Source: http://federal.elaws.us/fr/notice/2018-11542
Timestamp: 2019-08-21 13:32:18
Document Index: 215985832

Matched Legal Cases: ['art 430', 'art 430', 'art 430', 'art 430', 'art 429', 'art 430', 'art 429']

2018-11542. Notice of Petition for Waiver of National Comfort Products, Inc. (NCP) From the Department of Energy Central Air Conditioners and Heat Pumps Test Procedure, and Notice of Grant of Interim Waiver, Federal Register
Home » 2018 Issues » 83 FR (05/30/2018) » 2018-11542. Notice of Petition for Waiver of National Comfort Products, Inc. (NCP) From the Department of Energy Central Air Conditioners and Heat Pumps Test Procedure, and Notice of Grant of Interim Waiver
2018-11542. Notice of Petition for Waiver of National Comfort Products, Inc. (NCP) From the Department of Energy Central Air Conditioners and Heat Pumps Test Procedure, and Notice of Grant of Interim Waiver
Notice of petition for waiver, grant of an interim waiver, and request for comments.
This notice announces receipt of and publishes a petition for waiver from NCP seeking an exemption from the U.S. Department of Energy (DOE) test procedure for determining the efficiency of central air conditioners and heat pumps. NCP seeks to use an alternate test procedure to address issues involved in testing certain basic models identified in its petition. According to NCP, the basic models of space constrained central air conditioner and heat pump units listed in its petition are designed and intended to be sold exclusively with NCP's NCPAH-A series or other blower-coil indoor units with electronically commutated (“ECM”) motors. These efficient blower-coil indoor units operate at much lower wattage than the default required by the DOE test procedure. As such, the current DOE test procedure does not result in representative ratings for these basic models. NCP seeks to use an alternate test procedure to test and rate their basic models paired only with air handler indoor units (i.e., blower coil indoor units). This notice also announces that DOE grants NCP an interim waiver from the DOE central air conditioners and heat pumps test procedure for its specified basic models, subject to use of the alternative test procedure as set forth in the Order. DOE solicits comments, data, and information concerning NCP's petition and its suggested alternate test procedure.
DOE will accept comments, data, and information with respect to the NCP Petition until June 29, 2018.
Start Printed Page 24755
You may submit comments, identified by case number “2017-008” and Docket number “EERE-2017-BT-WAV-0030,” by any of the following methods:
Email: NCP2017WAV0030@EE.DOE.Gov. Include the case number [Case No. 2017-008] in the subject line of the message. Submit electronic comments in WordPerfect, Microsoft Word, PDF, or ASCII file format, and avoid the use of special characters or any form of encryption.
Postal Mail: Ms. Lucy deButts, U.S. Department of Energy, Building Technologies Office, Mailstop EE-5B, Petition for Waiver Case No. 2017-008, 1000 Independence Avenue SW, Washington, DC 20585-0121. Telephone: (202) 287-1604. If possible, please submit all items on a compact disc (CD), in which case it is not necessary to include printed copies.
Hand Delivery/Courier: Appliance and Equipment Standards Program, U.S. Department of Energy, Building Technologies Office, 950 L'Enfant Plaza SW, 6th Floor, Washington, DC 20024. Telephone: (202) 287-1445. If possible, please submit all items on a CD, in which case it is not necessary to include printed copies.
The docket web page can be found https://www.regulations.gov/​docket?​D=​EERE-2017-BT-WAV-0030. The docket web page will contain simple instruction on how to access all documents, including public comments, in the docket.
Ms. Lucy deButts, U.S. Department of Energy, Building Technologies Program, Mail Stop EE-2J, Forrestal Building, 1000 Independence Avenue SW, Washington, DC 20585-0121. Telephone: (202) 287-1604. Email: AS_Waiver_Requests@ee.doe.gov.
