Source: http://docplayer.net/266401-Type-b-industrial-gas-appliances-in-western-australia.html
Timestamp: 2017-01-20 14:51:29
Document Index: 133183588

Matched Legal Cases: ['art 3', 'art 2', 'art 2', 'ART 1', 'ARTS 3', 'art 1', 'ART 1']

⭐Type B (industrial) gas appliances in Western Australia
Download "Type B (industrial) gas appliances in Western Australia"
1 Government of Western Australia Department of Commerce EnergySafety Guidelines for the approval of Type B (industrial) gas appliances in Western Australia2 Guidelines for the approval of Type B (industrial) gas appliances in Western Australia These guidelines have been developed and issued by the Director of Energy Safety, EnergySafety Division of the Department of Commerce, Western Australia. The guidelines assist members of the gas industry by providing information on: how to obtain approval for installing and operating Type B gas appliances; the roles of industry participants in having a Type B gas appliance approved; and the regime used to manage approval of Type B gas appliances in WA. This is the second edition of the guidelines. Comments and suggestions for improvements during periodic reviews are welcome. Any enquiries or comments in relation to the guidelines can be addressed to: Principal Engineer Gas Utilisation EnergySafety WA 303 Sevenoaks Street Cannington WA Internet: K Bowron Director of Energy Safety EnergySafety WA July 2009 APPROVAL OF TYPE B (INDUSTRIAL) GAS APPLIANCES IN WA3 Table of contents 1 Scope and application Introduction Referenced documents Definitions Regulatory regime Approval of Type B gas appliances Performance of gasfitting by licensed gas fitters Notices of completion Request of gas for commissioning Compliance badges for gasfitting work Inspection and issue of certificate of compliance Approval process New Type B appliance Existing Type B appliance that is modified Relocating a Type B appliance Flowcharts of approval process Roles of industry participants involved in getting a Type B appliance approved for use The applicant The licensed gas fitter The commissioning person The Type B Gas Appliance Inspector The gas supplier The owner/operator EnergySafety WA Technical considerations Contents of a technical submission Installation Commissioning...27 Appendix A Notice of completion...28 Appendix B Appendix C Certificate of compliance...29 Typical technical submission...30 APPROVAL OF INDUSTRIAL GAS APPLIANCES (TYPE B APPLIANCES) IN WA4 1 Scope and application These guidelines outline the regulatory and technical requirements and the roles and responsibilities of the various industry participants involved in having a Type B gas appliance approved for use. Approval for use is a detailed gas appliance inspection and certification function designed to ensure the safety of people, plant and property. A Type B gas appliance is a defined term in the Gas Standards (Gasfitting and Consumer Gas Installations) Regulations 1999, and generally encompasses large commercial and industrial type gas appliances. Examples of such gas appliances include, but are not limited to the following: Calciners Gas turbines Bake ovens Industrial ovens Heat-treatment furnaces Incinerators Dry out burners Process kilns Stationary gas engines Steam and hot-water boilers. With the aid of flow charts, the guidelines explain each step of the various stages of the approval process from preparing a technical submission, applying for installation approval through to obtaining final certification and permanent gas supply. The guidelines apply to: new Type B gas appliances; modifications to existing installed Type B gas appliances; and existing Type B gas appliances that are relocated. If any part of these guidelines is found to be in conflict with legislation, the legislation takes precedence. APPROVAL OF INDUSTRIAL GAS APPLIANCES (TYPE B APPLIANCES) IN WA 15 2 Introduction The guidelines have been developed to assist gas appliance manufacturers, engineering consultants, licensed gas fitters and owner/operators of Type B gas appliances to understand the regulatory and technical requirements and processes involved in having these appliances approved for use in Western Australia. The legislation relevant to the inspection, approval and certification of industrial gas appliances is the Gas Standards Act 1972 and the associated Gas Standards (Gasfitting and Consumer Gas Installations) Regulations Type B Gas Appliance Inspectors certify to the owner/operator of the appliance and/or the gas supplier that any installed Type B appliances, whether new, modified after installation or relocated comply with regulatory requirements including any guidelines issued by the Director of Energy Safety (the Director ) and have been properly commissioned to ensure safe operation. The Director offers an advisory service to consultants and project managers for installations involving Type B appliances. This service, under the direction of the Principal Engineer Gas Utilisation, is intended to provide rulings on acceptable technical standards at the early planning stages of an installation, particularly for imported equipment, which does not carry Australian certification. 3 Referenced documents The following publications are referenced in this document: Gas Standards Act 1972* Gas Standards (Gasfitting and Consumer Gas Installations) Regulations 1999* AS 1375 Industrial fuel fired appliances AS 3814 Industrial and commercial gas-fired appliances* AS 5601 Gas installations* AS Fundamental safety of electrical/electronic/programmable electronic safety-related systems (* denotes the publication is for sale at the EnergySafety WA Licensing Centre) 2 APPROVAL OF INDUSTRIAL GAS APPLIANCES (TYPE B APPLIANCES) IN WA6 4 Definitions For the purpose of this guideline, the following definitions apply. Words or terms not specifically defined below are to be interpreted as defined in relevant legislation or relevant technical standards/codes. AGA Appliance, Type A Appliance, Type B Gas appliance Approval for installation Approved Certification Commissioning Gas for commissioning Director EnergySafety WA Gas supplier Australian Gas Association An appliance of a class or type specified in Regulation 42B of the Gas Standards (Gasfitting and Consumer Gas Installations) Regulations 1999 An appliance that has a maximum hourly input rate exceeding 10 megajoules, but is neither a Type A appliance nor a mobile engine An appliance that consumes gas as a fuel Means obtaining written approval from a Type B Gas Appliance Inspector (after the review of the technical submission) so that the appliance can be installed Means approved by the Director of Energy Safety The issuing of a certificate of compliance by a Type B Gas Appliance Inspector for the appliance to be permanently connected to a gas supply Bringing into operation of the appliance Gas made available for the testing and commissioning of the appliance for a defined period (which requires the approval of a Type B Gas Appliance Inspector) prior to the appliance being permanently connected to the gas supply Director of Energy Safety The EnergySafety Division of the Department of Commerce in Western Australia A gas undertaker; a pipeline licensee; an operator of a reticulated gas supply system; or a person who supplies gas through a pressurised container APPROVAL OF INDUSTRIAL GAS APPLIANCES (TYPE B APPLIANCES) IN WA 37 Licensed gas fitter Modification Regulation Technical submission TUV A gas fitter currently licensed by the Director - This includes a holder of a permit, an authorisation, or a certificate of competency Means an upgrade to the gas valve train equipment, combustion/purge air system, flame monitoring system, and/or burner management system (not involving only like for like exchange of components) that changes the safety integrity of the existing system or takes the appliance out of its original approval criteria. Also encompasses conversions to use gas of a different type from another fuel to gas or from LP gas to natural gas and vice versa One or more regulation(s) referred to in the Gas Standards (Gasfitting and Consumer Gas Installations) Regulations 1999 A submission referred to in Appendix A of AS 3814, as an aid to the assessment of a Type B gas appliance to gain approval for installation Technische Uberwachung Verein (Technical Surveying Organisation) 5 Regulatory regime The following information provides key features of the gas utilisation regime in Western Australia. It is not a substitute for legislation currently in force. 