Contractor Information Contractor: Total Filtration Services (TFS) Contact: Gary Ford (I-90 South Territory Manager) // David Frostad (I-90 North Territory Manager) Phone: 253.261.5427 // 253.261.5423 Fax: 253.852.5385 Email: // Internet address: Web catalog address: Federal ID No.: 31-1459761 Contract worth: $2,000,000.00 Payment address: Total Filtration Services (TFS) 130002 Collections Center Drive Chicago, IL 60693 Order placement address: Total Filtration Services (TFS) 4510 “B” Street NW, Suite C Auburn, WA 98001 Ordering procedures: Please contact Gary (above) to initiate the Purchase Order process utilizing your Master number, and this Contract number (05809). Credit card acceptance: Yes Delivery time: 10 15 days After Receipt of Order (ARO) Payment terms: Net-30 Shipping destination: Freight on Board (FOB) destination Freight: Prepaid and included THE CONTRACT
All filter frames shall be marked with a product identifier such that the manufacturer name/trade mark, product name, actual size, nominal size, filter type and indicated downstream side can be readily ascertained. Performance Data: Filters shall have been tested by Underwriters Laboratory as Class 2, Standard 900 and CAN 4-S111. Filters shall meet the following performance specifications as tested by ASHRAE 52.2 Standards. Resulting performance data and filter physical characteristics must meet the following performance requirements. Pleated Air Filter, Group A, type 1 HIGH CAPACITY Category Rating Minimum Efficiency Reporting Value MERV 8, ASHRAE 52.2 Average Dust Weight Arrestance 85-90%, ASHRAE 52.2 Continuous operating temperature limits 150 degrees F. or 66 degrees C., minimum degrees Final Resistance (inches W.G.) 1.0 Dust Holding Capacity, minimum per 2” Depth Filter 106 grams to 1.0” Final Particle Size Efficiency, minimum In accordance to ASHRAE 52.2-1999, Table 12-1, Particles in the 3.0-10.0 micron range, 35E5<50 Frame Material Thickness, minimum Single layer .028 inches thick, double layers .024 inches thick Actual Filter Frame Size Variance 5/8 inches Maximum Variance from Nominal Size dimensions Required Filter physical characteristics are as follows: Nominal filter size is 24 inches width by 24 inches height and based on ASHRAE 52.2. The following filter characteristics are provided in acceptable ranges: Filter nominal depth in inches Pleats per linear foot minimum Minimum sq. ft. media area per sq. ft. of face area Rated velocity FPM Test air flow rate CFM Initial restriction W.G. 1 13 2.0 300 1200 1 13 2.0 500 2000 2 13 4.1 300 1200 2 13 4.1 500 2000 2 13 4.1 625 2500 4 10 6.67 300 1200 4 10 6.67 500 2000 4 10 6.67 625 2500
MERV, Dust Spot Average Efficiency MERV 14, 90-95%, Average Atmospheric Dust Spot Efficiency Average Dust Weight Arrestance 95-98% Continuous operating temperature limits 150 degrees F. or 66 degrees C., minimum Final Resistance (inches W.G.) 1.0 Particle Size Efficiency, minimum In accordance to ASHRAE 52.2-1999, Table 12-1, Particles in the micron range, MERV 11= 65E2<80, MERV 13 & 14= 90E2. Actual Filter Frame Size Variance 5/8 inches Maximum Variance from Nominal Size dimensions Required Filter physical characteristics are as follows: Nominal filter size is 24 inches width by 24 inches height and based on ASHRAE 52.1. Airflow Capacity Rated, 2000 CFM The following filter characteristics are provided in acceptable ranges: Pocket Depth Inches Pockets per Filter Rated Filter Face Velocity FPM Media Area/sq. Ft. MERV 11 Rated Initial Resistance (in W.G.) Dust Holding Capacity (grams) for MERV 11 MERV 13 Rated Initial Resistance (in W.G.) MERV 14 Rated Initial Resistance (in W.G.) 21-22 6 375 45-50 400 21-22 8 375 60-66 450 Pocket Depth Inches Pockets per Filter Rated Filter Face Velocity FPM Media Area/sq. Ft. MERV 11 Rated Initial Resistance (in W.G.) Dust Holding Capacity (grams) for MERV 11 MERV 13 Rated Initial Resistance (in W.G.) MERV 14 Rated Initial Resistance (in W.G.) 29-30 6 500 64-68 600 29-30 8 500 84-90 800 29-30 10 500 107 900 36 8 500 104-108 950 Group F – Extended Surface Deep Cell Cartridge Filters