Title III, Part B [1] of the Energy Policy and Conservation Act of 1975 (EPCA), Public Law 94-163 (42 U.S.C. 6291-6309, as codified) established the Energy Conservation Program for Consumer Products Other Than Automobiles, which includes central air conditioners and heat pumps.[2] Part B includes definitions, test procedures, labeling provisions, energy conservation standards, and the authority to require information and reports from manufacturers. Further, Part B requires the Secretary of Energy to prescribe test procedures that are reasonably designed to produce results that measure energy efficiency, energy use, or estimated operating costs during a representative average-use cycle, and that are not unduly burdensome to conduct. (42 U.S.C. 6293(b)(3)) The test procedure for central air conditioners and heat pumps is contained in 10 CFR part 430, subpart B, appendix M (referred to in this notice as “appendix M”).
DOE's regulations set forth at 10 CFR 430.27 contain provisions that allow a person to seek a waiver from the test procedure requirements for a particular basic model of a covered product when the petitioner's basic model for which the petition for waiver was submitted contains one or more design characteristics that either (1) prevent testing according to the prescribed test procedure, or (2) cause the prescribed test procedures to evaluate the basic model in a manner so unrepresentative of its true energy consumption characteristics as to provide materially inaccurate comparative data. 10 CFR 430.27(a)(1). A petitioner must include in its petition any alternate test procedures known to the petitioner to evaluate the basic model in a manner representative of its energy consumption. 10 CFR 430.27(b)(1)(iii).
II. NCP's Petition for Waiver of Test Procedure and Application for Interim Waiver
On March 20, 2017, NCP filed a petition for waiver and an application for interim waiver from the CAC and HP test procedure set forth in 10 CFR part 430, subpart B, appendix M. According to NCP, basic models of space constrained central air conditioner and heat pump outdoor units listed in its petition [3] are designed and intended to be sold with NCP's NCPAH-A series or other blower-coil indoor units with electronically commutated (“ECM”) motors. These efficient blower-coil indoor units operate at much lower wattage than the default required by the DOE test procedure. As such, the current DOE test procedure does not result in a representative rating for these basic models. NCP seeks to use an alternate test procedure to test and rate using their space constrained central air conditioner and heat pump basic models paired only with blower-coil indoor units.
NCP also requests an interim waiver from the existing DOE test procedure. An interim waiver may be granted if it appears likely that the petition for waiver will be granted, and/or if DOE determines that it would be desirable for public policy reasons to grant immediate relief pending a determination of the petition for waiver. See 10 CFR 430.27(e)(2).Start Printed Page 24756
III. Requested Alternate Test Procedure
EPCA requires that manufacturers use DOE test procedures to make representations about the energy consumption and energy consumption costs of products covered by the statute. (42 U.S.C. 6293(c)) Consistent representations are important for manufacturers to use in making representations about the energy efficiency of their products and to demonstrate compliance with applicable DOE energy conservation standards. Pursuant to its regulations applicable to waivers and interim waivers from applicable test procedures at 10 CFR 430.27, and after consideration of public comments on the petition, DOE will consider setting an alternate test procedure for the equipment identified by NCP in a subsequent Decision and Order.
As an alternate test procedure, NCP proposes that the basic models listed in the petition be tested according to the test procedure for central air conditioners and heat pumps prescribed by DOE at 10 CFR part 430, subpart B, appendix M, as applicable, except for the requirement under 10 CFR 429.16 that represented values for each model of outdoor unit be determined based on testing with a model of a coil-only indoor unit that is the least efficient indoor unit distributed in commerce with that particular outdoor unit. Instead, NCP requests that the specified basic models be tested and representations be determined by pairing the models only with blower-coil indoor units.
IV. Summary of Grant of an Interim Waiver
On May 30, 2017, NCP submitted supplemental materials to their original petition consisting of public-facing materials (e.g., marketing materials, product specification sheets, and installation manuals) that include language consistent with their assertion that the basic models listed in its petition are distributed to be installed exclusively with blower-coil indoor units that incorporate high-efficiency fan motors.