5.1 Approval of Type B gas appliances The Gas Standards (Gasfitting and Consumer Gas Installations) Regulations 1999 (regulations) set out the requirements for approving, inspecting and certifying Type B appliances for permanent operation. The requirements apply to: new gas appliances; modifications to existing gas appliances; and gas appliances that are relocated. A brief summary of the regulatory regime that needs to be satisfied to allow these appliances to be approved for use is provided in Schedule 6, Clause 501 items (2) and (3) of the regulations as follows: Item (2) A Type B appliance must not be installed in a consumer s gas installation unless a) it is the same as an appliance that is currently approved for such installation by the Director; or b) it is individually approved in writing for such installation by an inspector. 4 APPROVAL OF INDUSTRIAL GAS APPLIANCES (TYPE B APPLIANCES) IN WA8 Item (3) Before a Type B appliance is installed by a gas fitter, the gas fitter must either a) obtain a copy of the appropriate approval by the Director under paragraph (2)(a) and satisfy himself or herself that the appliance is covered by that approval; or b) determine that the appliance has been individually approved for installation under paragraph (2)(b), by obtaining a copy of the approval. The following outlines the stages involved in approving a Type B gas appliance. Stage 1 Approval for installation Generally, an industrial gas appliance requires individual approval in writing by an inspector. This requires the owner/operator to satisfy a Type B Gas Appliance Inspector, through a technical submission (that is, a desktop appraisal), that the appliance will satisfy the technical standards required by the regulations, resulting in gaining an approval for installation. Stage 2 - Installation After obtaining approval for installation, the Type B gas appliance can be installed. Stage 3 Compliance demonstration This stage requires on-site demonstration to the Type B Gas Appliance Inspector that the installed appliance complies with all the technical and safety requirements for example, checks of the combustion process, and safety controls/interlocks. The Type B Gas Appliance Inspector issues a certificate of compliance when he/she is satisfied that the installation meets prescribed requirements. This is done in accordance with Regulation 22A(1) which states: An inspector may issue a certificate of compliance for a Type B appliance if the inspector has inspected the appliance and ascertained, so far as is practicable, that it complies with the requirements referred to in Regulation 32. Stage 4 Gas supplier approval Once a certificate of compliance is issued by the inspector, the appliance is allowed to be connected to a gas supply for permanent operation subject to the approval of the gas supplier. This usually involves an inspection of the total gas installation by the gas supplier. Alternative to inspection on-site (provision for inspection other than at place of installation) The inspection necessary under regulation 22A(1) and the necessary certification and badging may, with the approval of the Director (which must be sought), be carried out at another place for example, at the manufacturer s premises as provided for in the remainder of regulation 22A. This approach is an option to avoid unnecessary on-site inspections where simple appliances such as small kilns or furnaces are installed in remote areas. APPROVAL OF INDUSTRIAL GAS APPLIANCES (TYPE B APPLIANCES) IN WA 59 Examples where safety assurances can be demonstrated without on-site inspections are when: appliances are produced in quantity, to a specific design, are relatively small and merely require connection to a gas supply (similar to Type A appliances); and/or specific arrangements are in place for the installing gas fitter to install and commission to a demonstrated process or procedure. In this case, three copies of the certificate of compliance are to be issued to the manufacturer. The manufacturer must give a copy to the gas fitter, the owner/operator and the gas supplier. Generally, if an appliance manufacturer is seeking to obtain type approval (that is, for more than one appliance), approval must be sought from the Director. 5.2 Performance of gasfitting by licensed gas fitters Gasfitting work on an industrial gas installation must be carried out by a gas fitter with an appropriate gasfitting permit issued by EnergySafety WA. The following classes of gasfitting work are set out in Schedule 5 of the regulations. Class Class G Description All gasfitting work except gasfitting work classed as Class I, E or P Class I Gasfitting work (a) on a consumer s gas installation associated with a Type B appliance; or (b) on piping that has an operating pressure of more than 200 kpa, not being gasfitting work referred to in paragraph(a) or classified as Class E or P Class E Class P Gasfitting work associated with a mobile engine Gasfitting work on a gas installation associated with the storage and dispensing of gas for refuelling of a motor vehicle as defined in section 5 of the Road Traffic Act 1974 Class I is the class of gasfitting permit that applies to work on installations involving Type B appliances. Current holders of a certificate of competency are able to carry out such gasfitting work only if appropriate authorisation is registered on their certificates. The Director may also issue a gasfitting authorisation to an applicant employed by the owner/operator to carry out or supervise the gas installation or commissioning (classed as gasfitting work), on large complex projects or specialised work (coded welding) if the Director is satisfied that the applicant: 6 APPROVAL OF INDUSTRIAL GAS APPLIANCES (TYPE B APPLIANCES) IN WA10 has adequate theoretical and practical knowledge and adequate skills to carry out the gasfitting; has an adequate knowledge of the Act and its regulations; and is otherwise a fit and proper person to carry out the work. To obtain a gasfitting authorisation the applicant must submit the following information to the Director: scope of work to be carried out; location of the work; qualifications held to do the work; letter from employer or appliance manufacturer stating applicant is competent to do the work; the name of the Type B Gas Appliance Inspector who will carry out the final inspection of the appliance (if known); application form; and application fee. For further information on licensing matters, contact the Licensing Centre of EnergySafety WA. 5.3 Notices of completion The regulations require the licensed gas fitter to submit a notice of completion for the gas installation. These notices are available free of charge from EnergySafety WA or the gas supplier, in a book of sets of three forms with matching serial numbers. Within 48 hours of the completion of the work, the licensed gas fitter must give a notice of completion to the following: the original (blue form) to the gas supplier or EnergySafety WA as applicable; the duplicate copy (green form) to the person requesting the gasfitting work; and the triplicate copy (white form) to be retained by the gas fitter who performed the gasfitting work. In the notice of completion, the licensed gas fitter must certify that every part of the gas installation on which the gasfitting work was carried out, or that is affected by the work, complies with the requirements of the regulations, is safe to use and is completed to a trade finish. See Appendix A for a copy of a notice of completion. APPROVAL OF INDUSTRIAL GAS APPLIANCES (TYPE B APPLIANCES) IN WA 711 5.4 Request of gas for commissioning The permission of the gas supplier is required for the provision of gas for commissioning purposes. The gas fitter who is carrying out the commissioning of the appliance is responsible for applying to the gas supplier for commencement of gas. To satisfy the gas supplier s requirement, the request needs to be endorsed by a Type B Gas Appliance Inspector. The period during which the appliance can remain on gas for commissioning, that is, the period the appliance is connected to the gas supply for testing and commissioning prior to on-site inspection of the appliance by the Type B Gas Appliance Inspector, has to be approved by this Inspector. A Type B Gas Appliance Inspector may approve any period of no more than 28 days or a maximum of 90 days if a longer period for commissioning is required, provided he/she gives written notice to the Director of the approval. In special cases a further extension may be sought with the approval of the Director. 