Source: http://genemco.com/catalog/aircooledchillers.html
Timestamp: 2019-04-21 23:59:51+00:00

Document:
Air Cooled Chiller - Used Freon Package Air Cooled Chillers by Carrier, McQuay, York, Continental, Trane, Aircondex, Thermal Care.
Genemco sells Air Cooled Chillers - Used Freon Package Air Cooled Chillers.
1997 Trane Air Cooled Liquid Chiller. Model: RTAA3004XM01A3D2ABFG. Refrigerant: R-22. (8) condenser coils, 3 rows, 201690 cfm air flow. Evaporator design capacity: 720 gpm. (3) Trane Helirotor compressors: 460/400V, 60/50Hz, 3 phase. (3) electric compressor motors: 115 hp, 460 V, 60 Hz, 3 phase. Overall dimensions: 36 ft. 3 in. L x 7 ft. 5 in. W x 8 ft. H.
1997 Trane Air Cooled Liquid Chiller. Model: RTAA2154XN01A3COBK. Refrigerant: R-22. Refrigerant side factory test pressure hi/lo: 450/300 psig. System requirements: 460 V, 60 Hz, 3 phase. Trane Helirotor compressor: model: CHHB100TKA0R119AHNN, S/N: N09G00565, 460/400V, 60/50Hz, 3 phase. Trane Helirotor compressor: model: CHHB199TNKON119A, S/N: UA7M581, 460/400V, 60/50Hz, 3 phase. (14) Condenser Fan Motors, 1-1/2 hp, 460 V, 2.8 FLA, 60 Hz, 3 phase. Compressor A starts 2488. Compressor A hours 18158. Compressor B starts 3618. Compressor B hours 38905. Overall dimensions: 23 ft. 2 in. L x 7 ft. 5 in. W x 7 ft. 11 in. H.
McQuay Water Chiller. Model ALR195C-X. Approximate capacity: 195 nominal tons using R-22 based on conditions of 95°F ambient air and a 10°TD change between 55°F and 45°F. Test pressure hi/lo: 380/150 psig. Max relief pressure: 450 psig. (4) 8-cylinder compressors, 60 Hp each 460V 60 Hz 3 phase. (14), 26 in. dia. fans and motors: 1hp, 460V, 60 Hz, 3 phase. Total unit air flow 85,620 cfm. Total coil face surface area: 270 sq. ft. Fin height and fin length per circuit 80 in. x 243 in. Fins per inch x rows deep per circuit: 16 x 3. (4) Crankcase heater plus (1) evaporator heater 115V 60 Hz 1 phase. Overall dimensions: 22 ft. ¾ in. L x 6 ft. 11-1/2 in. x 7 ft. 6 in. H.(H15)(ACN880-95).
Carrier Air cooled chiller package, (3) Model 30GXN249-AE640FG, S/N 0801F, 460/3/60, R-134A, 0 running hours, less than 10 test hours.
Drake Industries chiller, Model PWCT90S2, S/N 99C0064, 3 ph 60 hz 460 volts.
Trane Air Cooled Chiller, year 1991, Model CGAA1204RJ51CC4C60361ARE, 460 volt, 3 phase, 120 ton, good condition, 2-60 ton R - model semi-hermetic compressors.
Carrier Liquid Chiller, year 1986, Model 30GB175650AA, S/M X697492, 460 volt, 175 ton, 7 reciprocating semi-hermetic compressors. Cleaned, painted, megged, all operational ready for install. Since the compressor has 7 compressors it can unload down to as low as 25 tons which is energy efficient. Chiller recently removed from a school in Dallas, Texas in running condition.
Trane 30 Ton Freon Glycol Chiller Package, Model CAUCC 204IC03, S/N J94H82269, 1994, 460 volt, motor 60 hp 230/460, 16 ft. 9 in. L x 7 ft. 10 in. W x 6 ft. 7 in. H.
United Technologies Carrier Air Cooled Refrigeration System Model 30G-245B-610KA, S/N 0596F89106. The Package is 134 in. long, 92 in. wide and 92 in. high. It has four compressors and six fans. Volts PH HZ RLA LRA R-22 Charge 3 Compressors 460 3 60 43.6 223 78 lbs. 1 Compressor 460 3 60 34.6 173 78 lbs. FLA HP Kw Out 4 Fan Motors 460 3 60 2.7 1 .746 2 Fan Motors 460 3 60 2.8 1 .746 Power Supply 460 volt, 3 phase, 60 HZ; Min. circuit amps 192.7, permissible voltage 414-506, max fuse amps 225. control power 115 volt, 1 phase, 60 HZ 30 amps. The unit has individual breakers for each compressor and three breakers for the 6 fans. The Heat Exhanger is Natnl. Bd. 10886, Model No. 10HB401-041, S/N 5295X11382, Blt 1995, State or CRN # K44005. The package has a temperature control/display on the panel.
Trane Air Cooled Chiller 120 tons, Model CGACD121RLNLL623GP, Serial J91K82401. Rated 460 volts, 60 Hz, 3 Phase. Utilization Voltage Range 416/508. Nominal System Voltage 440/461/480. Recommended dual element fuse 300. Minimum fuse size 300. Compressor motor, 460 volt, 60 Hz, 3 phase. Motor 2, 460 volt, 60 Hz, 3 phase. Condenser Fan Motor, 460 volt, 60 Hz, 3 phase, 1.0hp. Unit weight 8,595 lbs, 19 ft. L x 93 in. W x 73 in. H.
York Air Cooled Reciprocating Water Chiller, Model YCAZ74BB3-46PA, S/N RDFM3437AA. 65 nominal tons 460/3/60, dual circuit, R-22 refrigerant. Manufactured 1997, low ambient dampers, outlet glycol temp of 28 °F., microprocessor controller flow switch.
Gasair package chiller unit. It was converted in 1998 and new motors and chiller barrels were added then. This unit looks and runs great.The motors have been changed from gas powered engines to two 125 horsepower electric motors. The rated tons of refrigeration was 175 when it had gas engines, but has been increased to closer to 200 tons with the electric motor setup.
Trane Air Cooled Chiller, year 1988, Model CGACC303KBNDD320, S/N J88C80737, 230 volts, incudes (1) 30 Ton Hermetic Compressor. This unit was used for process service and has very low hours.
Carrier Chiller. Model 30GB075650, S/N T698196. Mfg Date: 6-86. Min Circuit Amps: 187.3, Max Overcurrent Protective Device: 225 fuse only. Control Power Supply: 115 Volts Phase: 1 Hz: 60, Amps: 20.
1996 Trane RTAA 100 Ton Air Cooled Chiller, Model RTAA 1004XF01A1COKBDFN, S/N U96D33776. (2) Trane Compressors, Model CHHN050, 84 amp draw, 460 volt each. (10) Fans, 2-1/2 hp, 1.5 amp draw, 460 volt. Overall Dimensions 87 in. H x 207 in. L x 90 in. W.
2004 McQuay Air Cooled Chiller 130 Ton. Model AGZ-130BS. S/N STNE04109521, 460 /60/3. This chiller is factory new used only for in house testing. Has 6 scroll compressors and is capable of producing glycol at 0 F.
McQuay Airmatic Air Cooled Chiller 175 Ton, 1995 model,Model ALR175C, S/N 5ZM8178401. Barrel information: year 1994, Model E1610, S/N 52M0003700, 6-1/2 in. outlet on barrel. (4) compressors, 50 hp, 83 rla, 535 lra, 460 volt, 60hz, 3ph. Overall dimensions 7ft. 5 in. x 22 ft. 6 in. x 7 ft.
Trane Chiller, Model RTUA0804XC01R360V, S/N U98D09738, 460 volts, 80 ton Screw Compressor, 6 ft. x 5 ft. 5 in. x 3 ft. never installed screw package. This requires a remote condenser as it is a split system.
York Liquid Chiller. Model YCAI-16-46D, S/N YBXM-446514. York microcomputer control center with digital number display. Refrigerant: R-22. Test pressure: 450 psig (high side); 300 psig (low side). Chiller: 460 V, 3 phase, 60 Hz, voltage limits: Min 414/Max 506. Factory refrigerant charge/ Min. circuit ampacity (amps)/ Max. dual element fuse size (amps)/ Max. circuit breaker size (amps) for Systems 1 and 2 and Unit are 116/ 173/ 225/ 225, 133/ 235/ 300/ 300, and n/a/ 378/ 450/ 450, respectively. (8) 30 in. dia. fan blades and (2) 8 in. water inlets/outlets. Compressor # 1: York International Corp. Model JS83F-S46/50L. S/N 44909404. 460/380/415 V, 3 phase, 50/60 Hz. Compressor #2: Compressor Products Incorporated. Model JS63F46S. S/N 10124. 460 V. Texas Instruments Electronic Protection Module. Model 15AA16008. Control circuit: 2.5 amps Max., 24/115/230 Vac, Line 115 Vac. (2) oil heaters, (2) cooler heaters, field chiller liquid line heater. Overall dimensions: 210 in. L x 91 in. W x 100 in. H. Coils were replaced 3 yrs ago. Compressor #2 is still under extended warranty from Compressor Products in Houston. Used at a Texas middle school; always under service contract; well maintained.
