Searched product:
Brand: Siemens
Part number: Siemens F-Digitaleingabemodul SIMATIC S7-1500 F-DI 16x 24VDC 6ES7526-1BH00-0AB0
Name: Siemens F-Digitaleingabemodul SIMATIC S7-1500 F-DI 16x 24VDC 6ES7526-1BH00-0AB0
Description: Produktart: Eingabemodul | SIMATIC S7-1500, F-Digitaleingabemodul, F-DI 16x 24VDC PROFIsafe 35mm Baubr. bis PL E (ISO 13849-1)/ SIL 3 (IEC 61508) Die SIMATIC ET 200MP ist ein modulares, skalierbares und universell einsetzbares Peripheriesystem in IP20 und bietet die gleichen Systemvorteile wie die S7-1500. Sie erlaubt kürzeste Buszykluszeiten und schnellste Reaktionszeiten auch bei großen Mengengerüsten. Das dezentrale Peripheriesystem ist besonders einfach zu montieren, zu verdrahten und in Betrieb zu nehmen. Durch den skalierbaren Aufbau können Sie die Peripheriestation exakt auf den jeweiligen Bedarf vor Ort ausrichten. Die skalierbare Konfiguration einer ET 200MP - Station wird durch das umfassende Spektrum von Signalbaugruppen gewährleistet. Es stehen zahlreiche digitale und analoge Ein- und Ausgabebaugruppen zur Verfügung, auch in fehlersicherer Ausführung. Dies garantiert die universelle Einsatzmöglichkeit des Systems.
Category: Schaltgeräte, Schaltanlagen, Industriesteuerung: Industriesteuerung / SPS
Price: 736.57 EUR
Supplier country: DEU

Found product:
Brand: Siemens AG
Part number: 6ES7526-1BH00-0AB0
Name: Simatic S7-1500, F Digital Input Module, F-DI 16x 24VDC PROFIsafe, W35mm, up to PL E (ISO 13849-1)/ SIL 3 (IEC 61508), SiemensKood: 6ES7526-1BH00-0AB0
Description: Overview Specification Downloadable files Simatic S7-1500, F Digital Input Module, F-DI 16x 24VDC PROFIsafe, W35mm, up to PL E (ISO 13849-1)/ SIL 3 (IEC 61508), SiemensSIMATIC S7-1500, F digital input module, F-DI 16x 24 V DC PROFIsafe; 35 mm width; up to PL E (ISO 13849-1)/ SIL 3 (IEC 61508) General information Product type designation F-DI 16x24VDC Firmware version ● FW update possible Yes Product function ● I&M data Yes; I&M0 to I&M3 Engineering with ● STEP 7 TIA Portal configurable/integrated as of version V13 SP1 with HSP 0086 Operating mode ● DI Yes Supply voltage Type of supply voltage 24 V DC Rated value (DC) 24 V permissible range, lower limit (DC) 19.2 V permissible range, upper limit (DC) 28.8 V Reverse polarity protection Yes Input current Current consumption (rated value) 50 mA Encoder supply Number of outputs 4 Short-circuit protection Yes; Electronic (response threshold 0.7 A to 1.8 A) 24 V encoder supply ● 24 V Yes; min. L+ (-1.5 V) ● Short-circuit protection Yes ● Output current, max. 300 mA; Max. 100 mA when mounted vertically Power Power available from the backplane bus 0.9 W Power loss Power loss, typ. 4.6 W Address area Address space per module ● Address space per module, max. 9 byte Hardware configuration Automatic encoding Yes ● Electronic coding element type F Yes Digital inputs Number of digital inputs 16 Source/sink input Yes; P-reading Input characteristic curve in accordance with IEC 61131, type 1 Yes Input voltage ● Type of input voltage DC ● Rated value (DC) 24 V ● for signal "0" -30 to +5V ● for signal "1" +15 to +30V Input current ● for signal "1", typ. 3.7 mA Input delay (for rated value of input voltage) for standard inputs — parameterizable Yes — at "0" to "1", min. 0.4 ms — at "0" to "1", max. 20 ms — at "1" to "0", min. 0.4 ms — at "1" to "0", max. 20 ms Cable length ● shielded, max. 1 000 m ● unshielded, max. 500 m Interrupts/diagnostics/status information Diagnostics function Yes Alarms ● Diagnostic alarm Yes ● Hardware interrupt No Diagnostic messages ● Monitoring the supply voltage Yes ● Wire-break No ● Short-circuit Yes ● Group error Yes Diagnostics indication LED ● RUN LED Yes; Green LED ● ERROR LED Yes; Red LED ● Channel status display Yes; Green LED ● for channel diagnostics Yes; Red LED ● for module diagnostics Yes; Red LED Potential separation Potential separation channels ● between the channels and backplane bus Yes Isolation Isolation tested with 707 V DC (type test) Standards, approvals, certificates Highest safety class achievable in safety mode ● Performance level according to ISO 13849-1 PLe ● SIL acc. to IEC 61508 SIL 3 Probability of failure (for service life of 20 years and repair time of 100 hours) — Low demand mode: PFDavg in accordance with SIL3 < 5.00E-05 — High demand/continuous mode: PFH in accordance with SIL3 < 1.00E-09 1/h Ambient conditions Ambient temperature during operation ● horizontal installation, min. 0 °C ● horizontal installation, max. 60 °C ● vertical installation, min. 0 °C ● vertical installation, max. 40 °C Dimensions Width 35 mm Height 147 mm Depth 129 mm Weights Weight, approx. 280 g last modified: 11/10/2018 File description File type Download link
Price: 899.9 EUR
Supplier country: EST

Same real-world product (1 = yes, 0 = no): 1