2 Overvoltage Category (III*) (P) 3 Assumed Voltage Drop for Package Plant (V) (P) 4 Supply Restrictions (P) 6 Lightning and Surge Protection Requirements (P) 5.0 PERFORMANCE SPECIFICATION 3 Minimum Design Life (20 years*) (P) 6.0 DESIGN SPECIFICATION 6.1 General 6.1.1 General and Safety Requirements 3 Method of Fault Protection (ADS*) (P/S) 6.1.6 O & M Manuals 1 Reference for O & M Manual Specification ([P) 6.2 The Assembly 6.2.1 General 2 Form of Internal Separation (P/S) Form 2 assemblies (2a or 2b) Form 4 assemblies (4a or 4b) 5 Control Circuit Test Facilities () (S) Internal push-button Test position on switching and isolation device 7 Diversity factor (S) 6.2.2 Electrical Components 4 Component (P) Details (S) 6.2.4 Construction 6.2.4.1 General 3 Material(s) of Construction (Including Details of Any Protective Coatings) (P/S) 4 Type of Assembly Construction () (P/S) a Cubicle/multi-cubicle b Box/multi-box 6 Degree of Ingress Protection (IP Code) (P/S) 7 Size/Weight Restrictions (P) 6.2.4.5 Mounting Arrangements 1 Mounting Arrangements () (P/S) Skid/frame mounted Wall mounted Other (specify) 6.2.5 Earthing and Bonding 4 Separate Earth Bars/ Studs Required (Y/N) (P) 6.2.6 Cabling and Wiring 6.2.6.1 General 3 Ratio of CSAs of Neutral and Line Conductors (100 %*) (P) 6.2.7 Requirements for Specific Components 6.2.7.1 Indicating Lamps 2 Lamp Colours/Meanings (P) Available/auto-available white Supply on Running Stopped Emergency stop Dangerous condition red Normal condition Alarm yellow/ amber Tripped/fault yellow/
amber On Off Process indicators 6.2.7.2 Push-Button and Control Switches 1 Push Button Switch Colours/Meanings (P) Start Stop Reset Emergency stop red Inch Lamp test Closed Open On Off 6.2.8 Functional Units 1 Method of Functional Unit Connection (P) 6.2.8.1 Incomer 1 Fuse Switch Rating & Configuration (S) Rating (A) 3 pole 3 pole + bolted neutral link 4 pole Short circuit capacity (kA) 6.2.8.2 Motor Starters Refer to APPENDIX C2 6.2.8.3 Control Circuit Supplies 3 CCS Voltage (P/S) 6.2.8.4 Equipment General 10 Type of HMI Required/Provided (P/S) 11 Method of Connecting Package Plant to Site Control System () (P) Hardwired Remote I/O unit Fieldbus connection 11 Reference for Purchaser’s Particular Specification Low Voltage and Extra Low Voltage Systems 1 Type and Configuration of and ELV Systems (P/S) Lighting and Socket Outlets 1 Lighting Facilities Required (Y/N) (P) PLC 1 PLC Provided (Y/N) (S) 6.2.8.5 Uninterruptible Power Supply (UPS) 1 UPS Requirements () (P) None required Provided within Assembly Provided within a separate assembly 3 Details of Loads to be Supported by the UPS (P) 4 UPS Rating and Autonomy Time (110% and 15 minutes (min)) (P) 6.2.8.6 Supervisory Control and Monitoring 2 Local & Remote Supervisory Control Signals Required/ Provided (P/S) Signal Description Signal Type1 1 – Volt-free (VF), Digital (D), Analogue (A) 3 Local & Remote Supervisory Monitoring Signals Required/Provided (P/S)
- MOTOR STARTER DATA SHEET PACKAGE PLANT (ELECTRICAL) DRIVE DESIGNATION ____________________ 1 Motor Starter Details (S) Type Direct-on-line Star delta Reversing Two speed Soft start/stop Variable speed Voltage 400 V 3 phase 230 V 1 phase Other (specify) Rating Output (kW) Full load current (A) Starting current (xFLC) Number of starts per hour Power Factor Uncorrected motor power factor DRIVE DESIGNATION ____________________ 1 Motor Starter Details (S) Type Direct-on-line Star delta Reversing Two speed Soft start/stop Variable speed Voltage 400 V 3 phase 230 V 1 phase Other (specify) Rating Output (kW) Full load current (A) Starting current (xFLC) Number of starts per hour Power Factor Uncorrected motor power factor DRIVE DESIGNATION ____________________ 1 Motor Starter Details (S) Type Direct-on-line Star delta Reversing Two speed Soft start/stop Variable speed Voltage 400 V 3 phase 230 V 1 phase Other (specify) Rating Output (kW) Full load current (A) Starting current (xFLC) Number of starts per hour Power Factor Uncorrected motor power factor DRIVE DESIGNATION ____________________ 1 Motor Starter Details (S) Type Direct-on-line Star delta Reversing Two speed Soft start/stop Variable speed Voltage 400 V 3 phase 230 V 1 phase Other (specify) Rating Output (kW) Full load current (A) Starting current (xFLC) Number of starts per hour Power Factor Uncorrected motor power factor