Abstract:
A compressor includes an orbiting member and a non-orbiting member mounted relative the orbiting member to define first and second chambers disposed between the orbiting and non-orbiting members. The non-orbiting member forms a seal to generally prevent fluid communication between the first and second chambers when in a first position and breaks the seal to allow fluid communication between the first and second chambers when in a second position. A structure supports the orbiting and non-orbiting members for relative orbital movement therebetween and a time pulsed actuation apparatus is coupled to the structure and configured to selectively break the seal.

Description:
CROSS-REFERENCE TO RELATED APPLICATIONS  
       [0001]     This is a continuation of U.S. Ser. No. 10/730,492, filed Dec. 8, 2003, which is a division of U.S. Ser. No. 10/306,030, filed Nov. 27, 2002, now U.S. Pat. No. 6,679,072; which is a division of U.S. Ser. No. 10/147,782, filed May 16, 2002, now U.S. Pat. No. 6,499,305; which is a division of U.S. Ser. No. 09/886,592, filed Jun. 21, 2001, now U.S. Pat. No. 6,467,280; which is a division of U.S. Ser. No. 09/524,364, filed Mar. 14, 2000, now U.S. Pat. No. 6,408,635; which is a division of U.S. Ser. No. 08/939,779, filed Sep. 29, 1997, now U.S. Pat. No. 6,047,557; which is a continuation-in-part of U.S. Ser. No. 08/486,118, filed Jun. 7, 1995, now U.S. Pat. No. 5,741,120; each of which is incorporated herein by reference in its entirety. 
     
    
     BACKGROUND AND SUMMARY OF THE INVENTION  
       [0002]     The present invention relates generally to cooling systems, compressor control systems and refrigerant regulating valve control systems. More particularly, the invention relates to a refrigeration system employing a pulse width modulated compressor or evaporator stepper regulator controlled by a variable duty cycle signal derived from a load sensor. Preferably an adaptive controller generates the variable duty cycle signal. The compressor has two mechanical elements separated by a seal, and these mechanical elements are cyclically movable relative to one another to develop fluid pressure. The compressor includes a mechanism to selectively break the seal in response to the control signal, thereby modulating the capacity of the system.  
         [0003]     The refrigeration system can be deployed as a distributed system in refrigeration cases and the like. The preferred arrangement allows the compressor and condenser subsystems to be disposed in or mounted on the refrigeration case, thereby greatly reducing the length of refrigerant conduit and refrigerant required.  
         [0004]     Conventionally, refrigeration systems for supermarket refrigeration cases have employed air-cooled or water-cooled condensers fed by a rack of compressors. The compressors are coupled in parallel so that they may be switched on and off in stages to adjust the system cooling capacity to the demands of the load. Commonly, the condensers are located outside, on the roof, or in a machine room adjacent the shopping area where the refrigeration cases are located.  
         [0005]     Within each refrigeration case is an evaporator fed by lines from the condensers through which the expanded refrigerant circulates to cool the case. Conventionally, a closed-loop control system regulates refrigerant flow through the evaporator to maintain the desired case temperature. Proportional-integral-derivative (PID) closed loop control systems are popular for this purpose, with temperature sensors and/or pressure sensors providing the sensed condition inputs.  
         [0006]     It is common practice within supermarkets to use separate systems to supply different individual cooling temperature ranges: low temperature (for frozen foods, ice cream, nominally −25 F); medium (for meat, dairy products, nominally +20 F); high (for floral, produce, nominally +35 to +40 F). The separate low, medium and high temperature systems are each optimized to their respective temperature ranges. Normally, each will employ its own rack of compressors and its own set of refrigerant conduits to and from the compressors and condensers.  
         [0007]     The conventional arrangement, described above, is very costly to construct and maintain. Much of the cost is associated with the long refrigerant conduit runs. Not only are long conduit runs expensive in terms of hardware and installation costs, but the quantity of refrigerant required to fill the conduits is also a significant factor. The longer the conduit run, the more refrigerant required. Adding to the cost are environmental factors. Eventually fittings leak, allowing the refrigerant to escape to atmosphere. Invariably, long conduit runs involve more pipefitting joints that may potentially leak. When a leak does occur, the longer the conduit run, the more refrigerant lost.  
         [0008]     There is considerable interest today in environmentally friendly refrigeration systems. Shortening the conduit run is seen as one way to achieve a more environmentally friendly system. To achieve this, new condenser/compressor configurations and new control systems will need to be engineered.  
         [0009]     Re-engineering condenser/compressor configurations for more environmentally friendly systems is not a simple task, because system efficiency should not be sacrificed. Generally, the conventional roof-mounted condenser system, supplied by condensers, benefits from economies of scale and is quite efficient. These systems serve as the benchmark against which more environmentally friendly systems of the future will need to be measured.  
         [0010]     To appreciate why re-engineering an environmentally yet efficient system has proven so difficult, consider these thermodynamic issues. The typical refrigeration case operates in a very unpredictable environment. From a design standpoint, the thermal mass being cooled is rarely constant. Within the supermarket environment, the temperature and humidity may vary widely at different times of day and over different seasons throughout the year. The product load (items in the refrigeration case) can also change unpredictably. Customers removing product and store clerks replenishing product rarely synchronize. Outside the supermarket environment, the outdoor air temperature and humidity may also vary quite widely between day and night and/or between summer and winter. The capacity of the system must be designed for the harshest conditions (when the condenser environment is the hottest). Thus systems may experience excess capacity in less harsh conditions, such as in the cool evenings or during the winter.  
         [0011]     Periodic defrosting also introduces thermal fluctuations into the system. Unlike thermal fluctuations due to environmental conditions, the thermal fluctuations induced by the defrost cycle are cause by the control system itself and not by the surrounding environment.  
         [0012]     In a similar fashion, the control system for handling multiple refrigeration cases can induce thermal fluctuations that are quite difficult to predict. If all cases within a multi-case system are suddenly turned on at once—to meet their respective cooling demands—the cooling capacity must rapidly be ramped up to maximum. Likewise, if all cases are suddenly switched off, the cooling capacity should be ramped down accordingly. However, given that individual refrigeration cases may operate independently of one another, the instantaneous demand for cooling capacity will tend to vary widely and unpredictably.  
         [0013]     These are all problems that have made the engineering of environmentally friendly systems more difficult. Adding to these difficulties are user engineering/ergonomic problems. The present day PID controller can be difficult to adapt to distributed refrigeration systems. Experienced controls engineers know that a well-tuned PID controller can involve a degree of artistry in selecting the proper control constants used in the PID algorithm. In a large refrigeration system of the conventional architecture (non-distributed) the size of the system justifies having a controls engineer visit the site (perhaps repeatedly) to fine tune the control constant parameters.  
         [0014]     This may not be practical for distributed systems in which the components are individually of a much smaller scale and far more numerous. By way of comparison, a conventional system might employ one controller for an entire multi-case, store-wide system. A distributed system for the same store might involve a controller for each case or adjacent group of cases within the store. Distributed systems need to be designed to minimize end user involvement. It would therefore be desirable if the controller were able to auto configure. Currently control systems lack this capability.  
         [0015]     The present invention provides a distributed refrigeration system in which the condenser is disposed on the refrigeration case and serviced by a special pulse width modulated compressor that may be also disposed within the case. If desired, the condenser and compressor can be coupled to service a group of adjacent refrigeration cases, each case having its own evaporator. The pulse width modulated compressor employs two mechanical elements, such as scroll members, that move rotationally relative to one another to develop fluid pressure for pumping the refrigerant. The compressor includes a mechanism that will selectively break the seal between the two mechanical elements, thereby altering the fluid pressure developed by the compressor while allowing the mechanical elements to maintain substantially constant relative movement with one another. The compressor can be pulse width modulated by making and breaking the fluid seal without the need to start and stop the electric motor driving the mechanical elements.  
         [0016]     The pulse width modulated compressor is driven by a control system that supplies a variable duty cycle control signal based on measured system load. The controller may also regulate the frequency (or cycle time) of the control signal to minimize pressure fluctuations in the refrigerant system. The on time is thus equal to the duty cycle multiplied by the cycle time, where the cycle time is the inverse of the frequency.  
         [0017]     The refrigeration system of the invention has a number of advantages. Because the instantaneous capacity of the system is easily regulated by variable duty cycle control, an oversized compressor can be used to achieve faster temperature pull down at startup and after defrost, without causing short cycling as conventional compressor systems would. Another benefit of variable duty cycle control is that the system can respond quickly to sudden changes in condenser temperature or case temperature set point. The controller adjusts capacity in response to disturbances without producing unstable oscillations and without significant overshoot. Also, the ability to match instantaneous capacity to the demand allows the system to operate at higher evaporator temperatures. (Deep drops in temperature experienced by conventional systems at overcapacity are avoided.)  
         [0018]     Operating at higher evaporator temperatures reduces the defrost energy required because the system develops frost more slowly at higher temperatures. Also, the time between defrosts can be lengthened by a percentage proportional to the accumulated runtime as dictated by the actual variable duty cycle control signal. For example, a sixty percent duty cycle would increase a standard three-hour time between defrosts to five hours (3/0.60=5).  
         [0019]     The pulse width modulated operation of the system yields improved oil return. The refrigerant flow pulsates between high capacity and low capacity (e.g. 100% and 0%), creating more turbulence which breaks down the oil boundary layer in the heat exchangers.  
         [0020]     Another benefit of the variable duty cycle control system is its ability to operate with a variety of expansion devices, including the simple orifice, the thermal expansion valve (TXV) and the electronic expansion valve. A signal derived from the expansion device controller can be fed to the compressor controller of the invention. This signal allows the variable duty cycle control signal and/or its frequency to be adjusted to match the instantaneous operating conditions of the expansion device. A similar approach may be used to operate variable speed fans in air cooled condenser systems. In such case the controller of the invention may provide a signal to control fan speed based on the current operating duty cycle of the compressor.  
         [0021]     Yet another benefit of the invention is its ability to detect when the system is low on refrigerant charge, an important environmental concern. Low refrigerant charge can indicate the presence of leaks in the system. Low charge may be detected by observing the change in error between actual temperature and set point temperature as the system duty cycle is modulated. The control system may be configured to detect when the modulation in duty cycle does not have the desired effect on temperature maintenance. This can be due to a loss of refrigerant charge, a stuck thermal expansion valve or other malfunctions.  
         [0022]     For a more complete understanding of the invention, its objects and advantages, refer to the following specification and to the accompanying drawings. 
     
