Question: what is the difference between mcb type b and c?
Answer: Type B devices are designed to trip at fault currents of 3-5 times rated current (In). For example a 10A device will trip at 30-50A. Type C devices are designed to trip at 5-10 times In (50-100A for a 10A device). Type D devices are designed to trip at 10-20 times In (100-200A for a 10A device).