In addition to the material submitted by NCP, DOE conducted a review of NCP's other public-facing materials including websites, marketing materials, product spec sheets, labels, installation manuals, other consumer facing disclosures, etc. to confirm that these materials support NCP's assertions set forth in the petition about how they distribute the specified basic models in commerce. The public-facing materials that DOE found state that these basic models are compatible with NCP air handlers or certain other air handlers with ECM motors (combinations that are rated in the DOE Compliance Certification Management System (CCMS) database) and that any combinations not rated in the DOE CCMS database will require factory testing and listing with DOE. DOE's review also indicates that NCP does not market the basic models for sale with indoor units that do not have electronically commutated fan motors. All materials reviewed by DOE can be found in the docket. DOE understands from NCP's petition that, absent an interim waiver, NCP's specified models cannot be tested and rated for energy consumption on a basis representative of their true energy consumption characteristics. DOE has reviewed the alternate test procedure suggested by NCP and concludes that it will allow for the accurate measurement of the efficiency of these specified models, while alleviating the testing problems associated with NCP's implementation of CAC and HP testing. DOE has determined that NCP's petition for waiver will likely be granted and that it is desirable for public policy reasons to grant NCP immediate relief pending a determination on the petition for waiver.
For the reasons stated above, DOE has granted NCP's application for interim waiver for its specified basic models of space constrained central air conditioners and heat pumps. The substance of DOE's Interim Waiver Order is summarized below.
Therefore, DOE has issued an Order, stating:
(1) NCP must test and rate the CAC and HP basic models listed in paragraph (A) with the alternate test procedure set forth in paragraph (2).
(A) NCPE-418-1010, NCPE-418-3010, NCPE-418-4010, NCPE-418-5010, NCPE-424-1010, NCPE-424-3010, NCPE-424-4010, NCPE-424-5010, NCPE-430-1010, NCPE-430-3010, NCPE-430-4010, NCPE-430-5010.
(2) The applicable method of test for the NCP basic models listed in subparagraph (1)(A) is the test procedure for CAC and HP prescribed by DOE at 10 CFR part 430, subpart B, appendix M, except the determination of represented value requirements and units required for test per 10 CFR 429.16(a)(1), (b)(2) and (b)(2)(i) shall be as detailed below. All other requirements of 10 CFR part 429.16 remain applicable.
In 429.16(a), Determination of Represented Value:
(1) Required represented values for single-split system space-constrained AC with single-stage or two-stage compressor. Determine the represented values (including SEER, EER, HSPF, SEER2, EER2, HSPF2, PW,OFF, cooling capacity, and heating capacity, as applicable) for the individual models/combinations (or “tested combinations”) specified in the following table.
Required represented values
Outdoor Unit and Indoor Unit (Distributed in Commerce by OUM) Single-Split System Space-Constrained AC with Single-Stage or Two-Stage Compressor Every individual combination distributed in commerce, including all coil-only and blower coil combinations. For each model of outdoor unit, this must include the least efficient combination distributed in commerce with the particular model of outdoor unit.
In 429.16(b), Units tested:
(2) Individual model/combination selection for testing of single-split system space-constrained AC with single-stage or two-stage compressor. (i) The table identifies the minimum testing requirements for each basic model that includes multiple individual models/combinations; if a basic model spans multiple categories or subcategories listed in the table, multiple testing requirements apply. For each basic model that includes only one individual model/combination, test that individual model/combination.Start Printed Page 24757
Outdoor Unit and Indoor Unit (Distributed in Commerce by an OUM) Single-Split System Space-Constrained AC with a Single-Stage or Two-Stage Compressor The model of outdoor unit A model of indoor unit.
(3) Representations. NCP is permitted to make representations about the efficiency of basic models that meet the requirements of paragraph (1) for compliance, marketing, or other purposes only to the extent that the basic model has been tested in accordance with the provisions set forth above and such representations fairly disclose the results of such testing in accordance with 10 CFR 429.16 and 10 CFR part 430, subpart B, appendix M.
(4) This interim waiver shall remain in effect consistent with the provisions of 10 CFR 430.27(h) and (k).
