Source: https://www.scribd.com/document/329902883/US-Version-Catalog-PSR-PSE-and-PSTX-1SXU132224C0201-Final
Timestamp: 2019-04-26 04:48:41+00:00

Document:
Motors use almost one third of the world’s generated electricity.
OEM. Our softstarters reduce the mechanical stress on your motor application. Torque control. motor brake and many other features enable you to operate your process at its full potential. 1/2 Softstarters | US Catalog . which will increase your uptime. Whether you are a consultant. Over ten motor protection features are included to keep your motor safe from different load and network irregularities.ABB softstarters How we are helping the industry 1 Softstarters from ABB offer multiple values and benefits. pump cleaning. Increase application Productivity Reduce the number of stops in your production by allowing your softstarter to do more than just starting. application and motor size. Secure motor Reliability ABB softstarters help increase your motor’s lifetime by protecting it from electrical stress. The built-in bypass saves energy and space while reducing heat generation—a complete motor starting solution in one unit. softstarters will add to your business value by securing motor reliability. panel builder or end-user. improving installation efficiency and increasing application productivity. Improve installation Efficiency Reduce your installation time and panel size by having all the features you need built into your softstarter. Starting currents are easily optimized to your load. Our softstarters are easy to install thanks to their compact design and many built-in features.
Reducing the number of components by 80 percent shortened installation time by 60 percent.South Africa ABB softstarters provide efficiency in the mining industry One of Xylem’s water solutions helps to prevent flooding in mines.abb. Xylem can sell twice as many panels with softstarters than before.com/lowvoltage/launches/pstx. By cutting costs in half.500 meters. Previous softstarters needed a lot of extra protection equipment.1 Xylem . US Catalog | Softstarters 1/3 . Xylem was looking for a simpler solution that would ensure reliability even at a depth of 3. Why softstarting matters to Xylem Installation time reduced by 60% Total panel cost reduced by 50% For more examples of how ABB softstarters are helping the industry. visit www.
Thanks to the feature that reverses the direction of the flow and starts again with kick-start. while reducing pump downtime. Packed with useful features. which makes starting tough and current high. It is possible to adjust the settings to fit almost any starting condition. This will cause reduced flow and increased risk of pump damage. Controlling pumps Controlling fans Eliminating water hammering with torque control Water hammering is a common problem with pumps. Keep pipes and pumps clean There is a risk of pumps clogging over time.ABB softstarters Improving industrial processes around the globe 1 Softstarters can do wonders for your operations. ABB softstarters feature torque control stop which eliminates water hammering and prolongs the lifetime of the system. the voltage is increased gradually during start. which reduces the current and removes the inrush peak. from unloaded to fully loaded. It typically results in a lot of wear on pipes and valves when stopping the pump. ABB softstarters can help prevent and solve pump clogging and associated downtime. Avoid running dry with underload protection Damage due to pumps running dry can be avoided with the softstarter feature underload protection. 1/4 Softstarters | US Catalog . improve the reliability of your processes. It stops the motor which saves the pump from additional wear and contributes to prolonging its lifetime. and increase overall productivity. Soft starting adjusted to application Fans normally have a high moment of inertia. Active braking using the dynamic brake feature reduces stopping times. they reduce the wear of your equipment. Fast stops with motor braking It can also take a long time to stop the fan. Avoid unwanted movements with stand-still brake An idle fan that is rotating backwards due to wind or airflow from another fan can be kept still using the stand-still brake. It prevents unwanted airflow and improves the control of the system without the need for an external mechanical brake. If an ABB softstarter is used. This improves process safety when the load has a high moment of intertia thereby making fan operation easier for the operator.
the network. Full voltage start is a start mode that gives you almost a direct start but without the current peak. it may be necessary to run the motor at low speed to correctly position the belt before resuming operation. Full voltage start for scroll compressors For scroll compressors it is often necessary to start the motor in a very short time while still maintaining a low starting current. the motor won’t start in the wrong direction. putting it out of operation until the component has been replaced. The jog with slow speed feature makes it possible to position the belt manually. Using phase reversal protection. reducing the reliability and longevity of the motor. improving the availability of the equipment and system. avoiding costly unplanned stoppages. which is a considerably more expensive solution. Phase reversal protection for problem-free commissioning A motor rotating in the wrong direction. and motor. Increased flexibility with jog with slow speed After stopping the belt. US Catalog | Softstarters 1/5 . before restarting the belt. Continuous operation with limp mode Shorted thyristor is a possible problem for a softstarter. avoiding costly compressor downtime and repairs. Full control of current with current limit Many applications are sensitive to high or variable starting currents. in both forward and reverse.1 Controlling conveyor belts Controlling compressors Avoid overheating with overload protection Too much material on a conveyor belt may cause overload and overheating. avoiding overheating. The feature current limit makes it possible to start the motor securely even in a weaker network. The ABB overload protection feature shuts down the motor in case of overload. the softstarter will continue to work with one thyristor shorted. Using limp mode. This improves process efficiency and eliminates the need for a variable speed drive. which may occur due to incorrectly connecting the phases. Reducing the current means reducing the stress on cables. may cause severe damage to a compressor.
Typical torque and current curves from starting a motor using DOL. the motor will not start. star-delta and softstarter. Using a VSD with the sole purpose of ensuring soft starting and stopping of full-speed motors is an unnecessary solution. so if the torque is reduced too much. However. different starting and stopping methods can be used. which means that the motor will start with maximum current and torque regardless of load type. 1/6 Softstarters | US Catalog . It eliminates common problems associated with motor starting and stopping. It is suitable for stable networks and mechanically stiff and well-dimensioned shaft systems due to the high current and torque generated during start. A star-delta starter reduces current and torque during start. resulting in energy efficient motor operation in variable speed applications.ABB softstarters Why motor starting and stopping matters 1 There are some common issues associated with starting and stopping electrical motors. a softstarter is the optimal compromise between a direct-online or star-delta starter and a variable speed drive in many full-speed motor applications. although it also reduces the starting torque to about 25 percent. Direct-on-line Star-delta Softstarter Direct-on-line starting (DOL. the VSD was designed primarily to control motor speed. also across the line starting) is the easiest and most commonly used starting method. Depending on the requirements. DOL starting is uncontrolled. Current peaks will happen when switching from star to delta connection. Motor current Because it offers soft starting and stopping. softstarters are used to start and stop motors in full-speed applications. Variable speed drive Like a softstarter. Like direct-on-line and star-delta starters. including electrical surges. Torque Star-delta is not adjustable. The starting current is about one third compared to direct-online starting. spikes and high inrush currents. a variable speed drive (VSD) can perform soft motor starting and stopping.
covering every need.ABB softstarters A solution for every need 1 The ABB softstarter offering consists of three ranges..600 V Control supply voltage 100.370 A Main motor voltage 208...240 V AC or 24 V AC/DC Control supply voltage 100....600 V Main motor voltage 208......250 V AC Cu rre n Cu t limi t rre n Ele t limi t ra ctr oni mp cm Du al o oto and d v ual ro er Un ver der load loa curre p Po load p rotec d pro nt lim we tion tec it rot r tion Loc facto ection ru ked nd rot erlo Cu o rre ad nt/ r pro pr tec vol Ph tag tion otect ase ion e r imb ev Cu a sto ersa l pr lance me o Mo rd efin tectio prote tor ctio ed n PT heati n pro ng C/P tec T t 1 ion Ov 0 0 erv olta input Ea for ge/ rth mo un Bu fault p dervo tor p ilt-i rot l r t ote ag nb e Ins ypa ction e pro ction ide tec -de ss tion Gra lta con ph nec De ical d ti tac is hab play on po Mo and ss l e tor key key ible pad Pro runtim pad gra ea nd Dia mma sta ble gno rt w sti arn coun Ov erlo cs ing t fun Ov ad tim ctio erlo ens An ad tim to-trip alo e go t Fie utp o-co ol ldb us ut Eve com nt mu nic Mu log atio ltip n le l Ele ang ctr uag icit es ym Tor qu e c eterin Tor ont g qu e li rol mit Co ate dP Lim C p m BA Jog ode w Dy ith slo nam ws pee Sta ic br df a nd ke orw s t ard i Se l l b qu /re enc rake ver se Ful es l vo tar t l t a Kic ge ks sta tar rt Au t tom atic pu mp cle ani ng Softstarter feature selection guide PSR – – – – – – – – – – – – – – • – – – – – – – – – o – – – – – – – – – – – – – – PSE • – • – • – • – – – – – – – • – • – – – – – – • o o – – • – • – – – – – – • – PSTX • • • • • • • • • • • • • • • • • • • • • • • • • • 17 • • • • • • • • • • • • Secure motor reliability • Standard o Optional Improve installation efficiency Increase application productivity – Not available US Catalog | Softstarters 1/7 ....105 A Rated motor current 30.250 V AC Rated motor current 30.. improve installation efficiency and increase application productivity. Our products help you secure motor reliability..1250 A (inside delta: 2160 A) Main motor voltage 208..690 V Control supply voltage 100.. PSR – The compact range PSE – The efficient range PSTX – The advanced range Technical data: Technical data: Technical data: Rated motor current 3.
1 1 Softstarter 4 5 6 8 − − Soft start and stop with reduced current 3 − − Features to improve process productivity − − Detachable kepyad for front on off 7 2 8 door mounting on a panel 1 2 Short circuit breaker MCCB − − Short circuit protection of motor − − Possibility for electrical isolation Can I use a softstarter for an ATEX motor? ABB softstarters PSR. either in another location or inside an ATEX approved panel. PSE and PSTX can be used to start ATEX classified motors in Ex environments if the following considerations are taken into account: −− The softstarter has to be placed outside the Ex area.ABB softstarters A part of your motor starting solution 1 Motor starting requires several components to work perfectly together. 1/8 Softstarters | US Catalog ATEX . − − A separate ATEX approved overload relay from ABB must be used together with a line contactor. − − Select softstarter according to normal or heavy-duty start depending on application and line contactor and overload relay with Type 2 coordination. offering all the necessary components and complete motor starting solutions. ABB is a one-stop shop for motor starting. This overload relay will replace the built-in EOL in the softstarter and has an ATEX approved tripping curve. proven by the numerous installations worldwide.
g.1 3 Pilot devices −− Remote control of motor 4 Power supply CP-E −− Possible to use 24 V AC/DC equipment in the panel. which means there is a floating electrical ground. It is possible to use an ABB softstarter in such a network. e. US Catalog | Softstarters 1/9 . Ships use IT networks. but it is recommended to not connect the functional earth or ground on the softstarter to the ship to avoid disturbances from the network to that would affect the electronics inside the softstarter. −− Indication of softstarter and 5 − − Monitoring and signalling the water level PLC motor status with light and Liquid level monitoring relays CM-ENS sound −− Emergency stop of motor 6 PLC 800M 7 − − Automatic control − − Easy installation of control − − Remote communication Terminal blocks SNK range wires 8 Line contactor AF − − Isolation at stop − − Isolation at faults − − Emergency stop − − Back-up DOL starter Can I use a softstarter on a ship? ABB softstarters PSE and PSTX have marine approvals and are certified for marine environment.
79) 20 (0.PSR45 PSR60.PSTX840 PSTX1050.39) 20 (0..38) Minimum distance to wall Maximum mounting angle 0 303 O C O O 303O 0 O 0 303 O O 303O 0 A D B A B Items included in the box with the softstarter Multi-language manual PSR3…PSR105 PSE18…PSE370 PSTX30…PSTX1250 1/10 Softstarters | US Catalog • • • Terminal kit Cable and mounting kit for detachable keypad - - • • • - ..39) (0.98) (0..79) (0.PSR30 PSR37.94) (5.39) (0......94) (3..ABB softstarters Wall mounting instructions 1 Softstarter.91) (5.39) (0...PSE370 PSTX PSTX30..39) 10 (0..79) (1..94) 10 (0.91) (0.PSE170 PSE210.91) (5.38) (1..PSTX370 PSTX470.39) 10 (0.79) (0.79) (0.59) (0.94) 100 (3.59) Minimum distance to front (0.PSTX170 PSTX210.. type PSR PSR3.PSR105 PSE PSE18.94) 100 (3.79) N/A N/A N/A 100 100 100 150 150 150 10 10 10 15 15 15 20 20 20 20 20 20 35 35 35 35 35 35 (3.98) (0.79) (0..79) 20 (0..PSR16 PSR25..38) (1.PSTX105 PSTX142.PSE105 PSE142.98) N/A N/A N/A N/A 100 (3...98) (0..PSTX570 PSTX720.PSTX1250 Minimum distance to wall mm (in) A B C D 0 0 0 0 0 0 0 0 25 25 25 25 (0.38) (1..59) (0.38) (1.38) (1..94) (3...79) (0.
Certifications and approvals	Approvals: ship classification societies Certifications Abbreviation CE approved in EU cULus Canada USA CCC China EAC Russia ANCE Mexico C-tick Australia ABS GL Lloyd’s Register DNV CCS PSR3. PSE370 • • • • • • • • • • • PSTX30.. PSTX1250 • • • • • Pending Pending Pending Pending Pending Pending • Standard design approved... the products bear the certification mark when it is required.... PSTX370 • • • • • • • • • • • PSTX470. PSR105 • • • • - • - - - - - PSE18. For other certifications and/or approvals. Directives and standards No. please contact ABB.2 No 14 Industrial Control Equipment US Catalog | Softstarters 1/11 ....ABB softstarters Certifications and approvals 1 The table below shows the certifications and approvals for ABB softstarters. PSTX570 • • • • • • Pending Pending Pending Pending Pending PSTX720.. 2004/108/EC Electromagnetic compability EN 60947-1 Low voltage switchgear and control gear—Part 1: General rules EN 60947-4-2 AC semiconductor motor controllers and starters UL 508 Industrial Control Equipment CSA C22. 2006/95/EC Low voltage equipment No.
2 Softstarters | US Catalog .
PSR – The compact range PSR .The compact range Introduction 2/2 Overview 2/4 Ordering details 2/5 Accessories 2/6 Technical data 2/7 Dimensions 2/8 Circuit diagrams 2/9 US Catalog | Softstarters 2/1 2 .
