Court Opinion

ID: 2929193
Source: CourtListenerOpinion
Date Created: 2015-09-14 20:00:16.975905+00
Date Added: 2024-06-11T12:46:14.692779
License: Public Domain

ARMED SERVICES BOARD OF CONTRACT APPEALS

Appeal of --                                  )
                                              )
Balfour/S&P Two, A Joint Venture              )      ASBCA No. 58067
                                              )
Under Contract No. W9126G-09-C-0054           )

APPEARANCE FOR THE APPELLANT:                        Douglas L. Patin, Esq.
                                                      Bradley Arant Boult Cummings LLP
                                                      Washington, DC

APPEARANCES FOR THE GOVERNMENT:                      Thomas H. Gourlay, Jr., Esq.
                                                      Engineer Chief Trial Attorney
                                                     Jane Holt-Duecaster, Esq.
                                                      Engineer Trial Attorney
                                                      U.S. Army Engineer District, Ft. Worth

                OPINION BY ADMINISTRATIVE JUDGE WILSON

       This appeal arises from the denial of a claim for costs associated with
performing remedial work to correct alleged deficiencies in drilled concrete foundation
piers due to alleged defective specifications and the government preclusion of
appellant's means and methods to complete construction. A six-day hearing was held
in San Antonio, Texas, on entitlement only. The parties have submitted post-hearing
and reply briefs. The Board has jurisdiction over this matter pursuant to the Contract
Disputes Act of 1978 (CDA), 41 U.S.C. §§ 7101-7109. For the reasons stated below,
we deny the appeal.

                                FINDINGS OF FACTS

        1. On 17 September 2009, the United States Army Corps of Engineers,
Fort Worth District (Corps or government), awarded Contract No. W9126G-09-C-0054
to Balfour/S&P Two, A Joint Venture (Balfour or appellant) in the amount of
$46,437,194 (R4, vol. 1, tab 4). The parties involved in the joint venture were Balfour
Beatty and Satterfield & Pontikes, JV (supp. R4, vol. 10, tab 168). The contract was for
the construction of the Airmen Training Complex Dormitory 1, at Lackland Air Force
Base (Lackland AFB), in San Antonio, Texas. This project, which was the first
dormitory to be constructed out of eight identical dormitories, was part of a larger
program at Lackland AFB called the Airman Training Complex (ATC). The contract
performance period was 730 days from receipt of the Notice to Proceed (NTP). (R4,
vol. 1, tab 4) The contract included a structural design for the foundation that consisted
of 136 reinforced drilled piers (also referred to as drilled caissons) installed to a depth of
approximately 65 feet below grade (R4, vol. 2, tabs 13-19). The relevant contract
drawings required that the upper section of each pier be installed using a sonotube, which
is a round cardboard formwork (akin to a giant cardboard paper towel roll) (R4, vol. 2,
tab 20; supp. R4, vol. 40, tab 797).

       2. The contract also contained the following special technical provisions:

                                    SECTION 31 63 26

                                  DRILLED CAISSONS
                                        08/08

              PART 1 GENERAL

              1.1     UNIT PRICES

              1.1.1     Basis of Bids

                    Base the bid on the number and total length of caissons,
                    established by top and bottom elevations and
                    diameters.... The Contractor will not receive payment
                    for rejected caissons or for those not conforming to
                    specifications.

              1.7     SEQUENCING

              1. 7 .1 Caisson Excavation

                    Perform excavation of caissons or groups of caissons so
                    that reinforcing steel and concrete placement is a
                    continuous operation performed the same day that the
                    excavation is completed. Do not leave excavations
                    open overnight.

              2.1     MATERIALS

              2.1.1    Concrete Work

                                             2
      Perform all concrete work in accordance with
      requirements of Section 03 3100.0010 CAST-IN-
      PLACE STRUCTURAL CONCRETE, as modified
      herein:

2 .1.1.1     Strength

      Provide 3000 psi strength concrete at 28 days, with
      slump from 4 to 6 inches.

