Patent Publication Number: US-6671654-B1

Title: Apparatus and method for measuring and reporting the reliability of a power distribution system

Description:
RELATED APPLICATIONS 
     The following co-pending and commonly assigned U.S. Patent Application has been filed on the same date as the present application. This application relates to and further describes other aspects of the embodiments disclosed in the present application and is herein incorporated by reference. 
     U.S. patent application Ser. No. 09/723,564, “INTRA-DEVICE COMMUNICATIONS ARCHITECTURE FOR MANAGING ELECTRICAL POWER DISTRIBUTION AND CONSUMPTION”, (Attorney Ref. No. 6270/48), filed concurrently herewith. 
    
    
     BACKGROUND 
     In a typical electrical distribution system, electrical energy is generated by an electrical supplier or utility company and distributed to consumers via a power distribution network. The power distribution network is the network of electrical distribution wires which link the electrical supplier to its consumers. Typically, electricity from a utility is fed from a primary substation over a distribution cable to several local substations. At the substations, the supply is transformed by distribution transformers from a relatively high voltage on the distributor cable to a lower voltage at which it is supplied to the end consumer. From the substations, the power is provided to industrial users over a distributed power network that supplies power to various loads. Such loads may include, for example, various power machines or computer/electronic equipment. 
     At the consumer&#39;s facility, there will typically be an intelligent electronic device (“IED”), such as an electrical energy/watt-hour meter, connected between the consumer and the power distribution network so as to measure quantities such as the consumer&#39;s electrical consumption or electrical demand. Such a meter may be owned by the consumer and used to monitor and control consumption and report costs or may be owned by the utility and used to monitor consumption and report revenue. 
     IED&#39;s include devices such as Programmable Logic Controllers (“PLC&#39;s”), Remote Terminal Unit (“RTU”), meters, protective relays and fault recorders. Such devices are widely available that make use of memory and microprocessors and have limited remote reporting capabilities. A PLC is a solid-state control system that has a user-programmable memory for storage of instructions to implement specific functions such as Input/output (I/O) control, logic, timing, counting, report generation, communication, arithmetic, and data file manipulation. A PLC consists of a central processor, input\output interface, and memory. A PLC is typically designed as an industrial control system. An exemplary PLC is the SLC 500 Series, manufactured by Allen-Bradley in Milwaukee, Wis. 
     A meter, is a device that records and measures electrical power consumption. Energy meters include, but are not limited to, electric watt-hour meters. In addition, meters are also capable of measuring and recording power events, power quality, current, voltages waveforms, harmonics, transients or other power disturbances. Revenue accurate meters (“revenue meter”) are revenue accuracy electrical power metering devices which may include the ability to detect, monitor, or report, quantify and communicate power quality information about the power which they are metering. An exemplary revenue meter is model 8500, manufactured by Power Measurement Ltd, in Saanichton, B.C. Canada. 
     A protective relay is an electrical device that is designed to interpret input conditions in a prescribed manner, and after specified conditions are met, to cause contact operation or similar abrupt change in associated electric circuits. A relay may consist of several relay units, each responsive to a specified input, with the combination of units providing the desired overall performance characteristics of the relay. Inputs are usually electric but may be mechanical, thermal or other quantity, or a combination thereof. An exemplary relay is type N and KC, manufactured by ABB in Raleigh, North Carolina. 
     A fault recorder is a device that records the waveform resulting from a fault in a line, such as a fault caused by a break in the line. An exemplary fault recorder is IDM, manufactured by Hathaway Corp in Littleton, Colo. 
     IED&#39;s can also be created from existing electromechanical meters or solid-state devices by the addition of a monitoring and control device which converts the mechanical rotation of the rotary counter into electrical pulses. An exemplary electromechanical meter is the AB1 Meter manufactured by ABB in Raleigh, N.C. Such conversion devices are known in the art. 
     In the early 1980&#39;s, the Computer Business Manufacturers Association (CBEMA), which is now the Information Technology Industry Council (ITIC), established a susceptibility profile curve to aid manufacturers in the design of power supply protection circuits. This power quality curve has since become a standard reference within the industry measuring all types of equipment and power systems and defines allowable disturbances that can exist on the power lines. Additionally, the semiconductor industry has established its own standard SEMI F47 curve for power quality, which is similar to the CBEMA curve but instead is focused on semiconductor power quality and associated supporting equipment. 