5.5 Compliance badges for gasfitting work An approved compliance badge (a label or metal plate) certifying compliance with the Gas Standards Act 1972 and its regulations must be attached to the appliance as described below. This identifies to the owner/operator and the gas supplier and subsequently to an EnergySafety WA Inspector that the gasfitting work complies with the requirements of the Gas Standards Act 1972 and its regulations. A compliance badge must be attached to the appliance in the following instances: a) Upon completion of the gas installation The licensed gas fitter must attach an approved metal badge to the appliance in an approved location, for example, alongside the appliance data plate. This badge signifies that the gas installation complies with the requirements of the relevant standards and the regulations. b) Upon completion of the commissioning of the gas appliance The commissioning gas fitter must attach an approved metal badge to the appliance in an approved location, for example alongside the appliance data plate. This badge signifies that the commissioning of the gas appliance complies with the requirements of the relevant standards and the regulations. 8 APPROVAL OF INDUSTRIAL GAS APPLIANCES (TYPE B APPLIANCES) IN WA12 Only approved metal compliance badges (shown below) must be used and they can be purchased from EnergySafety s Licensing Office. Gasfitting compliance badge 5.6 Inspection and issue of certificate of compliance People designated as Inspectors (Gas) for inspecting and approving Type B appliances are known as Type B Gas Appliance Inspectors. The Director has statutory authority under the provisions of the Energy Coordination Act 1994 to designate a person as an Inspector (Gas). Some Type B Gas Appliance Inspectors are employees of gas suppliers, such as WestNet Energy and Wesfarmers Kleenheat Gas, others are independent Inspectors employed by others or running their own inspection business. The current tendency is for independent inspectors to carry out much of this work. A list of independent Type B Gas Appliance Inspectors can be obtained: from EnergySafety WA s website; or by contacting the Gas Inspection Branch of EnergySafety WA. A Type B Gas Appliance Inspector has specific conditions attached to his/her designation, depending upon the holder s qualifications and experience. Currently there are three levels of Type B Gas Appliance Inspector: 1. Inspectors able to certify Type B gas appliances with an input capacity up to 10 GJ/h. 2. Inspectors able to certify Type B gas appliances with an input capacity up to 20 GJ/h. 3. Inspectors able to certify all Type B appliances. Independent inspectors normally offer their services on a fee-for-service basis and should be appointed by the owner/operator of the gas appliance installation or gas APPROVAL OF INDUSTRIAL GAS APPLIANCES (TYPE B APPLIANCES) IN WA 913 supplier, to ensure the certification is seen as independent of the work of persons that have designed or installed the appliance. After the Type B Gas Appliance Inspector has inspected the appliance installation and has ascertained that it complies with the requirements referred to in regulation 32 of the regulations, he/she is required to issue a certificate of compliance. This allows the appliance to remain permanently connected to a gas supply in a consumer s gas installation. The Type B Gas Appliance Inspector issues the certificate of compliance by: Providing the certificate in an approved form to the Director (refer Appendix B). Providing copies of the certificate to the: o o o licensed gas fitter who commissioned the appliance; consumer; and gas supplier. Attaching an approved metal badge (a sample of which is shown below) to the appliance in a conspicuous position. 6 Approval process 6.1 New Type B appliance The approval process, from getting approval to install the new gas appliance through to final certification and receiving permanent gas supply from the gas supplier to operate the appliance is broken up into four stages: 1. obtaining approval for installation ; 2. installation of the appliance; 3. commissioning of the appliance; and 4. certification by a Type B Gas Appliance Inspector. Approval badge issued by Type B Gas Appliance Inspector 10 APPROVAL OF INDUSTRIAL GAS APPLIANCES (TYPE B APPLIANCES) IN WA14 The following flowcharts that are shown in Section 6.4 illustrate the different phases of the approval process for the stakeholders Approval for installation The person seeking to have the gas appliance approved for installation must prepare a technical submission for review by a Type B Gas Appliance Inspector. It is recommended that the owner/operator of the installation engage the inspector to ensure the assessment is independent of the work of people contracted to design and/or install the appliance. For details of the contents of a technical submission, refer to Section 8 Technical considerations. A sample of a typical technical submission, demonstrating how technical compliance issues should be addressed in the submission, is provided in Appendix C of this document. After carrying out a desktop appraisal of the submission, and if satisfied that the proposed gas installation will meet the technical requirements of the prescribed code/standard, the Type B Gas Appliance Inspector will issue a notice advising that the appliance is approved for installation and can be installed. The inspector cannot be held responsible for giving an approval for installation for an appliance that is subsequently found not to work satisfactorily as a result of a fault or deficiency in the design of the appliance Installation of the appliance A gas fitter with a Class I permit or an appropriate certificate of competency or gasfitting authorisation issued by EnergySafety WA must carry out the gasfitting installation. Once installed, the licensed gas fitter must attach a compliance badge to the appliance, fill out the notice of completion and give a copy to the gas supplier and the owner. Refer to Appendix A for an approved form of the notice of completion Commissioning of the appliance The gas appliance must be commissioned by a licensed gas fitter. He/she can be the same gas fitter who carried out the installation or a commissioning person, who holds a Class I permit, working for the gas appliance s vendor. After satisfactorily completing the commissioning, the commissioning person must attach a compliance badge to the appliance, fill out the notice of completion and give a copy to the gas supplier and the owner/operator. A copy of his completed commissioning report and safety interlocks verification checklist must be forwarded to the Type B Gas Appliance Inspector for appraisal before requesting an on-site demonstration to the inspector of the operation of relevant safety interlocks. APPROVAL OF INDUSTRIAL GAS APPLIANCES (TYPE B APPLIANCES) IN WA 1115 6.1.4 Certification of the appliance Before the commissioning person leaves the site with the gas installation permanently connected a Type B Gas Appliance Inspector must first inspect the appliance and issue a certificate of compliance to allow the owner/operator to use the appliance in production mode. This requires the commissioning person to demonstrate to the Inspector the following compliance with regulatory requirements: all the safety interlocks, protective devices operate correctly; and the valve train equipment and burner management system installed are in accordance with the original approval given by the Inspector. If the Type B Gas Appliance Inspector is satisfied with the demonstration, and after inspection of the installation has ascertained that the installation complies with the requirements in regulation 32 of the regulations, the inspector will issue a certificate of compliance for the appliance and then attach an approval badge or label to the appliance. The following people receive a copy of the certificate of compliance: Director of Energy Safety; gas fitter who commissioned the appliance; owner/operator of the installed appliance; and gas supplier. The gas supplier may only give permission for gas to remain permanently connected to the appliance if the supplier: has received all notices of completion of the work; has received a copy of the certificate of compliance from the Type B Gas Appliance Inspector; and is satisfied that the gas installation complies with all prescribed statutory requirements (this may require additional checks and testing). A Type B Gas Appliance Inspector is not obliged to certify an appliance that he/she has given approval for installation, unless it works and it is demonstrated to comply with prescribed requirements. 