Source: https://www.federalregister.gov/documents/2001/07/23/01-18326/duke-energy-corporation-oconee-nuclear-station-units-1-2-and-3-exemption
Timestamp: 2017-09-22 07:00:27
Document Index: 601899322

Matched Legal Cases: ['art 50', 'art 50', 'art 50', 'art 50', 'art 50', 'art 50']

Federal Register :: Duke Energy Corporation; Oconee Nuclear Station, Units 1, 2, and 3; Exemption
Duke Energy Corporation; Oconee Nuclear Station, Units 1, 2, and 3; Exemption
66 FR 38327
https://www.federalregister.gov/d/01-18326 https://www.federalregister.gov/d/01-18326
The Duke Energy Corporation (the licensee) is the holder of Facility Operating License Nos. DPR-38, DPR-47, and DPR-55, which authorize operation of the Oconee Nuclear Station, Units 1, 2, and 3 (ONS). The licenses provide, among other things, that the facilities are subject to all rules, regulations, and orders of the U.S. Nuclear Regulatory Commission (NRC, the Commission) now or hereafter in effect.
By letter dated July 26, 2000, Duke Energy Corporation, licensee for the ONS, requested an exemption from certain requirements of 10 CFR 50.44, 10 CFR part 50, Appendix A, General Design Criterion 41, and 10 CFR part 50, Appendix E, Section VI pertaining to the hydrogen control system requirements (i.e., recombiners and containment post-accident hydrogen monitors) and the removal of these requirements from the ONS design basis.
Regulatory requirements for the hydrogen control system are specified in 10 CFR 50.44 and 10 CFR part 50, Appendix A, (General Design Criteria 41, 42, and 43). Additional staff guidance is provided in Regulatory Guide (RG) 1.7. Staff review and acceptance criteria are specified in Section 6.2.5 of the Standard Review Plan. With regard to combustible gas control system requirements, ONS is subject to the requirements of 10 CFR 50.44(g).
For this exemption, these special circumstances include consideration that the quantity of hydrogen prescribed by 10 CFR 50.44(d) and RG 1.7 which necessitated the need for hydrogen recombiners would be bounded by the hydrogen generated during a severe accident. As shown in the attached safety evaluation, the staff has found that the relative importance of hydrogen combustion for large, dry containments with respect to containment failure is quite low. This finding supports the argument that the hydrogen recombiners are not risk significant from a containment integrity perspective and that the risk associated with hydrogen combustion is not from design basis accidents but from severe accidents. Studies have shown that the majority of risk to the public is from accident sequences that lead to containment failure or bypass, and that the contribution to risk from accident sequences involving hydrogen combustion is actually quite small for large, dry containments such as Oconee's. This is true despite the fact that the hydrogen produced in these events is substantially larger than the hydrogen production postulated by 10 CFR 50.44(d) and RG 1.7. Hydrogen combustion sequences that could lead to early containment failure typically involve up to 75 percent core metal-water reaction. Hydrogen combustion sequences that could lead to late containment failure involve additional sources of hydrogen due to the interaction of corium and the concrete basemat after vessel breach. Although the recombiners are effective in maintaining the RG 1.7 hydrogen concentration below the lower flammability limit of 4 volume percent, they are overwhelmed by the larger quantities of hydrogen associated with severe accidents that would typically be released over a much shorter time period (e.g., 2 hours). However, NUREG/CR-4551 states that hydrogen combustion in the period before containment failure is considered to present no threat to large, dry containments. Table A.4-5 of NUREG/CR-4551 shows that the contribution of hydrogen combustion to late containment failure is also very small. Therefore, the relative importance of hydrogen combustion for large, dry containments with respect to containment failure has been shown to be quite low.