     In more recent years the electric utility marketplace has moved towards deregulation where utility consumers will be able to choose electrical service providers. Until now, substantially all end users purchased electric power they needed from the local utility serving their geographic area. Further, there was no way for utilities to guarantee the same reliability to all consumers from the utility because of different connection points to the transmission and distribution lines. With deregulation it is essential for consumers to be able to measure and quantify power reliability from their suppliers in order to ensure they are receiving the service they have opted for. Such service may involve various pricing plans, for example on volume, term commitments, peak and off-peak usage or reliability. 
     Power reliability is typically measured by several various indices. These indices include System Average Interruption Frequency Index (“SAIFI”), Customer Average Interruption Duration Index (“CAIDI”), System Average Interruption Duration Index (“SAIDI”), Average System Availability Index (“ASAI”) and Momentary Average Interruption Duration Index (“MAIFI”). Each index provides a measure, in terms of ratios or percentages, of interruptions in delivery of electrical power, wherein an interruption may be classified as a complete loss of electrical power or where the quality of the delivered electrical power falls below or exceeds a pre-determined threshold. SAIFI measures the ratio of the total number of customer interruptions to the total number of customers served, hence the average. Lower averages signify better reliability. CAIDI measures the total customer hours interrupted to the total customer interruptions, in minutes. The lower the measure, the better the reliability. SAIDI measures the ratio of customer hours interrupted to total customers served, in minutes. Again, the smaller the number the better the system. ASAI is a ratio of total number of customer hours the electric service has been turned on to the number of customer hours the service has been demanded. It is measured as a percentage and the higher the percentage, the better the reliability. The MAIFI measurement considers interruptions that last less than 5 minutes. System Average RMS Variation Frequency Index (“SARFI”) is another power quality index that provides counts or rates of voltage sags, swells and/or interruptions for the system. There are two types of SARFI indices—SARFI_x and SARFI_curve. SARFI_x corresponds to a count or rate of voltage sags, swells and/or interruptions below a threshold where SARFI_curve corresponds to a rate of voltage sags below an equipment compatibility curve, such as a CBEMA or SEMI curve. Mean Time Between Failure (“MTBF”) is another measurement to indicate reliability. MTBF is usually expressed in hours and is calculated by dividing the total number of failures into the total number of operating hours observed. For example a device may specify MTBF as 300,000 hours. If this device operates 24 hours a day, 365 days a year it would take an average of 34 years before the device will fail. 
     Today&#39;s networked economy has demanded a fundamental change in the standards by which acceptable electric power reliability is measured. In modern high technology industries, where a power interruption or deviance of even a few milliseconds can cause significant problems and lost resources, a power reliability measurement with an increased resolution is needed. Further, in today&#39;s deregulated market, a standard reliability specification based on this higher resolution reliability measurement is needed. One such specification which standardizes higher resolution reliability measurement, involves a method of measuring reliability by the use of “nines”, and is stated as a percentage of time the power is available and meeting a specified quality threshold. 
     A typical power distribution system, for example, provides “three nines” reliability, meaning the power is available 99.9% of the time. Fully reliable “high nines” power is becoming increasingly recognized as an essential element of business survival and the traditional reliability measurements on which the industry depends are no longer sufficient for today&#39;s technology as a measurement of downtime in minutes is no longer sufficient when only a few seconds, or even a few milliseconds, of downtime can result in large economic impact. CAIDI, SAIDI, ASAI and MAIFI do not allow a high enough resolution of time measurement for calculating reliability where events as short as 1 second may cause equipment downtime. Further, these traditional indices, are a function of aggregate loads and multiple locations, and do not provide the capability to measure reliability at single location. MTBF is usually related to a physical device, such as a generator, and not the power system attached to it and SARFI is measured in events, not in units of time. Many private corporations, such as SurePower Corporation, located in Danbury Conn., offer products such as the Sure Power System that guarantees high nines reliability. However, as technology becomes more integrated in our society a need for the consumer or utility to measure and monitor reliability coming from either the power distribution system, or a device such as the Sure Power System, is required. 
