Searched product:
Brand: 6ES7531-7KF00-0AB0 SIMATIC S7-1500
Part number: 6ES7531-7KF00-0AB0 SIMATIC S7-1500
Name: 6ES7531-7KF00-0AB0 SIMATIC S7-1500
Description: Spesifikasi ProdukStok100Dikirim DariKOTA TANGERANG SELATAN - SERPONG, BANTEN, IDDeskripsi ProdukSIMATIC S7-1500, analog input module AI 8xU/I/RTD/TC ST, 16 bit resolution, accuracy 0.3%, 8 channels in groups of 8, 4 channels for RTD measurement, common mode voltage 10 V; Diagnostics, hardware interrupts Incl. infeed element, shield bracket and shield terminal: Front connector (screw terminals or push-in) to be ordered separately
Price: 12643000 IDR
Supplier country: IDN

Found product:
Brand: Siemens AG
Part number: 6ES7531-7KF00-0AB0
Name: Simatic S7-1500, Analog Input Module, AI 8x U/I/RTD/TC ST, 16bit, acc. 0.3%, 8-ch., 4-ch. for RTD measurement, common mode voltage 10V, diag., hardware interrupts incl. infeed element, SiemensKood: 6ES7531-7KF00-0AB0
Description: Overview Specification Downloadable files Simatic S7-1500, Analog Input Module AI8x U/I/RTD/TC, 16bits of res., acc. 0.3%, 8-ch. groups of 8, 4-ch. For RTD measuring, common mode voltage appr. 10V, diagnostics, process alarms incl. infeed element, shield clamp ?terminal, Siemens General information Product type designation AI 8xU/I/RTD/TC ST HW functional status FS01 Firmware version V2.0.0 ● FW update possible Yes Product function ● I&M data Yes; I&M0 to I&M3 ● Measuring range scalable No ● Scalable measured values No ● Adjustment of measuring range No Engineering with ● STEP 7 TIA Portal configurable/integrated as of version V12 / V12 ● STEP 7 configurable/integrated as of version V5.5 SP3 / - ● PROFIBUS as of GSD version/GSD revision V1.0 / V5.1 ● PROFINET as of GSD version/GSD revision V2.3 / - Operating mode ● Oversampling No ● MSI Yes CiR – Configuration in RUN Reparameterization possible in RUN Yes Calibration possible in RUN Yes Supply voltage Rated value (DC) 24 V permissible range, lower limit (DC) 20.4 V permissible range, upper limit (DC) 28.8 V Reverse polarity protection Yes Input current Current consumption, max. 240 mA; with 24 V DC supply Encoder supply 24 V encoder supply ● Short-circuit protection Yes ● Output current, max. 20 mA; Max. 47 mA per channel for a duration < 10 s Power Power available from the backplane bus 0.7 W Power loss Power loss, typ. 2.7 W Analog inputs Number of analog inputs 8 ● For current measurement 8 ● For voltage measurement 8 ● For resistance/resistance thermometer measurement 4 ● For thermocouple measurement 8 permissible input voltage for voltage input (destruction limit), max. 28.8 V permissible input current for current input (destruction limit), max. 40 mA Technical unit for temperature measurement adjustable Yes; °C/°F/K Input ranges (rated values), voltages ● 0 to +5 V No ● 0 to +10 V No ● 1 V to 5 V Yes ● Input resistance (1 V to 5 V) 100 kΩ ● -1 V to +1 V Yes ● Input resistance (-1 V to +1 V) 10 MΩ ● -10 V to +10 V Yes ● Input resistance (-10 V to +10 V) 100 kΩ ● -2.5 V to +2.5 V Yes ● Input resistance (-2.5 V to +2.5 V) 10 MΩ ● -25 mV to +25 mV No ● -250 mV to +250 mV Yes ● Input resistance (-250 mV to +250 mV) 10 MΩ ● -5 V to +5 V Yes ● Input resistance (-5 V to +5 V) 100 kΩ ● -50 mV to +50 mV Yes ● Input resistance (-50 mV to +50 mV) 10 MΩ ● -500 mV to +500 mV Yes ● Input resistance (-500 mV to +500 mV) 10 MΩ ● -80 mV to +80 mV Yes ● Input resistance (-80 mV to +80 mV) 10 MΩ Input ranges (rated values), currents ● 0 to 20 mA Yes ● Input resistance (0 to 20 mA) 25 Ω; Plus approx. 42 ohms for overvoltage protection by PTC ● -20 mA to +20 mA Yes ● Input resistance (-20 mA to +20 mA) 25 Ω; Plus approx. 42 ohms for overvoltage protection by PTC ● 4 mA to 20 mA Yes ● Input resistance (4 mA to 20 mA) 25 Ω; Plus approx. 42 ohms for overvoltage protection by PTC Input ranges (rated values), thermocouples ● Type B Yes ● Input resistance (Type B) 10 MΩ ● Type C No ● Type E Yes ● Input resistance (Type E) 10 MΩ ● Type J Yes ● Input resistance (type J) 10 MΩ ● Type K Yes ● Input resistance (Type K) 10 MΩ ● Type L No ● Type N Yes ● Input resistance (Type N) 10 MΩ ● Type R Yes ● Input resistance (Type R) 10 MΩ ● Type S Yes ● Input resistance (Type S) 10 MΩ ● Type T Yes ● Input resistance (Type T) 10 MΩ ● Type TXK/TXK(L) to GOST No Input ranges (rated values), resistance thermometer ● Cu 10 No ● Cu 10 according to GOST No ● Cu 50 No ● Cu 50 according to GOST No ● Cu 100 No ● Cu 100 according to GOST No ● Ni 10 No ● Ni 10 according to GOST No ● Ni 100 Yes; Standard/climate ● Input resistance (Ni 100) 10 MΩ ● Ni 100 according to GOST No ● Ni 1000 Yes; Standard/climate ● Input resistance (Ni 1000) 10 MΩ ● Ni 1000 according to GOST No ● LG-Ni 1000 Yes; Standard/climate ● Input resistance (LG-Ni 1000) 10 MΩ ● Ni 120 No ● Ni 120 according to GOST No ● Ni 200 according to GOST No ● Ni 500 No ● Ni 500 according to GOST No ● Pt 10 No ● Pt 10 according to GOST No ● Pt 50 No ● Pt 50 according to GOST No ● Pt 100 Yes; Standard/climate ● Input resistance (Pt 100) 10 MΩ ● Pt 100 according to GOST No ● Pt 1000 Yes; Standard/climate ● Input resistance (Pt 1000) 10 MΩ ● Pt 1000 according to GOST No ● Pt 200 Yes; Standard/climate ● Input resistance (Pt 200) 10 MΩ ● Pt 200 according to GOST No ● Pt 500 Yes; Standard/climate ● Input resistance (Pt 500) 10 MΩ ● Pt 500 according to GOST No Input ranges (rated values), resistors ● 0 to 150 ohms Yes ● Input resistance (0 to 150 ohms) 10 MΩ ● 0 to 300 ohms Yes ● Input resistance (0 to 300 ohms) 10 MΩ ● 0 to 600 ohms Yes ● Input resistance (0 to 600 ohms) 10 MΩ ● 0 to 3000 ohms No ● 0 to 6000 ohms Yes ● Input resistance (0 to 6000 ohms) 10 MΩ ●
Price: 763.8 EUR
Supplier country: EST

Same real-world product (1 = yes, 0 = no): 1