Source: https://www.scribd.com/document/52677131/Sistema-de-anillados
Timestamp: 2017-03-27 19:13:56+00:00

Document:
BrowseInterestsStay InformedCareerPersonal GrowthFiction & BiographiesHealth & FitnessLifestyleCultureBrowse byBooksAudiobooksNews & MagazinesSheet MusicBrowse allUploadSign inJoinADJUDICACIÓN DE MENOR CUANTIA N° AMC- 104 -2005-ES“SISTEMA DE ANILLADO EN REDES PRIMARIAS EN 10 KV - MOQUEGUA”
BASES Y ANEXOS....................................................................................................7 1.1 ENTIDAD QUE CONVOCA: ...........................................................................7 1.2 OBJETO DEL PROCESO ................................................................................7 1.3 ALCANCE Y UBICACIÓN DE LA OBRA.....................................................7 1.4 PLAZO REFERENCIAL DE EJECUCIÓN DE OBRA ................................7 1.5 DE SU BASE LEGAL ........................................................................................7 1.6 VALOR REFERENCIAL TOTAL...................................................................8 1.7 FUENTE DE FINANCIAMIENTO..................................................................8 1.8 SISTEMA DE CONTRATACIÓN Y MODALIDAD DE EJECUCIÓN......8 1.9 PARTICIPANTES..............................................................................................8 1.10 DOCUMENTOS DE LA ADJUDICACIÓN DE MENOR CUANTIA. ........8 1.11 REGIMEN LEGAL............................................................................................8 1.12 CALENDARIO...................................................................................................9 1.13 DE LAS BASES ....................................................................................................9 1.14 DOCUMENTOS A ENTREGARSE AL POSTOR.........................................9 1.15 OBLIGACIONES DEL POSTOR ....................................................................9 1.16 FORMA DE LA PRESENTACIÓN Y ALCANCES DE LAS PROPUESTAS..............................................................................................................10 1.17 PRESENTACIÓN Y APERTURA DE PROPUESTAS ...............................11 1.18 EVALUACION Y CALIFICACION DE PROPUESTAS............................12 1.19 DE LAS GARANTIAS.....................................................................................13 1.20 DEL INGENIERO RESIDENTE ...................................................................13 1.21 INSPECTOR DE OBRA..................................................................................14 1.22 CUADERNO DE OBRA ..................................................................................14 1.23 DEL CALENDARIO VALORIZADO ...........................................................14 1.24 DE LOS ADELANTOS....................................................................................14 1.25 COMPUTO DEL PLAZO DEL CONTRATO ..............................................15 1.26 DE LAS VALORIZACIONES ........................................................................15 1.27 LICENCIAS AUTORIZACIONES Y PERMISOS ......................................15 1.28 CONDICIONES IMPORTANTES.................................................................15 1.29 SUSCRIPCION DEL CONTRATO ...............................................................16
I. MEMORIA DESCRIPTIVA. ......................................................................................35 1.1 INTRODUCCION. ...........................................................................................35 1.2 ALCANCES DEL PROYECTO .....................................................................35 1.3 AREA DE INFLUENCIA DEL PROYECTO ...............................................35 1.3.1 UBICACIÓN GEOGRAFICA .....................................................................35 1.3.2 CONDICIONES AMBIENTALES...............................................................35 1.3.3 VIAS DE ACCESO......................................................................................35 1.4 DESCRIPCION DEL PROYECTO ...............................................................36 1.4.1 BASES DE REFERENCIA..........................................................................36 1.4.2 DESCRIPCION DE TRABAJOS A EJECUTAR.........................................36 2
1.4.3 CARACTERISTICAS PRINCIPALES .........................................................36 1.5 FUENTE DE FINANCIAMIENTO................................................................36 II. ESPECIFICACIONES TECNICAS DE SUMINISTRO DE MATERIALES Y EQUIPOS. .........................................................................................................................38 2.1 INTRODUCCION ............................................................................................38 2.2 GARANTIA ......................................................................................................38 2.3 PROCEDIMIENTO PARA EL CONTROL DE CALIDAD DE MATERIALES .............................................................................................................38 2.4 RECEPCION ....................................................................................................38 2.5 SUMINISTRO DE POSTES DE CONCRETO............................................39 2.6 CRUCETAS Y MENSULAS ...........................................................................40 2.7 CAJA REGISTRO PARA PUESTA A TIERRA ..........................................43 2.8 ESPECIFICACIONES TECNICAS DE CONDUCTORES DE REDES PRIMARIAS .................................................................................................................43 2.9 ESPECIFICACIONES TECNICAS DE AISLADORES .............................44 2.9.1 AISLADORES DE PORCELANA TIPO PIN..............................................44 2.9.2 AISLADORES POLIMERICOS TIPO SUSPENSIÓN................................45 2.10 ACCESORIOS DE AISLADORES ................................................................47 2.11 ACCESORIOS DEL CONDUCTOR DE RED PRIMARIA .......................48 2.11.1 CARACTERISTICAS GENERALES ...........................................................48 2.11.2 CARACTERÍSTICAS ESPECÍFICAS .........................................................49 2.12 ACCESORIOS METALICOS PARA POSTES Y CRUCETAS EN M.T. .50 2.12.1 ALCANCES.................................................................................................50 2.12.2 NORMAS APLICABLES.............................................................................50 2.12.3 DESCRIPCIÓN DE LOS MATERIALES....................................................51 2.13 ESPECIFICACIONES TECNICAS DE RETENIDAS. ...............................52 2.13.1 RETENIDA TIPO SIMPLE.........................................................................52 2.13.2 RETENIDA TIPO CONTRAPUNTA ..........................................................54 2.13.3 RETENIDA TIPO VIOLIN..........................................................................54 2.14 ESPECIFICACIONES TECNICAS DEL SISTEMA DE PUESTA A TIERRA.........................................................................................................................54 2.15 SECCIONADORES FUSIBLE DE ALTA TENSION. ................................55 III. ESPECIFICACIONES TECNICAS PARA EL MONTAJE ELECTROMECANICO. .................................................................................................57
A. ESPECIFICACIONES TÉCNICAS GENERALES .......................57 3.1 DEL CONTRATO............................................................................................57 3.1.1 ALCANCE DEL CONTRATO.....................................................................57 3.1.2 3.1.2 CONDICIONES QUE AFECTAN A LA OBRA.................................57 3.1.3 3.1.3 OBSERVACIÓN DE LAS LEYES ......................................................57 3.1.4 3.1.4 SUB-CONTRATOS ............................................................................57 3.2 DE LA PROGRAMACIÓN.............................................................................58 3.2.1 CRONOGRAMA DE EJECUCIÓN ............................................................58 3.2.2 PLAZOS CONTRACTUALES.....................................................................58 3.2.3 CUADERNO DE OBRA .............................................................................58 3.3 DEL PERSONAL .............................................................................................58
..................59 3...61 3...............72 3.....2 PRUEBAS EN BLANCO.......................63 3................3..................77 3.........78
.............3 PRUEBA DE PUESTA EN SERVICIO...............6 DE LA ACEPTACIÓN ...................................................13 INSTALACION DE CADENA DE AISLADORES.3 OBLIGACIONES DEL CONTRATISTA...........................................................................5...............3 LEYES SOCIALES........................................................................................60 3..............60 3..............................................63 3................................77 3............................75 3..........................4...........2 MONTAJE DE PARTES IMPORTANTES...................4 CAMBIOS Y MODIFICACIONES...................4 RECEPCIÓN DE OBRA.................59 3..................................................................................4........................4..............................58 3..............4 DE LA EJECUCIÓN ...............................8 PROTECCIÓN DEL MEDIO AMBIENTE............11 INSTALACION DE CRUCETAS Y MENSULAS ...................6 DAÑOS DE OBRA.....................5.......................2 RESPONSABILIDAD DE LA OBRA .......................................7 DAÑOS Y PERJUICIOS A TERCEROS......................................67 3.....4 FACILIDADES DE INSPECCIÓN.......... .....................................67 3.........16 TENDIDO Y TEMPLADO DE CONDUCTORES.....4.............71 3..............................................................71 3................4.............5...24 INSPECCIÓN Y PRUEBAS...........................23 PINTADO DE CÓDIGO Y SEÑALIZACIÓN DE ESTRUCTURAS .....................................5 RESPONSABILIDAD DEL CONTRATISTA ..........60 3................1 ORGANIGRAMA DEL CONTRATISTA.........................................62 3.....................20 ATERRAMIENTO DE ESTRUCTURA ...........................................10 INSTALACION DE ARMADOS...................63 3.....................62 3..................................................12 CAMBIO DE ESPIGAS Y AISLADORES.......................................................................4....................4....................76 3.......9 VIGILANCIA Y PROTECCIÓN DE LA OBRA ...........21 INSTALACION DE CAJA REGISTRO....4 SEGURIDAD E HIGIENE..........................................................................................3.....2 DESEMPEÑO DEL PERSONAL...3.....................................5 RECHAZOS ...65 B..............................................3.........77 3....64 3.............................1 PROCEDIMIENTO GENERAL........................................4................................... ESPECIFICACIONES PARTICULARES ......65 3.........22 REFORZAMIENTO DE BASE DE POSTE.......4..........6.1 EJECUCIÓN DE LOS TRABAJOS .....................14 RETENIDAS Y ANCLAJE....3 HERRAMIENTAS Y EQUIPOS DE CONSTRUCCIÓN...............................65 3...............6..19 INSTALACION DE PUESTA A TIERRA ..........................6................................................................................9 DISTRIBUCION DE POSTES DE M............................................ ..................................................18 INSTALACION DE SECCIONADORES TIPO CUT-OUT .61 3....................76 3.........................10 LIMPIEZA ..................64 3.5 DE LA SUPERVISIÓN.................................................59 3......................................................7 REPLANTEO TOPOGRÁFICO ....................61 3................3......70 3...........................................................15 RETEMPLADO DE RETENIDA...............6.......................70 3.......63 3......... ..62 3................66 3.62 3..............................................................60 3..........................8 EXCAVACION DE HUECOS .................1 SUPERVISIÓN DE LA OBRA .........................63 3.............59 3......................................................5.6.........61 3.................70 3....................59 3...........T.................4................................75 3......17 RETEMPLADO DE CONDUCTORES....................
.........83 4.................................... VI
B CALCULO MECANICO DE CONDUCTORES – RED PRIMARIA .....................3......................27 MODIFICACION DE ARMADO DE M............ .......................83 4...................85 ECUACION DE CAMBIO DE ESTADO .....5 4....80 3..........................................81 IV....................3.......29 DESMONTAJE DE ARMADOS ....................................2 NIVEL DE AISLAMIENTO .......26 DESMONTAJE TEMPORAL DEL CONDUCTOR.......83 4...........81 3.........84 4........... ............................. CALCULOS JUSTIFICATIVOS..........4 SEPARACION MINIMA ENTRE CONDUCTORES Y SUS ESTRUCTURAS 85
4....................6 V...................T.......86
METRADO PRESUPUESTO PLANOS Y DETALLES
..................................... A ARMADO DE ANCLAJE ...............3 DISTANCIAS ELECTRICAS DE SEGURIDAD.....................................80 3................... INCLUIDO CABLE STAR................................3.............................................................1 SELECCION DE LA ALTURA DE LA ESTRUCTURA ........3 DISTANCIA DE LOS CONDUCTORES AL TERRENO..............................85 DEMANDA DE POTENCIA.................................................1 GENERALIDADES .4 4..................84 4.3..85
HIPOTESIS DE CALCULO ........3.........................................25 ACONDICIONAMIENTO DE INSTALACIONES DE RED SECUNDARIA EN POSTE DE MT........................................84 4.....................................................................81 3....................83
A) CALCULOS ELECTRICOS REDES PRIMARIAS ...2 DISTANCIA MINIMA DE LOS CONDUCTORES ENTRE SI ..................83 4........... UNIDADES DE AP Y CONEXIONES DOMICILIARES..........28 DESMONTAJE DE MENSULAS Y CRUCETAS........
PARTE I BASES AMC-104-2005
AMC -104.2
1. transporte. establecen las normas y procedimientos que seguirá Electrosur S.A. a satisfacción de Electrosur S. sobre la base de los documentos del presente Expediente Técnico será responsable del suministro de materiales. El área de influencia de la obra comprende la ciudad de Moquegua.2005-ES SISTEMA DE ANILLADO EN REDES PRIMARIAS EN 10 KV – MOQUEGUA 1. Liquidación de Contrato...5
. pruebas y puesta en servicio.BASES DEL CONCURSO POR ADJUDICACIÓN MENOR CUANTIA No. Pruebas Eléctricas.A..1 BASES Y ANEXOS ENTIDAD QUE CONVOCA: Electrosur S.S 083-20047
1. aprobado mediante D. La obra comprende: Suministro de materiales Control de calidad de los materiales Montaje Electromecánico. se entenderá que se está haciendo referencia al Texto Único Ordenado de la Ley Nº 26850 . montaje.A. para la evaluación y calificación de postores. así como para el otorgamiento de la Buena Pro y posterior contratación de la ejecución de la Obra 1.A. DE SU BASE LEGAL Cuando en las presentes Bases se menciona la palabra “Ley”. siendo el plazo mínimo de treinta (30) días calendarios. que incluye. Empresa Regional de Servicio Público de Electricidad. sin observaciones.3 ALCANCE Y UBICACIÓN DE LA OBRA El Contratista que obtenga la Buena Pro.4 PLAZO REFERENCIAL DE EJECUCIÓN DE OBRA El Plazo Base Referencial para la ejecución de la obra es de cuarenta y cinco (45) días calendarios. pruebas y puesta en servicio. suministro de materiales.Ley de Contrataciones y Adquisiciones del Estado. a satisfacción de Electrosur S. Estas Bases. transporte. montaje electromecánico. 1. 1. con domicilio legal en la calle Zela Nº 408 Tacna. OBJETO DEL PROCESO El presente tiene por objeto seleccionar al Contratista que proponga la oferta Técnico Económica más conveniente para ejecutar la obra “SISTEMA DE ANILLADO EN REDES PRIMARIAS EN 10 KV – MOQUEGUA”.
PCM, la mención al “Reglamento”, se entenderá referida al Reglamento de la Ley de Contrataciones y adquisiciones del Estado, aprobado por Decreto Supremo 0842004-PCM. 1.6 VALOR REFERENCIAL TOTAL El Valor Referencial referido al mes de Octubre del 2005, según el presupuesto del Proyecto objeto de la presente Base, representa la suma de TREINTA Y TRES MIL CUATROCIENTOS VEINTE Y TRES CON 50/100 (S/.33 423,50) incluido IGV. El 110% del monto del valor referencial representa la suma de S/. 36 765,85 incluido IGV. El 90% del monto del valor referencial representa la suma de S/. 30 081,15 incluido IGV. 1.7 1.8 FUENTE DE FINANCIAMIENTO Recursos propios. SISTEMA DE CONTRATACIÓN Y MODALIDAD DE EJECUCIÓN El presente proceso de Adjudicación de Menor Cuantía se efectuará por el Sistema de Precios Unitarios. Cuya modalidad de ejecución es por contrata. 1.9 PARTICIPANTES Podrán presentarse a la presente convocatoria solo los que se acrediten como Contratistas de Obras, debidamente inscritos en el Registro Nacional de Contratistas a cargo del Consejo Superior de Contrataciones y Adquisiciones del Estado; que no se encuentren incluidos en el Registro de Inhabilitados para contratar con el Estado; y con una capacidad libre de contratación de acuerdo al monto del Valor referencial. 1.10 DOCUMENTOS DE LA ADJUDICACIÓN DE MENOR CUANTIA. Los documentos del Proceso de Selección están conformados por: Bases Administrativas. Proforma de Contrato Expediente Técnico 1.11 REGIMEN LEGAL La presente Adjudicación de Menor Cuantía se regirá por lo siguiente: a) Expediente Técnico conformado por: Bases Administrativas. Proforma de Contrato Expediente Técnico 8
Ley de Presupuesto del Sector Público para el año fiscal 2005. D.S. N° 083-2004-PCM TUO de la Ley de Contrataciones y Adquisiciones del Estado y su Reglamento aprobado por el D.S. N° 084-2004-PCM y, demás normas modificatorias y complementarias.
Convocatoria Registro de participantes Plazo de presentación de consultas, aclaración de venta de Bases Fecha de absoluciones de consultas, e integración de bases Presentación y apertura de propuestas Fecha de otorgamiento de la Buena Pro : : : : : : El 25/10/2005 Del 25/10/2005 al 03/11/2005 Del 25/10/2005 al 27/10/2005 El 02/11/2005 El 07/11/2005 a las 10:00 horas El 07/11/2005 a las 10:00 horas
La convocatoria a este proceso de selección se realizará de conformidad a lo señalado por el artículo 106º del Reglamento del TUO de la Ley de Contrataciones y Adquisiciones del Estado. 1.13 DE LAS BASES
Los Postores podrán recabar los documentos del Proceso de Selección, Bases y Expediente Técnico sin costo para el participante en las oficinas del área de logística, sito en la calle Zela Nº 408, Tacna – Cercado
DOCUMENTOS A ENTREGARSE AL POSTOR a) ELECTROSUR S.A. proporcionará a los postores por la modalidad de venta, el Expediente Técnico que comprende los siguientes documentos: BASES Y ANEXOS • PROFORMA DEL CONTRATO • EXPEDIENTE TÉCNICO • El postor en caso de ser favorecido con la Buena Pro, deberá considerar que Electrosur S.A. mediante la entrega de los documentos anteriores, ha dado cumplimiento al inciso “2)” del artículo 240° del Reglamento de la Ley de Contrataciones y Adquisiciones del Estado.
OBLIGACIONES DEL POSTOR Comunicar por escrito, en el plazo previsto en el Calendario de la Convocatoria, las consultas y observaciones que encuentren en los documentos que están involucrados para la ejecución y que forman parte de las presentes Bases Administrativas de la obra, así como las discrepancias o falta de concordancia que se encuentren entre éstos, pues en el caso de no hacerlo se entenderá que el Adquirente de las Bases, los encuentra correctos y acepta todo lo contenido y dispuesto en los documentos del Proceso de Selección. 9
La presentación de la propuesta implicará la tácita aceptación del postor de no haber encontrado inconveniente alguno, tanto para la preparación de la oferta, como para la ejecución de la obra en el plazo previsto. 1.16 FORMA DE LA PRESENTACIÓN Y ALCANCES DE LAS PROPUESTAS Los Actos de Recepción de propuestas, Apertura de sobres y otorgamiento de la Buena Pro, se llevarán a cabo en acto publico. Las propuestas se presentarán en dos (02) sobres, de los cuales el primero contendrá la propuesta técnica y el segundo la propuesta económica, con la descripción indicada. Tanto la propuesta técnica como la económica se presentarán en original con una (01) copia simple. Las propuestas se redactarán por medios mecánicos o electrónicos, llevarán el sello y la rúbrica del postor y serán foliadas correlativamente. La omisión de la presentación o vicio de cualquiera de los documentos señalados anteriormente, impedirá la evaluación correspondiente y será eliminado del presente proceso de adjudicación. NOMBRE DEL POSTOR Señores: ELECTROSUR S.A. Calle Zela Nro. 408 - Tacna ADJUDICACIÓN DE MENOR CUANTIA N° AMC - .........-2005-ES OBRA: “SISTEMA DE ANILLADO EN REDES PRIMARIAS EN 10 KV – MOQUEGUA” SOBRE N° (01 PROPUESTA TÉCNICA Ó 02 PROPUESTA ECONOMICA, SEGÚN SEA EL CASO) PRESENTE.DOCUMENTOS DEL PRIMER SOBRE – PROPUESTA TECNICA: a) Copia Simple del Certificado de inscripción vigente en el Registro Nacional de Proveedores. b) Declaración Jurada conforme a lo establecido en el artículo 76° del Reglamento de la Ley de Contrataciones y Adquisiciones del Estado, de acuerdo al Anexo N° 01 c) Como documentación que acredite el cumplimiento de los requerimientos mínimos, el postor presentará las bases (incluido el expediente técnico), firmado en cada una de sus páginas. d) Documentación de presentación (Anexo N° 02) e) Declaración Jurada de ser una Pequeña o Microempresa, si fuera el caso. De acuerdo al Anexo N° 03, OPTATIVO f) Promesa de consorcio, de ser el caso. De acuerdo al Anexo N° 04. g) Propuesta del plazo de ejecución. Similar anexo N° 05 10
en la oficina de mesa de partes de Electrosur S.17. acerca del número de postores participantes y otras ocurrencias que se den lugar hasta ese momento. se procederá a escribir en el acta correspondiente. estando el postor obligado a presentar su oferta en forma integral y en la misma forma del Valor Referencial de las Bases.17. la Ley y el Reglamento.17. es inapelable.3 Recibidas las propuestas por el Comité Especial. no se aceptará la presentación de ningún otro postor. ni se aceptará la entrega de nuevos documentos. de uno o más postores. la evaluación y calificación de las propuestas. hora y lugar señalado en el Aviso de Convocatoria. Es obligatorio la presentación de todos los documentos requeridos y el Comité Especial comprobará que los documentos presentados por cada postor sean los solicitados por las Bases. El Comité Especial levantará el acta respectiva.5 Finalizada la apertura de los Primeros Sobres. a la revisión y visto bueno a su contenido.1 El postor realizará la presentación de su propuesta. 1.17 PRESENTACIÓN Y APERTURA DE PROPUESTAS 1. en acto privado. ni podrá interrumpirse el acto de la Adjudicación de Menor Cuantia.4 El Comité Especial procederá a la apertura de los Primeros Sobres. el Comité Especial los devolverá al postor conjuntamente con su segundo sobre sin que este sea abierto. gastos generales indirectos y sus utilidades. se realizarán en la fecha. de no ser así. 1.A. en la fecha indicada en el aviso de convocatoria.DOCUMENTOS DEL SEGUNDO SOBRE Carta propuesta de la oferta económica con sus respectivos documentos sustentatorios. el postor indicará en forma clara en porcentaje y en soles cuánto representan sus gastos generales directos. sobres uno y dos. según anexos N° 6 y 7.17. 1.2 El Acto de apertura de los sobres uno y dos. así como el otorgamiento de la Buena Pro. Calle Zela N° 408. por falta o presentación incorrecta de la documentación. Asimismo.17. La decisión del Comité Especial de declarar no conforme la presentación de la documentación. El detalle de las partidas del Valor Referencial es básico. 11
. dejándose en el Acta expresa constancia del motivo de la No Conformidad. 1. 1. no es necesario la inclusión de los análisis de costos unitarios. por el Comité Especial encargado de conducir la presente Adjudicación de Menor Cuantía. la cual deberá ser suscrita por todos sus miembros.
