Searched product:
Brand: Siemens
Part number: 6ES7526-2BF00-0AB0
Name: Siemens 6ES7526-2BF00-0AB0 F-Digitalausgabemodul SIMATIC S7-1500 F-DQ8x 24VDC
Description: SIMATIC S7-1500, F-Digitalausgabemodul, F-DQ 8x 24VDC 2A PPM PROFIsafe 35mm Baubr. bis PL E (ISO 13849-1) , SIL3 (IEC 61508) SIMATIC S7-1500, F-Digitalausgabemodul, F-DQ 8x 24VDC 2A PPM PROFIsafe; 35mm Baubr.; bis PL E (ISO 13849-1) , SIL3 (IEC 61508) Die SIMATIC ET 200MP ist ein modulares, skalierbares und universell einsetzbares Peripheriesystem in IP20 und bietet die gleichen Systemvorteile wie die S7-1500. Sie erlaubt kuerzeste Buszykluszeiten und schnellste Reaktionszeiten auch bei grossen Mengengeruesten. Das dezentrale Peripheriesystem ist besonders einfach zu montieren, zu verdrahten und in Betrieb zu nehmen. Durch den skalierbaren Aufbau koennen Sie die Peripheriestation exakt auf den jeweiligen Bedarf vor Ort ausrichten. Die skalierbare Konfiguration einer ET 200MP - Station wird durch das umfassende Spektrum von Signalbaugruppen gewaehrleistet. Es stehen zahlreiche digitale und analoge Ein- und Ausgabebaugruppen zur Verfuegung, auch in fehlersicherer Ausfuehrung. Dies garantiert die universelle Einsatzmoeglichkeit des Systems.
Category: Installation
Price: 721.85 EUR
Supplier country: DEU

Found product:
Brand: Siemens AG
Part number: 6ES7526-2BF00-0AB0
Name: Simatic S7-1500, F Digital Output Module, F-DQ 8x 24VDC 2A PPM PROFIsafe, W35mm, up to PL E (ISO 13849-1)/ SIL3 (IEC 61508), SiemensKood: 6ES7526-2BF00-0AB0
Description: Overview Specification Downloadable files Simatic S7-1500, F Digital Output Module, F-DQ 8x 24VDC 2A PPM PROFIsafe, W35mm, up to PL E (ISO 13849-1)/ SIL3 (IEC 61508), SiemensSIMATIC S7-1500, F digital output module, F-DQ 8x 24 V DC 2A PPM PROFIsafe; 35 mm width; up to PL E (ISO 13849-1)/ SIL3 (IEC 61508) General information Product type designation F-DQ 8x24VDC/2A PPM Firmware version ● FW update possible Yes Product function ● I&M data Yes; I&M0 to I&M3 Engineering with ● STEP 7 TIA Portal configurable/integrated as of version V13 SP1 with HSP 0086 Operating mode ● DQ Yes Supply voltage Type of supply voltage 24 V DC Rated value (DC) 24 V permissible range, lower limit (DC) 19.2 V permissible range, upper limit (DC) 28.8 V Reverse polarity protection Yes Input current Current consumption (rated value) 110 mA; without load Output voltage Rated value (DC) 24 V Power Power available from the backplane bus 0.8 W Power loss Power loss, typ. 11 W Address area Address space per module ● Address space per module, max. 6 byte Hardware configuration Automatic encoding Yes ● Electronic coding element type F Yes Digital outputs Number of digital outputs 8 Current-sinking Yes Current-sourcing Yes Short-circuit protection Yes Open-circuit detection Yes ● Response threshold, typ. 8 mA Overload protection Yes ● Response threshold, typ. 2.9 A Limitation of inductive shutdown voltage to PM-switching: -24 V + (-47 V), PP-switching: -24 V Switching capacity of the outputs ● with resistive load, max. 2 A ● on lamp load, max. 10 W Load resistance range ● lower limit 12 Ω ● upper limit 2 000 Ω Output voltage ● for signal "1", min. 24 V; L+ (-0.5 V) Output current ● for signal "1" rated value 2 A ● for signal "0" residual current, max. 0.5 mA; Current-sourcing, or current sourcing and sinking switches individually, current sinking: max. 1 mA Switching frequency ● with resistive load, max. 30 Hz ● with inductive load, max. 0.1 Hz ● on lamp load, max. 10 Hz Total current of the outputs ● Current per channel, max. 2 A Total current of the outputs (per module) horizontal installation — up to 40 °C, max. 16 A — up to 60 °C, max. 8 A vertical installation — up to 40 °C, max. 8 A Cable length ● shielded, max. 1 000 m ● unshielded, max. 500 m Interrupts/diagnostics/status information Diagnostics function Yes Substitute values connectable No Alarms ● Diagnostic alarm Yes Diagnostic messages ● Monitoring the supply voltage Yes ● Wire-break Yes ● Short-circuit Yes ● Group error Yes Diagnostics indication LED ● RUN LED Yes; Green LED ● ERROR LED Yes; Red LED ● Monitoring of the supply voltage (PWR-LED) Yes ● Channel status display Yes; Green LED ● for channel diagnostics Yes; Red LED ● for module diagnostics Yes; Red LED Potential separation Potential separation channels ● between the channels No ● between the channels and backplane bus Yes Isolation Isolation tested with 707 V DC (type test) Standards, approvals, certificates Highest safety class achievable in safety mode ● Performance level according to ISO 13849-1 PLe ● SIL acc. to IEC 61508 SIL 3 Probability of failure (for service life of 20 years and repair time of 100 hours) — Low demand mode: PFDavg in accordance with SIL3 < 6.00E-05 — High demand/continuous mode: PFH in accordance with SIL3 < 2.00E-09 1/h Ambient conditions Ambient temperature during operation ● horizontal installation, min. 0 °C ● horizontal installation, max. 60 °C ● vertical installation, min. 0 °C ● vertical installation, max. 40 °C Dimensions Width 35 mm Height 147 mm Depth 129 mm Weights Weight, approx. 300 g last modified: 11/10/2018 File description File type Download link
Price: 1034.9 EUR
Supplier country: EST

Same real-world product (1 = yes, 0 = no): 1