(5) This interim waiver is issued to NCP on the condition that: (1) The statements, representations, test data, and documentary materials provided by the petitioner are valid, (2) NCP continues to distribute the specified basic models for exclusive installation with air-handler units that include electronically commutated motors, (3) All public-facing materials, including websites, marketing materials, product spec sheets, labels, nameplates, etc., make no representations that these basic models be installed in any other way; and (4) All public-facing materials state “Please consult the DOE CCMS data base [link to DOE CCMS database] for a list of rated combinations of indoor and outdoor units. Combinations of outdoor and indoor units that are not rated will require factory testing and listing with DOE. Please consult the factory.” DOE may revoke or modify this waiver at any time if it determines the factual basis underlying the petition for waiver is incorrect, the above listed conditions are not met, or the results from the alternate test procedure are unrepresentative of the basic model's true energy consumption characteristics.
(6) Granting of this interim waiver does not release NCP from the certification requirements set forth at 10 CFR part 429, other than those explicitly stated in paragraph (2).
DOE makes decisions on waivers and interim waivers for only those models specifically set out in the petition, not future models that may be manufactured by the petitioner. NCP may submit a new or amended petition for waiver and request for grant of interim waiver, as appropriate, for additional models of central air conditioners and heat pumps. Alternatively, if appropriate, NCP may request that this interim waiver (or subsequent waiver, if applicable) be extended to additional basic models employing the same technology as basic models specifically set out in this petition (see 10 CFR 430.27(g)).
Through this notice, DOE announces receipt of NCP's petition for waiver from the DOE test procedure for certain basic models and announces DOE's decision to grant NCP an interim waiver from the test procedure for the basic models listed in NCP's petition. DOE is publishing NCP's petition for waiver in its entirety, pursuant to 10 CFR 430.27(b)(1)(iv). The petition contains no confidential information. The petition includes a suggested alternate test procedure, as specified in section III of this notice, to determine the energy consumption of NCP's specified space constrained central air conditioner and heat pump basic models. DOE may consider including the alternate procedure specified in the Order in a subsequent Decision and Order.
DOE invites all interested parties to submit in writing by June 29, 2018, comments and information on all aspects of the petition, including the suggested alternate test procedure and calculation and rating methodology. DOE also seeks comment and data on NCP's assertion that it exclusively distributes the space constrained air conditioner and heat pump basic models as blower-coil installations. Pursuant to 10 CFR 430.27(d), any person submitting written comments to DOE must also send a copy of such comments to the petitioner. The contact information for the petitioner is Jean-Cyril Walker, Keller and Heckman LLP, 1001 G Street NW, Suite 500 West, Washington, DC 20001.
Include contact information each time you submit comments, data, documents, Start Printed Page 24758and other information to DOE. If you submit via mail or hand delivery, please provide all items on a CD, if feasible. It is not necessary to submit printed copies. No facsimiles (faxes) will be accepted.
Signed in Washington, DC, on May 17, 2018.
End Signature Start Printed Page 24759
Start Printed Page 24760
Start Printed Page 24761
Start Printed Page 24762
3. The specific basic models for which the petition applies are central air conditioner basic models NCPE-418-1010, NCPE-418-3010, NCPE-418-4010, NCPE-418-5010, NCPE-424-1010, NCPE-424-3010, NCPE-424-4010, NCPE-424-5010, NCPE-430-1010, NCPE-430-3010, NCPE-430-4010, NCPE-430-5010. These basic model names were provided by NCP in its March 2017 petition.
[FR Doc. 2018-11542 Filed 5-29-18; 8:45 am]
24754-24762 (9 pages)
Case No. 2017-008
2018-11542.pdf
» National Comfort Products Thru-the-Wall Condensing Units NCPE Series NCPE 1000, NCPE 3000, NCPE 4000
» National Comfort Products Thru-the-Wall Condensing Units NCPE Series, NCPE 5000
» National Comfort Products Thru-the-Wall Heat Pumps NHPA Series, NHPA 3000
» National Comfort Products Split System Condensing Units Installation Guide
» National Comfort Products Deluxe New Yorker Condensing Units Series D, NCPE 1000/D, NCPE 3000/D, NCPE 4000/D
» 2017-03-20 National Comfort Products, Inc. Petition for Waiver from Residential Central Air Conditioners and Heat Pump Test Procedures