Trane Air Cooled Glycol Packaged Chiller- 30 Ton. S/N L78F12355. Compressor motor: 68.3 FLA, 60 LRA, 60 Hz, 3 phase, 460 V, utilization volt range: 414-506, nominal system voltages: 440-460-480, test pressure: 450 psi (high side), 300 psi (low side), factory charged: R-22 (circuit 1: 40 lbs.). (3) condenser fan motors: 1 hp, FLA: 1.82 (each), 60 Hz, 3 phase. Heater circuit: 115 V, 420 watts. Overall dimensions: 200 in. L x 96 in. W x 70 in. H.
Carrier Chiller. Model 30GB075650. S/N T698194. Minimum circuit amps: 187.3; max overcurrent protective device 225 fuse only. Control power supply: 115 V, 1 phase, 60 Hz, 20 amps.
Carrier Chiller. Model 30GB075650. S/N R697562. Min circuit amps: 187.3. Max overcurrent protective device: 225 fuse only. Control power supply: 115 V, 1 phase, 60 Hz, 20 amps.
2005 McQuay Air Cooled Water Chiller- 25 Ton. Model: AGZ025AS27-ER11. SN: STNUENG082905. Refrigerant: R-22. Maximum relief pressure: 450 psig. MAWP hi/lo: 450/150 psig. Total refrigerant charge: 36 lbs. (2) Copeland Scroll Compressors, Model: 2R16M3-TWD-570, S/N's: 00K66752G and 99195362G, 3,500/2,900 rpm, 460/380-420 V, 158/151-167 LRA, 60/50 Hz, 3 phase. Inlets/outlets: (2) 2 in. dia. NPT (male). Overall dimensions: 9 ft. L x 47 in. W x 51 in. H.
McQuay Air Cooled Water Chiller- 220 Ton. Model ALS220A, S/N 56K8146201. (2) Compressors. Refrigerant: R 22. Overall dimensions: 356 in. L x 84 in. W x 95 in. H.
(4) 1999 Carrier Air Cooled Screw Chiller Package-245 Ton. Model 30GX265Y631BA. Serial # 1399F08598, Serial # 1399F08595, Serial # 1399F08601, Serial # 1600F789349. 460 V, 3 Phase, 60 Hz. The 30GX also uses R-134a environmentally-sound refrigerant. These units were put into service May 2000 at Qwest in Sunnyvale CA area.
Wolf Tech/Cooling Tech Air Cooled Glycol Chiller- 20 Ton. Model: CID020-9. S/N: D2002050006. Outdoor use only. Refrigerant: R-22. Design pressure: 400 psig (2860 kPA). Suction pressure: 12-15 psi. Discharge pressure: 270-275 psi. Cooling temperature: 62 °F. Currently set up to cool to 32 °F. Heater temperature: 108 °F. Bitzen Kuhl Machinenebau GMBH Compressor: Type: 6J-22.2, S/N: 662803970, 54 hp, 6-cylinder, 208-230/460 V, 60 Hz, 3 phase. Compressor specifications: displacement: 4061.2 cfh, maximum speed: 1,750 rpm. Inlets: (1) 1-1/2 in. PVC ball valve (to process), (1) 1-1/2 in. female PVC fitting (to process). Outlets: (1) 3/4 in. NPT (female vent), (2) 1-1/2 in. PVC ball valve (from process). Overall dimensions: 14 ft. 3 in. L x 60 in. W x 93 in. H.
Carrier Air-Cooled Liquid Chiller- 25 Ton. Model: 30GT-025---600. S/N: 0494F81110. Outdoor use only. Refrigerant: R-22. Test pressure hi/lo: 480/235 psig. System requirements: 460 V, 60 Hz, 3 phase. Carlyle 6-Cylinder Reciprocating Compressor, Model: O6E7265310, S/N: 5293J01747 S/O, semi-hermetic, electrical requirements: 460 V, 43.6 RLA, 60 Hz, 3 phase. (2) Fan Motors, 460 V, 3.1 FLA, 60 Hz, 3 phase. Control requirements: 115 V, 7 amps, 60 Hz, single phase. Aluminum fin/copper tubes. Small in size, big in installation and operating savings; the ideal unit for exacting commercial requirements. Inlets/outlets: (2) 2 in. dia. copper pipes. Overall dimensions: 10 ft. 8 in. L x 68 in. W x 52 in. H.
York Liquid Chiller- 170 Ton. Model YCAI-16-46D, S/N YBXM-446514. York microcomputer control center with digital number display. Refrigerant: R-22. Test pressure: 450 psig (high side); 300 psig (low side). Chiller: 460 V, 3 phase, 60 Hz, voltage limits: Min 414/Max 506. Compressor # 1: York International Corp. Model JS83F-S46/50L. S/N 44909404. 460/380/415 V, 3 phase, 50/60 Hz. Compressor #2: Compressor Products Incorporated. Model JS63F46S. S/N 10124. 460 V. Texas Instruments Electronic Protection Module. Model 15AA16008. Control circuit: 2.5 amps Max., 24/115/230 Vac, Line 115 Vac. (2) oil heaters, (2) cooler heaters, field chiller liquid line heater. Overall dimensions: 210 in. L x 91 in. W x 100 in. H. Coils were replaced 3 yrs ago. Compressor #2 is still under extended warranty from Compressor Products in Houston. Used at a Texas middle school; always under service contract; well maintained.
2001 McQuay-Snyder General Air-Cooled Chiller- 75 Ton. Model: ALR075C. S/N: 5VH0181800. Refrigerant: R-22. Total refrigerant charge: 73 lbs. Max relief pressure: 450 psig. Test pressure hi/lo: 380/150 psig. Suction pressure: 65 psi. Discharge pressure: 300 psi. Discharge water temperature (setpoint): 50 °F. Copeland Discus Reciprocating Compressor, Model: 6DS3-4000-TSN-800, S/N: 99 K77401. Capacity: 281,000 BTU (20/120 °F). Electrical requirements: 230-460/200-400 V, 142-71 RLA, 60/50 Hz, 3 phase. Copeland Reciprocating Compressor, Model: 6DR1-4000-TSN, S/N: CT 90G 01706S. Electrical requirements: 200-230/400-460 V, 594/297 LRA, 50/60 Hz, 3 phase. Inlets/outlets: (2) 4 in. dia. pipes. Overall dimensions: 19 ft. L x 84 in. W x 59 in. H.
Carrier Flotronic Air Cooled Liquid Chiller- 150 Ton. Model: 30GTN150---620. SN: 3801F12663. For outdoor use only. Flotronic chillers offer outstanding EER's (Energy Efficiency Ratios). Exceptional part-load performance (chillers operate at part load 97% of the time) provides increased operating savings through use of multiple compressors per refrigeration circuit and suction cutoff unloading. (5) Carlyle Semi-Hermetic Reciprocating Compressor, Models: 06E6299310, 06EF29310, (2) 06EF265310 and 06E6265310. S/N's: 0901J00050, 3701J00038, 3601J00137, 3601J00141 and 3601J00796. Compressor electrical requirements: 208-230/460-400 V, 187-264/414-528/324-457 amps, 60/50 Hz, 3 phase. Overall dimensions: 19 ft. 6 in. L x 92 in. W x 98 in. H.
1997 McQuay Air Cooled Chiller- 90 Ton. Model ALS090, S/N 57G8140101. (1) Compressor: 130 hp motor, 343 LRA, 208-230 V, 3 phase. (8) Condenser fan motors: 1.5 hp, 5.8 LRA, 208 V, 3 phase. (1) Crankcase heater: 1.7 LRA, 115 V, 1 phase. Requires min 410 amp circuit breaker and 700 amp fuses. Uses 180 lbs. of refrigerant R22. Has zero run hours. Overall dimensions: 160 in. L x 84 in. W x 98 in. H.
1992 Carrier Air Cooled Liquid Chiller- 90 Ton. Model: 30GT090. S/N: 30GT090-64392F22496. Outdoor use only. Test pressure lo/hi (psi/kPa): 315/2174 (450/3105). Power supply electrical requirements: 460 V, 60 Hz, 3 phase. Control electrical requirements: 115 V, 30 amps, 60 Hz, single phase with a step down transformer. (4) Carlyle 6-Cylinder Reciprocating Compressors, Model: 06ET265-360, 1,800 rpm, 208-230/460V, 446/223 LRA, 60 Hz, 3 phase. Inlets/outlets: (2) 4 in. dia. pipes. Overall dimensions: 11 ft. 2-1/2 in. L x 92 1/2 in. W x 98 in. H.
