Source: https://www.pacode.com/secure/data/025/chapter73/s73.17.html
Timestamp: 2019-04-19 08:17:48+00:00

Document:
025 Pa. Code § 73.17. Sewage flows.
*For units of 3 bedrooms or less; for each bedroom over 3, add 100 gallons.
(c) Actual water meter or sewer meter flow data indicating peak daily flows different than those shown in this section over a 1-year period for a similar nonresidential establishment may be accepted for use in sizing the onlot disposal system. If average daily flows are used, the peak daily flow shall be calculated by multiplying the average daily flow by two.
(d) Establishments with food preparation facilities are required to install adequately designed pretreatment units and traps to reduce greases and biological oxygen demand (BOD) prior to discharge to an individual or community sewage system.
The provisions of this § 73.17 amended under section 9 of the Pennsylvania Sewage Facilities Act (35 P. S. § 750.9); The Clean Streams Law (35 P. S. § § 691.1691.1001); and section 1920-A of The Administrative Code of 1929 (71 P. S. § 510-20).
The provisions of this § 73.17 adopted January 21, 1983, effective January 22, 1983, 13 Pa.B. 508; amended November 7, 1997, effective November 8, 1997, 27 Pa.B. 5877. Immediately preceding text appears at serial pages (217318) to (217320).
This section cited in 25 Pa. Code § 71.52 (relating to content requirementsnew land development revisions); 25 Pa. Code § 72.22 (relating to permit issuance); 25 Pa. Code § 73.16 (relating to absorption area requirement); 25 Pa. Code § 73.31 (relating to standards for septic tanks); 25 Pa. Code § 73.32 (relating to standards for aerobic treatment tanks); and 25 Pa. Code § 73.161 (relating to general).

References: § 73
 § 73
 § 750
 § 691
 § 510
 § 73
 § 71
 § 72
 § 73
 § 73
 § 73
 § 73