6.2 Existing Type B appliance that is modified If a Type B appliance is to undergo a modification that changes the safety integrity of the existing gas system operation or takes the gas appliance out of its original approval criteria, one of the following processes needs to be followed to have the gas appliance installation approved depending on the appliance certification status. 12 APPROVAL OF INDUSTRIAL GAS APPLIANCES (TYPE B APPLIANCES) IN WA16 6.2.1 Existing Type B appliance without evidence of previous approval Prior to 1996, a Type B appliance required individual approval from a gas supplier inspector before provision of permanent gas supply by the gas supplier. However, certification of the appliance, with a certificate of approval or of compliance and the attachment of an approval badge, were not part of the approval process. The owner/operator of an existing gas appliance, installed prior to 1996, that is going to be modified is encouraged, as a matter of good engineering practice, to consider getting the appliance as part of the modification certified at the time Modification and certification of the modified appliance This approval process only applies to existing Type B appliances without evidence of previous approval, is considered good engineering practice and is preferred as a certificate of compliance and an approval badge is issued. A Type B Gas Appliance Inspector must give approval for installation in writing for the modified appliance before the gas appliance is modified. Where existing equipment that forms part of the gas system is to be reused in the installation, the submission must address the extent of any non-compliance of the existing equipment with the current code/standard requirements. The owner/operator can provide equivalent level of compliance/safety proposals for any issues of noncompliance from these requirements by submitting them in writing to the Type B Gas Appliance Inspector in order to enable the inspector to obtain approval from the Director. After carrying out a desktop appraisal of the submission, and if satisfied that the proposed modified appliance will meet the technical requirements of the prescribed codes/standards (including any approvals for variation/exemption granted by the Director), the Type B Gas Appliance Inspector will then issue a notice advising that the appliance, including the modification, is approved for installation and that work in modifying the appliance can commence. The installation, commissioning and certification requirements for the modified appliance are similar to that for a new appliance Modification without certification This approval process only applies to existing Type B appliances without evidence of previous approval. This process although acceptable, is not considered good engineering practice by EnergySafety and is therefore not the preferred process as a certificate of compliance and an approval badge are not issued. A Type B Gas Appliance Inspector must give approval for installation for the modification in writing before a gas appliance is modified. This requires the owner/operator to satisfy the Inspector, through a technical submission (a desktop appraisal), that the modification will satisfy the technical standards required by the regulations and the modified appliance will be safe to use. The Type B Gas Appliance Inspector, once satisfied that the modification meets the required standards, will issue a notice approving the modification. This is required before any work in modifying the appliance takes place. APPROVAL OF INDUSTRIAL GAS APPLIANCES (TYPE B APPLIANCES) IN WA 1317 After completion of the modification, the Type B Gas Appliance Inspector may inspect the gas appliance to ensure the modification is carried out in accordance with his/her earlier approval. As the existing uncertified modified appliance is already connected to the gas supply, there may not be a requirement for the gas supplier to give permission to supply gas for commissioning. Regulation 36(1aa) does however require the consumer to ensure the appliance is made available for testing and commissioning by a gas fitter before the consumer uses the appliance for production purposes. The existing gas appliance with the approved modification installed is safe to use but a certificate of compliance and an approval badge will not be issued Existing Type B Appliance with evidence of previous approval From May 1999, when the Gas Standards Regulations 1983 were replaced by the new Gas Standards (Gasfitting and Consumer Gas Installations) Regulations 1999, the Type B gas appliance approval process requires a Type B Gas Appliance Inspector to issue a certificate of compliance instead of a certificate of approval as well as an approval badge. Proposed modifications to a Type B appliance that has a certificate of approval or a certificate of compliance and an approval badge issued by an inspector are to be addressed in the following manner and the modified appliance must be re-certified. The owner/operator is still required to satisfy a Type B Gas Appliance Inspector, through a technical submission that the appliance, including the modification, will satisfy the technical standards required by the regulations. However, depending on the complexity of the proposed modification, the owner/operator may only need to address compliance of the proposed modifications with current standards. For example, an owner/operator proposes a modification, which replaces an existing Programmable Logic Controller (PLC) with a TUV certified PLC and intends using all other existing gas equipment, which are still currently approved for use by having a certificate of compliance or approval badge attached. Providing all existing protective devices and gas safety interlocks are utilised and set to within the gas appliance original approval criteria, the submission would only need to address in detail the PLC component. Subject to these modifications meeting the required standards, the Type B Gas Appliance Inspector will issue an approval for installation notice. This is required before any work in modifying the appliance can take place. The installation, commissioning and certification requirements for the modified appliance are similar to that for a new appliance. See note over page. 14 APPROVAL OF INDUSTRIAL GAS APPLIANCES (TYPE B APPLIANCES) IN WA18 Note: The following are examples of gasfitting work considered to be an appliance modification that do not require re-certification, but a Type B Gas Appliance Inspector s approval: relocating valve trains without any significant adjustment to protective limits or affecting the performance of the existing safety interlocks; adjusting protective limits, within the limits set in appliance s original operating range; and modifying pipework to allow the system to be pressure tested or to allow easier service access to valve train components. 6.3 Relocating a Type B appliance If a Type B appliance has to be dismantled and then re-assembled in a different location, the relocated appliance requires individual approval in writing by an inspector. The process for gaining approval for installation is similar to that of a modification to a Type B appliance. The inspection required under regulation 22A(1) and the necessary certification and badging may, with the approval of the Director, be waived if it can be demonstrated that relocating a Type B gas appliance does not involve re-assembly and meets the following criteria: relatively small gas appliance, eg small kilns and merely requires connection to a gas supply; adequate installation and commissioning instructions are in place for the installing gas fitter to install and commission; and has a certificate of approval or a certificate of compliance and a compliance badge (recognised by the Director) attached; This requires the owner/operator to apply in writing to the Director providing evidence to support the waiving of the requirement for having to re-certify and re-badge the appliance. After relocating the gas appliance, the installing gas fitter must then submit a notice of completion for the work to the relevant gas supplier who will inspect the gas installation in accordance with the requirements of the gas supplier s inspection plan. APPROVAL OF INDUSTRIAL GAS APPLIANCES (TYPE B APPLIANCES) IN WA 1519 6.4 Flowcharts of approval process Approval for installation and installation of an appliance TYPE B GAS APPLIANCE INSPECTOR APPLICANT, APPLIANCE PROVIDER, GAS FITTER OR COMMISSIONING PERSON OWNER / OPERATOR GAS SUPPLIER APPROVAL FOR INSTALLATION INSTALLATION OF APPLIANCE