel d'oxydo-réduction Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
IEC 62420 Edition 1.0 2008-04 INTERNATIONAL STANDARD NORME INTERNATIONALE Concentric lay stranded overhead electrical conductors containing one or more gap(s) Conducteurs pour lignes électriques aériennes Plus en détail INTERNATIONALE. Logiciels de dispositifs médicaux Processus du cycle de vie du logiciel
NORME INTERNATIONALE CEI 62304 Première édition 2006-05 Logiciels de dispositifs médicaux Processus du cycle de vie du logiciel Cette version française découle de la publication d origine bilingue dont Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 60512-12-4 Première édition First edition 2006-02 Connecteurs pour équipements électroniques Essais et mesures Partie 12-4: Essais de soudure Essai 12d: Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 60749-26 Première édition First edition 2003-10 Dispositifs à semiconducteurs Méthodes d'essais mécaniques et climatiques Partie 26: Essai de sensibilité Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD. Appareillage à basse tension
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 60947-5-6 Première édition First edition 1999-12 Appareillage à basse tension Partie 5-6: Appareils et éléments de commutation pour circuits de commande Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
IEC 62297-1 Edition 1.0 2005-05 INTERNATIONAL STANDARD NORME INTERNATIONALE colour inside Triggering messages for broadcast applications Part 1: Format Messages déclencheurs pour applications en radiodiffusion Plus en détail NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 61508-3 Première édition First edition 1998-12 PUBLICATION FONDAMENTALE DE SÉCURITÉ BASIC SAFETY PUBLICATION Sécurité fonctionnelle des systèmes électriques/ Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD. Partie 1: Emetteurs d'infrarouge cou rt
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI lec 240-1 Deuxième édition Second edition 1992-07 Caractéristiques des émetteurs électriques d'infrarouge pour chauffage industriel Partie 1: Emetteurs d'infrarouge Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD. Ensembles d'appareillage à basse tension
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 60439-2 Troisième édition Third edition 2000-03 Ensembles d'appareillage à basse tension Partie 2: Règles particulières pour les canalisations préfabriquées Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
IEC 62516-2 Edition 1.0 2011-07 INTERNATIONAL STANDARD NORME INTERNATIONALE colour inside Terrestrial digital multimedia broadcasting (T-DMB) receivers Part 2: Interactive data services using BIFS Récepteurs Plus en détail Méthodes de mesure applicables au matériel utilisé pour les systèmes de transmission numérique en hyperfréquence
NORME CEI INTERNATIONALE IEC INTERNATIONAL 60835-3-14 STAN DARD Première édition First edition 1996-03 Méthodes de mesure applicables au matériel utilisé pour les systèmes de transmission numérique en Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 60376 Deuxième édition Second edition 2005-06 Spécifications de la qualité technique de l'hexafluorure de soufre (SF 6 ) pour utilisation dans les appareils Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
IEC 60300-3-11 Edition 2.0 2009-06 INTERNATIONAL STANDARD NORME INTERNATIONALE Dependability management Part 3-11: Application guide Reliability centred maintenance Gestion de la sûreté de fonctionnement Plus en détail This document is a preview generated by EVS
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 61554 Première édition First edition 1999-10 Appareils montés en tableaux Instruments de mesure électriques Dimensions pour le montage en tableaux Panel Plus en détail NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 62304 Première édition First edition 2006-05 Logiciels de dispositifs médicaux Processus du cycle de vie du logiciel Medical device software Software Plus en détail NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 61347-2-9 2000 AMENDEMENT 2 AMENDMENT 2 2006-06 Amendement 2 Appareillages de lampes Partie 2-9: Prescriptions particulières pour les ballasts pour lampes Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 1241-2-1 Première édition First edition 1994-12 Matériels électriques destinés à être utilisés en présence de poussières combustibles - Partie 2: Méthodes Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
IEC 61975 Edition 1.0 2010-07 INTERNATIONAL STANDARD NORME INTERNATIONALE High-voltage direct current (HVDC) installations System tests Installations en courant continu à haute tension (CCHT) Essais systèmes Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
INTERNATIONAL STANDARD NORME INTERNATIONALE IEC 60706-5 Edition 2.0 2007-09 Maintainability of equipment Part 5: Testability and diagnostic testing Maintenabilité de matériel Partie 5: Testabilité et tests Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 60519-3 Troisième édition Third edition 2005-02 Sécurité dans les installations électrothermiques Partie 3: Règles particulières pour les installations Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STAN DARD. Telecontrol equipment and systems
NORME INTERNATIONALE INTERNATIONAL STAN DARD CEI IEC 870-3 Première édition First edition 1989-03 Matériels et systèmes de téléconduite Troisième partie: Interfaces (caractéristiques électriques) Telecontrol Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
IEC 62673 Edition 1.0 2013-06 INTERNATIONAL STANDARD NORME INTERNATIONALE colour inside Methodology for communication network dependability assessment and assurance Méthodologie pour l'évaluation et l'assurance Plus en détail NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 61000-4-4 Deuxième édition Second edition 2004-07 PUBLICATION FONDAMENTALE EN CEM BASIC EMC PUBLICATION Compatibilité électromagnétique (CEM) Partie Plus en détail This is a preview - click here to buy the full publication INTERNATIONAL STANDARD NORME INTERNATIONALE. Obsolescence management Application guide
