Searched product:
Brand: Siemens Indus.Sector
Part number: 6ES71356HD000BA1
Name: Siemens Indus.Sector Ausgangsmodul 4XU/I 6ES7135-6HD00-0BA1
Description: Siemens Indus.Sector Ausgangsmodul 4XU/I 6ES7135-6HD00-0BA1 Versorgungsspannung bei AC 50 Hz 0V, Versorgungsspannung bei AC 60 Hz 0V, Versorgungsspannung bei DC 24 ...24V, Spannungsart der Versorgungsspannung DC, Ausgang, Strom, Ausgang, Spannung, Auflösung der Analogausgänge 16Bit, Anzahl der analogen Eingänge 0, Anzahl der analogen Ausgänge 4, Anzahl der HW-Schnittstellen Industrial Ethernet 0, Anzahl der HW-Schnittstellen PROFINET 0, Anzahl der HW-Schnittstellen seriell RS-232 0, Anzahl der HW-Schnittstellen seriell RS-422 0, Anzahl der HW-Schnittstellen seriell RS-485 0, Anzahl der HW-Schnittstellen seriell TTY 0, Anzahl der HW-Schnittstellen parallel 0, Anzahl der HW-Schnittstellen Wireless 0, Anzahl der HW-Schnittstellen sonstige 0, Ausführung des elektrischen Anschlusses sonstige, Wand-/Direktmontage möglich, Fronteinbau möglich, Explosionsschutz-Kategorie für Gas ohne, Explosionsschutz-Kategorie für Staub ohne, Breite 15mm, Anzahl der HW-Schnittstellen USB 0, Analoge Elektronikmodule enthalten analoge Ein- und Ausgänge für die ET 200S.Sie werden immer auf ein Terminalmodul TM-E gesteckt.High Feature-Varianten für Analogwertverarbeitung mit erhöhter Performance, Genauigkeit und Auflösung.High Speed-Varianten für Analogwertverarbeitung mit extrem kurzen, taktsynchronen, Zykluszeit
Category: SPS-Analoges Ein-/Au…
Price: 217.37 EUR
Supplier country: DEU

Found product:
Brand: Siemens AG
Part number: 6ES7135-6HD00-0BA1
Name: Simatic ET 200SP, Analog Output Module, AQ 4XU/I, for BU type A0, A1, color code CC00, module diagnostics, 16bit, acc. ±0.3%, SiemensKood: 6ES7135-6HD00-0BA1
Description: Overview Specification Downloadable files Simatic ET 200SP, Analog Output Module, AQ 4XU/I, for BU type A0, A1, color code CC00, module diagnostics, 16bit, acc. ±0.3%, SiemensSIMATIC ET 200SP, Analog output module, AQ 4XU/I Standard, suitable for BU type A0, A1, Color code CC00, Module diagnostics, 16 bit, +/-0.3% General information Product type designation AQ 4xU/I ST HW functional status From FS07 usable BaseUnits BU type A0, A1 Color code for module-specific color identification plate CC00 Product function ● I&M data Yes; I&M0 to I&M3 ● Output range scalable No Engineering with ● STEP 7 TIA Portal configurable/integrated as of version V11 SP2 / V13 ● STEP 7 configurable/integrated as of version V5.5 SP3 / - ● PCS 7 configurable/integrated as of version V8.1 SP1 ● PROFIBUS as of GSD version/GSD revision One GSD file each, Revision 3 and 5 and higher ● PROFINET as of GSD version/GSD revision GSDML V2.3 Operating mode ● Oversampling No ● MSO No CiR – Configuration in RUN Reparameterization possible in RUN Yes Calibration possible in RUN No Supply voltage Rated value (DC) 24 V permissible range, lower limit (DC) 19.2 V permissible range, upper limit (DC) 28.8 V Reverse polarity protection Yes Input current Current consumption, max. 150 mA Power loss Power loss, typ. 1.5 W Address area Address space per module ● Address space per module, max. 8 byte; + 1 byte for QI information Analog outputs Number of analog outputs 4 Voltage output, short-circuit current, max. 45 mA Cycle time (all channels), min. 5 ms Analog output with oversampling No Output ranges, voltage ● 0 to 10 V Yes; 15 bit ● 1 V to 5 V Yes; 13 bit ● -5 V to +5 V Yes; 15 bit incl. sign ● -10 V to +10 V Yes; 16 bit incl. sign Output ranges, current ● 0 to 20 mA Yes; 15 bit ● -20 mA to +20 mA Yes; 16 bit incl. sign ● 4 mA to 20 mA Yes; 14 bit Connection of actuators ● for voltage output two-wire connection Yes ● for voltage output four-wire connection Yes ● for current output two-wire connection Yes Load impedance (in rated range of output) ● with voltage outputs, min. 2 kΩ ● with voltage outputs, capacitive load, max. 1 µF ● with current outputs, max. 500 Ω ● with current outputs, inductive load, max. 1 mH Destruction limits against externally applied voltages and currents ● Voltages at the outputs 30 V Cable length ● shielded, max. 1 000 m; 200 m for voltage output Analog value generation for the outputs Integration and conversion time/resolution per channel ● Resolution with overrange (bit including sign), max. 16 bit Settling time ● for resistive load 0.1 ms ● for capacitive load 1 ms ● for inductive load 0.5 ms Errors/accuracies Linearity error (relative to output range), (+/-) 0.03 % Temperature error (relative to output range), (+/-) 0.005 %/K Crosstalk between the outputs, min. -50 dB Repeat accuracy in steady state at 25 °C (relative to output range), (+/-) 0.05 % Operational error limit in overall temperature range ● Voltage, relative to output range, (+/-) 0.5 % ● Current, relative to output range, (+/-) 0.5 % Basic error limit (operational limit at 25 °C) ● Voltage, relative to output range, (+/-) 0.3 % ● Current, relative to output range, (+/-) 0.3 % Isochronous mode Isochronous operation (application synchronized up to terminal) No Interrupts/diagnostics/status information Diagnostics function Yes Substitute values connectable Yes Alarms ● Diagnostic alarm Yes Diagnostic messages ● Monitoring the supply voltage Yes ● Wire-break Yes ● Short-circuit Yes ● Group error Yes ● Overflow/underflow Yes Diagnostics indication LED ● Monitoring of the supply voltage (PWR-LED) Yes; Green PWR LED ● Channel status display Yes; Green LED ● for channel diagnostics No ● for module diagnostics Yes; green/red DIAG LED Potential separation Potential separation channels ● between the channels No ● between the channels and backplane bus Yes ● between the channels and the power supply of the electronics Yes Isolation Isolation tested with 707 V DC (type test) Ambient conditions Ambient temperature during operation ● horizontal installation, min. -30 °C ● horizontal installation, max. 60 °C; Observe derating ● vertical installation, min. -30 °C ● vertical installation, max. 50 °C; Observe derating Altitude during operation relating to sea level ● Installation altitude above sea level, max. 2 000 m; On request: Installation altitudes greater than 2 000 m Dimensions Width 15 mm Height 73 mm Depth 58 mm Weights Weight, approx. 31 g last modified: 05/30/2019 File description File type Download link
Price: 269.14 EUR
Supplier country: EST

Same real-world product (1 = yes, 0 = no): 1