    
     BRIEF DESCRIPTION OF THE DRAWINGS  
       [0023]      FIG. 1  is a system block diagram of a prior art refrigeration system configuration;  
         [0024]      FIG. 2  is a block diagram of a refrigeration system in accordance with the present invention;  
         [0025]      FIG. 3  is a cross-sectional view of an embodiment of the pulse width modulated compressor, shown in the loaded state;  
         [0026]      FIG. 4  is a cross-sectional view of the compressor of  FIG. 3 , shown in the unloaded state;  
         [0027]      FIG. 5  is another embodiment of a refrigeration or cooling system in accordance with the present invention;  
         [0028]      FIG. 6  is a block diagram of the controller;  
         [0029]      FIG. 7  is a block diagram showing how the controller may be used to modulate an evaporator stepper regulator;  
         [0030]      FIG. 8  is a block diagram of the signal conditioning module of the controller of  FIG. 6 ;  
         [0031]      FIG. 9  is a block diagram of the control module of the controller of  FIG. 6 ;  
         [0032]      FIG. 10  is a state diagram depicting the operating states of the controller;  
         [0033]      FIG. 11  is a flowchart diagram illustrating the presently preferred PI control algorithm;  
         [0034]      FIG. 12  is a waveform diagram illustrating the variable duty cycle signal produced by the controller and illustrating the operation at a constant frequency;  
         [0035]      FIG. 13  is a waveform diagram of the variable duty cycle signal, illustrating variable frequency operation;  
         [0036]      FIG. 14  is a series of graphs comparing temperature and pressure dynamics of system employing the invention with a system of conventional design;  
         [0037]      FIG. 15  is a block diagram illustrating the adaptive tuning module of the invention;  
         [0038]      FIG. 16   a  is a flowchart diagram illustrating the presently preferred operation of the adaptive tuning module, specifically with respect to the decision whether to start tuning;  
         [0039]      FIG. 16   b  is a flowchart diagram illustrating the presently preferred process performed by the adaptive tuning module in the integration mode;  
         [0040]      FIG. 16   c  is a flowchart diagram illustrating the operation of the adaptive tuning module in the calculation mode;  
         [0041]      FIG. 17  is a state diagram illustrating the operative states of the adaptive tuning module;  
         [0042]      FIG. 18  is a block diagram illustrating the fuzzy logic block of the adaptive tuning loop;  
         [0043]      FIG. 19  is a membership function diagram for the fuzzy logic block of  FIG. 18 ;  
         [0044]      FIG. 20  is a truth table relating to the membership function of  FIG. 19  as used by the fuzzy logic block of  FIG. 18 ;  
         [0045]      FIG. 21  is an output membership function diagram for the fuzzy logic block of  FIG. 18 ; and  
         [0046]      FIG. 22  is a schematic illustrating exemplary sensor locations for control-related and diagnostic-related functions of the present invention.  
     
