Searched product:
Brand: FRIGIDAIRE
Part number: 242221501
Name: AUGER MOTOR
Price: 128.71 USD
Supplier country: USA

Found product:
Brand: Square D
Part number: LUB12
Name: LUB12 - Square D LUB12 - TeSys U Motor Starter Non-Reversing Power Base (12A, 3P)
Description: Square D LUB12 - TeSys U Motor Starter Non-Reversing Power Base (12A, 3P) - TeSys U Motor Starter Non-Reversing Power Base (12A)<br><br> <b>Specifications:</b> <ul><li>Range: TeSys <li>Product Name: TeSys U <li>Product or Component Type: Non-Reversing Power Base <li>Device Application: Motor <li>Poles Description: 3P <li>Suitability for Isolation: Yes <li>[Ith] Conventional Free Air Thermal Current: 12 A <li>Utilisation Category: AC-44, AC-43, AC-41 <li>[Uc] Control Circuit Voltage: 24 V AC 50/60 Hz, 24 V DC, 48 V AC 50/60 Hz, 48...72 V DC, 110...220 V DC, 110...240 V AC 50/60 Hz <li>Auxiliary Contact Composition: 1 NO + 1 NC <li>Auxiliary Contacts Type: Linked Contacts 1 NO + 1 NC) IEC 60947-4-1, Mirror Contact 1 NC) State of the Power Draft IEC 60947-1 <li>[Ue] Rated Operational Voltage: 230 V, 440 V, 500 V, 690 V <li>Network Frequency: 40...60 Hz <li>[Ie] Rated Operational Current: 12 A <= 440 V, 12 A 500 V, 9 A 690 V <li>[Ics] Rated Service Breaking Capacity: 10 kA 500 V, 4 kA 690 V, 50 kA 230 V, 50 kA 440 V <li>Typical Current Consumption: 130 mA 24 V DC I maximum while closing with LUCA, LUCB, LUCC, LUCD, 140 mA 24 V AC I maximum while closing with LUCA, LUCB, LUCC, LUCD, 150 mA 24 V DC I maximum while closing with LUCM, 280 mA 110...220 V DC I maximum while closing with LUCA, LUCB, LUCC, LUCD, 280 mA 110...240 V AC I maximum while closing with LUCA, LUCB, LUCC, LUCD, 280 mA 48...72 V AC I maximum while closing with LUCA, LUCB, LUCC, LUCD, 280 mA 48...72 V DC I maximum while closing with LUCA, LUCB, LUCC, LUCD, 35 mA 110...220 V DC I rms sealed with LUCA, LUCB, LUCC, LUCD, 35 mA 110...240 V AC I rms sealed with LUCA, LUCB, LUCC, LUCD, 35 mA 48...72 V AC I rms sealed with LUCA, LUCB, LUCC, LUCD, 35 mA 48...72 V DC I rms sealed with LUCA, LUCB, LUCC, LUCD, 60 mA 24 V DC I rms sealed with LUCA, LUCB, LUCC, LUCD, 70 mA 24 V AC I rms sealed with LUCA, LUCB, LUCC, LUCD, 70 mA 24 V DC I rms sealed with LUCM <li>Safety Reliability Level: B10d = 1369863 Cycles Contactor with Nominal Load EN/ISO 13849-1, B10d = 20000000 Cycles Contactor with Mechanical Load EN/ISO 13849-1 <li>Operating Time: 35 ms opening with LUCA, LUCB, LUCC, LUCD, LUCM Control Circuit, 50 ms >= 72 V closing with LUCA, LUCB, LUCC, LUCD Control Circuit, 60 ms 48 V Closing with LUCA, LUCB, LUCC, LUCD Control Circuit, 70 ms 24 V Closing with LUCA, LUCB, LUCC, LUCD Control Circuit, 75 ms Closing with LUCM Control Circuit <li>Mechanical Durability: 15000000 Cycles <li>Maximum Operating Rate: 60 cyc/mn <li>[Ui] Rated Insulation Voltage: 600 V UL 508, 690 V IEC 60947-1 3, 600 V CSA C22.2 No 14 <li>[Uimp] Rated Impulse Withstand Voltage: 6 kVIEC 60947-6-2 <li>Safe Separation of Circuit: 400 V SELV between the Control and Auxiliary Circuits IEC 60947-1 appendix N, 400 V SELV between the Control or Auxiliary Circuit and the Main Circuit IEC 60947-1 appendix N <li>Connections - Terminals: Control Circuit Screw Clamp Terminals 1 0.00…0.00 in² (0.34…1.5 mm²) Flexible with Cable End, Control Circuit Screw Clamp Terminals 1 0.00…0.00 in² (0.75…1.5 mm²) Flexible without Cable End, Control Circuit Screw Clamp Terminals 1 0.00…0.00 in² (0.75…1.5 mm²) Rigid without Cable End, Control Circuit Screw Clamp Terminals 2 0.00…0.00 in² (0.34…1.5 mm²) Flexible with Cable End, Control Circuit Screw Clamp Terminals 2 0.00…0.00 in² (0.75…1.5 mm²) Flexible without Cable End, Control Circuit Screw Clamp Terminals 2 0.00…0.00 in² (0.75…1.5 mm²) Rigid without Cable End, Power Circuit Screw Clamp Terminals 1 0.00…0.02 in² (1…10 mm²) Rigid without Cable End, Power Circuit Screw Clamp Terminals 1 0.00…0.01 in² (1…6 mm²) Flexible with Cable End, Power Circuit Screw Clamp Terminals 1 0.00…0.02 in² (2.5…10 mm²) Flexible without Cable End, Power Circuit Screw Clamp Terminals 2 0.00…0.01 in² (1…6 mm²) Flexible with Cable End, Power Circuit Screw Clamp Terminals 2 0.00…0.01 in² (1…6 mm²) Rigid without Cable End, Power Circuit Screw Clamp Terminals 2 0.00…0.01 in² (1.5…6 mm²) Flexible without Cable End <li>Tightening Torque: Control Circuit 7.08…10.62 lbf.in (0.8…1.2 N.m) Flat 0.20 in (5 mm), Control Circuit 7.08…10.62 lbf.in (0.8…1.2 N.m) Philips no 1 0.20 in (5 mm), Power Circuit 16.82…22.13 lbf.in (1.9…2.5 N.m) Flat 0.24 in (6 mm), Power Circuit 16.82…22.13 lbf.in (1.9…2.5 N.m) Philips No 2 0.24 in (6 mm) <li>Heat Dissipation: 2 W Control Circuit with LUCA, LUCB, LUCC, LUCD, 1.7 W Control Circuit with LUCM <li>Immunity to Microbreaks: 3 ms <li>Immunity to Voltage Dips: 70 % / 500 ms IEC 61000-4-11 <li>Standards: UL 508 type E, with Phase Barrier, EN 60947-6-2, IEC 60947-6-2, CSA C22.2 No 14 Type E <li>IP Degree of Protection: IP20 IEC 60947-1 Front Panel and Wired Terminals, IP20 IEC 60947-1 Other Faces, IP40 IEC 60947-1 Front Panel outside Connection Zone <li>Protective Treatment: TH IEC 60068 <li>Ambient Air Temperature for Operation: -13…140 °F (-25…60 °C) with LUCM, -13…158 °F (-25…70 °C) with LUCA, LUCB, LUCC, LUCD <li>Ambient Air Temperature for Storage: -40…185 °F (-40…85 °C)
Category: Electrical Supplies
Price: 232.72 USD
Supplier country: USA

Same real-world product (1 = yes, 0 = no): 0