Searched product:
Brand: 6EP1333-2BA20 Блок питания импульсный; 144Вт, 24ВDC, Siemens 7 500,00 ₽
Part number: 6EP1333-2BA20 Блок питания импульсный; 144Вт, 24ВDC, Siemens 7 500,00 ₽
Name: 6EP1333-2BA20 Блок питания импульсный; 144Вт, 24ВDC, Siemens
Description: Описание товара85÷132/170÷264ВAC, выход номинал 24в, регулировка 22-28вУсловия оплаты и доставки ↓ Варианты оплаты: – Безналичный расчёт– Оплата наличными– Банковская картаукажите свою почту обязательноСпособы доставки: – Самовывоз– Доставка почтой– Транспортная компания– Доставка курьеромукажите свою почту обязательно Информация о технических характеристиках, комплекте поставки, стране изготовления, внешнем виде и цвете товара носит справочный характер и основывается на последних доступных к моменту публикации сведениях от продавца. Товарное предложение №14953464929 обновлено Вчера в 15:19.
Category: Источники питания
Price: 7500 RUB
Supplier country: RUS

Found product:
Brand: Siemens AG
Part number: 6EP1333-2BA20
Name: Sitop PSU100S 24V/5A, Stabilized Power Supply, input 120/230VAC, output 5A 24VDC, SiemensKood: 6EP1333-2BA20
Description: Overview Specification Downloadable files Sitop PSU100S 24V/ 5A stabilized, input 120/230VAC, output 5A 24VDC, Siemens SITOP PSU100S 24 V/5 A stabilized power supply input: 120/230 V AC output: 24 V DC/5 A Input Input 1-phase AC Supply voltage ● 1 at AC Rated value 120 V ● 2 at AC Rated value 230 V ● Note Automatic range selection Input voltage ● 1 at AC 85 ... 132 V ● 2 at AC 170 ... 264 V Wide-range input No Overvoltage resistance 2.3 × Vin rated, 1.3 ms Mains buffering at Iout rated, min. 20 ms; at Vin = 93/187 V Rated line frequency 1 50 Hz Rated line frequency 2 60 Hz Rated line range 47 ... 63 Hz Input current ● at rated input voltage 120 V 2.34 A ● at rated input voltage 230 V 1.36 A Switch-on current limiting (+25 °C), max. 40 A I²t, max. 1 A²·s Built-in incoming fuse T 3,15 A/250 V (not accessible) Protection in the mains power input (IEC 898) Recommended miniature circuit breaker: from 6 A characteristic C Output Output Controlled, isolated DC voltage Rated voltage Vout DC 24 V Total tolerance, static ± 3 % Static mains compensation, approx. 0.1 % Static load balancing, approx. 1 % Residual ripple peak-peak, max. 150 mV Residual ripple peak-peak, typ. 30 mV Spikes peak-peak, max. (bandwidth: 20 MHz) 240 mV Spikes peak-peak, typ. (bandwidth: 20 MHz) 140 mV Adjustment range 22.8 ... 28 V Product function Output voltage adjustable Yes Output voltage setting via potentiometer Status display Green LED for 24 V OK Signaling Relay contact (NO contact, rating 60 V DC/ 0.3 A) for "24 V OK" On/off behavior Overshoot of Vout < 3 % Startup delay, max. 0.3 s Voltage rise, typ. 15 ms Rated current value Iout rated 5 A Current range 0 ... 6 A ● Note 6 A up to +45°C; +60 ... +70 °C: Derating 1.6%/K Supplied active power typical 144 W Short-term overload current ● on short-circuiting during the start-up typical 18 A ● at short-circuit during operation typical 18 A Duration of overloading capability for excess current ● on short-circuiting during the start-up 800 ms ● at short-circuit during operation 800 ms Parallel switching for enhanced performance Yes Numbers of parallel switchable units for enhanced performance 2 Efficiency Efficiency at Vout rated, Iout rated, approx. 88 % Power loss at Vout rated, Iout rated, approx. 16 W Closed-loop control Dynamic mains compensation (Vin rated ±15 %), max. 0.3 % Dynamic load smoothing (Iout: 10/90/10 %), Uout ± typ. 3 % Load step setting time 10 to 90%, typ. 1 ms Load step setting time 90 to 10%, typ. 1 ms Protection and monitoring Output overvoltage protection protection against overvoltage in case of internal fault Vout < 33 V Current limitation 6 ... 7.1 A Property of the output Short-circuit proof Yes Short-circuit protection Constant current characteristic Enduring short circuit current RMS value ● typical 7.1 A Overcurrent overload capability in normal operation overload capability 150 % Iout rated up to 5 s/min Overload/short-circuit indicator - Safety Primary/secondary isolation Yes Galvanic isolation Safety extra-low output voltage Uout acc. to EN 60950-1 and EN 50178 Protection class Class I Leakage current ● maximum 3.5 mA ● typical 0.4 mA CE mark Yes UL/cUL (CSA) approval cULus-Listed (UL 508, CSA C22.2 No. 107.1), File E197259, cCSAus (CSA C22.2 No. 60950-1, UL 60950-1, UL 1604) Explosion protection IECEx Ex nA nC IIC T4 Gc; ATEX (EX) II 3G Ex nA nC IIC T4 Gc; cCSAus (CSA C22.2 No. 213-M1987, ANSI/ISA-12.12.01-2007) Class I, Div. 2, Group ABCD, T4 FM approval - CB approval Yes Marine approval GL, BV Degree of protection (EN 60529) IP20 EMC Emitted interference EN 55022 Class B Supply harmonics limitation EN 61000-3-2 Noise immunity EN 61000-6-2 Operating data Ambient temperature ● during operation -25 ... +70 °C — Note with natural convection ● during transport -40 ... +85 °C ● during storage -40 ... +85 °C Humidity class according to EN 60721 Climate class 3K3, no condensation Mechanics Connection technology screw-type terminals Connections ● Supply input L, N, PE: 1 screw terminal each for 0.5 ... 2.5 mm² single-core/finely stranded ● Output +, -: 2 screw terminals each for 0.5 ... 2.5 mm² ● Auxiliary Alarm signals: 2 screw terminals for 0.5 ... 2.5 mm² Connections signaling contact 2 screw terminals for 0.5 ... 2.5 mm² Width of the enclosure 50 mm Height of the enclosure 125 mm Depth of the enclosure 120 mm Required spacing ● top 50 mm ● bottom 50 mm ● left 0 mm ● right 0 mm Weight, approx. 0.5 kg Product feature of the enclosure housing for side-by-side mounting Yes Installation Snaps onto DIN rail EN 60715 35x7.5/15 Electrical accessories Buffer module MTBF at 40 °C 1 998 441 h Other information Specifications at rated input voltage and ambient temperature +25 °C (unless otherwise specified) 
Price: 133.7 EUR
Supplier country: EST

Same real-world product (1 = yes, 0 = no): 1