    
     DESCRIPTION OF THE PREFERRED EMBODIMENTS  
       [0047]      FIG. 1  illustrates how a conventional supermarket refrigeration system is configured. As previously discussed, it is conventional practice to place the compressors  30  and the condenser  32  in a location remote from the refrigeration cases  34 . In this illustration, the compressors  30  are configured in a parallel bank located on the roof  36  of the building. The bank of compressors supply a large condenser  32 , which may be air cooled or water cooled. The condenser supplies liquid refrigerant to a receiver  38 . The receiver  38 , in turn, supplies the individual refrigeration cases, which are connected in parallel, as illustrated. In most implementations a liquid line solenoid valve  40  is used to regulate flow to the associated evaporator  42 . The refrigerant is supplied to the evaporator through a suitable expansion device such as expansion valve  44 . The expansion valve  44  provides a restricted orifice that causes the liquid refrigerant to atomize into liquid droplets that are introduced into the inlet side of the evaporator  42 . The evaporator  42 , located within the refrigeration case  34 , extracts heat from the case and its contents by vaporization of the liquid refrigerant droplets into a gas. The compressors  30  extract this gas by suction and compress it back into the liquid state. The liquid refrigerant is then cooled in the condenser  32  and returned to the receiver  38 , whereupon the cycle continues.  
         [0048]     To match cooling capacity to the load, the compressors  30  may be switched on and off individually or in groups, as required. In a typical supermarket arrangement there may be several independent systems, each configured as shown in  FIG. 1 , to handle different operating temperature ranges. Note that the liquid line  46  and the suction line  48  may each need to be quite lengthy (e.g., up to 150 feet) to span the distance from refrigeration case to roof.  
         [0049]      FIG. 2  shows a refrigeration case  34  configured according to the principles of the present invention. The condenser  32  and compressor  30  are both disposed within case  34  or attached thereto. Evaporator  42  and the associated expansion valve  44  are likewise disposed within case  34 . The condenser  32  is provided with a heat removal mechanism  50  by which heat is transferred to ambient. The heat removal mechanism can be a water jacket connected to suitable plumbing for carrying waste heat to a water cooling tower located on the building roof. Alternatively, the heat removal mechanism can be a forced-air cooling system or a passive convection-air cooling system.  
         [0050]     The refrigeration system of the invention employs a compressor controller  52  that supplies a pulse width modulated control signal on line  54  to a solenoid valve  56  on compressor  30 . The compressor controller adjusts the pulse width of the control signal using an algorithm described below. A suitable load sensor such as temperature sensor  58  supplies the input signal used by the controller to determine pulse width.  
         [0051]      FIGS. 3 and 4  show the details of compressor  30 .  FIG. 3  shows the compressor in its loaded state and  FIG. 4  shows the compressor in its unloaded state. The solenoid valve  56  switches the compressor between these two states while the compressor motor remains energized. One important advantage of this configuration is that the compressor can be pulse width modulated very rapidly between the loaded and unloaded states without interrupting power to the compressor motor. This pulse width modulated cycling exerts less wear on the compressor, because the motor is not subjected to sudden changes in angular momentum.  
         [0052]     Referring to  FIGS. 3 and 4 , there is shown an exemplary compressor  30 . Compressor  30  may be used within a hermetic scroll compressor such as generally of the type described in assignee&#39;s U.S. Pat. No. 5,102,316.  
         [0053]     The exemplary compressor  30  includes an outer shell  61  and an orbiting scroll member  64  supported on upper bearing housing  63  and drivingly connect to crankshaft  62  via crank pin  65  and drive bushing  60 . A second non-orbiting scroll member  67  is positioned in meshing engagement with scroll member  64  and axially movably secured to upper bearing housing  63 . A partition plate  69  is provided adjacent the upper end of shell  61  and serves to define a discharge chamber  70  at the upper end thereof.  
         [0054]     In operation, as orbiting scroll member  64  orbits with respect to scroll member  67 , suction gas is drawn into shell  61  via suction inlet  71  and thence into compressor  30  through inlet  72  provided in non-orbiting scroll member  67 . The intermeshing wraps provided on scroll members  64  and  67  define moving fluid pockets which progressively decrease in size and move radially inwardly as a result of the orbiting motion of scroll member  64  thus compressing the suction gas entering via inlet  72 . The compressed gas is then discharged into discharge chamber  70  via discharge port  73  provided in scroll member  67  and passage  74 .  
         [0055]     In order to unload compressor  30 , solenoid valve  56  will be actuated in response to a signal from control module  87  to interrupt fluid communication to increase the pressure within chamber  77  to that of the discharge gas. The biasing force resulting from this discharge pressure will overcome the sealing biasing force thereby causing scroll member  67  to move axially upwardly away from orbiting scroll member  64 . This axial movement will result in the creation of a leakage path between the respective wrap tips and end plates of scroll members  64  and  67  thereby substantially eliminating continued compression of the suction gas.  
         [0056]     A flexible fluid line  91  extends from the outer end of passage  90  to a fitting  92  extending through shell  61  with a second line  93  connecting fitting  92  to solenoid valve  56 . Solenoid valve  56  has fluid lines  82  and  84  connected to suction line  83  and discharge line  85  and is controlled by control module  87  in response to conditions sensed by sensor  88  to effect movement of non-orbiting scroll member  67  between the positions shown in  FIGS. 3 and 4 .  
         [0057]     When compression of the suction gas is to be resumed, solenoid valve  56  will be actuated so as to move scroll member  67  into sealing engagement with scroll member  64 .  
         [0058]     The refrigeration case embodiment of  FIG. 2  may be packaged as a self-contained unit. While that may be a desirable configuration for many applications, the invention is not restricted to stand alone, self-contained refrigeration case configurations. Rather, the invention lends itself to a variety of different distributed refrigeration systems.  FIG. 5  shows an example of such a distributed system.  
         [0059]     Referring to  FIG. 5 , a single compressor  30  and condenser  32  can service several distributed refrigeration cases or several distributed cooling units in a heating and cooling (HVAC) system. In  FIG. 5  the refrigeration cases or cooling system housings are shown as dashed boxes, designated  34   a ,  34   b , and  34   c . Conveniently, the compressor  30  and condenser  32  may be disposed within or attached to one of the refrigeration cases or housings, such as refrigeration case or housing  34   a.    
         [0060]     Each refrigeration case or housing has its own evaporator and associated expansion valve as illustrated at  42  ( a, b, c ) and  44  ( a, b, c ). In addition, each refrigeration case or housing may have its own temperature sensor  58  ( a, b, c ) supplying input information to the compressor controller  52 . Finally, a pressure sensor  60  monitors the pressure of the suction line  48  and supplies this information to compressor controller  52 . The compressor controller supplies a variable duty cycle signal to the solenoid valve  56  as previously described.  
         [0061]     The multiple case or multiple cooling unit embodiment of  FIG. 5  shows how a single compressor can be pulse width modulated by compressor controller  52  to supply the instantaneous demand for cooling. The temperature sensors  58  ( a, b, c ) collectively provide an indication of the load on the system, as does pressure sensor  60 . The controller adjusts the pulse width of the control signal to modulate the compressor between its high capacity and low capacity states (100%, 0%) to meet the instantaneous demand for refrigerant.  
         [0062]     As an alternate control technique, one or more of the suction lines exiting the evaporator can be equipped with an electrically controlled valve, such as an evaporator pressure regulator valve  45   c . Valve  45   c  is coupled to controller  52 , as illustrated. It may be supplied with a suitable control signal, depending on the type of the valve. A stepper motor valve may be used for this purpose, in which case controller  30  would supply a suitable signal to increment or decrement the setting of the stepper motor to thereby adjust the orifice size of the valve. Alternatively, a pulse width modulated valve could be used, in which case it may be controlled with the same variable duty cycle signal as supplied to the compressor  30 .  
         [0063]     Controller  52  is not limited to solely compressor control applications. The variable duty cycle control signal can also be used to control other types of refrigerant flow and pressure control devices, such as refrigerant regulating valves.  FIG. 7  shows such an application, where the output of controller  52  supplies control signals to evaporator stepper regulator  43 . This device is a fluid pressure regulator that is adjusted by stepper motor  45 . The evaporator stepper regulator (ESR) valve  43  adjusts the suction pressure to thereby adjust the capacity of the system.  
         [0064]     A block diagram of the presently preferred compressor controller is illustrated in  FIG. 6 . A description of the various signals and data values shown in this and successive figures is summarized in Table I below.  
                           TABLE I                               Default           No.   Variable Name   Value   Description                   1   Signal Conditioning:                   Sensor Alarm   False   Indicates Sensor Reading is not                   within expected range           Sensor Mode   Min   User configuration to indicate if                   Min/Max/Avg is performed for all                   temperature Sensors           Sampling Time (Ts)   0.5 sec   Rate at which Signal conditioning                   block is executed           Control Type   T/P   if controlled by only Temp. or both               Type   Temp. &amp; Pressure       2   Control Block:           Sensor Alarm   False   Same as before           System Alarm   False   Generated by Adaptive Block                   indicative some system problem           SSL   0   Steady state loading %           Defrost Status   False   Whether system is in defrost           Pull_Down_Time   0   Time taken to pull down after                   defrost           Gain (K)   7   Gain used in PI algorithm           Integral Time (Ti)   100    used in PI           Control Time (Tc)   10 Sec   used in PI           Control Set Pt. (St)   0 F.   used in PI           Operating State   1   What state the machine is                   operating at       3   Defrost Control           Defrost Status   False   If defrost status of the case           Defrost Type   External   If the defrost is from external timer                   or Internal clock of controller           Defrost Interval   8 hrs   Time between defrost           Defrost Duration   1 hr   Defrost Duration           Defrost Termination   50 F.   Termination temperature for           Temp.       defrost                  
 
