CAPAdTY- PS. WIRE TO SPARE CIRCUIT BREAKER IN EXISTING PANEL P6. PROVIDE NEW
60A-3P ORCUlT BREAKER OF TYPE ID UATQI EXISTING IN EMSTING SPAQS Of EXISTING
PANEL. BULDING ENGINEER HAS PROVIDED LOAD READING OF IOA MAXMUM 3 PH. LOAD AT
277/4EOV.. S"H.. 4W. FOR THE PAST 12 MONTHS. THEREFORE PANELS HAVE AVAILABLE
SPARE CAPACITY TO FEED NEW RTU. P7. POWER POLE WITH CENTER DIVIDER FOR ACCESS OF
POWER AND DATA CABLJNG TO FURMTURE SYSTEM. COORDINATE EXACT SIZE. TYPE. HEIGHT
AND LOCATION IN FIELD MTH GENERAL CONTRACTOR. ARCHITECT AND FURMTURE VENDOR. PB-
ELECTRICAL CONTRACTOR SHALL PROVIDE CABLJNG BACK TO VOICE/DATA ROOM AS REQUIRED.
COORDINATE EXACT VOICE/DATA ROOM LOCATION FOR TERMINATION AND CONNECTION OF
VOICE/DATA DROPS WOH ULTA. COORDINATE EXACT CABLING. JACK AMI TERMINATION
SPECtfnCAIlGNS HTH ULTA IT DEPARTMENT. INCLUDE ALL COSTS IN BASE BO. PB. PftOVUE
CONDUIT STUB TO ACCESSIBLE CEILING FOR LOW VOLTAGE CABUNG ACCESS TO FURMTURE
PARTITION. COORDMATE EXACT CONDUIT SIZE REQUIREMENTS MTH ULTA IT DEPARTMENT
FWIOH TO SUBMITTING BID AND INCLUDE ALL COSTS M BASE ,
A-5