Se descalificará la propuesta económica cuyo monto sea superior al 110% del monto del valor referencial del ítem al cual postula el postor. 12
.18.18 EVALUACION Y CALIFICACION DE PROPUESTAS 1. el Comité Especial otorgará la Buena Pro a la propuesta que obtenga el mayor puntaje.S. o se encontrara documentación no conforme en este segundo sobre. por no establecerse un factor técnico de evaluación. Asimismo. el otorgamiento de la Buena Pro se efectuará observando estrictamente lo establecido en el artículo 133° del Reglamento. otorgará la Buena Pro a la propuesta que obtenga el mayor puntaje en la evaluación de la Propuesta Económica. según la siguiente fórmula: PTPi = Om/Oi x PMPE i : Propuesta postor i PTPi : Puntaje total de la propuesta económica i Oi : Propuesta económica i. dejándose expresa constancia en el Acta el motivo de la No Conformidad.18. 1.17. En el caso que dos o más postores obtengan el mismo puntaje. El punta total consistirá en asignar el puntaje máximo a la propuesta económica de menor monto. indicando el orden de prelación que corresponde a cada propuesta presentada.6 Acto seguido el Comité Especial procederá a la apertura de los segundos sobres de los postores que hayan sido considerados aptos. siendo el puntaje máximo 100 puntos. procediendo el Comité Especial a la revisión de su contenido y registrándose el visto bueno en cada uno de los documentos.2 El Comité Especial para el otorgamiento de la Buena Pro observará el siguiente procedimiento: Cuando el número de propuestas válidas sea uno ó más. conforme a los artículos 68° y 70° del Reglamento de la Ley de Contrataciones y Adquisiciones del Estado (D. Om : Propuesta económica de monto o precio más bajo PMPE : Puntaje máximo de la propuesta económica.1. Si faltase uno o más documentos exigidos. Al resto de propuestas se le asignará puntaje inversamente proporcional. Este puntaje total será calculado hasta el tercer decimal.1 El Comité Especial. se descalificará la propuesta económica cuyo monto sea inferior al 90% del valor referencial. 084-2004-PCM). se devolverá al Postor conjuntamente con el primer sobre. 1.
entregará una Carta Fianza o Póliza de Caución de Fiel Cumplimiento del Contrato que garantizará las penalidades por mora y el incumplimiento del Contrato. constituidas por las respectivas cartas fianzas o pólizas de caución emitidas por una entidad bancaria.19 DE LAS GARANTIAS GARANTÍA DE FIEL CUMPLIMIENTO El postor que resultase ganador. apertura de propuestas.. 219° del Reglamento de la Ley de Contrataciones y Adquisiciones del Estado. como requisito indispensable para poder suscribirlo. de acuerdo a lo estipulado en el Art. la misma que debe de estar dentro del ámbito de supervisión de la Superintendencia de Banca y Seguros y. 1. 132° del Reglamento de la Ley.1. el Comité Especial procederá a otorgar la Buena Pro a la propuesta ganadora. solidaria. antes de la suscripción del contrato.20 DEL INGENIERO RESIDENTE En Aplicación del artículo 242° del Reglamento de la Ley de Contrataciones y Adquisiciones del Estado. será especificada en el Acta correspondiente y será suscrita por los miembros del Comité Especial.A. en el mismo día de la firma del Contrato presentará la propuesta del Ing.A. Esta garantía será por un monto equivalente al diez por ciento del monto del Contrato.A. hasta la amortización total de los adelantos otorgados. y por la naturaleza de la presente Obra.18. Residente de Obra el cual será un ingeniero con no menos de 03 años de ejercicio 13
. En la fecha señalada en las bases. Esta Garantía de Fiel Cumplimiento de Contrato deberá ser extendida a favor de Electrosur S. las mismas que deben estar dentro del ámbito de supervisión de la Superintendencia de Banca y Seguros y. entregará los adelantos solicitados por el contratista. irrevocables y de realización automática al solo requerimiento de Electrosur S.18. solidarias. GARANTÍA POR ADELANTOS De conformidad al Art. el ganador de la Buena Pro. irrevocable y de realización automática al solo requerimiento de Electrosur S. y deberá tener vigencia hasta la aprobación de la liquidación final. Electrosur S. incondicionales.3 El proceso de presentación. incondicional. constituida por una carta fianza o póliza de caución emitida por una entidad bancaria con sede en la ciudad de Tacna. debe ser sin beneficio de excusión. previa entrega de una garantía emitida por idéntico monto y un plazo mínimo de vigencia de tres meses.. 1. Estas Garantías deberán ser extendidas a favor de Electrosur S. 1.4 El otorgamiento de la Buena Pro se realizará en acto público.A.A. renovable trimestralmente por el monto pendiente de amortizar. evaluación y el otorgamiento de la Buena Pro. deben ser sin beneficio de excusión.
será evaluada por Electrosur S.
. en la fecha en que se procede a la identificación y verificación del lugar o lugares donde se ejecutará la obra. entregará a éste. adjuntando el certificado de habilidad del referido profesional expedida por el Colegio de Ingenieros. a fin de ser aceptado o cambiado por otro profesional. los adelantos que se establecen en las presentes Bases y siempre que el Contratista los solicite oportunamente de acuerdo a lo siguiente: Días útiles para la solicitud de adelantos: Adelanto en efectivo (directo) en el mismo día de la firma del Contrato Adelanto de Materiales en el mismo día de la firma del Contrato Días útiles para la cancelación de los adelantos: Adelanto directo siete (07) días luego de la fecha de la firma del contrato. la Gerencia de Proyectos y Obras de Electrosur S.A.23 DEL CALENDARIO VALORIZADO El ganador de la Buena Pro en el mismo día de la firma del Contrato presentará los documentos indicados en el inciso 3) del artículo 239° del Reglamento de la Ley de Contrataciones y Adquisiciones del Estado. se abrirá el Cuaderno de Obra.A. Adelanto de materiales siete (07) días luego de la fecha de la firma del contrato.profesional. 1. a solicitud del Contratista. La Entidad Contratante. la referida propuesta respecto al Ing° Residente. 1.22 CUADERNO DE OBRA Para los fines de aplicación del Artículo 253° del Reglamento de la Ley de Contrataciones y Adquisiciones del Estado. 229º y 230º del Reglamento de la Ley de Contrataciones y Adquisiciones del Estado.24 DE LOS ADELANTOS Se ceñirá a lo dispuesto por los Artículos 219º. dentro del plazo máximo de siete (07) días útiles posteriores a la firma del contrato. 228º. designará al Profesional que se encargará de la inspección de la Presente Obra. 1.21 INSPECTOR DE OBRA En Aplicación del artículo 247° del Reglamento de la Ley de Contrataciones y Adquisiciones del estado. 1. El Cuaderno de Obra será presentado por el contratista y una vez abierto será ubicada en la oficina de la Obra bajo las condiciones más convenientes para las anotaciones de la ocurrencia de la presente Obra.
Se anexará a la valorización las hojas de sustentación de los metrados correspondientes a las partidas valorizadas incluyendo los croquis o dibujos correspondientes. 1. comienza a regir a partir desde el día siguiente que se cumplan las condiciones establecidas del Articulo 240º del Reglamento de la Ley de Contrataciones y Adquisiciones del Estado DE LAS VALORIZACIONES 1.S. el trámite y obtención de las Licencias.
1. autorizaciones.27 LICENCIAS AUTORIZACIONES y PERMISOS En aplicación del artículo 211° del reglamento de la Ley de Contrataciones y Adquisiciones del Estado y por la naturaleza de la presente Obra. CONDICIONES IMPORTANTES Según el porcentaje del avance físico de la Obra. fondo de garantía. etc. contado desde la oportunidad en que debió efectuarse.2 Las valorizaciones por concepto de contrato principal.3 A partir del vencimiento del plazo establecido en el Contrato para la cancelación de las valorizaciones.1 En aplicación del Art. las valorizaciones serán mensuales y serán según los metrados ejecutados con los precios unitarios del presupuesto del Valor Referencial afectado por el factor de relación. 1. adicionales y otros. Suma y saldos acumulados.26.26. 255° del Reglamento de la Ley de Contrataciones y Adquisiciones del Estado.26.25
COMPUTO DEL PLAZO DEL CONTRATO El plazo de duración del Contrato de la Obra. En las valorizaciones se consignará lo siguiente: Monto bruto valorizado.28
. N° 084-2004-PCM). permisos y similares estará a cargo del Contratista. Reajustes (el reajuste de precios se efectuará según el Sistema de Formulas Polinómicas de acuerdo al régimen legal vigente). serán canceladas de acuerdo a lo estipulado en el contrato respectivo y tendrán el carácter de pagos a cuenta. Amortizaciones y Deducciones (por adelanto directo y adquisición de materiales. el Contratista tendrá derecho al pago de los intereses conforme a lo establecido por el Código Civil.1. 1. de conformidad a lo dispuesto en el artículo 255º del Reglamento de la Ley de Contrataciones y Adquisiciones del Estado (D.) Monto liquido a pagarse. el Contratista presentará el documento emitido por la entidad correspondiente sobre la tenencia de una Carta Fianza o Póliza de Caución de Garantía por las Indemnizaciones de 15
en cumplimiento de lo establecido en el Art. contratación. Tacna. Electrosur S. ejecución y recepción de obra. 084-2004-PCM). El ganador de la Buena Pro se compromete a que el personal de obra estará debidamente uniformado y contará con sus respectivos implementos de seguridad. Todos los demás aspectos relativos al presente proceso de selección. El primer día del montaje electromecánico el contratista dará una charla a su personal de obra sobre aspectos de seguridad y riesgo eléctrico. 222° del Reglamento de la ley de Contrataciones y Adquisiciones del Estado (D. Octubre del 2005. deberán contar con Garantía de Calidad de los fabricantes y será obligatorio el cumplimiento de suministro de materiales y equipos ofertados. señalando una fecha que no excederá a los diez (10) días siguientes a la fecha de consentida la buena pro. así como las que se pudieren derivar de la ejecución o interpretación del correspondiente contrato. del Reglamento de la Ley de Contrataciones y Adquisiciones del Estado. considerando lo establecido en el Reglamento de la Ley de Contrataciones y Adquisiciones del Estado (Ley Nº 26850). citará al contratista para la firma del Contrato con cinco (5) días de anticipación. La custodia de los materiales y equipos que suministrará el contratista será de responsabilidad del contratista desde el inicio de la obra hasta la fecha de la firma del Acta de Recepción de Obra.A. así mismo le corresponderá la contratación de todos los seguros necesarios para resguardar la integridad de la prestación. Las controversias derivadas del presente concurso. ésta se efectuará según las sanciones establecidas en el Art.29
SUSCRIPCION DEL CONTRATO El Contenido del Contrato será elaborado de acuerdo a la Proforma del Contrato que forma parte de las presentes Bases y las Especificaciones. 203° del Reglamento de la Ley de Contrataciones y Adquisiciones del Estado. En caso de aplicarse las penalidades por atraso en la entrega de la obra.A..
1. Los materiales serán técnicamente aceptados por Electrosur S. de conformidad con lo establecido en el Capítulo IV: Solución de Controversias. con el debido control de calidad.-
Servicios y Pagos Vacacionales de sus servidores por las obras ejecutadas y/o en ejecución. no contemplados en estas Bases se regirán por la Ley y el Reglamento de la Ley de Contrataciones y Adquisiciones del Estado. se resolverán mediante procedimiento administrativo.
0832004-PCM Y SU REGLAMENTO APROBADO POR D. CONFORME AL ART. QUE ES RESPONSABLE DE LA VERACIDAD DE LOS DOCUMENTOS E INFORMACION QUE PRESENTA PARA EFECTOS DEL PROCESO. ASÍ COMO EN LA LEY N° 27444. QUE SE COMPROMETE A MANTENER SU OFERTA DURANTE EL PROCESO DE SELECCIÓN Y A SUSCRIBIR EL CONTRATO EN CASO DE RESULTAR FAVORECIDO CON LA BUENA PRO. y QUE CONOCE LAS SANCIONES CONTENIDAS EN LA LEY DE CONTRATACIONES Y ADQUISICIONES DEL ESTADO APROBADO POR D.S. 9° DE LA LEY.104 -2005-ES DECLARAMOS BAJO JURAMENTO. 084-2004-PCM. CONDICIONES Y PROCEDIMIENTOS DEL PROCESO DE SELECCIÓN. que es de nuestro conocimiento lo siguiente: QUE N0 TIENE IMPEDIMENTO PARA PARTICIPAR EN EL PROCESO DE SELECCIÓN NI PARA CONTRATAR CON EL ESTADO. en nombre de la empresa que representamos. LEY DEL PROCEDIMIENTO ADMINISTRATIVO GENERAL Tacna.ANEXO Nº 1 DECLARACION JURADA ADJUDICACION DE MENOR CUANTIA N° AMC. de del 2005
---------------------------------------------------------------------FIRMA Y SELLO DEL REPRESENTANTE LEGAL
. ACEPTA Y SE SOMETE A LAS BASES.S. QUE CONOCE.
RAZON SOCIAL DEL POSTOR: DOMICILIO LEGAL: INSCRIPCION EN REGISTROS PUBLICOS (cuando corresponda): TELEFONO: FAX : E-MAIL:
NOMBRE DEL REPRESENTANTE LEGAL: NUMERO DNI: NUMERO RUC:
6. 4. En mi calidad de Representante Legal de la…………………………………………… ……………………………………DECLARO BAJO JURAMENTO que los datos consignados en el presente formulario se sujetan a la verdad.3.-
FECHA DE INICIO DE ACTIVIDADES DECLARAMOS:
No ser Empleado Público ni estar impedidos de contratar con el Estado. De conocer y estar de acuerdo con las condiciones estipuladas en las Bases Administrativas y Especificaciones Técnicas de la Adjudicación de Menor Cuantia. De someternos al Fuero Judicial de la Provincia de Tacna. de 2005
---------------------------------------------------------------------NOMBRE Y FIRMA DEL REPRESENTANTE LEGAL
.7. Departamento Tacna.ANEXO Nº 2 DECLARACION JURADA DE INFORMACION EMPRESARIAL ADJUDICACION DE MENOR CUANTIA N° AMC-104-2005-ES
1. Tacna.2.
030-2000-MITINCI.ANEXO N° 3 DECLARACION JURADA DE SER UNA PEQUEÑA O MICROEMPRESA ADJUDICACIÓN DE MENOR CUANTIA N° AMC-104-2005-ES DECLARO BAJO JURAMENTO. 27268 Ley de la Pequeña y Microempresa y su reglamento D.S. que es una pequeña o Microempresa de acuerdo con lo establecido en la Ley Nro.
FIRMA Y SELLO DEL REPRESENTANTE (LEGAL) PERSONA NATURAL O JURIDICA
. Nro.
Tacna. en nombre de la empresa que represento.
en nombre de las Empresas que representamos. que de obtener la buena pro formalizaremos el consorcio ofrecido. aprobado por Decreto Supremo Nro.Nro.del 2005
FIRMA Y SELLO DEL REPRESENTANTE LEGAL DE LA EMPRESA “A”
FIRMA Y SELLO LEGAL DEL REPRESENTANTE LEGAL DE LA EMPRESA “B”
. al señor……………………………………identificado con ……………….ANEXO N° 4 PROMESA DE CONSORCIO ADJUDICACION DE MENOR CUANTIA N° AMC-104-2005-ES DECLARAMOS BAJO JURAMENTO. ………………de …………………. ………………………
Tacna. designando como representante común para los efectos de lo dispuesto en el Artículo 37° del Texto Unico Ordenado de la Ley de Contrataciones y Adquisiciones del Estado. 083-2004-PCM..
ofertamos ..ANEXO Nº 5 “PROPUESTA DEL PLAZO DE EJECUCION” ADJUDICACION DE MENOR CUANTIA N° AMC -104-2005-ES Señores: ELECTROSUR S. Atentamente.. transporte.Referencia : ADP-2005-ES
Por el presente en atención a las Bases de la presente Adjudicación de Menor Cuatia.A..A...
------------------------------Sello y Firma del Postor
.. suministro de los mismos.. días calendarios para la ejecución de la obra “SISTEMA DE ANILLADO EN REDES PRIMARIAS EN 10 KV – MOQUEGUA”. pruebas y puesta en servicio a satisfacción de Electrosur S. montaje electromecánico. Calle Zela 408 TACNA. estando comprendido el control de calidad de materiales.
. CALLE ZELA 408 – TACNA PRESENTE.. transporte... Adjunto al presente hago llegar los presupuestos en forma similar a los cuadros del Valor Referencial. que incluye.A... Atentamente. ofertamos la suma de S/... para la ejecución de la obra “SISTEMA DE ANILLADO EN REDES PRIMARIAS EN 10 KV – MOQUEGUA”..A..
... suministro de materiales.Referencia : ADP-2005-ES
Por el presente en atención a las Bases de la presente Adjudicación de Menor Cuantia.....ANEXO Nº 6 “PROPUESTA ECONOMICA” ADJUDICACION DE MENOR CUANTIA N° AMC -104-2005-ES Señores: ELECTROSUR S.... (en letras y números) Nuevos Soles incluido el IGV... pruebas y puesta en servicio a satisfacción de Electrosur S. montaje...
ANEXO N° 07 VALOR REFERENCIAL ADJUDICACION DE MENOR CUANTIA N° AMC -104-2005-ES
....... representada por su Representante Legal .)... N° 00419486 que en adelante se denominará "ELECTROSUR S............. y su Gerente Administrativo Financiero Licenciado Walter Bolaños Gandolfo con D... PARA EL SUMINISTRO Y MONTAJE DE LA OBRA : “SISTEMA DE ANILLADO EN REDES PRIMARIAS EN 10 KV – MOQUEGUA” Conste por el presente documento el contrato de obra que celebran de una parte ELECTROSUR S. ANTECEDENTES......... El Proyecto se encuentra incluido en el Programa de Inversiones de Electrosur S. para el año 2005. con RUC Nº . ES-C-2005
CELEBRADO ENTRE ELECTROSUR S. Jorge Rivadeneira Gamero con D. El Valor Referencial referido al mes de octubre del 2005 asciende a la suma de S/......... d/c...2
OBJETO El objeto del presente contrato es para la ejecución de la obra: “SISTEMA DE ANILLADO EN REDES PRIMARIAS EN 10 KV – MOQUEGUA” que incluye el suministro de materiales..............23 Nuevos Soles incluido el IGV..E..... por un monto de .......A.
...A Y LA FIRMA.-
PROFORMA DEL CONTRATO CONTRATO No... El Órgano Encargado en fecha ………… mediante ………. con L...... transporte......I......... MODALIDAD..
1..." y de otra parte El Contratista. Nº.A. ANTECEDENTES a.. b.. con domicilio en.N.3... debidamente representada por su Gerente General Ing........A.. y puesta en servicio a satisfacción de Electrosur S.... NUEVOS SOLES (S/. incluido IGV y para un plazo de ejecución de ....... c. con domicilio Legal en .................... montaje.. OBJETO. BASE
1...N.... otorgó la Buena Pro a la firma ..I.2.............. 87 744.... con domicilio en la calle Zela Nº 408 de esta ciudad..: Empresa Regional de Servicio Público de Electricidad..
MODALIDAD La modalidad del presente concurso es por el sistema a Precios Unitarios.. con RUC Nº 11920594...... a quien en adelante se denominará "EL CONTRATISTA" en los términos y condiciones siguientes: CLÁUSULA PRIMERA: LEGAL 1.1. N° 07952188.A.....
.. previa aprobación del avance de obra del Supervisor de la obra....S.1.. Bases integradas. previa presentación de una Carta Fianza o Póliza 25
. Ley del Presupuesto del Sector Público para el 2005
CLAUSULA SEGUNDA : PARTES INTEGRANTES DEL CONTRATO En aplicación del Art. N° 083-2004-PCM TUO de la Ley de Contrataciones y Adquisiciones del Estado D.. el Jefe del Departamento de Obras y de la Gerencia de Proyectos y Obras..CON /100 NUEVOS SOLES (S/.S. y cancelados al CONTRATISTA de acuerdo a valorizaciones.. Aviso de Convocatoria. Oferta ganadora (Contenido de los sobres N º1 y N º2).2 FINANCIAMIENTO La ejecución de los trabajos serán financiados con recursos propios de la Empresa ELECTROSUR S.). FORMAS DE PAGO Y ADELANTOS 3. FINANCIAMIENTO... Reglamento de la Ley de Contrataciones y Adquisiciones del Estado.. las partes integrantes del presente contrato son: Texto del presente Contrato..S.A.. 3. N° 084-2004-PCM. Proforma del Contrato.. etc.). un adelanto directo hasta el 20 % del monto del Contrato vigente de acuerdo a las Bases de la presente Adjudicación de Menor Cuantia.A abonará a solicitud del Contratista.
BASE LEGAL D. 3.4.. (Bases.. Consultas. expediente técnico.. N° 083-2004-PCM y D.3 FORMA DE PAGO Los pagos serán tramitados por ELECTROSUR S. Incluido el IGV.
CLÁUSULA TERCERA: MONTO DEL CONTRATO. N° 084-2004-PCM. Las valorizaciones serán procesadas de acuerdo al D.. .4 ADELANTOS ELECTROSUR S.A.1 MONTO DEL CONTRATO El monto total del Contrato por la ejecución de la obra señalada en la cláusula primera asciende a la suma de ...S. 201° del Reglamento de la Ley de Contrataciones y Adquisiciones del Estado.. 3.
