Question: where are duct detectors required?
Answer: NFPA 90A requires the first duct smoke detector to be installed on the supply side of air handler units of more than 2,000 cubic feet per minute (cfm) and requires one on the return side of units of more than 15,000 cfm and serving more than one story.