Source: https://www.justice.gov/crt/settlement-agreement-between-united-states-america-and-city-sedona-arizona-under-americans
Timestamp: 2019-04-19 13:00:55+00:00

Document:
The United States Department of Justice (Department) initiated this matter as a compliance review of the City of Sedona, Arizona (City) under title II of the Americans with Disabilities Act of 1990 (ADA), 42 U.S.C. Â§Â§ 12131-12134, and the Department’s implementing regulation, 28 C.F.R. Part 35. Because the City receives financial assistance from the Department of Justice, the review was also conducted under the authority of section 504 of the Rehabilitation Act of 1973, 29 U.S.C. Â§ 794, and the Department’s implementing regulation, 28 C.F.R. Part 42, Subpart G.
• physical changes to buildings (required to have been made by January 26, 1995), in accordance with the Department’s title II regulation, 28 C.F.R. Â§ 35.151, and the ADA Standards for Accessible Design (Standards), 28 C.F.R. pt. 36, App. A, or the Uniform Federal Accessibility Standards (UFAS), 41 C.F.R. Â§ 101-19.6, App. A.
• to provide signage at all inaccessible entrances to each of its facilities, directing users to an accessible entrance or to information about accessible facilities, 28 C.F.R. Â§ 35.163(b).
As part of its compliance review, the Department reviewed the following facilities, which – because construction or alterations commenced after January 26, 1992 – must comply with the ADA’s new construction or alterations requirements: City Hall Complex, Waste Water Treatment Plant, Teen Center, Sunset Park, and the Uptown Parking Lot.
The Department’s program access review covered those of the City’s programs, services, and activities that operate in the following facilities: Parks and Recreation Office and Posse Ground Park.
The Department reviewed the City’s policies and procedures regarding sidewalk maintenance to evaluate whether persons with disabilities have an equal opportunity to utilize this program.
Finally, the Department reviewed the City’s Police Department’s policies and procedures regarding providing effective communication to persons who are deaf or hard-of-hearing.
1. The ADA applies to the City because it is a “public entity” as defined by title II. 42 U.S.C. Â§ 12131(1).
2. The Department is authorized under 28 C.F.R. Part 35, Subpart F, to determine the compliance of the City with title II of the ADA and the Department's title II implementing regulation, to issue findings, and, where appropriate, to negotiate and secure voluntary compliance agreements. Furthermore, the Attorney General is authorized, under 42 U.S.C. Â§ 12133, to bring a civil action enforcing title II of the ADA should the Department fail to secure voluntary compliance pursuant to Subpart F.
3. The Department is authorized under 28 C.F.R. Part 42, Subpart G, to determine the City’s compliance with section 504 of the Rehabilitation Act of 1973, to issue findings, and, where appropriate, to negotiate and secure voluntary compliance agreements. Furthermore, the Attorney General is authorized, under 29 U.S.C. Â§ 794 and 28 C.F.R. Â§Â§ 42.530 and 42.108-110, to suspend or terminate financial assistance to the City provided by the Department of Justice should the Department fail to secure voluntary compliance pursuant to Subpart G or to bring a civil suit to enforce the rights of the United States under applicable federal, state, or local law.
4. The parties to this Agreement are the United States of America and the City of Sedona.
7. The City appointed a new ADA Coordinator after the previous Coordinator retired.
8. Within 3 months of the effective date of this Agreement, the City will adopt the attached Notice (Attachment A); distribute it to all agency heads; publish the Notice in a local newspaper of general circulation serving the City; post the Notice on its Internet Home Page; and post copies in conspicuous locations in its public buildings. It will refresh the posted copies, and update the contact information contained on the Notice, as necessary, for the life of this Agreement. Copies will also be provided to any person upon request.
9. Within 3 months of the effective date of this Agreement, and on yearly anniversaries of this Agreement until it expires, the City will implement and report to the Department its written procedures for providing information for interested persons with disabilities concerning the existence and location of the City’s accessible programs, services, and activities.
10. Within 4 months of the effective date of this Agreement, the City will adopt the attached ADA Grievance Procedure (Attachment B), distribute it to all agency heads, and post copies of it in conspicuous locations in each of its public buildings. It will refresh the posted copies, and update the contact information contained on it, as necessary, for the life of the Agreement. Copies will also be provided to any person upon request.
11. Within 9 months of the effective date of this Agreement, the City will identify sources of qualified sign language and oral interpreters, real-time transcription services, and vendors that can put documents in Braille, and will implement and report to the Department its written procedures, with time frames, for fulfilling requests from the public for sign language or oral interpreters, real-time transcription services, and documents in alternate formats (Braille, large print, cassette tapes, etc.).
12. The City will take steps to ensure that all appropriate employees are trained and practiced in using the Arizona Relay Service to make and receive calls.
13. Within 9 months of the effective date of this Agreement, the City will adapt for its own use and implement the Sedona Police Department Policy Statement on Effective Communication with People Who are Deaf or Hard of Hearing [Attachment C] and distribute to all police department officers the Guide for Law Enforcement Officers When in Contact with People Who are Deaf or Hard of Hearing [Attachment D].
14. Within 9 months of the effective date of this Agreement, the City will contract with one or more local qualified oral/sign language interpreter agencies to ensure that the interpreting services will be available on a priority basis, twenty-four hours per day, seven days a week, to its police department or make other appropriate arrangements (such as contracting directly with or hiring qualified interpreters).
15. Within 9 months of the effective date of this Agreement, the City will ensure that each police station or substation and each jail/detention facility is equipped with a working TTY to enable persons who are deaf, hard of hearing, or who have speech impairments to make outgoing telephone calls. Where inmate telephone calls are time-limited, the City will adopt policies permitting inmates who use TTY’s a longer period of time to make those calls, due to the slower nature of TTY communications compared with voice communications.
• will not discriminate on the basis of disability in its hiring or employment practices.
• will not ask a job applicant about the existence, nature, or severity of a disability. Applicants may be asked about their ability to perform specific job functions. Medical examinations or inquiries may be made, but only after a conditional offer of employment is made and only if required of all applicants for the position.
• will make reasonable accommodations for the known physical or mental limitations of a qualified applicant or employee with a disability upon request unless the accommodation would cause an undue hardship on the operation of the City’s business. If an applicant or an employee requests a reasonable accommodation and the individual’s disability and need for the accommodation are not readily apparent or otherwise known, the City may ask the individual for information necessary to determine if the individual has a disability-related need for the accommodation.
• will maintain any employee’s medical records separate from personnel files and keep them confidential.
• will make an individualized assessment of whether a qualified individual with a disability meets selection criteria for employment decisions. To the extent the City’s selection criteria have the effect of disqualifying an individual because of disability, those criteria will be job-related and consistent with business necessity.
17. Within 9 months of the effective date of this Agreement, the City will implement and report to the Department its written process for soliciting and receiving input from persons with disabilities regarding the accessibility of its sidewalks, including, for example, requests to add curb cuts at particular locations. For the purposes of this Agreement, natural trails are not considered sidewalks.
18. Within 12 months of the effective date of this Agreement, the City will identify and report to the Department all streets, roads, and highways that have been constructed or altered since January 26, 1992. Paving, repaving, or resurfacing a street, road, or highway is considered an alteration for the purposes of this Agreement. Filling a pothole is not considered an alteration for the purposes of this Agreement. Within three years of the effective date of this Agreement, the City will provide curb ramps or other sloped areas complying with the Standards or UFAS at all intersections of the streets, roads, and highways identified under this paragraph having curbs or other barriers to entry from a street level pedestrian walkway.
19. Beginning no later than three months after the effective date of this Agreement, the City will provide curb ramps or other sloped areas complying with the Standards or UFAS at any intersection having curbs or other barriers to entry from a street level pedestrian walkway, whenever a new street, road, or highway is constructed or altered.