. CLÁUSULA CUARTA: PLAZO DE EJECUCIÓN
El plazo de ejecución es de .. deficiencia en los métodos de trabajo. a favor de ELECTROSUR S. de acuerdo con las bases de la presente Adjudicación de Menor Cuantia podrá establecer adelantos para la Adquisición de Materiales. días calendarios vigentes a partir de la fecha en que se cumplan las condiciones establecidas en las bases. que tenga las características de solidaria. ELECTROSUR S. los que en conjunto no deberán superar el 40% del monto del Contrato vigente de acuerdo al Reglamento de la Ley de Contrataciones y Adquisiciones del Estado. con las características de solidaria. por un valor igual al monto del Adelanto.. conforme al artículo 240° del D. irrevocable. por un valor igual al monto del Adelanto.. artículos N° 219° y 243°.. CLÁUSULA QUINTA: INSPECCION DE LA OBRA
La Administración de la obra estará a cargo del Departamento Obras de la Gerencia de Proyectos y Obras de ELECTROSUR S.
La Carta Fianza o Póliza de Caución será otorgada por una entidad Bancaria con sede en la ciudad de Tacna. N° 084-2004-PCM (Base legal del contrato). La solicitud del contratista estará conformada por: Carta de solicitud del adelanto del contratista Solicitud de cotización del Contratista al proveedor de materiales Cotización del proveedor de materiales al contratista Orden de Compra Copia de la factura del Proveedor de materiales al contratista Carta Fianza o Póliza de Caución Factura del Contratista a ELECTROSUR S.S. materiales y/o insumos. La Gerencia de Proyectos y Obras designará al Ingeniero Supervisor o Inspector de Obra.A. incondicional.A.
. de realización automática y sin beneficio de excusión. extendida a favor de Electrosur S.A. insumos o servicios puestos a disposición del objeto del contrato. previa aceptación de Electrosur S.. incondicional. según Reglamento de la Ley de Contrataciones y Adquisiciones de Estado. en general causas imputables al contratista.A.A. irrevocable. de realización automática y sin beneficio de excusión. insuficiente capacidad o mala calidad del equipo. artículos N° 219° y 243°.de Caución emitida por una entidad bancaria con sede en la ciudad de Tacna. del fabricante propuesto por la firma contratista y solicitud del contratista. incumplimiento en los Plazos de adquisición de materiales. No se autorizará ninguna prórroga en el Plazo de Ejecución de la Obra por interrupciones o atrasos que puedan ser originadas por falta de personal calificado o deficiencia técnica del mismo.A..
Entregar el calendario de avance de obra valorizado en concordancia con el cronograma de desembolsos establecidos y sustentado en la programación de obra PERT-CPM concordante con el plazo.2
EL CONTRATISTA el mismo día de la firma del contrato solicitará los adelantos correspondientes. leyes sociales y otros gastos que sean necesarios para la ejecución total de la obra hasta su puesta en operación. Entregar el calendario de adquisición de materiales e insumos necesarios para la ejecución de obra en concordancia con el calendario de obra valorizado.
6.1. Asimismo.CLÁUSULA SEXTA: 6.4 6. Designar al residente de obra.1.5
. la razón social del proveedor al momento de la solicitud del adelanto y para el correspondiente trámite la aceptación de la entidad conforme a la cláusula tercera del presente contrato. caso contrario se darán por no presentados oportunamente. leyes. la misma que deberá ser presentada.3
EL CONTRATISTA declara que conoce los Reglamentos. A la firma del contrato.1. salvo autorización expresa escrita de ELECTROSUR S.1 EL CONTRATISTA declara haber examinado toda la documentación relacionada con el objeto del contrato y reconoce que no tendrá derecho a reclamar ningún pago adicional a título de mal entendimiento de las mismas ó razón similar. en caso de requerir el Adelanto para Adquisición de Materiales. dirección técnica. Resoluciones y Ordenanzas aplicadas a este tipo de Contrato y declara expresamente que dentro del monto del contrato.1.
6.1. equipo.
6. insumos y equipos necesarios para la ejecución de la obra.A.1
DEL CONTRATISTA 6. EL CONTRATISTA esta obligado a proveerse con la debida anticipación de los materiales. el CONTRATISTA presentará la documentación solicitada en la Bases y los siguientes requisitos adicionales de acuerdo al artículo 239° del Reglamento de la Ley de Contrataciones del Estado: Presentar la Constancia de capacidad libre de contratación expedida por el Registro Nacional de proveedores. quedan comprendidos específicamente mano de obra calificada. deberá especificar. gastos generales. EL CONTRATISTA no podrá transferir parcial o totalmente el presente contrato. utilidades.
. en coordinación con el Ingeniero Inspector. caso contrario el exceso de tiempo será de responsabilidad económica del contratista. 6.) debidamente inventariados a los almacenes de ELECTROSUR S.1...5 del presente Contrato. más un (1) diskette con el contenido de los trabajos. indicando la fecha de culminación y adjuntando dos ejemplares del expediente técnico de la obra ejecutada conformada por Memoria Descriptiva. presentará cuatro (4) copias del Expediente Técnico de la obra ejecutada y el correspondiente original.....1.A.9
6. EL CONTRATISTA mediante comunicación escrita solicitará a la entidad la recepción de la obra.Asimismo cuando se ejecuten trabajos con corte de energía el contratista deberá ejecutar dicho trabajo en el tiempo programado y aprobado por la inspección.2. N° 084-2004-PCM.6 EL CONTRATISTA para el inicio del trámite de las Valorizaciones.S.S.7
6.12 EL CONTRATISTA luego de concluida la obra.1.11 EL CONTRATISTA a la firma del contrato presentará la Carta Fianza o Póliza de Caución de Garantía de Fiel Cumplimiento de Contrato por la suma de S/..1.
6.. EL CONTRATISTA una vez superada el numeral 6. los cuales serán indispensables para dar cumplimiento al artículo 268° del D.. 6.S.. conjuntamente con la liquidación del contrato.1.1. la Carta Fianza o Póliza de Caución de garantía por las indemnizaciones de servicios y pagos de vacacionales de sus servidores. el documento que sustente estar al día con las obligaciones a favor de entidades de Seguridad Social.. 6.. N° 084-2004-PCM (Base legal del contrato). 255° del D. N° 084-2004PCM .. se obliga mantener en Obra en forma permanente al Ingeniero Residente.
... .1.S.8
6. así como el seguro complementario de trabajo de riesgo y posteriormente se cancelará de acuerdo al Art. presentará el Metrado de Avance de Obra el último día de cada mes. deberá devolver los materiales sobrantes de obra (materiales desmontados y sí hubiera materiales suministrados por Electrosur S.10 EL CONTRATISTA dará todas las facilidades que requiera el Inspector para la Inspección de las Obras. N° 084-2004-PCM (Base legal del contrato) EL CONTRATISTA luego de la recepción de la obra por parte del Comité de Recepción de Obra. Especificaciones Técnicas...A. 215° del D. válida por 90 d/c y en las condiciones establecidas en al Art. Inventario y Planos. de acuerdo al artículo 269° del D..
6.13 EL CONTRATISTA se obliga la custodia en obra. 6.A. procederá a la devolución de la Carta Fianza o Póliza de Caución de Fiel Cumplimiento de Contrato a partir de la liquidación del contrato. 6. ELECTROSUR S.4
6. a través de la Gerencia de Proyectos y Obras. el Departamento de Obras y su Ingeniero Inspector serán quienes velarán por el cumplimiento del presente contrato.2.2. ELECTROSUR S.1 ELECTROSUR S. ELECTROSUR S.2 6.2.A.A donde se realicen los trabajos. 6.3 6. de los materiales y/o equipos suministrados y las instalaciones de Electrosur S.2. efectuará la inspección o supervisión de la Obra sobre la base del Calendario de Avance de Obra.2.A.2 DE ELECTROSUR S.6
. se obliga a entregar al Contratista los formatos (cuadros) para la Liquidación del Contrato.2.A.15 EL CONTRATISTA durante el periodo de ejecución de obra cuando observe alguna deficiencia o requiera aclaración deberá presentar el detalle técnico con la alternativa de solución para el análisis y respuesta. ELECTROSUR S. EL CONTRATISTA asumirá con cargo a sus gastos generales el costo de los pasajes y estadía del Profesional designado por la Entidad para la realización del Control de Calidad de Materiales cuando el contratista suministre materiales del o los fabricantes ubicados fuera del Departamento de Tacna. aceptando al profesional que le parezca conveniente previa evaluación.3 del presente contrato.1.1.
6.1.14 EL CONTRATISTA deberá proveer a sus trabajadores uniformes de trabajo con su respectivo logotipo y los implementos de seguridad necesarios para la ejecución de la obra.A. evaluará al Ingeniero Residente tomando en cuenta sus antecedentes. de acuerdo a lo señalado en el Ítem 3.A cancelará las valorizaciones de avance de obra. en forma permanente en el periodo de ejecución de la obra hasta la firma del Acta de Recepción de Obra.A.6. ELECTROSUR S.
CLÁUSULA SETIMA: 7. N° 084-2004-PCM.1 Si el Contratista o su representante no concurrieran en la fecha señalada para la identificación y verificación del lugar o lugares donde se ejecutará la obra. 267° del D.2
. jornales. etapa o lote que debió ejecutarse. la Entidad Contratante tendrá derecho a rescindir el Contrato.S. Por incumplimiento de las condiciones y obligaciones contenidos en las cláusulas del presente Contrato.A. Si el Contratista no desarrolla los trabajos de acuerdo al Expediente Técnico y el Calendario de Avance de Obra. En el caso de retraso injustificado en la ejecución de las prestaciones objeto del contrato. Incumplimiento de pago de Honorarios. tramo.S. 225° del D. CLÁUSULA OCTAVA: SANCIONES
De conformidad al D. hasta por un monto máximo equivalente al diez por ciento (10%) del monto contractual. pese a haber sido requerido para corregir tal situación. beneficios sociales a su personal. N° 084-2004-PCM.S.y cuando se presenten los siguientes casos: a) b) c) e) f) Incumplimiento injustificado de los plazos de inicio. Esta penalidad será deducida de los pagos a cuenta. la Entidad le aplicará al contratista una penalidad por cada día de atraso. Paralización o reducción injustificadamente de la ejecución de la obra. la Entidad Contratante fijará una nueva fecha por Carta Notarial.1
IMPUTABLES AL CONTRATISTA La entidad contratante podrá practicar la resolución Contrato.2 IMPUTABLES A ELECTROSUR S. N° 084-2004-PCM. artículo N° 227° del Reglamento de la Ley de Contrataciones y Adquisiciones del Estado. 7. comunicando esta decisión al CONSUCODE y mediante Carta Notarial al Contratista. o. en los casos establecidos en el Art.
Consecuentemente será de aplicación lo establecido en el Art. de ejecución de la obra o de cualquier estipulación contractual o disposición legal y/o reglamentaria sobre la materia. con una anticipación no menor de tres (3) días. Por incumplimiento de las obligaciones y condiciones contenidas en las cláusulas del presente contrato que ameriten su resolución. del item. del pago final o en la liquidación 30
8. y de cualquier otro pago a terceros relacionados con el contrato. Si en esta nueva fecha el Contratista o su representante tampoco concurriera. de ser el caso. Reglamento de la Ley de Contrataciones y Adquisiciones del Estado 8. sueldos.
N° 084-2004-PCM).10 x Monto del Contrato F x Plazo en días. CLÁUSULA NOVENA: 9.
Donde F tendrá los siguientes valores: Para plazos menores o iguales a sesenta (60) días.15
Cuando se llegue a cubrir el monto máximo de la penalidad. su Reglamento (D. rigen las disposiciones y estipulaciones consignadas en las bases que forman parte del presente contrato y a las disposiciones legales que le son de aplicación. N° 0832004-PCM). la Entidad podrá resolver Contrato por incumplimiento.3
JURISDICCION CONTRACTUAL Las partes se someten expresamente a la jurisdicción de los jueces de Tacna.S.
9. precisando que no existe ninguna relación de orden laboral entre ELECTROSUR S.
9.A. Código Civil y Disposiciones Legales Vigentes. la penalidad se aplicará y calculará de acuerdo a la siguiente fórmula: Penalidad Diaria = 0. servicios y ejecución de obras: F = 0.4
DISPOSICIONES LEGALES QUE GOBIERNAN ESTE CONTRATO Además de lo especificado en este contrato. En todos los casos.40 Para plazos mayores a sesenta (60) días: * para obras: F = 0. y el Contratista. para bienes. o si fuere necesario se cobrará del monto resultante de la ejecución de las garantías a que se refieren los artículos 215º y 216º del Reglamento. rigiéndose el presente contrato a lo establecido por la Ley de Contrataciones y Adquisiciones del Estado (D.2
RELACIÓN ENTRE EL CONTRATISTA Y ELECTROSUR S.A Las partes reiteran que el contratista cancelará oportunamente las remuneraciones que le corresponden a sus servidores. Directivas y Disposiciones del FONAFE.1 DISPOSICIONES FINALES
VIGENCIA DEL CONTRATO Desde la fecha de consentido el inicio de la obra hasta la culminación del tiempo establecido en la cláusula cuarta.final.S. así como todos sus beneficios y derechos laborales de ley.
9.. del 2005...5
CAMBIO DE DOMICILIO El cambio de domicilio que pudiera ocurrir por parte del Contratista.
--------------------Contratista
-----------------------------------------Gerente Administrativo Financiero Electrosur S.).. será comunicado notarialmente a ELECTROSUR S.... de acuerdo a lo previsto en el Reglamento de la Ley de Contrataciones del Estado (D. Aviso de Convocatoria.A.... N° 084-2004-PCM).A. Consultas... CLÁUSULA DECIMA PRIMERA: RELACIÓN DE ANEXOS
Anexo al texto del presente Contrato se encuentran los siguientes documentos: Bases integradas (Bases...A POR EL CONTRATISTA
----------------------Gerente General Electrosur S...S.
Las partes acuerdan que cualquier controversia o reclamo que surja o se relacione con la ejecución y/o interpretación del presente Contrato.... ELECTROSUR S. Contenido de los Sobres Nº 2 de la oferta ganadora Estando las partes celebrantes conforme con las cláusulas precedentes se procede a firmar el presente contrato en quintuplicado en la ciudad de Tacna. a los ... será resuelto mediante procedimiento administrativo. Proyecto.. etc.....A.... Proforma del Contrato.
. días del mes de .. Contenido de los Sobres Nº 1 de la oferta ganadora..
PARTE II EXPEDIENTE TÉCNICO
debiendo el contratista ejecutar la obra a satisfacción de Electrosur S.I.2 CONDICIONES AMBIENTALES
La zona de trabajo presenta una superficie con una ligera pendiente.
1.3 AREA DE INFLUENCIA DEL PROYECTO
1.3.1 INTRODUCCION. 1. durante todo el año. 1. calidad de servicio y seguridad de nuestras instalaciones eléctricas en media tensión en la ciudad de Moquegua. redes primarias Especificaciones técnicas para el suministro de materiales y equipos Especificaciones técnicas para el montaje electromecánico Cálculos Justificativos Metrado y Presupuesto Planos y Detalles 1.3 VIAS DE ACCESO
Las principales vías de acceso son: La carretera Binacional Ilo -Desaguadero-La Paz. La ejecución de la obra comprende el suministro de materiales. equipos. transporte. Las velocidades de los vientos son moderadas.3.m.2 ALCANCES DEL PROYECTO El proyecto comprende: Diseño de instalaciones. – Moquegua”. con la finalidad de mejorar la confiabilidad. tal como se indica: Departamento Provincia Distrito : : : Moquegua.n. MEMORIA DESCRIPTIVA..3. montaje electromecánico.A. pruebas y puesta en servicio.s. de clima cálido. que conecta a la ciudad de
. Mariscal Nieto Moquegua
1. ubicadas a una altura sobre el nivel de mar de aproximadamente 1500 m. El presente expediente técnico denominado “Sistema de Anillado en Redes Primarias en 10 KV. con una temperatura promedio anual de 25°C. sin observación alguna.1 UBICACIÓN GEOGRAFICA El área del proyecto comprende la ciudad de Moquegua. Zona exenta de lluvias. salvo las esporádicas lloviznas similares a las costeras de poca duración. comprende la ejecución de obra de remodelación de redes primarias.
y su ejecución deberá ser encargada a contratistas de experiencia en trabajos de remodelación de redes de primarias. se obliga a entregar esta en condiciones operativas y/o en funcionamiento.80 Km de redes primarias y elementos de ferretería para postes y conductores.Aisladores utilizados . Asimismo.5 : : : : : : : : : 10 kV Aéreo. instalación de 5 pozos.Sistema . será financiada con recursos propias de Electrosur S.1 BASES DE REFERENCIA
Código Nacional de Electricidad Normas Itintec Recomendaciones de la empresa concesionaria
1. así como. indicados en los planos de redes distribución primaria parte del expediente.Tipo Suspensión 1.4.Soportes .4.3 CARACTERISTICAS PRINCIPALES
REDES DE DISTRIBUCION PRIMARIA -Tensión nominal .Tipo PIN .Frecuencia .Moquegua.4 DESCRIPCION DEL PROYECTO
1.4. 35 y 50 mm2 Porcelana ANSI 56-2 Poliméricos de anclaje 25kV
FUENTE DE FINANCIAMIENTO La ejecución de la obra comprendido en el proyecto “Sistema de Anillado en Redes Primarias en 10 KV – Moquegua”.2 DESCRIPCION DE TRABAJOS A EJECUTAR
El proyecto consiste en la ejecución 1.A. 36
. trifásico 60 Hz.Conductores . Los trabajos e efectuar se encuentran indicados en el presente expediente. Para lo cual se realizará la instalación de 03 estructuras de media tensión.Sección nominal . 1. el contratista encargado de la ejecución de la obra. a fin de cumplir con lo indicado en las Leyes y Normas Vigentes al respecto y dentro de los plazos programados. desmontaje y montaje de 3.
1. Postes de concreto armado centrifugado de 12 y 13 m de longitud Aluminio 25.28 Km de redes primarias a fin reducir las pérdidas técnicas y mejorar la confiabilidad en las redes de distribución primaria del Sistema Eléctrico Moquegua.
CAPITULO II ESPECIFICACIONES TECNICAS DE SUMINISTRO DE MATERIALES Y EQUIPOS
3 PROCEDIMIENTO MATERIALES PARA EL CONTROL DE CALIDAD DE 40 °C 15 °C 90 Km/h Moderado 1500 m. debiendo el contratista adjuntar el certificado de garantía del 38
. 2.Primera etapa . deberá constatarse que los materiales cumplan con las especificaciones técnicas de las Normas y prescripciones vigentes. ESPECIFICACIONES TECNICAS DE SUMINISTRO DE MATERIALES Y EQUIPOS...Temperatura máxima en el verano : . que serán adquiridos por el contratista bajo la supervisión técnica de Electrosur S.E. como consecuencia de defectos de diseño y fabricación.Velocidad del viento : .Altitud : 2. Los materiales serán técnicamente aceptados por Electrosur S.Temperatura mínima en el invierno : . 2. entendiéndose que si algún material o equipo resulte inservible dentro del periodo de garantía. por el proceso de Control de Calidad.A.1 INTRODUCCION Las presentes especificaciones técnicas generales y particulares de los diferentes materiales y equipos electromecánicos.Segunda etapa : Inspección visual a los materiales : Pruebas técnicas de acuerdo a Normas técnicas.A. Normas del MINEM vigentes e INDECOPI (EX-ITINTEC).Contaminación ambiental : .II. se basarán en las recomendaciones del C. sin costo alguno para Electrosur S.s.
El acto de Control de Calidad será efectuado en la planta y/o laboratorio del fabricante.A.n.N.m. el contratista y/o proveedor procederá a su reposición. 2.4 RECEPCION La recepción de los materiales se realizará en el lugar de la obra. Todos los equipos y materiales serán instalados teniendo en consideración las Normas mencionadas y para condiciones de operación que se indican: .2 GARANTIA El proveedor y/o el fabricante garantizará que los materiales y equipos funcionen adecuadamente y el periodo de garantía se contará a partir de la Recepción de Obra.