Carrier "Ecologic" Air Cooled Liquid Chiller- 80 Ton. Model: 30GX-080---610---. S/N: 1997F72786. Refrigerant: R-134a. Design test pressure hi/lo: 350/220 psig (2413/1517 KPa). Power supply: 460 V, 60 Hz, 3 phase. (2) Carlyle Screw Compressors, S/N's: 1697J01259 and 1697J02159, electrical requirements: 460 V (396 V min, 528 V max), 80.3 RLA, 580 LRA, 67.1 RLA, 485 LRA, 60 Hz, 3 phase. Refrigerant charge (each): 96 lbs. Control power supply: 115 V, 30 amps, 60 Hz, single phase. (4) Outdoor motor fans, 2.1 hp, 460 V, 3.4 FLA, 60 Hz, 3 phase. Inlets/outlets: (2) 4-1/2 in. dia. flanged ports. Overall dimensions: 10 ft. 8 in. L x 88-1/2 in. W x 86 in. H.
1991 Trane Air-Cooled Series R Rotary Liquid Chiller- 200 Tons. Model: RTAA2004XA01A0A0B. S/N: U91A03233. Refrigerant: R-22. Refrigerant charge: 170 Lbs. Power supply electrical requirements: 460 V, 60 Hz, 3 phase. Voltage range: 414 - 506 VAC. (2) Trane Helirotor Compressors, Model: CHHB100TKA0R119AHNN, S/N: N00F04190 and Model: CHHB100TNG0N119A, S/N: UA4H2091. Unit has (14) 1.5 hp fans, (7) per compressor. Inlet/Outlet: 6 in. diameter ports. Overall dimensions: 23 ft. L x 116 in. W x 88 in. H.
Frigomeccanica Programme Industriale Air-Cooled Water Chiller- 30 Ton. Model: MK. S/N: 110-T. Refrigerant: R-22. Waterflow: 96.8 gal/min. Electrical requirements: 480 V, 60 Hz. Minimum Feed tank capacity: 130 gal. (2) Maneurop Compressors, Model: MT200 HSS4, S/N's: 4039814 and 4168230, electrical requirements: 460/380 V, 22/44 amps, 60/50 Hz, 3 phase. Inlets/oultets: (2) 3 in. dia. ports (water). Overall dimensions: 12 ft. L x 50 in. W x 84 in. H.
Stock No: MMCT001. Serial No: U91A03230.
Trane Air-Cooled Series R Rotary Liquid Chiller- 200 Tons. Model: RTAA2004XA01A0A0B. S/N: U91A03230. Refrigerant: R-22. Refrigerant charge: 170 Lbs. Power supply electrical requirements: 460 V, 60 Hz, 3 phase. Voltage range: 414 - 506 VAC. (2) Trane Helirotor Compressors, Model: CHHB100TNC0N119AN, S/N: N3D00S4753 and Model: CHHB100TNK0N119A, S/N: UA9J4213. Inlet/Outlet: 6 in. diameter ports. Unit has (14) 1.5 hp fans, (7) per compressor. Overall dimensions: 278 in. L x 116 in. W x 88 in. H.
2005 Trane Air-Cooled Rotary Liquid Chiller-96 Ton. Model RTAA1004XQ01A3. S/N U05A09648.
2005 Trane Air-Cooled Rotary Liquid Chiller-80 Ton. Model RTAA0804XQ01A3. S/N U05A09647. R-22 Refrigerant 61 lbs, power 460 V, 3-60 hz, 250 amp disconnect, 225 amp circuit breaker, 79.8 tons at ARI rating of 44 out and 95 cond, RILE 62 amps, LRA 380 amps, MCA 160 amps.
1993 McQuay Snyder General Air-Cooled Liquid Chiller- 195 Ton. Model: ALR195C. S/N: 5YF8178400. Refrigerant: R-22. Refrigerant charge: 197 lbs. Maximum relief pressure: 450 psig. Test pressure hi/lo: 380/150 psig. Power supply electrical requirements: 460 V, 60 Hz, 3 phase. (4) Copeland 8-Cylinder Reciprocating Compressors, Model: 8DSI-6000-FSD, S/N's: LT01K7839S, BT93F01864S, LT99D21209S, and BT93F018675. Inlets/outlets: (2) 6 in. dia. ports. Overall dimensions: 22 ft. L x 84 in. W x 89-1/2 in. H.
York Air Cooled Chiller- 50 Ton. Model WILC530A46A. S/N NFBM039042. Refrigerant: R-22. Copeland Compressor #1: 20 ton. Copeland Compressor #2: 30 ton. 460 V. (7) Condenser fans: 3/4 hp. (1) Heater cooler. Inlet (1) 4 in.; outlet: (1) 4 in. (on bottom). Overall dimensions: 128 in. L x 91 in. W x 55 in. H.
1997 McQuay Air Cooled Chiller- 90 Ton. Model ALS090, S/N 57G8140101. (1) Compressor: 130 hp motor, 343 LRA, 406 V, 3 phase. (8) Condenser fan motors: 1.5 hp, 5.8 LRA, 460 V, 3 phase. (1) Crankcase heater: 1.7 LRA, 115 V, 1 phase. Requires min 410 amp circuit breaker and 700 amp fuses. Uses 180 lbs. of refrigerant R22. Has zero run hours. Overall dimensions: 160 in. L x 84 in. W x 98 in. H.
Carrier Chiller-75 Tons. Model 30GB075650. S/N T698198. 55 °F in and 45 °F out water temp. Min circuit amps: 187.3. Max overcurrent protective device 225 fuse only. Control power supply: 115 V, 1 phase, 60 Hz 20 amps.
McQuay Air Cooled Chiller, Model ALR115C, S/N 5UA0188400, 460 volts, 115 ton, 4 compressors.
McQuay package chiller, 115 ton unit with 4 semi-hermetic compressors, 460 volt, Model ALR 115C.
Aircondex Air Cooled Chiller- 15 Ton. Model CDC-105?, S/N W025620H87?. Refrigerants: R-12, R-22, R314A, R-404a, R-502, R-507, R-12, R-22, R-314A. Motor # : 060 138523, FLA: 71.2, LRA: 266.3. AC&R Vertical Refrigerant Accumulator: Model S-7063, 1-3/8 in. ODS gas connections, 208/230 V, 3-phase, 60 Hz. (2) 25 in. fans: Allen Bradley 509-DOD. (3) Starters: 200 V/25 hp, 230 V/30 hp, 460-575 V/ 50 hp. 2 in. connections, aluminum panels, mild steel skid base, (4) lifting lugs. Overall dimensions: 110 in. L x 71 in. W x 47 in. H.
Un-used Thermal Care/Mayer Air-Cooled Accuchiller- 3 Ton. Model: AQ0A0304X. S/N: CH-04483. Accuchiller series AQ are built for quiet performance, nonferrous construction. Min/max temperature: 30/60 °F. 1% Capacity reduction per degree operated above 95 °F. Maximum ambient temperature: 110 °F. Evaporative range: 20 to 55. Scroll compressor, Model: AH302TT-195. 31 in. L x 2-1/2 in. W x 18 in. H condenser unit with 11 fins per inch. (2) condenser fan motors, 1/16 hp. Thermal Care/Mayer Motorpump with Magnetek Motor, 3/4 hp, 3450 & 2850 rpm, 200-230/460 V, 60 & 50 Hz, 3.8-3.6/1.8 SF, 3 phase. Impeller diameter: 3.88 in. diameter. Microprocessor controller provides diagnostics, easy operation and accurate temperature control. (4) Casters for easy positioning. Inlets: 1-1/4 in. NPT (female). Outlets: (1) 1-1/4 in. NPT (female). Overall dimensions: 80 in. L x 34 in. W x 55 in. H.
York Air Cooled Liquid Chiller- 25 Ton. Model: LCHA25-46E. S/N: GM-423108. Power supply: 460 V, 73 min. ckt. ampacity, 100 amps max., 60 Hz, 3 phase. York/Borg Warner 6-Cylinder Reciprocating Compressor, Model: SS6213-J46G, S/N: LM11463211, date code: 1072403, refrigerant: R-22, test pressure (hi/lo): 450/330 psig, 460/380 V, 225/216 LRA, 60/50 Hz, 3 phase. York Chiller Barrel, S/N: 5242, shell side MAWP: 150 psi @ 150 °F, shell side MDMT: -20 °F @ 150 psi, tube side MAWP: 225 psi @ 150 °F, tube side MDMT: -20 °F @ 150 psi. (4) 24 in. Fan Motors, 3/4 hp, 208/230 V, 4.5 FLA, 12.4 LRA, 60 Hz, single phase. Controls power supply: 115 V, 15 amps, 60 Hz. Inlets/outlets: (2) 3 in. dia. flanged ports. Overall measurements: 10 ft. 9 in. L x 74 in. W x 50 in. H.