240 V AC. Soft start and stop with PSR will reduce mechanical wear and tear on the application and increase the availability and uptime. Set-up is done through three potentiometers making it very fast and easy. A PSR together with a manual motor starter makes up a far more compact starting solution than a star-delta starter. −− Two-phase controlled −− Operational voltage: 208. On the PSR. ... and with the built-in bypass.105 A − − Soft start with voltage ramp − − Soft stop with voltage ramp − − Built-in bypass for energy saving and easy installation − − Easy set-up by three potentiometers − − Fieldbus communication with FieldBusPlug adapter and the FieldBusPlug −− Run and Top of Ramp relays available for monitoring −− Connection kits available for connection to ABB manual motor starters (MMS) Secure motor Reduce the electrical stresses and keep the motor protected with the MMS Improve installation Saving time and money with built-in bypass and easy set-up Increase application Reduce the mechanical stresses on your motor Reliability Efficiency Productivity 2/2 Softstarters | US Catalog The PSR reduces the starting current for the motor. the bypass is built-in and verified by ABB.PSR – The compact range Introduction 2 The PSR softstarter is the most compact of all the softstarter ranges.. which allows for the design of compact starting equipment.. the energy losses inside the softstarter are highly reduced. saving you time during installation and providing more space in your panel.. 50/60 Hz or 24 V AC/DC − − Rated operational current: 3.600 V AC −− Wide rated control supply voltage: 100.. The possibility of connecting it to the manual motor starter makes it possible to build a compact and complete starting solution with overload and short-circuit protection.
LED indicators PSR has LED indicators for On/Ready and Run/Top of ramp.PSR45). Screw or DIN-rail mounted PSR is fast and easy to install by using screw mounting or DIN-rail mounting (PSR3.70% results in end voltage = 30. stop ramp time and initial/end voltage level.. for start ramp time.. Settings 1 Start = 1....including the step down voltage 3 2 Step down 1 Step down = 2% reduction for each second increased stop ramp 2 Uini = 40.PSR105).20 sec .. Connection kit (optional) The connection kits simplifies installation of the PSR by making the connection to the MMS screwless.... Output signal relays PSR has output relays for Run and Top of ramp (PSR25. Three potentiometers for settings Set-up is made very easy with only three potentiometers.60% 3 3 Uini 3 Uend 1 Start 2 Stop US Catalog | Softstarters 2/3 2 ....20 sec 2 Stop = 0.PSR – The compact range Introduction Motor protection with manual motor starter Use the PSR together with the MMS to get a complete motor starter with soft start and stop together with overload and short circuit protection.
8 3 6.5 16 10 15.2 11 25 15 24. 1) 1) J-90 AF65 TA110DU AF80 AF96 AF116 .5 12 7. A (440-480 V) hp UL. max. 40 ºC Max.2 15 30 20 28 18.5 11 7. 1) Fuse protection (50 kA) gG Fuse Suitable switch fuse for the above gG fuses. J-type (85 kA) J-35 J-type fuses for UL coordination 1) UL listed circuit breaker PSR3 1) J-60 Please see coordination tables at: applications. IEC coordination Using manual motor starters type 1 coordination will be achieved.com/low-voltage/products/softstarters/pstx.com/SOC or at new. For more examples see: applications.4 3 6. 2/4 Softstarters | US Catalog 50 A MS450 OS32G Thermal overload relay Overload protection is used to protect the motor from overheating.5 37 25 34 22 45 30 46.abb.9 2 3.2 30 60 40 59.PSR – The compact range Overview 2 Normal start In-line connected (400 V) kW IEC.1 4 9 5 9 5. 1) Switch fuse MS116 10 A 16 A MS132 25 A 32 A Line contactor The line contactor is not required for the softstarter itself but often AF9 used to open if OL trips.5 3. 1) 63 A 100 A 125 A TF42DU AF12 MS495 AF16 AF30 AF38 AF52 250 A OS250 TA75DU AF26 — 200 A OS125G This is an example of coordination. 40 ºC Manual motor starter (50 kA) Using gG fuses type 1 coordination will be achieved. FLA UL coordination PSR6 PSR9 PSR12 PSR16 PSR25 PSR30 PSR37 PSR45 PSR60 PSR72 PSR85 PSR105 1.abb.it.it.abb.com/SOC.4 37 72 50 68 45 85 60 80 55 105 75 104 J-110 J-125 J-150 J-200 600 V. 1) 400 V. fuse. max.
75 1.00) (5.. PSR30 Selection table for normal start.5 15 30 7.5 3 4 5. Us.27 (0.5 3 9 2 2 5 12 3 3 7.85) (5. 24 V AC/DC 0.45 0.. Typical applications: −− Bow thruster −− Centrifugal pump −− Compressor −− Conveyor belt (short) −− Elevator For a more precise selection.5 11 15 18.2 59.5 10 10 15 20 25 30 40 2 3 5 7. 100.5 15 18.5 15 18.85) (5.5 10 20 37 10 10 25 45 15 15 30 60 20 20 40 72 20 25 50 85 25 30 60 105 30 40 75 Catalog number Global reference code Weight (1 pce) current 550 / 600 V Pe hp 2 5 7.5 10 15 20 20 25 30 0.1 9 11 15.5 3 4 5. U s .45 0.. 50/60 Hz IEC UL/CSA 1SFC132299F0002 Rated operational power 230 V 400 V 500 V 1SFC132300F0002 PSR37 .99) (0. PSR16 PSR25 ..4 6.2 4 4 5.240 V AC.5 2 3 5 7.5 7.5 1 2 3 3 7.5 2.5 7.5 16 3 5 10 25 7.99) (1.43) (2.00) (5.2 28 34 46..45 0.20) (2.75 1.com/low-voltage/products/softstarters Rated operational voltage U e. use the online softstarter selection tool available by scanning the shown QR code or using the selection tool available at: new...99) (0.5 0.45 0..abb.5 11 15 22 22 30 1.5 7.00 2..45 0.20) (4.5 7.20 2.45 0.27 2.2 59.27 (lb) (0.99) (0.99) (0.27 2.8 1 1.27 2.5 10 10 20 25 30 40 50 60 75 100 3. 208.75 2 6.5 7.2 24.5 10 15 20 25 30 40 50 60 75 US Catalog | Softstarters 2/5 2 .5 22 30 37 45 55 2..00) 2 5 7.2 28 34 46.00) (5.65 0.27 2.9 0.5 7.1 9 11 15.45 0.00 1.45 0.2 3 4 5.20) (4.65 1.5 22 30 37 45 55 55 3.5 11 15 18.20 2.5 10 10 20 25 30 40 50 60 75 100 FLA A 3.00) (5.5 22 30 37 45 55 Pe kW 2..99) (0.00 1.5 7.5 11 15 22 22 30 Pe kW 1.4 6.600 V AC Rated control supply voltage.43) (1.5 7.4 68 80 104 PSR3-600-70 PSR6-600-70 PSR9-600-70 PSR12-600-70 PSR16-600-70 PSR25-600-70 PSR30-600-70 PSR37-600-70 PSR45-600-70 PSR60-600-70 PSR72-600-70 PSR85-600-70 PSR105-600-70 1SFA896103R7000 1SFA896104R7000 1SFA896105R7000 1SFA896106R7000 1SFA896107R7000 1SFA896108R7000 1SFA896109R7000 1SFA896110R7000 1SFA896111R7000 1SFA896112R7000 1SFA896113R7000 1SFA896114R7000 1SFA896115R7000 kg 0.99) (0. PSR105 Pe kW 0.2 24.2 4 4 5.99) (1.8 9 12 16 25 30 37 45 60 72 85 105 0.00 2.99) (0.43) (1.600 V AC Rated control supply voltage.75 1.65 1..00) Rated operational voltage U e. PSR45 PSR60 .9 6.. 208.4 68 80 104 PSR3-600-11 PSR6-600-11 PSR9-600-11 PSR12-600-11 PSR16-600-11 PSR25-600-11 PSR30-600-11 PSR37-600-11 PSR45-600-11 PSR60-600-11 PSR72-600-11 PSR85-600-11 PSR105-600-11 1SFA896103R1100 1SFA896104R1100 1SFA896105R1100 1SFA896106R1100 1SFA896107R1100 1SFA896108R1100 1SFA896109R1100 1SFA896110R1100 1SFA896111R1100 1SFA896112R1100 1SFA896113R1100 1SFA896114R1100 1SFA896115R1100 0..45 0.65 0.5 7.43) (2.PSR – The compact range Ordering details 1SFC132297F0002 Description 1SFC132298F0002 PSR3 .99) (0.5 22 30 37 45 55 55 Rated operational current power 200 / 220 / 440 / 208 V 240 V 480 V Ie Pe Pe Pe A hp hp hp 3.45 0.2 3 4 5.20) (2.5 7.5 2.
PSR105 with MS495 PSR16-MS116 PSR30-MS132 PSR45-MS450 PSR105-MS495 1SFA896211R1001 1SFA896212R1001 1SFA896213R1001 1SAM501903R1001 For softstarter type Catalog number Global reference code Pkg qty 1 1 1 1 Fan PSR3.060 (0..PSR45 with MS450 PSR60..088) (0.013 (0.010 0...50 mm 2..PSR105 PSR-FAN3-45A PSR-FAN60-105A 1SFA896311R1001 1SFA896313R1001 For softstarter type Catalog number Global reference code Pkg qty 1 1 Weight (1 pce) kg (lb) 0.034 0...075) (0.PSR45 PSR60...040 0. MS132-32 PSR37..049) (0.033) Weight (1 pce) kg (lb) 0.PSR105 2/6 Softstarters | US Catalog PS-FBPA 1SFA896312R1002 1 .110) Weight (1 pce) kg (lb) 0.150 (0.050 (0....PSR105 PSLW-72 Wire range mm2 1 x 10.PSR16 with MS116 or MS132 PSR25...132) Terminal enlargements 1SFC132168F0001 PSR60.029) Weight (1 pce) kg (lb) 0....022) (0.PSR30 with MS132-12 ..25 mm 2 PSLW For softstarter type Catalog number PS-FBPA 1SFA899002R1072 1 Global reference code Pkg qty FieldBusPlug connection accessory PSR3..022 0..PSR – The compact range Accessories 2 PSR16-MS116 1SFC13224F0001 1SFC132169F0001 For softstarter type 1SFC132170F0001 1SFC132208F0002 PSR30-MS132 PSR105-MS495 1SFC132325F0001 1SFC132171F0001 PSR45-MS450 PSR-FAN3-45A 1SFC132012F0202 PSR-FAN60-105A Catalog number Global reference code Pkg qty Connection kit PSR3. 2 x 10..
.+140 F)2) -40.16 mm2 2 x 2..75..x-1000 ] x = actual altitude of the softstarter in meter.6 AWG) mm2(14. US Catalog | Softstarters 2/7 .....5 W 20. 497 150 For derating of voltage.8% per ºC (0..75... [ % of Ie = 100 ..14 AWG) 2 x 0..75.14 AWG) 2 x 0...75...9 W 6.2. 0. [ % of Ie = 100 ....95 mm2 (8.+70 ºC (-40..5 W 11.5 mm2 (19. See table below for details 101) 201) Signal relays for run signal resistive load AC-15 (contactor) for top of ramp signal resistive load AC-15 (contactor) LED for On/Ready for Run/Top of ramp Settings Ramp time during start Ramp time during stop Initial and end voltage 1) 2) 3) PSR37 PSR45 PSR60 PSR72 PSR85 PSR105 2 -25. Above 40 ºC (104 ºF) up to max.35 mm2 1 x 2.. contact your local ABB office..2.600 V +10%/-15%. starting current of 4 x Ie and ramp time 6 seconds.5 W 8..4/0 AWG) 2 x 6.5... 40.8 AWG) (10.14 AWG) 2 x 0.5 mm2 (19....5.5 W 1 x 0. +10%/-15%....20 sec....2.5 mm2 (19..5 mm2 (19. de-rate the rated current using the following formula. Power loss at rated Ie Connectable cable area main circuit PSR3 PSR6 PSR9 PSR12 PSR16 PSR25 600 V 208.. When used at high altitudes...240 V AC at 24 V AC/DC Max... Number of starts per hour using PSR softstarters Motor current Ie 3A 6A 9A 12 A 16 A Starts/hour without auxiliary fan 10 20 30 40 50 60 PSR3 PSR6 PSR9 PSR12 PSR12 PSR16 PSR25 PSR16 PSR25 PSR30 25 A 30 A PSR25 PSR30 PSR30 PSR37 37 A 45 A PSR37 PSR45 PSR60 PSR72 PSR85 PSR105 PSR45 PSR60 PSR72 PSR85 PSR105 - PSR37 PSR45 60 A 72 A 85 A 105 A PSR60 PSR72 PSR85 PSR72 PSR85 PSR105 PSR85 PSR105 PSR105 - PSR60 PSR72 PSR85 PSR105 PSR37 PSR45 80 PSR9 PSR16 PSR25 PSR30 PSR37 PSR45 PSR60 PSR105 - 100 PSR6 PSR60 PSR72 - - Starts/hour with auxiliary fan 10 20 30 40 50 PSR3 PSR6 60 PSR9 PSR12 PSR16 PSR25 PSR30 PSR16 PSR25 PSR30 PSR37 80 100 PSR9 PSR12 PSR25 PSR30 PSR37 PSR45 PSR45 PSR45 PSR60 PSR60 PSR72 PSR72 PSR85 PSR105 PSR85 PSR105 PSR105 - - Data based on an ambient temperature of 40° (104 ºF)......y-3280 ] y = actual altitude of the softstarter in feet.. please use the softstarter selection tool.2..5 mm2 (19.5 A 3A 0.+60 ºC (-13.. For more optimized selection or to use PSR for heavy-duty starts.5 A – – 3A 0.... above 1000 meters (3281 ft) up to 4000 meters (13123 ft)..44% per ºF).PSR – The compact range Technical data Softstarter types Rated insulation voltage Ui Rated operational voltage Ue Rated control supply voltage Us Starting capacity at Ie Number of starts per hour standard with aux. 50/60Hz ±5% or 24 V AC/DC..5 mm2 (19.10 mm2 (14...6 W 5.70% Valid for 50% on time and 50% off time.10 (10..7 W 10 VA 2. contact your local ABB office. If other data is required.8 AWG) 1 x 0.20 sec.1 W 1 x 6.2 AWG) 2 x 6.240 V AC. 50/60 Hz ±5% 100..16 AWG) 3A 0.5 A 1 x 0.+158 F) 4000 m (13123 ft)3) IP20 IP20 IP10 12 VA 5W 0.75.2 W 6.2... fan Ambient temperature during operation during storage Maximum altitude Degree of protection main circuit control circuit Power consumption Supply circuit at 100.2 W 7... 4 x Ie for 6 sec...35 mm2 (10... 60 ºC (140 ºF) reduce the rated current with 0.14 AWG) 25 W 36 W 5.2 AWG) Green Green 1.1...6 W 1 x 10.14 AWG) control circuit PSR30 3..75.