El procedimiento para el control de calidad de materiales estará constituido por: .
sin la presentación de dicho certificado los materiales no serán aceptados. donde: l = longitud en m c = carga de trabajo en daN con coeficiente de seguridad 2 d = diámetro de la cima en mm D = diámetro de la base. cuando estén instalados. tendrán las características y dimensiones que se consignan a continuación. A 3 m de la base del poste. Base Esfuerzo en la punta del poste (daN) Peso del poste (Kg) Descripción Longitud (m Diámetros (mm): . cangrejeras y escoriaciones. libre de fisuras.027 “Postes de Hormigón (Concreto) Armado para Líneas Aéreas”. la información siguiente: a) b) Marca o nombre del fabricante Designación del poste: l/c/d/D.10 m debajo de la cima) y la carga de trabajo será igual o mayor a 2.5 SUMINISTRO DE POSTES DE CONCRETO Los postes materia de la presente especificación. bajo responsabilidad del supervisor encargado. en original. Los postes deberán llevar impresa con caracteres legibles e indelebles y en lugar visible. Punta .fabricante. deberá implementarse una marca que permita inspeccionar la profundidad de empotramiento luego de instalado el poste. Punta . Base Esfuerzo en la punta del poste (daN) Peso del poste (Kg) : : : : : : : : : : 12 160 340 200 940 13 160 355 Características 12 12 160 340 160 340
300 400 1160 1180 Características 13 14 14 160 355 210 210 420 420
300 400 400 500 1350 1370 2050 2100
La relación de la carga de rotura (a 0. Descripción Longitud (m Diámetros (mm): . el acabado exterior deberá ser homogéneo. en bajo relieve. cumplirán con las prescripciones de la norma INDECOPI NTP 339. Serán de concreto armado centrifugados y tendrán forma troncocónica. 2. en mm Fecha de fabricación 39
40 m medido desde la base del poste para caso de postes de media tensión (M.T.Coeficiente de seguridad (Cs) . los postes serán protegidos con pintura impermeabilizante incolora (poliméricos de alto lustre y rápida penetración en el concreto).). y sustancias corrosivas.A.Coeficiente de seguridad (Cs) : : : : (ZA/1. así como sus dimensiones y espaciamientos entre ellos se muestran en las láminas del proyecto.A. antes de la realización de las pruebas.Tiro horizontal (Rx) . provistos de 5 agujeros para espigas de aisladores y pernos de F°G°.6 CRUCETAS Y MENSULAS a) CRUCETA DE CONCRETO Serán de concreto armado vibrado. en una longitud de 2.50/300) 300 kg 150 kg 200 kg 2 1. provistas de agujeros para espigas de aisladores y pernos de cadena de aisladores de las siguientes características: DESCRIPCION . Los instrumentos y equipos a utilizarse en las mediciones y pruebas deberán tener un certificado de calibración vigente expedido por un organismo de control autorizado. lo cuál deberá ser verificado por el representante de Electrosur S.Los agujeros que deben tener los postes. contra la humedad.Tiro vertical (Ry) .Tiro horizontal (Rx) .Tiro longitudinal (Rz) . Asimismo. Las pruebas de recepción de los postes serán las siguientes: · Inspección visual · Verificación de dimensiones · Ensayo de carga · Ensayo de rotura 2. Respecto a pruebas.100/250) 250 kg 150 kg 150 kg 2 40
. a quien se le brindará todos los medios que le permitan verificar que los postes se suministran de acuerdo con la norma indicada en el primer párrafo del numeral 2. siendo sus características las siguientes: DESCRIPCION .Tiro longitudinal (Rz) . en presencia de un representante de Electrosur S.Longitud : : : : : (Z/1. se efectuarán en las instalaciones del fabricante.Tiro vertical (Ry) .50 m
b) MÉNSULAS DE CONCRETO Serán de concreto armado vibrado.
- Longitud c) CRUCETAS METÁLICAS
CRUCETA SIMPLE SIMETRICA DE 1,60 m Serán de perfil de fierro angular galvanizado en caliente por inmersión con 110 micras de espesor mínimo, de 3”x3”x¼x1,60 m de longitud (76,2x76,2x6,35mm x1,60 m), adicionalmente poseerán, dos brazos de F°G° de 2½”x2½”x¼”x 0,75 m de longitud (63,5x63,5x6,35 mm x 0,75 m), una abrazadera circular de 2”x1/4”x210 mm ø (50,8x6,35 mm x 210 mm ø), una abrazadera tipo UM redondo de 5/8” φ ( 16 mm ø) y dos pernos de ½”φx3” (12,7 mm ø x 76,2 mm) incluido arandelas y tuercas. Asimismo, incluirán tres piezas soldadas de fierro angular galvanizado de 3”x3”x¼x80 mm de longitud (76,2x76,2x6,35mm x 80 mm), con la finalidad de permitir la instalación de espigas y/o pernos de F°G° o seccionadores tipo Cut Out. CRUCETA SIMPLE TIPO MENSULA (BRAZO) DE 1,60 m Serán de perfil de fierro angular galvanizado en caliente por inmersión con 110 micras de espesor mínimo, de 3”x3”x¼x1,60 m de longitud (76,2x76,2x6,35mm x1,60 m), adicionalmente poseerán, un brazo de F°G° de 2½”x2½”x¼”x 1,25 m de longitud (63,5x63,5x6,35 mm x 1,25 m), una abrazadera circular de 2”x1/4”x210 mm ø (50,8x6,35 mm x 210 mm ø), una abrazadera tipo UM redondo de 5/8” φ ( 16 mm ø) y un perno de ½”φx3” (12,7 mm ø x 76,2 mm) incluido arandela y tuerca. Asimismo, incluirán tres piezas soldadas de fierro angular galvanizado de 3”x3”x¼x80 mm de longitud (76,2x76,2x6,35mm x 80 mm), con la finalidad de permitir la instalación de espigas y/o pernos de F°G° o seccionadores tipo Cut Out CRUCETA SIMPLE TIPO ASIMETRICA DE 2,40 m Serán de perfil de fierro angular galvanizado en caliente por inmersión con 110 micras de espesor mínimo, de 3”x3”x¼x2,40 m de longitud (76,2x76,2x6,35mm x2,40 m), adicionalmente poseerán, un brazo de F°G° de 2½”x2½”x¼”x 2,25 m de longitud (63,5x63,5x6,35 mm x 2,25 m), una abrazadera circular de 2”x1/4”x210 mm ø (50,8x6,35 mm x 210 mm ø), una abrazadera tipo UM redondo de 5/8” φ ( 16 mm ø) y un perno de ½”φx3” (12,7 mm ø x 76,2 mm) incluido arandela y tuerca. Asimismo, incluirán tres piezas soldadas de fierro angular galvanizado de 3”x3”x¼x80 mm de longitud (76,2x76,2x6,35mm x 80 mm), con la finalidad de permitir la instalación de espigas y/o pernos de F°G° o seccionadores tipo Cut Out
CRUCETA DOBLE TIPO ASIMETRICA DE 2,40 m Serán de perfil de fierro angular galvanizado en caliente por inmersión con 110 micras de espesor mínimo, de 3”x3”x¼x2,40 m de longitud (76,2x76,2x6,35mm x2,40 m), adicionalmente poseerán dos brazos de F°G° de 2½”x2½”x¼”x 2,25 m de longitud (63,5x63,5x6,35 mm x 2,25 m), una abrazadera circular de 2”x1/4”x210 mm φ (50,8x6,35 mm x 210 mm ø), dos pernos de doble armado de 5/8”øx10” de longitud (16 mm ø x 254 mm) incluido cuatro arandelas, tuercas y contratuercas; tres pernos doble armado de 5/8”øx14” de longitud (16 mm ø x 356 mm) incluido seis arandelas, tuercas y contratuercas; dos pernos de ½”øx3” de longitud (12,7 mm ø x 76,2 mm) incluido arandelas y tuercas. Asimismo, incluirán seis piezas soldadas de fierro angular galvanizado de 3”x3”x¼x80 mm de longitud (76,2x76,2x6,35mm x 80 mm), con la finalidad de permitir la instalación de espigas y/o pernos de F°G° o seccionadores tipo Cut Out. CRUCETA SIMPLE TIPO ASIMÉTRICA DE 3,00 m Serán de perfil de fierro angular galvanizado en caliente por inmersión con 110 micras de espesor mínimo, de 3”x3”x¼x3,00 m de longitud (76,2x76,2x6,35mm x3,00 m), adicionalmente poseerán un brazo de F°G° de 2½”x2½”x¼”x 3,10 m de longitud (63,5x63,5x6,35 mm x 3,10 m), una abrazadera circular de 2”x1/4”x210 mm φ (50,8x6,35 mm x 210 mm ø), dos pernos de doble armado de 5/8”øx10” de longitud (16 mm ø x 254 mm) incluido cuatro arandelas, tuercas y contratuercas; tres pernos doble armado de 5/8”øx14” de longitud (16 mm ø x 356 mm) incluido seis arandelas, tuercas y contratuercas; dos pernos de ½”øx3” de longitud (12,7 mm ø x 76,2 mm) incluido arandelas y tuercas. Asimismo, incluirán seis piezas soldadas de fierro angular galvanizado de 3”x3”x¼x80 mm de longitud (76,2x76,2x6,35mm x 80 mm), con la finalidad de permitir la instalación de espigas y/o pernos de F°G° o seccionadores tipo Cut Out. CRUCETA DOBLE TIPO ASIMÉTRICA DE 3,00 m Serán de perfil de fierro angular galvanizado en caliente por inmersión con 110 micras de espesor mínimo, de 3”x3”x¼x3,00 m de longitud (76,2x76,2x6,35mm x3,00 m), adicionalmente poseerán dos brazos de F°G° de 2½”x2½”x¼”x 3,10 m de longitud (63,5x63,5x6,35 mm x 3,10 m), una abrazadera circular de 2”x1/4”x210 mm φ (50,8x6,35 mm x 210 mm ø), dos pernos de doble armado de 5/8”øx10” de longitud (16 mm ø x 254 mm) incluido cuatro arandelas, tuercas y contratuercas; tres pernos doble armado de 5/8”øx14” de longitud (16 mm ø x 356 mm) incluido seis arandelas, tuercas y contratuercas; dos pernos de ½”øx3” de longitud (12,7 mm ø x 76,2 mm) incluido arandelas y tuercas. Asimismo, incluirán seis piezas soldadas de fierro angular galvanizado de 3”x3”x¼x80 mm de longitud (76,2x76,2x6,35mm x 80 mm), con la finalidad de permitir la instalación de espigas y/o pernos de F°G° o seccionadores tipo Cut Out.
CRUCETA DE DERIVACION ASIMETRICA (TD) Será similar a la cruceta simple asimétrica de 1,60 m de longitud 2.7 CAJA REGISTRO PARA PUESTA A TIERRA Será de c.a.v. de 0,40 m de lo lado, con agujeros en cada lado de tal forma que permitan el paso del conductor del sistema de puesta a tierra. La tapa llevará además un jalador metálico. 2.8 ESPECIFICACIONES TECNICAS DE CONDUCTORES DE REDES PRIMARIAS Será de aleación de aluminio, cumplirá con las prescripciones de las siguientes normas: Para inspección y pruebas: IEC 61089 ROUND WIRE CONCENTRIC LAY OVERHEAD ELECTRICAL STRANDED CONDUCTORS IEC 60104 ALUMINIUM-MAGNESIUM-SILICON ALLOY WIRE FOR OVERHEAD LINE CONDUCTORS Para fabricación: ASTM B398 ALUMINIUM ALLOY 6201-T81 WIRE FOR ELECTRICAL PURPOSES ASTM B399 CONCENTRIC-LAY-STRANDED ALUMINIUM ALLOY 6201T81 CONDUCTORS El conductor de aleación de aluminio será fabricado con alambrón de aleación de aluminio- magnesio-silicio, cuya composición química deberá estar de acuerdo con la Tabla 1 de la norma ASTM B 398; el conductor de aleación de aluminio será desnudo y estará compuesto de alambres cableados concéntricamente y de único alambre central; los alambres de la capa exterior serán cableados en el sentido de la mano derecha y las capas interiores se cablearán en sentido contrario entre sí. El conductor deberá ser protegido con una película de PVC ó polietileno, contra la contaminación salina (para evitar la corrosividad) y será del tipo C(AA)PI. El conductor tendrá las características y dimensiones que se indican a continuación: ESPECIFICACIONES DE CABLES DE ALUMINIO
CALIBRE Mm2 N° HILOS DIÁMETRO HIlO kg/km DIÁMETRO CONDUCTOR mm PESO kg/km CARGA DE ROTURA MINIMA kN RESISTENC. ELÉCTRICA Ohm/km CAPACIDAD CORRIENTE A(*)
2,52 3,02 2,15
7,6 9,1 10,8
96 137 190
10,35 14,79 20,71
0,952 0,663 0,484
1 7. de superficie exterior vidriada. sin la necesidad de emplear accesorios o materiales con características distintas a la porcelana.9.Negativa Tensión de perforación Características de radio interferencia: Prueba de tensión eficaz a tierra para interferencia Tensión máxima de radio interferencia a 1000 khz.1 6.Positiva .3 4.Nota (*): Temperatura en el conductor 85°C.0 3.1 6.9 : : : 60.82 kN/mm² 23E-6/°C 0.0 6.6 229 mm 165 mm 432 mm 35 mm 13 kN 110 kV 70 kV 175 kVp 225 kVp 145 kV 22 kV 100 uV
.3 7. El roscado del agujero en el que se alojara la espiga de cabeza de plomo será efectuado sobre la misma porcelana del aislador. cumplirán con las prescripciones de las siguientes normas: ANSI C.2 4.1 AMERICAN NATIONAL STANDARD TEST METHODS FOR ELECTRICAL POWER INSULATORS ANSI C29.6 AMERICAN NATIONAL STANDARD FOR WET-PROCESS PORCELAIN INSULATORS (HIGH-VOLTAGE PIN TYPE) Los aisladores tipo pin serán de porcelana.0 2.2 Clase ANSI Material aislante Norma de fabricación Dimensiones: Diámetro máximo Altura Longitud de línea de fuga Diámetro de agujero para acoplamiento Características mecánicas: Resistencia a la flexión Características eléctricas Tensión de flameo a baja frecuencia: .0 4. temperatura ambiente 40°C.1 4.0 5.00384/°C
ESPECIFICACIONES TECNICAS DE AISLADORES
2. velocidad del viento 2 km/h.1 AISLADORES DE PORCELANA TIPO PIN Los aisladores tipo pin. aislador tratado con barniz semiconductor : : : : : : : : : : : : : : : 56-2 Porcelana ANSI C 29. DESCRIPCION DE CARACTERISTICAS DEL AISLADOR 1.En seco .29.Bajo lluvia Tensión critica de flameo al impulso: .0 7. Modulo de elasticidad Coeficiente de dilatación a 20°C Coeficiente térmico de resistencia 20°C 2.0 4.2 6.4 5.
un perfil diseñado de acuerdo con las recomendaciones de la Norma IEC 815. también hidrófugos de goma de silicón. El recubrimiento y las aletas serán de color gris. libre de imperfecciones y estará firmemente unido al núcleo. cumplirán con las prescripciones de las siguientes normas:
ANSI C29. preferentemente. Recubrimiento del núcleo El núcleo de fibra de vidrio tendrá un revestimiento hidrófugo de goma de silicón de una sola pieza aplicado por extrusión o moldeo por inyección. Aletas aislantes Las aletas aislantes serán.
.11 IEC 1109 IEC 815 ASTM A153 AMERICAN NATIONAL STANDARD FOR COMPOSITE SUSPENSIÓN INSULATORS FOR OVERHEAD TRANSMISSION LINES TESTS COMPOSITE INSULATORS FOR A. sustancias extrañas o defectos de fabricación. Este recubrimiento no tendrá juntas ni costuras. C. presentarán diámetros iguales o diferentes y tendrán. TEST METHODS AND ACCEPTANCE CRITERIA GUIDE FOR SELECTION OF INSULATORS IN RESPECT OF POLLUTED CONDITIONS SPECIFICATION FOR ZINC COATING (HOT DIP) ON IRON AND STEEL HARDWARE
a) CARACTERÍSTICAS TÉCNICAS Núcleo El núcleo será de fibra de vidrio reforzada con resina epóxica de alta dureza.9. por tanto.0 9. resistente a los ácidos y. La resistencia de la interfase entre el recubrimiento de goma de silicón y el cilindro de fibra de vidrio será mayor que la resistencia al desgarramiento (tearing strength) de la Goma de silicón. El núcleo deberá estar libre de burbujas de aire.8. OVERHEAD LINES WITH A NOMINAL VOLTAGE GREATER THAN 1000 V – DEFINITIONS.0
Masa por unidad kg Material del roscado del agujero para la espiga de cabeza de plomo
2. y estarán firmemente unidos a la cubierta del cilindro de fibra de vidrio por moldeo como parte de la cubierta. tendrá un espesor mínimo de 3 mm en todos sus puntos.2 AISLADORES POLIMERICOS TIPO SUSPENSIÓN Los aisladores. tendrá forma cilíndrica y estará destinado a soportar la carga mecánica aplicada al aislador. La longitud de la línea de fuga requerida deberá lograrse con el necesario número de aletas. a la rotura frágil. será uniforme.
TABLA DE DATOS TÉCNICOS AISLADOR POLIMERICO TIPO SUSPENSIÓN 1
2 3 4 5 NORMAS APLICABLES TENSION DE DISEÑO MATERIAL DEL NUCLEO MATERIAL DEL RECUBRIMIENTO DEL NUCLEO MATERIAL DE LAS CAMPANAS IEC-1109. el galvanizado corresponderá a la clase “C” según la norma ASTM A153.POSITIVA 250 kV
.Herrajes extremos Los herrajes extremos para los aisladores de suspensión estarán destinados a transmitir la carga mecánica al núcleo de fibra de vidrio. La conexión entre los herrajes y el núcleo de fibra de vidrio se efectuará por medio de compresión radial.11 36 kV FIBRA DE VIDRIO REFORZADO GOMA DE SILICON GOMA DE SILICON
MATERIAL DE LOS HERRAJES NORMA DE GALVANIZACION HERRAJE EXTREMO DE ESTRUCTURA HERRAJE DEL EXTREMO DE LINEA
ACERO FORJADO O HIERRO MALEABLE ASTM 153 HORQUILLA (CLEVIS) LENGÜETA (TONGUE)
LONGITUD DE LINEA DE FUGA DISTANCIA DE ARCO EN SECO LONGITUD TOTAL DIAMETRO MINIMO DEL NUCLEO NUMERO DE CAMPANAS DIAMETRO DE CADA CAMPANA ESPACIAMIENTO ENTRE CAMPANAS MASA TOTAL
650 mm mm mm mm mm mm mm mm
VALORES DE RESISTENCIA MECANICA
CARGA MECANICA GARANTIZADA (SML) CARGA MECANICA DE RUTINA (RTL)
TENSIONES ELECTRICAS DE PRUEBA
TENSION CRITICA DE FLAMEO AL IMPULSO . de tal manera que asegure una distribución uniforme de la carga alrededor de este último. Los herrajes para los aisladores tipo suspensión deberán ser de acero forjado o hierro maleable. lo cual deberá ser probado por un certificado otorgado por una reconocida entidad certificadora en el país del fabricante. Una copia de este certificado deberá entregarse junto con la oferta. ANSI – 29. b) REQUERIMIENTOS DE CALIDAD El Fabricante deberá mantener un sistema de calidad que cumpla con los requerimientos de la Norma ISO 9001.
Las espigas tendrán una superficie suave y libre de rebabas u otras irregularidades.0 3.NEGATIVA TENSION DE FLAMEO A BAJA FRECUENCIA . La configuración física de las espigas.10
ACCESORIOS DE AISLADORES ACCESORIOS DE AISLADORES TIPO PIN DE PORCELANA Los materiales para la fabricación de las espigas serán de hierro maleable o dúctil.0 Material de fabricación Clase de galvanización Aislador tipo pin con el que se usara Longitud sobre la cruceta Longitud de empotramiento Diámetro de la cabeza de plomo : : : : : : Hierro maleable o acero forjado ASTM B ANSI 56-2 178 mm 178 mm 35 mm 47
. y accesorios se muestran en las láminas adjuntas.0 2. DESCRIPCION DE CARACTERISTICAS 1.0 6. después de su fabricación y antes del vaciado de la rosca de plomo. una contratuerca cuadrada de doble concavidad y una arandela cuadrada plana de 75x75x4.0 5. Las espigas serán galvanizadas en caliente por inmersión con 110 micras de espesor mínimo.17 AMERICAN NATIONAL STANDARD FOR GALVANIZED FERROUS BOLTTYPE INSULATOR PINS WITH LEAD THREADS FOR OVERHEAD LINE CONSTRUCTION ANSI C 135.76 mm. así como sus dimensiones detalladas.21
.BAJO LLUVIA
260 kV 160 KV 100 kV
2. o acero forjado.22 AMERICAN NATIONAL STANDARD FOR GALVANIZED FERROUS POLETOP INSULATOR PINS WITH LEADS THREADS FOR OVERHEAD LINE CONSTRUCTION ANSI B18.2. Cada espiga recta para cruceta deberá ser suministrada con una tuerca cuadrada. Los materiales a utilizarse serán de un grado y calidad tales que garanticen el cumplimiento de las características mecánicas establecidas en las normas señaladas.2 AMERICAN NATIONAL STANDARD FOR SQUARE AND HEX NUTS ASTM A 153 ZINC COATING (HOT DIP) ON IRON AND STEEL HARDWARE UNE 21-158-90 HERRAJES PARA LÍNEAS ELÉCTRICAS AÉREAS DE ALTA TENSIÓN
El roscado en la cabeza de las espigas se hará utilizando una aleación de plomo de probada calidad. Estos accesorios serán suministrados debidamente ensamblados a la espiga y no en forma separada. tal como se detalla en la lámina adjunta.0 4. de una sola pieza.EN SECO . Cumplirán con las siguientes normas:
ANSI C 135.
a) Normas Aplicables Los accesorios materia de esta especificación. El fabricante o proveedor.A. porosidades. Las piezas presentarán una superficie uniforme.0 8. aspecto y acabado La fabricación de los accesorios del conductor se realizará mediante un proceso adecuado.81 kN ANSI C 135. fisuras. acero forjado. bien por la propia naturaleza del material o bien por la aplicación de una protección adecuada. c) Fabricación.7.11. hierro maleable o ductil o.0 9.11
Diámetro de espiga en la parte encima de la cruceta Diámetro de la espiga en la parte del empotramiento Carga de prueba a 10 grados de deflexión Norma de fabricación y prueba
25 mm 19 mm 9.0 2. La elección de los materiales constitutivos de los elementos deberá realizarse teniendo en cuenta que no puede permitirse la puesta en contacto de materiales cuya diferencia de potencial galvánico pueda originar corrosión de naturaleza electrolítica. d) Protección anticorrosiva Todos los componentes de los accesorios deberán ser resistentes a la corrosión. rebabas y cualquier otra alteración del material.0 10. 48
. de una sola pieza. tendrá a disposición de Electrosur S. la documentación que garantice la correspondencia de los materiales utilizados con los ofertados.17
ACCESORIOS DEL CONDUCTOR DE RED PRIMARIA
2. cumplirán con las prescripciones de las siguientes normas:
UNE 21-159 IEC 61897 ASTM 153 ELEMENTOS DE FIJACION Y EMPALME PARA CONDUCTORES Y CABLES DE TIERRA DE LÍNEAS ELECTRICAS AEREAS DE ALTA TENSIÓN REQUIREMENTS AND TEST FOR STOCKBRIDGE TYPE AEOLIAN VIBRATION DAMPERS STANDARD SPECIFICATION FOR ZINC-COATING (HOT-DIP) ON IRON AND STEEL HARDWARE
b) Materiales Los materiales para la fabricación de los accesorios del conductor serán de aleaciones de aluminio procedentes de lingotes de primera fusión. libre de discontinuidades. en el que se incluyan los controles necesarios que garanticen el producto final.