REVIEWS APPLIANCE INSTALLATION SUBMISSION ACCEPTS SUBMISSION, ISSUES APPROVAL FOR INSTALLATION REQUESTS A COPY OF THE NOTICE OF COMPLETION (FOR INSTALLATION) PREPARES A TECHNICAL SUBMISSION FOR REVIEW BY A TYPE B GAS APPLIANCE INSPECTOR RECEIVES SUBMISSION REVIEW OUTCOME AND RESOLVES TECHNICAL COMPLIANCE ISSUES WITH THE INSPECTOR FINALISES TECHNICAL SUBMISSION APPLICANT RECEIVES NOTICE OF APPROVAL FOR INSTALLATIO N GAS FITTER INSTALLS APPLIANCE AND ATTACHES A COMPLIANCE BADGE ON COMPLETION GAS FITTER GIVES A NOTICE OF COMPLETION (FOR INSTALLATION) RECEIVES A COPY OF THE NOTICE OF COMPLETION (FOR INSTALLATION) RECEIVES A COPY OF THE NOTICE APPROVAL FOR INSTALLATION RECEIVES THE NOTICE OF COMPLETION (FOR INSTALLATION) VERIFIES THAT THE APPLIANCE IS INSTALLED IN ACCORDANCE WITH THE SUBMISSION 16 APPROVAL OF INDUSTRIAL GAS APPLIANCES (TYPE B APPLIANCES) IN WA20 6.4.2 Commissioning of the appliance TYPE B GAS APPLIANCE INSPECTOR APPLICANT APPLIANCE PROVIDER, GAS FITTER OR COMMISSIONING PERSON OWNER / OPERATOR GAS SUPPLIER ENDORSES APPLIANCE READY FOR COMMISSIONING COMMISSIONING PERSON REQUESTS GAS FOR COMMISSIONING VERIFIES APPLIANCE INSTALLATION COMPLIANCE GRANTS EXTENSION OF THE PERIOD TO COMMISSION THE APPLIANCE, IF REQUIRED COMMISSIONING PERSON COMMISSIONS APPLIANCE AND SUBMITS COMPLETED CHECKLIST(S) ALLOWS COMMENCEMENT OF GAS TO BE SUPPLIED FOR COMMISSIONING RECEIVES COMPLETED CHECKLIST(S) COMMISSIONING PERSON ATTACHES A COMPLIANCE BADGE (FOR COMMISSIONING) TO THE APPLIANCE WITNESSES THE DEMONSTRATION OF THE APPLIAN CE SAFETY REGIME COMPLIANCE COMMISSIONING PERSON DEMONSTRATES THE APPLIANCE S SAFETY REGIME COMMISSIONING PERSON GIVES A NOTICE OF COMPLETION (FOR COMMISSIONING) REQUESTS A COPY OF THE NOTICE OF COMPLETION (F OR COMMISSIONING) RECEIVES A COPY OF THE NOTICE OF COMPLETION (FOR COMMISSIONING) RECEIVES A COPY OF THE NOTICE OF COMPLETION (FOR COMMISSIONING) APPROVAL OF INDUSTRIAL GAS APPLIANCES (TYPE B APPLIANCES) IN WA 17 View more
Contractor Connect Scheme Electrical Contractor and Worker Handbook January 2016 Document release information Document number 13553681 Document title Revision status Contractor Connect Scheme handbook More information Programmable Safety and Control Systems for Use in Burner Control. Adam Hallinan Pilz Safe Automation Melbourne
Programmable Safety and Control Systems for Use in Burner Control Adam Hallinan Pilz Safe Automation Melbourne Abstract Programmable controllers for Burner control can simplify the installation of large More information Guidance notes to the CER s recently enacted Gas Works Regulations. These Guidance Notes should be read in conjunction with:
Guidance notes to the CER s recently enacted Gas Works Regulations These Guidance Notes should be read in conjunction with: ELECTRICITY REGULATION ACT 1999 (GAS WORKS) REGULATIONS 2009 Who should read More information On-Site Risk Management Audit Checklist for Program Level 3 Process
On-Site Risk Management Audit Checklist for Program Level 3 Process Auditor name: Date: I. Facility Information: Facility name: Facility location: County: Contact name: RMP Facility I.D. Phone Number: More information Gas Standards and Safety. Guidance Note GAS INSTALLATIONS SUPPLIED FROM BIOGAS FACILITIES - ACCEPTANCE REQUIREMENTS GAS ACT 2000
Gas Standards and Safety Guidance Note January 2015 (GN106) Version 1.0 GAS INSTALLATIONS SUPPLIED FROM BIOGAS FACILITIES - ACCEPTANCE REQUIREMENTS GAS ACT 2000 A guide to assist in the design of biogas More information APPLICATION PACKAGE FOR LISTING AS A WATER AND/OR WASTEWATER INFRASTRUCTURE PROVIDER FOR DESIGNERS, CONSTRUCTORS
APPLICATION PACKAGE FOR LISTING AS A WATER AND/OR WASTEWATER INFRASTRUCTURE PROVIDER FOR DESIGNERS, CONSTRUCTORS (Major & minor works) TO THE MANAGING NEW DEVELOPMENTS PROCESS For information regarding More information Australian Transport Council. National Standard for the Administration of Marine Safety SECTION 4 SURVEYS OF VESSELS
Australian Transport Council National Standard for the Administration of Marine Safety SECTION 4 SURVEYS OF VESSELS Edition 1 Draft for comment issued 20 December 2005 Endorsed by the Australian Transport More information Use of gas appliances in public venues
Government of Western Australia Department of Commerce EnergySafety Use of gas appliances in public venues This publication will assist event organisers, venue organisers, asset managers and catering vendors More information EA IAF/ILAC Guidance. on the Application of ISO/IEC 17020:1998
Publication Reference EA IAF/ILAC-A4: 2004 EA IAF/ILAC Guidance on the Application of ISO/IEC 17020:1998 PURPOSE This guidance document is for ISO/IEC 17020: General Criteria for the operation of various More information Owner-User Pressure Equipment Integrity Management Requirements
the pressure equipment safety authority Owner-User Pressure Equipment Integrity Management Requirements AB-512 Edition 2, Revision 0 Issued 2015-06-25 Owner-user Pressure Equipment Integrity Management More information Guidelines for the Acceptance of Manufacturer's Quality Assurance Systems for Welding Consumables
(1987) Guidelines for the Acceptance of Manufacturer's Quality Assurance Systems for Welding Consumables 1. General 1.1 Introduction 1.1.1 The present guidelines are to serve as a supplement to the IACS More information Strategic Industry Audit Report
Strategic Industry Audit Report www.tac.wa.gov.au 2012 Strategic Industry Audit of qualifications which lead to an electrician s licence in Western Australia The Training Accreditation Council conducted More information Certification Process Requirements
SAAS Certification Process Requirements SAAS Procedure 200 and ISO/IEC 17021 Social Accountability Accreditation Services, June 2010 Accreditation Process and Policies SAAS Normative Requirements SAAS More information LIFT MANAGEMENT. Version 01 / November 2015 Page 1 of 9 Approved by Health & Safety Committee
LIFT MANAGEMENT Version 01 / November 2015 Page 1 of 9 Approved by Health & Safety Committee This is a controlled document. It should not be altered in any way without the express permission of the author More information COMMISSIONING OF FIRE PROTECTION SYSTEMS
COMMISSIONING OF FIRE PROTECTION SYSTEMS OWNER FURNISHED The owner directly contracts an independent third party commissioning agent for this project. This Commissioning Plan has been included for reference More information 18.0 Flying Training Authorisation on an AOC
18.1 Introduction Flying training, is a commercial purpose as defined by CAR 206(1)(a)(vi), and it is required by s27(9) of the Act to be conducted under the authorisation of an AOC. CAR 206(1)(a)(vi) More information The city of Milwaukee s Sample Preventative maintenance manual for Electronically monitored boilers
The city of Milwaukee s Sample Preventative maintenance manual for Electronically monitored boilers Table of Contents Introduction... 1 Intention... 2 Authority and responsibility letter... 3 Organizational More information For the Design, Installation, Commissioning & Maintenance of Fixed Gaseous Fire Suppression Systems
BAFE Scheme: SP203-3 Version 1: July 2008 Amendment No: 1 Fire Protection Industry Scheme, Reference SP203 Part 3 For the Design, Installation, Commissioning & Maintenance of Fixed Gaseous Fire Suppression More information WHS Contractor Management Procedure
Wudinna District Council 1. Overview Wudinna District Council as part of its commitment under its Policy recognises its obligation to: Ensure, so far as is reasonably practicable, the health and safety More information Drinking Water Quality Management Plan Review and Audit Guideline
Drinking Water Quality Management Plan Review and Audit Guideline This publication has been compiled by Queensland Water Supply Regulator, Department of Energy and Water Supply. State of Queensland, 2013. More information WESTERN AUSTRALIA HEAVY VEHICLE ACCREDITATION SCHEME (WAHVAS) BUSINESS RULES (DRAFT)
WESTERN AUSTRALIA HEAVY VEHICLE ACCREDITATION SCHEME (WAHVAS) BUSINESS RULES (DRAFT) June 2015 DRAFT v1.3 Remove on final Contents 1. BUSINESS RULES OVERVIEW 3 1.1 Purpose 3 1.2 Legal Status of the Business More information Contractor Performance Report Scoring Guide
Report Main Roads Western Australia Table of Contents CONTRACTOR PERFORMANCE REPORT SCORING GUIDE... 3 1. APPLICATION... 3 2. REPORTING... 3 2.1 Objectives... 3 2.2 Frequency... 3 2.3 Responsibility... More information Electrical safety of grid-connected solar installations in Western Australia December 2011