2.1.1.3     Reinforcing Steel

       Provide reinforcing steel conforming to ASTM A
       615/A 61 SM Grade 60, welded into cages in
       accordance with AWS Dl . 4/Dl . 4M and inserted
       securely in the caissons, in position and alignment, as
       shown, prior to concrete placement.

2.1.3      Casing Steel

      ... Provide casings with an outside diameters [sic] not
      less than indicated shaft sizes and a minimum of 114 inch
      thick. Temporary casings shall extend down 40 feet
      below existing grade ....

3.2     INSTALLATION

      b. Bring concrete to a true level surface inside the
      shaft and a full width cross key formed, or dowels
      installed, if it becomes necessary to interrupt placing
      concrete in any caisson. Prior to placing additional
      concrete, clean surfaces of laitance and slush with one-

                                3
                                                                  •I
                                                                  '
                  to-one portland cement grout, having a water-cement
                  ratio not exceeding that of the concrete.

(R4, vol. 1, tab 12 at 417, 420-22) The drilled pier foundation is created as follows:

              The process begins with drilling a hole with an aug[ e]r.
              And the soils are displaced ....

                       ... [A] casing is placed down in the hole, as the hole
              is started. And then once placed inside the hole, the auger
              action goes inside and continues the drilling until it gets to
              what's called the proper bearing depth.

                     And once it reaches a certain resistance that is
              acceptable to the Government's geotechnical
              representatives it's considered proper to begin the
              placement of concrete.

(Tr. 1/14-15) Before the concrete is placed, a rebar cage (approximately 60 feet in
length) is inserted inside the drilled shaft. Additionally, the contractor is required to
"[ c]ontinuously remove all water that flows into the excavations and from the
excavation bottom, to the extent possible prior to concrete placement." The applicable
contract provisions further state:

              The maximum permissible depth of water is 2 inches. In
              the event of a severe water condition that makes it
              impossible or impractical to dewater the excavation, place
              concrete using an underwater tremie after water movement
              has stabilized.

(R4, vol. 1, tab 12 at 422) The record reflects that a "tremie" is a solid pipe that
concrete is pumped through to fill the previously-drilled shaft. The tremie may be
inserted directly in the freshly-poured concrete to continue filling the excavated area;
effectively filling the shaft with concrete while flushing out water and other              t
contaminates from below. (Tr. 1116)

        3. The contract contained the following Federal Acquisition Regulation clauses
in pertinent part:
                                                                                            I
              52.236-5, MATERIAL AND WORKMANSHIP (APR 1984)

                                             4
               (c) All work under this contract shall be performed in a
               skillful and workmanlike manner. The Contracting Officer
               may require, in writing, that the Contractor remove from
               the work any employee the Contracting Officer deems
               incompetent, careless, or otherwise objectionable.

(R4, vol. 1, tab 4 at 166)

               56 .23 6-21, SPECIFICATIONS AND DRAWINGS FOR
               CONSTRUCTION (FEB 1997)

               (a) The Contractor shall keep on the work site a copy of
               the drawings and specifications and shall at all times give
               the Contracting Officer access thereto. Anything
               mentioned in the specifications and not shown on the
               drawings, or shown on the drawings and not mentioned in
               the specifications, shall be of like effect as if shown or
               mentioned in both. In case of difference between drawings
               and specifications, the specifications shall govern. In case
               of discrepancy in the figures, in the drawings, or in the
               specifications, the matter shall be promptly submitted to
               the Contracting Officer, who shall promptly make a
               determination in writing. Any adjustment by the
               Contractor without such a determination shall be at its own
               risk and expense ....

(Id. at 171)
               52.246-12, INSPECTION OF CONSTRUCTION (AUG 1996)

               (b) The Contractor shall maintain an adequate inspection
               system and perform such inspections as will ensure that the
               work performed under the contract conforms to contract
               requirement. ...