38") 10 mm (0.18") 2x 153 mm (6.02") 5 mm (0.39") PSR60.20") 58 mm (2.20") 120 mm (4.09") 7 mm (0.39") 1SFB536147G1203 4 mm (0.51") 128 mm (5.5mm (Ø 0.5 mm (0.73") 208 mm (8.20") 1SFB536147G1204 10 mm (0.76") 5 mm (0.77") 4 mm (0.04") 2 1SFB536147G1202 Ø4.39") 160 mm (6.16") 10 mm (0.14") 44mm (1.39") 1SFB536147G1201 5.30") 4 mm (0.22") 35 mm (1.77") 220 mm (8.13") 5 mm (0.16") 10 mm (0.87") 180 mm (7.20") 10 mm (0.36") 179 mm (7.5mm (Ø 0.18") 2x 1SFB536147G1202 5.77") 200 mm (7.2/8 Softstarters | US Catalog 45 mm (1.5mm (Ø 0..19") Ø4.22") PSR – The compact range Dimensions PSR37…PSR45 54 mm (2.39") 1SFB536147G1201 Ø4..5 mm (0.49") PSR3…PSR16 1SFB536147G1204 35 mm (1.72") 114 mm (4.5 mm (0.28") 140 mm (5.66") PSR25…PSR30 1SFB536147G1203 187 mm (7.16") 3.05") 172 mm (6.PSR105 70 mm (2.39") 45 mm (1.38") 152 mm (5.28") Dimensions in mm (and in) .98") 140 mm (5.18") 2x 10 mm (0.51") 132 mm (5.
3 Softstarters | US Catalog .
PSE –The efficient range PSE .The efficient range Introduction 3/2 Overview 3/4 Ordering details 3/6 Accessories 3/8 Technical data 3/9 Dimensions 3/12 Circuit diagrams 3/13 US Catalog | Softstarters 3/1 3 .
the bypass is built-in and verified by ABB. Torque control for elimination of water hammering in pumps Torque control is the most efficient way to stop a full speed pump.g. and is specialized in pump operation. . 4X.. Saving time and money with built-in bypass and compact design On the PSE. Remote operation with external keypad or over fieldbus is available as an option. The keypad is language neutral and illuminated for easy set-up and operation in field..600 V AC −− Wide rated control supply voltage: 100.. It combines the requested protections with a very compact design and built-in bypass.250 V AC. saving you time during installation and providing space in your panel. overload and underload. The compact design makes installation fast and easy. moist and corrosive atmosphere Secure motor Reliability Improve installation Efficiency Increase application Productivity 3/2 Softstarters | US Catalog −− Illuminated display that uses symbols to become language neutral −− External keypad rated IP66 (Type 1. 50/60 Hz − − Rated operational current: 18. The PSE has a special torque stop ramp that is designed together with a pump manufacturer to eliminate water hammering in an optimal way..PSE – The efficient range Introduction The PSE has been designed to meet the most common requirements from the water management sector. 3 −− Two-phase controlled −− Operational voltage: 208. The current limit gives you more control of the motor during start and allows you to start your motor in weaker networks...370 A − − Voltage ramp and torque control for both start and stop − − Current limit − − Kick-start − − Built-in bypass for energy saving and easy installation − − Coated PCBA protecting from dust.12) as an option − − Fieldbus communication with FieldBusPlug adapter and the FieldBusPlug − − Analog output for display of motor current −− Electronic overload protection − − Underload protection − − Locked rotor protection Basic motor protection and current limit The PSE includes the most important protections for handling different load situations that can happen to pumps e.
This allows easy control with e. Set-up is done by using the four buttons on the keypad. that the softstarter is in top of ramp and if any event has happened. 3 Digital input for start.Ramping up/down Steady . LED indicators Green ready LED Flashing . Clear markings on the front for easy installation All markings are on the front.g. top of ramp and event Three output signal relays for indicating that the motor is running.PSE – The efficient range Introduction Screw mounting PSE is fast and easy to install by using screw mounting. Red fault LED US Catalog | Softstarters 3/3 . Each icon indicates a different parameter to set and makes navigation and setting of parameters easy.Suppy available Steady . making it very easy to read after installation.TOR Yellow protection LED Illuminated and language-neutral display with icons The display on PSE uses icons for fast and easy set-up of parameters. Output signal relays for run. with pilot lights or to control a line contactor. pushbuttons or relays.Main available Green run LED Flashing . The relays can be used e. stop and reset PSE is controlled through digital inputs using the internal 24 V DC source.g.
it. 1) Switch fuse The line contactor is not required for the softstarter itself but often used to open if OL trips.PSE – The efficient range Overview 3 Normal start In-line connected (400 V) kW PSE18 PSE25 PSE30 PSE37 PSE45 PSE60 PSE72 PSE85 PSE105 7.5 11 15 18.5 22 30 37 45 55 IEC.com/SOC. 40 ºC J-type fuses for UL coordination 1) Max fuse J-type (85 kA) J-40 J-50 UL circuit breaker 480VAC (65 kA) UL listed circuit breaker T4H250 1) IEC coordination Using MCCB only. 3/4 Softstarters | US Catalog AF52 OS125GD AF65 AF80 AF96 OS250D AF116 . FLA 18 25 28 34 42 60 68 80 104 J-60 J-80 J-100 J-125 J-150 J-175 J-225 170M1569 170M1571 170M1572 170M3819 UL coordination 600 V. 1) Line contactor 1) OS32GD AF26 OS63GD AF30 AF38 This is an example of coordination.abb. max. Semiconductor fuses. 1) Suitable switch fuse for recommended semiconductor fuses. A 18 25 30 37 45 60 72 85 106 (440-480 V) hp 10 15 20 25 30 40 50 60 75 UL. semiconductor 170M1563 170M1564 170M1566 170M1567 170M1568 fuses must be used. 1) 400 V. 40 ºC MCCB (35 kA) XT2N160 MCCB (50 kA) XT2S160 To achieve Type 2 Fuse protection (85 kA). max. For more examples see: applications. Type 1 coordination will be achieved. Bussmann coordination.
40 ºC MCCB (35 kA) XT2N160 T4N320 T5N400 T5N630 T4S320 T5S400 T5S630 MCCB (50 kA) XT2S160 XT4S250 To achieve Type 2 Fuse protection (85kA). US Catalog | Softstarters 3/5 . semiconductor 170M5809 170M5810 170M5812 fuses must be used .abb. A 143 171 210 250 300 370 (440-480 V) hp 100 125 150 200 250 300 UL. FLA 130 169 192 248 302 361 J-450 J-500 UL coordination 600 V. 1) T5H600 400 V. For more examples see: applications. Type 1 coordination will be achieved.PSE – The efficient range Overview 3 Normal start In-line connected (400 V) kW PSE142 PSE170 PSE210 PSE250 PSE300 PSE370 75 90 110 132 160 200 IEC. Semiconductor fuses. Bussmann coordination. max. 40 ºC J-type fuses for UL coordination 1) Max fuse J-type (85 kA) J-300 J-350 J-600 UL circuit breaker 480VAC (65 kA) UL listed circuit breaker T5L400 1) IEC coordination Using MCCB only. 1) Switch fuse The line contactor is not required for the softstarter itself but often used to open if OL trips 1) Line contactor 1) 170M5813 170M6812 OS400D AF140 AF190 AF205 170M6813 OS630D AF265 AF305 AF370 This is an example of coordination.it. max.com/SOC. 1) Suitable switch fuse for recommended semiconductor fuses.
51) (5.5 22 30 40 45 59 75 90 110 kW 7.29) (5.26) (27.90 13. Typical applications: −− Bow thruster −− Centrifugal pump −− Compressor −− Conveyor or belt (short) −− Elevator −− Escalator If more than 10 starts/h.26) (9. PSE105 PSE142 ..20 12...34) (30.5 7.40 2.90 13.600 V Rated control supply voltage Us.40 2.29) (5. 208..64) ..com/low-voltage/products/softstarters Rated operational voltage Ue. PSE370 Pe Pe Pe UL/CSA Rated operational current power 200 / 220 / 440 / 208 V 240 V 480 V Ie Pe Pe Pe kW 4 5.29) (5.20 4.5 7.40 2.5 11 15 18.50 2.90 current 550 / 600 V Pe FLA hp 15 20 25 30 40 50 60 75 100 125 150 200 250 300 350 A 18 25 28 34 42 60 68 80 104 130 169 192 248 302 361 (lb) (5.29) (5.40 13.29) (5. PSE170 For a more precise selection. 3 1SFC132312F0002 PSE18 ... 50/60 Hz 1SFC132310F0002 IEC Rated operational power 230 V 400 V 500 V PSE210 .5 10 10 15 20 25 30 40 50 60 75 100 100 150 hp 10 15 20 25 30 40 50 60 75 100 125 150 200 250 300 Catalog number Global reference code Weight (1 pce) PSE18-600-70 PSE25-600-70 PSE30-600-70 PSE37-600-70 PSE45-600-70 PSE60-600-70 PSE72-600-70 PSE85-600-70 PSE105-600-70 PSE142-600-70 PSE170-600-70 PSE210-600-70 PSE250-600-70 PSE300-600-70 PSE370-600-70 1SFA897101R7000 1SFA897102R7000 1SFA897103R7000 1SFA897104R7000 1SFA897105R7000 1SFA897106R7000 1SFA897107R7000 1SFA897108R7000 1SFA897109R7000 1SFA897110R7000 1SFA897111R7000 1SFA897112R7000 1SFA897113R7000 1SFA897114R7000 1SFA897115R7000 kg 2..250 V AC..5 10 10 20 20 25 30 40 60 60 75 100 125 hp 5 7.5 9 11 15 18.51) (9.5 22 30 37 45 55 75 90 110 132 160 200 kW 11 15 18.5 22 30 37 45 55 75 90 110 132 160 200 250 A 18 25 30 37 45 60 72 85 106 143 171 210 250 300 370 3/6 Softstarters | US Catalog hp 5 7. class 10.51) (5..PSE – The efficient range Normal starts. use the online softstarter selection tool available by scanning the shown QR code or using the selection tool available at: new.50 4.40 2.64) (30. ordering details Description 1SFC132311F0001 Selection table for normal start. in-line.abb.29) (5. 100.50 2. select one size larger than the standard selection.64) (30.40 2.40 2.
29) (5.51) (5.5 7..26) (9.34) (30.90 current 550 / 600 V Pe FLA hp 10 15 20 25 30 40 50 60 75 100 125 150 200 250 300 A 11 18 25 28 34 42 60 68 80 104 130 169 192 248 302 (lb) (5.40 2. 100. PSE370 3 Pe Pe Pe UL/CSA Rated operational current power 200 / 220 / 440 / 208 V 240 V 480 V Ie Pe Pe Pe kW 3 4 5..90 13..51) (9..5 10 15 20 25 30 40 50 60 75 100 125 150 200 250 Catalog number Global reference code Weight (1 pce) PSE18-600-70 PSE25-600-70 PSE30-600-70 PSE37-600-70 PSE45-600-70 PSE60-600-70 PSE72-600-70 PSE85-600-70 PSE105-600-70 PSE142-600-70 PSE170-600-70 PSE210-600-70 PSE250-600-70 PSE300-600-70 PSE370-600-70 1SFA897101R7000 1SFA897102R7000 1SFA897103R7000 1SFA897104R7000 1SFA897105R7000 1SFA897106R7000 1SFA897107R7000 1SFA897108R7000 1SFA897109R7000 1SFA897110R7000 1SFA897111R7000 1SFA897112R7000 1SFA897113R7000 1SFA897114R7000 1SFA897115R7000 kg 2. Typical applications: – Centrifugal fan – Conveyor belt (long) – Crusher – Mill – Mixer – Stirrer If more than 10 starts/h.29) (5.600 V PSE142 .29) (5. ordering details Heavy duty Description 1SFC132311F0001 Selection table for heavy-duty start..5 22 30 40 45 59 75 90 kW 5.5 10 10 15 20 25 30 40 50 60 75 100 100 hp 7..20 12.20 4.abb.5 11 15 18.90 13.5 7.64) (30.5 22 30 37 45 55 75 90 110 132 160 kW 7. PSE170 Rated control supply voltage Us.40 2. PSE105 For a more precise selection. 1SFC132312F0002 PSE18 .com/low-voltage/products/softstarters Rated operational voltage Ue.50 2.26) (27. in-line.5 10 10 20 20 25 30 40 60 60 75 100 hp 3 5 7. 50/60 Hz 1SFC132310F0002 IEC Rated operational power 230 V 400 V 500 V PSE210 .29) (5.5 11 15 18.40 2.50 2.250 V AC.. use the online softstarter selection tool available by scanning the shown QR code or using the selection tool available at: new..29) (5.64) US Catalog | Softstarters 3/7 .40 2.51) (5.PSE – The efficient range Heavy-duty starts. select one size larger than the standard selection.50 4.5 9 11 15 18.40 13. 208...64) (30.29) (5.40 2.40 2.5 7.5 22 30 37 45 55 75 90 110 132 160 200 A 12 18 25 30 37 45 60 72 85 106 143 171 210 250 300 hp 3 5 7. class 30.
Below find a curve for each tripping class in cold state. 5 6 7 8 Current (x Ie) 1SFC132134F0201 10 US Catalog | Softstarters 3/9 .PSE – The efficient range Technical data Tripping curves for the integrated electronic overload protection PSE has an integrated electronic overload protection that can be set to four different tripping classes. 3 Time (s) 10 000 1000 100 Class 30 Class 20 Class 10 Class 10 A 1 0 0 1 2 3 4 Tripping curves for electronic overload protection (cold) for PSE and PSTX.