         [0065]     At the heart of the controller is control block module  102 . This module is responsible for supplying the variable duty cycle control signal on lead  104 . Module  102  also supplies the compressor ON/OFF signal on lead  106  and an operating state command signal on lead  108 . The compressor ON/OFF signal drives the contactors that supply operating current to the compressor motor. The operating state signal indicates what state the state machine ( FIG. 10 ) is in currently.  
         [0066]     The control block module receives inputs from several sources, including temperature and pressure readings from the temperature and pressure sensors previously described. These temperature readings are passed through signal conditioning module  110 , the details of which are shown in the pseudocode Appendix. The control block module also receives a defrost status signal from defrost control module  112 . Defrost control module  112  contains logic to determine when defrost is performed. The present embodiment allows defrost to be controlled either by an external logic signal (supplied through lead  114 ) or by an internal logic signal generated by the defrost control module itself. The choice of whether to use external or internal defrost control logic is user selectable through user input  116 . The internal defrost control uses user-supplied parameters supplied through user input  118 .  
         [0067]     The preferred compressor controller in one form is autoconfigurable. The controller includes an optional adaptive tuning module  120  that automatically adjusts the control algorithm parameters (the proportional constant K) based on operating conditions of the system. The adaptive tuning module senses the percent loading (on lead  104 ) and the operating state (on lead  108 ) as well as the measured temperature after signal conditioning (on lead  122 ). Module  120  supplies the adaptive tuning parameters to control block  102 , as illustrated. The current embodiment supplies proportional constant K on lead  124  and SSL parameter on lead  126 , indicative of steady-state loading percent. A system alarm signal on lead  126  alerts the control block module when the system is not responding as expected to changes in the adaptively tuned parameters. The alarm thus signals when there may be a system malfunction or loss of refrigerant charge. The alarm can trigger more sophisticated diagnostic routines, if desired. The compressor controller provides a number of user interface points through which user-supplied settings are input. The defrost type (internal/external) input  116  and the internal defrost parameters on input  118  have already been discussed. A user input  128  allows the user to specify the temperature set point to the adaptive tuning module  120 . The same information is supplied on user input  130  to the control block module  102 . The user can also interact directly with the control block module in a number of ways. User input  132  allows the user to switch the compressor on or off during defrost mode. User input  134  allows the user to specify the initial controller parameters, including the initial proportional constant K. The proportional constant K may thereafter be modified by the adaptive tuning module  120 . User input  136  allows the user to specify the pressure differential (dP) that the system uses as a set point.  
         [0068]     In addition to these user inputs, several user inputs are provided for interacting with the signal conditioning module  110 . User input  138  selects the sensor mode of operation for the signal conditioning module. This will be described in more detail below. User input  140  allows the user to specify the sampling time used by the signal conditioning module. User input  142  allows the user to specify whether the controller shall be operated using temperature sensors only (T) or temperature and pressure sensors (T/P).  
         [0069]     Referring now to  FIG. 8 , the signal conditioning module is shown in detail. The inputs (temperature and/or pressure sensors) are shown diagrammatically at  144 . These inputs are processed through analog to digital convertor  146  and then supplied to the control type selector  148 . Temperature readings from the temperature and/or pressure sensors are taken sequentially and supplied serially through the analog to digital convertor. The control type selector codes or stores the data so that pressure and temperature values are properly interpreted.  
         [0070]     Digital filtering is then applied to the signal at  150  to remove spurious fluctuations and noise. Next, the data are checked in module  152  to ensure that all readings are within expected sensor range limits. This may be done by converting the digital count data to the corresponding temperature or pressure values and checking these values against the pre-stored sensor range limits. If the readings are not within sensor range an alarm signal is generated for output on output  154 .  
         [0071]     Next a data manipulation operation is performed at  156  to supply the temperature and/or pressure data in the form selected by the sensor mode user input  138 . The current embodiment will selectively average the data or determine the minimum or maximum of the data (Min/Max/Avg). The Min/Max/Avg mode can be used to calculate the swing in pressure differential, or a conditioned temperature value. The average mode can be used to supply a conditioned temperature value. These are shown as outputs  158  and  160 , respectively.  
         [0072]      FIG. 9  shows the control block module in greater detail. The conditioned temperature or pressure signal is fed to calculation module  162  that calculates the error between the actual temperature or pressure and the set point temperature or pressure. Module  162  also calculates the rate of change in those values.  
         [0073]     The control block module is designed to update the operating state of the system on a periodic basis (every T c  seconds, nominally once every second). The Find Operating State module  164  performs this update function. The state diagram of  FIG. 10  provides the details on how this is performed. Essentially, the operating state advances, from state to state, based on whether there is a sensor alarm (SA) present, whether there is a defrost status signal (DS) present and what the calculated error value is. The Find Operating State module  164  supplies the operating state parameter and the Pull Down Time parameter to the decision logic module  166 .  
         [0074]     Referring to  FIG. 10 , the Find Operating State module  164  advances from state to state as follows. Beginning in the initial state  168  the module advances to the normal operating state  170  after initialization. It remains in that state until certain conditions are met.  FIG. 10  shows by label arrows what conditions are required to cycle from the normal operating state  170  to the defrost state  172 ; to the pull down state  174 ; to the sensor alarm pull down state  176 ; to the sensor alarm operating state  178  and to the sensor alarm defrost state  180 .  
         [0075]     The decision logic module  166  ( FIG. 9 ) determines the duty cycle of the variable duty cycle signal. This is output on lead  182 , designated % Loading. The decision logic module also generates the compressor ON/OFF signal on lead  184 . The actual decision logic will be described below in connection with  FIG. 11 . The decision logic module is form of proportional integral (PI) control that is based on an adaptively calculated cycle time T cyc . This cycle time is calculated by the calculation module  186  based on a calculated error value generated by module  188 . Referring back to  FIG. 6 , the conditioned pressure differential signal on lead  122  (Cond dP) is supplied to the Calculate Error module  188  ( FIG. 9 ) along with the pressure differential set point value as supplied through user input  136  ( FIG. 6 ). The difference between actual and set point pressure differentials is calculated by module  188  and fed to the calculation module  186 . The adaptive cycle time T cyc  is a function of the pressure differential error and the operating state as determined by the find operating state module  164  according to the following calculation: 
 