     Further, with the advent of electrical power deregulation, a standardized specification for power reliability is necessary to facilitate uniform comparison of suppliers. The above mentioned reliability measurements, because they necessarily measure different quantities, fail to provide such a uniform method of specifying reliability. 
     Therefore, in view of the above it is a primary object of the invention to provide an intelligent electronic device, more specifically an electricity measurement device, which provides more accurate reliability monitoring and more useful reliability reporting for consumers operating devices requiring high power reliability. 
     SUMMARY 
     The present invention is defined by the following claims, and nothing in this section should be taken as a limitation on those claims. By way of introduction, the preferred embodiments described below relate to an intelligent electronic device (“IED”). The IED includes a first interface operative to couple the IED with an electrical power distribution network and a measurement component coupled with the first interface and operative to measure one or more parameters of the electrical power distribution network. In addition, the IED includes a reliability processor coupled with the measurement component and operative to receive the one or more parameters and compute a reliability of the electrical power distribution network as a percentage. The IED further includes a reporting module coupled with the reliability processor and operative to receive the percentage and report the reliability as the number of continuous digits equal to the number 9 constituting the numeric percentage, starting from the most significant digit. 
     The preferred embodiments further relate to a method in an intelligent electronic device (“IED”) coupled with an electrical power distribution network for reporting the reliability of the electrical power distribution network. The method includes measuring one or more parameters of the electrical power distribution network; computing a reliability of the electrical power distribution network as a percentage; counting the continuous number of digits equal to the number 9, starting with the most significant digit, in the numeric percentage; and reporting the number of 9&#39;s. 
     Further aspects and advantages of the invention are discussed below in conjunction with the preferred embodiments. 
    
    
     BRIEF DESCRIPTION OF THE DRAWINGS 
     FIG. 1 illustrates a preferred embodiment of a physical layout using an IED of the present invention. 
     FIG. 2 a  illustrates a preferred embodiment of the device circuitry of an IED. 
     FIG. 2 b  illustrates a preferred embodiment for calculating reliability. 
     FIG. 2 c  illustrates a sliding time window for calculating reliability over a time period. 
     FIG. 3 a  illustrates an alternate preferred embodiment for calculating reliability. 
     FIG. 3 b  illustrates an alternate preferred embodiment for calculating reliability. 
     FIG. 3 c  illustrates a preferred embodiment of multiple IED&#39;s connected to multiple loads. 
     FIG. 4 illustrates an alternate embodiment for benchmarking the module against previously determined nines. 
    
    
     DETAILED DESCRIPTION OF THE PRESENTLY PREFERRED EMBODIMENTS 
     Many consumers and their associated power equipment require high reliability of power to ensure production, and minimize downtime of sensitive equipment that requires clean, stable and reliable power. Further, such consumers require a standardized specification for power reliability to effectively manage their consumption in a deregulated market. Reliability is closely related to the level of power quality required for the specific equipment to remain in operation during disturbances. This includes total power outages as well as sags, swells or other disturbances which deviate from pre-defined tolerances. Power reliability can be affected by several factors such as surges induced by devices started on the power grid or various weather-induced interruptions. One method of measuring reliability involves the use of “nines”. Power reliability is established as a percentage of total system downtime versus total uptime. The numerical percentage is then decomposed to its digits, wherein each “9” represents an order of magnitude reduction of the probability of failure. The increasing need for substantially improved power quality and reliability that measures in the “high-9&#39;s”, is being driven by the digital, info-centric economy. Such niche markets serve as a disruptive force to the traditional power industry, and may well become mainstream markets.          Reliability                 %     =           Total                 System                 Runtime     -     Total                 System                 Downtime         Total                 System                 Runtime       ×   100               Reliability                 %     =         Total                 System                 Available                 Time       Total                 System                 Runtime       ×   100                     
     Where the actual number of consecutive 9&#39;s starting with the most significant digit in the resultant numeric percentage measured are counted up and equals the “number of nines” measurement. The total system downtime, total system available time, total elapsed time and total system runtime are measured in terms of time. The unit of time, i.e. the resolution, varies depending on the number of nines, i.e. the level of reliability, being measured. For instance a small number of nines could employ a measurement of time in minutes where a high number of nines may require time to be measured in milliseconds. In an alternate embodiment the total system downtime, total system available time, total elapsed time and total system runtime are measured in cycles, or parts thereof, of AC voltage waveform. Total system runtime can be a running computation, that starts when the IED is first powered up, or when the power system is first turned on, or total system runtime may be operated on a sliding window basis over a day, week, month or other time period. Total system downtime can also include qualifications that allow a user to change what downtime may be considered at, such as a power outage of a certain time interval or a voltage spike of at least a certain RMS value. Examples of total system runtime and downtime are given in more detail below. In the preferred embodiment, system downtime and system runtime are measured with a resolution of milliseconds and are computed as a running value when the IED is first powered on. It is preferred that the computation and reliability measures be stored in a non-volatile memory within the IED so that subsequent operating power interruptions do not reset the measure. A reset function may be provided. It will be appreciated that downtime and runtime can be measured with a high resolution and that the resultant percentage can be rounded or truncated prior to computing the nines measure so as to provide a standardized result. 
