Searched product:
Brand: Siemens Indus.Sector
Part number: 6EP14363BA00
Name: Siemens Indus.Sector Sitop Modular 3400VAC 24VDC 20A 6EP1436-3BA
Description: Siemens Indus.Sector Sitop Modular 3400VAC 24VDC 20A 6EP1436-3BA00 Spannungsart der Versorgungsspannung AC, 1.Ausgangsspannung 24 ...24V, Max.Ausgangsstrom 1 20A, Ausgangsspannung einstellbar, Kurzschlussfest, Bemessungsversorgungsspannung bei AC 50 Hz 400 ...400V, Bemessungsversorgungsspannung bei AC 60 Hz 500 ...500V, Ausgangsspannung geregelt, Leistungsabgabe 480W, Stabilisiert, Ausführung des elektrischen Anschlusses Schraubanschluss, Tragschienenmontage möglich, Geeignet für Reiheneinbau, Einbauhöhe 225mm, Direktmontage möglich, Breite 160mm, Höhe 125mm, Tiefe 125mm, Schutzart (IP) IP20, Die modulare Stromversorgung mit 1- und 2-phasigem Weitbereichseingang für weltweiten Einsatz, mit umschaltbarer Ausgangskennlinie, Funktionserweiterung durch Zusatzmodule möglich
Category: Gleichstromversorgung
Price: 267.13 EUR
Supplier country: DEU

Found product:
Brand: Siemens AG
Part number: 6EP1436-3BA00
Name: Sitop Modular 20, stabilized power supply, input 3A 400-500VAC, output 20A 24VDC, SiemensKood: 6EP1436-3BA00
Description: Overview Specification Downloadable files Sitop Modular 20, stabilized power supply, input 3A 400-500VAC, output 20A 24VDC, Siemens SITOP modular 20 A stabilized power supply input: 400-500 V 3AC output: 24 V DC/20 A Input Input 3-phase AC Rated voltage value Vin rated 400 ... 500 V Voltage range AC 320 ... 550 V ● Note Starting from Vin > 340 V Wide-range input Yes Overvoltage resistance 2.3 × Vin rated, 1.3 ms Mains buffering at Iout rated, min. 6 ms; at Vin = 400 V Rated line frequency 1 50 Hz Rated line frequency 2 60 Hz Rated line range 47 ... 63 Hz Input current ● at rated input voltage 400 V 1.1 A ● at rated input voltage 500 V 0.9 A Switch-on current limiting (+25 °C), max. 35 A I²t, max. 0.7 A²·s Built-in incoming fuse none Protection in the mains power input (IEC 898) Required: 3-pole connected miniature circuit breaker 6 ... 16 A characteristic C or circuit breaker 3RV2011-1DA10 (setting 3 A) or 3RV2711-1DD10 (UL 489) Output Output Controlled, isolated DC voltage Rated voltage Vout DC 24 V Total tolerance, static ± 3 % Static mains compensation, approx. 0.1 % Static load balancing, approx. 0.2 % Residual ripple peak-peak, max. 100 mV Spikes peak-peak, max. (bandwidth: 20 MHz) 200 mV Adjustment range 24 ... 28.8 V Product function Output voltage adjustable Yes Output voltage setting via potentiometer; max. 480 W Status display Green LED for 24 V OK Signaling via signaling module (6EP1961-3BA10) On/off behavior No overshoot of Vout (soft start) Startup delay, max. 2.5 s Voltage increase time of the output voltage maximum 500 ms Rated current value Iout rated 20 A Current range 0 ... 20 A ● Note +60 ... +70 °C: Derating 2%/K Supplied active power typical 480 W Short-term overload current ● at short-circuit during operation typical 60 A Duration of overloading capability for excess current ● at short-circuit during operation 25 ms Constant overload current ● on short-circuiting during the start-up typical 23 A Parallel switching for enhanced performance Yes; switchable characteristic Numbers of parallel switchable units for enhanced performance 2 Efficiency Efficiency at Vout rated, Iout rated, approx. 90 % Power loss at Vout rated, Iout rated, approx. 53 W Closed-loop control Dynamic mains compensation (Vin rated ±15 %), max. 1 % Dynamic load smoothing (Iout: 50/100/50 %), Uout ± typ. 2 % Load step setting time 50 to 100%, typ. 4 ms Load step setting time 100 to 50%, typ. 4 ms Setting time maximum 10 ms Protection and monitoring Output overvoltage protection < 35 V Current limitation, typ. 23 A Property of the output Short-circuit proof Yes Short-circuit protection Alternatively, constant current characteristic approx. 23 A or latching shutdown Enduring short circuit current RMS value ● typical 23 A Overload/short-circuit indicator LED yellow for "overload", LED red for "latching shutdown" Safety Primary/secondary isolation Yes Galvanic isolation Safety extra-low output voltage Uout acc. to EN 60950-1 and EN 50178 Protection class Class I Leakage current ● maximum 3.5 mA CE mark Yes UL/cUL (CSA) approval UL-Listed (UL 508), File E197259, CSA (CSA C22.2 No. 14, CSA C22.2 No. 107.1) Explosion protection IECEx Ex nA nC IIC T3 Gc; ATEX (EX) II 3G Ex nA nC IIC T3 Gc; cCSAus (CSA C22.2 No. 213, ANSI/ISA-12.12.01) Class I, Div. 2, Group ABCD, T3 FM approval - CB approval No Marine approval GL, ABS Degree of protection (EN 60529) IP20 EMC Emitted interference EN 55022 Class B Supply harmonics limitation EN 61000-3-2 Noise immunity EN 61000-6-2 Operating data Ambient temperature ● during operation 0 ... 70 °C — Note with natural convection ● during transport -40 ... +85 °C ● during storage -40 ... +85 °C Humidity class according to EN 60721 Climate class 3K3, no condensation Mechanics Connection technology screw-type terminals Connections ● Supply input L1, L2, L3, PE: 1 screw terminal each for 0.2 ... 4 mm² single-core/finely stranded ● Output +, -: 2 screw terminals each for 0.33 ... 4 mm² ● Auxiliary - Width of the enclosure 160 mm Height of the enclosure 125 mm Depth of the enclosure 125 mm Required spacing ● top 50 mm ● bottom 50 mm ● left 0 mm ● right 0 mm Weight, approx. 2 kg Product feature of the enclosure housing for side-by-side mounting Yes Installation Snaps onto DIN rail EN 60715 35x7.5/15 Electrical accessories Buffer module, signaling module MTBF at 40 °C 711 213 h Other information Specifications at rated input voltage and ambient temperature +25 °C (unless otherwise specified) File description File type Download link " 6EP1436-3BA00 datasheet PDF Download link
Price: 240.3 EUR
Supplier country: EST

Same real-world product (1 = yes, 0 = no): 1