30. 50/60 Hz ±5 % Rated control circuit voltage Uc Internal 24 V DC Starting capacity at Ie 4 x Ie for 10 sec. 4) A common voltage needs to be used for all 3 signal relays. If other data is required. 10...+158 F) 4000 m (13123 ft) 3) IP00 IP20 Yes Yes 4 7-segments and icons. Above 40 ºC (104 ºF) up to max..20 mA I Amp Fixed at 1.30 sec 30. the following formula. 60 ºC (140 ºF) reduce the rated current with 0.+158 F) IP66 Valid for 50% on time and 50% off time. de-rate the rated current using [ % of Ie = 100 ..x .30 sec 0.. reset of faults) Green flashing / steady Green flashing / steady Yellow Red Yes (Class 10A.2 x Ie 3 (start..+60 ºC (-13.+140 F) -40..600 V +10%/-15% Rated control supply voltage Us 100.100% 3 Run signal TOR (bypass) signal Event signal 250 V AC/24 V DC 4) 3A 1. 30) Yes Yes Yes (option) LCD type Ambient temperature Maximum altitude Degree of protection Main circuit HMI for settings Main settings Signal relays Analog output Control circuit Signal indication LED Protections Fieldbus connection External keypad Overload class During operation During storage Main circuit Supply and control circuit Built-in bypass Cooling system — fan cooled (thermostat controlled) Display Keypad Setting current Ramp time during start Ramp time during stop Initial/end voltage Current limit Torque control for start Torque control for stop Kick start Number of signal relays K2 K3 K1 Rated operational voltage Ue Rated thermal current Ith Rated operational current Ie at AC-15 (Ue = 250 V) Output signal reference Type of output signal Scaling Number of inputs On / Ready Run / TOR Protection Fault Electronic overload Locked rotor protection Underload protection Connection for ABB FieldBusPlug Display Ambient temperature During operation During storage Degree of protection -25.+140 F) 2) -40…+70 °C (-40. contact your local ABB office....+70 ºC (-40. 3) When used at high altitudes.5 A 4..7 x Ie Yes / No Yes / No Off. above 1000 meters (3281 ft) up to 4000 meters (13123 ft).70% 1. [ % of Ie = 100 . Number of starts per hour Overload capability 10 1) 10 -25…+60 °C (-13... PSE370 Rated insulation voltage Ui 600 V Rated operational voltage Ue 208....PSE – The efficient range Technical data 3 Softstarter type PSE18 .... contact your local ABB office..5.33% per ºF).6% per ºC (0... Illuminated 2 selection keys and 2 navigation keys Size dependent 1.. 1) 2) 3/10 Softstarters | US Catalog ...3280 ] y = actual altitude of the softstarter in feet.y .... stop.. 20..1000 ] x = actual altitude of the softstarter in meters. 480 150 For derating of voltage.250 V +10%/-15%.
37.402 in) 28 Nm (248 in lb) 6..Stranded 1 x mm2 Cu cable ..5.2 Clamp type Tightening torque Cu cable .4.5..1 4.0.0.0 7.6 8.0 11.2/0 6..0 18.5…70 mm2 Included 8 Nm 2.9 16/19...75…2..1.Stranded 1 x mm2 Clamp type Tightening torque ø L Lugs Width Diameter>= Tightening torque 2.106.5 mm2 (19.. DIN43 620 (Knife) A 40 50 80 100 125 160 250 315 400 450 500 630 700 800 900 Type 170M1563 170M1564 170M1566 170M1567 170M1568 170M1569 170M1571 170M1572 170M3819 170M5809 170M5810 170M5812 170M5813 170M6812 170M6813 Size 000 000 000 000 000 000 000 000 1* 2 2 2 2 3 3 Power requirements supply circuit Holding (VA) / Pull-in (VA) 16/19.5 Nm (4.72.3..210.945 in) 8..4 0..Flexible 2 x mm2 Clamp type Tightening torque Cu cable ...2 2.0 21..5 18.5 Cu cable .5 mm (0.5…70 mm2 Included 8 Nm 2.0..143.30.300 kcmil 4.18... US Catalog | Softstarters 3/11 3 .2 mm (0..0 1) Max power loss at rated Ie W 0.181 in) 10.75…1.256 in) 9 Nm (80 in lb) 6…120 mm2 1SDA066917R1 14 Nm 50…120 mm2 1SFN074709R1000 16 NM 6…120 mm2 1SDA066917R1 14 Nm 50…120 mm2 1SFN074709R1000 16 NM 95…185 mm2 1SDA054988R1 31 Nm 24 mm (0.85..400 kcmil Included 71 in lb ATK185 300 in lb ATK300 375 in lb - - 4...335 in) 18 Nm (159 in lb) 16…300 mm2 1SDA055016R1 25 Nm 16…300 mm2 1SDA055016R1 25 Nm 185…240 1SDA055020R1 43 Nm 30 mm (1.0 111.0 90.0 13.9 16/19.0 31..6.PSE – The efficient range Technical data Main terminals PSE18 … PSE105 PSE142 … PSE170 PSE210 … PSE370 17.9 16/19.Flexible 1 x mm2 Clamp type Tightening torque Cu cable .5 20 5 E1859D E1858D 5 ø 8.9 16/31 16/31 30/700 30/700 30/700 30/700 For the supply circuit 6 A delayed..5 0.5.0 51.0 75.9 16/19.9 16/19.9.4 in lb) Fuse ratings and power losses For softstarter Current range Type PSE18 PSE25 PSE30 PSE37 PSE45 PSE60 PSE72 PSE85 PSE105 PSE142 PSE170 PSE210 PSE250 PSE300 PSE370 A 5.250.1 17.0 42.5…70 mm2 Included 8 Nm 2.3 6.866 in) 6. for MCB use C characteristics.0 9..6 12.500 kcmil - - ATK300/2 375 in lb Connection capacity acc to UL / CSA 1 x AWG / kcmil Clamp type Tightening torque Connection capacity acc to UL / CSA 2 x AWG / kcmil Supply and control circuit ø 10.5 mm (0.2 0.60.25.8 1..5 mm2 (19.171.0..370.9 16/19..0 27.6....main circuit 1) Bussmann fuses.4 Max fuse rating .Stranded 2 x mm2 Clamp type Tightening torque Al cable .8..9 16/19.14 AWG) 0.8 12.5…70 mm2 Included 8 Nm 22 mm (0.Stranded 1 x mm2 Clamp type Tightening torque Cu cable .0 63.302.16 AWG) 0.....9 16/19...45...0..Stranded 2 x mm2 Tightening torque 0...2 3.0 25.
54") 3 mm (0.51") 19.54") 78 mm (3.12") 1. 28 mm (1 Ø Max.3m m (0 .75") 190 mm (7.70") 278 mm (10.19") mm (0 x4 .46") 26 mm (1.PSE170 13 mm (0.PSE370 125.75 mm 43.75 mm (1.11.5 mm (8. 35 mm (1.2 mm (0.5 mm (7.5 mm (0.38") 470 mm (18.9") 1SFC132266F0001 30 mm (1.57") 6.51") 24 mm (0.5 mm (4.05") 37 mm (1.67") 6.24") 35 mm (1.92") 5 mm (0..94") 245 mm (9.6 mm (0.06") 39 mm (1.24") 9.5 mm (6.62") 5 mm (0.5 mm (0.24") 30 mm (1.54") 3 mm (0.6 lb.35") 130 mm (5.42") PSE external keypad (PSEEK) m (0 .02") mm (1 .12") 183.46") Max .48") 17.5 mm (0.12") 236.PSE – The efficient range Dimensions PSE210.20") PSE142.2 Nm .53") 106 mm (4.4 mm (1.50") 295 mm (11.5 mm (4.69") 163.27") 6 mm (0.65") 7 mm (0.5 mm (4.53") Ø4..12") 90 mm (3.29") 90 mm (3.24") 6.94") 888 mm (3.18") 35 mm (1.18") 3 mm (0.5 mm (0.15") 43.38") 13 m 115 mm (4.20") 3 219.46") 40 mm (1.69") (1.02") 27.38") 113.20") 109.64") 230 mm (9.17") 115 mm (4.12") 1SFC132259F0001 1SFC132260F0001 221 mm (8.5 mm (9.07") 88 mm (3.10") Ø26 Min..." 3/12 Softstarters | US Catalog .45") 80 mm (3.61") 532 mm (20.8 T20 550 mm (21.29") PSE18…PSE105 .
rev. rev.abb.. US Catalog | Softstarters 3/13 .2 1L1 11 Start 2T1 4T2 6T3 U V W M 3~ 3 9 10 Run TOR 4 5 11 12 13 14 Fault NC NO 6 7 1SFC132237F0001..PSE – The efficient range Circuit diagrams PSE18.com/low-voltage/products/softstarters.3 L For more circuit diagrams see new.PSE370 With MCCB and line contactor	With fuses and line contactor L1 L1 L2 L2 L3 L3 N N MCCB 3 L N Start N Start Stop 8 9 Stop 9 8 11 Start KM1 Stop 3L2 2T1 4T2 U V 5L3 6T3 1 2 8 3 9 10 Run TOR 4 5 11 12 13 Stop 1L1 14 3L2 5L3 1 2 8 Fault NC NO 6 7 W M 3~ 1SFC132274F0001.
4 Softstarters | US Catalog .
The advanced range Introduction 4/2 Overview 4/4 Ordering details 4/6 Accessories 4/10 Technical data 4/11 Dimensions 4/16 Circuit diagrams 4/18 US Catalog | Softstarters 4/1 4 .PSTX – The advanced range PSTX .
12) −− Graphical display with 16 languages for easy setup and operation − − Built-in bypass for energy saving and easy installation − − Built-in Modbus RTU for monitoring andcontrol −− Support for all major communication protocols − − Analog output for measurement of current. 50/60 Hz −− PSTX rated operational current: 30.g. Three types of current limit PSTX offers three types of current limit: standard. Complete motor protection The PSTX offers complete motor protection in only one unit and is able to handle both load and network irregularities.250 V.690 V AC −− Wide rated control supply voltage: 100. It also allows you to use your motor in weaker networks.1250 A (inside-delta: 2160 A) −− Both in-line and inside-delta connection −− Coated circuit boards protecting from dust. It is our latest advancement in motor control and protection and adds new functionality and increased reliability.. The PSTX provides positioning capabilities. This saves energy while reducing the softstarter’s heat generation. 4 Secure motor Reliability Improve installation Efficiency Increase application Productivity 4/2 Softstarters | US Catalog −− Three-phase controlled −− Operational voltage: 208. power factor etc. The detachable keypad is standard on all PSTX softstarters.PSTX – The advanced range Introduction The PSTX combines many years of research and product development with extensive knowledge of application-specific requirements and needs. voltage. securing uptime of your pump system. moisture and corrosive atmosphere −− Detachable keypad rated IP66 (Type 1. 4X. Easy-to-use and detachable keypad A user-friendly and clear display saves you time and resources during both setup and operation. saving you time during installation and providing space in your panel. earth fault protection and over/under voltage protection along with many other functions keep your motor safer than ever. letting you take control of your process. The PSTX features many application enhancing features. .. Jog with slow speed The slow speed forward and backward jog feature will give you more flexibility when operating e. dual and ramp. including torque control: the most efficient way to start and stop pumps. Built-in bypass saves time and energy When reaching full speed. Complete control of pumps It’s time to use your processes to their full potential. the PSTX will activate its bypass.... conveyor belts and cranes. PT-100. This gives you full control of your motor during start. The pump cleaning feature can reverse pump flow and clean out pipes. With the PSTX.. the bypass is built-in and verified by ABB.
The interface resembles other interfaces from ABB that streamline and help with training of field personnel. which means you can save money by reducing the need for added cooling equipment. you do not need a manual to handle control circuit connections. A compact motor starting solution When your application reaches full speed. a bypass will reduce the softstarter’s energy consumption. It can be placed on your panel door. Customizable The PSTX has 17 pre-installed languages along with options to customize your own specific home screens (up to seven unique screens). saving you valuable time during the installation. meaning you do not have to interrupt your process in order to read status information or to change settings. Clear markings on the front With the PSTX. Detachable The PSTX comes with a detachable keypad as standard. With the self-explanatory markings on the front you can verify that the connections are done right. You can use your customized home screens to show status information important to your process – and hide information that is not. US Catalog | Softstarters 4/3 4 . With the PSTX.PSTX – The advanced range Introduction Keyhole mounting for quick installation The PSTX is simple and quick to install using keyhole mounting. And with basic data on the front. Easy to learn A large graphical display along with built-in assistants make learning how to handle the PSTX fun and simple. the bypass is built-in and verified by ABB. It also reduces heat generation. identification is simple without having to take the product down.
1) Switch fuse MCCB (50 kA) XT2S160 170M1567 170M1568 OS32GD Line contactor The line contactor is not required for the softstarter itself but often used to open AF30 AF38 if OL trips. 1) Fuse protection (80 kA). Type 1 coordination will be achieved. To achieve Type 2 coordination. 40 ºC Using gG fuses. Semiconductor fuses. A (440-480 V) hp UL. Bussmann Suitable switch fuse for the recommended semiconductor fuses. semiconductor fuses must be used. 40 ºC J-type fuses for UL coordination 1) Max fuse J-type (100 kA) J-90 J-125 J-150 J-175 J-225 J-250 J-250 J-60 J-70 UL circuit breaker 480VAC (65 kA) UL listed circuit breaker T4H100 1) T4H150 IEC coordination Using manual motor starter or MCCB. For more examples see: applications.5 37 25 34 22 45 30 42 30 60 40 60 37 72 50 68 45 85 60 80 55 106 75 104 75 143 100 130 90 171 125 169 UL coordination 600 V. 1) 1) 170M1569 AF52 XT4S250 170M1571 OS63GD 170M1572 OS125GD AF65 This is an example of short circuit coordination. 1) 400 V. A PSTX30 PSTX37 PSTX45 PSTX60 PSTX72 PSTX85 PSTX105 PSTX142 PSTX170 15 30 20 28 18. Max.it. 4/4 Softstarters | US Catalog T4H250 AF80 AF96 170M3819 170M5810 OS250D AF116 170M5812 OS400D AF140 AF190 .com/SOC. Type 1 coordination will be achieved.PSTX – The advanced range Overview 4 Normal start In-Line connected (400 V) kW IEC.abb. Max.
For more examples see: applications. Semiconductor fuses. semiconductor fuses must be used.it. Bussmann Suitable switch fuse for the recommended semiconductor fuses.PSTX – The advanced range Overview Normal start In-Line connected (400 V) kW IEC. Type 1 coordination will be achieved. 1) Fuse protection (80 kA).2N 2000 UL circuit breaker 480VAC (65 kA) UL listed circuit breaker 1) T5H300 T5H400 T5H600 IEC coordination Using manual motor starter or MCCB. 40 ºC Using gG fuses. 1) Switch fuse The line contactor is not required for the softstarter itself but often used to open if OL trips. To achieve Type 2 coordination. 1) Line contactor 1) MCCB (50 kA) T4S320 T5S400 170M5812 170M5813 170M6812 T5S630 170M6813 OS400D AF205 AF265 170M6813 170M6814 OS630D AF305 AF370 AF460 170M8554 170M6018 OS800D AF580 AF750 170M6020 170M6021 - AF1350 AF1650 - This is an example of short circuit coordination. 1) 400 V.com/SOC. A (440-480 V) hp UL. US Catalog | Softstarters 4/5 4 . Max. Max.abb. Type 1 coordination will be achieved. 40 ºC J-type fuses for UL coordination 1) Max fuse J-type (100 kA) J-400 J-500 J-600 L-1200 L-1600 L-2500 T7H1200 T8VH3000 - T7S800 T7S1250 E2. A PSTX210 PSTX250 PSTX300 PSTX370 PSTX470 PSTX570 PSTX720 PSTX840 PSTX1050 PSTX1250 110 210 150 192 132 250 200 248 160 300 250 302 200 370 300 361 250 470 400 480 315 570 500 590 400 720 600 720 450 840 700 840 560 1050 900 1062 710 1250 1000 1250 UL coordination 600 V.