Asimismo. pin y pasador de seguridad. galvanizado en caliente según ASTM A153. sujeto con pernos de ¼”x1 ¼”.Los materiales férreos. con un mínimo de 110 micras de espesor. 2. del tipo premoldeado. arandelas de presión. para cada caso. del tipo compresión y presentarán una resistencia eléctrica no mayor que la de los respectivos conductores. Serán simples y dobles y de longitudes adecuadas para cada sección de conductor. c) Varilla de armar La varilla de armar serán de aleación de aluminio. salvo el acero inoxidable. Las cargas de rotura y deslizamiento mínima para los manguitos de empalme serán como mínimo los siguientes porcentajes de la carga de rotura nominal del cable al que serán destinados: 49
. Estarán libres de todo defecto y no dañarán al conductor luego de efectuada la compresión pertinente. de los efectos abrasivos. tuercas. deberán protegerse en general mediante galvanizado en caliente por inmersión. No emitirá efluvios y perturbaciones radioeléctricas por encima de valores fijados. Tendrá por objeto proteger el punto de sujeción del conductor con el aislador tipo pin o grapa angular. incluye dos pernos en “U”. 50 y 70 mm2.11. así como de las descargas que se puedan producir entre conductor y tierra. la resistencia eléctrica de los accesorios vendrá limitada por lo señalado en esta especificación. 2535. para ser empleados con conductores de cobre de 6-16. por tanto. adecuada para conductor de aleación de aluminio. Deberá garantizar que la resistencia eléctrica del conjunto grapa-conductor no sea superior al 75% de la correspondiente a una longitud igual de conductor. no producirá calentamientos superiores a los del conductor. d) Manguito de empalme Será de cobre ó aleación de cobre.2 CARACTERÍSTICAS ESPECÍFICAS a) Grapa de anclaje tipo pistola Será fabricado de acero del tipo ductil. de acuerdo con la Norma ASTM 153. e) Características eléctricas Los accesorios presentarán unas características de diseño y fabricación que eviten la emisión de efluvios y las perturbaciones radioeléctricas por encima de los límites fijados. b) Conector doble vía Serán de cobre o bronce. El esfuerzo de rotura de la grapa tipo pistola será de 6 800 kg.
2.12.12 ACCESORIOS METALICOS PARA POSTES Y CRUCETAS EN M. g) Alambre de amarre El alambre de amarre será de aluminio recocido de 16 mm². según la versión vigente a la fecha de la convocatoria a concurso:
ASTM A 7 ANSI A 153 ANSI C 135. de alta eficiencia eléctrica e inhibidor contra la oxidación. f) Pasta para aplicación de empalmes El suministro de manguitos de empalme y reparación incluirá la pasta especial que se utilizará como relleno de estos accesorios.1 FORGED STEEL ZINC COATING (HOT DIP) ON IRON AND STEEL HARDWARE AMERICAN NATIONAL STANDARD FOR GALVANIZED STEEL BOLTS AND NUTS FOR OVERHEAD LINE CONSTRUCTION
. El costo estará incluido en el suministro de los accesorios.T. e) Manguito de reparación Será de cobre o aleación de cobre.-
Carga de Rotura Carga de Deslizamiento
: 95% : 90 %
Los planos de diseño deberán mostrar el número de compresiones que garantiza las cargas especificadas y el diseño del dado de compresión.12. pruebas y entrega de accesorios metálicos para postes y crucetas que se utilizarán en líneas y redes primarias. De preferencia deberá suministrarse en cartuchos incluyendo todos los accesorios necesarios para realizar un correcto uso de ellas en los empalmes. La pasta será una sustancia químicamente inerte (que no ataque a los conductores). del tipo compresión.
2. apropiado para reforzar los conductores con alambres dañados.1 ALCANCES Estas especificaciones cubren las condiciones técnicas requeridas para la fabricación. materia de la presente especificación. 2. Los planos de diseño deberán mostrar el diseño del dado de compresión requerido para el manguito de empalme.2 NORMAS APLICABLES Los accesorios metálicos. cumplirán con las prescripciones de las siguientes normas.
.2 AMERICAN NATIONAL STANDARD FOR SQUARE AND HEX NUTS UNE 21-158-90 HERRAJES PARA LINEAS ELECTRICAS AEREAS DE ALTA TENSION
ANSI C 135. La carga de rotura mínima será de 55 kN.3 AMERICAN NATIONAL STANDARD FOR ZINC-COATED FERROUS LAG SCREWS FOR POLE AND TRANSMISSION LINE CONSTRUCTION ANSI C 135. las que estarán debidamente ensambladas al perno. Las cargas de rotura mínima serán: . Las cabezas de estos pernos serán cuadrados y estarán de acuerdo con la norma ANSI C 135. Las otras dimensiones.ZINC COATED FERROUS INSULATOR CLEVISES ANSI C 135. se muestran en las láminas adjuntas.4
2. b) Perno .3 DESCRIPCIÓN DE LOS MATERIALES a) Pernos Maquinados Serán de acero forjado galvanizado en caliente. las que estarán debidamente ensambladas al perno.para pernos de 13 mm( ½” ø) : 55 kN : 35 kN
Cada perno maquinado deberá ser suministrado con una tuerca cuadrada y su respectiva contratuerca cuadrada de doble concavidad.2.para pernos de 16 mm (5/8” ø) . Cada perno ojo deberá ser suministrado con una tuerca cuadrada y su respectiva contratuerca cuadrada de doble concavidad. c) Tuerca . En uno de los extremos tendrá un ojal ovalado y será roscado en el otro extremo.5 AMERICAN NATIONAL STANDARD FOR GALVANIZED FERROUS EYENUTS AND EYELETS FOR OVERHEAD LINE CONSTRUCTION ANSI C 135. Su carga mínima de rotura será de 55 kN. así como su configuración geométrica. galvanizado en caliente de 304 mm de longitud y 16 mm de diámetro (5/8”øx12” longitud).12.AMERICAN NATIONAL STANDARD FOR GALVANIZED FERROUS EYEBOLTS AND NUTS FOR OVERHEAD LINE CONSTRUCTION ANSI C 135.1 Los diámetros y longitudes de los pernos se muestran en las láminas adjuntas.20 AMERICAN NATIONAL STANDARD FOR LINE CONSTRUCTION .Ojo Será de acero forjado o hierro maleable galvanizado en caliente. Será adecuada para perno de 16 mm de diámetro.Ojo Será de acero forjado.31 AMERICAN NATIONAL STANDARD FOR ZINC-COATED FERROUS SINGLE AND DOUBLE UPSET SPOOL INSULATOR BOLTS FOR OVERHEAD LINE CONSTRUCTION ANSI B18.
05 mm 50 mm² 30. las que estarán debidamente ensambladas al perno.1 RETENIDA TIPO SIMPLE La retenida tipo simple estará compuesta de los siguientes elementos y accesorios.35 mm (2”x1/4”).13.0 8.0 7. totalmente roscado. siendo el galvanizado que se aplique a cada alambre correspondiente a la clase B según la Norma ASTM A 90.COATED (GALVANIZED) IRON OF STEEL ARTICLES.0 9.92 kN Izquierdo 0.13 ESPECIFICACIONES TECNICAS DE RETENIDAS.0 2.0 3.0 4.0 10. e) Abrazadera de F°G° Será de platina de fierro galvanizado de 50 mm x 6.0 5. tipo partido. CARACTERISTICAS CABLE DE RETENIDA 1. Será de acero galvanizado de grado SIEMENS MARTIN. Tendrá las características y dimensiones que se indican a continuación. Cada perno deberá ser suministrado con cuatro tuercas cuadradas y cuatro contratuercas cuadradas de doble concavidad.400 kg/m ASTM 475 52
. tuercas y arandelas. a) CABLE PARA RETENIDA.0 6.La configuración geométrica y las dimensiones se muestran en las láminas adjuntas.
2. de 356 mm de longitud y 16 mm de diámetro. d) Perno Tipo Doble Armado Será de acero galvanizado en caliente. 2. cumplirá con las prescripciones de las siguientes normas: ASTM A 475 STANDARD SPECIFICATION FOR ZINC-COATED STEEL WIRE STRAND ASTM A 90 STANDARD TEST METHOD FOR WEIGHT OF COATING ON ZING . con tres pernos de 13 mm ø x 76 mm largo. La carga de rotura mínima será de 55 kN.0 11.0 Material Grado Clase de galvanizado Diámetro nominal Número de alambres Diámetro de cada alambre Sección nominal Carga de rotura mínima Sentido del cableado Masa Norma de fabricación : : : : : : : : : : : Acero Siemens-Martín Según Norma ASTM B 10 mm 7 3.
6 mm (1/16") de espesor.40 m.b) ABRAZADERAS Serán de platina galvanizada tipo partido de 50x6. c) GUARDACABOS Serán de plancha de A°G° de 1.6 mm (1/16") de espesor y 2. incluido arandelas y tuercas 01 arandela cuadrada de 101x101 mm de lado y 6. g) AISLADOR DE TRACCION Serán del tipo NUEZ. de 890 mm de longitud. La mínima carga de rotura será 60 kN. e) VARILLA DE ANCLAJE Serán de F°G° de 19 mm (3/4” φ) con ojo en un extremo y roscado en el otro en una longitud de 10 cm.15 m. con un canal para cable de 3/8"φ. i) CANALETA DE PROTECCION Serán de plancha de F°G° de 1. Cada varilla deberá ser suministrada con una tuerca cuadrada y una contratuerca cuadrada de doble concavidad. con tuercas y arandelas. j) ALAMBRE DE ACERO El alambre para el amarre de las puntas del cable de retenida a fin de evitar su deshilachado.40m de longitud. Un Juego de retenida simple estará conformado por: 15 m de cable de acero galvanizado de 10 mm ø (3/8” ø) 01 varilla de anclaje de 19 mm ø x 2. con agujero central adecuado para pasar varilla de 19 mm ø (¾” φ). 53
.35 mm espesor (4”x4”x1/4”) con agujero para varilla de 19 mm ø. Estará provista de un agujero central de 21. d) MORDAZAS PREFORMADAS Serán de acero galvanizado en caliente para cable de 10 mm ø (3/8"φ).50x0. h) BLOQUE DE ANCLAJE Serán de concreto armado de 0. será del tipo galvanizado N° 12 AWG.50x0. las que estarán debidamente ensambladas a la varilla. Deberá ser diseñada y fabricada para soportar los esfuerzos de corte por presión de la tuerca de 71 kN. clase 54-3. incluido accesorios de fijación para cable de 19 mm ø (3/8"φ).4x215 mm (2”x1/4”x215 mm ø) para postes de media tensión. con dos pernos de 13mmøx76mm longitud (1/2"φx3") y un perno de 16mm ø x76 mm longitud (5/8"φx3"). para una carga de 6980 kg y carga mínima de deslizamiento de 48 kN. f) ARANDELA CUADRADA PARA ANCLAJE Será de acero galvanizado en caliente y tendrá 102 mm de lado y 5 mm de espesor.
Serán de cobre de 16mmφx2. teniendo una conductibilidad del 100 % IACS a 20°C. c) CONECTOR PARA CONEXIÓN DE VARILLA. a) CARACTERISTICAS TECNICAS DEL CONDUCTOR. la cual será de tubo de fierro galvanizado de 50 mm ø x 1.40m de longitud (5/8"φ x 2. dosis de sales químicas. de 25 mm2 de sección. f) POZO DE PUESTA A TIERRA Está compuesta de tierra cernida. para cable de 19 mm ø 04 mordazas preformadas de 890 mm para carga de rotura de 6980 kg.35x210 mm ø (2”1/4”x215 mm ø) 02 guardacabos de 1. desnudo. 7 hilos. temple suave o blando. Serán de cobre electrolítico. 2.13. para el caso de redes primarias se utilizará del tipo J. además con una riel de 4 m de longitud.40 m"). y la adecuada dosis de tierra vegetal.20 m de longitud (2"φx1. 54
. según la Norma DGE 019-CA-2/1983.13. de tal manera que la resistencia de la puesta a tierra esté dentro de los rangos exigidos por lar Normas. d) CONECTOR PARA CONEXIÓN DEL CONDUCTOR Serán conectores A/Cu de 25/25 mm2 de sección incluido cubierta protectora y Gel protector en el caso de redes secundarias.40 m) 01 abrazadera de F°G° tipo partido de 50x6. b) ELECTRODO DE PUESTA A TIERRA.40 m por lado.50x0.14 ESPECIFICACIONES TECNICAS DEL SISTEMA DE PUESTA A TIERRA. 01 bloque de concreto de 0. incluyendo una contrapunta.3 RETENIDA TIPO VIOLIN Esta tipo de retenida estará conformada por los elementos descritos para las retenidas tipo simple y contrapunta y. incluido tapa de concreto para realizar el mantenimiento. incluido abrazadera en un extremo y sistema deslizante para cable de retenida en el otro. cableado. carga mínima de deslizamiento 48 kN.40 m (1/16”x2.-
01 aislador de tracción clase ANSI 54-3 01 guardacable de 1.50x0.20m). de dos vías de cobre y terminales de compresión.58 mm e (1/16”). e) CAJA DE REGISTRO Son de concreto de 0. El conector es ANDERSON ELECTRIC apto para conductor de 16 mm² y sirve para conectar el conductor de puesta a tierra con el electrodo de puesta a tierra.58 mm e x2. 2.2 RETENIDA TIPO CONTRAPUNTA Estará conformada por todos los elementos y accesorios indicados para la retenida tipo simple.15 m 03 m de alambre de acero N° 12 para amarre
con portafusibles de expulsión para maniobra sin carga. 10 A Completos.m. a través de una pértiga. similar Erico Gel 01 caja registro de concreto 01 m3 de tierra vegetal Otros accesorios (tubo PVC. 1500 m.Un juego de sistema de puesta a tierra estará conformada por: 2.s. Los seccionadores. 10 KA. temple suave. de 25 mm2 01 varilla de Cu de 16 mm ø x 2.
. 7 KA.15 15 m e conductor de cobre.40 m) 01 Conector tipo Anderson Electric Aditamento Químico (Gel) de 7 kg. Simétrica . 150 KV.n. etc)
SECCIONADORES FUSIBLE DE ALTA TENSION. Asimétrica Fusibles tipo K-ANSI. 10 KV Accesorios de Fijación Altura promedio de trabajo : : : : : : : : 15 KV. serán del tipo unipolar CUT-OUT. 100 A. conetores J.40 m (5/8” øx2. Las características de los seccionadores fusible de potencia son las siguientes: Clase Corriente Nominal NBA Capacidad de Interrupción . y apertura automática al fundirse el fusible.
CAPITULO III ESPECIFICACIONES TECNICAS PARA EL MONTAJE ELECTROMECANICO
1 ALCANCE DEL CONTRATO El Contratista. sus condiciones generales y locales. ordenanzas y reglamentos.1. descuido. de acuerdo con los documentos contractuales. realizar todos los servicios requeridos para la buena ejecución y completa terminación de la Obra.1. las pruebas y puesta en funcionamiento de todas las instalaciones y equipos. y se obliga a ceñirse a tales leyes. el equipo o material que utilice y en la forma de llevar a acabo la obra. La Supervisión no estará obligada a aceptar el subcontrato.3 3.
3.2 3.1.4 3.1
3. localización y finalidad de la obra. dada por escrito y previo conocimiento de la persona del subcontratista y de los términos y condiciones del subcontrato.1. Las únicas condiciones válidas para normar la ejecución de la obra serán las contenidas en el Contrato y en los documentos contractuales.1.4 SUB-CONTRATOS
No se permitirá la sub-contratación del todo o parte de la obra. sin la autorización de la Supervisión.
A. conservación y mantenimiento con arreglo a las prescripciones de los documentos contractuales.3 OBSERVACIÓN DE LAS LEYES
El Contratista es responsable de estar plenamente informado de todas las leyes que puedan afectar de alguna manera a las personas empleadas en el trabajo. error u omisión del Contratista en la obtención de la información mencionada no le releva la responsabilidad de apreciar adecuadamente las dificultades y los costos para la ejecución satisfactoria de la obra y el cumplimiento de las obligaciones que se deriven de los documentos contractuales. ESPECIFICACIONES TECNICAS PARA EL MONTAJE ELECTROMECANICO.
3.1.2 CONDICIONES QUE AFECTAN A LA OBRA
El Contratista es responsable de estar plenamente informado de todo cuanto se relacione con la naturaleza.
3.1. deberá ejecutar la totalidad de los trabajos. Cualquier falta.
3.III. su ejecución.
3. donde deberá anotar las ocurrencias importantes que se presenten durante el desarrollo de los trabajos.2.3 DEL PERSONAL
3. Fin de Pruebas e. De esta manera queda establecido que todas las comunicaciones serán hechas en forma escrita y no tendrán validez las indicaciones verbales. así como los acuerdos de reuniones efectuadas en obra entre el Contratista y la Supervisión. Fin del Montaje c. Este organigrama deberá contener particularmente:
3. Pruebas de Puesta en servicio d. El Contratista entregará a la Supervisión.1 ORGANIGRAMA DEL CONTRATISTA
El Contratista presentará a la SUPERVISION un Organigrama de todo nivel. tendrán estrecha relación con las partidas del presupuesto y el cronograma valorizado aprobado al Contratista.3. un diagrama PERT-CPM y un diagrama de barras (GANTT) de todas las actividades que desarrollará y el personal que intervendrá con indicación del tiempo de su participación. Inicio de Pruebas d. Estas fechas definen los períodos de duración de las siguientes actividades: a.2
3. Los diagramas serán los más detallados posibles. Este cuaderno será utilizado para comunicaciones entre el Contratista y la Supervisión. Montaje b. Período de Garantía.3 CUADERNO DE OBRA
El Contratista deberá llevar al día.2 PLAZOS CONTRACTUALES
El Cronograma de Ejecución debe definir con carácter contractual las siguientes fechas: a. un cuaderno de obra.2. Recepción de Obra. Pruebas a la terminación c. 3.
3.2.1 CRONOGRAMA DE EJECUCIÓN
Antes del inicio de obra. Inicio de Montaje b.
Nombres y calificaciones del o de los representantes calificados y habilitados para resolver cuestiones técnicas y administrativas relativas a la obra. Nombre y calificaciones del o de los ingenieros de montaje. reglamentos.
3. Tales destituciones no podrán servir de base a reclamos o indemnizaciones contra el Propietario o la Supervisión.4.
3. especializado y debidamente calificado para llevarlo a cabo de acuerdo con los documentos contractuales. el Contratista despedirá a cualquier persona desordenada. El Contratista deberá comunicar a la SUPERVISION de cualquier cambio en su organigrama.3. insubordinada.3 LEYES SOCIALES
El Contratista se obliga a cumplir todas las disposiciones de la Legislación del Trabajo y de la Seguridad Social. En todo tiempo.
. peligrosa. Nombre y calificaciones del o de los jefes montadores. respetando los Reglamentos de Seguridad Vigentes.1 EJECUCIÓN DE LOS TRABAJOS
Toda la Obra objeto del Contrato será ejecutada de la manera prescrita en los documentos contractuales y en donde no sea prescrita. el Contratista deberá tomar las medidas y precauciones necesarias para la seguridad de los trabajadores. medidas y precauciones que sean necesarias para evitar que se produzcan condiciones insalubres en la zona de los trabajos y en sus alrededores. de acuerdo con las directivas de la SUPERVISIÓN. incompetente o que tenga otros defectos a juicio de la Supervisión. 3. y prestar asistencia a su Personal. El Contratista no podrá efectuar ningún cambio.4 SEGURIDAD E HIGIENE
El Contratista deberá observar todas las leyes. prevenir y evitar accidentes. modificación o reducción en la extensión de la obra contratada sin expresa autorización escrita de la SUPERVISIÓN.3.4 DE LA EJECUCIÓN
3.2 DESEMPEÑO DEL PERSONAL
El trabajo debe ser ejecutado en forma eficiente por personal idóneo.
3. A solicitud de la Supervisión.3.
deducción o cualquier otra forma de variación de una o más partes de la obra. avisará al Contratista para que éste disponga de la parte de la obra.3. donde sea aplicable. será determinado de común acuerdo. suministro o material empleado por el Contratista o por cualquier Subcontratista.4. del suministro o del material impugnado para su reemplazo o reparación. según el caso.
3. al Contratista mediante una ORDEN DE CAMBIO la alteración.4. la SUPERVISIÓN encontrase que.
3. cualquier parte de la Obra.
3.2 MONTAJE DE PARTES IMPORTANTES
El Contratista y la SUPERVISIÓN acordarán antes del inicio del montaje. en todo caso. El monto de la diferencia será calculado de acuerdo con los precios del Metrado y Presupuesto del Contrato. equipo de construcción y montaje adecuado y suficiente. La diferencia en precio derivada de las modificaciones será añadida o deducida del Precio del Contrato. el cual deberá mantenerse permanentemente en condiciones operativas.3 HERRAMIENTAS Y EQUIPOS DE CONSTRUCCIÓN
El Contratista se compromete a mantener en el sitio de la obra. entre la SUPERVISIÓN y el CONTRATISTA.4. adición. a su juicio. sin demora alguna. cambio. las modificaciones ordenadas. de acuerdo con los requerimientos de la misma.4. es o son defectuosos o están en desacuerdo con los documentos contractuales.
