Source: https://www.law.cornell.edu/cfr/text/40/appendix-Table_13_to_subpart_G_of_part_63
Timestamp: 2017-09-25 03:03:56
Document Index: 243826186

Matched Legal Cases: ['art 63', 'art 63', 'art_63', 'art 63', 'art 63', '§ 63', '§ 63']

40 CFR Appendix Table 13 to Subpart G of Part 63, Wastewater - Monitoring Requirements for Control Devices | US Law | LII / Legal Information Institute
CFR › Title 40 › Chapter I › Subchapter C › Part 63 › Subpart G › Appendix Table_13_to_subpart_G_of_part_63
40 CFR Appendix Table 13 to Subpart G of Part 63, Wastewater - Monitoring Requirements for Control Devices
Table 13 to Subpart G of Part 63 - Wastewater - Monitoring Requirements for Control Devices
Monitoring equipment required
All control devices 1. Flow indicator installed at all bypass lines to the atmosphere and equipped with continuous recorder b or 1. Presence of flow diverted from the control device to the atmosphere or Hourly records of whether the flow indicator was operating and whether a diversion was detected at any time during each hour
2. Valves sealed closed with car-seal or lock-and-key configuration 2. Monthly inspections of sealed valves Monthly.
Thermal Incinerator Temperature monitoring device installed in firebox or in ductwork immediately downstream of firebox a and equipped with a continuous recorder b Firebox temperature Continuous.
Catalytic Incinerator Temperature monitoring device installed in gas stream immediately before and after catalyst bed and equipped with a continuous recorder b 1. Temperature upstream of catalyst bed or
2. Temperature difference across catalyst bed Continuous.
Flare Heat sensing device installed at the pilot light and equipped with a continuous recorder a Presence of a flame at the pilot light Hourly records of whether the monitor was continuously operating and whether the pilot flame was continuously present during each hour.
Boiler or process heater <44 megawatts and vent stream is not mixed with the primary fuel Temperature monitoring device installed in firebox a and equipped with continuous recorder b Combustion temperature Continuous.
Condenser Temperature monitoring device installed at condenser exit and equipped with continuous recorder b Condenser exit (product side) temperature Continuous.
Carbon adsorber (regenerative) Integrating regeneration stream flow monitoring device having an accuracy of ±10 percent, and Total regeneration stream mass or volumetric flow during carbon bed regeneration cycle(s) For each regeneration cycle, record the total regeneration stream mass or volumetric flow.
Carbon bed temperature monitoring device Temperature of carbon bed after regeneration [and within 15 minutes of completing any cooling cycle(s)] For each regeneration cycle and within 15 minutes of completing any cooling cycle, record the carbon bed temperature.
Carbon adsorber (Non-regenerative) Organic compound concentration monitoring device. c Organic compound concentration of adsorber exhaust Daily or at intervals no greater than 20 percent of the design carbon replacement interval, whichever is greater.
Alternative monitoring parameters Other parameters may be monitored upon approval from the Administrator in accordance with the requirements in § 63.143(e)(3)
b “Continuous recorder” is defined in § 63.111 of this subpart.
c As an alternative to conducting this monitoring, an owner or operator may replace the carbon in the carbon adsorption system with fresh carbon at a regular predetermined time interval that is less than the carbon replacement interval that is determined by the maximum design flow rate and organic concentration in the gas stream vented to the carbon adsorption system.