Searched product:
Brand: SIEMENS
Part number: 6ES7132-6BH01-0BA0
Name: 6ES7132-6BH01-0BA0 Manufactured by SIEMENS
Description: 6ES71326BH010BA0 DIGITAL OUTPUT MODULE SIMATIC ET 200SP DQ 16X 24V DC/0 5A STANDARD SOURCE OUTPUT (PNP P-SWITCHING) PACKING UNIT: 1 PIECE FITS TO BU-TYPE A0 COLOUR CODE CC00
Category: Data Control System
Price: 145 EUR
Supplier country: DEU

Found product:
Brand: Siemens AG
Part number: 6ES7132-6BH01-0BA0
Name: Simatic ET 200SP, Digital Output Module, 16DQ 24VDC/0.5A, suitable for BU type A0, color code CC00, module diagnostics, SiemensKood: 6ES7132-6BH01-0BA0
Description: Overview Specification Downloadable files Simatic ET 200SP, Digital Output Module, 16DQ 24VDC/0.5A, suitable for BU type A0, color code CC00, module diagnostics, SiemensSIMATIC ET 200SP, Digital output module, DQ 16x 24V DC/0,5A Standard, Source output (PNP,P-switching) Packing unit: 1 piece, fits to BU-type A0, Colour Code CC00, substitute value output, module diagnostics for: short-circuit to L+ and ground, wire break, supply voltage General information Product type designation DQ 16x24VDC/0.5A ST, PU 1 HW functional status From FS03 Firmware version V0.0 ● FW update possible No usable BaseUnits BU type A0 Color code for module-specific color identification plate CC00 Product function ● I&M data Yes; I&M0 to I&M3 Engineering with ● STEP 7 TIA Portal configurable/integrated as of version V14 ● STEP 7 configurable/integrated as of version V5.5 SP3 ● PCS 7 configurable/integrated as of version V8.1 SP1 ● PROFIBUS as of GSD version/GSD revision One GSD file each, Revision 3 and 5 and higher ● PROFINET as of GSD version/GSD revision GSDML V2.3 Operating mode ● DQ Yes ● DQ with energy-saving function No ● PWM No ● Oversampling No ● MSO No Supply voltage Rated value (DC) 24 V permissible range, lower limit (DC) 19.2 V permissible range, upper limit (DC) 28.8 V Reverse polarity protection Yes Input current Current consumption, max. 60 mA; without load Output voltage Rated value (DC) 24 V Power loss Power loss, typ. 1 W Address area Address space per module ● Address space per module, max. 2 byte; + 2 bytes for QI information Hardware configuration Automatic encoding Yes ● Mechanical coding element Yes Selection of BaseUnit for connection variants ● 1-wire connection BU type A0 ● 2-wire connection BU type A0 + Potential isolation module ● 3-wire connection BU type A0 + Potential isolation module ● 4-wire connection BU type A0 + Potential isolation module Digital outputs Type of digital output Source output (PNP, current-sourcing) Number of digital outputs 16 Current-sinking No Current-sourcing Yes Digital outputs, parameterizable Yes Short-circuit protection Yes ● Response threshold, typ. 1 A; 0.7 to 1.3 A Open-circuit detection Yes Limitation of inductive shutdown voltage to Typ. L+ (-50 V) Controlling a digital input Yes Switching capacity of the outputs ● with resistive load, max. 0.5 A ● on lamp load, max. 5 W Load resistance range ● lower limit 48 Ω ● upper limit 12 kΩ Output current ● for signal "1" rated value 0.5 A ● for signal "0" residual current, max. 0.1 mA Output delay with resistive load ● "0" to "1", typ. 50 µs ● "1" to "0", typ. 100 µs Parallel switching of two outputs ● for uprating No ● for redundant control of a load Yes Switching frequency ● with resistive load, max. 100 Hz ● with inductive load, max. 2 Hz ● on lamp load, max. 10 Hz Total current of the outputs ● Current per channel, max. 0.5 A ● Current per module, max. 8 A Total current of the outputs (per module) horizontal installation — up to 30 °C, max. 8 A — up to 40 °C, max. 8 A — up to 50 °C, max. 6 A — up to 60 °C, max. 4 A vertical installation — up to 30 °C, max. 8 A — up to 40 °C, max. 6 A — up to 50 °C, max. 4 A Cable length ● shielded, max. 1 000 m ● unshielded, max. 600 m Isochronous mode Isochronous operation (application synchronized up to terminal) No Interrupts/diagnostics/status information Diagnostics function Yes Substitute values connectable Yes Alarms ● Diagnostic alarm Yes Diagnostic messages ● Monitoring the supply voltage Yes ● Wire-break Yes; Module-wise ● Short-circuit to M Yes; Module-wise ● Short-circuit to L+ Yes; Module-wise ● Group error Yes Diagnostics indication LED ● Monitoring of the supply voltage (PWR-LED) Yes; Green PWR LED ● Channel status display Yes; Green LED ● for channel diagnostics No ● for module diagnostics Yes; green/red DIAG LED Potential separation Potential separation channels ● between the channels No ● between the channels and backplane bus Yes Isolation Isolation tested with 707 V DC (type test) Standards, approvals, certificates Suitable for safety functions No Suitable for safety-related tripping of standard modules Yes; From FS01 Highest safety class achievable in safety mode ● Performance level according to ISO 13849-1 PL d ● SIL acc. to IEC 61508 SIL 2 Ambient conditions Ambient temperature during operation ● horizontal installation, min. -30 °C ● horizontal installation, max. 60 °C ● vertical installation, min. -30 °C ● vertical installation, max. 50 °C Altitude during operation relating to sea level ● Installation altitude above sea level, max. 2 000 m; On request: Installation altitudes greater than 2 000 m Dimensions Width 15 mm Height 73 mm Depth 58 mm Weights Weight, approx. 30 g last modified: 05
Price: 117.7 EUR
Supplier country: EST

Same real-world product (1 = yes, 0 = no): 1