20. Within 12 months of the effective date of this Agreement, the City will identify all street level pedestrian walkways that have been constructed or altered since January 26, 1992. Paving, repaving, or resurfacing a walkway is considered an alteration for the purposes of this Agreement. Within three years of the effective date of this Agreement, the City will provide curb ramps or other sloped areas complying with the Standards or UFAS at all places where a street level pedestrian walkway identified under this paragraph intersects with a street, road, or highway.
21. Beginning no later than three months after the effective date of this Agreement, the City will provide curb ramps or other sloped areas complying with the Standards or UFAS at all newly constructed or altered pedestrian walkways where they intersect a street, road, or highway.
22. Within 3 months of the effective date of this Agreement, and on subsequent anniversaries of the effective date of this Agreement, the City will distribute to all persons – employees and contractors – who design, develop, maintain, or otherwise have responsibility for content and format of its website(s) or third party websites used by the City (Internet Personnel) the technical assistance document, “Accessibility of State and Local Government Websites to People with Disabilities,” which is Attachment E to this Agreement (it is also available at www.ada.gov/websites2.htm).
24. The elements or features of the City’s facilities that do not comply with the Standards, including those listed in Attachments F and G, prevent persons with disabilities from fully and equally enjoying the City’s services, programs, or activities and constitute discrimination on the basis of disability within the meaning of 42 U.S.C. Â§ 12132 and 28 C.F.R. Â§Â§ 35.149 and 35.150.
25. The City will comply with the cited provisions of the Standards when taking the actions required by this Agreement.
26. Within 9 months of the effective date of this Agreement, the City will install signage as necessary to comply with 28 C.F.R. Â§ 35.163(b), after having surveyed all facilities that are the subject of this Agreement for the purpose of identifying those that have multiple entrances not all of which are accessible.
27. Newly Constructed Facilities: In order to ensure that the spaces and elements in City facilities for which construction was commenced after January 26, 1992, are readily accessible to and usable by persons with disabilities, the City will take the actions listed in Attachment F.
28. Program Access in City Existing Facilities: In order to ensure that each of the City’s programs, services, and activities operating at a facility that is the subject of this Agreement, when viewed in its entirety, is readily accessible to and usable by persons with mobility impairments, the City will take the actions listed in Attachment G.
29. Except as otherwise specified in this Agreement, at yearly anniversaries of the effective date of this Agreement until it expires, the City will submit written reports to the Department summarizing the actions the City has taken pursuant to this Agreement. Reports will include detailed photographs showing measurements, architectural plans, work orders, notices published in the newspaper, copies of adopted policies, and proof of efforts to secure funding/assistance for structural renovations or equipment.
30. Throughout the life of this Agreement, consistent with 28 C.F.R. Â§ 35.133(a), the City will maintain the accessibility of its programs, activities, services, facilities, and equipment, and will take whatever actions are necessary (such as routine testing of accessibility equipment and routine accessibility audits of its programs and facilities) to do so. This provision does not prohibit isolated or temporary interruptions in service or access due to maintenance or repairs. 28 C.F.R. Â§ 35.133(b).
31. Within 9 months of the effective date of this Agreement, the City will develop or procure a two-hour training program on the requirements of the ADA and appropriate ways of serving persons with disabilities. The City will use the ADA technical assistance materials developed by the Department and will consult with interested persons, including individuals with disabilities, in developing or procuring the ADA training program.
32. Within 12 months of the effective date of this Agreement, the City will deliver its training program to all City employees who have direct contact with members of the public. At the end of that period, the City will submit a copy of its training curriculum and materials to the Department, along with a list of employees trained and the name, title, and address of the trainer.
33. If at any time the City desires to modify any portion of this Agreement because of changed conditions making performance impossible or impractical or for any other reason, it will promptly notify the Department in writing, setting forth the facts and circumstances thought to justify modification and the substance of the proposed modification. Until there is written Agreement by the Department to the proposed modification, the proposed modification will not take effect. These actions must receive the prior written approval of the Department, which approval will not be unreasonably withheld or delayed.
34. The Department may review compliance with this Agreement at any time. If the Department believes that the City has failed to comply in a timely manner with any requirement of this Agreement without obtaining sufficient advance written agreement with the Department for a modification of the relevant terms, the Department will so notify the City in writing and it will attempt to resolve the issue or issues in good faith. If the Department is unable to reach a satisfactory resolution of the issue or issues raised within 30 days of the date it provides notice to the City, it may institute a civil action in federal district court to enforce the terms of this Agreement, or it may initiate appropriate steps to enforce title II and section 504 of the Rehabilitation Act.
35. For purposes of the immediately preceding paragraph, it is a violation of this Agreement for the City to fail to comply in a timely manner with any of its requirements without obtaining sufficient advance written agreement with the Department for an extension of the relevant time frame imposed by the Agreement.
36. Failure by the Department to enforce this entire Agreement or any provision thereof with regard to any deadline or any other provision herein will not be construed as a waiver of the Department's right to enforce other deadlines and provisions of this Agreement.
37. This Agreement is a public document. A copy of this document or any information contained in it will be made available to any person by the City or the Department on request.
38. This Agreement constitutes the entire agreement between the parties on the matters raised herein, and no other statement, promise, or agreement, either written or oral, made by either party or agents of either party, that is not contained in this written Agreement (including its Attachments, which are hereby incorporated by reference), will be enforceable. This Agreement does not purport to remedy any other potential violations of the ADA or any other federal law. This Agreement does not affect the City’s continuing responsibility to comply with all aspects of the ADA and section 504 of the Rehabilitation Act.
39. This Agreement will remain in effect for three years or until full compliance with this Agreement is met, whichever is earlier.
40. The person signing for the City represents that he or she is authorized to bind the City to this Agreement.
In accordance with the requirements of title II of the Americans with Disabilities Act of 1990, the City will not discriminate against qualified individuals with disabilities on the basis of disability in the City’s services, programs, or activities.
Anyone who requires an auxiliary aid or service for effective communication, or a modification of policies or procedures to participate in a City program, service, or activity, should contact the Office of the City Manager, 102 Roadrunner Drive, Sedona, AZ 86336, as soon as possible but no later than 48 hours before the scheduled event.
Complaints that a City program, service, or activity is not accessible to persons with disabilities should be directed to the Office of the City Manager, 102 Roadrunner Drive, Sedona, AZ 86336.
Within 15 calendar days after receipt of the complaint, (name) or his/her designee will meet with the complainant to discuss the complaint and the possible resolutions. Within 15 calendar days of the meeting, (name) or his/her designee will respond in writing, and where appropriate, in format accessible to the complainant, such as large print, Braille, or audio tape. The response will explain the position of the City and offer options for substantive resolution of the complaint.
If the response does not satisfactorily resolve the issue, the complainant and/or his/her designee may appeal the decision within 15 calendar days after receipt of the response to the City Manager or his/her designee.
Within 15 calendar days after receipt of the appeal, the City Manager or his designee will meet with the complainant to discuss the complaint and possible resolutions. Within 15 calendar days after the meeting, the City Manager or his/her designee will respond in writing, and, where appropriate, in a format accessible to the complainant, with a final resolution of the complaint.
All written complaints received by (name) or his/her designee, appeals to the City Manager or his/her designee, and responses from these two offices will be retained by the City for at least three years.
● People who identify themselves as deaf or hard of hearing are entitled to a level of service equivalent to that provided hearing persons.
● The Agency will make every effort to ensure that its officers and employees communicate effectively with people who have identified themselves as deaf or hard of hearing.
● Effective communication with a person who is deaf or hard of hearing involved in an incident -- whether as a victim, witness, suspect, or arrestee -- is essential in ascertaining what actually occurred, the urgency of the matter, and type of situation.
● Various types of communication aids – known as “auxiliary aids and services” – are used to communicate with people who are deaf or hard of hearing. These include use of gestures or visual aids to supplement oral communication; an exchange of written notes; use of a computer or typewriter; use of assistive listening devices (to amplify sound for persons who are hard of hearing); or use of qualified oral or sign language interpreters.
