Searched product:
Brand: SQUARE D
Part number: LC1D12F7
Name: LC1D12F7
Category: SQUARE D
Price: 169.38 USD
Supplier country: USA

Found product:
Brand: Schneider Electric
Part number: LC1D12F7
Name: IEC contactor, TeSys Deca, nonreversing, 12A, 7.5HP at 480VAC, up to 100kA SCCR, 3 phase, 3 NO, 110VAC 50/60Hz coil, open
Description: Description TeSys D contactors have been designed for perfect integration into control systems. They can be used to create motor starters for almost any type of application. TeSys D contactors are available in 13 contactor ratings for inductive motor applications up to 150 full-load amps and resistive loads up to 200 amps. This 12A inductive 3 pole IEC contactor can be mounted on DIN rail or mounted directly to a panel. Contactors have both Horsepower and Kw motor rating for international acceptance. Contactor is rated for 3HP at 200-208VAC, 3HP at 240VAC, 7.5HP at 480VAC and 10HP at 600VAC three phase. Contactor is also rated for 0.5HP at 115VAC and 2HP at 240VAC single phase. When used with a 480VAC up to 35A circuit breaker, this contactor can have a SCCR up to 85kA. When used with up to a 600VAC 30A Class J or CC fuse, this contactor can have a SCCR up to 100kA. Contactor is supplied with a 110 VAC 50/60 Hz coil. Contactor has one normally open and one normally closed auxiliary contact built-in as standard. The NC contact is mirror certified. Screw clamp terminals are used for load and auxiliary connections. An extensive line of accessories makes it easy to meet the requirements of most applications. The contactor is 3.03 inches tall, 1.77 inches wide and 3.39 inches deep. It weighs 0.72 lbs. Contactor is certified to UL, CSA, IEC, CCC, EAC and Marine standards. Contactor also meets the requirements of RoHS/REACh making it a Green Premium product. Manuals and Documentation CAD Technical Drawing Service Manual Specification Sheet Technical Bulletin Specifications Catalog Number LC1D12F7 Manufacturer Schneider Electric Brand Schneider Electric Sub Brand TeSys D;TeSys Deca Warranty Description Contractual Warranty: 18 months Country of Origin Indonesia Made in USA No Application Resistive load;motor control Coil Power Rating 7.5-7.5 VA 60 HZ 0.3 20 A Degrees C)-7-7 VA 50 HZ 0.3 20 A Degrees C) Coil Voltage 110 V AC 50/60 Hz Connection Power circuit screw clamp terminals 1 1-4 mm2flexible without cable end;power circuit screw clamp terminals 2 1-4 mm2flexible without cable end;power circuit screw clamp terminals 1 1-4 mm2flexible with cable end;power circuit screw clamp terminals 2 1-2.5 mm2flexible with cable end;power circuit screw clamp terminals 1 1-4 mm2solid without cable end;power circuit screw clamp terminals 2 1-4 mm2solid without cable end;control circuit screw clamp terminals 1 1-4 mm2flexible without cable end;control circuit screw clamp terminals 2 1-4 mm2flexible without cable end;control circuit screw clamp terminals 1 1-4 mm2flexible with cable end;control circuit screw clamp terminals 2 1-2.5 mm2flexible with cable end;control circuit screw clamp terminals 1 1-4 mm2solid without cable end;control circuit screw clamp terminals 2 1-4 mm2solid without cable end Contact Configuration 1 NO + 1 NC;3 NO;Mechanically linked 1 NO + 1 NC IEC 60947-5-1;mirror contact 1 NC IEC 60947-4-1 Contact Rating 25 A 60 A Degrees C POWER CIRCUIT-10 A 60 A Degrees C SIGNALLING CIRCUIT Mounting Rail Plate Operating Cycles 25...400 Hz Special Features Without built-in suppressor module Standard CCC;BV;CSA;GL;UL;RINA;GOST;LROS (Lloyds register of shipping);DNV;UKCA;CSA C22.2 No 14;EN 60947-4-1;EN 60947-5-1;IEC 60947-4-1;IEC 60947-5-1;UL 508;IEC 60335-1 RoHS URL https://checkaproduct.se.com/DistantRequestDispatcher.aspx?action=export&pid=1471110&lang=en-us UPC 785901207023 Item Type Contactor Size 45 MM,77 MM,86 MM Operating Temperature -40-70 A Degrees C AT UC,-5-60 A Degrees C Wattage 0.36 W AC-3-1.56 W AC-1
Price: 212.95 USD
Supplier country: USA

Same real-world product (1 = yes, 0 = no): 1