Searched product:
Brand: Siemens
Part number: 3RV1011-1CA10
Name: Siemens 3RV1011-1CA10 Leistungsschalter S00 1,8-2,5S
Description: Technische Details Eigenschaft Wert Polzahl: 3 Bemessungsbetriebsspannung: 690 V Bemessungsbetriebsleistung bei AC-3, 230 V: 0.37 kW Überlastauslöser Stromeinstellung: 2.5 A Bemessungsbetriebsleistung bei AC-3, 400 V: 0.75 kW Bemessungsdauerstrom Iu: 2.5 A Auslösetechnik: magnetisch Phasenausfallempfindlich: ja Anschlussart Hauptstromkreis: Schraubanschluss Einstellbereich des unverzögerten Kurzschlussauslösers: 33 A Bemessungsgrenzkurzschlussausschaltstrom Icu bei 400 V, AC: 100.0 kA Mit integriertem Hilfsschalter: nein Mit integriertem Unterspannungsauslöser: nein Schutzart (IP) : IP20 Breite: 45.0 mm Höhe: 90.0 mm Tiefe: 75.0 mm Ausführung des Betätigungselements: Kipphebel Mit thermischem Schutz: nein
Category: Installation
Price: 55.1 EUR
Supplier country: DEU

Found product:
Brand: Siemens Circuit Breaker 3RV1011-1CA10
Part number: Siemens Circuit Breaker 3RV1011-1CA10
Name: Siemens Circuit Breaker 3RV1011-1CA10
Description: The Siemens Circuit Breaker is high quality! Circuit breaker size S00 for motor protection, CLASS 10 A-release1.8...2.5 A N-release 33 A Screw terminal Standard switchingcapacity product brand name SIRIUS product designation Circuit breaker design of the product For motor protection product type designation 3RV1 General technical data size of the circuit-breaker S00 size of contactor can be combined company-specific S00 product extension auxiliary switch Yes power loss W for rated value of the current at AC in hot operating state 7.25 W at AC in hot operating state per pole 2.4 W insulation voltage with degree of pollution 3 at ACrated value 690 V surge voltage resistance rated value 6 kV maximum permissible voltage for safe isolation in networks with grounded star point betweenmain and auxiliary circuit400 V protection class IP on the front IP20 of the termina lIP00 mechanical service life (switching cycles) of the main contacts typical 100 000 of auxiliary contacts typical 100 000 electrical endurance (switching cycles) typical 100 000 reference code acc. to DIN EN 81346-2 Q Ambient conditions installation altitude at height above sea level maximum 2 000 m ambient temperature during operation -20 - +60 degrees centigrade during storage -50 -- +80 degrees centigrade during transport -50 - +80 degrees centigrade temperature compensation -20 -- +60 degrees centigrade relative humidity during operation10 - 95 % Main circuit number of poles for main current circuit 3 adjustable pick-up value current of the current-dependent overload release 1.8 - 2.5 Aoperating voltage rated value 690 V at AC-3 rated value maximum 690 V operating frequency rated value 50 -- 60 Hz operating current rated value2.5A operating current at AC-3 at 400 V rated value 2.5 A operating power at AC-3 at 230 V rated value 370 W at 400 V rated value750 W at 500 V rated value1100 W at 690 V rated value1500 W operating frequency at AC-3 maximum 15 1/h number of CO contacts for auxiliary contacts 0 Protective and monitoring functions product function ground fault detection No phase failure detection Yes trip class CLASS 10 design of the overload release thermal operational short-circuit current breaking capacity(Ics) at AC at 240 V rated value 100 kA at 400 V rated value 100 kA at 500 V rated value 100 kA at 690 V rated value 2 kA maximum short-circuit current breaking capacity (Icu) at AC at 240 V rated value 100 kA at AC at 400 V rated value 100 kA at AC at 500 V rated value 100 kA at AC at 690 V rated value 2 kA response value current of instantaneous short-circuit trip unit 33 A UL CSA ratings full-load current (FLA) for three-phase AC motor at 480 V rated value2.5A at 600 V rated value2.5 A yielded mechanical performance hp for single-phase AC motor at 200/208 V rated value 0.5 hp at 220/230 V rated value 0.5 hp at 460/480 V rated value 1 hp at 575/600 V rated value1.5 hp product function short circuit protection Yes design of the short-circuit trip magnetic design of the fuse link for IT network for short-circuit protection of the main circuit at 240 V none required at 400 V gL/gG 35 A at 500 V gL/gG 25 A at 690 V gL/gG 25 A Installation mounting dimensions mounting position any mounting type screw and snap-on mounting onto 35 mm standard mounting railaccording to DIN EN 60715 height 90 mm width 45 mm depth 75 mm
Price: 324.89918262264183 USD
Supplier country: CHN

Same real-world product (1 = yes, 0 = no): 1