. Ninguna parte o pieza importante del equipo podrá ser montada sin que el Contratista haya solicitado y obtenido de la SUPERVISIÓN la autorización de que la parte o pieza en cuestión puede ser montada.5 RECHAZOS
Si en cualquier momento anterior a la Aceptación Provisional. modificación. La SUPERVISIÓN dará la autorización escrita a la brevedad. salvo razones que justifiquen una postergación de la misma. por escrito. El Contratista deberá llevar a cabo. Se entiende por ORDEN DE CAMBIO la que se refiere a cambio o modificación que la SUPERVISIÓN considere técnicamente necesaria introducir. las partes o piezas importantes cuyo montaje requiere de autorización de la SUPERVISIÓN.4 CAMBIOS Y MODIFICACIONES
La Supervisión tiene el derecho de ordenar.
reparar a su costo el daño o perjuicio ocasionado.
3. en todo momento. extendiéndose tal responsabilidad a los casos no imputables al Contratista.El Contratista. El Propietario podrá efectuar la labor que debió realizar el Contratista cargando los costos correspondientes a este último. En tal sentido.9 VIGILANCIA Y PROTECCIÓN DE LA OBRA
El Contratista debe. deberá subsanar las deficiencias. El Contratista estará obligado a restaurar. proteger y conservar las instalaciones. en opinión de la SUPERVISIÓN. en consecuencia. completamente a su costo. materiales y efectos de cualquier naturaleza. en el más breve lapso y a su costo.4. El Contratista tomará medidas contra el corte y destrucción que cause su personal y contra los daños que produzcan los excesos o descuidos en las operaciones del equipo de construcción y la acumulación de materiales.4. arbustos y hierbas. no obstaculice la ejecución de los trabajos.
. que exista en el sitio de la Obra o en los adyacentes y que.7 DAÑOS Y PERJUICIOS A TERCEROS
El Contratista será el único responsable de las reclamaciones de cualquier carácter a que hubiera lugar por los daños causados a las personas o propietarios por negligencia en el trabajo o cualquier causa que le sea imputable.4.
3. la vegetación que su personal o equipo empleado en la Obra. hasta su recepción. así como también toda la obra ejecutada. incluyendo el personal de vigilancia diurna y nocturna del área de construcción. hubiese destruido o dañado innecesariamente o por negligencia. Todas las piezas o partes de reemplazo deberán cumplir con las prescripciones de garantía y estar conformes con los documentos contractuales.8 PROTECCIÓN DEL MEDIO AMBIENTE
El Contratista preservará y protegerá toda la vegetación tal como árboles. podrá asegurar la obra adecuadamente y en tiempo oportuno contra todo riesgo asegurable y sin prejuicio de lo estipulado en el Contrato sobre tal responsabilidad. provisiones. equipos.
3.4. maquinarias. deberá.
3.6 DAÑOS DE OBRA
El Contratista será responsable de los daños o pérdidas de cualquier naturaleza y que por cualquier causa pueda experimentar la Obra hasta su Recepción. En caso que el Contratista no cumpliera con lo mencionado anteriormente. instrumentos.
3. Los gastos ocasionados los deducirá de cualquier saldo que adeude al Contratista. equipos. provisiones y materiales de su propiedad. no releva al Contratista de su responsabilidad por la correcta ejecución y funcionamiento de las instalaciones del proyecto.5
3. El Propietario comunicará al Contratista el nombre del ingeniero responsable de la Supervisión quién estará habilitado para resolver las cuestiones técnicas y administrativas relativas a la obra. es decir. el área de la construcción.4. Asimismo. incluyendo los locales de almacenamiento usados por él. estará constantemente sujeta a la inspección y fiscalización de ingenieros responsables a fin de asegurar el estricto cumplimiento de los documentos contractuales. de modo que deje la obra y el área de construcción en condiciones de aspecto y limpieza satisfactorios.
3. las instalaciones. cargando el correspondiente costo al Contratista. materiales y efectos mencionados no son protegidos adecuadamente por el Contratista. La labor de supervisión podrá ser hecha directamente por. a nombre del Propietario. 62
. En caso de que el Contratista no cumpla esta obligación.10
LIMPIEZA El Contratista deberá mantener en todo momento. En todo caso.
3.5. Antes de la recepción de la Obra deberá retirar todas las herramientas. El Propietario tendrá derecho a hacerlo.Los requerimientos hechos por la SUPERVISION al Contratista acerca de la protección adecuada que haya que darse a un determinado equipo o material.1 SUPERVISIÓN DE LA OBRA
La Obra se ejecutará bajo una permanente supervisión. Si. por parte de la supervisión. en ningún caso ni en ningún modo. la aprobación. de acuerdo con las instrucciones de la SUPERVISION. o bien por una empresa Consultora contratada para tal fin. provisiones. maquinarias. de documentos técnicos para la ejecución de trabajos.2 RESPONSABILIDAD DE LA OBRA
La presencia de la Supervisión en las operaciones del Contratista no releva a éste. a través de un Cuerpo especialmente designado para tal fin. libres de toda acumulación de desperdicios o basura. El Propietario podrá efectuar la limpieza a expensas del Contratista. de su responsabilidad por la cabal y adecuada ejecución de las obras de acuerdo con los documentos contractuales.5. instrumentos. deberán ser atendidos. El Propietario.
Dentro del plazo indicado.6 DE LA ACEPTACIÓN
3. Tres copias de los Planos de la Obra y Sección de Obra en su última revisión.
3. con sus características técnicas. Un programa detallado de las pruebas a efectuarse. la SUPERVISION verificará la suficiencia de la documentación y el estado de la obra o de la Sección de Obra y autorizará al Contratista a proceder con las pruebas de puesta en servicio. para el conjunto de la obra. a fin de que la inspección se efectúe en la forma más satisfactoria. se harán las pruebas en servicio.6. con la debida y suficiente anticipación.
. oportuna y eficaz. acerca de su inmediato programa de trabajo y de cada una de sus operaciones. en los términos y plazos prescritos en los documentos contractuales.
3. en todo tiempo. 3.5. Después de concluidas estas pruebas. Las Planillas de los Protocolos de Pruebas. d. los equipos e instalaciones serán objeto de pruebas al término del montaje respectivo.6. cualquiera sea el estado en que se encuentre.5. se harán las pruebas sin tensión del sistema (pruebas en blanco). e. y el Contratista deberá prestarle toda clase de facilidades para el acceso a la obra y su inspección.3.4 FACILIDADES DE INSPECCIÓN
La Supervisión tendrá acceso a la obra. El procedimiento de Pruebas. el Contratista notificará por escrito a la SUPERVISION del inicio de las pruebas.2 PRUEBAS EN BLANCO
Antes de la fecha prevista para los términos del Montaje de la Obra. La Relación de los Equipos de Pruebas a utilizarse. c. b. el Contratista dará todas las facilidades y los elementos adecuados de que dispone.1 PROCEDIMIENTO GENERAL
Para la aceptación de la obra por parte de la Supervisión.3 OBLIGACIONES DEL CONTRATISTA
El Contratista estará obligado a mantener informado a la Supervisión con la debida y necesaria anticipación. remitiéndole tres copias de los documentos indicados a continuación: a. A este fin.
Los gastos de estas pruebas estarán a cargo del Contratista. también.
. materiales y equipos necesarios para las pruebas "en blanco". Planos conforme a Obra. estarán a cargo del Contratista. materiales y equipo necesario para la ejecución de las pruebas de puesta en servicio. las cuales consistirán en la energización de las Redes y registro de variables de tensión corriente y otros. El personal.Si alguna prueba no resultase conforme con las prescripciones de los documentos contractuales. El personal. según los términos de los documentos contractuales. Inventario físico de materiales y equipos instalados en obra b.3 PRUEBA DE PUESTA EN SERVICIO
Antes de la conclusión de las Pruebas "en blanco" de toda la obra.6. será tomada como la fecha de conclusión de obra.6.4 RECEPCIÓN DE OBRA
La fecha en que terminen satisfactoriamente todas las pruebas de Puesta en Servicio se efectuará bajo la responsabilidad del Contratista y consistirá de un período de funcionamiento satisfactorio sin necesidad de arreglos o revisiones. La fecha de conclusión satisfactoria de las pruebas de puesta en servicio. no encontrándose comprendida dentro del plazo de ejecución del proyecto. según el o los regímenes de carga solicitados por el Propietario. se obtuviesen resultados que no estuvieran de acuerdo con los documentos contractuales y normas del caso. será repetida.
3. durante la ejecución de las Pruebas de Puesta en Servicio. a pedido de la SUPERVISION. hecha en forma conjunta entre La Supervisión y el Contratista y su inicio será después de la conclusión de las Pruebas "en blanco" de toda la obra a satisfacción de La Supervisión. estarán a cargo del Contratista. La Programación de las Pruebas de Puesta en Servicio será.
3. la Supervisión y el Contratista acordarán el Procedimiento de Pruebas de Puesta en Servicio. Condición previa para la Recepción de Obra será la entrega por parte del Contratista de los documentos siguientes: a. el Contratista deberá efectuar los cambios o ajustes necesarios para que en una repetición de la prueba se obtenga resultados satisfactorios. Inventario físico de materiales y equipos entregados al propietario (nuevos y desmontados) c. Si.
a su juicio.La Recepción de Obra será objeto de un Acta firmada por los representantes del contratista y los miembros integrantes del comité de recepción de Obra.
. siempre que. En caso de ser destruidos. así como el inventario físico de materiales y equipos objeto de la Recepción de Obra.
3. Para su firma. estará en libertad de hacer uso de la respectiva obra o sección de obra. Los ejes y vértices del trazo . equipos de estación total. Si.7
REPLANTEO TOPOGRÁFICO El Contratista será responsable de efectuar todos los trabajos de campo necesarios para replantear la ubicación de: .
B. el Acta de Recepción de Obra no pudiera ser firmada.6. El replanteo se materializará en el terreno mediante: Hitos de concreto en los vértices. extremos de líneas y puntos de control importantes a lo largo del trazo. por cualquier razón o defecto imputable al Contratista. serán de cuenta del Contratista el costo del reemplazo. contado a partir de la Recepción de Obra por parte del Propietario. El (los) poste (s) de la (s) estructuras . Estacas pintadas de fierro corrugado en la ubicación y referencias para postes y retenidas. Tal uso no significará la recepción de la obra o de la sección de obra y su mantenimiento y conservación será por cuenta del Contratista con excepción del deterioro que provenga del uso por El Propietario de la obra o parte de ésta. se verificará la suficiencia de la documentación presentada. Los ejes de las retenidas y los anclajes.
3. El Propietario. El replanteo será efectuado por personal experimentado empleando distanciómetros. desplazados o dañados por el Contratista o por terceros.5 RESPONSABILIDAD DEL CONTRATISTA
El contratista es el responsable por la calidad ofrecida y por los vicios ocultos de los bienes o servicios ofertados por un plazo no menor de siete años. la obra o sección de obra esté en condiciones de ser usada. Los hitos de concreto y estacas serán adecuadamente protegidos por el Contratista durante el período de ejecución de las obras. teodolitos y otros instrumentos de medición de probada calidad y precisión para la determinación de distancias y ángulos horizontales y verticales.
aprobará las planillas de replanteo u ordenará las modificaciones que sean pertinentes. será rellenada y compactada por el Contratista a su costo. y reduciendo al mínimo el volumen del terreno afectado por la excavación. entradas a locales de espectáculos públicos. alrededor de la cimentación. luego de revisarlas. los postes se alinearán en forma paralela a la línea de fachada de las viviendas. 66
. el Contratista efectuará tales trabajos de levantamiento topográficos. El eje del poste estará ubicado a 0. iglesias. con el fin de no alterar su cohesión natural. Cualquier excavación en exceso realizado por el Contratista.30 m perpendicularmente al borde de vereda. fuese necesario introducir variantes en el trazo. el Contratista coordinará con las autoridades locales la solución de estos inconvenientes. fenómenos geológicos o errores en el levantamiento topográfico del proyecto. La Supervisión. medida sobre la proyección horizontal 3. El replanteo topográfico se medirá y pagará por km de línea. Se evitará ubicar los postes frente a garajes. El costo de estos trabajos estará considerado dentro de la partida correspondiente al Replanteo Topográfico. El Contratista deberá someter a la aprobación de la Supervisión. sin orden de la Supervisión.En principio. En los tramos donde. dibujo de planos y la pertinente localización de estructuras. Se considera terreno rocoso cuando sea necesario el uso de explosivos para realizar la excavación y terreno moro moro cuando el terreno sea del tipo calichozo típico de la ciudad de Ilo. no permitiéndose por ningún motivo. El fondo de la excavación deberá ser plano y firmemente compactado para permitir una distribución uniforme de la presión de las cargas verticales actuantes.8 EXCAVACION DE HUECOS El Contratista ejecutará las excavaciones con el máximo cuidado y utilizando los métodos y equipos más adecuados para cada tipo de terreno. El Contratista someterá a la aprobación de la Supervisión las planillas de replanteo de cada tramo de línea de acuerdo con el cronograma de obra. En todos los otros casos se considerará terreno normal. la instalación en la propia esquina. etc. los métodos y plan de excavación que empleará en el desarrollo de la obra. En el caso que las calzadas y veredas no estuvieran plenamente definidas. Ningún poste deberá ubicarse a menos de un metro de la esquina. debido a modificaciones en el uso del terreno.
deberán ser cuidadosamente verificados a fin de que no presenten defectos y sean adecuados al peso que soportarán. 3. para lo cual se preverá una grúa de 6 toneladas.80 m de diámetro por 1. de 12 ó 13 m de longitud. de 14 m de longitud.80 m de diámetro por 2. los postes se izarán mediante trípodes o cabrías.50 m de profundidad. deberán ser cuidadosamente verificados a fin de que no presenten defectos y sean adecuados al peso que soportarán. La medición y el pago por distribución de poste se realizará por unidad transportada. estribos.9 DISTRIBUCION DE POSTES DE M. como mínimo. todo los equipos y herramientas. estribos. En lugares con caminos de acceso carrozables.10 INSTALACION DE ARMADOS IZADO Y CIMENTACION DE POSTES El Contratista deberá someter a la aprobación de la Supervisión el procedimiento que utilizará para el izaje de los postes. cables de acero. cables de acero.T. no se pagarán el transporte de aquellos postes que hayan sufrido daño o hayan sido sometidos a esfuerzos excesivos. En los lugares que no cuenten con caminos de acceso para vehículos. 67
. No se pagarán las excavaciones realizados por error o conveniencia del Contratista.Las dimensiones de la excavación serán las siguientes: Para postes de M. tales como ganchos de grúa. los postes serán instalados mediante una grúa de 6 toneladas montada sobre la plataforma de un camión. tales como ganchos de grúa. todos los equipos y herramientas.. El contratista deberá solicitar la autorización de la Supervisión. debiendo estos ser reemplazados. excavación de 0. 3. En ningún caso los postes serán sometidos a daños o esfuerzos excesivos. excavación de 0. Para postes de M.
La unidad de medida y pago será por excavación realizada de las dimensiones indicadas en el párrafo anterior para el tipo de suministro a instalar. En ningún caso los postes serán sometidos a daños o a esfuerzos excesivos.T. para el inicio del traslado de los postes desde los almacenes del contratista a los lugares donde irán estos instalados. Antes del inicio del transporte. Para retenidas y sistemas de puesta a tierra. excavación de 0. montado sobre la plataforma de un camión.T.80 m de diámetro por 2.10 m de profundidad.70 m de profundidad. Antes del izaje.
presentadas a la Supervisión para la correspondiente inspección y posterior aprobación o rechazo. No se permitirá el escalamiento a ningún poste hasta que éste no haya sido completamente cimentado. Solo se aceptará la instalación del poste en el que se haya verificado la protección con pintura impermeabilizante incolora en una longitud de 2. Las piezas ligeramente curvadas. cumplirán con las prescripciones del Reglamento Nacional de Construcciones para la resistencia a la compresión. INSTALACION DE ELEMENTOS QUE CONFORMAN EL ARMADO Una vez izado y cimentado el poste. Los elementos antes de ser instalados serán convenientemente limpiados. Los postes de anclaje o ángulo se colocarán con una ligera inclinación opuesta a la resultante de fuerzas. El cemento. serán enderezadas por el Contratista empleando recursos aprobados. la dosificación y las pruebas. los cuáles no afectarán el galvanizado. La instalación de estos elementos será por el método propuesto por el contratista y aprobado por la supervisión. torcidas o dañadas de otra forma durante el manipuleo. cuerdas en tensión. los agregados. La Supervisión se reserva el derecho de prohibir la aplicación del método de izaje propuesto por el Contratista si no presentara una completa garantía contra daños a las estructuras y la integridad física de las personas.Durante el izaje de los postes. almacenamiento y montaje. Todas las superficies de los elementos de acero serán limpiadas antes del ensamblaje y deberá removerse del galvanizado. o en el agujero donde se instalará el poste. ménsulas aisladores y accesorios metálicos. todo moho que se haya acumulado durante el transporte.
.40 m medido desde la base del poste. El Contratista tomará las debidas precauciones para asegurar que ninguna parte de los armados sea forzada o dañada. Tales piezas serán. ningún obrero. a fin de que queden verticales cuando estén sometidas a su carga de trabajo. el agua. La cimentación de los postes será con concreto tipo ciclópeo con una dosificación de 1:3+30% de piedra mediana. se procederá a la instalación de los demás elementos que conforman el armado tales como: crucetas. ni persona alguna se situará por debajo de postes. No se arrastrarán elementos o secciones ensambladas sobre el suelo o sobre otras piezas. luego. en cualquier forma durante el transporte.
la reparación no fuese aceptable. crucetas ó ménsulas. Si en opinión de ella. El ajuste final de todos los pernos se efectuará. Limpieza con escobilla y remoción de las partículas del zinc sueltas y los indicios de óxido. o en la dirección de la bisectriz del ángulo de desvío en estructuras de ángulo. el Contratista desmontará y corregirá el montaje sin costo adicional para el Propietario. Los daños menores serán reparados con pintura especial antes de aplicar la protección adicional contra la corrosión de acuerdo con el siguiente procedimiento: a. La magnitud de los torques de ajuste deben ser previamente aprobados por la Supervisión. cuidadosa y sistemáticamente. Cubrimiento con una capa de resina-laca. los postes deben quedar verticales y las crucetas horizontales y perpendiculares al eje de trazo en alimentación. b. en caso de dos o tres ternas. Recubrimiento con dos capas sucesivas de una pintura rica en zinc (95% de zinc en la película seca) con un portador fenólico a base de estireno. pintado del código de la estructura. c. la pieza será reemplazada y los gastos que ello origine serán de cuenta del contratista. se considera el 69
. A fin de no dañar la superficie galvanizada de pernos y tuercas.5 cm Orientación 0. ferretería de estructuras. pintado de símbolos puesta a tierra y/o peligro Solo para el caso de armados con postes de 12 y 13 m de longitud. Las tolerancias máximas son las siguientes: Verticalidad del poste 0. El precio unitario comprenderá el montaje del poste. El ajuste deberá ser verificado mediante torquímetros de calidad comprobada. se considera que el armado es para una sola terna. Cuando se superen las tolerancias indicadas. Luego de concluida la instalación de las estructuras. La medición y pago será por cada tipo de armado e incluirá los ensambles correspondientes para cada tipo de estructura.5 cm/m Alineamiento +/. La pintura será aplicada de acuerdo con las instrucciones del fabricante. Desgrasado si fuera necesario. Todas las partes reparadas del galvanizado serán sometidas a la aprobación de la supervisión. por una cuadrilla especial. los ajustes deberán ser hechos con llaves adecuadas.5° Desviación de crucetas 1/200 Le Le = Distancia del eje de la estructura al extremo de la cruceta.Los daños mayores a la galvanización serán causa suficiente para rechazar la pieza ofertada.
se considera la instalación de crucetas y/o ménsulas en estructuras existentes o nuevas para permitir la instalación de otra terna o ternas (en la misma estructura) o permita ejecutar derivaciones de la línea que no necesariamente forman parte de una estructura de alineamiento o ángulo.suministro e instalación de elementos adicionales necesarios (crucetas o ménsulas. 3. será necesario soltar los amarres que sostienen a la línea de M. pudiendo ser reinstalados en caso se compruebe su buen estado.11 INSTALACION DE CRUCETAS Y MENSULAS Se considera la instalación de crucetas y/o ménsulas. debiendo el contratista prever que los conductores no sufran daños y permanezcan anclados a una estructura en forma conveniente.12 CAMBIO DE ESPIGAS Y AISLADORES El contratista efectuará el reemplazo de espigas o aisladores tipo PIN existentes por otros nuevos.. se verificará su galvanizado procediendo de forma similar al mencionado para el caso de instalación de armados. Las crucetas serán instaladas previa verificación de su estado y limpieza. con todos los aisladores y accesorios necesarios que permitan la conformación del armado para la instalación de la línea de M. Asimismo. para el caso de cambio de crucetas y ménsulas existentes y deterioradas y/o que no permiten cumplir con las distancias de seguridad conforme al Código Nacional de Electricidad Suministro. Para el reemplazo. 70
. Serán instalados con las tolerancias indicadas para el caso de crucetas en el punto anterior. incluido aisladores y demás accesorios.T.10la instalación de los armados galvanizado.T. se considera todos los elementos que lo conforman. hasta para tres ternas. Para el caso de armados con postes de 14 m de longitud. 3. aisladores y otros accesorios) los cuales tienen su propia medición y pago. en caso de que alguno de ellos o ambos presenten deterioro o defectos. conjunto. En caso de crucetas y elementos metálicos.13 INSTALACION DE CADENA DE AISLADORES Se instalarán cadenas de aisladores en las estructuras existentes que lo requieran. La medición y pago será por el cambio del conjunto aislador espiga. de presentar defectos serán tratados de forma similar para 3. reemplazo de uno de los elementos mencionados o la reinstalación de ambos. La medición y pago será por tipo de cruceta a instalar. 3.
de los demás accesorios tales como grapas. Cuando. debiendo el contratista tomar las previsiones del caso para anclar temporalmente la línea en caso de ser requerido. Al concluirse el relleno y la compactación. se fijará. se requerirá realizar la excavación correspondiente. Los cables de retenidas deben ser tensados de tal manera que los postes se mantengan en posición vertical.80 m de diámetro por 2. En la excavación de 0. la varilla de anclaje debe sobresalir 0. no pueda aplicarse al ángulo de inclinación previsto en el proyecto. incluido sus accesorios tales como grapas pernos y otros necesarios. La medición y pago será por tipo de retenida instalada. mediante la utilización de grapas tipo 71
.estructuras de fin de línea y/o anclaje. pernos. La medición y pago será por cadena de aisladores instalado. después que los conductores hayan sido puestos en flecha y engrapados. así como. 3. La disposición final del cable de las retenidas se muestra en los planos del proyecto.40 m de profundidad. La varilla de anclaje y el correspondiente cable de acero deben quedar alineados y con el ángulo de inclinación que señalen los planos del proyecto. 3. la varilla de anclaje con el bloque de concreto correspondiente. las rieles deberán ser instalados conjuntamente que los armados (poste). debido a la disposición de las viviendas y vías públicas.15 m de nivel del terreno. Se tendrá en cuenta que estarán alineadas con las cargas o resultante de cargas de tracción a las cuales van a contrarrestar. El relleno se ejecutará después de haber alineado y orientado adecuadamente la varilla de anclaje y compactándose en capas sucesivas de 20 cm. y en caso de ser poste existente. verificando la operatividad de sus elementos. Los cables de retenidas se instalarán antes de efectuarse el tendido de los cables. se verificará su buen estado y limpieza. Antes de la instalación de las cadenas de aisladores.15 RETEMPLADO DE RETENIDA El contratista realizará el retemplado del cable de tracción de la retenida. las alternativas de ubicación de los anclajes.14 RETENIDAS Y ANCLAJE. Para el caso de retenidas tipo violín. de tal forma que permita la instalación de la cadena de aisladores. La ubicación y orientación de las retenidas serán las que se indiquen en los planos del proyecto. el Contratista someterá a la aprobación de la Supervisión. etc. en el fondo de la excavación.