 T   cyc(new)   =T   cyc(old)   +K   c *Error  (1) 
 
         [0076]     where: 
        K c : proportional constant; and     Error: (actual—set point) suction pressure swing.        
 
         [0079]     The presently preferred PI control algorithm implemented by the decision logic module  166  is illustrated in  FIG. 11 . The routine begins at step  200  by reading the user supplied parameters K, T i , T c  and S t . See  FIG. 6  for a description of these user supplied values. The constant K p  is calculated as being equal to the initially supplied value K; and the constant K i  is calculated as the product of the initially supplied constant K and the ratio T c /T i .  
         [0080]     Next, at step  202  a decision is made whether the absolute value of the error between set point temperature and conditioned temperature (on lead  190 ,  FIG. 9 ) is greater than 5° F. If so, the constant K p  is set equal to zero in step  204 . If not, the routine simply proceeds to step  206  where a new loading percent value is calculated as described by the equation in step  206  of  FIG. 11 . If the load percent is greater than 100 (step  208 ), then the load percent is set equal to 100% at step  210 . If the load percent is not greater than 100% but is less than 0% (step  212 ) the load percent is set equal to 0% at step  214 . If the load percent is between the 0% and 100% limits, the load percent is set equal to the new load percent at step  216 .  
         [0081]     The variable duty cycle control signal generated by the controller can take several forms.  FIGS. 12 and 13  give two examples.  FIG. 12  shows the variable duty cycle signal in which the duty cycle varies, but the frequency remains constant. In  FIG. 12 , note that the cycle time, indicated by hash marks  220 , are equally spaced. By comparison,  FIG. 13  illustrates the variable duty cycle signal wherein the frequency is also varied. In  FIG. 13 , note that the hash marks  220  are not equally spaced. Rather, the waveform exhibits regions of constant frequency, regions of increasing frequency and regions of decreasing frequency. The variable frequency illustrated in  FIG. 13  is the result of the adaptive modulation of the cycle time T cyc .  
         [0082]      FIG. 14  graphically shows the benefits that the control system of the invention has in maintaining tighter temperature control and higher suction pressure with improved system efficiency. Note how the temperature curve  222  of the invention exhibits considerably less fluctuation than the corresponding temperature curve  224  of a conventional controller. Similarly, note that the pressure curve  226  of the invention has a baseline well above that of pressure curve  228  of the conventional controller. Also, the peak-to-peak fluctuation in pressure exhibited by the invention (curve  226 ) is much smaller than that of the conventional controller (curve  228 ).  
         [0083]     The controller of the invention operates at a rate that is at least four times faster (typically on the order of at least eight times faster) than the thermal time constant of the load. In the presently preferred embodiment the cycle time of the variable duty cycle signal is about eight times shorter than the time constant of the load. By way of non-limiting example, the cycle time of the variable duty cycle signal might be on the order of 10 to 15 seconds, whereas the time constant of the system being cooled might be on the order of 1 to 3 minutes. The thermal time constant of a system being cooled is generally dictated by physical or thermodynamic properties of the system. Although various models can be used to describe the physical or thermodynamic response of a heating or cooling system, the following analysis will demonstrates the principle.  
         [0000]     Modeling the Thermal Time Constant of the System Being Cooled.  
         [0084]     One can model the temperature change across the evaporator coil of a refrigeration system or heat pump as a first order system, wherein the temperature change may be modeled according to the following equation: 
 
Δ T=ΔT   ss [1−exp(− t /γ)]+Δ T   0 exp(−τ/γ). 
 
 where: 
        ΔT=air temperature change across coil     ΔT ss =steady state air temperature change across coil     ΔT 0 =air temperature change across the coil at time zero     t=time     γ=time constant of coil. 
 
 The transient capacity of the unit can be obtained by multiplying the above equation by the air mass flow rate (m) and specific heat at constant pressure (C p ) and integrating with respect to time. 
       