85) (101.45) (13.10 9. 100..99) (55. in-line.70 12..10 9.... PSTX1250 4/6 Softstarters | US Catalog Rated operational voltage Ue.10 6.. 50/60 Hz 15 18.. PSTX840 1SFC132101V0001 4 1SFC132053V0001 PSTX30 .PSTX – The advanced range Normal starts.250 V AC.20 64.5 10 20 25 28 18.12) (55. Typical applications: −− Bow thruster −− Centrifugal pump −− Compressor −− Conveyor belt (short) −− Elevator For a more precise selection.5 10 20 25 28 18.54) (142.690 V Rated control supply voltage Us.99) (55.70 12.60 9. use the online softstarter selection tool available by scanning the shown QR code or using the selection tool available at: new.10 6.20 64.16) (27.10 6.85) (141..16) (27.10 6.64) .00 25..70 12.10 6.5 25 30 7. ordering details 1SFC132038V0001 Description Selection table for normal start. class 10.85) (141. PSTX170 1SFC132058V0001 1SFC132098V0001 PSTX210 ..54) (142.45) (13.00 46.45) (13. 50/60 Hz IEC UL/CSA Rated operational Rated operational power current power current 400 V 500 V 690 V 200 / 220 / 440 / 550 / 208 V 240 V 480 V 600 V Pe Pe Pe Ie Pe Pe Pe Pe FLA kW kW kW A hp hp hp hp A 15 18.99) (27. PSTX370 1SFC132103V0001 PSTX470 . PSTX105 PSTX1050 ..99) (27.16) (21.00 25.10 6. 100.99) (27.5 30 7.10 6. PSTX570 PSTX720 .10 6.250 V AC.60 9.70 12.16) (21..99) (27.600 V Rated control supply voltage Us..abb.5 22 30 37 10 10 25 30 34 22 25 37 45 10 15 30 40 42 30 37 55 60 20 20 40 50 60 37 45 59 72 20 25 50 60 68 45 55 75 85 25 30 60 75 80 55 75 90 106 30 40 75 100 104 75 90 132 143 40 50 100 125 130 90 110 160 171 50 60 125 150 169 110 132 184 210 60 75 150 200 192 132 160 220 250 75 100 200 250 248 160 200 257 300 100 100 250 300 302 200 257 355 370 125 150 300 350 361 250 315 450 470 150 200 400 500 480 315 400 560 570 200 200 500 600 590 400 500 710 720 250 300 600 700 720 450 600 800 840 300 350 700 800 840 560 730 1000 1050 400 450 900 1000 1062 710 880 1200 1250 400 500 1000 1200 1250 PSTX30-690-70 PSTX37-690-70 PSTX45-690-70 PSTX60-690-70 PSTX72-690-70 PSTX85-690-70 PSTX105-690-70 PSTX142-690-70 PSTX170-690-70 PSTX210-690-70 PSTX250-690-70 PSTX300-690-70 PSTX370-690-70 PSTX470-690-70 PSTX570-690-70 PSTX720-690-70 PSTX840-690-70 PSTX1050-690-70 PSTX1250-690-70 1SFA898203R7000 1SFA898204R7000 1SFA898205R7000 1SFA898206R7000 1SFA898207R7000 1SFA898208R7000 1SFA898209R7000 1SFA898210R7000 1SFA898211R7000 1SFA898212R7000 1SFA898213R7000 1SFA898214R7000 1SFA898215R7000 1SFA898216R7000 1SFA898217R7000 1SFA898218R7000 1SFA898219R7000 1SFA898220R7000 1SFA898221R7000 6.45) (13.45) (13.12) (101.64) Rated operational voltage Ue.12) (55.45) (13.70 25.70 25.. 208.60 12.10 6.70 (13..70 12..20 64.com/low-voltage/products/softstarters PSTX142 .20 46.45) (13..10 6. 208.99) (27.70 (lb) (13.45) (13.10 6...20 46.45) (13.45) (13.20 64.45) (21.10 6.12) (101.00 46.85) (101.45) (21.70 12.99) (27.45) (13.45) (13..5 22 37 10 10 25 30 34 22 25 45 10 15 30 40 42 30 37 60 20 20 40 50 60 37 45 72 20 25 50 60 68 45 55 85 25 30 60 75 80 55 75 106 30 40 75 100 104 75 90 143 40 50 100 125 130 90 110 171 50 60 125 150 169 110 132 210 60 75 150 200 192 132 160 250 75 100 200 250 248 160 200 300 100 100 250 300 302 200 257 370 125 150 300 350 361 250 315 470 150 200 400 500 480 315 400 570 200 200 500 600 590 400 500 720 250 300 600 700 720 450 600 840 300 350 700 800 840 560 730 1050 400 450 900 1000 1062 710 880 1200 400 500 1000 1200 1250 Catalog number Global reference code Weight (1 pce) PSTX30-600-70 PSTX37-600-70 PSTX45-600-70 PSTX60-600-70 PSTX72-600-70 PSTX85-600-70 PSTX105-600-70 PSTX142-600-70 PSTX170-600-70 PSTX210-600-70 PSTX250-600-70 PSTX300-600-70 PSTX370-600-70 PSTX470-600-70 PSTX570-600-70 PSTX720-600-70 PSTX840-600-70 PSTX1050-600-70 PSTX1250-600-70 1SFA898103R7000 1SFA898104R7000 1SFA898105R7000 1SFA898106R7000 1SFA898107R7000 1SFA898108R7000 1SFA898109R7000 1SFA898110R7000 1SFA898111R7000 1SFA898112R7000 1SFA898113R7000 1SFA898114R7000 1SFA898115R7000 1SFA898116R7000 1SFA898117R7000 1SFA898118R7000 1SFA898119R7000 1SFA898120R7000 1SFC898121R7000 kg 6.60 12.
100.70 12.60 12.45) (13.99) (55.70 12.60 9.10 6.250 V AC...5 15 20 25 15 18.10 6.99) (27.10 6.00 46.64) PSTX30-690-70 PSTX37-690-70 PSTX45-690-70 PSTX60-690-70 PSTX72-690-70 PSTX85-690-70 PSTX105-690-70 PSTX142-690-70 PSTX170-690-70 PSTX210-690-70 PSTX250-690-70 PSTX300-690-70 PSTX370-690-70 PSTX470-690-70 PSTX570-690-70 PSTX720-690-70 PSTX840-690-70 PSTX1050-690-70 PSTX1250-690-70 1SFA898203R7000 1SFA898204R7000 1SFA898205R7000 1SFA898206R7000 1SFA898207R7000 1SFA898208R7000 1SFA898209R7000 1SFA898210R7000 1SFA898211R7000 1SFA898212R7000 1SFA898213R7000 1SFA898214R7000 1SFA898215R7000 1SFA898216R7000 1SFA898217R7000 1SFA898218R7000 1SFA898219R7000 1SFA898220R7000 1SFA898221R7000 6.16) (27.99) (27.45) (13..5 15 20 25 15 18...70 (lb) (13.85) (141..45) (13.54) (142.99) (27....PSTX – The advanced range Heavy-duty.10 6.5 22 5 7.690 V Rated control supply voltage Us. ordering details Heavy duty 1SFC132038V0001 Description Selection table for heavy-duty start..10 6.10 9. PSTX170 1SFC132098V0001 PSTX210 ..45) (13. PSTX105 4 For a more precise selection..com/low-voltage/products/softstarters 1SFC132058V0001 PSTX142 . 208.70 25.5 30 7.10 6.. Typical applications: – Centrifugal fan – Conveyor belt (long) – Crusher – Mill – Mixer – Stirrer 1SFC132053V0001 PSTX30 ..99) (27. 50/60 Hz IEC UL/CSA Rated operational Rated operational power current power current 400 V 500 V 690 V 200 / 220 / 440 / 550 / 208 V 240 V 480 V 600 V Pe Pe Pe Ie Pe Pe Pe Pe FLA kW kW kW A hp hp hp hp A 11 15 22 5 7. PSTX840 PSTX1050 .20 46.5 25 30 7. PSTX370 1SFC132103V0001 PSTX470 .16) (21.12) (55.5 10 20 25 28 18.600 V Rated control supply voltage Us.45) (13.10 9.64) US Catalog | Softstarters 4/7 .85) (101.45) (21.45) (13..20 64. 208..12) (55.16) (27.16) (21.5 22 37 10 10 25 30 34 22 25 45 10 15 30 40 42 30 37 60 20 20 40 50 60 37 45 72 20 25 50 60 68 45 55 85 25 30 60 75 80 55 75 106 30 40 75 100 104 75 90 143 40 50 100 125 130 90 110 171 50 60 125 150 169 110 132 210 60 75 150 200 192 132 160 250 75 100 200 250 248 160 200 300 100 100 250 300 302 200 257 370 125 150 300 350 361 250 315 470 150 200 400 500 480 315 400 570 200 200 500 600 590 400 500 720 250 300 600 700 720 450 600 840 300 350 700 800 840 560 730 1050 400 450 900 1000 1062 Rated operational voltage Ue. class 30.99) (27.45) (13. in-line.5 10 20 25 28 18.70 12.60 9..45) (13. PSTX1250 Rated operational voltage Ue.00 46.54) (142.abb.45) (13.70 12.45) (13.70 25.10 6..20 64.12) (101.10 6.12) (101.85) (141.45) (13.250 V AC.70 12.20 64. 100..20 64.10 6. use the online softstarter selection tool available by scanning the shown QR code or using the selection tool available at: new. 50/60 Hz 11 15 18.00 25.. PSTX570 1SFC132101V0001 PSTX720 .99) (55.99) (27.20 46.45) (21.70 12.5 22 30 37 10 10 25 30 34 22 25 37 44 10 15 30 40 42 30 37 55 60 20 20 40 50 60 37 45 59 72 20 25 50 60 68 45 55 75 85 25 30 60 75 80 55 75 90 106 30 40 75 100 104 75 90 132 143 40 50 100 125 130 90 110 160 171 50 60 125 150 169 110 132 184 210 60 75 150 200 192 132 160 220 250 75 100 200 250 248 160 200 257 300 100 100 250 300 302 200 257 355 370 125 150 300 350 361 250 315 450 470 150 200 400 500 480 315 400 560 570 200 200 500 600 590 400 500 710 720 250 300 600 700 720 450 600 800 840 300 350 700 800 840 560 730 1000 1050 400 450 900 1000 1062 Catalog number Global reference code Weight (1 pce) PSTX30-600-70 PSTX37-600-70 PSTX45-600-70 PSTX60-600-70 PSTX72-600-70 PSTX85-600-70 PSTX105-600-70 PSTX142-600-70 PSTX170-600-70 PSTX210-600-70 PSTX250-600-70 PSTX300-600-70 PSTX370-600-70 PSTX470-600-70 PSTX570-600-70 PSTX720-600-70 PSTX840-600-70 PSTX1050-600-70 PSTX1250-600-70 1SFA898103R7000 1SFA898104R7000 1SFA898105R7000 1SFA898106R7000 1SFA898107R7000 1SFA898108R7000 1SFA898109R7000 1SFA898110R7000 1SFA898111R7000 1SFA898112R7000 1SFA898113R7000 1SFA898114R7000 1SFA898115R7000 1SFA898116R7000 1SFA898117R7000 1SFA898118R7000 1SFA898119R7000 1SFA898120R7000 1SFA898121R7000 kg 6.60 12.45) (13.10 6.10 6.10 6.85) (101.00 25.70 (13.
99) (27.10 6.10 9.45) (21.45) (13..10 6.00 46.600 V 1SFC132058V0001 1SFC132098V0001 PSTX210 .20 46.99) (55.54) (142.10 6.70 12.10 6.10 9.00 25.60 9.70 25.99) (27. 100..60 12.45) (13.99) (27..20 64.12) (101.45) (21. ordering details 1SFC132038V0001 Description Selection table for normal start.85) (141.. Typical applications: −− Bow thruster −− Centrifugal pump −− Compressor −− Conveyor belt (short) −− Elevator For a more precise selection.85) (101.16) (27..70 12. class 10. 50/60 Hz 25 30 45 52 10 15 30 40 48 30 37 55 64 15 20 40 50 58 37 45 59 76 20 25 50 60 72 55 75 90 105 30 40 75 100 103 59 80 110 124 30 40 75 100 117 75 90 132 147 40 50 100 125 138 90 110 160 181 60 60 150 150 180 132 160 220 245 75 75 150 200 225 160 200 257 300 75 100 200 250 292 184 250 315 360 100 125 250 300 332 220 295 400 430 150 150 350 450 429 257 355 500 515 150 200 450 500 523 355 450 600 640 200 250 500 600 625 450 600 800 814 250 300 600 700 720 540 700 960 987 300 350 700 800 840 710 880 1200 1247 400 500 1000 1200 1247 800 1000 1400 1455 500 600 1200 1500 1454 1000 1250 1700 1810 600 700 1500 1800 1839 1200 1500 2000 2160 800 900 1800 2000 2160 PSTX30-690-70 PSTX37-690-70 PSTX45-690-70 PSTX60-690-70 PSTX72-690-70 PSTX85-690-70 PSTX105-690-70 PSTX142-690-70 PSTX170-690-70 PSTX210-690-70 PSTX250-690-70 PSTX300-690-70 PSTX370-690-70 PSTX470-690-70 PSTX570-690-70 PSTX720-690-70 PSTX840-690-70 PSTX1050-690-70 PSTX1250-690-70 1SFA898203R7000 1SFA898204R7000 1SFA898205R7000 1SFA898206R7000 1SFA898207R7000 1SFA898208R7000 1SFA898209R7000 1SFA898210R7000 1SFA898211R7000 1SFA898212R7000 1SFA898213R7000 1SFA898214R7000 1SFA898215R7000 1SFA898216R7000 1SFA898217R7000 1SFA898218R7000 1SFA898219R7000 1SFA898220R7000 1SFA898221R7000 6..PSTX – The advanced range Normal starts.10 6..10 6.70 12. 50/60 Hz IEC UL/CSA Rated operational Rated operational power current power current 400 V 500 V 690 V 200 / 220 / 440 / 550 / 208 V 240 V 480 V 600 V Pe Pe Pe Ie Pe Pe Pe Pe FLA kW kW kW A hp hp hp hp A 25 30 52 10 15 30 40 48 30 37 64 15 20 40 50 58 37 45 76 20 25 50 60 72 55 75 105 30 40 75 100 103 59 80 124 30 40 75 100 117 75 90 147 40 50 100 125 138 90 110 181 60 60 150 150 180 132 160 245 75 75 150 200 225 160 200 300 75 100 200 250 292 184 250 360 100 125 250 300 332 220 295 430 150 150 350 450 429 257 355 515 150 200 450 500 523 355 450 640 200 250 500 600 625 450 600 814 250 300 600 700 830 540 700 987 300 350 700 800 1020 710 880 1247 400 500 1000 1200 1240 800 1000 1455 500 600 1200 1500 1450 1000 1250 1810 600 700 1500 1800 1830 1200 1500 2160 800 900 1800 2000 2160 Catalog number Global reference code Weight (1 pce) PSTX30-600-70 PSTX37-600-70 PSTX45-600-70 PSTX60-600-70 PSTX72-600-70 PSTX85-600-70 PSTX105-600-70 PSTX142-600-70 PSTX170-600-70 PSTX210-600-70 PSTX250-600-70 PSTX300-600-70 PSTX370-600-70 PSTX470-600-70 PSTX570-600-70 PSTX720-600-70 PSTX840-600-70 PSTX1050-600-70 PSTX1250-600-70 1SFA898103R7000 1SFA898104R7000 1SFA898105R7000 1SFA898106R7000 1SFA898107R7000 1SFA898108R7000 1SFA898109R7000 1SFA898110R7000 1SFA898111R7000 1SFA898112R7000 1SFA898113R7000 1SFA898114R7000 1SFA898115R7000 1SFA898116R7000 1SFA898117R7000 1SFA898118R7000 1SFA898119R7000 1SFA898120R7000 1SFA898121R1000 kg 6.00 46.690 V Rated control supply voltage Us.. PSTX370 1SFC132103V0001 PSTX470 .10 6. 208.70 12.64) Rated operational voltage Ue.70 (13..250 V AC.85) (101..12) (55.10 6. 100.20 64.00 25...45) (13.16) (21.com/low-voltage/products/softstarters PSTX142 .45) (13.12) (55.70 12.99) (27.16) (21.99) (27.45) (13. 208. PSTX170 Rated operational voltage Ue.45) (13. PSTX105 PSTX1050 .99) (27.45) (13.. use the online softstarter selection tool available by scanning the shown QR code or using the selection tool available at: new. PSTX1250 4/8 Softstarters | US Catalog Rated control supply voltage Us.45) (13.54) (142.10 6.70 (lb) (13.45) (13.. PSTX570 PSTX720 .. inside delta.70 25..64) ..60 9.abb.45) (13...250 V AC.45) (13. PSTX840 1SFC132101V0001 4 1SFC132053V0001 PSTX30 .10 6.45) (13.10 6.20 46.70 12.10 6.60 12.16) (27..99) (55.85) (141.20 64.12) (101.20 64.