La Supervisión se reserva el derecho de rechazar los métodos propuestos por el Contratista si ellos no presentaran una completa garantía contra daños a la Obra. la correcta operación de los equipos. Para tal fin. estructuras. estructuras y otros obstáculos durante todas las operaciones de desarrollo y tendido. aisladores y demás componentes de la línea. Equipos Todos los equipos completos con accesorios y repuestos. Antes de comenzar el montaje y el tendido. el tendido y la puesta en flecha de los conductores serán llevados a acabo de acuerdo con los métodos propuestos por el contratista y aprobados por la supervisión.16 TENDIDO Y TEMPLADO DE CONDUCTORES a) PRESCRIPCIONES GENERALES Metodo de Montaje El desarrollo. en el sitio. Los conductores serán continuamente mantenidos separados del terreno. 72
. El Contratista tomará todas las medidas a fin de evitar perjuicios a la Obra durante tales suspensiones. serán sometidos por el Contratista a la inspección y aprobación de la Supervisión. el tendido de los conductores se efectuará por un método de frenado mecánico aprobado por la Supervisión. 3. propuestos para el tendido.rana para cable de acero y equipos de tracción como tilfors. La medición y pago será por el templado corregido de una retenida. zanjas. Suspensión del Montaje El trabajo de tendido y puesta en flecha de los conductores será suspendido si el viento alcanzara una velocidad tal que los esfuerzos impuestos a las diversas partes de la Obra. sobrepasen los esfuerzos correspondientes a la condición de carga normal. vegetación. b) MANIPULACION DE CONDUCTORES Criterios Generales Los conductores serán manipulados con el máximo cuidado a fin de evitar cualquier daño en su superficie exterior o disminución de la adherencia entre los alambres de las distintas capas. el Contratista demostrará a la Supervisión. La aplicación de estos métodos no producirá esfuerzos excesivos ni daños en los conductores. árboles.
En vanos que crucen líneas de energía eléctrica o de telecomunicaciones. el Contratista someterá a la aprobación de la Supervisión por lo menos dos (2) compresores hidráulicos. serán del tipo de mandíbulas paralelas con superficies de contacto alisadas y rectas. Donde estén separadas por menos de dos vanos b. el número de juntas o empalmes. c) EMPALMES DE LOS CONDUCTORES Criterios de Empleo El Contratista buscará la mejor utilización de tramos máximos a fin de reducir. Herramientas Antes de iniciar cualquier operación de desarrollo. El radio de curvatura de tales herramientas no será menor que la especificada para las poleas de tendido. Grapas y Mordazas Las grapas y mordazas empleadas en el montaje no deberán producir movimiento relativos de los alambres o capas de los conductores. Las mordazas que se fijen en los conductores. y no serán levantados por medio de herramientas de material. la naturaleza del metal y las condiciones de la superficie serán tales que la fricción sea reducida a un mínimo y que los conductores estén completamente protegidos contra cualquier daño. carreteras importantes. El número y ubicación de las juntas de los conductores serán sometidos a la aprobación de la Supervisión antes de comenzar el montaje y el tendido. tamaño o curvatura que pudieran causar daño. El tamaño y la forma de la ranura. La ranura de la polea tendrá un recubrimiento de neopreno o uretano. Las juntas no estarán a menos de 15 m del punto de fijación del conductor más cercano.Los conductores deberán ser desenrollados y tirados de tal manera que se eviten retorcimientos y torsiones. al mínimo. Poleas Para las operaciones de desarrollo y tendido del conductor se utilizarán poleas provistas de cojinetes. No se emplearán juntas de empalme en los siguientes casos: a. Tendrán un diámetro al fondo de la ranura igual. Su largo será tal que permita el tendido del conductor sin doblarlo ni dañarlo. a 30 veces el diámetro del conductor. cada
. La profundidad de la ranura será suficiente para permitir el paso del conductor y de los empalmes sin riesgo de descarrilamiento. por lo menos.
El Contratista proporcionará apropiados teodolitos. Estos dos vanos estarán suficientemente alejados uno del otro para permitir una verificación correcta de la uniformidad de la tensión. d) PUESTA EN FLECHA Criterios Generales La puesta en flecha de los conductores se llevará a cabo de manera que las tensiones y flechas indicadas en la tabla de tensado. Manguitos de Reparación En el caso que los conductores hayan sido dañados.uno de ellos completo con sus accesorios y repuestos. Los manguitos de reparación no serán empleados sin la autorización de la Supervisión. miras topográficas. una vez terminados presenten el valor más alto de sus características mecánicas y eléctricas. Preparación de los Conductores El Contratista pondrá especial atención en verificar que los conductores y los tubos de empalme estén limpios. taquímetros y demás aparatos necesarios para un apropiado control de la flechas. Se aplicará las tensiones de regulación tomando en cuenta los asentamientos (CREEP) durante este período. La flecha y la tensión de los conductores serán controlados por lo menos en dos vanos por cada sección de tendido. Los extremos de los conductores serán cortados mediante cizallas que aseguren un corte transversal que no dañe los alambres del conductor. Ejecución de los Empalmes Los empalmes del tipo a compresión para conductores serán ajustados en los conductores de acuerdo con las prescripciones del fabricante de tal manera que. Procedimiento de puesta en flecha del conductor Se dejará pasar el tiempo suficiente después del tendido y antes de puesta en flecha para que el conductor se estabilice. y con dos juegos completos de moldes para el conductor. La Supervisión 74
. no sean sobrepasadas para las correspondientes condiciones de carga. la Supervisión determinará si pueden utilizarse manguitos de reparación o si los tramos dañados deben cortarse y empalmarse. La puesta en flecha se llevará a cabo separadamente por secciones delimitadas por estructuras de anclaje.
aisladores y ferretería metálica. crucetas.podrá disponer con la debida anticipación. los conductores estarán permanentemente puesto a tierra para evitar accidentes causados por descargas atmosféricas. serán trasladados a los aisladores tipo PIN para su amarre definitivo. Los amarres se ejecutarán de acuerdo con los detalles mostrados en los planos del proyecto. 3.18 INSTALACION DE SECCIONADORES TIPO CUT-OUT El contratista efectuará la limpieza y verificación del buen estado de los equipos. teniendo presente que el retemplado de la línea es de una línea desmontada temporalmente y que se encuentra suspendida adecuadamente el pos postes que le sirven de apoyo. las cuáles deberán ser aprobadas por la Supervisión. Fijación del conductor a los aisladores tipo PIN y grapas de anclaje Luego que los conductores hayan sido puestos en flecha. será por metro instalado. suministrados por el Contratista. y por fase.17 RETEMPLADO DE CONDUCTORES Será de la firma descrita para el tendido y templado de conductores. La unidad de medida y pago para el tendido del conductor. La unidad de medida y pago para el retemplado del conductor. la verificación y recalibración de los teodolitos y los otros instrumentos que utilizará el Contratista. La verificación se hará con torquímetro de probada calidad y precisión.
. será por metro instalado. Puesta a Tierra Durante el tendido y puesta en flecha. 3. inducción electrostática o electromagnética. en lo que corresponda. y por fase. Los torques de ajuste aplicados a las tuercas de las grapas de anclaje serán los indicados por los fabricantes. el conductor se fijará a las grapas de anclaje de la cadena de aisladores. El Contratista será responsable de la perfecta ejecución de las diversas puestas a tierra. con el fin de removerlas antes de la puesta en servicio de la línea. antes del inicio de los trabajos. El Contratista anotará los puntos en los cuáles se hayan efectuado las puestas a tierra de los conductores. En los extremos de la sección de puesta en flecha.
3. Los pernos de sujeción de las cadenas de suspensión angular y de anclaje El conductor neutro. Posteriormente a la instalación de puesta a tierra. El conjunto incluirá la fijación del conductor de bajada en los postes y la instalación del electrodo vertical y la medición de la resistencia de puesta a tierra. La unidad de medida y pago será por juego de tres seccionadores tipo Cut Out instalados en una cruceta metálica.20 ATERRAMIENTO DE ESTRUCTURA El contratista efectuará el trabajo de poner a tierra. el Contratista medirá la resistencia de cada puesta a tierra y los valores máximos a obtenerse serán de 16 ohmios. en caso que existiera Los soportes metálicos de los seccionadores .fusibles El borne pertinente de los pararrayos El electrodo de puesta a tierra será instalado en un pozo de puesta tierra el cual incluirá tierra vegetal y luego una aplicación de aditivos químicos (sales químicas) similar Erico Gel de 7 kg. Los detalles constructivos de la puesta a tierra se muestran en los planos del proyecto. las siguientes partes de las estructuras:
. La orientación de los interruptores será tal manera que permita su maniobralidad con facilidad y no requiriéndose la exposición del personal que realice la maniobra a situaciones de peligro por tensión o tráfico vehicular. En estructuras bipostes se considerarán 2 conjuntos. 3. incluido la instalación de la cruceta y aisladores tipo PIN o cadena de aisladores. mediante conectores. mediante conectores.Los seccionadores tipo Cut-Out irán instalados en crucetas metálicas simples o dobles. Se pondrán a tierra. La medición será por conjunto. conjuntamente que los aisladores tipo Pin o cadenas de aisladores en caso de requerirse estos.19 INSTALACION DE PUESTA A TIERRA Las estructuras serán puestas a tierra mediante conductores de cobre fijados a los postes y conectados a electrodos verticales de cobre instalados en pozos en el terreno. las siguientes partes de las estructuras: Las espigas de los aisladores tipo PIN.
a fin de lograr una mejor protección y reparación. para efectuar su mantenimiento mediante el suministro e instalación de una dosis de aditivos químicos. 3.23 PINTADO DE CÓDIGO Y SEÑALIZACIÓN DE ESTRUCTURAS a) PINTADO DE SEÑALIZACION DE LAS PUESTAS A TIERRA EN LAS ESTRUCTURAS DE ANCLAJE. El pintado de señalización de las puestas a tierra. 3. el tamaño de las letras y números será de acuerdo al modelo (ver anexo).22 REFORZAMIENTO DE BASE DE POSTE. se efectuará tomando en consideración el modelo (ver anexo) y serán pintados de color negro. 3. El contratista efectuará el reforzamiento de la base del poste mediante un cono de concreto. Los pernos de sujeción de las cadenas de suspensión angular y de anclaje El conductor neutro. directamente sobre la superficie del poste el cual será pintado de fondo amarillo. 77
.fusibles El borne pertinente de los pararrayos
La unidad de medida y pago será por el aterramiento efectuado y por tipo de estructura. En estructuras bipostes se consideran 2 conjuntos.-
Las espigas de los aisladores tipo PIN. b) PINTADO DE CODIGO DE POSTES POSTES DE MEDIA TENSION El pintado de la codificación de postes en media tensión se efectuará con 04 campos en fondo azul eléctrico y las letras y números serán de color blanco. La altura del cono de concreto será de 0. en caso que existiera Los soportes metálicos de los seccionadores . La unidad de medida y pago será por el reforzamiento efectuado a un poste.35 m de longitud. para lo cual requerirá realizar excavaciones a la base del poste.21 INSTALACION DE CAJA REGISTRO El contratista ubicará el pozo del sistema de puesta a tierra de la estructura. similar Erico Gel de 7 kg y una caja registro para su posterior mantenimiento. La unidad de medida y pago será por mantenimiento de un pozo de puesta a tierra con aditivos químicos y la instalación de una caja registro.
se efectuara en todos los postes y estructuras que comprende el proyecto y en los existentes en la zona de influencia. Concluidos los trabajos de pintado. 3. El pintado de codificación y señalización. pintura esmalte colores negro.24 INSPECCIÓN Y PRUEBAS a) INSPECCIÓN DE OBRA TERMINADA Después de concluida la Obra. el contratista presentara los planos de replanteo de las Redes de Distribución con la codificación y señalización definitiva. El contratista presentara a la Supervisión el plano de replanteo con la codificación correspondiente de acuerdo al modelo que se indica en las especificaciones técnicas y a los planos de detalles para su aprobación. sea esta vereda. plantillas. blanco. amarillo y azul eléctrico. de acuerdo al metrado del presupuesto. La altura a considerar para el pintado de la codificación de postes. el contratista preverá el suministro de materiales tales como. Deberá verificarse lo siguiente: 78
.Como ejemplo se anota lo siguiente: __B__ 041 donde: “B”. Las dimensiones de las letras y trazos serán de forma horizontal de acuerdo con los modelos que se adjuntan en los anexos. antes de efectuar el pintado de la codificación. deberán ser retirados dichos afiches. d) CONSIDERACIONES EN LA EJECUCION DEL PINTADO En caso de existir afiches y propagandas pegados sobre la zona de pintado del código ó avisos de seguridad. identifica a la terna “041”. subestaciones será a 3. thinner. antes de efectuar los trabajos de pintado. la Supervisión efectuará una inspección general a fin de comprobar la correcta ejecución de los trabajos y autorizar las pruebas de puesta en servicio.5 metros del nivel del piso. y brochas. pista o tierra firme. También se considera la verificación de la información de codificación de postes de media conforme a las coordinaciones con ELECTROSUR S. representa el numero correlativo del poste c) ALCANCES DEL PINTADO DE POSTES Para realizar los trabajos de Pintado de Codificación de Postes de Media Tensión.A.
El cumplimiento de las distancias mínimas de seguridad. 79
. Ajuste de las grapas de ángulo y de anclaje. anclaje a la estructura.
c) PRUEBAS DE PUESTA EN SERVICIO Las pruebas de puesta en servicio serán llevadas a cabo por el Contratista de acuerdo con las modalidades y el protocolo de pruebas aprobado. En el Interruptor de potencia: estanqueidad.
b) INSPECCIÓN DE CADA ESTRUCTURA En cada estructura se verificará que se hayan llevado a cabo los siguientes trabajos: Reparación de veredas. limpieza y estado físico de los aisladores tipo PIN y de suspensión. Al medir el aislamiento entre una fase y cada una de las otras fases debe obtenerse una resistencia de valor nulo. Los pasadores de seguridad de los aisladores y accesorios deben estar correctamente ubicados. Los residuos de embalajes y otros desperdicios deben haberse retirado. Entre Fases 2. relleno. y de los conductores de fase respecto a tierra. compactación y nivelación alrededor de las cimentaciones. nivel del aislante. y el traslado de materiales de desmonte u otros. Ajuste de pernos y tuercas. Montaje. Instalación de los accesorios del conductor. propios del trabajo ejecutado. conforme a las recomendaciones del fabricante. El correcto montaje de las estructuras dentro de las tolerancia permisibles y de conformidad con los planos aprobados. La limpieza de los conductores La magnitud de las flechas de los conductores debe estar de acuerdo con lo establecido en la tabla de tensado. El programa de las pruebas de puesta en servicio deberá abarcar: Medición de aislamiento Se efectuarán las mediciones de la resistencia de aislamiento de los conductores de fase entre sí. Los valores mínimos de resistencia de aislamiento que deben obtenerse son los siguientes: Descripción de Mediciones En Media Tensión: 1. De fase a tierra Valores de Aislamiento Aceptables Condiciones Normales Condiciones Húmedas 100 M-Ohmios 50 M-Ohmios 50 M-Ohmios 20 M-Ohmios
Prueba de Continuidad Esta prueba consiste en cortocircuitar los conductores de fase al inicio del circuito en la subestación y comprobar la continuidad en el otro extremo. ajuste de barras y conexionado en general.
se procederá a la aplicación de tensión en vacío por un período de 24 horas. estando esta desconectada del sistema. este deberá ser instalado en el nuevo poste.Prueba de tensión Luego que se hayan realizado las mediciones de aislamiento y las pruebas de continuidad.T. Es decir deberán realizarse todas las conexiones necesarias. 3. siendo el valor máximo tolerado de dieciocho (16) ohmios para una varilla de puesta a tierra. cuando corresponda. Asimismo en caso de haberse requerido la desconexión de acometidas domiciliarias. 80
. y habiéndose obtenido valores satisfactorios. acondicionará las instalaciones eléctricas del subsistema de distribución secundaria al nuevo poste de M.26 DESMONTAJE TEMPORAL DEL CONDUCTOR El contratista deberá realizar el desmontaje del conductor existente. UNIDADES DE AP Y CONEXIONES DOMICILIARES. pudiendo coordinar en este último caso con sus propietarios a fin de que se sirvan realizar utilizara el nuevo poste como sostén de sus cables. La resistencia de puesta a tierra en los puntos más desfavorables.25 ACONDICIONAMIENTO DE INSTALACIONES DE RED SECUNDARIA EN POSTE DE MT. estando conectadas todas las puestas a tierra no deberá superar los tres (03) ohmios. Prueba de Puesta a tierra Debe verificarse los valores de resistencia de puesta a tierra. para lo cual es necesario soltar los amarres efectuados a los aisladores tipo PIN que los sostienen y soltar las grapas tipo pistola que lo sujetan en caso de ser necesario. INCLUIDO CABLE STAR. Durante este tiempo se efectuarán las mediciones de tensión en los puntos más importantes de cada circuito y se determinará la secuencia de fases. 3. La unidad de medida y pago será por acondicionamiento realizado en una estructura de tal forma que queden las conexiones como antes de realizar el retiro del poste dañado. El contratista. En caso de haber existido alumbrado público en el poste retirado. instalación de alumbrado público. de tal forma que estos queden de forma similar a como estaban antes de retirar el poste en mal estado. instalado por reemplazo de otro en mal estado. estas deberán ser reconectadas a fin de continuar atendiendo con el servicio del suministro eléctrico al cliente (en el plazo mas breve). así como otras instalaciones que se encontraban apoyadas tales como cable Star.
son considerados aparte con su respectivo presupuesto de desmontaje. Todos los materiales desmontados serán trasladados a los almacenes de Electrosur S. 3. La unidad de medida y pago será por metro de conductor desmontado y por fase. o soltar los anclajes desde las grapas tipo pistola. mediante la instalación de tres o seis cadenas de aisladores. aisladores tipo PIN y/o tipo suspensión.En vista que el conductor ha de ser reinstalado. de tal forma que no sufran daños y permitan realizar los desmontajes de los elementos que han de ser cambiados. para lo cual se requiere soltar los amarres a los aisladores que sostienen. 3.A.29 DESMONTAJE DE ARMADOS El contratista efectuará el retiro del armado de línea primaria existente. en las zonas de trabajo.
.27 MODIFICACION DE ARMADO DE M. La unidad de medida y pago será por armado modificado. crucetas y/o ménsulas.28 DESMONTAJE DE MENSULAS Y CRUCETAS El contratista efectuará el desmontaje de las ménsulas y crucetas incluido sus aisladores. aisladores tipo PIN o suspensión. Todos los elementos desmontados serán entregados en almacén de Electrosur S. 3. correspondientes a una sola terna. A ARMADO DE ANCLAJE El contratista efectuará el cambio de una estructura de alineamiento que actualmente es utilizado como fin de línea o anclaje a estructura de fin de línea o anclaje según corresponda. deberá ser convenientemente sujeto temporalmente a las estructuras que los sostienen. conformada por: un poste de M.A. El contratista de ser necesario deberá prever el anclaje temporal del conductor al poste o cruceta existente. es decir los correspondientes a una línea trifásica de una sola terna.T. La unidad de medida y pago será por ménsula o tipo de cruceta desmontada. El desmontaje de los elementos requeridos para. a fin de permitir la instalación de las cadenas de aisladores. así como para efectuar derivaciones para alimentar circuitos adyacentes o la instalación de seccionadores incluido soporte para derivación. incluido crucetas y/o ménsulas. etc. La unidad de medida y pago será el desmontaje del conjunto. la instalación de otra terna en la misma estructura. poste.T.
N.2 (2) 14.9 (2) 25.