● The type of aid that will be required for effective communication will depend on the individual’s usual method of communication, and the nature, importance, and duration of the communication at issue.
● To serve each individual effectively, primary consideration should be given to the communication aid or service that works best for that person. Officers must ask persons who are deaf or hard of hearing what type of auxiliary aid or service they need. Officers must defer to those expressed choices, unless there is another equally effective way of communicating, given the circumstances, length, complexity, and importance of the communication, as well as the communication skills of the person who is deaf or hard of hearing.
● The input of people who are deaf or hard of hearing who are involved in incidents is just as important to the law enforcement process as the input of others. Officers must not draw conclusions about incidents unless they fully understand -- and are understood by -- all those involved, including persons who are deaf or hard of hearing.
● People who are deaf or hard of hearing must never be charged for the cost of an auxiliary aid or service needed for effective communication.
● The Agency will maintain a list of sign language and oral interpreting services that are available (on-call 24 hours per day) and willing to provide qualified interpreters as needed. Each of these services will be chosen after having been screened for the quality and skill of its interpreters, its reliability, and other factors such as cost. The Agency will update this list annually.
● In situations when a nondisabled person would have access to a telephone, officers must provide persons who are deaf or hard of hearing the opportunity to place calls using a text telephone (TTY, also known as a telecommunications device for deaf people, or TDD). Officers must also accept telephone calls placed by persons who are deaf or hard of hearing through the Telecommunications Relay Service.
1. Within 12 months of the effective date of this agreement, except where otherwise noted, the City will complete the following modifications to the City Hall Complex.
i. The parking reserved for persons with disabilities behind the City Hall Building is inaccessible because the van access aisle is only 92 inches wide. Provide designated van accessible parking space that is a minimum of 96 inches wide and served by an access aisle at least 96 inches wide. Standards §§ 4.1.2(5)(b), 4.6.3, Fig.9.
(1) The City Manager/Human Resources/Arts and Culture Counter in the Administration Building is inaccessible because it is 30 inches wide. Provide a counter on an accessible route such that a portion of the counter is at least 36 inches wide and no more than 36 inches above the finished floor, or provide an auxiliary counter with a maximum height of 36 inches in close proximity to the main counter, or provide equivalent facilitation. Equivalent facilitation may be provided in the form of a folding shelf attached to the main counter, an auxiliary table nearby, a clip board made available to the public, or other means. Standards §§ 4.1.1(2), 7.2(2), 4.1.3(1), 4.3.
(2) The Finance and Waste Water Counter in the Administration Building is inaccessible because it is 30 inches wide. Provide a counter on an accessible route such that a portion of the counter is at least 36 inches wide and no more than 36 inches above the finished floor, or provide an auxiliary counter with a maximum height of 36 inches in close proximity to the main counter, or provide equivalent facilitation. Equivalent facilitation may be provided in the form of a folding shelf attached to the main counter, an auxiliary table nearby, a clip board made available to the public, or other means. Standards §§ 4.1.1(2), 7.2(2), 4.1.3(1), 4.3.
(1) The toilet room sign is mounted too high at 62 inches above the finished floor. Provide a toilet room sign with raised and Braille characters. The sign shall be mounted on the wall adjacent to the latch side of the door with the centerline of the sign at 60 inches above the finished floor and situated such that a person can approach within 3 inches of the sign without encountering an obstruction or standing within a door swing. Standards §§ 4.1.2(7)(d), 4.30.1, 4.30.4, 4.30.5, 4.30.6.
(2) The door to the toilet room, which is accessed through a front approach, is inaccessible because it has only 9 inches of latch side maneuvering clearance on the pull side of the door because of the trash can. On the pull side of the door, provide maneuvering clearance at least 60 inches deep and provide a minimum of 18 inches (24 inches is preferred) of maneuvering clearance on the latch side of the door. Standards §§ 4.1.3(7)(b), 4.13.6, Fig. 25(a).
(3) The mirror is inaccessible. Provide a mirror with the bottom edge of its reflecting surface no more than 40 inches above the finished floor. Standards §§ 4.1.3(11), 4.22.6, 4.19.6.
(4) The toilet seat cover dispenser is inaccessible because the it is mounted at 54 inches above the finished floor over the toilet, where a side approach is not available. Provide a toilet seat cover dispenser such that the controls comply with Fig. 5 for a forward reach or with Fig. 6 for a side reach and such that it is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach, respectively, by a person using a wheelchair. Standards §§ 4.1.3(13), 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
(5) The toilet is inaccessible because its centerline measures 16½ inches from the side wall. Within 18 months of the effective date of this agreement, provide a toilet with a centerline that measures 18 inches from the near side wall. Standards §§ 4.1.3(11), 4.22.4, 4.16.2, Fig. 28.
(6) The toilet is inaccessible because the flush control is on the closed side. Within 18 months of the effective date of this agreement, provide a flush control mounted on the “open” side of the toilet’s clear floor space; 44 inches or less above the finished floor; and requiring a maximum of 5 pounds of force to operate; or provide an automatic flush device. Standards §§ 4.1.3(11), 4.22.4, 4.16.5, 4.27.4.
i. The free standing drinking fountain in the reception area is inaccessible because the door into the employee area swings into the clear floor space of the drinking fountain. Provide a drinking fountain with a clear floor space of at least 30 inches by 48 inches that allows a person in a wheelchair to make a parallel approach to the unit. Standards §§ 4.1.3(10), 4.15.5(2), 4.2.4, Figs. 27(c), (d).
ii. Although an accessible drinking fountain is provided for persons who use wheelchairs, there is no drinking fountain provided for people who have difficulty bending or stooping. For each accessible drinking fountain, provide a drinking fountain that is accessible to people who have difficulty bending or stooping. This can be accommodated by the use of a “hi-lo” fountain; by providing one fountain accessible to those who use wheelchairs and one fountain at a standard height convenient for those who have difficulty bending; by providing a fountain accessible to people who use wheelchairs and a cup dispenser, or by such other means as would achieve the required accessibility for each group of people. Standards § 4.1.3(10)(a).
iii. Because the single user Employee toilet room cannot be made accessible, the City will close this toilet room and convert it for a different use.
(1) The toilet room sign is mounted on the hinge side of the door. Provide a toilet room sign with raised and Braille characters. The sign shall be mounted on the wall adjacent to the latch side of the door with the centerline of the sign at 60 inches above the finished floor and situated such that a person can approach within 3 inches of the sign without encountering an obstruction or standing within a door swing. Standards §§ 4.1.2(7)(d), 4.30.1, 4.30.4, 4.30.5, 4.30.6.
(2) The toilet room is inaccessible because the pressure required to open the door is 10 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards §§ 4.1.3(7)(b), 4.13.11(2)(b).
(3) The toilet room door swings into the required clear floor space at the lavatory. Ensure that no door swings into the required clear floor space at any accessible fixture. Standards §§ 4.1.3(11), 4.22.2.
(4) The mirror is inaccessible. Provide a mirror with the bottom edge of its reflecting surface no more than 40 inches above the finished floor. Standards §§ 4.1.3(11), 4.22.6, 4.19.6.
(5) The paper towel dispenser is inaccessible because the controls are mounted at 53 inches above the finished floor. Provide a paper towel dispenser such that the controls comply with Fig. 5 for a forward reach or with Fig. 6 for a side reach and such that it is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach, respectively, by a person using a wheelchair. Standards §§ 4.1.3(13), 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
(6) The urinal is inaccessible because the flush control is mounted 45 inches above the finished floor. Within 18 months of the effective date of this agreement, provide a urinal with an elongated rim mounted 17 inches or less above the finished floor, a clear floor space of at least 30 inches wide and 48 inches deep centered on the urinal, and a flush control height of 44 inches or less above the finished floor. Standards §§ 4.1.3(11), 4.22.5, 4.18.2, 4.18.3, 4.18.4.
