Searched product:
Brand: SIEMENS
Part number: 6ES7155-6AA01-0BN0
Name: Schnittstellenmodul, 32 I/O, 50mm x 74mm x 117mm
Description: 6ES7155-6AA01-0BN0 - Siemens - Schnittstellenmodul, 32 I/O, 50mm x 74mm x 117mm kaufen. Farnell bietet schnelle Angebotserstellungen, Versand am gleichen Werktag, schnelle Lieferung, einen umfangreichen Lagerbestand, Datenblätter und technischen Support.
Category: Automatisierung & Prozesssteuerung
Price: 386.57 EUR
Supplier country: DEU

Found product:
Brand: Siemens AG
Part number: 6ES7155-6AA01-0BN0
Name: Simatic ET 200SP, Bundle ProfiNet IM, IM155-6PN ST, 32 periphery ^16 ET 200AL modules, hot SWAP, cont.: interface module (6ES7155-6AU01-0BN0), server module (6ES7193-6PA00-0AA0), bus adapter BA 2x RJ45 (6ES7193-6AR00-0AA0), SiemensKood: 6ES7155-6AA01-0BN0
Description: Overview Specification Downloadable files Simatic ET 200SP, Bundle ProfiNet IM, IM155-6PN ST, 32 periphery ˄16 ET 200AL modules, hot SWAP, cont.: interface module (6ES7155-6AU01-0BN0), server module (6ES7193-6PA00-0AA0), bus adapter BA 2x RJ45 (6ES7193-6AR00-0AA0), SiemensSIMATIC ET 200SP, PROFINET bundle IM, IM 155-6PN ST, max. 32 I/O modules and 16 ET 200AL modules, single hot swap, bundle consists of: Interface module (6ES7155-6AU01-0BN0), Server module (6ES7193-6PA00-0AA0), BusAdapter BA 2xRJ45 (6ES7193-6AR00-0AA0) General information Product type designation IM 155-6 PN ST HW functional status FS01 Firmware version V4.1 Product function ● I&M data Yes; I&M0 to I&M3 ● Module swapping during operation (hot swapping) Yes; Single hot swapping Engineering with ● STEP 7 TIA Portal configurable/integrated as of version V14 ● STEP 7 configurable/integrated as of version V5.5 SP4 and higher ● PROFINET as of GSD version/GSD revision V2.3 / - Configuration control via dataset Yes Supply voltage Rated value (DC) 24 V permissible range, lower limit (DC) 19.2 V permissible range, upper limit (DC) 28.8 V Reverse polarity protection Yes Short-circuit protection Yes Mains buffering ● Mains/voltage failure stored energy time 10 ms Input current Current consumption (rated value) 450 mA Current consumption, max. 550 mA Inrush current, max. 3.7 A I²t 0.09 A²·s Power Infeed power to the backplane bus 4.5 W Power loss Power loss, typ. 1.9 W Address area Address space per module ● Address space per module, max. 256 byte; per input / output Address space per station ● Address space per station, max. 512 byte; Dependent on configuration Hardware configuration Rack ● Modules per rack, max. 32; + 16 ET 200AL modules Submodules ● Number of submodules per station, max. 256 Interfaces Number of PROFINET interfaces 1; 2 ports (switch) 1. Interface Interface types ● Number of ports 2 ● integrated switch Yes ● RJ 45 (Ethernet) Yes; Pre-assembled BusAdapter BA 2x RJ45 ● BusAdapter (PROFINET) Yes; Applicable BusAdapter: BA 2x RJ45, BA 2x FC Protocols ● PROFINET IO Device Yes ● Open IE communication Yes ● Media redundancy Yes; PROFINET MRP Interface types RJ 45 (Ethernet) ● Transmission procedure PROFINET with 100 Mbit/s full duplex (100BASE-TX) ● 10 Mbps Yes; for Ethernet services ● 100 Mbps Yes; PROFINET with 100 Mbit/s full duplex (100BASE-TX) ● Autonegotiation Yes ● Autocrossing Yes Protocols PROFINET IO Device Services — Isochronous mode No — Open IE communication Yes — IRT Yes; with send cycles of between 250 µs and 4 ms in increments of 125 µs — PROFIenergy Yes — Prioritized startup Yes — Shared device Yes — Number of IO Controllers with shared device, max. 2 Redundancy mode ● MRP Yes ● MRPD No ● PROFINET system redundancy (S2) No Open IE communication ● TCP/IP Yes ● SNMP Yes ● LLDP Yes Isochronous mode Isochronous operation (application synchronized up to terminal) No Interrupts/diagnostics/status information Status indicator Yes Alarms Yes Diagnostics function Yes Diagnostics indication LED ● RUN LED Yes; Green LED ● ERROR LED Yes; Red LED ● MAINT LED Yes; Yellow LED ● Monitoring of the supply voltage (PWR-LED) Yes; Green PWR LED ● Connection to network LINK (green) Yes; 2x green link LEDs on BusAdapter Potential separation between backplane bus and electronics No between PROFINET and all other circuits Yes; 1500 V AC between supply and all other circuits No Permissible potential difference between different circuits Safety extra low voltage SELV Isolation Isolation tested with 707 V DC (type test) Standards, approvals, certificates Network loading class 2 Security level According to Security Level 1 Test Cases V1.1.1 Ambient conditions Ambient temperature during operation ● horizontal installation, min. 0 °C ● horizontal installation, max. 60 °C ● vertical installation, min. 0 °C ● vertical installation, max. 50 °C Connection method ET-Connection ● via BU/BA Send Yes; + 16 ET 200AL modules Dimensions Width 50 mm Height 117 mm Depth 74 mm Weights Weight, approx. 190 g; IM 155-6 PN BA with 2x RJ45 ports and server module last modified: 05/30/2019 File description File type Download link
Price: 353.1 EUR
Supplier country: EST

Same real-world product (1 = yes, 0 = no): 1