54) (142.00 25.10 6.99) (27.10 9.600 V Rated control supply voltage Us. PSTX1250 4 Rated operational voltage Ue.10 6.60 12.45) (13..10 6.64) PSTX30-690-70 PSTX37-690-70 PSTX45-690-70 PSTX60-690-70 PSTX72-690-70 PSTX85-690-70 PSTX105-690-70 PSTX142-690-70 PSTX170-690-70 PSTX210-690-70 PSTX250-690-70 PSTX300-690-70 PSTX370-690-70 PSTX470-690-70 PSTX570-690-70 PSTX720-690-70 PSTX840-690-70 PSTX1050-690-70 PSTX1250-690-70 1SFA898203R7000 1SFA898204R7000 1SFA898205R7000 1SFA898206R7000 1SFA898207R7000 1SFA898208R7000 1SFA898209R7000 1SFA898210R7000 1SFA898211R7000 1SFA898212R7000 1SFA898213R7000 1SFA898214R7000 1SFA898215R7000 1SFA898216R7000 1SFA898217R7000 1SFA898218R7000 1SFA898219R7000 1SFA898220R7000 1SFA898221R7000 6.64) US Catalog | Softstarters 4/9 .45) (13.12) (55.00 25..70 12..690 V Rated control supply voltage Us.10 6.85) (101.PSTX – The advanced range Heavy-duty.10 6.5 10 25 30 34 25 30 52 10 15 30 40 48 30 37 64 15 20 40 50 58 37 45 76 20 25 50 60 72 55 75 105 30 40 75 100 103 59 80 124 30 40 75 100 117 75 90 147 40 50 100 125 138 90 110 181 60 60 150 150 180 132 160 245 75 75 150 200 225 160 200 300 75 100 200 250 292 184 250 360 100 125 250 300 332 220 295 430 150 150 350 450 429 257 355 515 150 200 450 500 523 355 450 640 200 250 500 600 625 450 600 814 250 300 600 700 720 540 700 987 300 350 700 800 840 710 880 1247 400 500 1000 1200 1247 800 1000 1455 500 600 1200 1500 1454 1000 1250 1810 600 700 1500 1800 1830 1SFC132098V0001 PSTX210 ... PSTX105 For a more precise selection.70 12.99) (55.45) (13.85) (141.10 6..10 6.20 46.99) (27.99) (27.5 10 25 30 34 25 30 45 52 10 15 30 40 48 30 37 55 64 15 20 40 50 58 37 45 59 76 20 25 50 60 72 55 75 90 105 30 40 75 100 103 59 80 110 124 30 40 75 100 117 75 90 132 147 40 50 100 125 138 90 110 160 181 60 60 150 150 180 132 160 220 245 75 75 150 200 225 160 200 257 300 75 100 200 250 292 184 250 315 360 100 125 250 300 332 220 295 400 430 150 150 350 450 429 257 355 500 515 150 200 450 500 523 355 450 600 640 200 250 500 600 625 450 600 800 814 250 300 600 700 720 540 700 960 987 300 350 700 800 840 710 880 1200 1247 400 500 1000 1200 1247 800 1000 1400 1455 500 600 1200 1500 1454 1000 1250 1700 1810 600 700 1500 1800 1830 Catalog number Global reference code Weight (1 pce) PSTX30-600-70 PSTX37-600-70 PSTX45-600-70 PSTX60-600-70 PSTX72-600-70 PSTX85-600-70 PSTX105-600-70 PSTX142-600-70 PSTX170-600-70 PSTX210-600-70 PSTX250-600-70 PSTX300-600-70 PSTX370-600-70 PSTX470-600-70 PSTX570-600-70 PSTX720-600-70 PSTX840-600-70 PSTX1050-600-70 PSTX1250-600-70 1SFA898103R7000 1SFA898104R7000 1SFA898105R7000 1SFA898106R7000 1SFA898107R7000 1SFA898108R7000 1SFA898109R7000 1SFA898110R7000 1SFA898111R7000 1SFA898112R7000 1SFA898113R7000 1SFA898114R7000 1SFA898115R7000 1SFA898116R7000 1SFA898117R7000 1SFA898118R7000 1SFA898119R7000 1SFA898120R7000 1SFA898121R7000 kg 6.70 12.70 25.70 12. 100. inside delta.45) (21.85) (101. PSTX170 1SFC132058V0001 Rated operational voltage Ue. 208.60 12.45) (13. PSTX840 PSTX1050 .16) (21. class 30.99) (27.16) (27.85) (141.12) (101.10 9.10 6..20 64.10 6..70 12..5 25 37 42 7. 50/60 Hz IEC UL/CSA Rated operational Rated operational power current power current 400 V 500 V 690 V 200 / 220 / 440 / 550 / 208 V 240 V 480 V 600 V Pe Pe Ie Pe Pe Pe Pe FLA Pe kW kW kW A hp hp hp hp A 18.00 46. use the online softstarter selection tool available by scanning the shown QR code or using the selection tool available at: new. 100.5 25 42 7.60 9..45) (13. PSTX370 1SFC132103V0001 PSTX470 .00 46.45) (13.70 12..45) (13.99) (55..70 25.45) (13.70 (lb) (13.45) (13..12) (101.10 6.20 64.250 V AC.12) (55.16) (21.45) (13. 208..70 (13.99) (27.45) (13.20 64..45) (13...20 46. PSTX570 1SFC132101V0001 PSTX720 .10 6.54) (142.16) (27.60 9..com/low-voltage/products/softstarters PSTX142 .abb.. ordering details Heavy duty 1SFC132038V0001 Description Selection table for heavy-duty start.10 6.45) (21..250 V AC. 50/60 Hz 18. Typical applications: – Centrifugal fan – Conveyor belt (long) – Crusher – Mill – Mixer – Stirrer 1SFC132053V0001 PSTX30 .20 64.99) (27.
short for use with cable clamps PSTX210.850 (5..... Tightening torque max..133 0.243) – – – 1SDA054988R1 1SDA055020R1 1SDA023380R1 Catalog number Global reference code Pkg qty Weight (1 pce) kg (lb) bar mm 8...825 (1..PSTX170 95.31 (2.250 0.240 PSTX470..230 (0..500 MCM PSTX210…PSTX370 (2 per phase) 2/0 .5 10.75) PSLK-300 6 .500 MCM PSTX470…PSTX1050 (2 per phase) 2/0 .. long for use with compression lugs PSTX720....077) 2 LT370-30L 1SFN125403R1000 2 0.102) (1..240) 1SFT98000-012C3 For softstarter type 1SFT98000-011C3 LW.PSTX370 PSTX470.874) 6.350 0..PSTX370.PSTX – The advanced range Accessories For softstarter type 1SFT98099-095C2 mm2 Terminal lug kits for Al and Cu cables #6 .110 (0..110) 2 LT205-30L 2 LT370-30C 1SFN125401R1000 2 0. long for use with compression lugs PSTX210.617) 2 LT370-30D 1SFN125406R1000 2 0. short for use with cable clamps PSTX720.0 1SAJ611000R0101 1 0. 24 V DC digital input PS-FBPA 1SFA896312R1002 1 0.PSTX370..63) PSLK-300/2 6 1..5 10..220 Terminal shrouds PSTX142.331) 2 LT460-AC 1SFN125701R1000 2 0..5 13 15 x 3 17..185 PSTX210.PSTX840 Terminal enlargements PSTX30…PSTX105 PSTX142..79 (1.609) (2..730 1.485) .5 10. -AC LT ....PSTX570 PSTX720.220) 2 LT460-AL 1SFN125703R1000 2 0.992) (1.PSTX170 PSTX210..PSTX840.5 10.150 (0.060 (0. 1SFT98099-125 1SFT98099-019C3 LT .. long for use with compression lugs PSTX210..712) Req..82) PSLK580/2 6 1. ATK300/2 and OZXB4 PSTX470.220 (0..078 0..PSTX1250 I/O module.800 (1.PSTX370. long for use with compression lugs (0.PSTX840.28 (2.PSTX170..050 1SFN124803R1000 2 0.PSTX570 PSTX720....265) 2 LT750-AL 1SFN126103R1000 2 0..172) (0.89) PSLK750/3 6 2.300 MCM PSTX142…PSTX170 (1 per phase) #4 .100 (0.PSTX570..035 (0.77) Terminal extensions PSTX142…PSTX170 PSTX210. -C Catalog number *PSLK contains 2 ...280 (0...100 0.5 (275 lb-in) 43 (375 lb-in) 43 (375 lb-in) 43 (375 lb-in) 43 (375 lb-in) Weight (1 pce) kg (lb) PSLK-185 6 .120 (0. long and deep for use with extending cable clamps. -L Nm 13.5 x 5 20 x 5 25 x 5 40 x 6 LW110 LW205 LW370 LW460 LW750 1SFN074307R1000 1SFN074807R1000 1SFN075407R1000 1SFN075707R1000 1SFN076107R1000 1 1 1 1 1 0. LX.551) (0.5 x 5 20 x 5 25 x 5 40 x 6 LX205 LX370 LX460 LX750 1SFN074810R1000 1SFN075410R1000 1SFN075710R1000 1SFN076110R1003 1 1 1 1 0..16 (4.PSTX370 PSTX470.764) 2 LT750-AC 1SFN126101R1000 2 0..PSTX570 2 x (120. (0.5 10...220) (5..500 0.819) Catalog number Global reference code Pkg qty Weight (1 pce) kg (lb) FieldBusPlug connection accesssory PSTX30..PSTX370 185...ATK kits plus softstarter hardware LZ...551) (0..293) (0.485) For softstarter type 4/10 Softstarters | US Catalog Global reference code Pkg qty Dimensions hole ø mm2 For softstarter type LT .400 MCM PSTX210…PSTX370 (1 per phase) #4 .....PSTX570.500 MCM PSTX720…PSTX1050 (3 per phase) SB8054C2 4 Wire range Cable connectors for Al cables PSTX142. short for use with cable clamps PSTX142.772) (1.250 0.132) PSTX30…PSTX1250 DX111-FBP.74 (1.PSTX840 31 43 31 3 3 3 0. qty Catalog number Global reference code Pkg qty Weight (1 pce) kg (lb) 2 LT205-30C 1SFN124801R1000 2 0.450 0..PSTX170.. -AL LT . short for use with cable clamps PSTX470.5 13 17.
Time (s) 10 000 4 1000 100 Class 30 Class 20 Class 10 Class 10 A 1 0 0 1 2 3 4 Tripping curves for electronic overload protection (cold) for PSE and PSTX. 5 6 7 8 Current (x Ie) 1SFC132134F0201 10 US Catalog | Softstarters 4/11 .PSTX – The advanced range Technical data Tripping curves for the integrated electronic overload protection PSTX has an integrated electronic overload protection that can be set to four different tripping classes. Below you find a curve for each tripping class in cold state.