(7) The toilet is inaccessible because its centerline measures 16 inches from the side wall. Within 18 months of the effective date of this agreement, provide a toilet with a centerline that measures 18 inches from the near side wall. Standards §§ 4.1.3(11), 4.22.4, 4.17.3, Fig. 30.
(8) The coat hook is inaccessible. Provide a coat hook at a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.1.3(12)(a), 4.25.2, 4.25.3, 4.2.4, 4.2.5, 4.2.6.
(9) The toilet paper dispenser is inaccessible because it is mounted 39 inches from the rear wall and not within the reach range of many people with disabilities. Provide a toilet paper dispenser that is mounted with its top at least 1½ inches under the side grab bar and 36 inches or less from the rear wall and is centered at least 19 inches above the finished floor. Standards §§ 4.1.3(11), 4.22.4, 4.17.3, Fig. 30(d).
(1) The toilet room door is inaccessible because the pressure required to open the door is 12 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards §§ 4.1.3(7)(b), 4.13.11(2)(b).
(2) The toilet room door swings into the required clear floor space at the lavatory and soap dispenser. Ensure that no door swings into the required clear floor space at any accessible fixture. Standards §§ 4.1.3(11), 4.22.2.
(3) The accessible stall door swings into the required clear floor space at the lavatory. Ensure that no door swings into the required clear floor space at any accessible fixture. Standards §§ 4.1.3(11), 4.22.2.
(5) The toilet is inaccessible because its centerline measures 16 inches from the side wall. Within 18 months of the effective date of this agreement, provide a toilet with a centerline that measures 18 inches from the near side wall. Standards §§ 4.1.3(11), 4.22.4, 4.17.3, Fig. 30.
(6) The toilet is inaccessible because the flush control is on the closed side of the stall. Within 18 months of the effective date of this agreement, provide a flush control mounted on the “open” side of the toilet’s clear floor space; 44 inches or less above the finished floor; and requiring a maximum of 5 pounds of force to operate; or provide an automatic flush device. Standards §§ 4.1.3(11), 4.22.4, 4.16.5, 4.17.2, 4.27.4.
(7) The coat hook is inaccessible. Provide a coat hook at a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.1.3(12)(a), 4.25.2, 4.25.3, 4.2.4, 4.2.5, 4.2.6.
(1) The toilet room door is inaccessible because the pressure required to open the door is 7 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards §§ 4.1.3(7)(b), 4.13.11(2)(b).
(2) The mirror is inaccessible. Provide a mirror with the bottom edge of its reflecting surface no more than 40 inches above the finished floor. Standards §§ 4.1.3(11), 4.22.6, 4.19.6.
(3) The lavatory is inaccessible because the trash can is in the clear floor space of the lavatory. Provide a lavatory with clear floor space at least 30 inches wide and 48 inches deep centered on the lavatory. Standards §§ 4.1.3(11), 4.22.6, 4.19.3, Fig. 32.
(4) The urinal is inaccessible because the flush control is mounted outside the reach range of many people with disabilities at 45 inches above the finished floor. Within 18 months of the effective date of this agreement, provide a urinal with an elongated rim mounted 17 inches or less above the finished floor, a clear floor space of at least 30 inches wide and 48 inches deep centered on the urinal, and a flush control height of 44 inches or less above the finished floor. Standards §§ 4.1.3(11), 4.22.5, 4.18.2, 4.18.3, 4.18.4.
(1) The first and second door into the women’s toilet room are inaccessible because the pressure required to open the first door is 7 pounds and 8 pounds to open the second. Provide doors that require no more than 5 pounds of force to open. Standards §§ 4.1.3(7)(b), 4.13.11(2)(b).
(3) The paper towel dispenser is inaccessible because the controls are mounted at 54 inches above the finished floor over an obstruction. Provide a paper towel dispenser such that the controls comply with Fig. 5 for a forward reach or with Fig. 6 for a side reach and such that it is accompanied by clear floor space of 30 by 48 inches that allows an unobstructed forward or parallel approach, respectively, by a person using a wheelchair. Standards §§ 4.1.3(13), 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
(4) The toilet is inaccessible because the flush control is on the closed side of the stall. Within 18 months of the effective date of this agreement, provide a flush control mounted on the “open” side of the toilet’s clear floor space; 44 inches or less above the finished floor; and requiring a maximum of 5 pounds of force to operate; or provide an automatic flush device. Standards §§ 4.1.3(11), 4.22.4, 4.16.5, 4.17.2, 4.27.4.
(5) The coat hook is inaccessible. Provide a coat hook at a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.1.3(12)(a), 4.25.2, 4.25.3, 4.2.4, 4.2.5, 4.2.6.
(1) The courtroom/City Council Chambers is inaccessible to people with hearing impairments because it only has one headset for the infrared system installed in the room. Provide a permanently installed assistive listening system (ALS) or a portable ALS with an adequate number of electrical outlets or other supplementary wiring necessary to support a portable assistive listening system. Also provide at least 3 receivers for use by the general public and signage indicating their availability. Standards §§ 4.1.3(19)(b), 4.30, 4.33.
(1) There is inadequate latch side maneuvering space on the pull side of the door because this space is obstructed by the water cooler. On the pull side of the door, provide an unobstructed path of travel at least 48 inches wide for a side approach and at least 24 inches of clear maneuvering space adjacent to the latch side of the door. Standards §§ 4.1.3(7)(b), 4.13.6, Fig. 25(c).
(3) The paper towel dispenser is inaccessible because it is mounted at 53 inches above the finished floor over the sink. Provide a paper towel dispenser such that it complies with Fig. 5 for a forward reach or with Fig. 6 for a side reach and such that it is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach, respectively, by a person using a wheelchair. Standards §§ 4.1.3(13), 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
(4) The lavatory is inaccessible because the water purification system and trash can encroach upon the clear floor space under the lavatory. Provide a lavatory with clear floor space at least 30 inches wide and 48 inches deep centered on the lavatory. Standards §§ 4.1.3(11), 4.22.6, 4.19.3, Fig. 32.
(5) The rear grab bar at the toilet is inaccessible because it has an overall length of only 24 inches. Provide a rear grab bar that is at least 36 inches in overall length with the closer end no more than 6 inches from the side wall. Standards §§ 4.1.3(11), 4.22.4, 4.16.4, Fig. 29.
(1) The door to the employee toilet room, which is accessed through a front approach, is inaccessible because it has only 3 inches of maneuvering clearance on the latch side of the door. On the pull side of the door, provide maneuvering clearance at least 60 inches deep and provide a minimum of 18 inches (24 inches is preferred) of maneuvering clearance on the latch side of the door. Standards §§ 4.1.3(7)(b), 4.13.6, Fig. 25(a).
(3) The rear grab bar at the toilet is inaccessible because it has an overall length of only 24 inches. Provide a rear grab bar that is at least 36 inches in overall length with the closer end no more than 6 inches from the side wall. Standards §§ 4.1.3(11), 4.22.4, 4.16.4, Fig. 29.
(1) The toilet room sign is mounted 58 inches above the finished floor. Provide a toilet room sign with raised and Braille characters. The sign shall be mounted on the wall adjacent to the latch side of the door with the centerline of the sign at 60 inches above the finished floor and situated such that a person can approach within 3 inches of the sign without encountering an obstruction or standing within a door swing. Standards §§ 4.1.2(7)(d), 4.30.1, 4.30.4, 4.30.5, 4.30.6.
