Searched product:
Brand: Manufactured_bySIEMENSFURNAS_ELECTRIC_CO
Part number: 3RN1013-1BW10
Name: 3RN1013-1BW10 Manufactured by SIEMENS FURNAS ELECTRIC CO
Description: 3RN10131BW10 DISCONTINUED BY MANUFACTURER DISCONTIUED BY MANUFACTURER SINCE: 01.10.2020 MONITORING RELAY 24-240V AC/DC 50/60HZ SUCCESSOR: 3RN2013-1BW30
Category: Components
Price: 219.11 EUR
Supplier country: DEU

Found product:
Brand: 5A_Micom_Alstom_Relay_Agile_P441_P442_and_P444_230__415_V_Ac__ID_23630634262
Part number: 5A_Micom_Alstom_Relay_Agile_P441_P442_and_P444_230__415_V_Ac__ID_23630634262
Name: 5A Micom Alstom Relay Agile P441, P442 and P444, 230 & 415 V Ac, | ID: 23630634262
Description: Guideform Specification–Distance Protection Relays:MiCOM Alstom P441, P442, P44410thJan, 2020Mechanical SpecificationsDesign· The device shall be presented in a 4U case height format (177mm), for ease of integration/standardization in standard protection racks and panels.· The device shall be housed in a case width between 40TE (8 inches, 206mm) and 80TE (16 inches, 412mm) depending of the model (P441 – 40TE, P442 – 60TE and P444 – 80TE).· The case width must be a multiple of 10TE (2 inches) to ensure easy engineering in 19 inch rack panels.Enclosure ProtectionThe degree of protection offered shall be as per IEC 60529: 2002:· IP 52 Protection (front panel) against dust and dripping water.· IP 50 Protection for the rear and sides of the case against dust.· IP 10 Product safety protection for the rear due to live connections on the terminal block.· The device shall be housed in a metallic case wrapper.· The device case shall not include any ventilation louvres or other deliberate holes – it shall be an enclosed unit.WeightThe weight of the device shall be less than 3.5kg.General Input/Output TerminalsAll terminals shall be ring-lug screw type for security and robustness:· The screw size shall be M4 to allow suitable torque tightness.· Connection of up to two independent ring lugs per terminal shall be supported, to permit daisy-chaining of connections where required, without resorting to inserting two wires in a ferrule.Front Port Serial PC Interface A front panel USB communication port shall be provided for service access by relay technicians/engineers, communicating with the PC tool suite software:· Isolation shall be to ELV level.· The maximum cable length supported up to the PC connection shall be 5m.Rear Ethernet Connections for IEC 61850Station bus (IEC 61850-8-1) ports shall be provided:The relay shall have two fibre optic or RJ45 ports as an ordering option, to support communication redundancy, for IEC61850-8-1 or DNP3.0 communication. A choice of redundancy protocols shall be available, such as IEC 62439-3 PRP or HSR, RSTP based on IEEE 802.1w, Self-Healing Ring (SHR) and Dual Homing Star (DHS). PRP and HSR shall be provided in a single ordering option, switchable with a software configurator.
Category: Protective Relays
Price: 145 INR

Same real-world product (1 = yes, 0 = no): 0