York Air Cooled Liquid Chiller- 100 Ton. Model: YCAS08746PA. S/N: YBWM179579. Refrigerant: R-22. Evap: 170 gpm @ EWT: 53 °F, LWT: 42 °F, AMB: 100. For outdoor use. Power supply: 460 V, 60 Hz, 3 phase. Control power supply: 115 V, 60 Hz, single phase. (2) Compressors- 50 HP, 80 RLA, 510 LRA. (2) Condenser fans- 5hp, 7.1 RLA, 41.8 LRA. (1) Cooler: 18 in. dia x 104 in. L. Overall dimensions: 115 in. L x 86 in. W x 88 in. H.
1992 McQuay Snyder General Air-Cooled Liquid Chiller- 195 Ton. Model: ALR195C. S/N: 5Y81783-00. For outdoor use only. Refrigerant: R-22. Refrigerant charge: 197 lbs. Test pressure hi/lo: 380/150 psig. Max relief pressure: 450 psig. Power supply electrical requirements: 460 V, 60 Hz, 3 phase, minimum ckt ampacity: 455 amps, max fuse size: 500 amps. Chiller is equipped with (14) condenser fan motors (115 V, 1.74 FLA, 60 Hz, single phase), evaporator heater (115 V, 3.2 amps, 60 Hz, single phase). Inlets/outlets: (2) 6 in. dia. ports. Overall dimensions: 22 ft. L x 96 in. W x 92-1/2 in. H. Current Model:AGS195C. (ACN880-92).
1994 York Packaged Liquid Chiller- 185 Ton. Model VCA187AU6-46PA. S/N FNBM116770. With chiller barrel and (2) compressors. Chiller barrel- 21 in. dia x 104 in L. Inlets/ outlets- (2) 8-1/2 in. Chiller: R-22 refrigerant, 140 lbs. charge each circuit. Test pressure: high/low- 450/300 psig, 460 V, 3- phase. Min/max voltage limits- 414/506 V. Min. circuit ampacity: 238/210 amps for System 1/System 2, Max. dual element fuse 400/350 amps for System 1/System 2. (2) York International Corporation Compressors. Models: JS83FS46/50S and JS64FS-46/50. S/Ns: KGGR070069 and KAGR200012. System 1 Compressor: 460 V, 3 phase, 60 Hz, RLA/LRA- 759/575; System 2 Compressor: 380/416 V, 50 Hz, RLA/LRA- 761/570. (2) 3 hp condensers with 4 fan each. (2) Oil heaters- 115 volts, 350 watts, 1 phase. (2) Cooler heaters 115 volts, 560 watts. Both compressors replaced in 1998 with valve springs updated to wave type. Control panel updated 2004. Unit was well maintained and working well when removed from service.
McQuay Air Cooled Water Chiller 155 Ton. Model ALS155C. S/N 5YD0185400. (2) Compressors, 120 Hp each RLA-136, LRA- 700 (EA). , 460 volts, 60 Hz, 3 phase. (12) Condenser fans, 1.0 hp (EA), FLA- 2.0, LRA- 9.9 (EA), 460 Volts, 60 Hz, 3 phase. (2) Crankcase Heaters, 1.8A, 115 Volts, 60 Hz, 1 phase. (1) Evaporator Heater, 3.2A, 115 Volts, 60 Hz, 1 phase. Unit consists of two Mcquay- remanufactured screw compressors. Model SAL167RA12DA, S/N 50BR7021-10 & 52BR7058-10. Both compressors are 460 Volts, 3 phase, 60 Hz, LRA- 489, and START- 764. This unit also consists of a Snyder General / Multi- Tube. National Board Number- 19823, STYLE # - 581595AG08, MODEL E1610, S/N 5YC0024300, AND CRN- C4312.6. MAWP for Multi-Tube is 225 psi @ 109 °F, MDMT is 20 °F at 225 psi. The multi-tube measures 129-1/2 in. L x 20-1/2 in. Diameter. Multi-tube inlet 6 in. Outlet 6 in. Overall measurements are: 19 ft. 1 in. L x 7 ft. 3 in. W x 7 ft. 5 in. H.
York Chiller-25 Ton. Model LCHA25-46E. S/N KM047926. 460 V, 3 phase, 60 Hz. Minimum circuit ampacity 73, 100 amps, max fuse size 72. Compressor: 460 V, 3 phase, 60 Hz, FLA51, LRA 225. (4) fan motors: 3/4 hp, 208/230 V, 1 phase, 60 Hz, FLA 4.5, LRA 12.4. Voltage limits of terminals 414 min, 506 max. 115 V supply, 60 hz, 15A. Inlet: 3-1/2 in.; outlet: 3-1/2 in. Overall dimensions: 129 in. L x 74 in. W x 49 in. H.
Thermal Care/Mayer Chiller- 2 Ton (31x10^3 Btu). Model: MMA-100. S/N: Y018618. Refrigerant R-12. Scroll compressor, Model: AJ131GT-193. Electrical requirements: 230 V, 3 phase, 60 Hz; control voltage: 115 V. Condenser dimensions: 15 in. L x 2-1/4 in. W x 12 in. H. Condenser has 11 fins per inch. Thermal Care/Mayer Motorpump, Model 7230006, impeller diameter: 4.0 in. Thermal Care/Mayer Motor, 1/3 hp, 3450 rpm, 115/230 V, 60 Hz, single phase. Inlet/outlets: (2) 3/4 in. dia. NPT ball valves (from process, to process). Overall dimensions: 36 in. L x 25 in. W x 29 in. H.(ACN67).
2000 McQuay Air Cooled Chiller-350 Tons. Model: ALS370BS-27ER10. S/N: STNU000600277. Refrigerant R-22, max pressure 300 psi. Power supply 460V, 60Hz, 3phase. (24) Condenser fans, 2.0 HP motor, 28 in. dia.1140 rpm, 60 Hz. High efficiency fin and tube type condensers with integral sub cooler, (12) fins per in. and 4 rows deep. Baffled Shell and Through Tube, Direct Expansion Evaporator, Water Vol. 107 gallons, Max. water pressure 175 psi. Overall Dimensions: 459 in. L x 83.4 in. W x 94.5 in. H. Weight 22,050 lbs. (ACN1230).
2000 McQuay Air Cooled Chiller-350 Tons. Model: ALS370BS-27ER10. S/N: STNU000600257. Refrigerant R-22, max pressure 300 psi. Power supply 460V, 60Hz, 3phase. (24) Condenser fans, 2.0 HP motor, 28 in. dia.1140 rpm, 60 Hz. High efficiency fin and tube type condensers with integral sub cooler, (12) fins per in. and 4 rows deep. Baffled Shell and Through Tube, Direct Expansion Evaporator, Water Vol. 107 gallons, Max. water pressure 175 psi. Overall Dimensions: 459 in. L x 83.4 in. W x 94.5 in. H. Weight 22,050 lbs. (ACN1230).
2000 McQuay Air Cooled Chiller-350 Tons. Model: ALS370BS-27ER10. S/N: STNU000600228. Refrigerant R-22, max pressure 300 psi. Power supply 460V, 60Hz, 3phase. (24) Condenser fans, 2.0 HP motor, 28 in. dia.1140 rpm, 60 Hz. High efficiency fin and tube type condensers with integral sub cooler, (12) fins per in. and 4 rows deep. Baffled Shell and Through Tube, Direct Expansion Evaporator, Water Vol. 107 gallons, Max. water pressure 175 psi. Overall Dimensions: 459 in. L x 83.4 in. W x 94.5 in. H. Weight 22,050 lbs. (ACN1230).
2000 McQuay Air Cooled Chiller-350 Tons. Model: ALS370BS-27ER10. S/N: STNU000700023. Refrigerant R-22, max pressure 300 psi. Power supply 460V, 60Hz, 3phase. (24) Condenser fans, 2.0 HP motor, 28 in. dia.1140 rpm, 60 Hz. High efficiency fin and tube type condensers with integral sub cooler, (12) fins per in. and 4 rows deep. Baffled Shell and Through Tube, Direct Expansion Evaporator, Water Vol. 107 gallons, Max. water pressure 175 psi. Overall Dimensions: 459 in. L x 83.4 in. W x 94.5 in. H. Weight 22,050 lbs. (ACN1230).
1996 Carrier Air Cooled Chiller-150 Ton. Model 30GT-245A-610KA, S/N 0796F91850. Factory Charged Refrigeration system R22. (5) Compressors, (10) Fan units. Overall measurements are 92 in. W x 253 in. L x 97 in. H. (ACN517).
