Source: https://www.sustainable.co.za/sma-sunny-boy-3-0-inverter.html
Timestamp: 2019-04-20 07:23:10+00:00

Document:
Simple system design with Sunny Design.
Secure plug-and-play installation without opening the inverter.
Compact and lightweight (< 16 kg).
Quick commissioning using a tablet, smartphone or laptop.
Future-proof communication via Ethernet and WLAN.
Choose between local and online monitoring via Sunny Portal and Sunny Places.
Compatible with intelligent energy management and SMA storage solutions.
Max. generator power: 5500 Wp.
Max. input voltage: 600 V.
MPP voltage range: 110 V to 500 V.
Rated input voltage: 365 V.
Min. input voltage / initial input voltage: 100 V / 125 V.
Max. input current input A / input B: 15 A / 15 A.
Max. input current per string input A / input B: 15 A / 15 A.
Number of independent MPP inputs / strings per MPP input: 2 / A:2; B:2.
Rated power (at 230 V, 50 Hz): 3000 W.
Max. apparent power AC: 3000 VA.
Nominal AC voltage / range: 220 V, 230 V, 240 V / 180 V to 280 V.
AC power frequency / range: 50 Hz, 60 Hz / −5 Hz to +5 Hz.
Rated power frequency / rated grid voltage: 50 Hz / 230 V.
Max. output current: 16 A.
Power factor at rated power: 1.
Adjustable displacement power factor: 0.8 overexcited to 0.8 under excited.
Feed-in phases / connection phases: 1 / 1.
Max. efficiency / European Efficiency: 97.0% / 96.4%.
Dimensions (W / H / D): 435 mm x 470 mm x 176 mm.
Operating temperature range: ‒25°C to +60°C.
Noise emission, typical: 25 dB.
Self-consumption (at night): 1.0 W.
Degree of protection (as per IEC 60529): IP65.
Climatic category (as per IEC 60721-3-4): 4K4H.
Max. permissible value for relative humidity (non-condensing): 100%.

References: V.

 V.

 V.

 V.

 V.

 V.