Searched product:
Brand: Eaton
Part number: 010224
Name: Eaton 11DILE Hilfsschalterbaustein , 010224
Description: Technische Details Eigenschaft Wert Anzahl der Kontakte als Schließer: 1 Anzahl der Kontakte als Öffner: 1 Montageart: Frontbefestigung Ausführung des elektrischen Anschlusses: Schraubanschluss Ausführung: aufsteckbar Bemessungsbetriebsstrom Ie bei AC-15, 230 V: 4 A Fassung: ohne
Category: Installation
Price: 5.99 EUR
Supplier country: DEU

Found product:
Brand: Midel 7131 - 1.000kg IBC Container- High-End Transformer Fluid
Part number: Midel 7131 - 1.000kg IBC Container- High-End Transformer Fluid
Name: Midel 7131 - 1.000kg IBC Container- High-End Transformer Fluid
Description: MIDEL® 7131 Dielectric Insulating Fluid Overview MIDEL 7131 Product Overview MIDEL 7131 is a synthetic ester-based dielectric fluid that has been serving the global transformer market for over 30 years. MIDEL 7131 has been specifically formulated to provide a safe, superior alternative to traditional fluid and dry-type transformers and can be used in indoor or outdoor locations. MIDEL 7131 is a high performance fluid that offers increased fire safety, greater environmental protection and superior moisture tolerance. Testing has also proven that MIDEL 7131 has excellent dielectric properties. IEC 61099 Conformity MIDEL 7131 conforms to IEC 61099 “Specifications for Unused Synthetic Organic Esters for Electrical Purposes”. It is classified as type T1, a halogen-free pentaerythritol ester. Areas of Application MIDEL 7131 filled transformers are available from all major transformer manufacturers. MIDEL 7131 is suitable for a wide range of transformer applications, including sealed and breathing.  Distribution transformers  Power transformers  Traction transformers  Rectifier transformers  Pole-type transformers  Tapchangers  Thyristor cooling Retrofilling MIDEL 7131 has been used to retrofill thousands of distribution transformers to improve service life, reduce environmental hazards or increase fire safety. Corrosive Sulphur MIDEL 7131 has been tested by independent laboratories to ASTM D1275 B and IEC 62535, it was found to be non-corrosive. Increased Fire Safety MIDEL 7131 has a high fire point and a low net calorific value (<32 MJ/kg) and is therefore classified as a K3 class liquid.  100% fire safety record  High fire point (>300°C)  K-class to IEC 61100 / 61039  FM Global® approved transformer fluid  Reduced fire safeguarding costs Greater Environmental Protection MIDEL 7131 is an environmentally friendly alternative to conventional transformer fluids because it is classified as readily biodegradable and non-water hazardous.  Readily biodegradable (OECD 301)  Fully biodegradable (IEC 61039)  Classified as non-water hazardous by (UBA)  Non-toxic  Will not evaporate into the environment  Not detrimental to activated sludge in biological treatment plants  RoHS compliant High Performance MIDEL 7131 is an extremely robust fluid that delivers long-term stability even when exposed to extreme temperature variations. MIDEL 7131 also has excellent oxygen stability allowing it to be used in breathing transformers.  Robust and stable at high temperatures over long periods  Suitable for compact transformer design  Superior oxygen stability  Excellent lubricant  No sludge formation Moisture Tolerance MIDEL 7131 is moisture tolerant and can absorb far more water than alternative fluids, without compromising the breakdown voltage.  No reduction of breakdown voltage (up to 600ppm / 20°C)  Allows moisture to migrate from cellulose into the fluid  Potentially keeps the cellulose drier and slows the rate of ageing  Very high saturation limit making condensation virtually impossible  Reduced risk of bubble formation Delivery MIDEL 7131 can be delivered in 24.5kg, 195kg or 1000kg sealed containers; bulk tanker deliveries available for >20 tonnes. Disposal For disposal, it is recommended that used MIDEL 7131 or remains of the insulating
Price: 0 EUR
Supplier country: DEU

Same real-world product (1 = yes, 0 = no): 0