Trane Air Cooled Liquid Chiller- 80 Ton. Model CGACC806RANJJ42MK. S/N J87L60146. Refrigerant: R-22. Power supply: 200 V (range 187-220), 60 Hz, 3 phase. Minimum circuit ampacity: 398 amps. Recommended element fuse: 450 amps (max 500 amps. (2) Trane 4-Cylinder Reciprocating Compressors, Models: CCRHR 400A-2HAT and CRHR 400A 3H AT, S/N’s: 70401 1232 and 97B67490, power supply: 200 V, 729 LRA, 60 Hz, 3 phase. (8) Condenser fans, power supply: 1 hp, 200 V, 4.1 FLA, 60 Hz, 3 phase. Overall dimensions: 14 ft. 9 in. L x 7 ft. 5 in. W x 7 ft. 1 in. H.
1996 Trane Air Cooled Chiller – 70 Tons. Model: RTAA0704XFQ1A1D0BFGR. S/N: U96D33922. (2) Trane Helirotor Compressors A & B 460 V, 50 RLA, 330 LRA, 60 Hz, 3 phase. (8) 29 in. dia fans with Motor, 1 hp, 60 Hz, 850 rpm, 200-230/460 V, 5.1-5.0/2.5 amps, Control Circuit, 115 V, 750 amps (max), 60 Hz, 1 phase. Evaporator Heat Tape, 115 V, 750 amps (max), 60 Hz, 1 phase. R-22 refrigerant with 58 lb. charge each. Overall dimensions: 17 ft. L x 94 in. W x 8 ft. H. (ACN400).
York Air Cooled Liquid Chiller- 100 Ton. Model: YCAS08446. S/N: YBWL101498. Outdoor use. Refrigerant: R-22. Test pressure (hi/lo): 450/300 psig. Power supply: 460 V, 60 Hz, 3 phase. Minimum circuit ampacity: 202 amps. Max. dual element fuse size: 225 amps. Maximum circuit breaker size: 225 amps. (2) Copeland 8-Cylinder Reciprocating Compressors, Models: 8DP2-5000FSD and 8DP15000FSD, S/N's: 11516 and 11104, power supply: 460 V, 80 RLA, 510 LRA. (2) Condenser Fans, 5 hp, power supply: 460 V, 7.1 FLA, 41.8 LRA. Electronic Controls, power supply: 115 V, 60 Hz, single phase. (2) Oil Heaters, power supply: 115 V, 60 Hz, single phase, 100 watts (ea). Cooler heater, power supply: 115 V, 60 Hz, single phase. Inlets/outlets: (2) 4 in. dia. ports. Overall dimensions: 9 ft. 7 in. L x 8 ft. W x 7 ft. 10 in. H.
1993 York Air-Cooled Liquid Chiller- 104 Ton. Model: YCAJ44MR6-46PB. S/N: MKBM000933. Outdoor use only. Refrigerant: R-22. Refrigerant charge per system: 78 lbs. Test pressure: 450 psig. System requirements: 460 V, 60 Hz, 3 phase. (2) York International Corporation reciprocating compressors. Electrical requirements: 3 hp, 100 RLA, 318 LRA, 135 amp minimum circuitry ampacity, 175 amp max. dual element fuse size. Unit is equipped with (4) 37 in. dia. cooling fans, each having (4) 35 in. blades per fan. Inlets: (1) 6 in. inlet port. Outlet: (1) 6 in. outlet port. Overall Dimensions: 9 ft. 7 in. L x 7ft. 7 in. W x 7 ft. 6 in. H. (ACN410).
Schroder Brine Chillers. Type: LK200. S/N: S980201. Capacity: approx. 2 ton. Refrigerant: R-22. MAWP: 377.09 psi. (26 Bar), 2 hp (1.5 Kw), 3 x 440 V, 60 Hz, 5.7 amps. Evaporator: 18 in. L x 4-3/4 in. W x 17 in. H. (9) Fins per inch. Fan diameter: 14 in. Unit is for liquid refrigeration systems. Stainless steel submersible tube: 8-1/2 in. diameter x 35 in. H. Overall system dimensions: 23-1/2 in. L x 21 in. W x 22 in. H.
1993 Trane R-Series Air Cooled Rotary Chiller. Model: RTAA1104XE02A1AOBFGE. Rated capacity: 110 tons using R-22. Design test pressure (hi/lo): 450/300 psig. Power supply: 460 V. Shell and tube heat exchanger. (2) Trane Helirotor compressor. Model(s): CHHN050TKA0N057A, CHNN060TKA0N069A. Number of fans: 10. Hours on compressor (A): 4922, starts on compressor (A): 5910. Hours on compressor (B): 11283, starts on compressor (B): 2371. Overall dimensions: 19 ft. 2 in. L x 7 ft. 4 in. W x 8 ft. 1 in. H.
1999 Remcor CH-Series Liquid Cooling System. Model: CH750A. Cooling capacity: 2640 Watts/9000 BTU. Pump capacity: 4 gpm @ 60 psi. Reservoir capacity: 5 gallons. Reservoir drain and fill-port. Digital display of 30-100 °F (0-39 °C). Power supply: 115 V, 20 amps, 60 Hz, 3 phase. These small chillers offer compact design with high efficiency heat transfer. Remcor's unique evaporator design and refrigeration packaging provides long-life and tight temperature control for continuous operation. Compressor, 3/4 hp. Inlet/outlet: (2) 3/4 in. dia. NPT (female) ports. Overall dimensions: 2ft. 2 in. L x 1ft. 6 in. W x 2ft. 5-1/2 in. H. (ACN36).
1991 Trane Air Cooled Liquid Chiller- 20 Ton. Refrigerant: R-22. Design pressure: 450 psig. Test pressure (hi/lo): 563/300 psig. Power supply: 230V, 60 Hz, 3 phase. (2) Trane 3-D Scroll Compressors, power supply: 200/230 V, 41.4 RLA (ea), 247 LRA (ea), 60 Hz, 3 phase. York Chiller Barrel, shell side MAWP: 150 psi @ -20 to 150ºF, head radius: flat, tube side MAWP: 225 psi @ -20 to 150ºF. (2) Fan Motors, 1 hp, 200/230 V, 4.1 FLA (ea), 60 Hz, 3 phase. Inlets: (1) 3 in. dia. NPT port. Outlets: (1) 3 in. dia. NPT port. Overall dimensions: 8 ft. 5 in. L x 7 ft. 6 W x 7 ft. H. (ACN157a).
2002 Continental Portable Packaged Air Cooled Chiller -1.5 Ton. Model: CCAC-015PPT, S/N: 26009-041503. Refrigerant: R-22 only. Chiller dimensions: 19.5 in. dia x 18.5 in. H. (1) Chiller Pump: 1/6 hp, 2 FLA. (1) Process pump: 1/6 hp, 2 FLA. Goodman 1.5 ton Air Conditioner. Model: CKL18-1, S/N: 0112446244. AC Volts: 208/230, phase 1, 60 Hz. Volt range: 197 min - 253 max, Min circuit ampacity: 12.5, Compressor RLA: 9, Compressor LRA: 45. Fan motor: 1/6 hp, 1.3 FLA. Factory test pressure: 150 low, 300 high. Overall dimensions: 6ft. 5 in. L x 2ft. 1in. W x 5ft. 5 in. H.(ACN34).
1998 McQuay Air Cooled Liquid Chiller. Model: ALS125AS27. Rated capacity: 125 tons. Refrigerant: R-22. Maximum relief pressure: 450 psig. Design pressure hi/lo: 450/150 psig. System requirements: 460 V, 274 amps, 60 Hz, 3 phase. (2) McQuay Screw Compressors, Models: SAL155QA10DA and SAL155QA10DA, 380/460 V, 461/489 LRA, 50/60 Hz, 3 phase. McQuay Chiller Barrel, Model: E2010, refrigerant side MAWP: 225 psi @ 109 °F, refrigerant side MDMT: 0 °F @ 225 psi. (8) Condenser fans motors, 1.5 hp (each), 460 V, 2.8 FLA, 10.7 LRA, 60 Hz, 3 phase. (2) Crankcase heaters, 115 V, 1.74 amps, 60 Hz, single phase. (1) Evaporator heater, 115 V, 3.7 amps, 60 Hz, single phase. Inlets/Outlets: (2) 4 in diameter pipe. Overall dimensions: 18 ft. 10 in. L x 10 ft. 7 in.. W x 8 ft. 4in. H.(ACN700).
Trane Air-Cooled Package Chiller - 10 Ton. Model: CGA120B300BA. S/N: J34198525. Unit rated Power 208/230 volt, 3 phase, 60 Hz. MA Fuse Amp (60) Compressor Motor 1, 208/230 volt, 3 phase, 60 Hz, 18.8 RLA, LRA 118. Compressor motor 2, 208/230 volt, 3 phase, 60 Hz, 18.8 RLA, 118 LRA. Condenser fan motor 1: 3 phase, 60 Hz, 6.0 fla, 1 hp. Overall dimensions 38 in. W x 51 in. L x 30-1/2 in. H.(H15)(ACN150).
