Searched product:
Brand: Phoenix Contact
Part number: 2866226
Name: 2866226 | QUINT-DC-UPS/24DC/10 | Phoenix Contact
Description: Produktbeschreibung zu "QUINT-DC-UPS/24DC/10" Herstellernummer: 2866226 Unterbrechungsfreie Stromversorgung 24 V DC/10 A, mit integriertem 1,3 Ah Akku-Modul. Im Download-Bereich stehen u.a. eine übersichtliche Auswahltabelle mit Lastströmen und Pufferzeiten sowie die Aufladezeiten nach Pufferbetrieb bereit. "QUINT-DC-UPS/24DC/10" Weiterführende Links zu "QUINT-DC-UPS/24DC/10"
Category: Produkte nach Herstellern: Phoenix Contact
Price: 397.51489866792986 EUR
Supplier country: DEU

Found product:
Brand: Phoenix
Part number: 2320212
Name: Uninterruptible Power Supply QUINT-UPS/24DC/24DC/5, PhoenixKood: 2320212
Description: Overview Specification Downloadable files Uninterruptible Power Supply QUINT-UPS/24DC/24DC/5, PhoenixDimensions Width 35 mm Height 130 mm Depth 125 mm Width with alternative assembly 123 mm Height with alternative assembly 130 mm Depth with alternative assembly 39 mm Installation distance right/left 5 mm / 5 mm Installation distance top/bottom 50 mm / 50 mm Ambient conditions Degree of protection IP20 Ambient temperature (operation) -25 °C ... 70 °C Ambient temperature (storage/transport) -40 °C ... 85 °C Max. permissible relative humidity (operation) ≤ 95 % (25 °C, non-condensing) Climatic class 3K3 (in acc. with EN 60721) Input data Input voltage 24 V DC Nominal input voltage 24 V DC Input voltage range 18 V DC ... 30 V DC Current consumption (maximum) 9.4 A (maximum, mains operation) Current consumption (charging process) 1.8 A (Charging, mains operation) Fixed backup threshold ≤ 22 V DC Variable connect threshold 1 V/0.1 s Output data (24 V DC mains operation) Nominal output voltage 24 V DC Output voltage range (depends on the input voltage) 18 V DC ... 30 V DC Nominal output current (IN) 5 A (-25 °C ... 60 °C) POWER BOOST (IBoost) 7.5 A (-25°C ... 40°C) Selective Fuse Breaking (ISFB) 30 A (-25 °C ... 60 °C) Output data (24 V DC battery operation) Nominal output voltage 24 V DC Output voltage range (depends on the input voltage) 19.2 V DC ... 27.6 V DC (UOUT = UBAT - 0,5 V DC) Nominal output current (IN) 5 A (-25 °C ... 60 °C) POWER BOOST (IBoost) 7.5 A (-25°C ... 40°C) Selective Fuse Breaking (ISFB) 32.5 A (-25 °C ... 60 °C) General output data Efficiency > 98 % (Mains operation, with charged energy storage) General IQ technology Yes Net weight 0.5 kg Protection class III MTBF (IEC 61709, SN 29500) > 500000 h (25 °C) > 500000 h (40 °C) Mounting position horizontal DIN rail NS 35, EN 60715 Assembly instructions alignable: horizontal 5 mm, vertical 50 mm Connection data, input Connection method Pluggable screw connection Conductor cross section solid min. 0.2 mm² Conductor cross section solid max. 2.5 mm² Conductor cross section flexible min. 0.2 mm² Conductor cross section flexible max. 2.5 mm² Conductor cross section AWG min. 20 Conductor cross section AWG max. 12 Stripping length 7 mm Screw thread M4 Connection data, output Connection method Pluggable screw connection Conductor cross section solid min. 0.2 mm² Conductor cross section solid max. 2.5 mm² Conductor cross section flexible min. 0.2 mm² Conductor cross section flexible max. 2.5 mm² Conductor cross section AWG min. 20 Conductor cross section AWG max. 12 Stripping length 7 mm Screw thread M4 Connection data for signaling Conductor cross section solid min. 0.2 mm² Conductor cross section solid max. 2.5 mm² Conductor cross section flexible min. 0.2 mm² Conductor cross section flexible max. 2.5 mm² Conductor cross section AWG min. 24 Conductor cross section AWG max. 12 Screw thread M4 Standards EMC requirements for noise immunity EN 61000-6-1 EN 61000-6-2 EMC requirements for noise emission EN 61000-6-3 EN 61000-6-4 Standard - Electrical safety EN 60950-1/VDE 0805 (SELV) Standard – Electronic equipment for use in electrical power installations and their assembly into electrical power installations EN 50178/VDE 0160 (PELV) Rail applications EN 50121-4 Conformance/approvals UL approvals UL Listed UL 508 UL/C-UL Recognized UL 60950-1 UL ANSI/ISA-12.12.01 Class I, Division 2, Groups A, B, C, D (Hazardous Location) EMC data Electromagnetic compatibility Conformance with EMC Directive 2014/30/EU Low Voltage Directive Conformance with Low Voltage Directive 2014/35/EC Electrostatic discharge EN 61000-4-2 Contact discharge 8 kV (Test Level 4) Discharge in air 15 kV (Test Level 4) Electromagnetic HF field EN 61000-4-3 Frequency range 80 MHz ... 1 GHz Test field strength 20 V/m Frequency range 1 GHz ... 2 GHz Test field strength 10 V/m Frequency range 2 GHz ... 3 GHz Test field strength 3 V/m Comments Criterion A Fast transients (burst) EN 61000-4-4 Input 2 kV (Test Level 3 - asymmetrical) Output 2 kV (Test Level 3 - asymmetrical) Signal 2 kV (Test Level 4 - asymmetrical) Comments Criterion A Surge voltage load (surge) EN 61000-4-5 Input 1 kV (Test Level 2 - symmetrical) 2 kV (Test Level 3 - asymmetrical) Output 1 kV (Test Level 2 - symmetrical) 2 kV (Test Level 3 - asymmetrical) Signal 1 kV (Test Level 2 - asymmetrical) 
Price: 207.2 EUR
Supplier country: EST

Same real-world product (1 = yes, 0 = no): 0