Searched product:
Brand: Eaton PowerWare
Part number: 278800
Name: EATON FAZ-K25/2 Leitungsschutz-Schalter K-Char 25A, 2p (278800)
Description: EATON FAZ-K25/2 Leitungsschutz-Schalter K-Char 25A, 2p (278800)
Category: Divers
Price: 94.2 EUR
Supplier country: DEU

Found product:
Brand: Eaton
Part number: 278808 & FAZ-S4/2
Name: 2 POLE TYPE S CIRCUIT BREAKER,10KA 4A
Description: Technical Reference docPdf Catalogue docPdf Catalogue docPdf FAZ-S4-2-5325146 Datasheet Legislation and Compliance RoHS Status: Not Applicable Statement of Conformity RS Components Statement of Conformity This statement confirms that the product detailed below complies with the specifications currently published in the RS media and has been subject to the strict quality conditions imposed by RS Components’ internal management systems. Furthermore and where applicable, it confirms that all relevant semiconductor devices have been handled and packed under conditions that meet the administrative and technical requirements of ANSI/ESD S20.20 and EN61340-5-1 electrostatics control standards. Compliant Product Details RS stock number 5325146 Product description 2 POLE TYPE S CIRCUIT BREAKER,10KA 4A Manufacturer / Brand Eaton Manufacturer part number 278808 & FAZ-S4/2 The foregoing information relates to product sold on, or after, the date shown below. RS COMPONENTS Date Mar 6, 2022 RS Components Pte Ltd Robinson Road, P.O. Box 1582, Singapore 903132 Print this statement Product Details Residual current devicesEaton Miniature Circuit Breakers (MCBs) - FAZ SeriesThe FAZ series of miniature circuit breakers (MCBs) from Eatons xEffect range has a current limiting design providing fast short-circuit interruption that reduces the let-through electrical energy and overload currents that can damage the circuit.Ideally suited to control circuits and electrical distribution boards the FAZ series of MCBs offer a wide range of diverse protection characteristics, protecting your electrical equipment against overload damage. For additional safety, the MCB breaker cannot be defeated by holding the handle in the ON position, these MCBs are also finger proof and have a trip-free mechanism.These MCBs have both a thermal and electromagnetic release, with rated currents of 0.16 A up to 63 A and a switching capacity of 15kA or 10kA depending on the device type. The FAZ series includes miniature circuit breakers, interlocks, busbars and snap-on accessories including auxiliaries and tripping modules.Features and Benefits• Thermal-magnetic overcurrent protection• Power to the miniature circuit breakers can be fed from the line or load side• Clear indication of contact position via front switch toggle• Easy installation on DIN rail. MCB module width of only 17.5 mm (per pole)• Six levels of short-circuit protection, categorized by Type B, C, D, K, S and Z curves• Small modular width of the device and accessories saves space in the panel or equipment, which can lead to cost savings• Available in single pole up to 4 pole• Dual rating for IEC 60947-2 standard• MCB Module widths: 1P 17.5mm, 2P 35mm and 3P 52.5mmStandardsIEC 898; BS/EN60-898; EN50 022/DIN46277-3 (BS5584).FAZ-C*/* & FAZ-S*/* = IEC/EN60947-2IEC 60947-2 Relates to Low Voltage Circuit Breakers for use in industrial and similar installations. In the UK these are traditionally known as miniature circuit breakers (MCBs), moulded case circuit breakers(MCCBs) and also air circuit breakers (ACBs).What are the differences between the Tripping Curves?Type B: Instantaneous trip when the electrical current through the device is 3 to 5 times the rated current. The type B trip curve MCBs are designed for standard circuit protection, typically protection of generators, persons and very long cablesType C: Instantaneous trip when the flow-through current is 5 to 10 times the rated current. Type C trip curve residential and domestic MCBs are used for higher inrush currents such as in machines and lighting, providing overload protection of circuits and other consumer units.Type D: Instantaneous trip when the flow-through current is 10 to 14 times the rated current.D curve MCBs are suitable for inductive and capacitive loads like transformers condensers. and electric motors.Type K: Instantaneous trip when the flow-through current is 10 to 14 times the rated current.Type K curve MCBs are suitable for inductive loads like transformers, condensers. and electric motors.Type S: Instantaneous trip when the flow-through current is 13 to 17 times the rated current.Suitable for applications where high levels of inrush current are expected. The high magnetic trip point of type S curve MCBs prevents nuisance tripping in high inductive applications such as motors, transformers and power supplies.Type Z: Instantaneous trip when the flow-through current is 2 to 3 times the rated current.Z curve MCBs are intended for use in electrical circuits that require a very low short circuit trip setting, for example, semiconductors. Specifications Attribute Value Brand Eaton Series FAZ Depth 73.5 mm Breaking Capacity at Maximum Voltage Rating 10 kA Width 35 mm Current Rating 4 A Tripping Characteristics Type S Length 80 mm Number of Poles 2 Range xEffect Rated AC Voltage 230 V
Category: Circuit Protection & Circuit Breakers
Price: 1260358.24 IDR
Supplier country: IDN

Same real-world product (1 = yes, 0 = no): 0