Searched product:
Brand: Siemens Indus.Sector
Part number: 6ES71354GB010AB0
Name: Siemens Indus.Sector Elektronikmodul F.ET 200S,2AO I 6ES7135-4GB
Description: Siemens Indus.Sector Elektronikmodul F.ET 200S,2AO I 6ES7135-4GB01-0AB0 Versorgungsspannung bei AC 50 Hz 0V, Versorgungsspannung bei AC 60 Hz 0V, Versorgungsspannung bei DC 28,8 ...20,4V, Spannungsart der Versorgungsspannung DC, Ausgang, Strom, Ausgangssignal konfigurierbar, Auflösung der Analogausgänge 14Bit, Anzahl der analogen Eingänge 0, Anzahl der analogen Ausgänge 2, Anzahl der HW-Schnittstellen Industrial Ethernet 0, Anzahl der HW-Schnittstellen PROFINET 0, Anzahl der HW-Schnittstellen seriell RS-232 0, Anzahl der HW-Schnittstellen seriell RS-422 0, Anzahl der HW-Schnittstellen seriell RS-485 0, Anzahl der HW-Schnittstellen seriell TTY 0, Anzahl der HW-Schnittstellen parallel 0, Anzahl der HW-Schnittstellen Wireless 0, Anzahl der HW-Schnittstellen sonstige 0, Systemkomponente, Schutzart (IP) IP20, Ausführung des elektrischen Anschlusses Steckanschluss, Feldbusanschluss über seperaten Buskoppler möglich, Tragschienenmontage möglich, Wand-/Direktmontage möglich, Fronteinbau möglich, Explosionsschutz-Kategorie für Gas ohne, Explosionsschutz-Kategorie für Staub ohne, Breite 15mm, Höhe 81mm, Tiefe 52mm, Anzahl der HW-Schnittstellen USB 0, Durch den Einsatz der F-Elektronikmodule der ET 200S ist es möglich die sicherheitsgerichteten Applikationsanforderungen integriert in der Gesamtautomation zu lösen.Die für den fehlersicheren Betrieb erforderlichen Sicherheitsfunktionen sind in die Baugruppen integriert
Category: SPS-Analoges Ein-/Au…
Price: 200.93 EUR
Supplier country: DEU

Found product:
Brand: Siemens AG
Part number: 6ES7135-4GB01-0AB0
Name: Simatic DP, Electronic Module ET 200S, 2AOI, ±20mA, 13bit+sign, 4..20mA, 13bit cycle time <1ms/ch., LED SF (ground fault), W15mm, SiemensKood: 6ES7135-4GB01-0AB0
Description: Overview Specification Downloadable files Simatic DP, electronic module ET200S, 2AO I, W15mm, ±20mA, 13bit +sign, 4..20mA, 13bit cycle time <1ms/ch., LED SF (ground fault), Siemens Supply voltage Load voltage L+ ● Rated value (DC) 24 V; From power module ● Reverse polarity protection Yes Input current from load voltage L+ (without load), max. 150 mA from backplane bus 3.3 V DC, max. 10 mA Power loss Power loss, max. 2 W Address area Address space per module ● Address space per module, max. 4 byte Analog outputs Number of analog outputs 2 Current output, no-load voltage, max. 18 V Cycle time (all channels) max. 1.5 ms Output ranges, current ● -20 mA to +20 mA Yes ● 4 mA to 20 mA Yes Connection of actuators ● for current output two-wire connection Yes ● for current output four-wire connection No Load impedance (in rated range of output) ● with current outputs, max. 500 Ω ● with current outputs, inductive load, max. 1 mH Destruction limits against externally applied voltages and currents ● Voltages at the outputs towards MANA 15 V; max. 15 V continuous; 75 V for max. 1 s (mark to space ratio 1:20) ● Current, max. 50 mA; DC Cable length ● shielded, max. 200 m Analog value generation for the outputs Integration and conversion time/resolution per channel ● Resolution with overrange (bit including sign), max. 14 bit; 4 to 20 mA: 13 bits, ±20 mA: 14 bits Settling time ● for resistive load 0.1 ms ● for capacitive load 0.5 ms ● for inductive load 0.5 ms Errors/accuracies Output ripple (relative to output range, bandwidth 0 to 50 kHz), (+/-) 0.02 % Linearity error (relative to output range), (+/-) 0.02 % Temperature error (relative to output range), (+/-) 0.01 %/K Crosstalk between the outputs, min. -40 dB Repeat accuracy in steady state at 25 °C (relative to output range), (+/-) 0.05 % Operational error limit in overall temperature range ● Current, relative to output range, (+/-) 0.5 % Basic error limit (operational limit at 25 °C) ● Current, relative to output range, (+/-) 0.3 % Isochronous mode Isochronous operation (application synchronized up to terminal) No Interrupts/diagnostics/status information Substitute values connectable Yes; 0 to 65535 (range of values must be within the rated range) Diagnostic messages ● Diagnostic information readable Yes ● Wire-break Yes ● Group error Yes Diagnostics indication LED ● Group error SF (red) Yes Parameter Remark 7 byte Diagnostics wire break Disable / enable Output type/range deactivated / ±20 mA / 4 to 20 mA Group diagnostics Disable / enable Response to CPU/master STOP Output current and de-energized/substitute a value/keep last value Potential separation Potential separation analog outputs ● between the channels No ● between the channels and backplane bus Yes ● Between the channels and load voltage L+ Yes Permissible potential difference between MANA and M internally (UISO) 75 V DC/60 V AC Isolation Isolation tested with 500 V DC Dimensions Width 15 mm Height 81 mm Depth 52 mm Weights Weight, approx. 40 g last modified: 11/21/2017 File description File type Download link " 6ES7135-4GB01-0AB0 datasheet PDF Download link
Price: 230.78 EUR
Supplier country: EST

Same real-world product (1 = yes, 0 = no): 1