Electrical safety of grid-connected solar installations in Western Australia December 2011 Level 1, 303 Sevenoaks Street (cnr Grose Avenue) Cannington, Western Australia 6107 PO Box 135 Cannington WA 6987 More information TRANSNET PIPELINES. TPL 25 Tarlton Commissioning Plan
TPL 25 Tarlton Commissioning Plan Issue Date: 03/07/2015 Revision No.: A Project No.: 11992 Date: 03/07/2015 Document Title: TPL25 Tarlton Commissioning Plan Author: Edward Standen Revision Number: A Checked More information INDEX 9-7-100 GENERAL
REGULATION 9 INORGANIC GASEOUS POLLUTANTS RULE 7 NITROGEN OXIDES AND CARBON MONOXIDE FROM INDUSTRIAL, INSTITUTIONAL AND COMMERCIAL BOILERS, STEAM GENERATORS AND PROCESS HEATERS INDEX 9-7-100 GENERAL 9-7-101 More information GUIDELINE NO. 22 REGULATORY AUDITS OF ENERGY BUSINESSES
Level 37, 2 Lonsdale Street Melbourne 3000, Australia Telephone.+61 3 9302 1300 +61 1300 664 969 Facsimile +61 3 9302 1303 GUIDELINE NO. 22 REGULATORY AUDITS OF ENERGY BUSINESSES ENERGY INDUSTRIES JANUARY More information SECTION A... 3 SECTION B... 7
BRITISH COLUMBIA SAFETY AUTHORITY Manual for Owners and Operators of Special Status Plants Risk Assessed and General Supervision Date: March 12, 2012 Controlled Document: MAN -4000-03 I TABLE OF CONTENTS More information WHS CONTRACTOR MANAGEMENT PROCEDURE
1. Overview The Port Augusta City Council as part of its commitment under its WHS Contractor Management policy, recognises its obligation to: Ensure, so far as is reasonably practicable, the health and More information RTP s NUCLEAR QUALITY ASSURANCE PROGRAM
RTP s NUCLEAR QUALITY ASSURANCE PROGRAM RTP operates under one quality program, whether you purchase products that are commercial grade, nuclear safety-related or industrial safety compliant (IEC 61508). More information Preparation of a Rail Safety Management System Guideline
Preparation of a Rail Safety Management System Guideline Page 1 of 99 Version History Version No. Approved by Date approved Review date 1 By 20 January 2014 Guideline for Preparation of a Safety Management More information Policies and Procedures Gas Technician/Oil Burner Technician Certification
Gas Technician/Oil Burner Technician Certification (under Ontario Regulation 215/01 Technical Standards and Safety Act, 2000) TSSA Training & Certification Services www.tssa.org Table of Contents Introduction... More information CER Audit and Inspection System. part of the Petroleum Safety Framework
CER Audit and Inspection System part of the Petroleum Safety Framework DOCUMENT TYPE: Consultation REFERENCE: CER/15/221 DATE PUBLISHED: 04 th September 2015 VERSION 1.0 The Commission for Energy Regulation, More information EN 4179/NAS 410 Interpretation
EN 4179/NAS 410 Interpretation The NANDTB has adopted NAS 410 / EN 4179 in lieu of AS 3669 as the standard for the qualification and approval of NDT technicians. Employers applying these standards sometimes More information MANAGEMENT AND USE OF WORK EQUIPMENT: PRESSURE SYSTEMS
Health & Safety Services Unit name goes here Safety Code of Practice 46, Part 2 1st Edition, November 2009 MANAGEMENT AND USE OF WORK EQUIPMENT: PRESSURE SYSTEMS University of Reading 2015 Page 1 Contents More information Australian Standard Industrial and commercial gas-fired appliances
Australian Standard Industrial and commercial gas-fired appliances AS 3814 2009 (Incorporating Amendment No. 1) Page i of 16 This page is left intentionally blank Page ii of 111 Industrial and commercial More information APPLICATION FOR GAS WORK AUTHORISATION (MOTOR FUEL)
Applicant Details APPLICATION FOR GAS WORK AUTHORISATION (MOTOR FUEL) Petroleum and Gas (Production and Safety) Act and Regulation 2004 Corporation Application Details Do NOT complete if you are an Individual More information APES 320 Quality Control for Firms
APES 320 Quality Control for Firms APES 320 Quality Control for Firms is based on International Standard on Quality Control (ISQC 1) (as published in the Handbook of International Auditing, Assurance, More information SAFETY and HEALTH MANAGEMENT STANDARDS
SAFETY and HEALTH STANDARDS The Verve Energy Occupational Safety and Health Management Standards have been designed to: Meet the Recognised Industry Practices & Standards and AS/NZS 4801 Table of Contents More information QA Procedure Page 1 Appendix A
*Changes from the previous QASE noted by "yellow" highlight of block Evaluation Summary Company: Prepared By: Section Element Manual Audit OK Objective Evidence 2.1 Objective of Quality Assurance Program More information ENERGYSAFETY DIVISION BUSINESS PLAN 2013/14. December 2012
ENERGYSAFETY DIVISION BUSINESS PLAN 2013/14 December 2012 This Business Plan was approved under Part 2 of the Energy Safety Act 2006 by the Hon Simon O Brien MLC Minister for Commerce on 14 January 2013 More information COMPLIANCE FRAMEWORK AND REPORTING GUIDELINES
COMPLIANCE FRAMEWORK AND REPORTING GUIDELINES DRAFT FOR CONSULTATION June 2015 38 Cavenagh Street DARWIN NT 0800 Postal Address GPO Box 915 DARWIN NT 0801 Email: utilities.commission@nt.gov.au Website: More information Building Commissioning 17900-1
SECTION 17900 BUILDING COMMISSIONING PART 1 - GENERAL 1.01 WORK DESCRIPTION: A. General: 1. The Commissioning process is a joint team effort to ensure that all mechanical equipment, controls, and systems More information Benchmark OHS Consulting Pty Ltd Self Assessment WHS Audit Tool
Benchmark OHS Consulting Pty Ltd Self Assessment WHS Audit Tool This WHS Auditing System Tool is to be used as a self-assessment of YOUR COMPANY compliance with AS 4801 and the Work Health and Safety Act More information EA-6/02 M: 2013. EA Guidelines on the Use of EN 45 011 and ISO/IEC 17021 for Certification to EN ISO 3834. Publication Reference PURPOSE
Publication Reference EA-6/02 M: 2013 EA Guidelines on the Use of EN 45 011 and ISO/IEC 17021 for Certification to PURPOSE EN ISO 3834 The purpose of this document is to provide the basis for the harmonisation More information Licence condition handbook
Licence condition handbook January 2016 Office for Nuclear Regulation page 1 of 24 The standard licence conditions attached to nuclear site licences Introduction This booklet has been produced as an aide-memoire More information Gas Supply (General) Regulation 1997
New South Wales Gas Supply (General) Regulation 1997 under the Gas Supply Act 1996 His Excellency the Lieutenant-Governor, with the advice of the Executive Council, has made the following Regulation under More information Prequalification of Roading Contractors
Prequalification of Roading Contractors Manual for Roading Contractor Prequalification for Authorised CCC Roading Work Please send prequalification applications to Chris Nordstrom Project Manager Capital More information GUIDE TO IMPLEMENTING A REGULATORY FOOD SAFETY AUDITOR SYSTEM
GUIDE TO IMPLEMENTING A REGULATORY FOOD SAFETY AUDITOR SYSTEM FEBRUARY 2016 2 Contents Introduction... 4 Scope and objectives... 5 Scope... 5 Objectives... 5 Responsibilities... 5 The role of the licensee More information CONTRACTOR SAFETY MANAGEMENT PROCEDURE
CONTRACTOR SAFETY MANAGEMENT PROCEDURE Version 1.0 TRIM file number Short description Relevant to Authority Responsible officer Responsible office Date introduced July 20, 2015 Date(s) modified June 11, More information Application for Approved (Overseas/Local) Third Party Inspection Agency for Lifting Equipment
Occupational Safety and Health Division 18 Havelock Road #03-02 Singapore 059764 Tel: 64385122 www.mom.gov.sg mom_oshd@mom.gov.sg Application for Approved (Overseas/Local) Third Party Inspection Agency More information ASBESTOS REMOVAL LICENCE ASBESTOS NOTIFICATIONS
GUIDE FOR APPLICANTS ASBESTOS REMOVAL LICENCE ASBESTOS NOTIFICATIONS TABLE OF CONTENTS INTRODUCTION... 2 WHY YOU NEED A LICENCE... 2 WHY YOU NEED TO NOTIFY... 2 LICENCE TYPES... 2 SCOPE... 2 WHO MAY APPLY More information MP Plumbing & Heating Ltd Quality Policy Manual THE QUALITY POLICY STATEMENT OF:
THE QUALITY POLICY STATEMENT OF: MP Plumbing & Heating Ltd Unit 8,The Metro Centre, Bridge Road, Orpington BR5 2BE Telephone: 01689 822188 Fax: 01689 897 733 E-Mail: info@mpplumbingheating.co.uk Web page: More information NABL NATIONAL ACCREDITATION
NABL 160 NABL NATIONAL ACCREDITATION BOARD FOR TESTING AND CALIBRATION LABORATORIES GUIDE for PREPARING A QUALITY MANUAL ISSUE NO. : 05 AMENDMENT NO : 00 ISSUE DATE: 27.06.2012 AMENDMENT DATE: -- Amendment More information Guidance on Safe Operation of Boilers
Guidance on Safe Operation of Boilers Ref: BG01 A joint document by the Safety Assessment Federation and Combustion Engineering Association produced in consultation with the Health & Safety Executive. More information Is your current safety system compliant to today's safety standard?
