Searched product:
Brand: Siemens
Part number: 6ES71346HD010BA1
Name: 6ES71346HD010BA1
Description: ET 200SP, AI 4XU/I 2-WIRE ST PU
Category: Industrial Automation and Controls
Price: 474814 KRW
Supplier country: KOR

Found product:
Brand: Siemens AG
Part number: 6ES7134-6HD01-0BA1
Name: Simatic ET 200SP, Analog Input Module, 4AI U/I 2wire, fits to BU-type A0, A1, color code CC03, module diagnosis, 16bit, acc. ±0.3%, SiemensKood: 6ES7134-6HD01-0BA1
Description: Overview Specification Downloadable files Simatic ET 200SP, Analog Input Module, 4AI U/I 2wire, fits to BU-type A0, A1, color code CC03, module diagnosis, 16bit, acc. ±0.3%, SiemensSIMATIC ET 200SP, ANALOG INPUT MODULE, AI 4XU/I 2-WIRE STANDARD, PACKING UNIT: 1 PIECE, FITS TO BU-TYPE A0, A1, COLOR CODE CC03, MODULE DIAGNOSIS, 16BIT, +/-0,3% General information Product type designation AI 4x U/I 2-wire HW functional status From FS02 Firmware version V2.0 ● FW update possible Yes usable BaseUnits BU type A0, A1 Color code for module-specific color identification plate CC03 Product function ● I&M data Yes; I&M0 to I&M3 ● Measuring range scalable No Engineering with ● STEP 7 TIA Portal configurable/integrated as of version V14 / - ● STEP 7 configurable/integrated as of version V5.6 and higher ● PCS 7 configurable/integrated as of version V8.1 SP1 ● PROFIBUS as of GSD version/GSD revision One GSD file each, Revision 3 and 5 and higher ● PROFINET as of GSD version/GSD revision GSDML V2.3 Operating mode ● Oversampling No ● MSI No CiR – Configuration in RUN Reparameterization possible in RUN Yes Calibration possible in RUN No Supply voltage Rated value (DC) 24 V permissible range, lower limit (DC) 19.2 V permissible range, upper limit (DC) 28.8 V Reverse polarity protection Yes Input current Current consumption, max. 37 mA; without sensor supply Encoder supply 24 V encoder supply ● 24 V Yes ● Short-circuit protection Yes ● Output current, max. 20 mA; max. 50 mA per channel for a duration < 10 s Power loss Power loss, typ. 0.85 W; Without encoder supply voltage Address area Address space per module ● Address space per module, max. 8 byte; + 1 byte for QI information Hardware configuration Automatic encoding ● Mechanical coding element Yes Selection of BaseUnit for connection variants ● 2-wire connection BU type A0, A1 Analog inputs Number of analog inputs 4; Differential inputs permissible input voltage for voltage input (destruction limit), max. 30 V permissible input current for current input (destruction limit), max. 50 mA Cycle time (all channels), min. Sum of the basic conversion times and additional processing times (depending on the parameterization of the active channels) Input ranges (rated values), voltages ● 0 to +10 V Yes; 15 bit ● Input resistance (0 to 10 V) 120 kΩ ● 1 V to 5 V Yes; 15 bit ● Input resistance (1 V to 5 V) 120 kΩ ● -10 V to +10 V Yes; 16 bit incl. sign ● Input resistance (-10 V to +10 V) 120 kΩ ● -5 V to +5 V Yes; 16 bit incl. sign ● Input resistance (-5 V to +5 V) 120 kΩ Input ranges (rated values), currents ● 0 to 20 mA Yes; 15 bit ● Input resistance (0 to 20 mA) 100 Ω; + approx. 0.7 V diode forward voltage ● 4 mA to 20 mA Yes; 15 bit ● Input resistance (4 mA to 20 mA) 100 Ω; + approx. 0.7 V diode forward voltage Cable length ● shielded, max. 1 000 m; 200 m for voltage measurement Analog value generation for the inputs Measurement principle integrating (Sigma-Delta) Integration and conversion time/resolution per channel ● Resolution with overrange (bit including sign), max. 16 bit ● Integration time, parameterizable Yes ● Interference voltage suppression for interference frequency f1 in Hz 16.6 / 50 / 60 Hz ● Conversion time (per channel) 180 / 60 / 50 ms Smoothing of measured values ● Number of smoothing levels 4; None; 4/8/16 times ● parameterizable Yes Encoder Connection of signal encoders ● for voltage measurement Yes ● for current measurement as 2-wire transducer Yes — Burden of 2-wire transmitter, max. 650 Ω ● for current measurement as 4-wire transducer No Errors/accuracies Linearity error (relative to input range), (+/-) 0.01 % Temperature error (relative to input range), (+/-) 0.005 %/K Crosstalk between the inputs, min. 50 dB Repeat accuracy in steady state at 25 °C (relative to input range), (+/-) 0.05 % Operational error limit in overall temperature range ● Voltage, relative to input range, (+/-) 0.5 % ● Current, relative to input range, (+/-) 0.5 % Basic error limit (operational limit at 25 °C) ● Voltage, relative to input range, (+/-) 0.3 % ● Current, relative to input range, (+/-) 0.3 % Interference voltage suppression for f = n x (f1 +/- 1 %), f1 = interference frequency ● Series mode interference (peak value of interference < rated value of input range), min. 70 dB ● Common mode voltage, max. 10 V ● Common mode interference, min. 90 dB Isochronous mode Isochronous operation (application synchronized up to terminal) No Interrupts/diagnostics/status information Diagnostics function Yes Alarms ● Diagnostic alarm Yes ● Limit value alarm No Diagnostic messages ● Monitoring the supply voltage Yes ● Wire-break Yes; at 4 to 20 mA ● Short-circuit Yes; with 1 to 5 V or 2-wire mode: Short-circuit of the encoder supply to ground or of an input to the en
Price: 203.8 EUR
Supplier country: EST

Same real-world product (1 = yes, 0 = no): 1