               (f) The Contractor shall, without charge, replace or correct
               work found by the Government not to conform to contract
               requirements, unless in the public interest the Government

                                            5
              consents to accept the work with an appropriate adjustment
              in contract price. The Contractor shall promptly segregate
              and remove rejected material from the premises.

(R4, vol. 1, tab 5 at 207)

              52.246-21, WARRANTY OF CONSTRUCTION (MAR 1994)

              (a) In addition to any other warranties in this contract, the
              Contractor warrants, except as provided in paragraph (i) of
              this clause, that work performed under this contract
              conforms to the contract requirements and is free of any
              defect in equipment, material, or design furnished, or
              workmanship performed by the Contractor or any
              subcontractor or supplier at any tier.

              (c) The Contractor shall remedy at the Contractor's
              expense any failure to conform, or any defect ....

              (d) The Contractor shall restore any work damaged in
              fulfilling the terms and conditions of this clause ....

              (i) Unless a defect is caused by the negligence of the
              Contractor or subcontractor or supplier at any tier, The
              Contractor shall not be liable for the repair of any defects
              of material or design furnished by the Government nor for
              the repair of any damage that results from any defect in
              Government-furnished material or design.

(Id. at 208-09)

    4. The contract also contained numerous drawings, including No. A-S502
"CONCRETE DETAILS" which illustrated the "SONOTUBE FORMING AND
CLAY CAP DETAILS" (R4, vol. 2, tab 20)

                                            6
       5. The NTP was issued by the Corps on 23 September 2009, and was
acknowledged as having been received by appellant on 6 October 2009 (R4, vol. 2,
tab 26). Thus, 6 October 2011 was the original contract completion date.

        6. By transmittal dated 1 December 2009, appellant submitted its shop
drawings for the piers, which included the "TYPICAL PIER REINFORCING
SUPPORT DETAIL" and proposed the usage of"3" CONCRETE MACON PIER
BOLSTER (3 -PCS. PER CAGE)" and "PIER SLEDS" to secure the rebar cage
inside the concrete piers in the alignment and position shown on the drawings in order
to meet the contract requirement that the rebar cage have at least 3 inches of concrete
coverage around the cage (R4, vol. 2, tab 27 at 442, 463, 479, 495). It is undisputed
that these sleds and bolsters proposed by appellant were made of concrete (tr. 3/71 ). It
is further undisputed that appellant ultimately used plastic wheel spacers (tr. 3171,
161).

      7. On 24 December 2009, appellant submitted Request for Information (RFI)
No. 0035, which stated:

              After further coordination with the subcontractors that will
              be drilling and placing the concrete piers, we have
              determined that there are some options that will alleviate
              constructability issues regarding the placement of the pier
              extensions that extend above grade.

             Based on geotechnical information, we are assuming that
             all piers will require casing. The casing will prevent
             formwork and reinforcing ties for the portion of the pier
             above grade from being installed prior to placement of the
             concrete and removal of the casing. This would require
             that concrete be placed up to 5'0" below grade elevation,
             casing completely removed, reinforcing steel pier ties
             above grade installed, sonotubes cut to correct length,
             sonotubes set, formed, plumbed, and elevations marked,
             then a continuation of concrete placement. This work
             would have to be performed in an amount of time to not
             create an unintentional cold joint in the pier.

             Logistically this will be difficult to achieve and will
             significantly decrease the production of pier placement.
             We propose that a construction joint in the piers be
             designed and located at or near the grade elevation and the

                                            7
             extension of the piers above grade be formed and placed
             the following day.

             Please advise if this will be acceptable.

The Corps responded on 30 December 2009 stating: "Place the construction joint at 5
feet below grade. Form the top tiers with sonotube per Detail 6/B-S502." This
response was sent by Yijie Qiang, Senior Design Engineer. (R4, vol. 2, tab 29)

        8. Subsequently, on 4 January 2010 the Corps offered an additional response to
RFI No. 0035. This response, sent by Mr. Joshua Alley, the Corps' Quality Assurance
Representative (QAR), provided the following: "It is acceptable to place a cold joint
3' above grade on the piers. The government considers this to be a clarification of the
contract requirements, it does not constitute a change to the contract and does not
require a change to the cost or time." The response also noted that several email
attachments were included in the response authored by Messrs. Ken McCleskey and
Steve McCall. (R4, vol. 2, tab 30) Mr. McCleskey was the lead geotechnical engineer
for the Dormitory 1 ATC project (tr. 2/172). Mr. McCall was the lead QAR for the
Corps (tr. 3/54).

