Searched product:
Brand: Siemens
Part number: 6ES71316BF010BA0
Name: 6ES7131-6BF01-0BA0 Siemens Simatic Et 200sp
Description: SIMATIC ET 200SP, Digital input module, DI 8x 24V DC Standard, type 3 (IEC 61131), sink input, (PNP, P-reading), Packing unit: 1 piece, fits to BU-type A0, Colour Code CC01, input delay time 0,05..20ms, module diagnostics for: short-circuit of sensor supply, wire break, supply voltage SKU:6ES71316BF010BA0
Category: MODULES
Price: 110 EUR
Supplier country: DEU

Found product:
Brand: Siemens AG
Part number: 6ES7131-6BF01-0BA0
Name: Simatic ET 200SP, Digital Input Module, 8DI 24VDC, type 3 (IEC 61131), sink input, (PNP, P-reading), fits BU-type A0, color code CC01, input delay time 0.05..20ms, module diagnostics for short-circuiting of sensor supply, wire break, supply voltage, Kood: 6ES7131-6BF01-0BA0
Description: Overview Specification Downloadable files Simatic ET 200SP, Digital Input Module, 8DI 24VDC, type 3 (IEC 61131), sink input, (PNP, P-reading), fits to BU-type A0, colour code CC01, input delay time 0.05..20ms, module diagnostics for: short-circuit of sensor supply, wire break, supply voltage, SieSIMATIC ET 200SP, Digital input module, DI 8x 24V DC Standard, type 3 (IEC 61131), sink input, (PNP, P-reading), Packing unit: 1 piece, fits to BU-type A0, Colour Code CC01, input delay time 0,05..20ms, module diagnostics for: short-circuit of sensor supply, wire break, supply voltage General information Product type designation DI 8x24 VDC ST Firmware version V0.0 ● FW update possible No usable BaseUnits BU type A0 Color code for module-specific color identification plate CC01 Product function ● I&M data Yes; I&M0 to I&M3 Engineering with ● STEP 7 TIA Portal configurable/integrated as of version V14 ● STEP 7 configurable/integrated as of version V5.5 SP3 or higher ● PCS 7 configurable/integrated as of version V8.1 SP1 ● PROFIBUS as of GSD version/GSD revision One GSD file each, Revision 3 and 5 and higher ● PROFINET as of GSD version/GSD revision GSDML V2.3 Operating mode ● DI Yes ● Counter No ● Oversampling No ● MSI No Supply voltage Rated value (DC) 24 V permissible range, lower limit (DC) 19.2 V permissible range, upper limit (DC) 28.8 V Reverse polarity protection Yes Input current Current consumption, max. 50 mA; All channels are supplied from the encoder supply Encoder supply Number of outputs 8 Output voltage encoder supply, min. 19.2 V Short-circuit protection Yes; per module 24 V encoder supply ● 24 V Yes ● Short-circuit protection Yes ● Output current, max. 700 mA; Total current of all encoders ● Output current per channel, max. 700 mA ● Output current per module, max. 700 mA Power loss Power loss, typ. 1 W; 24 V, 8 inputs supplied via encoder supply Address area Address space per module ● Inputs 1 byte; + 1 byte for QI information Hardware configuration Automatic encoding Yes ● Mechanical coding element Yes Submodules ● Number of configurable submodules, max. 4 Selection of BaseUnit for connection variants ● 1-wire connection BU type A0 ● 2-wire connection BU type A0 ● 3-wire connection BU type A0 with AUX terminals ● 4-wire connection BU type A0 + Potential isolation module Digital inputs Number of digital inputs 8 Digital inputs, parameterizable Yes Source/sink input P-reading Input characteristic curve in accordance with IEC 61131, type 3 Yes Input voltage ● Type of input voltage DC ● Rated value (DC) 24 V ● for signal "0" -30 to +5V ● for signal "1" +11 to +30V Input current ● for signal "1", typ. 2.5 mA Input delay (for rated value of input voltage) for standard inputs — parameterizable Yes; 0.05 / 0.1 / 0.4 / 0.8 / 1.6 / 3.2 / 12.8 / 20 ms (in each case + delay of 30 to 500 µs, depending on line length) — at "0" to "1", min. 0.05 ms — at "0" to "1", max. 20 ms — at "1" to "0", min. 0.05 ms — at "1" to "0", max. 20 ms Cable length ● shielded, max. 1 000 m ● unshielded, max. 600 m Encoder Connectable encoders ● 2-wire sensor Yes — permissible quiescent current (2-wire sensor), max. 1.5 mA Isochronous mode Isochronous operation (application synchronized up to terminal) No Interrupts/diagnostics/status information Diagnostics function Yes Alarms ● Diagnostic alarm Yes Diagnostic messages ● Diagnostic information readable Yes ● Monitoring the supply voltage Yes — parameterizable Yes ● Monitoring of encoder power supply Yes; Module-by-module, optional protective circuit for preventing wire-break diagnostics in the case of simple encoder contacts: 25 kOhm to 45 kOhm ● Wire-break Yes; Module-wise ● Short-circuit Yes; Module-wise Diagnostics indication LED ● Monitoring of the supply voltage (PWR-LED) Yes; green PWR LED ● Channel status display Yes; Green LED ● for channel diagnostics No ● for module diagnostics Yes; green/red DIAG LED Potential separation Potential separation channels ● between the channels No ● between the channels and backplane bus Yes ● between the channels and the power supply of the electronics No Isolation Isolation tested with 707 V DC (type test) Ambient conditions Ambient temperature during operation ● horizontal installation, min. 0 °C ● horizontal installation, max. 60 °C ● vertical installation, min. 0 °C ● vertical installation, max. 50 °C Altitude during operation relating to sea level ● Ambient air temperature-barometric pressure-altitude On request: Ambient temperatures lower than 0 °C (without condensation) and/or installation altitudes greater than 2 000 m Dimensions Width 15 mm Height 73 mm Depth 58 mm Weights Weight, approx. 28 g last modified: 11/10/2018 File description File type Download link
Price: 59.2 EUR
Supplier country: EST

Same real-world product (1 = yes, 0 = no): 1