The recombiners can, however, prevent a subsequent hydrogen burn if needed due to radiolytic decomposition of water and corrosion in the long term. Analysis performed in accordance with the methodology of RG 1.7 shows that the hydrogen concentration will not reach 4 volume percent for 15 days after initiation of a design basis Loss of Coolant Accident (LOCA). Additionally, as described in the attached safety evaluation, hydrogen concentrations on the order of 6 percent or less are bounded by hydrogen generated during a severe accident and would not be a threat to containment integrity since there is ample time between burns to reduce elevated containment temperatures using the installed containment heat removal systems. The ONS Individual Plant Examination (IPE) concluded that containment survival is almost certain following hydrogen combustion when the Reactor Building Cooling Units and the Reactor Building Spray System are operating.
The underlying purpose of 10 CFR 50.44 is to show that, following a LOCA, an uncontrolled hydrogen-oxygen recombination would not take place, or that the plant could withstand the consequences of uncontrolled hydrogen-oxygen recombination without loss of safety function. Based on the analysis, which includes the staff's evaluation of the risk from hydrogen combustion, resolution of Generic Issue 121, “Hydrogen Control for PWR Dry Containments,” and the ONS IPE, the plant could withstand the consequences of uncontrolled hydrogen-oxygen recombination without loss of safety function without credit for the hydrogen recombiners for not only the design basis case, but the more limiting severe accident with up to 100 percent metal-water reaction. Therefore, the requirements for hydrogen recombiners as part of the ONS design basis are unnecessary and their removal from the design basis is justified. Additionally, elimination of the hydrogen recombiners from the Emergency Operating Instructions would simplify operator actions in the event of an accident and, therefore, would be a safety benefit. Consequently, pursuant to 10 CFR 50.12(a)(2)(ii), application of the regulation is not necessary to achieve the underlying purpose of the rule.
In the submittal, the licensee also requested an exemption from the functional requirement for hydrogen monitoring as promulgated in part 50, Appendix E, Section VI, “Emergency Response Data System (ERDS),” or any commitments made in regard to NUREG-0737, Item II.F.1, Attachment 6, “Containment Hydrogen Monitor.” In the Statement of Considerations for Appendix E to part 50, the Commission stated that the ERDS data (which includes the continuous hydrogen monitors) provides the data required by the NRC to perform its role during an emergency. This conclusion is still valid Start Printed Page 38328for not only the staff but licensees. The major vendors' core damage assessment methodologies continue to include continuous hydrogen monitoring. Core damage assessment methodologies were reviewed by the staff in response to NUREG-0737, Item II.B.3(2)(a). Continuous hydrogen monitoring is needed to support a plant's emergency plan as described in 50.47(b)(9). Implementing documents such as Regulatory Guide (RG) 1.101, Revision 2, which endorsed NUREG-0654, and RG 1.101, Revision 3, which endorsed NEI-NESP-007, Revision 2 define the highest Emergency Action Level, a General Emergency, as a loss of any two barriers and potential loss of the third barrier. Potential loss of a third barrier depends on whether or not an explosive mixture exists inside containment. The continuous hydrogen monitors are used for determining whether an explosive mixture exists inside containment. Therefore, the licensee's request for exemption from the functional requirements for hydrogen monitoring is not approved.
Accordingly, the Commission has determined that, pursuant to 10 CFR 50.12(a), the exemption pertaining to the recombiners is authorized by law, will not endanger life or property or common defense and security, and is, otherwise, in the public interest. Also, pursuant to 10 CFR 50.12(a)(2)(ii), special circumstances are present. Therefore, the Commission hereby grants Duke Energy Corporation an exemption from the recombiner requirements of 10 CFR 50.44 and 10 CFR part 50, appendix A, General Design Criterion 41 for the Oconee Nuclear Station, Units 1, 2, and 3.
Pursuant to 10 CFR 51.32, the Commission has determined that the granting of this exemption will not have a significant effect on the quality of the human environment (66 FR 37073).
[FR Doc. 01-18326 Filed 7-20-01; 8:45 am]