Searched product:
Brand: Siemens/西门子
Part number: 3RV1021-1JA10
Name: 【******3RV1021-1JA10断路器 西门子3RV1021断路器 SIEMENS断路器】价格_厂家 - 中国供应商
Description: 欢迎前来中国供应商(www.china.cn)了解武汉协宇电气有限公司发布的******3RV1021-1JA10断路器 西门子3RV1021断路器 SIEMENS断路器价格,******3RV1021-1JA10断路器 西门子3RV1021断路器 SIEMENS断路器厂家信息，产品和服务质量好，性价比高，为您节省采购成本!
Category: <上一个
Price: 300.0531983849067 CNY
Supplier country: CHN

Found product:
Brand: Siemens Circuit Breaker 3RV1021-1JA10
Part number: Siemens Circuit Breaker 3RV1021-1JA10
Name: Siemens Circuit Breaker 3RV1021-1JA10
Description: The Siemens Circuit Breaker is high quality! Circuit breaker size S0 for motor protection CLASS 10 A-release7...10 A Short-circuit release 130 A Screw terminal Standardswitching capacity !!! Phased-out product !!! Successor is SIRIUS3RV2 Preferred successor type is 3RV2011-1JA10 product brand name SIRIUS product designation Circuit breaker design of the product For motor protection General technical data product extension auxiliary switch Yes power loss W for rated value of the current at AC in hot operating state 9.25 W at AC in hot operating state per pole 3.1 W surge voltage resistance rated value 6 kV maximum permissible voltage for safe isolation protection class IP on the front IP20 mechanical service life (switching cycles) shock resistance 25g / 11 ms mechanical service life (switching cycles) of the main contacts typica 100 000 continuous current rated value 10 A Ambient conditions installation altitude at height above sea level maximum 2 000 m ambient temperature during operation -20 - +60 degrees centigrade during storage -50 -- +80 degrees centigrade during transport -50 - +80 degrees centigrade Main circuit number of poles for main current circuit 3 adjustable pick-up value current of the current-dependent overload release 7 -10A operating voltage rated value 690 V at AC-3 rated value maximum 690 V operating current at AC-3 at 400 V rated value 10 A operating power at AC-3 at 400 V rated value 4000 W operating frequency at AC-3 maximum 15 1/h number of CO contacts for auxiliary contacts 0 Protective and monitoring functions product function ground fault detection No phase failure detection Yes trip class CLASS 10 design of the overload release thermal maximum short-circuit current breaking capacity (Icu) at AC at 240 V rated value 100 kA at AC at 400 V rated value 100 kA at AC at 500 V rated value 42 kA at AC at 690 V rated value 6 kA Installation mounting dimensions mounting position any mounting type screw and snap-on mounting onto 35 mm standard mounting railaccording to DIN EN 50022 height 97 mm width 45 mm depth 96 mm
Price: 459.97780460023466 USD
Supplier country: CHN

Same real-world product (1 = yes, 0 = no): 1