 
         [0090]     Generally, it is the removal of the refrigerant from the evaporator that controls the time required to reach steady state operating condition, and thus the steady state temperature change across the condenser coil. If desired, the system can be modeled using two time constants, one based on the mass of the coil and another based on the time required to get the excess refrigerant from the evaporator into the rest of the system. In addition, it may also be desirable to take into account, as a further time delay, the time lag due to the large physical distance between evaporator and condenser coils in some systems.  
         [0091]     The thermal response of the evaporator coil may be modeled by the following equation: 
 
∂=½[(1− e   1/γ1 )+( 1−e   1/γ2 )]
 
         [0092]     where:  
         [0093]     ∂=temperature change across coil/steady state temperature change across coil  
         [0094]     t=time  
         [0095]     γ 1 =time constant based on mass of coil  
         [0096]     γ 2 =time constant based on time required to remove excess  
         [0097]     refrigerant from evaporator  
         [0098]     In practice, the controller of the invention cycles at a rate significantly faster than conventional controllers. This is because the conventional controller cycles on and off in direct response to the comparison of actual and set-point temperatures (or pressures). In other words, the conventional controller cycles on when there is demand for cooling, and cycles off when the error between actual and set-point temperature is below a predetermined limit. Thus the on-off cycle of the conventional controller is very highly dependent on the time constant of the system being cooled.  
         [0099]     In contrast, the controller of the invention cycles on and off at a rate dictated by calculated values that are not directly tied to the instantaneous relation between actual and set-point temperatures or pressures. Rather, the cycle time is dictated by both the cycle rate and the duty cycle of the variable duty cycle signal supplied by the controller. Notably, the point at which the controller cycles from on to off in each cycle is not necessarily the point at which the demand for cooling has been met, but rather the point dictated by the duty cycle needed to meet the demand.  
       Adaptive Tuning  
       [0100]     The controller Geneva described above can be configured to perform a classic control algorithm, such as a conventional proportional-integral-derivative (PID) control algorithm. In the conventional configuration the user would typically need to set the control parameters through suitable programming. The controller may also be of an adaptive type, described here, to eliminate the need for the user to determine and program the proper control parameters.  
         [0101]     Thus, one important advantage of the adaptive controller is its ability to perform adaptive tuning. In general, tuning involves selecting the appropriate control parameters so that the closed loop system is stable over a wide range of operating conditions, responds quickly to reduce the effect of disturbance on the control loop and does not cause excessive wear of mechanical components through continuous cycling. These are often mutually exclusive criteria, and a compromise must generally be made. In  FIG. 18  (and also  FIG. 6 ) there are two basic control loops: the refrigeration control loop and the adaptive tuning loop. The refrigeration control loop is administered by control block module  102 ; the adaptive loop is administered by adaptive tuning module  120 . Details of the adaptive tuning module  120  are shown in  FIGS. 15, 16   a - 16   c  and  17 . The presently preferred adaptive tuning module uses a fuzzy logic control algorithm that will be described in connection with  FIGS. 18-20 .  
         [0102]     Referring to  FIG. 15 , the adaptive tuning module performs basically three functions. First, it decides whether to perform adaptive tuning. This is handled by module  240 . Second, it gathers the needed parameters for performing adaptive tuning. This is handled by module  242 . Third, it calculates the adaptive gain used by the control loop. This is handled by module  244 .  
         [0103]     Module  240  bases the decision on whether to start tuning upon two factors: the current operating state of the system and the control set point. The flowchart of  FIG. 16   a  shows the steps involved in this decision. Module  242  integrates key parameters needed for the calculations performed by module  244 . Essentially, module  242  inputs the percent loading, the temperature and pressure values and the set point temperature. It outputs the following data: S_ER (the total number of conditioned temperature and pressure data points that are within 0.5 degrees or 1 Psig of the set point value), S_Close (the total number of percent loading data points that goes to zero percent during a given sampling interval, e.g. 30 min.), S_Open (the total number of percent loading data points that goes to 100% in the sampling interval) and SSLP (a moving average or rolling average of the percent loading during the sampling interval). Module  242  is responsive to a tuning flag that is set by module  240 . Module  242  performs the integration of these key parameters when signaled to do so by the tuning flag.  FIG. 16   b  shows the steps involved in performing integration of these key parameters.  
         [0104]     Finally, the calculation block takes the data supplied by module  242  and calculates the adaptive gain using the process illustrated in  FIG. 16   c.    
         [0105]     The adaptive tuning module  120  will cycle through various operating states, depending on the state of a timer.  FIG. 17  is a state diagram showing how the presently preferred embodiment will function. Note that the sequence transitions from the initialization mode to either the integration mode or the no tuning mode, depending on whether the tuning flag has been set. Once in the integration mode, the system performs integration until the timer lapses (nominally 30 minutes), whereupon the calculation mode is entered. Once the calculations are completed the timer is reset and the system returns to the initialization mode.  
         [0106]     The block diagram of the adaptive scheme is shown in  FIG. 18 . There are two basic loops—The first one is the PID control loop  260  that runs every “dt” second and the second is the adaptive loop  262  that runs every “ta” second. When the control system starts, the PID control loop  260  uses a default value of gain (K) to calculate the control output. The adaptive loop  262 , checks the error e(t)  264  every “ta” seconds  266  (preferably less than 0.2*dt seconds). At module  268  if the absolute value of error, e(t), is less than desired offset (OS), a counter Er_new is incremented. The Offset (OS) is the acceptable steady-state error (e.g. for temperature control it may be +/1° F.). This checking process continues for “tsum” seconds  270  (preferably 200 to 500 times dt seconds). After “tsum” seconds  270 , the value Er_new is converted into percentage (Er_new %  272 ). The parameter Er_new %  272  indicates the percentage of sampled e(t) that was within accepted offset (OS) for “tsum” time. In other words, it is a measure of how well the control variable was controlled for past “tsum” seconds. A value of 100% means “tight” control and 0% means “poor” control. Whenever Er_new % is 100%, the gain remains substantially unchanged as it indicates tighter control. However, if Er_new happens to be between 0 and 100%, adaptive fuzzy-logic algorithm module  274  calculates a new gain (K_new  276 ) that is used for next “tsum” seconds by the control algorithm module  278 .  
         [0107]     In the preferred embodiment, there is one output and two inputs to the fuzzy-logic algorithm module  274 . The output is the new gain (K_new) calculated using the input, Er_new %, and a variable, Dir, defined as follows: 
 
 Dir =Sign[( ER −new %− ER -old %)*( K _new− K -old)]  (2) 
 
         [0108]     where: 
        Sign stands for the sign (+ve, −ve or zero) of the term inside the bracket;     Er_new % is the percentage of e(t) that is within the offset for past “tsum” seconds;     Er_old % is the value of Er_new % in “(tsum−1)” iteration;     K_new is the gain used in “tsum” time; and     K_old is the gain in (tsum−1) time.        
 