(3) The toilet seat cover dispenser is inaccessible because it is mounted at 56 inches above the finished floor over the toilet. Provide a toilet seat cover dispenser with the controls a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.1.3(13), 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
(4) The toilet is inaccessible because the flush control is on the closed side of the stall. Provide a flush control mounted on the “open” side of the toilet’s clear floor space; 44 inches or less above the finished floor; and requiring a maximum of 5 pounds of force to operate; or provide an automatic flush device. Standards §§ 4.1.3(11), 4.22.4, 4.16.5, 4.27.4.
i. There is no accessible holding cell. Provide an accessible holding cell on the main level of the Police Department. Standards §§ 4.1.3(1), 4.2, 4.3, 4.13, 4.16, 4.19.
ii. Although an accessible drinking fountain is provided, there is no drinking fountain provided for people who have difficulty bending or stooping. For each accessible drinking fountain, provide a drinking fountain that is accessible to people who have difficulty bending or stooping. This can be accommodated by the use of a “hi-lo” fountain; by providing one fountain accessible to those who use wheelchairs and one fountain at a standard height convenient for those who have difficulty bending; by providing a fountain accessible to people who use wheelchairs and a cup dispenser, or by such other means as would achieve the required accessibility for each group of people. Standards § 4.1.3(10)(a).
(1) The door to the public toilet room, which is accessed through a front approach, is inaccessible because it has only three inches of maneuvering clearance on the latch side of the door. On the pull side of the door, provide maneuvering clearance at least 60 inches deep and provide a minimum of 18 inches (24 inches is preferred) of maneuvering clearance on the latch side of the door. Standards §§ 4.1.3(7)(b), 4.13.6, Fig. 25(a).
(3) The toilet seat cover dispenser is inaccessible because it is mounted at 57 inches above the finished floor over the side grab bar. Provide a toilet seat cover dispenser that is a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.1.3(13), 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
(4) The toilet paper dispenser is inaccessible because it is mounted 38 inches from the rear wall. Provide a toilet paper dispenser that is mounted within reach, with its top at least 1½ inches under the side grab bar, and centered at least 19 inches above the finished floor. Standards §§ 4.1.3(11), 4.22.4, 4.16.6, Fig. 29(b).
(1) The two doors into the women’s employee locker room are inaccessible because the pressure required to open the first door is 8 pounds and 10 pounds on the second door. Provide doors that require no more than 5 pounds of force to open. Standards §§ 4.1.3(7)(b), 4.13.11(2)(b).
(3) The soap dispenser is inaccessible because the controls are mounted at 49½ inches above the finished floor over the lavatory. Provide a soap dispenser such that the controls comply with Fig. 5 for a forward reach or with Fig. 6 for a side reach and such that it is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach, respectively, by a person using a wheelchair. Standards §§ 4.1.3(13), 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
(4) The paper towel dispenser is inaccessible because it is mounted at 53½ inches above the finished floor over the lavatory. Provide a paper towel dispenser such that the controls comply with Fig. 5 for a forward reach or with Fig. 6 for a side reach and such that it is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach, respectively, by a person using a wheelchair. Standards §§ 4.1.3(13), 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
(5) The toilet is inaccessible because the flush control is on the closed side of the stall. Provide a flush control mounted on the “open” side of the toilet’s clear floor space; 44 inches or less above the finished floor; and requiring a maximum of 5 pounds of force to operate; or provide an automatic flush device. Standards §§ 4.1.3(11), 4.22.4, 4.16.5, 4.17.2, 4.27.4.
(6) The coat hook is inaccessible. Provide a coat hook at a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.1.3(12)(a), 4.25.2, 4.25.3, 4.2.4, 4.2.5, 4.2.6.
(7) The shower in the women’s employee locker room is inaccessible because there is a 2 inch curb into the shower and the grab bar is not continuous. Provide a shower in this room that is exactly 36 inches wide and 36 inches deep with a 48 inch long and 36 inch wide clear floor space alongside the shower opening, and an L-shaped shower seat mounted on the wall opposite the controls and extending the full depth of the stall; OR a shower that is at least 30 inches deep and 60 inches wide with no curb or threshold and with a 36 inch deep and 60 inch wide clear floor space at the shower opening. Ensure that the shower has grab bars, controls, a shower spray unit, and a seat, curb, and enclosure, if provided, that comply fully with the Standards and with Figs. 35, 36, and 37, as applicable. Standards §§ 4.1.3(11), 4.21, Figs. 35, 36, 37.
(8) Although the facility contains an emergency alarm system, the alarm system is inaccessible because there are no visual alarms in the locker room to alert the hearing impaired to emergencies. Provide visual alarm devices in toilet rooms and any other general usage areas (e.g., meeting rooms), hallways, lobbies, and any other area for common use. Such devices shall be integrated into the facility alarm system and shall meet the requirements of the Standards for lamp type, color, pulse duration, intensity, and flash rate. Visual alarm appliances shall be placed 80 inches above the highest floor level within the space or 6 inches below the ceiling, whichever is lower. Visual alarm appliances shall be located such that no place in any room or space, including common corridors or hallways, required to have a visual alarm appliance shall be more than 50 feet from the signal. In large rooms and spaces exceeding 100 feet across, without obstructions 6 feet above the finished floor, devices may be placed around the perimeter, spaced a maximum of 100 feet apart, in lieu of suspending appliances from the ceiling. Standards §§ 4.1.3(14), 4.28.3.
(1) The soap dispenser is inaccessible because the controls are mounted at 50 inches above the finished floor over the lavatory. Provide a soap dispenser such that the controls comply with Fig. 5 for a forward reach or with Fig. 6 for a side reach and such that it is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach, respectively, by a person using a wheelchair. Standards §§ 4.1.3(13), 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
(3) The urinal is inaccessible because the rim is mounted 19 inches above the finished floor and the flush control is mounted 46 inches above the finished floor. Within 18 months of the effective date of this agreement, provide a urinal with an elongated rim mounted 17 inches or less above the finished floor, a clear floor space of at least 30 inches wide and 48 inches deep centered on the urinal, and a flush control height of 44 inches or less above the finished floor. Standards §§ 4.1.3(11), 4.22.5, 4.18.2, 4.18.3, 4.18.4.
(6) The shower in the men’s employee locker room is inaccessible because there is a 2 inch curb into the shower and the grab bar is not continuous. Provide a shower in this room that is exactly 36 inches wide and 36 inches deep with a 48 inch long and 36 inch wide clear floor space alongside the shower opening, and an L-shaped shower seat mounted on the wall opposite the controls and extending the full depth of the stall; OR a shower that is at least 30 inches deep and 60 inches wide with no curb or threshold and with a 36 inch deep and 60 inch wide clear floor space at the shower opening. Ensure that the shower has grab bars, controls, a shower spray unit, and a seat, curb, and enclosure, if provided, that comply fully with the Standards and with Figs. 35, 36, and 37, as applicable. Standards §§ 4.1.3(11), 4.21, Figs. 35, 36, 37.
(7) Although the facility contains an emergency alarm system, the alarm system is inaccessible because there are no visual alarms in the locker room to alert the hearing impaired to emergencies. Provide visual alarm devices in toilet rooms and any other general usage areas (e.g., meeting rooms), hallways, lobbies, and any other area for common use. Such devices shall be integrated into the facility alarm system and shall meet the requirements of the Standards for lamp type, color, pulse duration, intensity, and flash rate. Visual alarm appliances shall be placed 80 inches above the highest floor level within the space or 6 inches below the ceiling, whichever is lower. Visual alarm appliances shall be located such that no place in any room or space, including common corridors or hallways, required to have a visual alarm appliance shall be more than 50 feet from the signal. In large rooms and spaces exceeding 100 feet across, without obstructions 6 feet above the finished floor, devices may be placed around the perimeter, spaced a maximum of 100 feet apart, in lieu of suspending appliances from the ceiling. Standards §§ 4.1.3(14), 4.28.3.
(a) The toilet room sign is inaccessible to persons who are blind because it is mounted on the door and has no raised characters or Braille. Provide a toilet room sign with raised and Braille characters. The sign shall be mounted on the wall adjacent to the latch side of the door with the centerline of the sign at 60 inches above the finished floor and situated such that a person can approach within 3 inches of the sign without encountering an obstruction or standing within a door swing. Standards §§ 4.1.2(7)(d), 4.30.1, 4.30.4, 4.30.5, 4.30.6.