Carrier Air Cooled Chiller-225 Ton. Model 30GT-225-601AJ. Amp ratings at 460V, maximum: 500, minimum: 487. (8) Carlyle Compressors. 208-230 V, 60 Hz, 3 phase. (16) Condenser Fan Motors, 1 hp, 2.0/5.6 Fla, 9.9/14.5 LRA, 230/460 V, 60 Hz, 1 phase. Shell and tube, Direct expansion type: M.D.W.P 235 PSIG (Refrig. side), 300 PSIG (Water side). Inlet/outlet: 6 in. dia. port. Refrig. R22. Overall dimensions: 29 ft. 9 in. L x 8 ft. 8 in. W x 8 ft.1 in. H. (ACN1460).
1992 Thermal Care/Mayer Air-Cooled Accuchiller- 5.6 Ton. Model: AQ0A0604. S/N: CH-95252. Refrigerant: R-22. Heat transfer fluid: 30% Glycol. Maximum/minimum temperatures: 60/30 °F. Electrical requirements: 460 V, 17 FLA, 60 Hz, 3 phase. Compressor, Model: AG144UT-001, 5.5 hp. Evaporative condenser unit:12 fins/inch Feed tank: 18 gallon. Thermal Care/Mayer Process Pump, 1-1/2 hp, 3450/2850 rpm, 200-230/460 V, 5.6-5.6/2.8 amps, 60/50 Hz, 3 phase. Accuchiller series AQ are built for quiet performance and are of nonferrous construction with easily removable side and top panels and Insulated polyethylene reservoirs. Inlet/outlet: 1-1/2 in. dia. threaded fittings. Overall dimensions: 60 in. L x 33 in. W x 54 in. H.(H16)(ACN96).
1998 McQuay Air Cooled Liquid Chiller- 204 Ton. Model: ALS204AS12. S/N: 58G8128101. Refrigerant: R-22. Maximum relief pressure: 450 psig. Design pressure hi/lo: 450/150 psig. System requirements: 208 V, 881 amps, 60 Hz, 3 phase. (2) McQuay Screw Compressors, Models: SAL175RA13DA and SA175BA13DA, S/N's: 52ER7027-10 and 58G05504-07, 208/230 V, 934/1042 LRA, 60 Hz, 3 phase. McQuay Chiller Barrel, Model: E2010, S/N: 58G0021800, Nat'l Bd: 36545, refrigerant side MAWP: 225 psi @ 109 °F, refrigerant side MDMT: 0 °F @ 225 psi. (14) Condenser fans motors, 2 hp (each), 208 V, 7.8 FLA, 30.5 LRA, 60 Hz, 3 phase. (2) Crankcase heaters, 115 V, 1.74 amps, 60 Hz, single phase. (1) Evaporator heater, 115 V, 3.7 amps, 60 Hz, single phase. Overall dimensions: 22 ft. L x 7 ft. W x 7 1/2 ft. H.
Frigomeccanica Programme Industrial Refrigerated Chiller- 4 Ton. Model: MK. Matriculate: 13783. Refrigerant: R-22. Air cooled. Motor pump: 1.47 hp (1.1Kw), 3480 rpm (3480 1/min), 277/248 V, 5/2.9 amps, 60 Hz. Pump, Type: NM 25/160 BE, H maximum 31 cu. m/hr & m-Q minimum 3 cu. m/hr, H minimum 20 cu m/hr & m-Q maximum 10.8 cu m/hr. Evaporator Panel, dimensions: 55 in. L x 36 in. W. Chiller dimensions: 18-1/2 in. diameter x 55-1/2 in. L. Gruppo Industrial Ercole Marrelli Fan motor, matricula: MA 9084B3. Fan dimensions: 16 in. diameter x 18-1/2 in. L, outlet air aperture: 18 in. L x 15 in. W. Oil container dimensions: 11-1/2 in. diameter x 13 in. H. Control panel: pump switch, compressor switch. Chiller pipe components: low pressure switch, high pressure switch, water gauge: 0-100 mH2O. Inlets/outlets: 2-1/2 in. threaded female, 2-1/2 in. threaded male. Overall dimensions: 85 in. L x 45 in. W x 67 in. H.
1997 Trane air cooled liquid chiller. Model: CGAFC20EAAA1T. Rated capacity: 20 tons. Refrigerant: R-22. Refrigerant side factory test pressure hi/lo: 450/300 psig. System requirements: 200 V, 60 Hz, 3 phase. (2) Trane 3 D scroll compressors. Compressor A, Model: CSHA093A0A00, charge: 40 lbs, electrical requirements: 200 V, 39.4 RLA, 269 LRA, 60 Hz, 3 phase. Compressor B, Model: CSHA093A0A00, charge: 40 lbs, electrical requirements: 200 V, 39.4 RLA, 269 LRA, 60 Hz, 3 phase. (2) Condenser fan motors, 1.0 hp, 200 V, 4.1 FLA, 60 Hz, 3 phase. Control circuit requirements: 115 V, 250 VA max, 60 Hz, single phase. Evaporator heat tape, 120 V, 210 VA maxes, 60 Hz, single phase. Inlets/outlets: (2) 2 in. dia. ports. Overall dimensions: 7 ft. 5 in. L x 6 ft. 4 in. W x 5 ft. 8 in. H.(H15).
1999 Dunham-Bush Air Cooled Chiller-420 Tons. Model ACDX420B. S/N 12329701A99G. Refrigerated System. 460/3/60 Electrics, R-22 refrigerant, 1117# Charge. Compressor motor model numbers. 1215 NHF6X6K & 1218NHF6X6K. Compressor run times: no.1: 27690 hours, no. 2: 18234 hours, no. 3: 8608 hours.(ACN1434).
1999 Dunham-Bush Air-Cooled Liquid Chiller. Model: ACDX420B. Capacity: 420 Nominal tons. For outdoor use only. Refrigerant: R-22. Test pressure hi/lo: 400/250 psig. Power supply: 460 V, 60 Hz, 3 phase. Control supply: 115 V, 60 Hz, single phase. (2) Dunham-Bush Scroll Compressors, Model: 1215NHF6X6K0EMBJ0C, design pressure hi/lo: 410/250 psig, power supply: 460/400 V, 1330 LRA, 60/50 Hz, 3 phase. (1) Dunham-Bush scroll compressors, Model: 1218NHF6X6K0EMBJ0C, power supply: 460/400 V, 1485 LRA, 60/50 Hz, 3 phase. Dunham-Bush chiller barrel, Model: FXT24149J09CVR0, shell side MAWP: 200 psi @ 150 °F, shell side MDMT: -20 °F @ 200 psi, tube side MAWP: 250 psi @ 150 °F, shell side MDMT: -20 °F @ 60 psi. (22) condenser fan motors (ea.), 1.5 hp, 3.0 FLA, 460 V, 60 Hz, 3 phase. Inlets/outlets: (2) 10 in. dia. Victaulic ports. Compressor run times: no.1: 63179 hours, no. 2: 47652 hours, no. 3: 60105 hours. Overall dimensions: 44 ft. L x 7 ft. 6 in. W x 8 ft. 5 in. H.
Applied Process Equipment Recirculating Air-Cooled Water Chiller- 5 Ton. Model: QAC-5. S/N: 863059. System electrical requirements: 208 V, 29.4 amps, 60 Hz, 3 phase. Copeland Compressor, Model: CR1-0500-TF5, S/N: 86F11745H, requirements: 200/240 V at 50 Hz, 200/230 volts at 50 Hz, refrigerant R-22. Pump model: AE211, 1/2 hp, 1.8 amps. Evaporator panel dimensions: 62 in. L x 42-1/2 in. W. Oil separator tank, MAWP: 400 psi at 150 °F, MDMT: 20 °F at 400 psi., pressure relief valve: 400 psi. Chiller barrel dimensions: 25 in. L x 12 in. diameter (insulated). Control box, return water temperature gauge, pump pressure, R-22 gauge. Oversized shell and tube heat exchangers provide maximum heat transfer surface. Water or water/glycol temperatures from 0 °F to 60 °F. Chiller inlet/outlet: 2 in. threaded (female), water inlet/outlet: 1-1/2 in. diameter copper pipe. Overall dimensions: 76 in. L x 36 in. W x 80 in. H.
