Source: https://www.sustainable.co.za/sma-sunny-boy-2-5tl-2-5kw-inverter.html
Timestamp: 2019-04-20 07:22:35+00:00

Document:
It's so easy to reap the benefits of solar power: The completely redesigned Sunny Boy 2.5 is the perfect inverter for customers who want to take full advantage of their small PV system. Among other features, it enables an increase in consumption of self-generated power, allows versatile uses, and is very easy to integrate into the home network. In addition, its innovative design and new communication concept offer many advantages during installation and commissioning. Thanks to direct communication with the SMA Energy Meter, both limitation to 70 percent, which is required in Germany, and limitation to 0 percent is possible.
The innovative design of the Sunny Boy 2.5 is not only easy to install, but also allows for quick DC and AC connections. For example, because it weighs just 9 kg, it can be suspended from just two screws, with no additional wall mounting bracket. Commissioning is equally easy, because the integrated user interface (Web UI) makes it possible to choose the necessary settings in next to no time – without opening the cover.
• Easy installation thanks to a low weight of just 9 kg and an intelligent connection concept.
• Broad input voltage range of 80 to 600 V.
• Max. DC Power (at cos φ = 1) - 2650 W.
• Max. Input Voltage - 600 V.
• MPP Voltage Range - 260 V to 500 V.
• Rated Input voltage 360 V.
• Min. input voltage / initial input voltage 50 V / 80 V.
• Max. Input current - 10 A.
• Max. Input current per string - 10 A.
• Number of independent MPP inputs / strings per MPP input 1 / 1.
• Rated power (at 230 V, 50 Hz) - 2500 W.
• Max. Apparent AC power - 2500 VA.
• Nominal AC voltage - 220 V / 230 V / 240 V.
• Nominal AC voltage range - 180 V to 280 V.
• AC power frequency/range - 50 Hz, 60 Hz / −5 Hz to +5 Hz.
• Rated power frequency/rated grid voltage - 50 Hz / 230 V.
• Max. Output current - 11 A.
• Power factor at rated power - 1.
• Adjustable displacement power factor - 0.8 overexcited.
• Feed-in phases/connection phases - 1 / 1.
• H x L x D - 460mm x 357mm x 122mm.

References: V.

 V.

 V.

 V.

 V.

 V.

 V.

 V.