Is your current safety system compliant to today's safety standard? Abstract It is estimated that about 66% of the Programmable Electronic Systems (PES) running in the process industry were installed before More information Quality Management System
LH Sleightholme Ltd, Westfield Works, Helperthorpe, Malton, North Yorkshire YO17 8TQ Quality Management System MANUAL ISO 9001:2008 This Quality Management System Manual has been issued on the authority More information G2 Contract Management Plan Date: July 2014 Edition 1 / Revision 0
G2 Contract Management Plan Date: Edition 1 / Revision 0 REVISION REGISTER Ed/Rev Number Ed 1 / Rev 0 Clause Number All G2.1 G2.2 G2.3 G2.4 G2.5 G2.5 G2.6.1 G2.6.2 G2.6.3 G2.6.4 G2.6.5 G2.6.6 G2.6.7 G2.7 More information ELECTRICAL SAFETY REGULATION 2002
Queensland Electrical Safety Act 2002 ELECTRICAL SAFETY REGULATION 2002 Reprinted as in force on 1 January 2004 (includes commenced amendments up to 2003 Act No. 63) Reprint No. 1F This reprint is prepared More information GUIDELINES FOR THE APPROVAL OF NATURAL GAS APPLIANCE INSTALLATIONS IN ISRAEL
GUIDELINES FOR THE APPROVAL OF NATURAL GAS APPLIANCE INSTALLATIONS IN ISRAEL 1 Scope These guidelines outline the regulatory and technical requirements and the roles and Responsibilities of the various More information Requirements. for. CCTV Installation
PSA 2006_12 Requirements for CCTV Installation Table of Contents Page No. 1. Introduction...3 2. Normative References...3 3. Definitions...4 4. Overview...6 5. Location Survey...6 6. System Design...6 More information Code of Practice. for Inspecting and Certifying Buildings and Works. Building Control Regulations 2014
for Inspecting and Certifying Buildings and Works Building Control Regulations 2014 February, 2014 Table of Contents 1. Introduction 1 1.1 Status and Purpose of Code 1 1.2 Overview of Code 1 1.3 Application More information CP14 ISSUE 5 DATED 1 st OCTOBER 2015 BINDT Audit Procedure Conformity Assessment and Certification/Verification of Management Systems
Certification Services Division Newton Building, St George s Avenue Northampton, NN2 6JB United Kingdom Tel: +44(0)1604-893-811. Fax: +44(0)1604-893-868. E-mail: pcn@bindt.org CP14 ISSUE 5 DATED 1 st OCTOBER More information TG 47-01. TRANSITIONAL GUIDELINES FOR ISO/IEC 17021-1:2015, ISO 9001:2015 and ISO 14001:2015 CERTIFICATION BODIES
TRANSITIONAL GUIDELINES FOR ISO/IEC 17021-1:2015, ISO 9001:2015 and ISO 14001:2015 CERTIFICATION BODIES Approved By: Senior Manager: Mpho Phaloane Created By: Field Manager: John Ndalamo Date of Approval: More information ASSET CREATION DEVELOPER PROCESS INSTRUCTIONS TO DESIGNERS - MAJOR WORKS -
ASSET CREATION DEVELOPER PROCESS INSTRUCTIONS TO DESIGNERS - MAJOR WORKS - INSTRUCTIONS TO DESIGNERS CONTENTS 1. INTRODUCTION 3 2. ROLE OF THE WATER SERVICING COORDINATOR 3 3. ROLE OF THE DESIGNER 3 4. More information CHECKLIST ISO/IEC 17021:2011 Conformity Assessment Requirements for Bodies Providing Audit and Certification of Management Systems
Date(s) of Evaluation: CHECKLIST ISO/IEC 17021:2011 Conformity Assessment Requirements for Bodies Providing Audit and Certification of Management Systems Assessor(s) & Observer(s): Organization: Area/Field More information Designation of Inspectors (Electricity) in Western Australia
Government of Western Australia Department of Commerce Application and Renewal Designation of Inspectors (Electricity) in Western Australia DP0668_2015_01 Explanatory notes Purpose of this document This More information EUROPEAN INDUSTRIAL GASES ASSOCIATION
WORK PERMIT SYSTEMS IGC Doc 40/02/E EUROPEAN INDUSTRIAL GASES ASSOCIATION AVENUE DES ARTS 3-5 B 1210 BRUSSELS Tel : +32 2 217 70 98 Fax : +32 2 219 85 14 E-mail : info@eiga.org Internet : http://www.eiga.org More information Land Agents Regulations 2010
Version: 21.11.2015 South Australia Land Agents Regulations 2010 under the Land Agents Act 1994 Contents Part 1 Preliminary 1 Short title 3 Interpretation 4 Fees payment, waiver, reduction and refund Part More information Clients in Construction Best Practice Guidance
Clients in Construction Best Practice Guidance Published in 2009 by the, Metropolitan Building, James Joyce Street, Dublin 1. Copyright The January 2009 Clients in Construction: Best Practice Guidance More information Procedure PS-TNI-001 Information Security Management System Certification
Table of Contents 1. Purpose 2. Scope 3. Definitions 4. Responsibilities 4.1 Head of the Certification Body 4.2 QM Manager / Management Representative 4.3 Auditors 4.4 Order Service 4.5 Certification Service More information HOW TO BECOME AN APPROVED PROVIDER OF WHS ENTRY PERMIT HOLDER (WHS-EPH) TRAINING IN SOUTH AUSTRALIA. WHS-EPH Training Course Guidance
HOW TO BECOME AN APPROVED PROVIDER OF WHS ENTRY PERMIT HOLDER (WHS-EPH) TRAINING IN SOUTH AUSTRALIA WHS-EPH Training Course Guidance Contents INTRODUCTION... 4 PURPOSE... 5 WHS-EPH Training Course Requirements... More information Rule 1146.2 - EMISSIONS OF OXIDES OF NITROGEN FROM LARGE WATER HEATERS AND SMALL BOILERS
Rule 1146.2 - EMISSIONS OF OXIDES OF NITROGEN FROM LARGE WATER HEATERS AND SMALL BOILERS (a) Purpose and Applicability The purpose of this rule is to reduce NOx emissions from natural gas-fired large (commercial) More information Quality Manual. This manual is proprietary and no part thereof shall be copied without written authorisation from the company. Ref: Quality Manual.
