Source: http://etpo.khpi.edu.ua/article/view/93627
Timestamp: 2019-04-24 03:02:40+00:00

Document:
The efficiency of operation of the steam turbines of a high power is defined by the values of steam leakage through the seals, and first of all through the end seals that can occupy more than 30% of the length of high pressure rotor. The seals of a step type used at the present time change their performances if the crests are worn down during the overhaul period and can be restored at mid-life and/ or subjected to capital repairs. Therefore, the search for the rotor seal construction that would allow for an increase in the reliability of turbine operation is rather vital. The purpose of this research was to estimate appropriateness of the replacement of HPC step-type seals by noncontact seals with crossed crests. The method used for the solution of stated problem was the computation investigation of the flow of viscous high temperature steam through the sealing sector with crossed crests at different values of the radial clearance and axial movements. The flow rate comparison data showed that the original step-type seal with the radial clearance of 0.7 mm can be replaced by the noncontact seal with crossed crests with the radial clearance of 0.5 to 0.6 mm at the typical operation to provide a reliable operation. Moreover, steam leakages through the front end seal can be reduced for the offered structure option in comparison with the original option.
(1986), Labyrinth packing standard steam and gas turbines and compressors. Engineering and design. RTM 108.020.33-86.Moscow, Russian.
Lisyanskiy, A. S., Gribin, V. S., Sahnin, Yu. A., Fatkov, O. V., Gorlitsyn, K. V. and Ushinin, S. V. (2013), "Prakticheskiyopytvnedreniya sotovyh nadbandashnyh uplotneniy na blokah sverhkriticheskogo davleniya moschostyu 250-800MVt[Practicalexperience in implementing cellular nadbandazhnyh seals on power units of supercritical pressure 250-800MVt]",Powerstations [Power stations], No. 10. pp. 8–13, ISSN 0201-4564.
Buglaev, V. T., Klimtsov, A. A., Perevezentsev, V. T. and Perevezentsev, S. V. (2002), Sotovye uplotneniya v turbinah[CallMobile seal in turbomachines], BGTU, Bryansk, Russian.
Goloschapov, V. N., Alexina, S. V., Kotulskaya, O. V., Paramonova T. N. and Konev, V. A. (2015),"Harakteristikinadbandashnyh uplotneniy so vstrechnymi grebnyami stupeney tselindra vysokogo I srednegolavleviyparovyh turbin[Featuresnadbandazhnyh seals with high and medium pressure steam turbine stages ofthecounter cylinderridges]",ReportsofХV Intern conf. "An Improvement of turbine units by the methods of mathem. andphys.modeling" 15 Sept.[Electronic],IPMashofNASU, Zmiev, Ukraine (accessed 28 September 1015).
Shegliaev, А. V. (1993), Parovye turbiny [Steam Turbines], Jenergoatomizdat [Energoatomizdat], Moscow, Russian.
1 Уплотнения лабиринтные стандартных паровых и газовых турбин икомпрессоров.Проектированиеирасчет:РТМ108.020.33-86. – М.-Л.: Госстандарт, 1986. – 51 с.
2 Лисянский, А. С. Практический опыт внедрения сотовых надбандажных уплотнений на блокахсверхкритическогодавления мощностью 250-800 МВт / А. С. Лисянский, В. Г. Грибин, Ю. А. Сахнин, О.В.Фатьков, К. В.Горлицын,С.В.Ушинин // Электрические станции. – 2013. – № 10. – С. 8–13. – ISSN 0201-4564.
3 Буглаев, В. Т. Сотовые уплотнения в турбомашинах / В. Т. Буглаев, А. А. Климцов, В. Т. Перевезенцев, С.В.Перевезенцев. – Брянск : БГТУ, 2002. – 148 с.
4 Голощапов, В. Н. Характеристики надбандажных уплотнений со встречными гребнями ступеней цилиндра высокогоисреднего давлений паровых турбин [Электронный ресурс] / В. Н. Голощапов, С. В. Алёхина,О.В.Котульская,Т.Н.Парамонова, В. А. Конев // Материалы ХV междунар. н/т конф.«Соверш.турбоустановокметодамиматем. ифиз.моделирования» 15 сентября 2015. – Змиев : ИПМаш НАНУ, 2015.–5 c. –1электрон. опт. диск (СD-ROM). – Загл.сэтикетки диска.
5 Щегляев, А. В. Паровые турбины / А. В. Щегляев. – Москва : Энергоатомиздат, 1993. – 416 с.

References: V. 
 V. 
 V. 
 V. 
 V. 
 V. 
 V. 
 V. 
 V.