     Some residential consumers may have 99% reliability, or “Two Nines” which translates into 3.65 days of outage per year, computed as total system downtime of 3.65 days divided by total system runtime of 365 days. For this residential user there typically is no need to measure reliability in terms of 9&#39;s. A typical residential consumer has three Nines, or 99.9% reliability, which translates to approximately 8.7 hours of outage per year, computed as total system downtime of 8.76 hours divided by total system runtime of 8760 hours. Other consumers, such as phone companies, hospitals or airports, require better than Three Nines and may employ stand-by generator systems if only Three Nines reliability is available. Four Nines translates into just under 1 hour of downtime per year, computed as total system downtime of 52.56 minutes divided by total system runtime of 526500 minutes, where Five Nines translates into minutes of down time, computed as total system downtime of 5.256 minutes divided by total system runtime of 526500 minutes, which may still be unacceptable to any company working 24 hours, 365 days of the year. The electricity infrastructure needed for the new digital information society used by the telecom and dot-com world starts at Six Nines, or 99.9999% up time which translates to a maximum of 31 seconds of outage per year, computed as total system downtime of 31.536 seconds divided by total system runtime of 31536000 seconds. Seven Nines, or several seconds of disruption per year, computed as total system downtime of 3.1536 seconds divided by total system runtime of 31566000 seconds, protects against minor disturbances on power lines that may cause network crashing events but the Eighth Nine, or 99.99999%, computed as total system downtime of 315.4 milliseconds divided by total system runtime of 31536000000 milliseconds, measures interruptions in the hundreds of milliseconds that may crash the most delicate of equipment. These examples assume a 1 year duration of measurement, although longer or shorter windows of time may be used as is discussed below. As can be seen, the number of 9&#39;s specified directly translates into a reliable and standardized measure of the expected failure rate of the power distribution system. 
     While it is advantageous to have the highest Nine&#39;s possible, increasing power distribution system reliability is expensive, with the supplier&#39;s costs and committed resources increasing exponentially for each additional Nine added. For example, for every Nine after the standard 99.9% reliability, costs can rise from 200 to 1000% to reach Six Nines. Some utilities offer a particular number of 9&#39;s plus an 8, such as 99.99976%, stating that they don&#39;t quite have enough reliability to offer, for example, Six Nines, but offer much better than Five Nines. 
     Electricity with high nines, allows devices, such as web hosting centers, collection centers, ISP&#39;s, corporate data centers and other major financial, commercial and industrial facilities to substantially increase uptime, thereby raising revenues and decreasing cost. For businesses relying on data centers or e-business sites, clean, stable and reliable power for critical devices is paramount to ensure that costly breakdowns which result in immediate lost revenue do not occur. 
     Typically, for lower Nines, the utility or consumer defines an outage according to a standard which considers the level of susceptibility of their devices to shut down from a disturbance. For example a utility may consider an outage or disturbance if the voltage falls below 90% of the required RMS Voltage. For higher Nines, where the outage is of a smaller magnitude or duration, the measured voltage may be compared with a CBEMA or SEMI F47 curve to determine what is considered an outage. Disturbances include, surges, sags, swells, flicker, spikes, transients, line noise or complete disruptions. Additionally, other factors such as phase imbalance or voltage harmonics may have an effect on the reliability of the delivered electrical power and the devices that are supplied by it. For example, a utility measures the incoming power and measures a first surge of power 1 cycle in duration and 130% in magnitude of the normal RMS Voltage, and a second surge of power 0.02 of a cycle in duration and 135% in magnitude of the normal RMS Voltage. The utility applies this data to the CBEMA curve and determines the first surge to be unreliable power as it falls outside the curve, but deems the second surge to be reliable as it falls inside the curve. 