This manual is proprietary and no part thereof shall be copied without written authorisation from the company Ref: Quality Manual.ind Issue: June 2009 INDEX 1 Amendment Status 2 Controlled Distribution More information Policies and Procedures Industrial Maintenance Technician Customized Training Programs and Challenges to IMT Training Requirements
Policies and Procedures Industrial Maintenance Technician Customized Training Programs and Challenges to IMT Training Requirements NOTE: There is also a Policies and Procedures Document for IMT Training More information IN FIDIC 99 RED BOOK COULD IT BE SUPERVISION CONSTRUCTION. Dr. Munther M. Saket. The Role of the Engineer
THE ROLE OF THE ENGINEER IN FIDIC 99 RED BOOK COULD IT BE PERFORMED BY A SUPERVISION CONSULTANT & A CONSTRUCTION MANAGER? Dr. Munther M. Saket December 2010 The Role of the Engineer 1 The ENGINEER S ROLE More information Release 1. BSBWHS508A Manage WHS hazards associated with plant
Release 1 BSBWHS508A Manage WHS hazards associated with plant BSBWHS508A Manage WHS hazards associated with plant Modification History Release Release 1 Comments This Unit first released with BSB07 Business More information Gatekeeper PKI Framework. February 2009. Registration Authority Operations Manual Review Criteria
Gatekeeper PKI Framework ISBN 1 921182 24 5 Department of Finance and Deregulation Australian Government Information Management Office Commonwealth of Australia 2009 This work is copyright. Apart from More information Standards Compliance and User Requirements for Industrial and Utility Boiler Control Systems By: Dr. Issam Mukhtar & Geoff Rogers
Standards Compliance and User Requirements for Industrial and Utility Boiler Control Systems By: Dr. Issam Mukhtar & Geoff Rogers Presented at IDC Boilers Conference, Perth November 2008 Abstract: The More information The Electrical Contractor Safety Program Guide
The Electrical Contractor Safety Program Guide September 2013 Electrical Hazard Warning Sign Disclaimer Whilst this guide endeavors to provide general information on work health and safety issues relating More information Management of Contractors and Suppliers Procedure
Management of Contractors and HSE P1101 Table of Content 1 DOCUMENT CONTROL... 2 2 PURPOSE... 3 3 SCOPE... 3 4 DEFINITIONS... 3 5 ROLES AND RESPONSIBILITIES... 5 6 PROCESS DETAILS... 9 6.1 Confirm Need More information Inspect and Test FPAS Units of Competencies descriptions
Inspect and Test FPAS Units of Competencies descriptions FPAS incorporates the following units of competency across ten (10) categories of inspect and test activities. CPPCMN2002A Participate in workplace More information BUILDING STANDARDS DIVISION IMPROVING COMPLIANCE WITH BUILDING REGULATIONS CONSULTATION REPORT
BUILDING STANDARDS DIVISION IMPROVING COMPLIANCE WITH BUILDING REGULATIONS CONSULTATION REPORT EXECUTIVE SUMMARY 1. INTRODUCTION 2. THE CONSULTATION PROCESS 3. CONSULTATION RESPONSES 4. ANALYSIS 5. RESPONSES More information Network Certification Body
Network Certification Body Scheme rules for assessment of railway projects to requirements of the Railways Interoperability Regulations as a Notified and Designated Body 1 NCB_MS_56 Contents 1 Normative More information A. The Commissioning Authority (CxA) has been contracted or will be contracted directly with the Owner for this project.
DIVISION 23 HEATING, VENTILATING, AND AIR CONDITIONING (HVAC) SECTION 23 08 02 PART 1 GENERAL 1.01 AUTHORITY (CxA) A. The Commissioning Authority (CxA) has been contracted or will be contracted directly More information GUIDELINES FOR INVESTMENT ADVISERS AND INVESTMENT REPRESENTATIVES UNDER THE SECURITIES INDUSTRY ACT 1983
GUIDELINES FOR INVESTMENT ADVISERS AND INVESTMENT REPRESENTATIVES UNDER THE SECURITIES INDUSTRY ACT 1983 Date Issued: 4 March 2004 1 GUIDELINES FOR INVESTMENT ADVISERS AND INVESTMENT REPRESENTATIVES UNDER More information CIS Asset Identification and Labelling Standard
CIS Asset Identification and Labelling Standard The University of Sydney Engineering & Sustainability Team Document Control Document Name: CIS Asset Identification and Labelling Standard Document ID: CIS-PLA-STD-Asset More information Energy Products (Safety and Efficiency) Regulations 2012
Version: 10.5.2012 South Australia Energy Products (Safety and Efficiency) Regulations 2012 under the Energy Products (Safety and Efficiency) Act 2000 Contents 1 Short title 2 Commencement 3 Interpretation More information HKCAS Supplementary Criteria No. 8
Page 1 of 12 HKCAS Supplementary Criteria No. 8 Accreditation Programme for Information Security Management System (ISMS) Certification 1 INTRODUCTION 1.1 HKAS accreditation for information security management More information Memorandum of Understanding between the NSW Ministry of Health and Sydney Water Corporation
Page 1 of 11 Memorandum of Understanding between the NSW Ministry of Health and Sydney Water Corporation This work is copyright. It may be reproduced in whole or in part for study or training purposes More information EXETER TOWNSHIP DRY OR WET CHEMICAL FIRE SUPPRESSION SYSTEMS
DRY OR WET CHEMICAL FIRE SUPPRESSION SYSTEMS POLICY STATEMENT This policy applies to NEW Dry or Wet chemical fire suppression systems. The Authority Having Jurisdiction will not waive major criteria in More information An Alternative Method for Maintaining ISO 9001/2/3 Certification / Registration
International Accreditation Forum, Inc. An Alternative Method for Maintaining ISO 9001/2/3 Certification / Registration A Discussion Paper The International Accreditation Forum, Inc. (IAF) operates a program More information Spillemyndigheden s Certification Programme Change Management Programme
SCP.06.00.EN.1.0 Table of contents Table of contents... 2 1 Objectives of the change management programme... 3 1.1 Scope of this document... 3 1.2 Version... 3 2 Certification... 4 2.1 Certification frequency... More information Rail Network Configuration Management
Division / Business Unit: Function: Document Type: Enterprise Services Engineering Procedure Rail Network Configuration Management Applicability ARTC Network Wide SMS Publication Requirement Internal / More information CCD MARINE LTD QUALITY MANUAL PROCEDURE Q0.000. Date: Title. Revision: QUALITY MANUAL PROCEDURE Q0.000. 29 September 2014
Title: Quality Manual Uncontrolled if Hardcopy CCD MARINE LTD th Date: 29 September 2014 Doc Ref: Q0.000 Issued By: Sarah Leighton Rev No: 2 Title Revision: Date: QUALITY MANUAL PROCEDURE Q0.000 2 29 September More information Working Party on Control of Medicines and Inspections. Final Version of Annex 15 to the EU Guide to Good Manufacturing Practice
EUROPEAN COMMISSION ENTERPRISE DIRECTORATE-GENERAL Single market, regulatory environment, industries under vertical legislation Pharmaceuticals and cosmetics Brussels, July 2001 Working Party on Control More information IGEM/UP/16 Communication 1756
Communication 1756 Design for Natural Gas installations on industrial and commercial premises with respect to hazardous area classification and preparation of risk assessments Founded 1863 Royal Charter More information CORPORATE QUALITY MANUAL
Corporate Quality Manual Preface The following Corporate Quality Manual is written within the framework of ISO 9001:2008 Quality System by the employees of CyberOptics. CyberOptics recognizes the importance More information People and Business Division comprises four directorates: Investment Services, Information Services, Customer Experience and People and Performance.
Role Statement TITLE OF POSITION: CLASSIFICATION LEVEL: Regulatory Compliance Officer OPS4 Organisation Overview The Department of Planning, Transport and Infrastructure (DPTI) serves the South Australian More information Guide Document for Development of WHS Management Plans
DISCLAIMER: THIS DOCUMENT IS PROVIDED AS GUIDANCE TO ASSIST CONTRACTORS IN MEETING THEIR OBLIGATIONS UNDER THE WHS LAW AND NTG CONTRACTS. NTG DOES NOT ACCEPT ANY RESPONSIBILITY FOR THE CONTENTS OF CONTRACTORS More information 2017 © DocPlayer.net Privacy Policy | Terms of Service | Feedback