       9. On 11 January 2010, Mr. McCall sent an email to Mr. McCleskey requesting
that he review RFI No. 0035 and the Corps' response (via Senior Design Engineer
Qiang). Mr. McCall added:

             The contractor is voicing concern about the potential of
             water and mud being at the top of the concrete 5' below
             grade making it very difficult to clean off. If the concrete
             was brought to grade then the water and mud would not be
             an issue. Pat Finley said that this was a Corp detail and he
             did not want to very [sic] from it without your input.

Mr. McCleskey replied, by email dated 14 January 2010 (9:21 am) as follows:

             I'm not sure I understand what the contractor's issue is.

             Typically, they should drill the pier, using casing to seal
             off any groundwater or sloughing materials from the walls
             of the excavation. They would then underream and
             cleanout the pier with their belling tool, and, once
             approved by us (USACE COR), install their rebar cage
             into the pier hole. Next they would place their concrete to
             near the surface. Lastly, they would seat the sonotube

                                           8
              within the uppermost part of the pier, per our detail (i.e.,
              with sonotube placed within the upper 5 feet of pier to
              ensure the formed concrete at the top of the pier is
              cylindrical in shape ....

              If they use the sonotube, per the contract drawings, I see no
              reason why they can't place the pier concrete to the
              elevation indicated on the structural drawings (i.e., there
              should be no reason why they would have to stop pier
              placement below grade).

              Therefore, their requested deviation should be refused.

(R4, vol. 2, tab 31)

       10. Mr. McCall replied via email at 1:30 pm on the same day, which read as
follows:

              The question is how hard is it to place the sonotube once
              the casing is removed and maintain a continuous column of
              concrete in the pier without having a cold joint at the
              bottom of the sonotube, especially since the top of the
              son[ o ]tube in some cases is 8' above the dirt grade?
              Pat Finley's [the designer of record] response would leave
              us to believe that a cold joint is permissible at this point, do
              you concur with his response? If you do concur then what
              is the recommended method for cleaning the top of the
              concrete to avoid having compressible materials at the cold
              joint?

Mr. McCleskey responded by email also on the same date, stating in pertinent part:
           There shouldn't be an issue removing the casing and
           placing the sonotube and remaining concrete. The entire
            operation of placing the concrete to near the top of the
            casing, removing the casing ... placing the sonotube, and
            completing concrete placement should take less than 30
           minutes on a typical pier. Properly done, this should be a
            *continuous* operation ....

                                             9
              So, to reiterate, I advise that we refuse the contractor's
              proposed deviation. The piers should not be constructed
              with a cold joint, and, following the typical/common
              practice drilled pier construction procedure outlined above,
              a cold joint shouldn't even come into play.

(R4, vol. 2, tab 32)

        11. On 16 January 2010, the site was flooded due to a water main break,
thereby delaying the project (supp. R4, vol. 10, tab 178). The record also contains
numerous references to water at the site as an issue in the pier construction process and
a significant number of piers that had to be drilled at least twice prior to completion
(supp. R4, vol. 26, tabs 349-83). By email dated 18 January 2010, Mr. McCall
communicated to Messrs. Finley and McCleskey to relay the following information:

              This e-mail is to document and confirm a conversation
              between Pat Finley and me on Friday 15 January 2010.
              The subject of the conversation was to discuss means and
              methods of installation of the son[ o ]tube extinctions [sic]
              for the piers. Pat reported that he would accept a joint in
              the columns that extend the piers to the 1st floor slab. If
              the contractor installs the son[ o]tube to 2 or 3 feet above
              the dirt grade in the crawl space and places the concrete in
              a simultaneous pour once the pier casing is removed, this
              would avoid a cold joint below grade in the pier. This
              removes the contractor[']s constructability issues with
              having mud and water in the piers ....