     In order to determine the reliability of an electrical power distribution network, or portion thereof, devices must be deployed to measure the desired parameters. Further, those measurements must be collected and the measure of reliability computed. Electric power meters are already deployed at the optimal locations for measuring power reliability as they are typically coupled between the power distribution system and the load which is supplied by the system. Unfortunately, there are no electric meters currently available which offer high accuracy power reliability measurement coupled with standardized reporting on the device. Accordingly, there is a need for an electricity meter that provides power reliability computation and monitoring, and permits viewing as a number of nines or percentages. 
     Referring now to FIG. 1, there is schematically illustrated how an IED  102  is coupled with an electrical power distribution system/network  100 , which is further coupled with a load  101 . One of ordinary skill in the art will recognize that the disclosed embodiments can also be coupled with a portion of the electrical power distribution network/system  100  to determine reliability of that portion only. Herein, the phrase “coupled with” is defined to mean directly connected to or indirectly connected with through one or more intermediate components. Such intermediate components may include both hardware and software based components. In the preferred embodiments, the IED  102  is an electric watt-hour revenue meter which primarily measures the consumption of electrical power by the load  101  from the distribution system  100 . An exemplary revenue meter which can be used with the disclosed embodiment is the model 8500, manufactured by Power Measurement Ltd, in Saanichton, B.C. Canada. The reliability functionality described below is preferably implemented as an ION module created with the Pegasys development software, manufactured by Power Measurement Ltd, in Saanichton, B.C. Canada 
     In the preferred embodiment the IED  102  is further coupled with a network  110  for communicating with other IED&#39;s  102  as well as data collection servers (not shown). The network  110  can be a private or public intranet, an extranet or combinations thereof, including a virtual private network coupling multiple intranets or extranets together via the Internet. In addition to measuring power consumption, the IED  102  includes device circuitry  105  which monitors the reliability and/or quality of the electrical power delivered to the load  101  by the power distribution system  100 . The device circuitry  105  includes the internal hardware and software of the device, such as the CPU, memory, firmware and software applications, data measurement functions and other programmed features. 
     FIG. 2 a  illustrates the preferred embodiment where the device circuitry  205  includes Software Applications  213  which further includes a power reliability module  214   a  which computes and measures the reliability of the power, or number of nine&#39;s, and a reporting module  214   b  which compiles and reports the reliability data for the user. In a preferred embodiment, these modules  214   a    214   b  are implemented in software. In alternative embodiments, the modules  214   a    214   b  are implemented in hardware or a combination or hardware and software. 
     FIG. 2 b  illustrates the preferred embodiment&#39;s reliability calculation as implemented in the reliability module  214   a.  As described above, this functionality is implemented as an ION software module executing on the IED. An IED  102  monitors the power lines for a disturbance or power outage  250  for one time unit. In the preferred embodiment where high nines of reliability is measured, such as 7 or 8 nines, a time unit is one millisecond. However for lower resolution in calculating nines, such as 4 or 5 nines, a larger time unit, such as seconds, may be used. In an alternate embodiment the preferred unit of time is measured as the time taken for a ½ cycle of power. If no disturbance is detected  258  in that time unit one time unit is added to the Total Uptime  260  value. If a disturbance is detected it is compared against the threshold limit to determine if it should be considered as an outage  252  or within tolerable limits  253 . For example, a user may consider an outage if a disturbance exceeds a certain voltage, or exceeds a certain length in time. Examples of disturbances are outlined in more detail below and in FIGS. 3 a  and  3   b.  If the disturbance is deemed to fall within the specified threshold or tolerance limits the time measured is added to the Total Uptime  253  and the IED continues to monitor for disturbances  250 . If the disturbance is determined to fall outside the limits, the disturbance is timed  254  and the duration added to the Total Downtime  256 . Determining whether the disturbance falls within or outside of the threshold limit is discussed in more detail in FIGS. 3 a  and  3   b  below. To compute reliability the module requires an input value of Total Uptime  266 , Total Downtime  262  and desired timeframe  264 . The desired timeframe may include calculating the reliability over a sliding window of time, from beginning of time to current time, or beginning of the IED or power system power-up to current time, or as a function of historical data. The outputs of the module comprises the number of nines or, alternatively, the actual computed percentage of reliability. In the preferred embodiment reliability is calculated in the following way:          Reliability                 %     =           Total                 Uptime     -     Disturbance                 Time           Total                 Uptime     +     Offline                 Time         ×   100                     
     Offline Time is considered to be time where the IED  102  was not recording reliability. This occurs, for example, when an attached load is shut down for scheduled maintenance or the IED  102  is taken offline for re-configuration. 