         [0114]     For example, suppose the controller starts at 0 seconds with a default value of K=10 and, ta=1 seconds, tsum=1000 seconds and OS=1. Suppose 600 e(t) data out of a possible 1000 data was within the offset. Therefore, after 1000 sec, Er_new %=60 (i.e., 600/1000*100), K_new=10. Er_old % and K_old is set to zero when the adaptive fuzzy-logic algorithm module  274  is used the first time. Plugging these numbers in Eq.(2) gives the sign of the variable “Dir” as positive. Accordingly, the inputs to the adaptive fuzzy-logic module  274  for the first iteration are respectively, Er_new %=60 and Dir=+ve.  
         [0115]     The next step is to perform fuzzification of these inputs into fuzzy inputs by using membership functions.  
         [0000]     Fuzzification:  
         [0116]     A membership function is a mapping between the universe of discourse (x-axis) and the grade space (y-axis). The universe of discourse is the range of possible values for the inputs or outputs. For ER_new % it is preferably from 0 to 100. The value in the grade space typically ranges from 0 to 1 and is called a fuzzy input, truth value, or a degree of membership.  FIG. 19  shows graph  300  which contains the membership functions for the input, Er_new %. Er_new % is divided into three linguistic variables—LARGE ( 304 ), MEDIUM ( 306 ) AND SMALL ( 308 ). For Er_new %=60, the fuzzy inputs (or degree of membership function) are −0.25 of LARGE and 0.75 of MEDIUM. The input variable “Dir” is well defined (+ve, −ve or zero) and thus does not require a membership function in this application. The next step is to create the “Truth Table” or Rule Evaluation.  
         [0000]     Rule Evaluation:  
         [0117]     Rule evaluation takes the fuzzy inputs from the fuzzification step and the rules from the knowledge base and calculates fuzzy outputs.  FIG. 20  shows the rules as truth table. For the first column and first row, the rule is:  
         [0118]     “IF ER_new % is LARGE AND Dir is NEGATIVE THEN New Gain is NO CHANGE (NC)” (i.e. if the percentage of e(t) data that is within the offset (OS) for last “tsum” seconds is LARGE and the direction (DIR) is NEGATIVE/ZERO then do not change the existing K value (NO CHANGE)).  
         [0119]     In the example, because ER_new % has fuzzy inputs LARGE (0.25) AND MEDIUM (0.75) with POSITIVE Dir, the rules that will be used are:  
         [0120]     IF ER_new % is LARGE (0.25) AND Dir is POSITIVE THEN New Gain is NO CHANGE (NC=1)  
         [0121]     IF ER_new % is MEDIUM (0.75) AND Dir is POSITIVE THEN New Gain is POSITIVE SMALL CHANGE (PSC=1.2)  
         [0000]     Defuzzification:  
         [0122]     Finally, the defuzzification process converts the fuzzy outputs from the rule evaluation step into the final output by using Graph  310  of  FIG. 21 . Graph  310 , uses the following labels=“NBC” for negative big change; “NSC” for negative small change; “NC” for no change; “PSC” for positive small change; and PBC for positive big change. The Center of Gravity or centroid method is used in the preferred embodiment for defuzzification. The output membership function for change in gain is shown in  FIG. 21 .  
         [0123]     The centroid (the Fuzzy-Logic Output) is calculated as:  
       Centroid   =     K_new   ·     [               ∑             ⁢           ⁢       μ   ⁡     (   x   )       ·   x                 all   ·   x                   ∑           ⁢     μ   ⁡     (   x   )                   all   ·   x             ]           
 
         [0124]     where:  
         [0125]     (x) is the fuzzy output value for universe of discourse value x.  
         [0126]     In our example, the output (K_new) becomes  
       Output   =       10   ·     [         0.25   ⁢     (   1   )       +     0.75   ⁢     (   1.2   )           0.25   +   0.75       ]       ≈   11.50         
 
         [0127]     Once the three steps of fuzzification, rule evaluation, and defuzzification are finished and the output has been calculated, the process is repeated again for new set of Er_new %.  
         [0128]     In the above example, after the first 1000 sec, the adaptive algorithm calculates a new gain of K_new=11.50. This new gain is used for the next 1000 sec (i.e. from t=1000 to 2000 sec in real time) by the PID control loop. At t=1001 sec, counter Er_new is set to zero to perform counting for the next 1000 seconds. At the end of another 1000 seconds (ie. at t=2000 seconds), Er_new % is calculated again.  
         [0129]     Suppose this time, Er_new % happens to be 25. This means, by changing K from 10 to 11.5, the control became worse. Therefore, it would be better to change gain in the other direction, i.e., decrease the gain rather than increase. Thus, at t=2000 sec, Er_new %=25, Er_old %=60 (previous value of Er_new %), K_new=11.5 and K_old=10 (previous value of K). Applying Eq.(2), a negative “Dir” is obtained. With Er_new % of 25 and Dir=Negative, the fuzzy-logic calculation is performed again to calculate a new gain for the next 1000 seconds. The new value of gain is K_new=7.76 and is used from t=2000 to 3000 seconds by the PID Loop.  
         [0130]     Suppose for the third iteration, i.e., from t=2000 to 3000 seconds, Er_new % comes out to be 95% (which represents tighter control). Performing the same fuzzy-logic operation gives the same value of K_new, and the gain remains unchanged until Er_new % again degrades.  
         [0000]     Exemplary Applications:  
         [0131]     Both pulse width modulated (PWM) Compressors and electronic stepper regulator (ESR) Valves can be used to control evaporator temperature/pressure or evaporator cooling fluid (air or water) temperature. The former controls by modulating the refrigerant flow and the latter restricts the suction side to control the flow. Referring back to  FIG. 18 , the block diagram of the control system for such an actuator working in a refrigeration system  279  is shown. In  FIG. 18  one and preferably up to four temperatures of evaporator cooling fluid or one evaporator suction pressure (generally shown at  282 ) is sampled every dt seconds. A sampling time of dt=10 seconds was found to be optimum for both the applications. After processing by the analog to digital module  284 , the sampled signal is then reduced to one number by taking the average or the minimum or the maximum of the four temperatures depending on the system configuration or the user preference at module  286 . Typically, in a single actuator (PWM/ESR) systems where the complete evaporator coil goes into defrost at one time, averaging of control signal is preferred. In a multiple evaporator-single actuator system where defrost of evaporator coils does not occur at the same time, minimum is the preferred mode. The value obtained after avg/min/max is called conditioned signal. At comparison module  288  this is compared with the desired set point to calculate the error, e(t).  
         [0132]     The control algorithm used in the loop is a Proportion-integral (PI) control technique (PID). The PI algorithm calculates the valve position (0-100%) in case of ESR or calculates the percentage loading (0 to 100%) in case of PWM compressor. A typical integral reset time, Ti, for both the actuators is 60 seconds. The gain is tuned adaptively by the adaptive loop. The adaptive algorithm is turned off in the preferred embodiment whenever: the system is in defrost; is going through pull-down; there a big set point change; sensor failure has been detected; or any other system failure is detected.  
         [0133]     Consequently, the adaptive algorithm is typically used when the system is working under normal mode. The time “ta” preferably used is about 1 seconds and “tsum” is about 1800 seconds (30 minutes).  
         [0000]     Diagnostics Related to PWM Compressor/ESR Valves:  
         [0134]     Referring to  FIG. 22 , a discharge cooling fluid temperature sensor  312  (Ta), an evaporator coil inlet temperature sensor  314  (Ti) and an evaporator coil exit temperature sensor  316  (To) can provide diagnostic features for the evaporator control using PWM/ESR. The Inlet temperature sensor  314  can be anywhere in evaporator coil  318 . However, the preferred location is about one third of the total evaporator length from the evaporator coil distributor  320 .  
         [0135]     Using these three temperature sensors, system learning can be performed that can be used for diagnostics. For example, diagnostics can be performed for ESR/PWM when it is used in a single evaporator along with an expansion valve. In this example, the following variables are tracked every “tsum” second in the adaptive loop. The variables can be integrated just after ER_new integration is done in the adaptive loop. 
        N-Close: Number of times Valve position/PWM loading was 0%.     N-Open: Number of times Valve position/PWM loading was 100%.     MAVP: The moving average of the Valve position/PWM loading for “tsum” seconds.     SSLP: The steady-state Valve position/PWM loading is set equal to MAVP if for the “tsum”     duration ER_new % is greater than 50%.     dT: Moving average of the difference between Ta and Ti (Ta-Ti).     SH: Moving average of the difference between To and Ti (To-Ti) in the said duration. This is approximately the evaporator superheat.     N_FL: Number of times To was less than Ti during the said duration, i.e., “tsum” seconds. This number will indicate how much the expansion valve is flooding the evaporator.        
 