(b) The toilet is inaccessible because its centerline measures 19 inches from the side wall. Within 18 months of the effective date of this agreement, provide a toilet with a centerline that measures 18 inches from the near side wall. Standards §§ 4.1.3(11), 4.22.4, 4.16.2, Fig. 28.
(c) The mirror is inaccessible. Provide a mirror with the bottom edge of its reflecting surface no more than 40 inches above the finished floor. Standards §§ 4.1.3(11), 4.22.6, 4.19.6.
(d) The lavatory is inaccessible because the hot water pipes are not insulated or otherwise configured to protect against contact. Provide hot water and drain pipes that are insulated or otherwise configured to protect against contact. Standards §§ 4.1.3(11), 4.22.6, 4.19.4.
(a) The mirror is inaccessible. Provide a mirror with the bottom edge of its reflecting surface no more than 40 inches above the finished floor. Standards §§ 4.1.3(11), 4.22.6, 4.19.6.
(b) The toilet is inaccessible because the top of the seat is 15½ inches above the finished floor. Provide a toilet with a seat that measures 17 to 19 inches above the finished floor. Standards §§ 4.1.3(11), 4.22.4, 4.16.3, Fig. 29(b).
(c) The toilet is inaccessible because its centerline measures 19 inches from the side wall. Within 18 months of the effective date of this agreement, provide a toilet with a centerline that measures 18 inches from the near side wall. Standards §§ 4.1.3(11), 4.22.4, 4.16.2, Fig. 28.
(d) The toilet paper dispenser is inaccessible because it is mounted 38 inches from the rear wall. Provide a toilet paper dispenser that is mounted within reach, with its top at least 1½ inches under the side grab bar, and centered at least 19 inches above the finished floor. Standards §§ 4.1.3(11), 4.22.4, 4.16.6, Fig. 29(b).
i. The toilet room sign is inaccessible to blind people because mounted on the wrong side of the door. Provide a toilet room sign with raised and Braille characters. The sign shall be mounted on the wall adjacent to the latch side of the door with the centerline of the sign at 60 inches above the finished floor and situated such that a person can approach within 3 inches of the sign without encountering an obstruction or standing within a door swing. Standards §§ 4.1.2(7)(d), 4.30.1, 4.30.4, 4.30.5, 4.30.6.
ii. The toilet seat cover dispenser is inaccessible because it is mounted at 53 inches above the finished floor over the toilet. Provide a toilet seat cover dispenser that complies with Fig. 5 for a forward reach or with Fig. 6 for a side reach and such that it is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach, respectively, by a person using a wheelchair. Standards §§ 4.1.3(13), 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
iii. The paper towel dispenser is inaccessible because it is mounted at 49 inches above the finished floor with only a forward reach possible. Provide a paper towel dispenser with the controls a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.1.3(13), 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
iv. The toilet room door swings into the required clear floor space at the lavatory. Ensure that no door swings into the required clear floor space at any accessible fixture. Standards §§ 4.1.3(11), 4.22.2.
2. Within 12 months of the effective date of this agreement, except where otherwise noted, the City will complete the following modifications to the Waste Water Treatment Plant.
(1) The toilet room sign is mounted on the door at 68 inches above the finished floor. Provide a toilet room sign with raised and Braille characters. The sign shall be mounted on the wall adjacent to the latch side of the door with the centerline of the sign at 60 inches above the finished floor and situated such that a person can approach within 3 inches of the sign without encountering an obstruction or standing within a door swing. Standards §§ 4.1.2(7)(d), 4.30.1, 4.30.4, 4.30.5, 4.30.6.
(2) The men’s toilet room door is inaccessible because the pressure required to open the door is 11 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards §§ 4.1.3(7)(b), 4.13.11(2)(b).
(3) The coat hook is inaccessible. Provide a coat hook at a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.1.3(12)(a), 4.25.2, 4.25.3, 4.2.4, 4.2.5, 4.2.6.
(2) The women’s toilet room door is inaccessible because the pressure required to open the door is 11 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards §§ 4.1.3(7)(b), 4.13.11(2)(b).
(3) The toilet is inaccessible because its centerline measures 16½ inches from the side wall. Within 18 months of the effective date of this agreement, provide a toilet with a centerline that measures 18 inches from the near side wall. Standards §§ 4.1.3(11), 4.22.4, 4.17.3, Fig. 30.
(6) The shower in the women’s locker room is inaccessible because it is 37 inches deep by 35 inches wide. Within 18 months of the effective date of this agreement, provide a shower in this room that is exactly 36 inches wide and 36 inches deep with a 48 inch long and 36 inch wide clear floor space alongside the shower opening, and an L-shaped shower seat mounted on the wall opposite the controls and extending the full depth of the stall; OR a shower that is at least 30 inches deep and 60 inches wide with no curb or threshold and with a 36 inch deep and 60 inch wide clear floor space at the shower opening. Ensure that the shower has grab bars, controls, a shower spray unit, and a seat, curb, and enclosure, if provided, that comply fully with the Standards and with Figs. 35, 36, and 37, as applicable. Standards §§ 4.1.3(11), 4.21, Figs. 35, 36, 37.
i. The wall-mounted drinking fountain next to the single user toilet room is inaccessible because there is only 25 inches of knee clearance. Provide a drinking fountain with clear knee space between the bottom of the apron and the finished floor or ground of at least 27 inches high, 30 inches wide, and 17 to 19 inches deep; and a minimum clear floor space of 30 inches by 48 inches to allow a person in a wheelchair to approach the unit facing forward. Standards §§ 4.1.3(10), 4.15.5(1), Figs. 27(a), (b).
ii. Although an accessible drinking fountain for persons using wheelchairs has been provided, there is no drinking fountain provided for people who have difficulty bending or stooping. For each accessible drinking fountain, provide a drinking fountain that is accessible to people who have difficulty bending or stooping. This can be accommodated by the use of a “hi-lo” fountain; by providing one fountain accessible to those who use wheelchairs and one fountain at a standard height convenient for those who have difficulty bending; by providing a fountain accessible to people who use wheelchairs and a cup dispenser, or by such other means as would achieve the required accessibility for each group of people. Standards § 4.1.3(10)(a).
(1) The toilet room sign is mounted 53 inches above the finished floor. Provide a toilet room sign with raised and Braille characters. The sign shall be mounted on the wall adjacent to the latch side of the door with the centerline of the sign at 60 inches above the finished floor and situated such that a person can approach within 3 inches of the sign without encountering an obstruction or standing within a door swing. Standards §§ 4.1.2(7)(d), 4.30.1, 4.30.4, 4.30.5, 4.30.6.
(2) The toilet room door is inaccessible because the pressure required to open the door is 6 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards §§ 4.1.3(7)(b), 4.13.11(2)(b).
(3) The lavatory is inaccessible because the hot water pipes are not insulated or otherwise configured to protect against contact. Provide hot water and drain pipes that are insulated or otherwise configured to protect against contact. Standards §§ 4.1.3(11), 4.22.6, 4.19.4.
(4) The toilet is inaccessible because the flush control is on the closed side of the stall. Within 18 months of the effective date of this agreement, provide a flush control mounted on the “open” side of the toilet’s clear floor space; 44 inches or less above the finished floor; and requiring a maximum of 5 pounds of force to operate; or provide an automatic flush device. Standards §§ 4.1.3(11), 4.22.4, 4.16.5, 4.27.4.
(5) The rear grab bar at the toilet is inaccessible because it is only 30 inches long. Provide a rear grab bar that is at least 36 inches in overall length with the closer end no more than 6 inches from the side wall. Standards §§ 4.1.3(11), 4.22.4, 4.16.4, Fig. 29.
(1) The toilet room sign is inaccessible because it is mounted on the door at a height of 63 inches above the finished floor. Provide a toilet room sign with raised and Braille characters. The sign shall be mounted on the wall adjacent to the latch side of the door with the centerline of the sign at 60 inches above the finished floor and situated such that a person can approach within 3 inches of the sign without encountering an obstruction or standing within a door swing. Standards §§ 4.1.2(7)(d), 4.30.1, 4.30.4, 4.30.5, 4.30.6.