Thyristor temperature (%). 3) When used at high alitudes. Enable. Motor heating. Italian. 10 for PSTX30.x-3280 ] x = actual altitude of the softstarter in feet.250 V +10% / -15%. Swedish and Turkish Keypad 2 selection keys. Start 1. Main frequency (Hz).600 V.. Reactive power (kVAr).20 mA. PSTX1250 1) Overload class 10 During operation -25.. forward and reverse Yes (3 speed levels) Start reverse (external contactors) Yes Dynamic brake	Yes Fieldbus connection Built-in Modbus RTU Yes Connection for Anybus Yes Connection for ABB FieldBusPlug Yes.. cos phi. Ue 250 V AC/24 V DC Rated thermal current Ith 5A Rated operational current Ie at AC-15 (Ue=250 V) 1. (-40.. 150 497 4/12 Softstarters | US Catalog ..10 V. 50/60Hz ±5% Internal or external 24 V DC 4 x Ie for 10 sec... stop key. Stand still brake. Run.5 A Analog output Output signal reference 0.. above 1000 meters (3281 ft) up to 4000 meters (13123 ft). contact your local ABB office. Sequence 1-3 Run.+158 ºF) Degree of protection IP66 (Type 1.+60 ºC.+60 ºC... 3 different sets of settings Current limit Yes Dual current limit Yes Current limit ramp Yes Torque limit Yes Pre-start function Yes (Motor heating or Stand still brake) Jog with slow speed. Active power (HP). Reset.+70 ºC. Greek.PSTX370 1) 6 for PSTX470 .. 50/60Hz ±5% 100.. Emergency mode (active low)... graphical (Human Machine Interface) Languages Arabic. User defined protection. Emergency mode (active high). Reactive energy (kVArh).. German. Spanish. info key and remote/local key Signal relays Number of programmable signal relays 3 (each relay can be programmed to None. Main voltage (V)... 2) Above 40 ºC (104 º F) up to max. (-13..10 mA. (-40. Indonesian.. graphical Ambient temperature During operation -25. PT100 temperature (centigrade). 60 º C (140 º F) reduce the rated current with 0. Start 2. Slow speed reverse (Jog). Portuguese.+70 ºC. Polish. contact your local ABB office.. Dutch. 208. English.. Chinese. Event group 0-6. Apparant power (kVArh)... Active power (kW). stop) Number of additional programmable inputs 3 (each input can be programmed to: None. For derating of voltage. French.. PTC resistance (Ohm) Control circuit Number of inputs 2 (start. Fieldbus disable control.+158 ºF) Maximum altitude 4000 m (13123 ft) 3) Degree of protection Main circuit Supply and control circuit IP20 Main circuit Built-in bypass contactor Yes Cooling system .PSTX – The advanced range Technical data Softstarter type Rated insulation voltage Ui Rated operational voltage Ue Rated control supply voltage Us Rated control circuit voltage Uc Starting capacity at Ie Number of starts per hour Overload capability Ambient temperature 4 PSTX30.8% per ºC (0.690V +10% / -15%.. 4 navigation keys. Active energy (kWh).. [ % of Ie = 100... 0. Czech. Russian.. Start reverse. Motor temperature (%). Start 3.PSTX1250 690V 208..44% per º F). start key. Finnish.. 0.. (-13.. If other data if required. [% of Ie = 100 ..+140 ºF) 2) During storage -40. Top of ramp.x-1000 ] x = actual altitudes of the softstarter in meter. Switch to remote control or Cancel brake) Signalling indication LED Ready Green Run Green Fault Red Protection Yellow External keypad Detachable keypad Yes Display LCD type. 12) Start and stop functions Soft start with voltage ramp Yes Soft stop with voltage ramp Yes Soft start with torque control Yes Soft stop with torque control Yes Kick start Yes Full voltage start Yes Sequence start Yes.fan cooled Yes (thermostat controlled) HMI for settings Display LCD type. Slow speed forward (Jog).. derate the rated current using the following formula. 4. Sequence 1-3 Top of ramp or Run reverse) K4 Default as Run signal K5 Default as Top of Ramp (Bypass) signal K6 Default as Event group 0 (Faults) Rated operational voltage.+140 ºF) During storage -40.20 mA Type of output signal Motor current (A). 4X. with adapter 1) Valid for normal start (class 10) for 50% on time and 50% off time. Motor voltage (%)..
US Catalog | Softstarters 4/13 . 20. 10.com/low-voltage/products/softstarters.g..PSTX – The advanced range Technical data Softstarter type Protections Warnings External faults detection Internal faults detection PTC input Other functions Electronic overload protection.PSTX1250 Yes (Class 10A. 1SFC132081M0201 available at new. EOL Dual overload (separate overload for start and run) PTC connection PT-100 connection Locked rotor protection Current underload protection Current imbalance protection Power factor underload protection Under voltage protection Over voltage protection Voltage imbalance protection Earth fault protection / ground fault protection Phase reversal protection 24 V output protection Frequency range protection Bypass open protection User defined protection Too long current limit protection HMI failure protection Fieldbus failure protection Extension IO failure protection Max number of starts/hour Too long start time protection Current underload warning Current imbalance warning Voltage imbalance warning Thyristor overload warning (SCR) Electronic overload time-to-trip Short circuit warning (for Limp mode) Over voltage warning Under voltage warning Power factor underload warning Locked rotor warning Faulty fan warning THD(U) — Total Harmonic Distortion warning Motor runtime limit warning Phase loss warning (for stand by) EOL warning Phase loss Hight current Low control supply voltage Faulty usage (e.. 30) Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes 2825 ohm ± 20% 1200 ohm ± 20% Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes Yes 4 For all functions and features see installation and commissioning manual.abb. using limp mode inside-delta)	Faulty connection Bad network quality Thyristor overload Short circuit Open circuit thyristor or gate Heat sink over temperature Shunt fault Switch off resistance Switch on resistance Real time clock Event log Emergency mode Automatic restart Secure settings Keypad password Electronic overload time-to-cool Thyristor runtime measurement Auto phase sequence detection Electricity metering Motor heating Stand still brake Voltage sags detection Limp mode with two-phase motor control if one set of thyristors is shorted PSTX30.
.370...0 111.0 141..8 1. 4) For 690 V version.0 31..7 6...2 1.0 252..1.0 171...0 11.106.0 216.840.0 63.0 51..171...PSTX – The advanced range Technical data Fuse ratings and power losses 4 For softstarter Current range Max power loss at rated Ie Max fuse rating .0 90..5...0.0.0 75.72.0 21.8 3..6..0 315.300..3..0. 1) 2) 3) PSTX Integrated bypass ratings Softstarter Integrated contactor AC-3 rating at 400 V (A) IEC AC-3 Rated operational power at 400 V (kW) UL/CSA 3-phase motor rating at 480 V (hp) 4/14 Softstarters | US Catalog PSTX470 PSTX570 AF370 370 200 300 PSTX720 PSTX840 AF750 750 400 600 PSTX1050 PSTX1250 AF1250 - .9.5 10 18 26 48 68 97 148 99 146 78 106 165 234 A 100 125 160 160 250 315 400 500 630 630 700 800 900 900 1000 1250	1500 1800 2000 Type 170M1567 170M1568 170M1569 170M1569 170M1571 170M1572 170M3819 170M5810 170M5812 170M5812 170M5813 170M6812 170M6813 170M6813 170M6814 170M8554 170M6018 170M6020 170M6021 Power requirements supply circuit Holding (VA) / Pull-in (VA) Size 000 000 000 000 000 000 1* 2 2 2 2 3 3 3 3 3 3 3 3 49/51 49/51 49/51 49/51 49/51 49/51 49/51 49/53 49/53 56/276 56/276 56/276 56/276 67/434 67/434 61/929 61/929 68/929 68/929 For the supply circuit 6 A delayed.1250.0..210.0.37.570.60.0 13.2 4..0... For inside delta connection the fuses shall be placed inside the delta.0 18.85. for MCB use C characteristics.45.0...main circuit 1) 2) Bussmann fuses.. Contact ABB for more information.0.0.0. 170M6019 with fuse rating 1600 A should be used for 690 V version..1050. Bussmann fuses are only available for motors with rated current up to 1150 A.250.0 22.5.0..470.8.....0.0 42. DIN43 620 (Knife) Type PSTX30 PSTX37 PSTX45 PSTX60 PSTX72 PSTX85 PSTX105 PSTX142 PSTX170 PSTX210 PSTX250 PSTX300 PSTX370 PSTX470 PSTX570 PSTX720 PSTX840 PSTX1050 3) PSTX1250 3) 4) A 9.0 W 0...30...143..720.0 375.
5 Nm (4.4 in lb) Terminal shrouds 1SFN125406R1000 must be used..240 mm 2 - - Width ≤ - 24 mm (0.35 mm 2 Included E1859D E1858D ø 8.240 mm 2 - 1SDA013956R1 45 Nm - - 2 x mm 2 - 1SDA0549881R1 31 Nm - 1SDA055020R1 43 Nm - 120..969 in) 50 mm (1.240 mm 2 1SDA066917R1 1SDA055016R1 14 Nm 25 Nm 50.260 in) 1SDA023380R1 31 Nm 47 mm (1...... US Catalog | Softstarters 4/15 4 .5 6 22.185 mm 2 - 3 x mm 2 8 Nm - 1 x mm 2 - 95.16 AWG) 0.......120 mm 2 16..969 in) 6.95 mm 2 2 x mm 2 Included 8 Nm 6..492 in) 13 mm (0.35 mm 2 Included 2) ø 10...5 mm2 (19.185 mm 2 LZ185-2C/120 OZXB4 1) 1SFN074709R1000 1SCA022194R0890 16 Nm 22 Nm 6....5 ø 10...300 kcmil 10.500 kcmil ATK580/2 375 in lb 2/0.flexible Clamp type Tightening torque Cu cable ..5 mm (0.355 in) 18 Nm (160 in lb) 6...2C/120 OZXB4 1) 1SFN074709R1000 1SCA022194R0890 16 Nm 22 Nm - E1860D E1861D 22..PSTX105 PSTX142..2 mm (0.402 in) 28 Nm (248 in lb) 4.....850 in) 50 mm (1.75…1.2 6.240 mm 2 - - 1SDA013922R1 - - 35 Nm 70..400 kcmil Included 71 in lb - ATK185 300 in lb - ATK300 375 in lb 4....500 kcmil 2/0..185 mm 2 LZ185 ..945 in) 32 mm (1...5 ø 6.PSTX370 PSTX470.....5 ø 13 - - - - - - 120.....500 kcmil 2/0.flexible Clamp type Tightening torque Cu cable Stranded Clamp type Tightening torque Cu cable Stranded Clamp type ø L Tightening torque Cu cable Stranded Clamp type Tightening torque Al cable Stranded Clamp type Tightening torque Al cable Stranded Clamp type Tightening torque Lugs 1 x mm 2 2 x mm 2 1 x mm 2 8 Nm 10.5 - 10..5 mm2 (19.....14 AWG) 0.413 in) 12..PSTX570 PSTX720..75…2.PSTX – The advanced range Technical data Main terminals PSTX30.120 mm 2 1SDA055016R1 25 Nm 70.PSTX1050 PSTX1250 50 Cu cable .300 mm 2 1SDA066917R1 14 Nm 50.5 mm (0.500 kcmil - - - - ATK750/3 375 in lb ATK750/3 375 in lb - Diameter >= Tightening torque Connection capacity acc to UL / CSA 1 x AWG / kcmil Clamp type Tightening torque Connection capacity acc to UL / CSA 2 x AWG / kcmil Clamp type Tightening torque Connection capacity acc to UL / CSA 3 x AWG / kcmil Clamp type Tightening torque Supply and control circuit Cu cable ...70 mm 2 Included 8 Nm 6....95 mm 2 70.150 mm 2 16.500 kcmil - - - ATK300/2 2) 375 in lb - ATK580/2 375 in lb 2/0..Stranded 2 x mm2 Tightening torque 1) 10.5 ø 6.5 ø 12..519 in) 35 Nm (310 in lb) 45 Nm (398 in lb) 45 Nm (398 in lb) - 0. Terminal shrouds 1SFN125406R1000 can be used..2/0 8 mm (0.5 8 40 6 5 5 27 25 20 17.185 mm 2 185..PSTX170 PSTX210.Stranded 1 x mm2 Cu cable ..
For more circuit diagrams see new.abb.com/low-voltage/products/softstarters.
PSTX1250 Line with main contactor closed only during operation. 20 +24V V1 Coil consumption for main contactors.1 .1 E .5A 3-wire control O U1 2T1 4T2 6T3 13 Start Inside-delta connected with contactor and fuses Björn Johansson Approved RE Lars Eriksson 150817 A ABB O/I Application diagram 1SFB536005G5006 ABB AB.PSTX .. with fuses F1..5A 3-wire control W1 V1 U1 20 +24V E O I E M W2 V2 U2 If the pull-in or holding values are higher..3 17 In2 16 In1 K4 K5 Com 3 18 DGND 100-250V 50/60 Hz 19 GND K7 HMI K6 Analog out 15 In0 14 Stop 13 Start 22 2 K7 5 6 8 9 11 5/L3 4 6/T3 K1 Com 2 23 +(B) 24 -(A) 1L1 3L2 5L3 25 T1 Temp In 20 Com 1 + 24V Default: Event 21 K7 Default:Top of ramp E Default: Run I 1/L1 10 2/T1 7 4/T2 4 Anybus 1 Soft starter PSTX 3/L2 O PSTX 26 T2 27 T3 28 +24V 29 + 30 GND 12 2T1 4T2 6T3 K1 19 GND E 18 DGND I E 14 Stop W1 M If the pull-in or holding values are higher. the main contactors must be controlled via an auxiliary contactor.The advanced range Circuit diagrams PSTX30. with fuses 2-wire control O/I F1. In-line connected Inwith line contactor and fuses 1L1 3L2 5L3 Alt..370 PSTX30. 14 Stop 13 Start US Catalog | Softstarters 4/19 .2 . the Inside Delta contactor must be controlled via an auxiliary contactor. Pull-in max 15A Holding max 1.2 . Control Products 1L1 3L2 5L3 2-wire control Alt.3 Anybus 1 E O 7 10 Com 2 Com 1 14 Stop 13 Start 26 T2 1L1 3L2 5L3 PSTX K3 27 T3 28 +24V 5/L3 25 T1 3/L2 Analog out 15 In0 24 -(A) 1/L1 16 In1 K6 2/T1 17 In2 K5 6/T3 K7 K4 23 +(B) 4/T2 18 DGND HMI Com 3 + 24V 19 GND Temp In 20 Default: Event K7 Default: Run 21 E Default:Top of ramp Soft starter PSTX 100-250V 50/60 Hz I 4 29 + 30 GND 2T1 4T2 6T3 22 2 5 6 8 9 11 12 K3 K7 Coil consumption for Inside Delta contactor. Pull-in max 15A Holding max 1.
5 Softstarters | US Catalog .
Fieldbus communication Fieldbus communication Introduction 5/2 Anybus ordering details 5/3 FieldBusPlug ordering details 5/4 FieldBusPlug accessories ordering details 5/6 5 US Catalog | Softstarters 5/1 .
All major industrial fieldbus protocols include different accessories.Fieldbus communication Introduction PSR. 1 4 Protocols with FieldBusPlug − − Modbus-RTU − − Profibus − − DeviceNet − − Modbus TCP (only PSE) 5 5 Protocols with Anybus − − Modbus-RTU − − Profibus − − DeviceNet − − EtherNet/IP −− Modbus TCP −− Profinet 6 2 Integrated protocol −− Modbus-RTU 3 5/2 Softstarters | US Catalog 1 Softstarter PSR 2 Softstarter PSE 3 Softstarter PSTX 4 FieldBusPlug adapter 5 FieldBusPlug 6 Anybus . PSE and PSTX softstarters can be connected to a fieldbus network for monitoring and control. making the installation very flexible.