     Referring to FIG. 2 c,  the reliability module  214   a  also includes a sliding window  275  of time over which the reliability is measured. For example, the IED  102  may be programmed to calculate reliability and issue a daily report to the user showing the reliability for the past 24 hours. A sliding window  275  of one day is placed on the timeline  270  and the reliability module  214   a  utilizes this window to measure the instantaneous reliability of the most recent 24 hour period. 
     FIG. 3 a  illustrates a preferred embodiment which determines if a disturbance falls within a specified tolerances for measuring reliability. In this preferred embodiment the IED  102  is an electric meter which senses the voltage and current in each phase of the connected electric circuit (not shown). The IED  102  circuitry includes a power reliability module  305  which monitors the waveforms of all of the voltage phases of the electric circuits for deviations beyond allowable limits. In one preferred embodiment, the allowable limits for high limit  311  is 110% and the low limit  312  is 90% of the full waveform  310   a.  When a disturbance or deviation is detected  310   b  the module  305  provides information about the entire disturbance, such as the time stamp, magnitude and duration. The module  305  is also capable of breaking up the disturbance into discrete components (sub-disturbances) for a more detailed analysis. More detailed information about modules can be found in U.S. Pat. No 5,650,936. Further, more detailed information regarding power quality measurement and reporting can be found in U.S. patent application Ser. No. 09/370,317, entitled “REVENUE METER WITH POWER QUALITY FEATURES”, filed Aug. 9, 1999. 
     The duration of the disturbance beyond the allowable limits is then translated by the module  320  into a measure of the reliability. In this preferred embodiment the module  305  is coupled with a reporting module  306  which allows the user to view the number of nines measured over a specific time period, such as this week, month, quarter or year. Furthermore, this cumulative time period can be reset by the user. In the preferred embodiment a sliding window is utilized when calculating the reliability over the cumulative time period as set to the desired length of time by the user. Furthermore, users may instruct the IED  102  to measure downtime in terms of equipment downtime, not the actual power outage downtime. For example, an outage may last 20 seconds, however in that 20 seconds, devices which require up to 2 minutes to restart may be affected, thus the IED  102  may count the 2 minutes as the downtime. In an alternate embodiment, the IED contains ride-through capabilities where the IED maintains power for a period of time after the power supply from the power distribution system is disconnected. The reliability module further contains a detection module which determines if the power has been disconnected because the power distribution system is unavailable, or the IED user has powered down the IED but the power distribution line still is operable. This module enables the system downtime to be property calculated by determining if the power outage is due to an actual distribution outage, or the power outage is due to a user taking the IED offline. For example, if a user powers down an IED for maintenance, that downtime should not be considered as downtime, but rather added to the uptime, as the distribution grid was not inoperable. When the IED is reconnected to the distribution grid if the module detects the downtime was due to the distribution grid then the downtime is added to the total downtime, whereas if the module detects the downtime was due to a user taking the IED offline and the distribution grid was not affected, then the downtime is still to be considered as system runtime. 