INTERNATIONAL STANDARD NORME INTERNATIONALE IEC CEI 62402 First edition Première édition 2007-06 Obsolescence management Application guide Gestion de l obsolescence Guide d application Commission Electrotechnique Plus en détail This document is a preview generated by EVS
IEC 62474 Edition 1.0 2012-03 INTERNATIONAL STANDARD NORME INTERNATIONALE colour inside Material declaration for products of and for the electrotechnical industry Déclaration de matière pour des produits Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
IEC 60095-2 Edition 4.0 2009-10 INTERNATIONAL STANDARD NORME INTERNATIONALE Lead-acid starter batteries Part 2: Dimensions of batteries and dimensions and marking of terminals Batteries d'accumulateurs Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 61557-8 Deuxième édition Second edition 2007-01 Sécurité électrique dans les réseaux de distribution basse tension de 1 000 V c.a. et 1 500 V c.c. Dispositifs Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
IEC 60721-2-2 Edition 2.0 2012-12 INTERNATIONAL STANDARD NORME INTERNATIONALE Classification of environmental conditions Part 2-2: Environmental conditions appearing in nature Precipitation and wind Classification Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
INTERNATIONAL STANDARD NORME INTERNATIONALE IEC CEI 62264-3 First edition Première édition 2007-06 Enterprise-control system integration Part 3: Activity models of manufacturing operations management Intégration Plus en détail FINAL DRAFT INTERNATIONAL STANDARD PROJET FINAL DE NORME INTERNATIONALE
PROJECT IEC 62148-2 Edition 2.0 2010-09 FINAL DRAFT INTERNATIONAL STANDARD PROJET FINAL DE NORME INTERNATIONALE Fibre optic active components and devices Package and interface standards Part 2: SFF 10-pin Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE IEC/ISO 31010. Risk management Risk assessment techniques
INTERNATIONAL STANDARD IEC/ISO 31010 Edition 1.0 2009-11 NORME INTERNATIONALE colour inside Risk management Risk assessment techniques Gestion des risques Techniques d'évaluation des risques INTERNATIONAL Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD. Couples thermoélectriques
This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 584-1 Deuxième édition Second edition 1995-09 Couples thermoélectriques Partie 1: Tables de Plus en détail This document is a preview generated by EVS
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 1213 Première édition First edition 1993-12 Enregistrement audio-analogique sur bande vidéo - Polarité de magnétisation Analogue audio recording on video Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 60118-7 Deuxième édition Second edition 2005-10 Electroacoustique Appareils de correction auditive Partie 7: Mesure des caractéristiques fonctionnelles Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD. Microphones de mesure. Measurement microphone
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 1094-3 Première édition First edition 1995-11 Microphones de mesure Partie 3: Méthode primaire pour l'étalonnage en champ libre des microphones étalons Plus en détail NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 60601-2-26 Deuxième édition Second edition 2002-11 Appareils électromédicaux Partie 2-26: Règles particulières de sécurité pour les électroencéphalographes Plus en détail ISO 85494 INTERNATIONAL STANDARD NORME INTERNATIONALE
INTERNATIONAL STANDARD NORME INTERNATIONALE ISO 85494 First edition Premiere Edition 1989-07-01 Prosthetics and orthotics - Vocabulary - Part 1: General terms for external limb prostheses and external Plus en détail FINAL DRAFT INTERNATIONAL STANDARD PROJET FINAL DE NORME INTERNATIONALE
PROJECT IEC 62572-3 Edition 1.0 2011-07 FINAL DRAFT INTERNATIONAL STANDARD PROJET FINAL DE NORME INTERNATIONALE Fibre optic active components and devices Reliability standards Part 3: Laser modules used Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
IEC 61010-2-033 Edition 1.0 2012-04 INTERNATIONAL STANDARD NORME INTERNATIONALE colour inside Safety requirements for electrical equipment for measurement, control, and laboratory use Part 2-033: Particular Plus en détail INTERNATIONAL STANDARD NORME INTERNATIONALE
IEC 62198 Edition 2.0 2013-11 INTERNATIONAL STANDARD NORME INTERNATIONALE colour inside Managing risk in projects Application guidelines Gestion des risques liés à un projet Lignes directrices pour l'application Plus en détail NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 60191-4 1999 AMENDEMENT 1 AMENDMENT 1 2001-11 Amendement 1 Normalisation mécanique des dispositifs à semiconducteurs Partie 4: Système de codification Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 61190-1-3 Première édition First edition 2002-03 Matériaux de fixation pour les assemblages électroniques Partie 1-3: Exigences relatives aux alliages Plus en détail COPYRIGHT Danish Standards. NOT FOR COMMERCIAL USE OR REPRODUCTION
COPYRIGHT Danish Standards. NOT FOR COMMERCIAL USE OR REPRODUCTION COPYRIGHT Danish Standards. NOT FOR COMMERCIAL USE OR REPRODUCTION COPYRIGHT Danish Standards. NOT FOR COMMERCIAL USE OR REPRODUCTION Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 1180-2 Première édition First edition 1994-06 Techniques des essais à haute tension pour matériel à basse tension - Partie 2: Matériel d'essai High-voltage Plus en détail This is a preview - click here to buy the full publication NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 62090 Première édition First edition 2002-11 Etiquettes d'emballage de produits pour composants électroniques, utilisant un code à barres et une symbologie Plus en détail NORME INTERNATIONALE INTERNATIONAL STANDARD
NORME INTERNATIONALE INTERNATIONAL STANDARD CEI IEC 61511-2 Première édition First edition 2003-07 Sécurité fonctionnelle Systèmes instrumentés de sécurité pour le secteur des industries de transformation Plus en détail 2016 © DocPlayer.fr Politique de confidentialité | Conditions de service | Feed-back