Patent GB-1084138-A (GB)
IPC: H01H33/59
Abstract: 1,084,138. Surge diverter circuit arrangements. GENERAL ELECTRIC CO. Jan. 27, 1966 [Jan. 28, 1965], No. 3609/66. Heading H2H. To limit switching surges on a very high voltage system, a vacuum-type surge diverter 39 is connected between the line terminal 10 of a circuit-breaker 14 and earth and is arranged to be triggered upon the occurrence of a surge voltage of 1À5 to 2 times the normal line-toground peak voltage or of a surge voltage increasing at more than a predetermined rate. The former contingency is met by the arrangement shown in Fig. 3 in which the diverter 39 comprises an evacuated housing 40 containing main electrodes 46, 48, a tubular metallic shield 74 to intercept and condense arc-generated metallic vapours, and a trigger gap 54 which consists of spaced metal layers 58, 60 bonded to a ceramic support 57 and respectively connected to the winding 130 of a pulse transformer (through a metal end cap 66) and to the main electrode 48. The layers 58, 60 are of gas-absorbing metal, in this case titanium charged with hydrogen, such that when the gap 54 sparks over due to a surge of predetermined value on the line 10, hydrogen is evolved and' ionized and then driven into the main gap 50 to cause breakdown between the electrodes 46, 48. The arc extinguishes at the first current zero and will not re-strike unless the line voltage again reaches the predetermined trigger value. The trigger circuit comprises a normally non- conductive unijunction transistor 110 whose emitter 114 is fed with a signal representative of line voltage via the conventional step-down circuit shown. When a surge of sufficient magnitude occurs, the transistor 110 conducts to fire a thyratron 118 and so allow a charged capacitor 127 to discharge through the winding 128 of the pulse transformer, thus causing breakdown of the diverter 39. A similar opertion is produced by a lightning surge and a non- linear resistor 76 is provided for such circumstances. To prevent internal flashover of the circuit-breaker 14 during opening, the setting of the trigger circuit may be temporarily reduced during this period by means of a switch 140, which normally short-circuits a resistor 99 in the step-down circuit and which is opened by a cam 139 when the breaker 14 opens, the switch 140 being reclosed by a time delay arrangement 143, 144. An auxiliary switch 148 is connected in parallel with the switch 140 to ensure that if the breaker 14 is quickly reclosed after opening, the setting of the trigger circuit is immediately restored to its normal value. The temporary alteration in the setting of the trigger circuit may be made dependent on the value of load current being broken by the breaker 14, this being achieved by a normally-closed switch 162 in parallel with the switch 140 and operable in response to the current in the line 10, the reclosing time delay for switch 162 being longer than that for the switch 140. Fig. 4 shows an arrangement in which the trigger circuit 170 responds to the rate of change of voltage on the line 10 and thus operates for all surges irrespective of their magnitude. In this arrangement, another trigger circuit 170a is provided to produce operation of the diverter 39 when the polarity of the voltage across the resistor 172 is opposite to that required for operation with the circuit 170. The circuits 170, 170a may be modified to make them insensitive to low magnitude surges, Fig. 5 (not shown). An arrangement using three series-connected diverters 39 is also described, Fig. 2 (not shown).