Applied Process Equipment Recirculating Air-Cooled Water Chiller- 5 Tons. Model: QAC-5. S/N: 863059. System electrical requirements: 208 V, 29.4 amps, 60 Hz, 3 phase.. Copeland Compressor, Model: CR1-0500-TF5, S/N: 86F11745H, requirements: 200/240 V at 50 Hz, 200/230 volts at 50 Hz, refrigerant R-22. Pump model: AE211, 1/2 hp, 1.8 amps. Evaporator panel dimensions: 62 in. L x 42-1/2 in. W. Oil separator tank, MAWP: 400 psi at 150 °F, MDMT: 20 °F at 400 psi., pressure relief valve: 400 psi. Chiller barrel dimensions: 25 in. L x 12 in. diameter (insulated). Control box, return water temperature gauge, pump pressure, R-22 gauge. Oversized shell and tube heat exchangers provide maximum heat transfer surface. Water or water/glycol temperatures from 0 °F to 60 °F. Chiller inlet/outlet: 2 in. threaded (female), water inlet/outlet: 1-1/2 in. diameter copper pipe. Overall dimensions: 76 in. L x 36 in. W x 80 in. H.
2006 GCI Refrigeration Technologies Chiller. Model: 660ACTLTOD. Refrigerant: R-404a. Tank capacity: 200 gallons. Rated at 159,600 BTU/hr @ -20ºF. Respective minimum and maximum design pressures are: 5 psi and 395 psi. Maximum ambient temperature: 95ºF. Main power: 460V, 60 Hz, 3 phase. FLA 135(NRA 115.2). Max fuse 60. (3) 22 HP Copeland compressors: model 4DT3F76KE-TSK-200. (3) 1-1/2 HP Fans. Features include: internal and external circulating pumps regulated by two flow switches for optimal flow, electrical phase monitor sensing, “on demand” temperature control provided by a Tecnologic S.P.A. TLK 31C microprocessor-based digital electronic multistep controller, auxiliary contacts capable of actuating pneumatic valves, and by employing extra insulation, a compressor fitted suction accumulator and crankcase heater, this unit is equipped for better control of heat gained from the environment and optimized use at low temperatures(+10°F to -30°F). Inlet/outlet: (2) 4 in. Overall dimensions: 13 ft. L x 7 ft. 2 in. W x 6 ft. 8 in. H.(ACN1123).
1999 Remcor CH-Series Liquid Cooling System- 3/4 Ton. Model: CH750A. S/N: 62A0019LC201. Cooling capacity: 2640 Watts/9000 BTU. Pump capacity: 4 gpm @ 60 psi. Reservoir capacity: 5 gallons. Reservoir drain and fill-port. Digital display of 30-100 °F (0-39 °C). Power supply: 115 V, 20 amps, 60 Hz, 3 phase. These small chillers offer compact design with high efficiency heat transfer. Remcor's unique evaporator design and refrigeration packaging provides long-life and tight temperature control for continuous operation. Compressor, 3/4 hp. Inlet: (1) ½ in. dia. push hose type, (1) 1 in. reservoir tank fill port. Outlet: (1) ½ in. push hose type (1) ¼ in drain. Overall dimensions: 26 in. L x 18 in. W x 29-1/2 in. H.(ACN37).
2002 Carrier Air Cooled Chiller. Model: 30GTN110 620KA. Rated nominal cooling capacity: 110 tons. Refrigerant: R-22. (4) Carlyle compressors. Models: 06EF299610 and 06E6265610: 400/460V, 50/60Hz, 3 phase. (8) fans, 6 blades, 30 in. diameter, 950 rpm, 76000 cfm (6) at 2 hp, (2) 1.7 hp,460V, 60 Hz, 3 phase. Control power supply: 115V, 30 amps, 60 Hz, 1 phase. Comfort Link™ control panel enabling a cable ready connection to a Carrier Comfort Network(CCN). Overall dimensions: 14 ft. 7 in. L x 8 ft. W x 8 ft. 2 in. H.(ACN488).
2002 Carrier Air Cooled Chiller. Model: 30GTN110 620KA. Rated nominal cooling capacity: 110 tons. Refrigerant: R-22. (4) Carlyle compressors. Models: 06EF275610 and 06E6265610: 400/460V, 50/60Hz, 3 phase. (8) fans, 6 blades, 30 in. diameter, 950 rpm, 76000 cfm (6) at 2 hp, (2) 1.7 hp,460V, 60 Hz, 3 phase. Control power supply: 115V, 30 amps, 60 Hz, 1 phase. Comfort Link™ control panel enabling a cable ready connection to a Carrier Comfort Network(CCN). Overall dimensions: 14 ft. 7 in. L x 8 ft. W x 8 ft. 2 in. H.(ACN488).
1996 McQuay Air Cooled Screw Chiller 200 Ton. Model: ALS204A27. Rated at 204 tons using R-22. (2) McQuay Screw Compressor model no.’s: SAL175RA13DA. McQuay Chiller Barrel Model no. E 2010. Refrigeration side MAWP: 225 psi @ 109°F, MDMT: 20°F at 225 psi. (14) Conditioning Fan. (2) Crankcase. (1) Evaporator. Supply circuit 460 V, 60 Hz, 3 phase. 399 amps, max 500 amps. Overall dimensions: 21 ft. 10in. L x 7 ft. W x 7 ft. 10 in. H.
2010 Carrier Air Cooled Screw Chiller. Model: 30XAB2606M-OGSD3. S/N: 1710Q91422. Refrigerant: R-134A. (2) compressors. (14) fans. 460 volt. 3 phase (ACN1285).
York "Millennium" Air Cooled Liquid Chiller- 110 Ton. Model: YCAZ77CB3-46PA. S/N: RCGM3959AA. Outdoor use only. Refrigerant: R-22. Test pressure hi/lo: 450/300 psig. System requirements: 460 V, 60 Hz, 3 phase. (2) York International Corporation 6-Cylinder Rotary Screw Compressors, Model: ZB6S1-D46/50S, S/N's: GAGR210320 and GMFR077137, 460/380 V, 363/348 FW LRA, 297/298 RW LRA, 60/50 Hz, 3 phase. York Chiller Barrel- 12 x 8, design working pressure shell side: 235 psig, design working pressure tube side: 150 psig, capacity: 30 gal, gpm (min/max): 90/315. (2) Condenser Fan Motors, 3 hp, 460 V, 6.8 RLA, 36.0 LRA, 60 Hz, 3 phase. Total fan airflow: 34,400 cfm. Control requirements: 115 V, 60 Hz, single phase. Inlets/outlets: (2) 4 in.dia. flanged ports. Overall dimensions: 113-1/2 in. L x 100 in. W x 92 in. H.
1999 Carrier Air Cooled Chiller. Model: 30GT100 610KA. Rated nominal cooling capacity: 100 tons. Refrigerant: R-22. Respective high and low design/test pressures: 450/278 psi. (4) compressors: 460V, 60 Hz, 3 phase, or 400V, 50 Hz, 3 phase. (8) fans, 6 blades, 30 in. diameter, 1.0 hp, 460V, 60 Hz, 3 phase. Overall dimensions: 15 ft. 2 in. L x 8 ft. 2 in. W x 8 ft. 2 in. H.
1999 Carrier Air Cooled Chiller. Model: 30GT100 610KA. Rated nominal cooling capacity: 100 tons. Refrigerant: R-22. Respective high and low design/test pressures: 450/278 psi. (4) Carlyle compressors. Model: 06EF275310: 208/230-460V, 60 Hz, 3 phase, or 400V, 50 Hz, 3 phase. (8) fans, 6 blades, 30 in. diameter, 1.0 hp, 460V, 60 Hz, 3 phase. Overall dimensions: 15 ft. 2 in. L x 8 ft. 2 in. W x 8 ft. 2 in. H.(H).
1997 Carrier Air Cooled Chiller. Model: 30GT100 610KA. Rated nominal cooling capacity: 100 tons. Refrigerant: R-22. Respective high and low design/test pressures: 450/278 psi. (3) Carlyle compressors. Model: 06EF275310: 208/230-460V, 60 Hz, 3 phase, or 400V, 50 Hz, 3 phase. (1) Carlyle compressor. Model: 06E6265310: 230/460V, 60 Hz, 3 phase. (8) fans, 6 blades, 30 in. diameter, 1.0 hp, 460V, 60 Hz, 3 phase. Overall dimensions: 15 ft. 2 in. L x 8 ft. 2 in. W x 8 ft. 2 in. H.(H).
2001 Carrier Air Cooled Chiller. Model: 30GTN090 620KA. Rated nominal cooling capacity: 90 tons. Refrigerant: R-22. Respective high and low design/test pressures: 450/278 psi. (4) compressors: Model: 6EABBC2T2H600R: 460V, 60 Hz, 3 phase. (6) fans, 2 hp and 1.7 hp, 460V, 60 Hz, 3 phase. Chiller barrel and condenser both failed leak test. Overall dimensions: 11 ft. 7 in. L x 8 ft. 8 in. W x 8 ft. 1 in. H.(ACN400).
