Searched product:
Brand: Rittal
Part number: SK3186930
Name: Rittal SK3186930 SK Blue e+ cooling unit, Wall-mounted, 2 kW, 110-240 V, 1~, 380-480 V, 3~, 50-60 Hz, Sheet steel, WHD: 450x1600x294 mm
Description: Benefits: 75% energy saved due to speed-regulated components and heat pipe technology Suitable for international use due to a unique multi-voltage capability Longer service life of the components inside the enclosure and the cooling unit due to component-friendly cooling Intuitive operation due to touch display and intelligent interfaces Material: Sheet steel Colour: RAL 7035 Protection category IP to IEC 60 529: Internal circuit IP 55 Supply includes: Assembly parts Packs of: 1 pc(s). EAN: 4028177709584 Customs tariff number: 84158200 eCl@ss 5.1: 27180704 eCl@ss 7.0: 27180704 ETIM 6.0: EC000855 Total cooling output to DIN EN 14511: L 35 L 35 at 50 Hz: 2 kW L 35 L 35 at 60 Hz: 2 kW L 35 L 50 at 50 Hz: 1.29 kW L 35 L 50 at 60 Hz: 1.29 kW Air throughput (unimpeded air flow): External circuit: 1250 m³/h Internal circuit: 1250 m³/h Rated operating voltage: 110 V - 240 V, 1~, 50 Hz/60 Hz 380 V - 480 V, 3~, 50 Hz/60 Hz Dimensions: Width: 450 mm Height: 1600 mm Depth: 294 mm Temperature control: e+ controller (factory setting +35°C) Temperature range: Bearing: -40°C...+70°C Operation (environment): -20°C...+60°C Setting range: +20°C...+50°C Refrigerant/cooling medium: Refrigerant: R134a Quantity: 1150 g Power consumption Pel: L 35 L 35 at 50 Hz: 0.57 kW L 35 L 35 at 60 Hz: 0.57 kW L 35 L 50 at 50 Hz: 0.6 kW L 35 L 50 at 60 Hz: 0.6 kW Rated output: 0.73 kW Energy efficiency ratio (EER) 50 Hz L35 L35 to DIN EN 14511: 3.5 8.1 Weight/pack: 55.2 kg Type: SK 3186.930
Category: Electrics
Price: 2755 EUR
Supplier country: DEU

Found product:
Brand: SK 3187930 Rittal SK Blue e+ Air Conditioning Unit
Part number: SK 3187930 Rittal SK Blue e+ Air Conditioning Unit
Name: SK 3187930 Rittal SK Blue e+ Air Conditioning Unit
Price: 0 GBP
Supplier country: GBR

Same real-world product (1 = yes, 0 = no): 0