(2) The men’s locker room door is inaccessible because the pressure required to open the door is 15 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards §§ 4.1.3(7)(b), 4.13.11(2)(b).
(4) The lavatory is inaccessible because the hot water pipes are not insulated or otherwise configured to protect against contact. Provide hot water and drain pipes that are insulated or otherwise configured to protect against contact. Standards §§ 4.1.3(11), 4.22.6, 4.19.4.
(5) The toilet is inaccessible because its centerline measures 20 inches from the side wall. Within 18 months of the effective date of this agreement, provide a toilet with a centerline that measures 18 inches from the near side wall. Standards §§ 4.1.3(11), 4.22.4, 4.17.3, Fig. 30.
(6) The stall coat hook is inaccessible. Provide a coat hook at a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.1.3(12)(a), 4.25.2, 4.25.3, 4.2.4, 4.2.5, 4.2.6.
(7) The toilet paper dispenser is inaccessible because it is mounted 18 inches above the finished floor. Provide a toilet paper dispenser that is mounted with its top at least 1½ inches under the side grab bar and 36 inches or less from the rear wall and is centered at least 19 inches above the finished floor. Standards §§ 4.1.3(11), 4.22.4, 4.17.3, Fig. 30(d).
(8) The shower in the men’s locker room is inaccessible because it is 38 inches deep by 37 inches wide, it has no shower seat, and the grab bar is inaccessible because it is not continuous and is mounted incorrectly. Within 18 months of the effective date of this agreement, provide a shower in this room that is exactly 36 inches wide and 36 inches deep with a 48 inch long and 36 inch wide clear floor space alongside the shower opening, and an L-shaped shower seat mounted on the wall opposite the controls and extending the full depth of the stall; OR a shower that is at least 30 inches deep and 60 inches wide with no curb or threshold and with a 36 inch deep and 60 inch wide clear floor space at the shower opening. Ensure that the shower has grab bars, controls, a shower spray unit, and a seat, curb, and enclosure, if provided, that comply fully with the Standards and with Figs. 35, 36, and 37, as applicable. Standards §§ 4.1.3(11), 4.21, Figs. 35, 36, 37.
(9) The shower coat hook is inaccessible. Provide a coat hook at a maximum height above the finished floor of 48 inches for a forward approach or 54 inches for a side approach and that is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach by a person using a wheelchair. Standards §§ 4.1.3(12)(a), 4.25.2, 4.25.3, 4.2.4, 4.2.5, 4.2.6.
3. Within 24 months of the effective date of this agreement, the City will complete the following modifications to the Teen Center.
a. Although the parking lot has a total of 27 parking spaces, there are no van accessible spaces and the existing sign is too low and cannot be see over parked vehicles. On the shortest accessible route to the accessible entrance, provide 1 van accessible space and 1 standard accessible space designated as reserved for people with disabilities. Ensure that van accessible spaces are a minimum of 96 inches wide and served by access aisles at least 96 inches wide. At all spaces designated as reserved for persons with disabilities, provide vertical signs with the International Symbol of Accessibility located such that they cannot be obstructed by parked vehicles. At van accessible spaces, provide an additional “Van-Accessible” sign located below the International Symbol of Accessibility. Ensure that all spaces and access aisles for persons with disabilities are flat and level, with slopes and cross-slopes not exceeding 1:50 in all directions, and that their surfaces are firm, stable, and slip-resistant. Standards §§ 4.1.2(5), 4.6, 4.30.7(1).
b. Although an accessible drinking fountain is provided, there is no drinking fountain provided for people who have difficulty bending or stooping. For each accessible drinking fountain, provide a drinking fountain that is accessible to people who have difficulty bending or stooping. This can be accommodated by the use of a “hi-lo” fountain; by providing one fountain accessible to those who use wheelchairs and one fountain at a standard height convenient for those who have difficulty bending; by providing a fountain accessible to people who use wheelchairs and a cup dispenser, or by such other means as would achieve the required accessibility for each group of people. Standards § 4.1.3(10)(a).
i. The toilet room sign is mounted 45 inches above the finished floor. Provide a toilet room sign with raised and Braille characters. The sign shall be mounted on the wall adjacent to the latch side of the door with the centerline of the sign at 60 inches above the finished floor and situated such that a person can approach within 3 inches of the sign without encountering an obstruction or standing within a door swing. Standards §§ 4.1.2(7)(d), 4.30.1, 4.30.4, 4.30.5, 4.30.6.
ii. Although the facility contains an emergency alarm system, the alarm system is inaccessible because there are no visual alarms to alert the hearing impaired to emergencies. Provide visual alarm devices in toilet rooms and any other general usage areas (e.g., meeting rooms), hallways, lobbies, and any other area for common use. Such devices shall be integrated into the facility alarm system and shall meet the requirements of the Standards for lamp type, color, pulse duration, intensity, and flash rate. Visual alarm appliances shall be placed 80 inches above the highest floor level within the space or 6 inches below the ceiling, whichever is lower. Visual alarm appliances shall be located such that no place in any room or space, including common corridors or hallways, required to have a visual alarm appliance shall be more than 50 feet from the signal. In large rooms and spaces exceeding 100 feet across, without obstructions 6 feet above the finished floor, devices may be placed around the perimeter, spaced a maximum of 100 feet apart, in lieu of suspending appliances from the ceiling. Standards §§ 4.1.3(14), 4.28.3.
ii. The toilet room door is inaccessible because the pressure required to open the door is 7 pounds. Provide a door that requires no more than 5 pounds of force to open. Standards §§ 4.1.3(7)(b), 4.13.11(2)(b).
iii. Although the facility contains an emergency alarm system, the alarm system is inaccessible because there are no visual alarms. Provide visual alarm devices in toilet rooms and any other general usage areas (e.g., meeting rooms), hallways, lobbies, and any other area for common use. Such devices shall be integrated into the facility alarm system and shall meet the requirements of the Standards for lamp type, color, pulse duration, intensity, and flash rate. Visual alarm appliances shall be placed 80 inches above the highest floor level within the space or 6 inches below the ceiling, whichever is lower. Visual alarm appliances shall be located such that no place in any room or space, including common corridors or hallways, required to have a visual alarm appliance shall be more than 50 feet from the signal. In large rooms and spaces exceeding 100 feet across, without obstructions 6 feet above the finished floor, devices may be placed around the perimeter, spaced a maximum of 100 feet apart, in lieu of suspending appliances from the ceiling. Standards §§ 4.1.3(14), 4.28.3.
iv. The mirror is inaccessible. Provide a mirror with the bottom edge of its reflecting surface no more than 40 inches above the finished floor. Standards §§ 4.1.3(11), 4.22.6, 4.19.6.
v. The toilet is inaccessible because the flush control is on the closed side. Provide a flush control mounted on the “open” side of the toilet’s clear floor space; 44 inches or less above the finished floor; and requiring a maximum of 5 pounds of force to operate; or provide an automatic flush device. Standards §§ 4.1.3(11), 4.22.4, 4.16.5, 4.17.2, 4.27.4.
