Searched product:
Brand: Siemens
Part number: 6ES73311KF020AB0
Name: Siemens 6ES7331-1KF02-0AB0 6ES73311KF020AB0 PLC-analoginmatningsmodul
Description: Siemens analog inmatning 6 DET73311KF020AB0 SM 331 Analog inmatning 6 DET73311KF020AB0 SM 331OBS! Denna text är maskinöversatt.OBS! Vi beklagar att vi inte har hunnit översätta denna produkttext. Texten nedan är maskinöversatt från tyska. Kommentarer
Category: Automation & pneumatik
Price: 6872 SEK
Supplier country: SWE

Found product:
Brand: Siemens AG
Part number: 6ES7331-1KF02-0AB0
Name: Simatic S7-300, Analog Input SM331, optically isolated, 8AI 13bit, U/I/ resistance/ PT100 ^NI100 ^NI1000 ^LG-NI1000, PTC/KTY, 66ms module update, 40pin, SiemensKood: 6ES7331-1KF02-0AB0
Description: Overview Specification Downloadable files Simatic S7-300, Analog Input SM331, optically isolated, 8AI, 13bit, U/I/resistance/PT100 ?NI100 ?NI1000 ?LG-NI1000, PTC/KTY, 66ms module update, 40pin, Siemens Input current from backplane bus 5 V DC, max. 90 mA Power loss Power loss, typ. 0.4 W Analog inputs Number of analog inputs 8 ● For resistance measurement 8 permissible input voltage for voltage input (destruction limit), max. 30 V; 12 V continuous, 30 V for max. 1 s permissible input current for current input (destruction limit), max. 40 mA Input ranges ● Voltage Yes ● Current Yes ● Thermocouple No ● Resistance thermometer Yes ● Resistance Yes Input ranges (rated values), voltages ● 0 to +10 V Yes ● Input resistance (0 to 10 V) 100 kΩ ● 1 V to 5 V Yes ● Input resistance (1 V to 5 V) 100 kΩ ● 1 V to 10 V No ● -1 V to +1 V Yes ● Input resistance (-1 V to +1 V) 100 kΩ ● -10 V to +10 V Yes ● Input resistance (-10 V to +10 V) 100 kΩ ● -2.5 V to +2.5 V No ● -250 mV to +250 mV No ● -5 V to +5 V Yes ● Input resistance (-5 V to +5 V) 100 kΩ ● -50 mV to +50 mV Yes ● Input resistance (-50 mV to +50 mV) 100 kΩ ● -500 mV to +500 mV Yes ● Input resistance (-500 mV to +500 mV) 100 kΩ ● -80 mV to +80 mV No Input ranges (rated values), currents ● 0 to 20 mA Yes ● Input resistance (0 to 20 mA) 100 Ω ● -10 mA to +10 mA No ● -20 mA to +20 mA Yes ● Input resistance (-20 mA to +20 mA) 100 Ω ● -3.2 mA to +3.2 mA No ● 4 mA to 20 mA Yes ● Input resistance (4 mA to 20 mA) 100 Ω Input ranges (rated values), thermocouples ● Type B No ● Type C No ● Type E No ● Type J No ● Type K No ● Type L No ● Type N No ● Type R No ● Type S No ● Type T No ● Type U No ● Type TXK/TXK(L) to GOST No Input ranges (rated values), resistance thermometer ● Cu 10 No ● Ni 100 Yes; Standard/climate ● Input resistance (Ni 100) 100 MΩ ● Ni 1000 Yes ● Input resistance (Ni 1000) 100 MΩ ● LG-Ni 1000 Yes; Standard/climate ● Input resistance (LG-Ni 1000) 100 MΩ ● Ni 120 No ● Ni 200 No ● Ni 500 No ● Pt 100 Yes; Standard/climate ● Input resistance (Pt 100) 100 MΩ ● Pt 1000 No ● Pt 200 No ● Pt 500 No Input ranges (rated values), resistors ● 0 to 150 ohms No ● 0 to 300 ohms No ● 0 to 600 ohms Yes ● Input resistance (0 to 600 ohms) 100 MΩ ● 0 to 6000 ohms Yes ● Input resistance (0 to 6000 ohms) 100 MΩ Thermocouple (TC) Temperature compensation — parameterizable No — internal temperature compensation No — external temperature compensation with compensations socket No Characteristic linearization ● parameterizable Yes — for thermocouples No — for resistance thermometer yes; Pt100 standard/air con.; Ni100 standard/air con.; Ni1000 standard/air con.; LG-Ni1000 standard/air con. Cable length ● shielded, max. 200 m; max. 50 m at 50 mV Analog value generation for the inputs Measurement principle integrating Integration and conversion time/resolution per channel ● Resolution with overrange (bit including sign), max. 13 bit ● Integration time, parameterizable Yes; 60 / 50 ms ● Basic conversion time (ms) 66 / 55 ms ● Interference voltage suppression for interference frequency f1 in Hz 50 / 60 Hz Encoder Connection of signal encoders ● for current measurement as 2-wire transducer Yes; with external supply ● for current measurement as 4-wire transducer Yes ● for resistance measurement with two-wire connection Yes ● for resistance measurement with three-wire connection Yes ● for resistance measurement with four-wire connection Yes Errors/accuracies Operational error limit in overall temperature range ● Voltage, relative to input range, (+/-) 0.6 %; ±0.6 % (±5 V, 10 V, 1 to 5 V, 0 to 10 V); ±0.5 % (±50 mV, 500 mV, 1 V) ● Current, relative to input range, (+/-) 0.5 %; ±20 mA, 0 to 20 mA, 4 to 20 mA ● Resistance, relative to input range, (+/-) 0.5 %; 0 to 6 kohms, 0 to 600 kohms ● Resistance thermometer, relative to input range, (+/-) 1 Kelvin (Pt100, Ni100, climatic; Ni1000, LG-Ni1000, standard; Ni1000, LG-Ni1000, climatic); 1.2 Kelvin (Pt100, Ni100, standard) Basic error limit (operational limit at 25 °C) ● Voltage, relative to input range, (+/-) 0.4 %; 0.4% (±5 V, 10 V, 1 to 5 V, 0 to 10 V); 0.3% (±50 mV, 500 mV, 1 V) ● Current, relative to input range, (+/-) 0.3 %; ±20 mA, 0 to 20 mA, 4 to 20 mA ● Resistance, relative to input range, (+/-) 0.3 %; 0 to 6 kohms, 0 to 600 kohms ● Resistance thermometer, relative to input range, (+/-) 1 Kelvin (Pt100, Ni100, standard); 0.8 Kelvin (Pt100, Ni100, climatic; Ni1000, LG-Ni1000, standard; Ni1000, LG-Ni1000, climatic) Interrupts/diagnostics/status information Diagnostic functions No Alarms ● Diagnostic alarm No ● Limit value alarm No Diagnostic messages ● Diagnostic information readable No Diagnostics indication LED ● Group error SF (red) No Potential separation Potential separation
Price: 445.4 EUR
Supplier country: EST

Same real-world product (1 = yes, 0 = no): 1