Searched product:
Brand: SIEMENS
Part number: 6ES7513-1AL02-0AB0.
Name: Prozessormodul, 300kB, 24V DC, 20 Digitaleingänge, 20 Digitalausgänge Neu
Description: 6ES7513-1AL02-0AB0. - Siemens - Prozessormodul, 300kB, 24V DC, 20 Digitaleingänge, 20 Digitalausgänge kaufen. Farnell bietet schnelle Angebotserstellungen, Versand am gleichen Werktag, schnelle Lieferung, einen umfangreichen Lagerbestand, Datenblätter und technischen Support.
Category: Automatisierung & Prozesssteuerung
Price: 1938.9 CHF
Supplier country: CHE

Found product:
Brand: Siemens AG
Part number: 6ES7513-1AL02-0AB0
Name: Simatic S7-1500, CPU 1513-1 PN, CPU w. working memory| 300kB progr. ^1.5MB data, 1. interface: ProfiNet IRT w. 2port switch, 40ns bit-performance, Simatic memory card necessary, SiemensKood: 6ES7513-1AL02-0AB0
Description: Overview Specification Downloadable files Simatic S7-1500, CPU 1513-1 PN, CPU w. working memory| 300kB progr. ˄1.5MB data, 1. interface: ProfiNet IRT w. 2port switch, 40ns bit-performance, Simatic memory card necessary, SiemensSIMATIC S7-1500, CPU 1513-1 PN, central processing unit with working memory 300 KB for program and 1.5 MB for data, 1. interface: PROFINET IRT with 2 port switch, 40 NS bit-performance, SIMATIC memory card necessary General information Product type designation CPU 1513-1 PN HW functional status FS01 Firmware version V2.6 Product function ● I&M data Yes; I&M0 to I&M3 Engineering with ● STEP 7 TIA Portal configurable/integrated as of version V15.1 (FW V2.6) / V15 (FW V2.5) or higher; with older TIA Portal versions configurable as 6ES7513-1AL01-0AB0 Configuration control via dataset Yes Display Screen diagonal [cm] 3.45 cm Control elements Number of keys 8 Mode buttons 2 Supply voltage Type of supply voltage 24 V DC permissible range, lower limit (DC) 19.2 V permissible range, upper limit (DC) 28.8 V Reverse polarity protection Yes Mains buffering ● Mains/voltage failure stored energy time 5 ms ● Repeat rate, min. 1/s Input current Current consumption (rated value) 0.7 A Current consumption, max. 0.95 A Inrush current, max. 1.9 A; Rated value I²t 0.02 A²·s Power Infeed power to the backplane bus 10 W Power consumption from the backplane bus (balanced) 5.5 W Power loss Power loss, typ. 5.7 W Memory Number of slots for SIMATIC memory card 1 SIMATIC memory card required Yes Work memory ● integrated (for program) 300 kbyte ● integrated (for data) 1.5 Mbyte Load memory ● Plug-in (SIMATIC Memory Card), max. 32 Gbyte Backup ● maintenance-free Yes CPU processing times for bit operations, typ. 40 ns for word operations, typ. 48 ns for fixed point arithmetic, typ. 64 ns for floating point arithmetic, typ. 256 ns CPU-blocks Number of elements (total) 2 000; Blocks (OB, FB, FC, DB) and UDTs DB ● Number range 1 ... 60 999; subdivided into: number range that can be used by the user: 1 ... 59 999, and number range of DBs created via SFC 86: 60 000 ... 60 999 ● Size, max. 1.5 Mbyte; For DBs with absolute addressing, the max. size is 64 KB FB ● Number range 0 ... 65 535 ● Size, max. 300 kbyte FC ● Number range 0 ... 65 535 ● Size, max. 300 kbyte OB ● Size, max. 300 kbyte ● Number of free cycle OBs 100 ● Number of time alarm OBs 20 ● Number of delay alarm OBs 20 ● Number of cyclic interrupt OBs 20; With minimum OB 3x cycle of 500 µs ● Number of process alarm OBs 50 ● Number of DPV1 alarm OBs 3 ● Number of isochronous mode OBs 2 ● Number of technology synchronous alarm OBs 2 ● Number of startup OBs 100 ● Number of asynchronous error OBs 4 ● Number of synchronous error OBs 2 ● Number of diagnostic alarm OBs 1 Nesting depth ● per priority class 24 Counters, timers and their retentivity S7 counter ● Number 2 048 Retentivity — adjustable Yes IEC counter ● Number Any (only limited by the main memory) Retentivity — adjustable Yes S7 times ● Number 2 048 Retentivity — adjustable Yes IEC timer ● Number Any (only limited by the main memory) Retentivity — adjustable Yes Data areas and their retentivity Retentive data area (incl. timers, counters, flags), max. 128 kbyte; In total; available retentive memory for bit memories, timers, counters, DBs, and technology data (axes): 88 KB Extended retentive data area (incl. timers, counters, flags), max. 1.5 Mbyte; When using PS 6 0W 24/48/60 V DC HF Flag ● Number, max. 16 kbyte ● Number of clock memories 8; 8 clock memory bit, grouped into one clock memory byte Data blocks ● Retentivity adjustable Yes ● Retentivity preset No Local data ● per priority class, max. 64 kbyte; max. 16 KB per block Address area Number of IO modules 2 048; max. number of modules / submodules I/O address area ● Inputs 32 kbyte; All inputs are in the process image ● Outputs 32 kbyte; All outputs are in the process image per integrated IO subsystem — Inputs (volume) 8 kbyte — Outputs (volume) 8 kbyte per CM/CP — Inputs (volume) 8 kbyte — Outputs (volume) 8 kbyte Subprocess images ● Number of subprocess images, max. 32 Hardware configuration Number of distributed IO systems 32; A distributed I/O system is characterized not only by the integration of distributed I/O via PROFINET or PROFIBUS communication modules, but also by the connection of I/O via AS-i master modules or links (e.g. IE/PB-Link) Number of DP masters ● Via CM 6; A maximum of 6 CMs (PROFINET + PROFIBUS) can be inserted in total Number of IO Controllers ● integrated 1 ● Via CM 6; A maximum of 6 CMs (PROFINET + PROFIBUS) can be inserted in total Rack ● Modules per rack, max. 32; CPU + 31 modules ● Number of lines, max. 1 PtP CM ● Number of PtP CMs the number of connectab
Price: 2021.2 EUR
Supplier country: EST

Same real-world product (1 = yes, 0 = no): 1