     FIG. 3 b  illustrates a second preferred embodiment for calculating nines using a CBEMA curve  312  or SEMI F47 curve (not shown) function in the module  305 . In the embodiment, the module  305  contains software and hardware implemented functions which perform the specific functions. As above the IED  102  circuitry includes a power reliability module  305  which monitors the waveforms of all of the voltage phases of the electric circuits for deviations beyond allowable limits as applied to the pre-selected curve  313 . When a disturbance or deviation is detected  314  the module  305  provides information about the entire disturbance, and converts this information into the measured number of nines. In the preferred embodiment a user may select a pre-defined curve, such as the curve  312 , or program an alternate curve into the module  305  corresponding to the specific load the IED  102  is connected to. For example, the device circuitry  205  described in FIG. 2 is set to measure disturbances within a certain time interval, such as 1 millisecond. In the preferred embodiment the preferred time interval is measured in milliseconds, although alternative time intervals are contemplated. The device circuitry  205  timestamps the current time to a log on every time interval. When a disturbance is detected by the IED  102 , the module  305  computes and plots the magnitude and duration of the voltage disturbance on the CBEMA curve  312  and then, through software algorithms, such as a Boolean pass/fail when plotted against the curve, determines if it falls outside or inside the curve, signifying either unreliable or reliable. If the disturbance is of some length, such as several minutes, such that it renders the device circuitry without power and prohibits it from functioning, the IED is preferably provided with hardware enabled software, such as a backup battery, that continues to monitor time and further instructs the device upon re-start-up to compare the actual monitored time to the last measured timestamp in the log. This allows the IED  102  the ability to compute reliability when the IED  102  is rendered inoperable due to an extended power failure. 
     Furthermore, in an alternate preferred embodiment, the power reliability module  305  logs into the reporting module  306  those disturbances  316  which do not fall outside of the allowable limits, but are in the near proximity to the pre-defined limits. 
     FIG. 3 c  illustrates a preferred embodiment having multiple IED&#39;s  350 ,  351 ,  352  connected to multiple loads  353 ,  353 ,  355 . IED&#39;s  350 ,  351 ,  352 , are connected to loads  353 ,  354 ,  355  on the power system  361 . Further, IED  356  is provided to monitor the power system  361 . In the preferred embodiment each IED  350 ,  351 ,  352 ,  356  contains a reporting and a power reliability module, as described above, and is connected via a network  362 . The power reliability module  305 , coupled with the reporting module  306 , analyzes power and reports to the user at what rates of recurrence unreliable power occurs. In an alternative embodiment, lED&#39;s  350 ,  351 ,  352  report their reliability measurements from each of their branch circuits of power system  361  to IED  356  which computes a cumulative reliability measure for the entire system  361 . The power reliability module and a description of the operation modes while connected to multiple lED&#39;s is discussed in more detail in U.S. patent application Ser. No. 09/723,564, “INTRA-DEVICE COMMUNICATIONS ARCHITECTURE FOR MANAGING ELECTRICAL POWER DISTRIBUTION AND CONSUMPTION”, filed concurrently herewith, which is incorporated by reference herein. 
     FIG. 4 illustrates an alternate embodiment for benchmarking the module against a previously determined nines reliability measure. In operation an IED  402  is connected to a power system  400  of known reliability. The power reliability module is then calibrated to measure the appropriate number of nines. Alternately, the IED  402  is connected to a power system  400  of unknown reliability and the power reliability module gives the user the reliability, or number of nines, at that location. 
     In another alternate embodiment the IED  402  is connected to a power system of  400  where it measures reliability for a specified period of time. From this data, a historical baseline of reliability is created. For example an IED  402  is connected to the power system  400  where it measures 99.999% reliability over a one month period. The IED then changes from benchmarking mode to analyze mode where 5 nines&#39; reliability is set as the benchmark at that location. If the reliability drops below or above 5 nines an alarm is given to the user notifying them of a change in measured reliability. Further, the user views both the reliability, in number of nines, such as 99.9999% and in actual percentage, such as 99.9994687%. In another preferred embodiment, the power reliability module in the IED contains a historical reporting function which allows analyzing of historical disturbances to give the historical nines measure. This function is useful for analyzing various power vendors historical data to determine reliability. This function further allows a user to analyze historical data and return the power reliability measurement for various tolerance input values. For example, a consumer be may required to determine what %RMS tolerance values, such as a low and high tolerance limit, which are to be specified in order to pass as a certain number of nines reliability. Further, the user can re-compute the reliability measure with different thresholds for what constitutes an outage. For example, the user can compute reliability of the power system to deliver voltage within 99% RMS and then re-compute the reliability of the power system to deliver voltage within 90% RMS. 
     It is therefore intended that the foregoing detailed description be regarded as illustrative rather than limiting, and that it be understood that it is the following claims, including all equivalents, that are intended to define the spirit and scope of this invention.