              Please respond to this to voice any concerns you might
              have.

(R4, vol. 2, tab 33) The record reflects that Mr. McCleskey had no concerns regarding
the methods proposed in the above-mentioned email (tr. 2/214). We find that the
Corps decision to allow the use of a cold joint at 3' above grade was reasonable.

       12. On 15 February 2010, the first piers were drilled by subcontractor
Batten Drilling. The record reflects that Mr. McCleskey made a site visit to Lackland
AFB to inspect the start of pier drilling operations. In his detailed memorandum for
the record, he observed the excavation of 3 piers, designated as C-3, C-4, and D-5.
Several issues arose including: 1) concrete slump was initially 3 inches, later
corrected by adding water to achieve the requisite 6 inch slump (C-3); ground water
seepage and material sloughing into the previously drilled cavity and casing placement

                                            10
(C-4); and suspending the rebar cage by a crane during concrete placement due to over
drilling the pier cavity (C-3 and D-5). Mr. McCleskey concluded:

              Batten Drilling appeared to be having difficulties, as noted
              herein, drilling and underreaming the piers on the date of
              the inspection. It is the opinion of the undersigned that
              these issues are primarily attributable to the "first day" lack
              of familiarity with the site-specific subsurface conditions.
              Drilling efficiency and pier construction processes are
              anticipated to improve as more experience is gained at the
              site. However, the issues regarding casing placement and
              withdrawal from Pier C-4 cause greater concern for the
              understanding of basic drilling principles in areas of
              known water-bearing sloughing materials.... It should be
              noted that the subsurface conditions encountered on the
              date of the inspection were very similar to those described
              in the logs of borings included in the USACE Foundation
              and Pavement Design Analysis and presented in the
              contract drawings.

(R4, vol. 2, tab 65)

       13. On 18 March 2010, Mr. Joshua Alley, the Corps' QAR sent appellant the
following email:

              From approximately 1630 on, the only representative of
              [appellant] in the area that the work was being performed
              was Mike Dugger, the SSHO [Site Safety and Health
              Officer].

              Mike Dugger was performing the work of the SSHO, the
              Superintendent, and the QC. As per the terms of the
              contract, the SSHO is only to have the duties of the SSHO.

              Further, during the placement of one of the piers, I had to
              stop work before the concrete could be placed in the
              sonotube because it was visibly obvious that the sonotube
              was out of plumb. Upon checking the sonotube, I found
              that the sonotube was several inches out of plumb. I asked
              to have the pier corrected and it was brought to within the
              tolerances described in the specifications ....

                                            11
              If you intend to continue working the hours that you
              worked yesterday, then you also need to provide adequate
              Quality Control and Superintendence to ensure that the
              work being done meets the contract requirements, and to
              allow the SSHO to perform his work without interruption
              or distraction.

(R4, vol. 3, tab 130)

       14. Appellant responded via email on 19 March 2010 indicating that several
representatives were on site and that "[t]he piers in question will be checked and dealt
with accordingly" (R4, vol. 3, tab 133).

        15. On 20 March 2010, QAR Alley forwarded via email a spreadsheet to
appellant detailing several piers that were not plumb and were marked "Fail." He
stated further: "Please examine the data and let me know when you are ready to meet
to discuss what the next step should be." (R4, vol. 3, tab 135)

       16. By letter dated 12 May 2010, the Corps identified several deficiencies in
the pier construction including:

                 1. Piers not within tolerances for plumb or out of
                    tolerance for alignment.
                 2. Reinforcement inside piers does not have the
                    required clearance to the surface of the concrete.
                 3. Concrete in piers does not meet contract
                    requirements.
                 4. [H]ook bars in perimeter beam and slab were tied to
                    the inside of the reinforcement cages and not
                    outside as per the details[.]
                 5. The required number of dowels between the Pier
                    Cap in Area A and the surrounding slab has not
                    been provided.