042 (lb) (0.042 0.1SFC132120V0001 Fieldbus communication Anybus ordering details 1SFC132121V0001 Profibus Modbus-RTU For communication protocol Catalog number Global reference code Pkg qty Weight (1 pce) Profibus DeviceNet Modbus-RTU EtherNet/IP (1-port) EtherNet/IP (2-port) Modbus TCP (1-port) Modbus TCP (2-port) Profinet (2-port) AB-PROFIBUS-1 AB-DEVICENET-1 AB-MODBUS-RTU-1 AB-ETHERNET-IP-1 AB-ETHERNET-IP-2 AB-MODBUS-TCP-1 AB-MODBUS-TCP-2 AB-PROFINET-2 1SFA899300R1001 1SFA899300R1002 1SFA899300R1003 1SFA899300R1005 1SFA899300R1006 1SFA899300R1007 1SFA899300R1008 1SFA899300R1010 1 1 1 1 1 1 1 1 kg 0.042 0.093) (0.093) 5 1SFC132118V0001 DeviceNet 1SFC132119V0001 EtherNet/IP (1-port) Modbus TCP (1-port) EtherNet/IP (2-port) Modbus TCP (2-port) Profinet (2-port) US Catalog | Softstarters 5/3 .042 0.093) (0.042 0.042 0.093) (0.093) (0.042 0.093) (0.093) (0.093) (0.042 0.
(GSD file) which is available at new.36 m m m m (lb) (0.00 m DNP21-FBP.10 (0. diagnostic LED DNP21-FBP MRP21-FBP COP21-FBP Designation Cable length Catalog number Global reference code Pkg qty Weight (1 pce) MODBUS-RTU-FBP MODBUS-RTU-FBP MODBUS-RTU-FBP MODBUS-RTU-FBP 0.050 1SAJ230000R1005 1 0.13 0.025 MRP21-FBP.025 1SAJ230000R1003 1 0.22) (0.Fieldbus communication FieldBusPlug ordering details Black cable DeviceNet FieldBusPlug −− Ready-made DeviceNet fieldbus interface with various cable lengths −− Applicable on all FBP motor starters and other devices −− Degree of protection IP65.abb.79) 5 Modbus-RTU FieldBusPlug −− Ready-made Modbus-RTU fieldbus interface with various cable lengths −− Applicable on all FBP motor starters and other devices −− Degree of protection IP65.44) (0.29) (0. you need specific software for PLC setup.500 1SAJ230000R1050 1 0.25 m DNP21-FBP.00 5. diagnostic LED Designation Cable length Catalog number Global reference code Pkg qty Weight (1 pce) kg (lb) DeviceNet-FBP 0.36 (0. 5/4 Softstarters | US Catalog ..50 m DNP21-FBP. please contact your local ABB office.20) (0.500 1SAJ250000R0003 1SAJ250000R0005 1SAJ250000R0010 1SAJ250000R0050 1 1 1 1 kg 0.150 CDP11-FBP.02) (0.09 0.100 1SAJ230000R1010 1 0.050 MRP21-FBP.01 0.79) Ethernet Modbus TCP interface MTQ22-FBP −− Ethernet connectivity for up to four units −− Modbus TCP protocol −− Supports all network topologies −− No special Ethernet connectors required in MCCs −− Easy to use in widthdrawable applications Designation Cable length Catalog number Global reference code Pkg qty Weight (1 pce) kg (lb) 1.100 MRP21-FBP.4 1SAJ260000R0100 1SAJ929170R0015 1SAJ929100R0004 1 1 4 0.5 m MTQ22-FBP CDP17-FBP.22) DeviceNet-FBP 1.25 0.01 (0.20) DeviceNet-FBP 0.20 0.09 (0.00 MRP21-FBP.com/low-voltage/products/softstarters If you need help or advice.00 m DNP21-FBP.50 1.10 0..02) MTQ22-FBP Ethernet Modbus TCP interface Cable MTQ to FieldBusPlug adapter Passive cable fixing bracket To connect the softstarter to a Profibus DP fieldbus system.29) DeviceNet-FBP 5.13 (0.
44) (0.10) 2CDC34101S0010 Configuration software −− This cable and software can be used for setup and commissioning of the softstarter as well as to keep back-up of the parameter settings.50 (lb) (0. Designation Catalog number Global reference code Pkg qty USB to FBP interface cable PDP22/PDQ22 Device Type Manager (DTM) incl.10 0..24) (1. −− Supports PROFIBUS DP V0 and V1 −− Applicable on all FBP motor starters and other devices −− Degree of protection IP65.00 m m m m m Catalog number PDP22-FBP.100 PDP22-FBP.44) (0.36 (0. There are separate diagnosis LEDs for bus and device status.50 1.02) - To connect the softstarter to a Profibus DP fieldbus system..200 PDP22-FBP.22) (0.Fieldbus communication FieldBusPlug ordering details Purple cable Profibus DP FieldBusPlug −− Ready-made Profibus DP fieldbus interface with various cable lengths. PDQ22-FBP Designation Catalog number Global reference code Pkg qty Quadruple bus connector DIN rail adapter for PDQ22-FBP Fixing bracket for passive plug of connection cable PDQ22-FBP CDA11-FBP.com/low-voltage/products/softstarters If you need help or advice. 0 CDP11-FBP.abb.00 2.050 PDP22-FBP.09 0.00 5.25 0. diagnostic LED Designation Profibus Profibus Profibus Profibus Profibus PDP22-FBP DP DP DP DP DP FBP FBP FBP FBP FBP Cable length 0.20 0. The degree of protection is IP66. It allows the connection of up to four devices to Profibus DP by just using one Profibus node access. you need specific software for PLC setup.20) (0.500 Global reference code 1SAJ240100R1003 1SAJ240100R1005 1SAJ240100R1010 1SAJ240100R1020 1SAJ240100R1050 Pkg qty 1 1 1 1 1 Weight (1 pce) kg (lb) 0.29) (0. This allows a cost-efficient device integration for devices that are physically located nearby. FDT/DTM frame application UTF21-FBP PBDTM-FBP 1SAJ929400R0002 1SAJ924012R0005 1 1 Weight (1 pce) kg 0.20 0.13 0. US Catalog | Softstarters 5/5 5 . (GSD file) which is available at new. Note that the accessory PDQ22-FBP only works with the PSR and PSE softstarter.025 PDP22-FBP.0 1SAJ240200R0050 1SAJ929300R0001 1SAJ929100R0001 1 1 1 Weight (1 pce) kg 0.11 0. please contact your local ABB office. PDQ22 supports DP-V0 and DP-V1.01 - (lb) (0.79) 2CDC 341 048 F0006 Profibus DP FieldBusPlug for four devices −− PDQ22 is a member of the ABB FieldBusPlug family of bus connectors.
33) 0.50 m DNF11-FBP.050 Designation Cable length Catalog number Global reference code Pkg qty Round cable with female connector Round cable with male connector 0.050 DNM11-FBP.0 1SAJ923005R0001 1SAJ923006R0001 5 5 Weight (1 pce) kg (lb) 0.050 1SAJ923002R0005 1SAJ923003R0005 1 1 Weight (1 pce) kg (lb) 0.35) DNX11-FBP DeviceNet and Modbus-RTU round cable connectors Bus cable and coupling accessories DNM11-FBP.60 (lb) (0.120 5/6 Softstarters | US Catalog Designation Catalog number Global reference code Pkg qty Termination Resistor.04 (0.999 1SAJ923001R0010 1SAJ923001R0030 1SAJ923001R0050 1SAJ923004R0001 1 1 1 1 Weight (1 pce) kg 0.08 0.00 m 100.300 DNX11-FBP.100 DNX11-FBP.31 5.09) 0.44) (0.0 Designation Catalog number Global reference code Pkg qty Male connector for round cable Female connector for round cable DNM11-FBP.120 1SAJ923007R0001 1 Weight (1 pce) kg (lb) 0.09) Devicenet and Modbus-RTU round cable for bus extension Ready-made bus cable with M12 male and female connectors Designation Cable length Catalog number Global reference code Pkg qty Extension cable Extension cable Extension cable Round cable 1.Fieldbus communication FieldBusPlug accessories ordering details Black cable Accessories for the DeviceNet and Modbus-RTU bus connetor DeviceNet and Modbus-RTU round cable for bus junctions Ready-made bus cable with an M12 connector and an open cable end DNF11-FBP.050 5 DNM11-FBP.0 DNF11-FBP. 120 Ohm DNR11-FBP.0 DeviceNet and Modbus-RTU termination resistor DNR11-FBP.18) (0.68) (12.04 (0.00 m 5.20 0.500 DNC11-FBP.04) .15 (0.00 m 3.00 m DNX11-FBP.15 (0.02 (0.50 m 0.33) DNF11-FBP.
0 PDF11-FBP.09) (0.050 1SAJ924002R0005 1 Weight (1 pce) kg (lb) 0.20 0. PDV12-FBP PDA12-FBP. Code A-A Adaptor M12-Dsub9-M12 Cable length 0. shielded (female/male).07) (0.50 m 1. Code B-A Feeding connector 24 V DC.07) 0.04 Termination resistor.50 m Adaptor M12-Dsub9-M12 Cable length 2 x 0.44) (0.04 (0.68) (12.02) (0.6 1.050 (lb) (0.150 CDP16-FBP. shielded m m m m US Catalog | Softstarters 5/7 .500 PDC11-FBP.20 0. 150 Ohm Feeding connector 24 V DC.050 2CDC 341 006 F0004 PDV11-FBP.050 1SAJ924007R0001 1SAJ924008R0001 1SAJ924011R0001 1SAJ924009R0001 (lb) (0.03 (0.50 m PDM11-FBP.50 Purple cable Designation Cable length Catalog number Global reference code Pkg qty Round cable with female connector Round cable with male connector 0.50 m PDR11-FBP.060 CDP15-FBP. shielded (male/open).50 m PDF11-FBP.08 0.150 PDV11-FBP.050 1SAJ924010R0001 1 0.00 m 100.04 (0. shielded (female/male).04 0.0 PDV12-FBP.050 PDX11-FBP.01 0.02) (0.300 PDX11-FBP.04 0.050 1SAJ924003R0005 1 0.00 m PDX11-FBP.5 (lb) (0.0 1SAJ924005R0001 1SAJ924006R0001 5 5 PDF11-FBP PDR11-FBP. miscellaneous accessories Designation Catalog number Global reference code Pkg qty 1 1 1 1 Weight (1 pce) kg 0.g.09) (0.100 PDX11-FBP.00 m 3.0 PDA11-FBP.18) (0.09) PDA12-FBP.00 m 5.Fieldbus communication FieldBusPlug accessories ordering details 2CDC 341 048 F0003 Accessories for the Profibus DP Bus Connector Profibus DP Round cable for Bus Junctions −− Ready-made bus cable with an M12 connector and an open cable end.20 0.07) Profibus DP termination resistor.5 1.3 0.09) (0. Profibus DB couplers or devices with an integrated Profibus DB interface PDM11-FBP.09) 0.150 Weight (1 pce) kg 0.04 0.44) (0.44) Extension cable Designation Extension Extension Extension Extension cable cable cable cable (female/male).60 Weight (1 pce) kg (lb) 0.35) Profibus DP accessories for bus extension Designation Catalog number Global reference code Pkg qty Male connector for round cable Female connector for round cable PDM11-FBP.04 (0.999 1SAJ924001R0005 1SAJ924001R0010 1SAJ924001R0030 1SAJ924001R0050 1SAJ924004R1000 1 1 1 1 1 2CDC 341 050 F0003 2CDC 341 051 F0003 PDX11-FBP PDM11-FBP 2CDC 341 053 F0003 2CDC 341 054 F0003 2CDC 341 007 F0004 PDA11-FBP. −− Application on bus junctions such as e.150 1SAJ929140R0003 1SAJ929140R0006 1SAJ929140R0015 1SAJ929150R0015 1 1 1 1 Weight (1 pce) kg 0.03 (0.01 0.50 2CDC 341 049 F0003 PDF11-FBP.030 CDP15-FBP.03 0.09) Cable length Catalog number Global reference code Pkg qty CDP15-FBP.09) 5 2CDC 341 047 F0003 Profibus DP round cable for bus extension −− Ready-made bus cable with M12 male and female connectors −− Round cable on coil Designation Cable length Catalog number Global reference code Pkg qty Extension cable Extension cable Extension cable Extension cable Round cable 0.31 5.
abb.com/SOC SOC Coord Selected O ptimiz in ed Coord ation ination motor ta b le s for protec tion 6/1 Softstarters | US Catalog .fr/softstarter Coordination tables Online tool for coordination with short circuit protection.abbcontrol. Online softstarter selection tool Fast and easy selection of softstarter on any device. overload protection and line contactor. coordination tables. 6 www. On our web page you will find tools for selection.it. applications.ABB softstarters Marketing material and tools It is easy to access more information about ABB softstarters online. CAD drawings and a variety of documentation.
abb.Download 2D and 3D drawings in any format Use our Cadenas portal to download CAD drawings for all of our softstarters.abb. Cadenas portal for CAD drawings 6 More information online −− Product catalogs and brochures − − Certificates and approvals − − Case studies −− Product simulator − − Circuit diagrams and application diagrams −− Manuals − − EDS.abb.com/low-voltage/launches/pstx SoftstarterCare™ – Service Engineer Tool Software for easy set-up of PSE and PSTX.com/low-voltage/ products/softstarters US Catalog | Softstarters 6/2 .and GSD-files for fieldbus connection −− Softstarter selection tool new. new.com/low-voltage/products/softstarters http://new. using a PC.
TN 38125 www. June 2016 Contact us ..5:30 p. Any reproduction. We reserve all rights in this document and in the subject matter and illustrations contained therein.m.abb.m.com Technical Support: 888-385-1221.. Option 1 7:00 a. Monday-Friday elec_custserv@tnb. Monday-Friday lvps.m.ABB Electrification Products 8155 T&B Boulevard Memphis. © Copyright 2016 ABB.5:00 p.m. 1SXU132224C0201. With regard to purchase orders and/or contracts. ABB does not accept any responsibility whatsoever for potential errors or possible lack of information in this document.com We reserve the right to make technical changes or modify the contents of this document without prior notice. .us/lowvoltage Customer Service: 800-816-7809 7:00 a. All rights reserved. disclosure to third parties or utilization of its contents – in whole or in parts – is forbidden without prior written consent of ABB.abb. CST. CST.support@us. the agreed particulars shall prevail. .

References: V. 
 V. 
 V. 
 V. 
 V. 
 V. 
 V. 
 V. 
 V.

 V.