1996 Trane air cooled liquid chiller. Model: RTAA110AYF01A1COBK. Rated capacity: 110 tons. Refrigerant: R-22. Refrigerant side factory test pressure hi/lo: 450/300 psig. System requirements: 200 V, 60 Hz, 3 phase. (2) Trane Helirotor compressors. Compressor A: model: CHHN060AKB0N069A, charge: 98 lbs, electrical requirements: 200 V, 233 RLA, 1190 LRA, 60 Hz, 3 phase. Compressor B, Model: CHHN050AKB0N057A, charge: 73 lbs, electrical requirements: 200 V, 192 RLA, 990 LRA, 60 Hz, 3 phase. (10) Condenser Fan Motors, 1.5 hp, 200 V, 5.1 FLA, 60 Hz, 3 phase. Control circuit requirements: 115 V, 750 VA max, 60 Hz, single phase. Evaporator heat tape, 115 V, 420 VA max, 60 Hz, single phase. Includes Trane adaptive control panel. Inlets/outlets: (2) 4 in. dia. ports. Overall dimensions: 19 ft. 3 in. L x 7 ft. 4 ½ in. W x 7 ft. 2 in. H.(H15)(ACN550).
2001 Carrier Air Cooled Chiller - 225 Tons. Model: 30GXN225-A-640PT. S/N: 1201F71092. Unit currently has 3 Compressors installed (A1, A2, B1). Compressors A1/B1 are Carlyle model 06NA2250S7EA-A00, Mfg. NCBUHA6001, S/N 1001J09133 and 1001J09340, 460V 185.3 Rla (motors are rated for both 50Hz and 60Hz). Compressor A2 is Carlyle model 06NA2146S7EA-A00, Mfg. NCEQHA6001, S/N: 1001J09363, 460V 103.4 Rla (motors are rated for both 50Hz and 60Hz). Condenser has 10 fan motors, each 1.9 HP, 460 V, 60 Hz, 3.2 Fla, 3-phase. Chiller barrel model 10HX400156, s/n 0901X09384, nat'l bd. 40873, shell side rating: WP 220 PSI at 150 F, MDMT -20 F at 220 PSI, test pressure 242 PSI. (2) Henry Technologies accumulators, year 2001, part S-4618, s/n 62748, CRN 5550.7C, MAWP 220 PSI at 650 F, MPMT -20 F at 220 PSI. (2) Henry Technologies horizontal oil separators, part S-5464A, ASME, Carrier model 30GX503661, 2.125 in. ODS, 375 PSIg Max WP. Electrical requirement: 460 V, 3-phase, 60 Hz. Min circuit amps 458.3 / max over-current protection device amps 600. Control power requirements: 115 V, 1-phase, 60 Hz, 30 Amps. Overall dimensions: 233 in. L x 89 in. W x 89 in H.
2001 Carrier Air Cooled Chiller - 225 Tons. Model: 30GXN225-A-640PT. S/N: 1201F71102. Unit currently has 3 Compressors installed (A1, A2, B1). Compressors A1/B1 are Carlyle model 06NA2250S7EA-A00, Mfg. NCBUHA6001, S/N 1101J09251 and 1001J09127, 460V 185.3 Rla (motors are rated for both 50Hz and 60Hz). Compressor A2 is Carlyle model 06NA2146S7EA-A00, Mfg. NCEQHA6001, S/N: 1001J09251, 460V 103.4 Rla (motors are rated for both 50Hz and 60Hz). Condenser has 10 fan motors, each 1.9 HP, 460 V, 60 Hz, 3.2 Fla, 3-phase. Chiller barrel model 10HX400156, s/n 0901X09340, nat'l bd. 40785, shell side rating: WP 220 PSI at 150 F, MDMT -20 F at 220 PSI, test pressure 242 PSI. (2) Henry Technologies accumulators, year 2001, part S-4618, CRN 5550.7C, MAWP 220 PSI at 650 F, MPMT -20 F at 220 PSI. (2) Henry Technologies horizontal oil separators, part S-5464A, ASME, Carrier model 30GX503661, 2.125 in. ODS, 375 PSIg Max WP. Electrical requirement: 460 V, 3-phase, 60 Hz. Min circuit amps 458.3 / max over-current protection device amps 600. Control power requirements: 115 V, 1-phase, 60 Hz, 30 Amps. Overall dimensions: 233 in. L x 89 in. W x 89 in H.
1994 Dunham-Bush Air Cooled Chiller-225 Tons. Model ACDX225B. S/N 2864401A94F. Pressure Test: 400 PSI high side, 250 PSI low side. Unit: 460 V, 60 Hz, 3 phase. CNT: 115 V, 60 Hz, 1 phase. (4) Compressor Motors, Model: SSCA075AR, 103 RLA, 180 LRA, 460 V, 60 Hz, 3 phase. (4) Condenser Fan Motors, 1 hp, 460 V, 2.4 amps, 60 Hz, 3 phase. (16) Condenser Fan Motors, 1-1/2 hp, 460 V, 2.0 amps, 60 Hz, 3 phase. (4) Crankcase Heaters, 200 hp, 115 V, 1.7 amps, 60 Hz, 1 phase. (3) Chiller Heater, 420 hp, 115 V, 3.7 amps, 60 Hz, 1 phase. Cond. Of Service – 599 gpm/43 pgR-22 refrigerant with 484 lb. charge. Inlet: (1) 6 in. dia port. Outlet: (1) 8 bolt 6 in. dia flange. Overall dimensions: 37 ft. 4 in. L x 100 in. W x 92-1/2 in. H. (ACN1035).
Giltron Water Recirculating Chiller. Model: WC-40, S/N: R-4144. Input Volts: 480. Tecumseh compressor, Model: AK100AT. Refrigerant: R-22. Capacity: 10,000 BTU/hr. Procon pump with Dayton motor: 1/4 hp, 1725 rpm, 115 V, 5 amps, 60 Hz, 1 phase. Reservoir tank dimensions: 14 in. L x 10 in. W x 11 in. H. GE Fan motor: 1/20 hp, 1550 rpm, 115 V, 2.5 amps, 60 Hz, 1 phase. Overall dimensions: 33 in. L x 15 in. W x 40 in. H.
Giltron Water Recirculating Chiller. Model: WC-40, S/N: R-4138. Tecumseh compressor, Model: AK100AT. Refrigerant: R-22. Capacity: 10,000 BTU/hr. Procon pump with Dayton motor: 1/4 hp, 1725 rpm, 115 V, 5 amps, 60 Hz, 1 phase. Reservoir tank dimensions: 14 in. L x 10 in. W x 11 in. H. GE Fan motor: 1/20 hp, 1550 rpm, 115 V, 2.5 amps, 60 Hz, 1 phase. Overall dimensions: 33 in. L x 15 in. W x 40 in. H.
Giltron Water Recirculating Chiller. Model: WC-40, S/N: R-4134. Tecumseh compressor, Model: AK100AT. Refrigerant: R-22. Capacity: 10,000 BTU/hr. Procon pump with Dayton motor: 1/4 hp, 1725 rpm, 115 V, 5 amps, 60 Hz, 1 phase. Reservoir tank dimensions: 14 in. L x 10 in. W x 11 in. H. GE Fan motor: 1/20 hp, 1550 rpm, 115 V, 2.5 amps, 60 Hz, 1 phase. Overall dimensions: 33 in. L x 15 in. W x 40 in. H.
Trane Air Cooled Liquid Chiller- 200 Tons Model: RTAA2004XB01A1B0E. S/N: U91E04416. Refrigerant: R-22. Refrigerant side factory test pressure hi/lo: 450/300 psig. System requirements: 460 V, 60 Hz, 3 phase. Trane Helirotor Compressor, Model: CHHB100TNB0N119AN, S/N: UA1E4418, electrical requirements: 460 V, 163 RLA, 896 LRA, 60 Hz, 3 phase. (14) Condenser Fan Motors, 1 hp, 460 V, 2.8 RLA, 60 Hz, 3 phase. Control circuit requirements: 115 V, 750 RLA, 60 Hz, single phase. Evaporator heat tape, 115 V, 480 RLA, 60 Hz, single phase. Inlets/outlets: (2) 6 in. dia. flanged ports. Note: two end original doors have been replaced by two shop fabricated doors. Overall dimensions: 23 ft. L x 8 ft. 2 in. W x 7 ft. 9 in. H.(ACN741).
Frick RXB-50 Outdoor Chiller Skid – 20 TR. Refrigerant: R-22. Ethylene glycol DX-chiller package. Frick rotary screw compressor model RXB-50. 480V, 60 Hz, 3-phase. Cooling medium: 60% ethylene glycol / 40% water. Requires air cooled condenser to operate. Weight: 15,500 lbs. Dimensions: 16 ft. L x 8 ft. W x 9 ft. 7 in. H.
Purchase Used Air Cooled Chillers, Used Freon Package Air Cooled Chillers from Genemco.

References: V. 
 V. 
 V. 
 V. 
 V. 
 V.