         [0144]     In addition, Pull-down time after defrost, tpd, is also learnt. Based on these variables, the following diagnostics are performed: temperature sensor failure; degraded expansion valve; degraded ESR valve/PWM Compressor; oversized ESR/PWM; undersized ESR/PWM; and no air flow.  
         [0000]     Temperature Sensor Failure:  
         [0145]     Failures of temperature sensors are detected by checking whether the temperature reading falls within the expected range. If PWM/ESR is controlled using Ta as the control variable, then when it fails, the control is done as follows. The above said actuator is controlled based on Ti, or the Ta values are estimated using the learned dT (i.e., add dT to Ti value to estimate Ta). During pull down, the valve/PWM can be set to full-open/load for the learned pull-down time (tpd). If Ti also fails at the same time or is not available, the actuator is opened 100% during pull down time and then set to steady-state loading percent (SSLP) after pull-down-time. An alarm is sent to the supervisor upon such a condition.  
         [0000]     Degraded Expansion Valve:  
         [0146]     If an expansion valve sticks or is off-tuned or is undersized/oversized, the following combinations of the tracked variable can be used to diagnose such problems. N_FL&gt;50% and ER_new %&gt;10% indicate the expansion valve is stuck open or is off-tuned or may be even oversized and thus is flooding the evaporator coil. An alarm is sent upon such a condition. Moreover, SH&gt;20 and N_FL=0% indicate an off-tuned expansion valve or an undersized valve or the valve is stuck closed.  
         [0000]     Degraded ESR Valve/PWM Compressor:  
         [0147]     A degraded ESR is one that misses steps or is stuck. A degraded PWM Compressor is one whose solenoid is stuck closed or stuck open. These problems are detected in a configuration where defrost is performed by setting the ESR/PWM to 0%. The problem is detected as follows.  
         [0148]     If ER_new %&gt;50% before defrost and during defrost Ti&lt;32□F and SH&gt;5□F, then the valve is determined to be missing steps. Accordingly, the valve is closed by another 100% and if Ti and SH remain the same then this is highly indicative that the valve is stuck.  
         [0149]     If ER_new %=0 and N_Close is 100% and Ti&lt;32 F and SH&gt;5 F then PWM/ESR is determined to be stuck open. If ER_new %=0 and N_Open is 100% and Ti&gt;32 F and SH&gt;5 F then PWM/ESR is determined to be stuck closed.  
         [0000]     Over-Sized ESR/PWM:  
         [0150]     If N_Close&gt;90% and 30%&lt;ER_new %&lt;100%, then an alarm is sent for oversized valve/PWM Compressor.  
         [0000]     Under-Sized ESR/PWM:  
         [0151]     If N_Open&gt;90% and ER_new %=0 and SH&gt;5, then an alarm is sent for undersized valve/PWM Compressor.  
         [0000]     No Air Flow:  
         [0152]     If N_Open=100%, ER_new %=0, SH&lt;5 F and Ti&lt;25 F and N_FL&gt;50%, then either the air is blocked or the fans are not working properly.  
         [0153]     Additionally, these diagnostic strategies can also be applied to an electronic expansion valve controller.  
         [0154]     The embodiments which have been set forth above were for the purpose of illustration and were not intended to limit the invention. It will be appreciated by those skilled in the art that various changes and modifications may be made to the embodiments discussed in this specification without departing from the spirit and scope of the invention as defined by the appended claims.  
                         APPENDIX                       Pseudocode for performing signal conditioning                                    Repeat the following every Ts Seconds:           Read User Inputs:            -Sampling Time (Ts)            -Control Type (P or T)            -Sensor Mode (Avg/Min/Max)           Perform Analog to Digital Conversion (ADC)            -on all (four) Temp. Sensor Channels            output data as Counts           Digitally Filter Counts            -Ynew = 0.75 * Yold + 0.25 * Counts            -output data as Filtered Counts           Convert Filtered Counts to Deg F.           Test if at least one Sensor is within normal operating limits            -e.g. within −40 and +90 F.            If none are within limit--Set Sensor Alarm to TRUE            Else Perform Avg/Min/Max operation based on Sensor Mode           If Control Type is NOT a T/P Control Type            Then End Signal Conditioning Routine (until next Ts cycle)            Else (Control Type is T/P) Do the Following:           Perform ADC on Pressure Sensor Channel            -output data as Counts           Digitally Filter Counts            -Ynew = 0.75 * Yold + 0.25 * Counts            -output data as Filtered Counts           Convert Filtered Counts to Psig           Test if pressure Sensor is within normal operating limits            -e.g. within 0 and +200            If not within limit:             Set dP = dP Set Pt.            Else:             Calculate dP = Pmax−Pmin           Set Sensor Alarm to Conditioned T/dP           End Signal Conditioning Routine (until next Ts cycle)