Searched product:
Brand: WAGO Corporation
Part number: 750-600
Name: 750-600
Description: COMMUNICATIONS MODULE
Category: Industrial Automation and Controls
Price: 45.85 EUR
Supplier country: DEU

Found product:
Brand: Tripp-Lite
Part number: SMART750RMXL2U
Name: Tripp-Lite SMART750RMXL2U SmartPro 120V 750VA 600W Line-Interactive Sine Wave UPS
Description: Product Overview Overview Tripp Lite SmartPro Line Interactive UPS with enhanced LCD interface offers network-grade power protection for critical server, network and telecommunications equipment. Line Interactive Uninterruptible Power Supply (UPS) with built-in Auto-Voltage Regulation (AVR) actively corrects brownouts and overvoltages back to usable levels while maintaining a full battery charge in case of power failure. Interactive LCD interface reports UPS operating mode, detailed UPS and site-power data, plus enables a variety of UPS setup and configuration options. Super-fast switchover from line to battery power occurs within milliseconds to maintain operation of connected equipment without interruption or reboot. 95% line-mode efficiency offers reduced heat emissions and operating costs. Network management interfaces support communications via USB, RS-232 and slot for optional Network Management Card options. HID-compliant USB interface enables integration with built-in power management and auto shutdown features of Windows and Mac OS X. Network communications ports enable detailed monitoring of equipment load levels, self-test data and utility power conditions. PowerAlert UPS monitoring software is available via free download. Switched output load banks enable scheduled and real-time remote reboot and load shedding of select outlets. Emergency Power Off (EPO) interface. LCD display panel easily rotates for viewing in rackmount or tower configurations. Audible alarm with push-button momentary alarm-cancel and silent-mode configuration options. Programmable self-test. Field-replaceable, hot-swappable battery modules. Features Tripp Lite SMART750RMXL2U line interactive 2U rack/tower UPS with 750VA / .75kVA / 600W capacity and extended runtime options Line interactive UPS with Automatic Voltage Regulation (AVR) corrects brownouts and overvoltages from 83 to 147V NEMA 5-15P input plug; 6 NEMA 5-15R output receptacles, Two independently switched output load banks Maintains uninterrupted operation of connected networking equipment during blackouts, surges, brownouts and overvoltages High 95% efficiency rating in line-power mode offers reduced power consumption and BTU emisssions Internal batteries offer 20.7 minutes at 50% load (300W) and 8.5 minutes at 100% load (600W) Extended runtime is available with optional BP24V15RT2U (limit 1), BP24V28-2U (limit 1), BP24V70-3U (multi-pack compatible) and BP24V36-2US (multi-pack compatible); Output is reduced to 450 watts maximum with external battery packs External battery configurations require the use of Tripp Lite's External Battery Configuration Software (see manual) Hot-swappable, user-replaceable internal batteries and external battery packs can be replaced with no disruption to connected equipment Intelligent battery management system extends battery life Front panel LCD monitoring screen with MODE and ENTER buttons reports operating mode with 5-bar battery charge graphic, plus 7 selectable screens of detailed UPS and site power information LCD interface also supports a number of advanced user setup and operating preferences Ships with 4 post rackmount installation hardware; Optional 2POSTRMKITWM enables 2 post rackmount/wallmount installation; Optional 2-9USTAND enables tower placement Built-in USB, RS-232 and slot for optional Network Management Card options Compatible with Tripp Lite UPS management card options TLNETCARD, WEBCARDLX, SNMPWEBCARD and RELAYIOCARD HID-compliant USB interface enables integration with built-in power management and auto shutdown features of Windows and Mac OS X USB & Serial ports enable data-saving unattended shutdown when used with Tripp Lite's PowerAlert software, available via FREE download from www.tripplite.com/poweralert Built-in Emergency Power Off (EPO) interface with cable Package Includes SMART750RMXL2U UPS System USB, Serial & EPO cabling 4 post installation kit Owner's manual Specifications OVERVIEW UPC Code 037332123527 UPS Type Line-Interactive INPUT Rated input current (Maximum Load) 7.5A Nominal Input Voltage(s) Supported 120V AC UPS Input Connection Type 5-15P Input Circuit Breakers 10A UPS Input Cord Length (ft.) 10 Recommended Electrical Service 15A 120V Input Phase Single-Phase OUTPUT Output Volt Amp Capacity (VA) 750 Output Watt Capacity (Watts) 600 Output Capacity Details 6.3A. Output is reduced to 450 watts maximum when used with external battery packs Power Factor 0.8 Nominal Voltage Details 120v nominal output in battery mode Frequency Compatibility 60 Hz Frequency Compatibility Details Output is regulated to +/-0.05Hz when input frequency exceeds +/-5Hz of nominal. Output Voltage Regulation (Line Mode) -21%, +8% Output Voltage Regulation (Battery Mode) +/- 5% Load Management Receptacles Two switchable two-outlet 5-15R load banks Output AC Waveform (AC Mode) Sine wave Output AC Waveform (Battery Mode) Pure Sine wave Nominal Output Voltage(s) Supported 110V; 115V; 120V Output Receptacles (6) 5-15R Individu
Category: Power
Price: 805.71 USD
Supplier country: USA

Same real-world product (1 = yes, 0 = no): 0