Additionally, appellant was directed to submit proposals for the methods of evaluation
to the Corps for review. After acceptance of the proposed testing methods, appellant
was required to test and document the condition of all of the piers. For those piers
found to be deficient, appellant was to submit a repair plan to the Corps for approval.
Upon approval, appellant was further directed to treat the repair work as "a new
feature of work, and will require a full preparatory meeting, initial inspection, and
follow-up inspections." Finally, in addition to indicating that appellant's quality        t

                                           12
control had been lacking, the Corps concluded that appellant's performance had been
unsatisfactory. (R4, vol. 3, tab 149)

         17. By letter dated 19 May 2010, appellant replied to the Corps' 12 May 2010
letter indicating that it had taken immediate action on the issues. First, appellant fired
its structural quality control inspector "due to a systemic failure of enforcing the
appropriate quality control measure required for this project." Appellant reported that
it was bringing on a new QC inspector with significant experience as well as using the
general superintendent to "take an active and increased role to monitor and control the
quality control department." With regard to the other issues, pier plumbness and
location, underground pier plumbness, poor concrete, pier rebar cover and length, open
piers, and other problems, appellant proposed a "MOVE FORWARD PLAN" as
follows:

              1. Refine method to identify and fix deficient issues.
                    a. Utilizing the pachometer we will
                           1) Locate rebar depth, top and bottom at
                              above grade pier extension
                           2) Locate top of pier cage reinforcing
                    b. Core and perform penetration test (Windsor
                           Probe) on a sampling of pier extensions as
                           identified by our third party engineer to
                           verify concrete strength
                    c. Excavate 5' below grade at piers Jll, F12 and
                           K 10 identified by our third party engineer to
                           inspect and test below grade concrete.
              2. Submit identification and fix process to USACE for
                    approval.
              3. Proceed with identification and fix.

(R4, vol. 3, tab 150) Based upon the foregoing, we find that appellant did not employ
the appropriate quality control measures at the site.

        18. On 25 May 2010, the Corps informed appellant that it's proposed QC
representative's personnel qualifications had not been received and that until a new
structural QC qualified per Specification § 01 45 01 had been submitted and approved,
no further work on "structural functions" of the project may proceed. The Corps
further noted that the requirement for maintaining documentation was also not being
met. (R4, vol. 3, tab 151)

      19. By letter dated 14 July 2010 appellant advised that it had retained
Mr. Edward Ulrich, P.E., to assist with the resolution of the foundation construction

                                            13
issues. Appellant conveyed Mr. Ulrich's findings that "most of the conditions
observed in the piers are inherent in the USACE's design and instructions and its
denial of Balfour/S&P's request to modify the design in RFI 0035, and as such, could
not reasonably have been avoided under the circumstances." Thus, appellant put the
Corps on notice that it was reserving its rights with regard to all costs and schedule
delays associated with the foundation repairs. (R4, vol. 4, tab 152, attach. 11)

        20. The record reflects that the defective piers were identified and repairs were
commenced (supp. R4, vol. 26, tab 383 at 10176). The parties attempted to resolve the
issues, which culminated in a handwritten settlement agreement dated 6 May 2011.
This agreement, which was signed by appellant and the Corps, was "Subject to
Availability of Funds." (Supp. R4, vol. 40, tab 776) However, it was later determined
that funding was not available for the entire amount (tr. 5/51). The parties reentered
into negotiations and, on 17 June 2011, settled other issues via Modification
No. P00032, while reserving the pier claim (supp. R4, vol. 38, tab 6).

       21. On 19 September 2011, appellant filed a claim with the contracting officer
(CO) in the amount of $4,769,979 which appellant believed it was due because of "the
Government's defective pier design and ensuing constructive changes to Balfour
Beatty/S&P's contractual obligations with respect to the piers both during the original
pier construction and the repair of conditions that the Government considered
defective" (R4, vol. 4, tab 152).

