Question: when a 400 hz transformer is operated at 50hz?
Answer: If magnetizing current goes beyond certain limit, the transformer core may saturate. Therefore, it is required to reduce applied voltage along with frequency in same proportion to keep the magnetizing current same. This will reduce applied voltage (400/50=8) by 8 times and thus its KVA rating too will reduce 8 times.