Searched product:
Brand: Rittal
Part number: SK3307700
Name: Kühlmodul 1,5kW 1,5kW Profiltür-Anbau RAL7035 SK3307700
Description: Rittal: Kühlmodul 1,5kW 1,5kW Profiltür-Anbau RAL7035 SK3307700 (SK3307700, 4028177559448) in 'Verteilerschränke / Schaltschrank (Netzwerkschrank' > 'Schrank-Klimagerät (Schaltschrank)': Order best price offe<supplier> for Kühlmodul 1,5kW 1,5kW Profiltür-Anbau RAL7035 SK3307700 direct at <supplier>, the procurement platform for business customers.
Category: Server cabinet systems, Switchgear cabinet: Control cabinet cooling device
Price: 1660.82 EUR
Supplier country: DEU

Found product:
Brand: Rittal
Part number: SK3307740
Name: Rittal SK3307740 SK Modular climate control concept, Blue e cooling module, 1.55/1.55 kW, 400/460 V, 1~, 50/60 Hz
Description: Description: All cooling modules can be combined individually with every section door. Material: Sheet steel Colour: RAL 7035 Protection category IP to IEC 60 529: External circuit IP 34 Internal circuit IP 34 Supply includes: Cooling module prepared for installation in section door Nano-coated condenser Integral electric condensate evaporation Note: A base/plinth with a height of 100 or 200 mm is required for efficient operation Packs of: 1 pc(s). EAN: 4028177559462 Customs tariff number: 84158200 eCl@ss 5.1: 27180702 eCl@ss 7.0: 27180702 ETIM 6.0: EC002510 Total cooling output to DIN EN 14511: L 35 L 35 at 50 Hz: 1.55 kW L 35 L 35 at 60 Hz: 1.55 kW L 35 L 50 at 50 Hz: 0.93 kW L 35 L 50 at 60 Hz: 0.95 kW Air throughput (unimpeded air flow): External circuit: 1100 m³/h Internal circuit: 600 m³/h Rated operating voltage: 400 V, 3~, 50 Hz 460 V, 3~, 60 Hz Temperature control: e-Comfort controller (factory setting +35°C) Temperature range: Operation (environment): +10°C...+55°C Setting range: +20°C...+55°C Refrigerant/cooling medium: Refrigerant: R134a Quantity: 700 g Power consumption Pel: L 35 L 35 at 50 Hz: 0.79 kW L 35 L 35 at 60 Hz: 1 kW L 35 L 50 at 50 Hz: 0.9 kW L 35 L 50 at 60 Hz: 1.1 kW Rated current (max.): At 50 Hz: 2.5 A At 60 Hz: 2.7 A Start-up current max.: At 50 Hz: 8.5 A At 60 Hz: 9.2 A Pre-fuse: Motor circuit-breaker: 6.3 A...10 A A Permissible operating pressure (p. max.): 28 bar Energy efficiency ratio (EER) 50 Hz L35 L35 to DIN EN 14511: 1.9 Weight/pack: 68 kg Note: Includes section door weight Type: SK 3307.740
Category: Electrics
Price: 1829.61 EUR
Supplier country: DEU

Same real-world product (1 = yes, 0 = no): 0