Air Flow Direction Setting Air flow 2-step direction (Swing/Stop) Air flow operation varies depending on the model. Each Group Each Group ON/OFF Timer ON/OFF single event timer Can set to turn unit ON and/or OFF 30 minutes ~ 18 hours. Each Group Each Group Button lock Button permission level setting (On/Off / setting / Mode button / Fan Temperature limit setting After power reset, the setting value is Various restriction capabilities Each Group Each Group Service Mode Viewing/Setting indoor unit option code Viewing/setting indoor unit MAIN address Viewing/setting indoor unit RMC address Viewing indoor unit cycle data Viewing/setting indoor unit temperature compensation during Heating (+2°F +5°F) Each Unit Each Unit Error When an error is currently occurring in the system, the afflicted unit and the error code are displayed Each Group Each Group Permit / Prohibit Local Operation Setting/releasing of simplified locking of remote control buttons Each Group N/A Quiet Mode Select the quiet mode to lower the fan noise level. Each Group N/A SIMPLE TOUCH WIRED CONTROLLER (MWR-SH10N) Connection: The wired controller shall control up to 16 SAMSUNG indoor units (defined and as one group). Dimensions: The wired controller shall be approximately 4 13/16” x 3 11/16” x 3/4” in size and in color. The wired controller shall have the following features and control capability: The wired controller shall have an internal infrared receiver to allow control of
Connection: The On/Off Controller shall be capable of controlling up to 128 indoor units (defined as 16 groups). Dimensions: The On/Off Controller shall be approximately 2.3” x 4.7” in size and white in color 17 LED displays. The On/Off Controller shall install recessed in wall. An NEC approved box shall be required for installation. Function: The On/Off Controller shall be capable of turning ON/OFF up to sixteen groups of units (1 – 16 units per group), for a maximum of 128 indoor units. Each of the 16 individual groups shall have ON/OFF control separate from other All of the indoor units shall be turned ON/OFF using the main ALL ON/ALL OFF button. An LED for each group of indoor units, up to 16 groups, shall be indicated if there is a failure within each group by flashing. An All LED shall be ON if all the indoor units controlled by MCM-A202DN are turned ON. An LED for each group of indoor units shall indicate the ON/OFF status of the 208/230 VAC 50/60 Hz. power. Must install in an NEC approved box (field ON/OFF Controller Item Description Operation Display ON/OFF Run and stop operation for the air conditioner units Group or Collective Group or Collective Operation Mode Setting Auto/Cooling/Heating mode control using mode switch + ALLO ON/ALL OFF button N/A All Unit Groups LED Error LED flashes during failure. N/A Each Group Schedule Operation Not Available N/A N/A Connection Position Water-source unit Communication Line (R1/R2) N/A N/A
External Contact Interface Full indoor unit control with simple contact input (Emergency/Lock) State output (Operation/Error) for control 10 digital outputs (2 reserved) / 8 digital (2 reserved) Each Channel Each Channel Smart Central Management Control & monitoring zone edition Wireless/wired remote control restriction Temperature limit setting Operation mode restriction Each Group Each Group User editable control logic User can edit control logic with operators and parameters. Efficient energy saving realization for operation conditions. EHP/ERV/AHU parameters + AND/OR + Arithmetic equation Function Each Group Each Group Data backup/ useful history management Important data is stored SD memory Record the operation history and error Each Group Each Group Unoccupied Room Control Configuration Specify unoccupied room settings for indoor units Mode Fan speed Set temperature Each Group - DVM Chiller Control Operation ON/OFF Mode: Heat, cool, cool storage, hot water Operation pattern: standard, rotation, Enable/disable Water Law Enable/disable quiet mode Forced fan mode Demand/maximum current control of design current) Each Group Each Group VRF LonWorks® Gateway 2.5 Input Variables (Control) Output Variables (Monitor) On/Off control On/Off state In/out contact state Operation mode Operation mode Emergency Stop Temperature setting Set/Room temperature Error code Fan speed/direction Fan speed/direction Indoor time duration