APPROVALS: Tara G. Reed Buyers Technical Representative (Print) Sign Date Tom Kisenwether Construction Manager (Print) Sign Date Rick Rast Engineering Design Authority (Print) Sign Date Tom Goedjen Project Construction Manager (Print) Sign Date Other (Print) Sign Date Other (Print) Sign Date TABLE OF CONTENTS
This section identifies construction controls for mobilizing equipment, installation of temporary field office and facilities, including temporary utilities and maintaining the work site for the Low Activity Waste Pretreatment System Project (LAWPS) Hereinafter, the construction SUBCONTRACTOR (includes lower tier subcontractors and suppliers) shall be referred to as “SUBCONTRACTOR” and Washington River Protection Solutions LLC (WRPS) shall be referred to as “BUYER.” References 29 CFR 1926, “Occupational Safety and Health Administration” 49 CFR 325-399 Transportation ASCE/SEI 7 10, Minimum Design Loads for Buildings and Other Structures DOE-STD-1066-2012, Fire Protection DOE-STD-1088-95, Fire Protection for Relocatable Structures HNF-36174, DOE Fire Protection Handbook IBC, 2012 “International Building Code” MSC-PRO-FROP-2827, “Facility and Mobile Office Number Management” National Electric Code (NEC), 2014 NFPA 70 “National Electrical Code” NFPA 101, “Life Safety Code” NFPA 701, “Standard Methods of Fire Tests for Flam Propagation of Textiles and Films” NFPA 230, “Standard for Fire Protection Storage” Section 01 35 00 “LAWPS Construction Safety & Health” TFC-ENG-STD-06 Design Loads for Tank Farms Facilities WAC 296-150F “Factory-Built Housing and Commercial Structures” General Submittals for Approval Submittals that are listed within this section shall be prepared and processed in accordance with requirements and related Section 01 33 00 ”Submittals” and shall include all of the required Quality Assurance documentation in accordance with related Section 01 40 00 “Quality Assurance” Mobilization Plan: SUBCONTRACTOR shall submit a Mobilization Plan prior to initiating mobilization of equipment, materials, tools, facilities, and personnel to the site in accordance with section 2.1 below. Construction Site layout Plan: SUBCONTRACTOR shall submit a construction site layout plan prior to initiating mobilization of equipment, materials, tools, facilities,
Designed in accordance with NFPA 230. Must be designed to meet local building, fire, and life-safety codes. The warehouse will have heated (30’ x 62’) and unheated space. One side of the warehouse shall be isolated and be serviced with heating, ventilation, and air conditioning (HVAC). Insulated exposed duct work with overhead diffusers. The HVAC shall be designed to provide controlled environment for storage of the LAWPS resin. Include electric lighting system and electric outlets (110 and 240). Lighting to provide required lumen for light industrial storage with 3 way switches at each entrance for each bay. Exterior automatic day/night lighting at each exterior man door. One 240 volt outlet in each bay and wall mounted duplex outlets every 50’ OC. The entire warehouse shall be insulated. Include non-slip surface treatments on floors subject to wetting, such as outdoor docks, to eliminate slips and falls to personnel Include signage (life safety, exit, emergency lighting, etc.). Incorporate energy efficiency designs (light colored roof, white painted interior metal roof decking, energy efficient fixtures, etc.). 4 each exterior concealed overhead coiling door 8’W by 12’H with bumper guards and weather seal. Bottom lock powered operation with manual override. One 8’W by 12’H interior powered roll up door with bumper guards into the heated space. 4 exterior and 3 interior man doors 3’ by 7’. Door frames minimum 14 gauge metal frames, hardware to be latch sets with emergency crash bar on interior. 12’ by 10’ exterior concrete pad at each roll up door. 4’ by 4’ exterior concrete pad at each exterior man door. Provide a Radio Fire Alarm Reporter (RFAR) box to be connected to the site fire alarm system. Foundation design shall utilize LAWPS Geotechnical Report Concrete and rebar design and construction shall be in accordance with ACI 318-11 and ACI 301-10