THE NOTES. AND REQUIRED BY LOCAL CODE
AUTHORITIES. E2. ALL WORK SHALL COMPLY MTH THE tOCAL COOES AND THEIR GOVERNING
AUTHORITIES. E3. OBTAIN AND PAY FOR ALL PERMITS AND FEES RELATING TO ELECTRICAL
SYSTEM. £1. IT IS INTENDED THAT ALL ITEMS OF WORK AND SYSTEMS BE FURNISHED AND
INSTALLED COMPLETE IN ALL DETAILS. READY FOR SATISFACTORY OPERATION AND SERVICE.
APPARATUS REQUIRED SHALL BE FURNISHED, EVEN THOUGH NOT SPECIFICALLY MENTIONED
HEHEW. OR SHOWN ON THE DRAWINGS. ES PROVOE CROUNOINS OF ELECTRICAL WORK IN
STRICT ACCOHJANCC WITH 1HE APPLICABLE COOES AND THEIR AUTHORITIES EG. COORDINATE
ALL WORK MTH OTHER TRADES PRIOR TO ANT INSTALLATION. E7. PROVIDE CODE APPflOVtO
OEAHAWH5 AROUND ELECTRICAL EQUIPMENT. Efl. MATERIALS AND EQUIPMENT SHALL 8£ NEW
AND SHALL CONFORM TO THE N.E.M.A.. 2005 NATIONAL ELECTRICAL CODE (NEC), AND
UNDERWATERS LABORATORIES (UL> STANDARDS IN EVERY CASE. WHERE SUCH STANDARDS HAVE
BEEN ESTABLISHED. EB. COORDINATE STAQNC OF MATERIAL WTH BUILDING MANAGEMENT
REPRESENTATIVE AT THE OF BODING. £10 TESTING - AFTER WIRES ARE IN H.ACE AND
CONNECTED TO OEMCES AND EQUIPMENT, THE SYSTEM SHALL BE TESTED FOR SHORTS AND
GROUNDS. ALL HOT WIRES, f SHORTED 00 GROUNDED, SHALL BE REMOVED AND REFtACED.
Elt ALL METERS, INSTRUMENTS, CABLE CONNECTION. EQUIPMENT, OR APPARATUS NECESSARY
FOR MAKING ALL TESTS. SHALL BE FURNISHED BT THIS CONTRACTOR AT HIS OHM EXPENSE.
£12. AFTER THE COMPLETION OF THE INSTALLATION. THE ENTIRE SYSTEM SHALL BE
THOROUGHLY CLEANED. CLEAN ALL FOREIGN MATTER. PAINT. 04. DIRT. UNREQURED LABELS.
GREASE. AND STICKERS FROU FIXTURES AND EQUIPMENT. REMOVE FROM THE PREMISES ALL
RUBBISH DEBRIS, ETC. ACCUMULATED 8Y THE ELECTRICAL INSTALLATION. E1J THE
CONTRACTOR SHALL BE RESPONSIBLE FOR PROTECTING AIL EQUIPMENT AND SYSTEMS AGAINST
HARMFUL EXPOSURE. OR ACCUMULATION OF DUST/MOISTURE. aOOOWG. CORROSION. OR OTHER
FORMS OF DAMAGE. CLEAN AND RESTORE DAMAGED FINISHES AND EQUIPMENT TO PLACE
MSTALLATION IN A LIKE-NEW CONDITION. El 4. ALL EQUIPMENT LOCATED OUTDOORS SHALL
BE WEATHERPROOF TYPE. EIS EXPANSION FITTINGS - PROVIDE EXPANSION FITTINGS FOR
CONDUITS CROSSNG EXPANSION JOINTS. Elfl. PERMANENT RECORDS - UPON COMPLETION OF
THE INSTALLATION. FURNISH TO THE OWNER WIRING DIAGRAMS OF SPECIAL EQUIPMENT, LOW
VOLTAGE SYSTEMS AND CONTROLS ALOftC WITH RECORD DRAW4GS. CATALOGS AND OPERATING
INSTRUCTIONS FOR ALL EQUIPMENT AND CONTROLS SHALL BE ASSEMBLED, BOUND. AH) OVEN
TO THE OWNER AS A CODE FOR FUTURE OPERATION AND REPAIR. E17 GUARANTEE - ALL
ITEMS. MATERIALS. AND WORKMANSHIP FURNISHED UNDER THIS SPECIFICATION SHALL BE
GUARANTEED FOR A PERIOD OF ONE(l) •itAR. AFTER ACCEPTANCE OF THE WORK AS
EVIDENCED BY THE DATE OF FINAL CERTIFICATE, ANY DEFECTIVE MATERIAL OR FAULTY
WORKMANSHIP SHALL BE REPLACED WITHOUT COST TO OWNER. EIS. VERIFY M FIELD IF THE
SUSPENDED CQUNC SPACE IS UTILIZED AS A PLENUM SPACE. AIL WORK SHALL COMPLY WITH
LOCAL CODE REQUIREMENTS FOR H5TALLATION IN PLENUM CEILING SPACES. Elfl- U4LESS
SPECIFICALLY NOTED OTHENWSE. ALL WRING SHALL BE INSTALLED IN CONDUIT. EM
ELECTRICAL METALLIC TUBND - UfUESS NOTED OTHERWISE. EMI "THINWALL" CONDUIT SHALL
BE UTILIZED, IN GENERAL, WHERE PERMUTED BY CODE. MINIMUM SIZE CONDUIT SHALL BE
3/*". UNLESS SPECtflCAU-Y NOTED OTHERWISE. £21. CONDUIT SHALL BE AS MANUFACTURED
BY ALUED. TRIANGLE OR