Searched product:
Brand: Siemens
Part number: 3RV20111JA10
Name: Siemens 3RV2011-1JA10 Leistungsschalter 1 St. Einstellbereich (Strom): 7 - 10 A Schaltspannung (max.): 690 V/AC (B x H
Description: Leistungsschalter Baugröße S00 für den Motorschutz, CLASS 10 A-Auslöser 7...10 A N-Auslöser 130 A Schraubanschluss Standardschaltvermögen Leistungsschalter SIRIUS 3RV2 für Motorschutz zum sicheren Abschalten bei Kurzschluss und Schutz der Verbraucher und Anlage vor Überlast, sowie zur sicheren Trennung der Anlage vom Netz.<br>Die kompakten und klimafesten Leistungsschalter sind durch ihre geringe Abwärme für den Einsatz in Verbraucherabzweigen optimiert, natürlich auch für IE3/IE4-Motoren und gleichermaßen für das Schalten von Gleichstrom. Weltweite Zulassungen (z.B. IEC und UL/CSA) und Anwendungen in explosionsgefährdeten Applikationen (ATEX bzw. IEC Ex) sind selbstverständlich.<br>Verfügbar sind Gerätevarianten für Motorschutz (auch mit Überlastrelais-Funktion), Anlagenschutz, Kurzschlussschutz von Starterkombinationen, Transformatorschutz, als Haupt- und NOT-AUS-Schalter und für den Einsatz in IT-Netzen. Sie sind mit Schraub- oder Federzuganschluss für einen schnellen, wartungsfreien und rüttelsicheren Anschluss, und wahlweise mit eingebautem Hilfsschalter erhältlich.<br>Das umfassende Zubehör, wie z.B. Hilfsschalter, Hilfsauslöser, Meldeschalter etc. ist einheitlich für alle Baugrößen. Der Einsatz verschiedener Energieeinspeisemöglichkeiten, wie dem zugehörigen Einspeisesystem SIRIUS 3RV29, reduziert die Hauptstromkreisverdrahtung erheblich.<br>Die Leistungsschalter 3RV2 lösen die bewährte Baureihe 3RV1 ab.<br>Einfach, effizient, immer aktuell - der SIRIUS Systembaukasten.
Price: 90.28 EUR
Supplier country: AUT

Found product:
Brand: Sprecher & Schuh
Part number: KTA7-45H-10A-EZ
Name: Sprecher & Schuh KTA7-45H-10A-EZ Explosion Proof Type 4/7/9 Motor Controller
Description: Product Overview UL Approved For A Wide Variety Of Applications Sprecher + Schuh's KT7 series of Motor Circuit Controllers are some of the most versatile and technologically advanced control products available today. These devices can be used in a variety of control schemes that reduce panel space, simplify installation and eliminate the need for more expensive equipment. Features Current-limiting short circuit protection Class 10 thermal overload protection Switching Signaling Variety Of Models... Increased Ratings... Sprecher + Schuh's KT7 controller family offers higher interrupting capacities (KAIC ratings), improved Type 2 Coordination and a midsize frame rated to 45A. In addition, the line includes "high break" 25A and 32A devices which offer greater withstand ratings in a smaller frame size. Designed For Multiple Applications UL rules allow KT7 Motor Circuit Controllers to be used in a wide variety of applications, including: Manual Starter Applications Traditional Group Motor Applications with compliance to the new Tap Conductor Ratings Motor Disconnect Applications Self-Protected Manual Combination Starter Applications (Type E) Individual Combination Starter Applications Multi-motor Starter Combination Applications Construction Type E Listing Improved current limiting and breaking capacity has allowed KT7s to be UL / CSA listed as self-protected (Construction Type E) manual combination motor controllers. This eliminates the need for an upstream fuse or circuit breaker when using the KT7 as a manual motor starter. In addition, KT7s also meet UL requirements for "at-motor disconnects," which means they can be used in an enclosure with a lockable handle as a manual motor starter for individual circuits, and are also an approved means of motor disconnect. Type E + Combo Starter + Economy = "Ecombo" Starter When the KT7 self-protected manual combination starter is combined with Sprecher + Schuh's CA7 contactor to provide remote operation, we now have an alternative to the classic combination starter. We call these "Ecombo" starters, which save significant dollars and panel space over conventional combo starters. Ecombo starters are available for applications up to 30HP (@460/600V). Multi-Motor Applications... Popular And Money Saving Because of KT7's Construction Type E-UL Rating as a self-protected combination starter, many group motor installations can utilize an even simpler design and less expensive equipment. The result is minimum panel size and maximum flexibility while avoiding cumbersome NEC group motor rules. 60mm Bus Bar systems can be utilized to provide a cost effective and flexible multi-starter panel assembly. For design assistance or technical clarification on multi-motor or bus bar systems contact Sprecher & Schuh Technical Support. Excellent Short Circuit Protection Characteristics In the event of a short circuit, the contacts are opened by magnetic, non-adjusting tripping elements in times approaching 3/1000 of a second. This results in the extremely rapid buildup of an arc voltage which limits the current of the short circuit to a very low level. Because of this superb current limiting capability, KTA Motor Circuit Controllers have a short circuit capacity of up to 65kA at 480V and up to 47kA at 600V. Superb Thermal Overload Protection Every KT7 device is individually calibrated at the factory for the smallest and largest current it can handle. When coupled with automatic ambient temperature compensation over a range of -25°C to +60°C, very accurate thermal overload protection is obtained. In addition, the KT7 is a Class 10 device. It trips within 10 seconds under locked rotor conditions (6 x FLA). This better protects today's T-Frame motors. Special Units For Special Applications KTC7 controllers are available with a fixed magnetic trip set at 16...20x the maximum value of the current adjustment range (as opposed to 13x for the KTA and KTB7). This prevents nuisance tripping in applications utilizing high efficiency motors for example. The KTB7 model is available without the thermal trip feature if a separate motor overload is required. Combine KTB7 with a CA7 Contactor and CEP7 Overload Relay to create the CLT7 3-component Ecombo starter. The KTV7 multi-motor controllers are suitable for application at the output of variable frequency drive (VFD) installations. Check out our White Paper on using KT7 controllers with VFDs. Other Protection Features All KT7 Motor Circuit Controllers provide accelerated tripping under single phase conditions. This is accomplished with a special "differential tripping" mechanism built into each device.
Category: Automation & Control
Price: 2010.16 USD
Supplier country: USA

Same real-world product (1 = yes, 0 = no): 0