Searched product:
Brand: Schneider Electric Leistungsschütz LC1D128BD
Part number: LC1D128BD
Name: Schneider Electric Leistungsschütz LC1D128BD
Description: Beschreibung Schneider Electric Leistungsschütz LC1D128BDAbbildung ähnlich.Bitte achten Sie auf die technischen Daten und die EAN des Produkts.Hersteller:Schneider ElectricBezeichnung:Leistungsschütz Typ:LC1D128BDBemessungssteuerspeisespannung Us bei DC:24 VSpannungsart zur Betätigung:DCBemessungsbetriebsstrom Ie bei AC-1, 400 V:25 ABemessungsbetriebsstrom Ie bei AC-3, 400 V:12 ABemessungsbetriebsleistung bei AC-3, 400 V:5,5 kWGeeignet für Reiheneinbau:neinAnzahl der Hilfskontakte als Schließer:1Anzahl der Hilfskontakte als Öffner:1Anschlussart Hauptstromkreis:SchraubanschlussAnzahl der Öffner als Hauptkontakte:2Anzahl der Schließer als Hauptkontakte:2Schneider Electric Leistungsschütz LC1D128BD: weitere DetailsLeistungsschütz TeSys LC1D. 4 polig, 2 Schließer + 2 Öffner. Zusätzliche Hilfskontakte- 1 Schließer + 1 Öffner, Spule 24 V DC. Abmessung (BxHxT) 45x85x99 mm, Gewicht 0,525 kg. Kategorie AC-1. mit integraler Unterdrückungseinheit. Schnelle und einfache Einrichtung. Sichere und langlebige Stromverbindung mit Everlink und Federklemmen. Geeignet für Sicherheitsanwendungen durch mechanisch gekoppelte Kontakte und Spiegelkontakte. Zertifizierungen nach UL, CCC, GOST, DNV, BV, LROS (Lloyds register of shipping), RINA, GL, CSA. Produktstandards gem. EAN: 3389110334111Geliefert wird: Schneider Electric Leistungsschütz LC1D128BD, Verpackungseinheit: 1 Stück, EAN: 3389110334111 Technische Daten Bemessungssteuerspeisespannung Us bei DC: 24 VSpannungsart zur Betätigung: DCBemessungsbetriebsstrom Ie bei AC-1, 400 V: 25 A Typ Schneider Electric Inhalt 1 St.
Price: 83.892721862012 EUR
Supplier country: DEU

Found product:
Brand: Schneider Electric
Part number: LC1D258BD
Name: 4P CONTACTOR 40A AC-1 (2NO 2NC) 24VDC
Description: Previous Next Technical Reference docPdf Datasheet docPdf Product Change Notice (PCN) Legislation and Compliance RoHS Certificate of Compliance RS Components RoHS Certificate of Compliance EU Directives 2011/65/EU and 2015/863 restrict the use of the 10 substances below in the manufacture of specified types of electrical equipment. Whilst this restriction does not legally apply to components, it is recognised that component “compliance” is relevant to many customers. RS definition of RoHS Compliance: The product does not contain any of the restricted substances in concentrations and applications banned by the Directive, and for components, the product is capable of being worked on at the higher temperatures required by lead–free soldering The restricted substances and maximum allowed concentrations in the homogenous material are, by weight: SubstanceConcentration Lead0.1% Mercury0.1% PBB (Polybrominated Biphenyls)0.1% PBDE ( Polybrominated Diphenyl Ethers)0.1% Hexavalent Chromium0.1% Cadmium0.01% DEHP (Bis (2-Ethylhexl) phthalate)0.1% BBP (Benzyl butyl phthalate)0.1% DBP (Dibutyl phthalate)0.1% DIBP (Diisobutyl phthalate)0.1% The supplier of the item listed below has informed RS Components that the product is "RoHS Compliant". RS Components has taken all reasonable steps to confirm this statement. Information relates only to products sold on or after the date of this certificate. Compliant Product Details RS stock number 7447320 Product description 4P CONTACTOR 40A AC-1 (2NO 2NC) 24VDC Manufacturer / Brand Schneider Electric Manufacturer part number LC1D258BD RS Components Ltd, Birchington Road, Corby, Northants, NN17 9RS, UK Print this certificate Statement of Conformity RS Components Statement of Conformity This statement confirms that the product detailed below complies with the specifications currently published in the RS media and has been subject to the strict quality conditions imposed by RS Components’ internal management systems. Furthermore and where applicable, it confirms that all relevant semiconductor devices have been handled and packed under conditions that meet the administrative and technical requirements of ANSI/ESD S20.20 and EN61340-5-1 electrostatics control standards. Compliant Product Details RS stock number 7447320 Product description 4P CONTACTOR 40A AC-1 (2NO 2NC) 24VDC Manufacturer / Brand Schneider Electric Manufacturer part number LC1D258BD The foregoing information relates to product sold on, or after, the date shown below. RS COMPONENTS Date Mar 10, 2022 RS Components Pte Ltd Robinson Road, P.O. Box 1582, Singapore 903132 Print this statement Country of Origin: ID Product Details Schneider Electric LC1D TeSys D ContactorsTeSys D Contactors from Schneider Electric combine long mechanical and electrical life to offer a high reliable contactor. The range has been designed for integration in control systems and can be used to create motor starters for any type of application. The TeSys D contactors offer quick simple setup while maintaining compliance with international standards.Features and Benefits • Built-in auxiliary contacts for added switching capability• Screw connections: IP20 finger-safe terminals with both North American and International terminal markings• Can be panel mounted with screws or DIN Rail mounted• Bidirectional peak limiting diode suppressor to protect the coil• Easily installed accessories• Flexible control circuit to suit a wide range of applicationsWhat does the utilisation category AC1 and AC3 mean for the TeSys contactors?Contactor utilisation categories define the current making and breaking values, based on the type of load to be controlled and the operating cycle conditions. AC-1: This applies to all AC devices with a power factor of at least 0.95. Example of use: resistive load, heating, distribution.AC-3: This applies to squirrel cage motors where breaking occurs while the motor is running. Example of use: all squirrel cage motors, lifts, escalators, conveyors, bucket elevators, compressors, pumps, mixers, air conditioning units.What accessories are available?• Auxiliary contact blocks with serrated wiping action• Front mount dust tight auxiliary contact blocks• Pneumatic time delay blocks• Transient voltage surge suppressors• Interface modules and electronic timers• Mechanical latching blocksIs the TeSys D range a double break pole type contactor?Yes the Tesys D range uses linear translation movement that provides double breaking of the poles. Specifications Attribute Value Brand Schneider Electric Coil Voltage 24 V dc Number of Poles 4 Contact Current Rating 40 A Range TeSys D Normal State Configuration 2NO + 2NC Series LC1D Auxiliary Contact Configuration 1NO + 1NC Contact Voltage Rating 690 V ac/dc Number Of Auxiliary Contacts 2 
Category: Contactors
Price: 2835176.7 IDR
Supplier country: IDN

Same real-world product (1 = yes, 0 = no): 0