       22. By letter dated 6 December 2011, the CO informed appellant that she had
received the claim and expected to issue a decision on or before 28 February 2012
(notice of appeal, ex. 1).

      23. By letter dated 4 April 2012 appellant filed a notice of appeal with the
Board on a deemed denial basis, due to the CO' s failure to issue a final decision on the
aforementioned claim by 28 February 2012. The appeal was docketed as ASBCA
No. 58067.

       24. At the hearing, appellant offered the expert testimony of Mr. Edward Ulrich, P.E.
He was qualified without objection as an expert in soil mechanics and foundation
engineering with a special expertise in drilled piers (tr. 1/60). He opined that the pier
sonotube detail shown in the project drawings was not buildable in one continuous pour
without a cold joint below the ground surface under the conditions of water and mud behind
the temporary casings. Also, he concluded that the Corps improperly rejected the use of a
crane to position the rebar during the process of pouring the concrete piers. This refusal, he
concluded, created many of the issues uncovered. (Supp. R4, vol. 40, tab 775)

                                           14
        25. The government offered expert testimony* of Robert Brehm, Ph.D., P.E.,
Chief Executive Officer of Construction Analysts, LLC (CA), a construction
management and consulting firm (supp. R4, vol. 39, tab 711). Dr. Brehm has over 40
years of experience in construction engineering including private industry and
academia (tr. 6/22). Appellant objected to his qualifications as an expert, contending
"[s]imply being a civil engineer or having years of construction management
experience does not give him the necessary expertise or qualifications to give opinions
on the drilled pier issues that are involved in this case" (tr. 6/21 ). The Corps countered
that Dr. Brehm has extensive experience in the construction industry and has taught
the concepts that are being applied by people working in the industry who apply those
same means and methods he teaches in the classroom. The Board, upon consideration
of the depth and breadth of construction experience, allowed Dr. Brehm to offer expert
testimony in the instant appeal (tr. 6/23).

       26. Dr. Brehm offered the following summary of opinions and conclusions in
pertinent part:

                  1. CA opines that the design requirements established
                     by the USACE in the contract documents are
                     consistent with standard industry practice and
                     buildable in the geotechnical conditions at Lackland
                     Air Force Base, San Antonio, Texas.

Further, he concludes that appellant "failed to perform the work on the drilled concrete
caisson piers in reasonable conformance with the contract documents and
demonstrated a lack of quality control to ensure compliance as required by the contract
documents and standard industry practice. (Supp. R4, vol. 39, tab 711) With regard to
the issue of the allowance of a cold joint, he testified that a monolithic pour would
have flushed out the contaminants from the concrete due to the fact that the concrete
used was denser than the water. As the concrete was pumped into the pier cavity, the
heavier concrete would essentially cause the water to rise to the top and ultimately
flushed out at the top (see tr. 6/30-33). Moreover, with regard to using a crane to
stabilize the rebar cage he testified that it is not industry practice to hold the rebar cage
to ensure vertical alignment while concrete is being placed. He further added that the
lack of concrete coverage around the rebar cage was more than likely due to the failure
to maintain the plumbness of the cage resulting from improperly installed spacers.
(Tr. 6/43) We find this testimony persuasive.

*The government also offered Mr. William Manginelli as an expert in delay analysis
      (tr. 4/129). As this decision denies the appeal in its entirety, the Board need not
      consider his testimony in relation to the instant appeal.

                                             15
       27. Based on the facts in the record, as presented at the hearing and Mr.
Ulrich's lack of analysis contained in his report, we find that Mr. Ulrich's testimony
was not as persuasive as that of Dr. Brehm.

                                        DECISION

        Both parties acknowledge that several of the piers were defective and not
compliant with the contract specifications. However, the parties disagree as to which
bears responsibility for these defects and ultimately should bear the cost burden of the
subsequent repairs. Under the applicable contract clause (finding 3), the contractor is
liable for defects in workmanship, unless the deficiencies were caused by defects in
government-furnished materials or design.