4. Within 12 months of the effective date of this agreement, except as otherwise noted, the City will complete the following modifications to the Sunset Park.
a. The van accessible parking reserved for persons with disabilities lacks the appropriate signage. At van accessible spaces, provide a “Van-Accessible” sign located below the International Symbol of Accessibility such that the sign cannot be obstructed by vehicles parked in the space. Standards §§ 4.1.2(5), 4.6.4, 4.30.7(1).
b. There is no accessible route from the parking lot to the playground equipment. Provide at least one accessible route within the boundary of the site connecting these elements that, to the maximum extent feasible, coincides with the route for the general public. The accessible route must have a minimum clear width of 36 inches, or a minimum clear width of 42 inches if there is a turn around an obstruction less than 48 inches wide; have passing spaces at least 60 inches by 60 inches at least every 200 feet; have a minimum clear headroom of 80 inches; have a surface that is firm, stable, and slip resistant; have, in the absence of a curb ramp, ramp, elevator, or platform lift, no level changes in excess of ½ inch vertically; and have a running slope of less than 1:20 (5%) (or have been constructed as a fully accessible ramp) and a cross slope of less than 1:50 (2%). Standards §§ 4.1.3(1), 4.3, 4.5, Fig. 7.
i. The toilet room sign is inaccessible because it is mounted on the door and has no raised letters or Braille. Provide a toilet room sign with raised and Braille characters. The sign shall be mounted on the wall adjacent to the latch side of the door with the centerline of the sign at 60 inches above the finished floor and situated such that a person can approach within 3 inches of the sign without encountering an obstruction or standing within a door swing. Standards §§ 4.1.2(7)(d), 4.30.1, 4.30.4, 4.30.5, 4.30.6.
ii. The urinal is inaccessible because it is mounted so the rim is 18 inches above the finished floor. Within 18 months of the effective date of this agreement, provide a urinal with an elongated rim mounted 17 inches or less above the finished floor, a clear floor space of at least 30 inches wide and 48 inches deep centered on the urinal, and a flush control height of 44 inches or less above the finished floor. Standards §§ 4.1.3(11), 4.22.5, 4.18.2, 4.18.3, 4.18.4.
ii. The toilet seat cover dispenser is inaccessible because it is mounted at 51½ inches above the finished floor over the toilet. Provide a toilet seat cover dispenser that complies with Fig. 5 for a forward reach or with Fig. 6 for a side reach and such that it is accompanied by clear floor space of 30 by 48 inches that allows a forward or parallel approach, respectively, by a person using a wheelchair. Standards §§ 4.1.3(13), 4.27.2, 4.27.3, 4.2.4, 4.2.5, 4.2.6.
5. Within 12 months of the effective date of this agreement, the City will complete the following modifications to the Uptown Parking Lot.
a. Although the parking lot has a total of 156 parking spaces, an inadequate number are designated as reserved for people with disabilities. On the shortest accessible route to the accessible entrance, provide 1 additional accessible space designated as reserved for people with disabilities. Standards §§ 4.1.2(5), 4.6, 4.30.7(1), A4.6.3, Fig. A5.
Please Note: Paragraph 26 of the Agreement requires that within 9 months of the effective date of this Agreement, the City will provide signage as necessary to comply with 28 C.F.R. § 35.163(b), after having surveyed all facilities that are the subject of this Agreement for the purpose of identifying those that have multiple entrances not all of which are accessible.
3. Within 24 months of the effective date of this agreement, the City will complete the following modifications to the Parks and Recreation Office.
a. The single user toilet room contains a number of inaccessible elements and is not accessible to people with disabilities. Provide an accessible toilet room such that all of the room’s elements, including signage, door, door hardware, clear floor space, water closet, urinal (if provided), grab bars, lavatory, mirror, controls, and dispensers, comply with the Standards. Standards §§ 4.13, 4.16, 4.18, 4.19, 4.26, 4.27, 4.30, Figs. 28, 29.
4. Within 24 months of the effective date of this agreement, the City will complete the following modifications to the Posse Ground Park.
a. The route from the parking lot to the picnic shelters and soccer building is inaccessible because there is no route that is stable, firm, or slip resistant to the picnic shelters and there is a step up into the soccer building. Provide at least one accessible route within the boundary of the site connecting these elements that, to the maximum extent feasible, coincides with the route for the general public. The accessible route must have a minimum clear width of 36 inches, or a minimum clear width of 42 inches if there is a turn around an obstruction less than 48 inches wide; have passing spaces at least 60 inches by 60 inches at least every 200 feet; have a minimum clear headroom of 80 inches; have a surface that is firm, stable, and slip resistant; have, in the absence of a curb ramp, ramp, elevator, or platform lift, no level changes in excess of ½ inch vertically; and have a running slope of less than 1:20 (5%) (or have been constructed as a fully accessible ramp) and a cross slope of less than 1:50 (2%). Standards §§ 4.3, 4.5, Fig. 7.Picnic shelters around soccer building are not accessible.
b. The parking reserved for persons with disabilities lacks appropriate signage. At all spaces designated as reserved for persons with disabilities, provide vertical signs with the International Symbol of Accessibility located such that they cannot be obstructed by parked vehicles. At van accessible spaces, provide an additional “Van-Accessible” sign located below the International Symbol of Accessibility. Standards §§ 4.6.4, 4.30.7(1).
c. There is no designated van accessible space. On the shortest accessible route to the accessible entrance, provide 1 van accessible space designated as reserved for people with disabilities. Ensure that van accessible spaces are a minimum of 96 inches wide and served by access aisles at least 96 inches wide. At all spaces designated as reserved for persons with disabilities, provide vertical signs with the International Symbol of Accessibility located such that they cannot be obstructed by parked vehicles. At van accessible spaces, provide an additional “Van-Accessible” sign located below the International Symbol of Accessibility. Ensure that all spaces and access aisles for persons with disabilities are flat and level, with slopes and cross-slopes not exceeding 1:50 in all directions, and that their surfaces are firm, stable, and slip-resistant. Standards §§ 4.1.2(5), 4.6, 4.30.7(1).
d. There is no accessible route from the sidewalk to the dugouts. Provide at least one accessible route within the boundary of the site connecting these elements that, to the maximum extent feasible, coincides with the route for the general public. The accessible route must have a minimum clear width of 36 inches, or a minimum clear width of 42 inches if there is a turn around an obstruction less than 48 inches wide; have passing spaces at least 60 inches by 60 inches at least every 200 feet; have a minimum clear headroom of 80 inches; have a surface that is firm, stable, and slip resistant; have, in the absence of a curb ramp, ramp, elevator, or platform lift, no level changes in excess of ½ inch vertically; and have a running slope of less than 1:20 (5%) (or have been constructed as a fully accessible ramp) and a cross slope of less than 1:50 (2%). Standards §§ 4.3, 4.5, Fig. 7.
e. The route from the parking lot to the basketball court is inaccessible because there is a 3 inch step into the court. Provide at least one accessible route within the boundary of the site connecting these elements that, to the maximum extent feasible, coincides with the route for the general public. The accessible route must have a minimum clear width of 36 inches, or a minimum clear width of 42 inches if there is a turn around an obstruction less than 48 inches wide; have passing spaces at least 60 inches by 60 inches at least every 200 feet; have a minimum clear headroom of 80 inches; have a surface that is firm, stable, and slip resistant; have, in the absence of a curb ramp, ramp, elevator, or platform lift, no level changes in excess of ½ inch vertically; and have a running slope of less than 1:20 (5%) (or have been constructed as a fully accessible ramp) and a cross slope of less than 1:50 (2%). Standards §§ 4.3, 4.5, Fig. 7.
f. The route from accessible parking to the accessible portable toilet room is inaccessible because the portable toilet is placed in an inaccessible location. Provide at least one accessible route within the boundary of the site connecting these elements that, to the maximum extent feasible, coincides with the route for the general public. The accessible route must have a minimum clear width of 36 inches, or a minimum clear width of 42 inches if there is a turn around an obstruction less than 48 inches wide; have passing spaces at least 60 inches by 60 inches at least every 200 feet; have a minimum clear headroom of 80 inches; have a surface that is firm, stable, and slip resistant; have, in the absence of a curb ramp, ramp, elevator, or platform lift, no level changes in excess of ½ inch vertically; and have a running slope of less than 1:20 (5%) (or have been constructed as a fully accessible ramp) and a cross slope of less than 1:50 (2%). Standards §§ 4.3, 4.5, Fig. 7.

References: § 4
 § 4
 § 4
 § 4

v. 
 § 35