Searched product:
Brand:  Siemens
Part number: Siemens Power Supply Sitop 6EP1334-2BA20
Name: Siemens Power Supply Sitop 6EP1334-2BA20
Description: Siemens Power Supply Sitop 6EP1334-2BA20 merupakan perlengkapan untuk kebutuhan industrial. Produk ini yang terbuat dari material berkualitas tinggi. Alat ini berfungsi sebagai pengganti komponen pada mesin. Telah teruji kualitasnya, alat ini aman untuk digunakan. Selain itu, mempunyai bentuk simpel dan tahan lama. Gunakan produk ini dan dapatkan penawaran menarik hanya di Mbiz.co.id.
Category: Aksesoris & Perkakas
Price: 4240300 IDR
Supplier country: IDN

Found product:
Brand: Siemens AG
Part number: 6EP1334-2BA20
Name: Stabilized Power Supply Sitop PSU100S 10A, 120/230VAC, 24VDC 10A, SiemensKood: 6EP1334-2BA20
Description: Overview Specification Downloadable files Stabilized Power Supply Sitop PSU100S 10A, 120/230VAC, 24VDC 10A, SiemensSITOP PSU100S 24 V/10 A SITOP PSU100S 24 V/10 A Stabilized power supply input: 120/230 V AC, output: DC 24 V/10 A Input Input 1-phase AC Supply voltage ● 1 at AC Rated value 120 V ● 2 at AC Rated value 230 V ● Note Automatic range selection Input voltage ● 1 at AC 85 ... 132 V ● 2 at AC 170 ... 264 V Wide-range input No Overvoltage resistance 2.3 × Vin rated, 1.3 ms Mains buffering at Iout rated, min. 20 ms; at Vin = 93/187 V Rated line frequency 1 50 Hz Rated line frequency 2 60 Hz Rated line range 47 ... 63 Hz Input current ● at rated input voltage 120 V 4.49 A ● at rated input voltage 230 V 1.91 A Switch-on current limiting (+25 °C), max. 60 A I²t, max. 5.6 A²·s Built-in incoming fuse T 6.3 A/250 V (not accessible) Protection in the mains power input (IEC 898) Recommended miniature circuit breaker: from 10 A characteristic C Output Output Controlled, isolated DC voltage Rated voltage Vout DC 24 V Total tolerance, static ± 3 % Static mains compensation, approx. 0.1 % Static load balancing, approx. 1 % Residual ripple peak-peak, max. 150 mV Residual ripple peak-peak, typ. 20 mV Spikes peak-peak, max. (bandwidth: 20 MHz) 240 mV Spikes peak-peak, typ. (bandwidth: 20 MHz) 160 mV Adjustment range 22.8 ... 28 V Product function Output voltage adjustable Yes Output voltage setting via potentiometer Status display Green LED for 24 V OK Signaling Relay contact (NO contact, rating 60 V DC/ 0.3 A) for "24 V OK" On/off behavior Overshoot of Vout < 3 % Startup delay, max. 0.3 s Voltage rise, typ. 20 ms Rated current value Iout rated 10 A Current range 0 ... 12 A ● Note 12 A up to +45°C; +60 ... +70 °C: Derating 3%/K Supplied active power typical 288 W Short-term overload current ● on short-circuiting during the start-up typical 32 A ● at short-circuit during operation typical 32 A Duration of overloading capability for excess current ● on short-circuiting during the start-up 1 000 ms ● at short-circuit during operation 1 000 ms Parallel switching for enhanced performance Yes Numbers of parallel switchable units for enhanced performance 2 Efficiency Efficiency at Vout rated, Iout rated, approx. 90 % Power loss at Vout rated, Iout rated, approx. 25 W Closed-loop control Dynamic mains compensation (Vin rated ±15 %), max. 0.3 % Dynamic load smoothing (Iout: 10/90/10 %), Uout ± typ. 3 % Load step setting time 10 to 90%, typ. 1 ms Load step setting time 90 to 10%, typ. 1 ms Protection and monitoring Output overvoltage protection protection against overvoltage in case of internal fault Vout < 33 V Current limitation 12 ... 14.6 A Property of the output Short-circuit proof Yes Short-circuit protection Constant current characteristic Enduring short circuit current RMS value ● typical 14.6 A Overcurrent overload capability in normal operation overload capability 150 % Iout rated up to 5 s/min Overload/short-circuit indicator - Safety Primary/secondary isolation Yes Galvanic isolation Safety extra-low output voltage Uout acc. to EN 60950-1 and EN 50178 Protection class Class I Leakage current ● maximum 3.5 mA ● typical 0.8 mA CE mark Yes UL/cUL (CSA) approval cULus-Listed (UL 508, CSA C22.2 No. 107.1), File E197259; cCSAus (CSA C22.2 No. 60950-1, UL 60950-1) Explosion protection IECEx Ex nA nC IIC T4 Gc; ATEX (EX) II 3G Ex nA nC IIC T4 Gc; cULus Class I Div. 2 (ANSI/ISA-12.12.01-2007, CSA C22.2 No. 213-M1987) Group ABCD, T4; cCSAus (CSA C22.2 No. 213, ANSI/ISA-12.12.01) Class I, Div. 2, Group ABCD, T4 FM approval - CB approval Yes Marine approval BV, DNV GL Degree of protection (EN 60529) IP20 EMC Emitted interference EN 55022 Class B Supply harmonics limitation EN 61000-3-2 Noise immunity EN 61000-6-2 Operating data Ambient temperature ● during operation -25 ... +70 °C — Note with natural convection ● during transport -40 ... +85 °C ● during storage -40 ... +85 °C Humidity class according to EN 60721 Climate class 3K3, no condensation Mechanics Connection technology screw-type terminals Connections ● Supply input L, N, PE: 1 screw terminal each for 0.5 ... 2.5 mm² single-core/finely stranded ● Output +, -: 2 screw terminals each for 0.5 ... 2.5 mm² ● Auxiliary Alarm signals: 2 screw terminals for 0.5 ... 2.5 mm² Connections signaling contact 2 screw terminals for 0.5 ... 2.5 mm² Width of the enclosure 70 mm Height of the enclosure 125 mm Depth of the enclosure 120 mm Required spacing ● top 50 mm ● bottom 50 mm ● left 0 mm ● right 0 mm Weight, approx. 0.8 kg Product feature of the enclosure housing for side-by-side mounting Yes Installation Snaps onto DIN rail EN 60715 35x7.5/15 Electrical accessories Buffer module Mechanical accessories Device identification labe
Price: 203.2 EUR
Supplier country: EST

Same real-world product (1 = yes, 0 = no): 1