Searched product:
Brand: Siemens Indus.Sector
Part number: 6ES71344MB020AB0
Name: Siemens Indus.Sector Elektronikmodul 6ES7134-4MB02-0AB0
Description: Siemens Indus.Sector Elektronikmodul 6ES7134-4MB02-0AB0 Versorgungsspannung bei AC 50 Hz 0V, Versorgungsspannung bei AC 60 Hz 0V, Versorgungsspannung bei DC 28,8 ...20,4V, Spannungsart der Versorgungsspannung DC, Eingang, Strom, Eingangssignal konfigurierbar, Auflösung der Analogeingänge 16Bit, Anzahl der analogen Eingänge 2, Anzahl der analogen Ausgänge 0, Anzahl der HW-Schnittstellen Industrial Ethernet 0, Anzahl der HW-Schnittstellen PROFINET 0, Anzahl der HW-Schnittstellen seriell RS-232 0, Anzahl der HW-Schnittstellen seriell RS-422 0, Anzahl der HW-Schnittstellen seriell RS-485 0, Anzahl der HW-Schnittstellen seriell TTY 0, Anzahl der HW-Schnittstellen parallel 0, Anzahl der HW-Schnittstellen Wireless 0, Anzahl der HW-Schnittstellen sonstige 0, Systemkomponente, Schutzart (IP) IP20, Ausführung des elektrischen Anschlusses sonstige, Feldbusanschluss über seperaten Buskoppler möglich, Tragschienenmontage möglich, Wand-/Direktmontage möglich, Fronteinbau möglich, Explosionsschutz-Kategorie für Gas ohne, Explosionsschutz-Kategorie für Staub ohne, Breite 15mm, Höhe 81mm, Tiefe 52mm, Anzahl der HW-Schnittstellen USB 0, Durch den Einsatz der F-Elektronikmodule der ET 200S ist es möglich die sicherheitsgerichteten Applikationsanforderungen integriert in der Gesamtautomation zu lösen.Die für den fehlersicheren Betrieb erforderlichen Sicherheitsfunktionen sind in die Baugruppen integriert
Category: SPS-Analoges Ein-/Au…
Price: 273.74 EUR
Supplier country: DEU

Found product:
Brand: Siemens AG
Part number: 6ES7134-4MB02-0AB0
Name: Simatic DP, Electronics Module, 2AI I high feature for ET 200S, W15mm, cycle time per module: 0.5ms, ±20mA, 15bit+sign, 4..20mA, 15bit, operational limit ±0.1%, SF LED (group fault), SiemensKood: 6ES7134-4MB02-0AB0
Description: Overview Specification Downloadable files Simatic DP, Electronics Module, 2AI I high feature for ET 200S, W15mm, cycle time per module: 0.5ms, ±20mA, 15bit+sign, 4..20mA, 15bit, operational limit ±0.1%, SF LED (group fault), SiemensSIMATIC DP, Electronics module 2 AI I High Feature for ET 200S, 15 mm width, Cycle time per module: 0.5 ms, +/-20mA; 15 bit+sign, 4.. 20mA; 15 bit, Operational limit +/-0.1% with SF LED (group fault) Supply voltage Load voltage L+ ● Rated value (DC) 24 V ● Reverse polarity protection Yes Input current from load voltage L+ (without load), max. 48 mA from backplane bus 3.3 V DC, max. 10 mA Output voltage Power supply to the transmitters ● present Yes ● short-circuit proof Yes Power loss Power loss, typ. 1.2 W Address area Address space per module ● Address space per module, max. 4 byte Analog inputs Number of analog inputs 2 permissible input current for current input (destruction limit), max. 50 mA Cycle time (all channels) max. 0.5 ms; 0.5 ms for 2 channels without noise suppression, 18 / 21 ms per channel with noise suppression Input ranges (rated values), currents ● -20 mA to +20 mA Yes ● 4 mA to 20 mA Yes Cable length ● shielded, max. 200 m Analog value generation for the inputs Measurement principle Sigma Delta Integration and conversion time/resolution per channel ● Resolution with overrange (bit including sign), max. 16 bit ● Interference voltage suppression for interference frequency f1 in Hz 60 / 50 Hz / no ● Conversion time (per channel) 0.04 ms; Without noise suppression 17/20 ms per channel with error Smoothing of measured values ● parameterizable Yes; In 4 stages: 1x, 4x, 16x, 32x cycle time ● Step: None Yes; 1x ● Step: low Yes; 4x ● Step: Medium Yes; 16x ● Step: High Yes; 32x Encoder Connection of signal encoders ● for current measurement as 2-wire transducer — Burden of 2-wire transmitter, max. 750 Ω Errors/accuracies Linearity error (relative to input range), (+/-) 0.03 % Temperature error (relative to input range), (+/-) 0.003 %/K Crosstalk between the inputs, min. -100 dB Repeat accuracy in steady state at 25 °C (relative to input range), (+/-) 0.01 % Operational error limit in overall temperature range ● Current, relative to input range, (+/-) 0.1 %; 0.2% without interference frequency suppression Basic error limit (operational limit at 25 °C) ● Current, relative to input range, (+/-) 0.05 %; 0.1% without interference frequency suppression Interference voltage suppression for f = n x (f1 +/- 1 %), f1 = interference frequency ● Series mode interference (peak value of interference < rated value of input range), min. 90 dB ● Common mode interference (USS < 2.5 V) , min. 100 dB Isochronous mode Isochronous operation (application synchronized up to terminal) Yes Interrupts/diagnostics/status information Alarms ● Hardware interrupt Yes Diagnostic messages ● Wire-break Yes; Measuring range 4 to 20 mA only ● Group error Yes ● Overflow/underflow Yes Diagnostics indication LED ● Group error SF (red) Yes Parameter Remark 12 bytes, 4 bytes in compatibility mode Diagnostics wire break Disable / enable Measurement type/range deactivated / ±20 mA / 4 to 20 mA Group diagnostics Disable / enable Overflow/underflow Disable / enable Potential separation Potential separation analog inputs ● between the channels No; however, increased permissible potential difference between the inputs. ● between the channels and backplane bus Yes ● Between the channels and load voltage L+ Yes Dimensions Width 15 mm Height 81 mm Depth 52 mm Weights Weight, approx. 45 g last modified: 06/07/2019 File description File type Download link
Price: 188.54 EUR
Supplier country: EST

Same real-world product (1 = yes, 0 = no): 1