4.2 (2) 25/14.5 (1) PRACTICA EUROPEA (2) PRACTICA USA Y CANADA
95 75 125
(2) 34 50 40
TENSION DISRRUPTIVA BAJO LLUVIA: Uc = 2.IV. el que considera la distancia mínima entre fases en el punto
.00 kV 4.2 22.1 (U+5) Uc = 31. CALCULOS JUSTIFICATIVOS. se han tomado en cuenta las recomendaciones del código Americano de Seguridad Eléctrica (NESC).3 DISTANCIAS ELECTRICAS DE SEGURIDAD Con el objeto de asegurar el aislamiento de las fases ante el riesgo de cortocircuitos.50 kV TENSION DISRRUPTIVA EN SECO Uc = 2. CUADRO 4. El cuadro siguiente muestra las características de aislamiento para los diferentes niveles de tensión adoptados.2
NIVEL DE AISLAMIENTO El sistema debe soportar las tensiones de operación nominal y además aquellas sobretensiones momentáneas que pueden ser de origen externo o interno sin que se llegue a producir flameo.5 22.9/13.1 NIVELES DE AISLAMIENTO
TENSION NOMINAL DEL SISTEMA KV EFICAZ TENSIÓN MAXIMA DEL SISTEMA KV EFICAZ CLASE DE AISLAMIENT O KV TENSION NO DISRRUPTIVA AL IMPULSO (NIVEL BASICO DE AISLAMIENTO) TENSION NO DISRRUPTIVA A 60 Hz KV EFICAZ
10 (1) 11 13.1
CALCULOS ELECTRICOS REDES PRIMARIAS
GENERALIDADES Todos los cálculos se han desarrollado en base al C. Normas Vigentes y Disposiciones reglamentarias relacionadas con este fin.2 (U + 5) Uc = 33..E.
.60 m 7. 4.3.60 m
Por consiguiente se utilizará soportes de 13 m de altura.
4.45 m De acuerdo al C.00 m 12.3 DISTANCIA DE LOS CONDUCTORES AL TERRENO
Esta distancia viene determinada por la siguiente expresión: d = 5. será: Para conductores menores a 35 mm2 D = 0.00 m.N.
.1 SELECCION DE LA ALTURA DE LA ESTRUCTURA H = D + fmax + H1 + He Donde: H : D : Fmax : H1 : He : He Fmax D H1 H = = = = = Altura total del poste en m Distancia de la punta del poste a la cruceta en m Flecha máxima a 45 °C Altura mínima sobre la superficie Altura de empotramiento 1.E.30 m 1. que para este caso es de 60 m. se adopta una distancia mínima al terreno de 7. para la condición de armados de alineamiento.70 m 2.medio del vano máximo.3 + U/150 Luego para Un = 10 kV d = 5.3.22 m
4.2 DISTANCIA MINIMA DE LOS CONDUCTORES ENTRE SI
a) Separación mínima en sus postes para una tensión de 10 kV estará dada por: D = 0.3.40 m La separación mínima a la mitad del vano.
CALCULO PRIMARIA
HIPOTESIS DE CALCULO HIPOTESIS I Temperatura Velocidad de viento Coeficiente de seguridad Sobrecarga de hielo HIPOTESIS II Temperatura media Presión del viento Tensión de cada día HIPOTESIS III Temperatura máxima Presión del viento HIPOTESIS IV Temperatura Presión del viento Vano promedio : : : : : : : : : : : : : : : : Condiciones de temperatura mínima.00 Nula Condiciones de templado 16 °C Nula 18% Condiciones de flecha máxima 45 °C Nula Condiciones de flecha mínima 5 °C Nula 60 m
4.3.1 + U/150 dce = 0.4 SEPARACION MINIMA ENTRE CONDUCTORES Y SUS ESTRUCTURAS
Para aisladores tipo PIN. se tiene: dce = 0.σ1 = (E/24)((Wr2d)/S)2 Donde: α E t σ Wr d S : : : : : : : Coeficiente de dilatación lineal 1/°C Módulo de elasticidad en kg/mm2 Temperatura en °C esfuerzo en kg/mm2 Peso unitario resultante en kg/m Vano en m Sección del conductor de mm2
4. 5 °C 90 km/h 3.4.5
ECUACION DE CAMBIO DE ESTADO (σ2)2*(σ2+αE(t2-t1) + (E/24)((Wr1d)/(Sσ1))2 .
6 DEMANDA DE POTENCIA Para la determinación de la demanda se ha considerado la planilla de medición del Sistema Eléctrico Moquegua.54 Demanda Total (kW) 4 165.E. Así también se tiene: Presión del Viento Pv = K V2 (kg/m2) K = 0.E. Alto Zapata (kW) 2 818.N.40 S.Nota: Los subíndices 1 y 2. San Antonio (kW) 1 347. a partir de los cuales se ha planteado una demanda conforme a lo que se indica en el siguiente cuadro:
S.02 kg/m2 Peso resultante del conductor Wr = ((Wc)2 + (Pv*dc*10-3)2)1/2 4. indican condiciones iniciales y finales respectivamente.0042 V = 90 km/h (Dato del C.) Pv = 34.94
METRADO PRESUPUESTO
VII. III. IV.88 28 086.TOTAL 1 (I + II + III) GASTOS GENERALES (7 % de IV) UTILIDADES (5 % de IV)
TOTAL (S/.VALOR REFERENCIAL DEL PROYECTO
PROYECTO FINANCIA UBICACION FECHA
SISTEMA DE ANILLADO EN REDES PRIMARIAS EN 10 KV .66 1 755. V.50
VI.44 1 253.53 33 423. II.A.
.48 25 077. ITEM SUMINISTROS DE MATERIALES MONTAJE Y DESMONTAJE ELECTROMECANICO TRANSPORTE (5 % de I) SUB .MOQUEGUA ELECTROSUR S.TOTAL 2 (IV + V)
IMPUESTO GENERAL A LAS VENTAS (19 % de VI)
VIII.51 4 340.
SUB .97
TOTAL (VI + VII)
S/.) 19 749.67 987. MOQUEGUA OCTUBRE 2005
1.5/250 de 170 mm de díametro u 7 1.5"x1/4"x3.04
0.00 m .Una (01) cruceta de 3"x3"x1/4"x3.45 999.C.C.Un (01) brazo de FoGo de 2.75 350.5"x2. de Z/1.00
1. conformado por: . de diámetro .V.05 Ménsula de C.Una (01) abrazadera tipo UM redondo de 5/8" de diámetro . de diámetro .5"x1/4"x1.30 41. de 13/300/ m u 0 1. Unitario Total S/.90 434.Una (01) abrazadera circular de 2"x1/4"x210 mm.Una (01) cruceta de 3"x3"x1/4"x2. de diámetro .00 0. incluído arandelas y tuercas Cruceta doble de Fo Go tipo simple asimétrica.
116.Un (01) brazo de FoGo de 2.70
187.60 m .00
.C. incluído arandelas y tuercas Jgo. conformado por: .METRADO Y PRESUPUESTO REFERENCIAL PROYECTO FINANCIA UBICACION FECHA SISTEMA DE ANILLADO EN REDES PRIMARIAS EN 10 KV .40 m . incluído arandelas y tuercas Cruceta de Fo Go Para Seccionamiento tipo asimetrica.Una (01) abrazadera tipo UM redondo de 5/8" de diámetro .Un (01) perno de 1/2" diámetro x 3". conformado por: .10 m. de diámetro .Una (01) abrazadera circular de 2"x1/4"x210 mm.A.Una (01) abrazadera circular de 2"x1/4"x210 mm.60 40.5"x1/4"x0.A.Un (01) brazo de FoGo de 2.06 Cruceta de C.02 Poste de C.11
Jgo.5"x2. incluído arandelas y tuercas Cruceta doble de Fo Go tipo simple asimétrica.80
0.A. MOQUEGUA OCTUBRE 2005 METRADO ITEMS DESCRIPCION UniCantidad dad 1.Un (01) perno de 1/2" diámetro x 3".Un (01) perno de 1/2" diámetro x 3". .Un (01) brazo de FoGo de 2.Una (01) abrazadera circular de 2"x1/4"x210 mm.Una (01) abrazadera circular de 2"x1/4"x210 mm. conformado por: Jgo.A.5"x2.01 Poste de C.A. .45 499. 3 .10 m.09
Jgo.60 m .00 m . 434.08 Cruceta de Fo Go tipo simple asimétrica.Un (01) perno de 1/2" diámetro x 3".Una (01) abrazadera tipo UM redondo de 5/8" de diámetro . .Una (01) cruceta de 4"x4"x1/4"x1. conformado por: .60 m .Una (01) abrazadera tipo UM redondo de 5/8" de diámetro .5"x2.Un (01) perno de 1/2" diámetro x 3".58
1.25 116.00
0.00 ESTRUCTURAS 1.5"x1/4"x0.V.10/250 de 170 mm de diámetro u 0 1.Un (02) brazo de FoGo de 2. de diámetro .C.Una (01) cruceta de 3"x3"x1/4"x1.Una (01) cruceta de 3"x3"x1/4"x1.Un (02) brazo de FoGo de 2.75 m.75 m. conformado por: .Una (01) abrazadera circular de 2"x1/4"x210 mm.07 Cruceta de Fo Go tipo simple asimétrica.04 Poste de C.Una (01) abrazadera tipo UM redondo de 5/8" de diámetro . 0 : : : :
PRESUPUESTO Precio Presup. m/1.A.00 281. u 2 1.79
503. de diámetro . .
Jgo. u 1 1.24 0.10
Jgo. incluído arandelas y tuercas 1.5"x2. incluído arandelas y tuercas Cruceta de Fo Go tipo simple asimétrica.Una (01) cruceta de 3"x3"x1/4"x3.62 613.90
116. de 12/200/160/340 m.25 m.00 0. de 12/300/160/340 m.5"x1/4"x2.MOQUEGUA ELECTROSUR S.00 m.5"x1/4"x3.Un (01) perno de 1/2" diámetro x 3". .5"x2.A.Una (01) abrazadera tipo UM redondo de 5/8" de diámetro .03 Poste de C.
239.20 693. de 13/400/ m u 0 1. .
00 0.2 incluido Cjto.85 1. X 254 mm C/T y CT Tuerca ojo 16 mm dia.07 3.32
102.01 Aislador de porcelana tipo PIN Clase 56.Aisladores tipo suspensión.09 4.10 2. incluye .G. PS/1.61 70. bimetálico p/cond.02 4.36 2 392.68
0. para aislador Clase 56.90
159.07 4.04 3. 16 mm2 sección.Un (01) perno ojo de F°G° de 5/8"¢x8".00 194.00
m m m m m Pza Pza Pza m
96 1156 2600 37.01 0.03 Cadena de aisladores conformada por: Cjto. De 5 Vías.36 12. sólido Varilla de armar preformada simple para conductor de 35 y 50 mm2 Conector doble vía de aluminio. poliméricos 25 kV.29 3.20 1.03 3.80 102.66 2. Conductor de aleación de aluminio.05 4.Una (01) Grampa de Anclaje tipo ángulo de F°G° .00
. Unitario Total S/. para conductor de 35-50 mm² de sección Conector doble vía.08 3. con pelicula aislante protectora.02 3.00 33.Un (01) grillete .41 105.44 109.2 2. de Al/Cu de 50/35 mm2 Cinta plana para armar MATERIAL DE FERRETERÍA DE POSTES Y CRUCETAS Varilla roscada 16 mm dia. Presillas para cinta bando-it de 3/4" Pastoral de F. tipo C(AA)PI de 35 mm² de sección.45 89.00 0. : : : :
PRESUPUESTO Precio Presup.00 0.07 3.Un (01) perno ojo de F°G° de 5/8"¢x8".2 0 31 27 42 0
1.33 5. poliméricos 25 kV .03 4.05 3. tipo C(AA)PI de 25 mm² de sección.30 1. Conductor de Al desnudo.68 1 326.00 AISLADORES Y ACCESORIOS 2. con pelicula aislante protectora. 12" long. 42.Aisladores tipo suspensión.89 6.01 4.04 4.00 3.70 0.48 0.38 92.50/1.00 0.00 4. MOQUEGUA OCTUBRE 2005 METRADO ITEMS DESCRIPCION UniCantidad dad 2.23 2. incluido arandelas y demás accesorios 3.0/1 1/2" diam.20 7. y demas accesorios. 31 Espiga de 3/4" .Un (01) grillete . con pelicula aislante protectora.06 3. incluido arandelas y demás accesorios 2.90 0. 24 .02 Cadena de aisladores conformada por: Cjto.06 4. 0 .43 4.MOQUEGUA ELECTROSUR S.00 43.01 3.40 5.Una (01) Grampa de Anclaje tipo Pistola de F°G° . incluye pernos de 2"x1/2" diam. temple suave.99 91.A. Conductor de aleación de aluminio. Perno ojo de 16 mm diámetro contratuerca cuadrada para perno de 16 mm Arandela cuadrada curvada de 57x57x5 mm Arandela cuadrada plana 57x57x5 mm Aislador de porcelana marrón clase Ansi 53-1 Portalínea de F.80 245.METRADO Y PRESUPUESTO REFERENCIAL PROYECTO FINANCIA UBICACION FECHA SISTEMA DE ANILLADO EN REDES PRIMARIAS EN 10 KV .45
107.92 7 826.00 0.11 CONDUCTORES Conductor de aleación de aluminio. tipo C(AA)PI de 50 mm² de sección.80 2 464. Con diametro interior de 215 mm.00
Pza Pza Pza Pza Pza Pza Pza Pza Rollo Pza Cjto
17 14 8 26 6 40 0 0 0 0 0
6. sólido Conductor de cobre aislado de 10 mm² tipo TW.G. para una separación de 15 cm entre ejes de aisladores Cinta Band-it de 3/4".09 4.00 5.08 4.10 4.
5 . Unitario Total S/. 0 5.00 6. arandelas y tuercas . de 5/8"¢x2. T. 3 3 227.02 Retenida tipo Contrapunta.Bil 150 kV.99 19 749.01 Conector tipo Anderson Electric .Aditamento Químico de P.70 173.33 682.MOQUEGUA ELECTROSUR S.80 0.40m.15m 5.02 SISTEMA DE PROTECCIÓN Seccionador Tipo Cut-Out 100 A.50x0. 7 Kgr. Fusibles tipo chicote 10 A.50x0.01 aislador tipo tracción 54-3 .00 865. 2 contrapunta de F°G° de 1. 134.00
168. 15 kV.01 guardacable de 1/16"x2.01 varilla de anclaje de 3/4"¢x2.04 Sistema de Puesta a tierra Equ. TOTAL SUMINISTRO DE MATERIALES Pza.01 6.40 0. para cable de 1/2"¢ . temple suave.50 12.40 m . Pza.01 arandela cuadrada de 4"x4"x1/4" con agujero para varrilla de 3/4"¢ .01 varilla de Cu.51 : : : :
PRESUPUESTO Precio Presup.03 Retenida tipo Violin según especificaciones Jgo.00
337.03 m3 de tierra vegetal 6. (GEL).02 guardacabos de 1/16".01 bloque de concreto armado de 0.00 FERRETERÍA DE ALTA CORROSIÓN 5.50 4.01 abrazadera de F°G° tipo partido de 2"x1/4"x210mm .15 m de conductor de cobre.70 168.04 grapas de F°G° de vias paralelas tres pernos . . 0 . de 25mm² sección .01 Retenida tipo simple Conformada por: Jgo. idém anterior mas una Jgo..40m .01 caja de puesta a tierra . MOQUEGUA OCTUBRE 2005 METRADO ITEMS DESCRIPCION UniCantidad dad 5. 5. incluido abrazadera y acces.A.15m de cable de acero galvanizado de 1/2"¢ .00
.2 m.METRADO Y PRESUPUESTO REFERENCIAL PROYECTO FINANCIA UBICACION FECHA SISTEMA DE ANILLADO EN REDES PRIMARIAS EN 10 KV .
Cjto. u u u u Jgo. Jgo.57 226.32
0.84 62. Cjto.39 0.16 7.10 88.60 1 5 8 0 1
203.10 7.48 25 077.00 437.64 106.22 222.20 88. incluido aisladores Tendido y Puesta en Flecha de Conductor de aleación de aluminio de 25 mm² Tendido y Puesta en Flecha de Conductor de aleación de aluminio de 35 mm² Tendido y Puesta en Flecha de Conductor de aleación de aluminio de 50 mm² Instalación de Seccionador Cut Out Instalación de sistemas de puesta a tierra Pintado de postes y señalización de estructuras Acondicionamiento de la terna B y D para ser una sola terna Pruebas y puesta en operación DESMONTAJE ELECTROMECÁNICO Desmontaje de conductor de cobre de red primaria existente 16 mm² Desmontaje de conductor de cobre de red primaria existente 25 mm² Desmontaje de conductor autoportante de media tensión Desmontaje de cruceta simple incluido aisladores Retiro de postes de C.03 7.65 45. Cjto.52 0.67 987.A. Km Km Km Cjto. Cjto.00 426.04 7.C.15 7.22 8.15 27.13 30.02 8.67 329.A. trazo y estacado Transporte de postes al punto de izaje Excavación de huecos para poste de 12 m Excavación de huecos para poste de 13 m Excavación de huecos para retenida y puesta a tierra Instalación de puesta a tierra Instalación de retenida tipo Simple Instalación de retenida tipo Contrapunta Armado de Alineamiento Trifásico tipo A1.3 2.11 7.07 7.14 7.01 7.
1.00 67.97
.56 46.46 44.68 140.76 956.A.48 10. Cjto.49 112.09
Km.V.03 8.02 7.44 1 253.58 0. A13 Armado de Anclaje ó Cambio de Dirección Trifásico Tipo A72.C.09 7. A3.16 31.
0.19 7. considerando romper loza asfáltica de calzada o vereda y resane Desmontaje de seccionamientos incluye accesorios y soporte del seccionamiento Desmontaje de cadena de aisladores incluye accesorios de fijación y soporte Retiro de postes de C. hasta 9 metros.76 58.84
85.58 38.18 7.45
37. Cjto.10 1. A1F Armado de Alineamiento Trifásico tipo A12.20 7.17 7.67 19 749.05 0. Jgo.A.92 0.00 0.66 1 755. A4 Armado de Anclaje ó Cambio de Dirección Trifásico Tipo A73.66 222. A7. Cjto.00 90.00 8.11 0. incluye elementos de BT. A33 Montaje de Armado de Seccionamiento con Derivación Montaje de Armado de Derivación TD Instalación de mensulas de C.71 98.04 8.METRADO Y PRESUPUESTO REFERENCIAL PROYECTO FINANCIA UBICACION FECHA ITEMS : : : : SISTEMA DE ANILLADO EN REDES PRIMARIAS EN 10 KV .19 206.38
Km Km Km Cjto.00 7.75 27.12 7.51 4 340.66 44. hasta 13 metros. Cjto.28 367. existentes (alineamiento ó ángulo) incluye desmontaje elementos de baja tensión considerando romper loza asfáltica de calzada o vereda y resane Desmontaje y montaje de conductor existente a nueva estructura
km.00 30.90 0.13 7.06 8.00
8.06 7. Cjto.71 0.43 0 3 0 1 3 0
284.00 0.00 20.28 789.07 8.19 121. Cjto.26
TOTAL MONTAJE y DESMONTAJE ELECTROMECÁNICO I II III IV V VI VII RESUMEN SUMINISTRO MONTAJE TRANSPORTE 5% SUB TOTAL -1 GASTOS GENERALES (7 % de IV) UTILIDADES (5 % de IV) SUB TOTAL -2
4 340.00 0.75 284.88 28 086.47 22. Cjto.56 0.16 2.08
MONTAJE ELECTROMECÁNICO Replanteo.05 8.90 4. Cjto.28 3 3 0 7 5 0 2 1 0 0 0 3 0 0. A7F.MOQUEGUA ELECTROSUR S.00 7. MOQUEGUA OCTUBRE 2005 METRADO DESCRIPCION UniCantidad dad
PRESUPUESTO Precio Presup. Cjto. A773.89 997.46 62.28 324.33 46.
7.16 10.38
260.72 19.08 7.63 12.01 8. Cjto.83 426. A77. Cjto. Unitario Total S/.00 12.37 126.21 7.48 0.
More From This UserSkip carouselAPLICACIÓN DE LAS NORMAS DE ILUMINACIONLianlizacion de Tendencias LogaritmicasIluminacion Industrialletra de miley
Sign up to vote on this titleUsefulNot usefulSistema de anillados by alejolibido0.0 (0)EmbedDownloadRead on Scribd mobile: iPhone, iPad and Android.Copyright: Attribution Non-Commercial (BY-NC)List price: $0.00Download as PDF, TXT or read online from ScribdFlag for inappropriate contentMore informationShow less
RelatedI Ingenieria Basicaby edwinddccARMADOS DE OSINEGMINby Amilkr Lopez RamosMemoria Descriptivaby César Milián Santa CruzAISLADORES TIPO PINby estefanicueva3Mby xhadeusolx34296119 Curso Electrificacion Rural 24 27 Mayoby CesarAmpueroProyecto Completo- Alumbrado Exteriorby divisionticVe Gue Tap Roy Ecto 022012 Simonby Santiago LunaSU-CMby Uli CarEspecificaciones Tecnicas Suministro Media Tensiónby sergioyebel01.- PERFIL CATACHEby César Milián Santa CruzArmados Media Tensionby tunradotProyecto de Media Tension Aereaby Raul Ortizcoord protec.by Jesus Orosco LeguiaPERFIL ELECTRIFICACIÓN LA COLINA 2010 - ACTUALIZADOby 210568Spat 082007 Aby api-3741560Similar To Sistema de anilladosSkip carouselI Ingenieria BasicaARMADOS DE OSINEGMINMemoria DescriptivaAISLADORES TIPO PIN3M34296119 Curso Electrificacion Rural 24 27 MayoProyecto Completo- Alumbrado ExteriorVe Gue Tap Roy Ecto 022012 SimonSU-CMEspecificaciones Tecnicas Suministro Media Tensión01.- PERFIL CATACHEArmados Media TensionProyecto de Media Tension Aereacoord protec.PERFIL ELECTRIFICACIÓN LA COLINA 2010 - ACTUALIZADOSpat 082007 AEspecificacionesbajaymediatensionFormulas Para Calculos Electricos Mecanicos Para ProyectosPROYECTOSistema de anillados

References: artículo 106
 artículo 240
 artículo 76
 artículo 133
 artículo 242
 artículo 239
 Artículo 253
 artículo 247
 artículo 211
 artículo 255
 Artículo 37
 artículo 240
 artículo 239
 artículo 268
 artículo 269
 resolución