and Modules
The characteristics of the subsystem to be assessed in the different phases of design, installation and operation are marked by X in Table B.1.
Table B.1
EC verification of the energy subsystem
Basic parameters
Assessment phase
Design develop. phase
Production phase
Design review
Construction, assembly, mounting
Assembled, before putting into service
Validation under full operating conditions
Particular assessment procedures
Voltage and frequency - 4.2.3
X
N/A
N/A
N/A
Parameters relating to system performance - 4.2.4
X
N/A
N/A
N/A
Assessment of mean useful voltage acc. to clause
Continuity of power supply in case of disturbances in tunnels - 4.2.5
X
N/A
X
N/A
Current capacity, DC systems, trains at standstill - 4.2.6
X (7)
N/A
N/A
N/A
Regenerative braking - 4.2.7
X
N/A
N/A
N/A
Acc. to clause
Electrical protection coordination arrangements - 4.2.8
X
N/A
X
N/A
Acc. to clause
Harmonics and dynamic effects for AC systems - 4.2.9
X
N/A
N/A
N/A
Acc. to clause
Geometry of the overhead contact line: contact wire height -
X (7)
N/A
N/A
N/A
Geometry of the overhead contact line: Variation in contact wire height -
X (7)
N/A
N/A
N/A
Geometry of the overhead contact line: Lateral deviation -
X (7)
N/A
N/A
N/A
Pantograph gauge - 4.2.14
X
N/A
N/A
N/A
Mean contact force - 4.2.15
X (7)
N/A
N/A
N/A
Dynamic behaviour and quality of current collection - 4.2.16
X (7)
N/A
X
N/A
Verification as per clause by validated simulation according to for design review.
Verification of assembled overhead contact line as per clause by measurements according to EN 50317:2002
Pantograph spacing - 4.2.17
X (7)
N/A
N/A
N/A
Contact wire material - 4.2.18
X (7)
N/A
N/A
N/A
Phase separation sections - 4.2.19
X
N/A
N/A
N/A
System separation sections - 4.2.20
X
N/A
N/A
N/A
Management of power supply in case of danger -
X
N/A
X
N/A
Maintenance rules - 4.5
N/A
N/A
X
N/A
Acc. to clause
Protection against electric shock 4.7.2, 4.7.3, 4.7.4
X
X
X
N/A1)
1)
Validation under full operating conditions shall only be done when the validation in the phase 'Assembly before putting into service' is not possible
N/A: not applicable
ANNEX C
REGISTER OF INFRASTRUCTURE, INFORMATION ON THE ENERGY SUBSYSTEM
C.1. Scope
This Annex covers the information concerning the energy subsystem to be included in the Register of infrastructure for each homogeneous section of compliant lines which has to be established according to clause 4.8.2.
C.2. Characteristics to be Described
Table C.1 contains those characteristics of the energy subsystem interoperability for which data are to be given for each line section.
Table C.1
Information to be given in the Register of infrastructure
Parameter, interoperability element
Clause
Voltage and frequency
4.2.3
Maximum train current
Maximum current at standstill, DC systems only
4.2.6
Conditions to accommodate regenerated energy
4.2.7
Nominal contact wire height
Accepted pantograph profile(s)
Maximum line speed with one operating pantograph (if