        Appellant contends that the government restricted its means and methods of
completing the work according to the specifications contained in the contract.
Specifically, appellant avers: (1) despite the contract allowing cold joints in the pier
installation (Section 31 63 26, Drilled Caissons, Part 3 .2(b)), the government arbitrarily
did not permit cold joints; (2) the government's decision to bar appellant from stabilizing
the rebar cages with cranes during the concrete pour operations caused misalignment of
the rebar cages and poor concrete coverage on the completed piers; and (3) the
government's prohibition on relief hole excavations to expunge contaminates from the
piers prior to placing the sonotubes contributed to the poor concrete in the pier extensions.
Additionally, appellant argues that the government did not prove that appellant's faulty
workmanship or lack of quality control caused the pier defects. (App. br. at 30-37)

        The government contends, inter alia, that appellant failed to comply with many
of the contract requirements, including: (1) failure to control water at the site;
(2) pre-drilling several of the piers in violation of the express provisions to the
contrary; (3) installing rebar cages that did not extend the full depth of the drilled pier;
(4) the usage of plastic wheels as spacers on the rebar cages rather than concrete sleds
they proposed and the Corps accepted, and these plastic spacers broke off or bent
during the placement of the rebar cages inside the piers thus failing to keep the cages
plumb and the requisite 3 inches away from the side of the pier; (4) failure to flush
contaminants (soil and/or water) out of the pier concrete properly; (5) misplaced
dowels outside of the rebar cage rather than within the cages in accordance with the
contract requirements; and (6) failure to ensure proper quality control over the pier
excavations and concrete placement. (Gov't br. passim)

        It is well settled that when government plans or specifications specify, in design
detail, the precise manner or method of performance, the government impliedly
warrants a satisfactory performance result ifthe plans and specifications are followed.
United States v. Spearin, 248 U.S. 132 (1918). This implied warranty, however, only

                                             16
runs to contractors that comply with the plans and specifications. Al Johnson
Construction Co. v. United States, 854 F.2d 467, 469 (Fed. Cir. 1988). As the
claimant, the burden is on the contractor to prove that it complied with the plans and
specifications and that despite compliance, defective work resulted. Mae con, Inc.,
ASBCA No. 31081, 89-2 BCA iJ 21,855 at 109,945.

        Here the record shows numerous instances of QC failures and we found that
appellant failed to maintain an adequate quality control system (finding 17). Moreover,
appellant did not comply with the plans and specifications, particularly with regard to
the rebar cage, thus creating piers out of plumb and the rebar not properly aligned
within the concrete (finding 6). With regard to the contract interpretation issue
regarding the use of a cold joint, we found that the government's engineering concerns
and ultimately allowing a cold joint above grade were reasonable (finding 11).
Moreover, the government's expert gave a more plausible reason for the pier defaults
that we found persuasive (finding 27). Thus appellant failed to meet its burden to prove
that the defects were due to the government's plans and specifications and/or actions.

      · In light of our decision we need not consider appellant's claim for a time
extension due to government-caused delay.

                                    CONCLUSION

       Accordingly, the appeal is denied.

       Dated: 1 September 2015

                                                  0
                                                  Administrative Judge
                                                  Armed Services Board
                                                  of Contract Appeals

I concur                                          I concur

4
: .    ~
MARK. N.
          5----~.L-------'---------
       STEMPL~                                    RICHARD SHACKLEFORD
Administrative Judge                              Administrative Judge
Acting Chairman                                   Vice Chairman
Armed Services Board                              Armed Services Board
of Contract Appeals                               of Contract Appeals

                                            17
      I certify that the foregoing is a true copy of the Opinion and Decision of the
Armed Services Board of Contract Appeals in ASBCA No. 58067, Appeal of
Balfour/S&P Two, A Joint Venture, rendered in conformance with the Board's
Charter.

       Dated:

                                                 JEFFREY D. GARDIN
                                                 Recorder, Armed Services
                                                 Board of Contract Appeals

                                           18