Location Details Material Details Results / Management Details Photographs Building ID: - Identified During Demolition - Site Grounds Material Type: Cement Status of ACM: Presumed Elevation: Ground Floor Quantity: Unknown - - Sample #: Position Installed: - Refer to Comments Condition: - Sample Result: Primary Location: External Friability: Non-friable Risk Rating: 5 - Moderate Secondary Location: Grounds Surface Treatment: Not Applicable Recommendation: Manage & Review Comments: Pipe junction remains below level of required works - left in ground to intersection between former locations of Buildings 6, 7, & 9 Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: - Identified During Demolition - Site Grounds Material Type: Refer to Comments Status of ACM: Presumed Elevation: Ground Floor Quantity: Unknown - - Sample #: - Position Installed: Other - Refer to Comments Condition: Good Sample Result: - Primary Location: External Friability: Non-friable Risk Rating: 6 - Moderate Secondary Location: Grounds Surface Treatment: Sealed Recommendation: Manage & Review Comments: Fuel tank bund separator Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: Building 02 Material Type: - Status of ACM: - Elevation: Ground Quantity: - - - Sample #: - Position Installed: - Condition: - Sample Result: - Primary Location: External Friability: - Risk Rating: Secondary Location: - Surface Treatment: - Recommendation: - Comments: Building ID Entry - Building B2. Refurbished. Inaccessible vinyl floor coverings remain in discrete areas below walls (refer to marked site map in Appendices) Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: Building 02 Material Type: Vinyl Sheeting Status of ACM: Confirmed Elevation: Ground Floor Quantity: - - - Sample #: N10101-s01 Position Installed: Floor Condition: Fair Sample Result: Chrysotile Primary Location: Refer to Marked Site Map Friability: Non-friable Risk Rating: 5 - Moderate Secondary Location: - Surface Treatment: Sealed Recommendation: Manage & Review Comments: Vinyl floor tiles remain in discrete areas below walls (refer to marked site map in Appendices) Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: Building 03 - Warehouse (DEMOLISHED) Material Type: - Status of ACM: - Elevation: Ground Floor Quantity: - - - Sample #: - Position Installed: - Condition: - Sample Result: - Primary Location: - Friability: - Risk Rating: Secondary Location: - Surface Treatment: - Recommendation: - Comments: Building Identification - No Suspected Asbestos or ACM Identified Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: Building 03 - Warehouse (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Quantity: 8 - m2 Sample #: N10102-S04 / 32412 Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: External Friability: - Risk Rating: Secondary Location: Beneath windows to office space Surface Treatment: - Recommendation: - Comments: Infill panels beneath windows to office space. Sampled during previous assessment Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: Building 03 - Warehouse (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 20 - m2 Sample #: 32330 Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: Lunch room Friability: - Risk Rating: Secondary Location: External wall sheeting Surface Treatment: - Recommendation: - Comments: Wall sheeting to external areas on west elevation and south east corner Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: Building 03 - Warehouse (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Quantity: 3 - m2 Sample #: N10102-S03 / Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: Main warehouse area Friability: - Risk Rating: Secondary Location: Infill above eastern elevation fire hose reel Surface Treatment: - Recommendation: - Comments: Infill above eastern fire hose reel. Sampled during a previous assessment Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: Building 03 - Warehouse (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 4 - m2 Sample #: 32336 / 32409 Position Installed: Wall Condition: - Sample Result: Chrysotile Primary Location: Office Friability: - Risk Rating: Secondary Location: West elevation entrance passage Surface Treatment: - Recommendation: - Comments: Upper wall panel to walkway. It is noted that two different sheets are used across this area Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: Building 03 - Warehouse (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 3 - m2 Sample #: 21502 / 32405 Position Installed: Wall Condition: - Sample Result: Chrysotile Primary Location: Old Warehouse Collection Deck Friability: - Risk Rating: Secondary Location: Upper Wall Surface Treatment: - Recommendation: - Comments: Upper wall and infill panel Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: Building 03 - Warehouse (DEMOLISHED) Material Type: Cement Status of ACM: REMOVED Elevation: Ground Floor Quantity: 2.5 - m2 Sample #: Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: External Friability: - Risk Rating: Secondary Location: elevation entrance Surface Treatment: - Recommendation: - Comments: Wall west elevation, at north entrance alcove Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: Building 03 - Warehouse (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 1 - items Sample #: 21509 Position Installed: Preformed Moulded Product Condition: - Sample Result: No Asbestos Detected Primary Location: External Friability: - Risk Rating: Secondary Location: Opposite Car Park Surface Treatment: - Recommendation: - Comments: Service Pit carpark opposite (west side) of Building 3 Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: Building 04 - Amenities (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 6 - m2 Sample #: 32328 Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: External Friability: - Risk Rating: Secondary Location: Cleaners utility cupboard Surface Treatment: - Recommendation: - Comments: Wall to south elevation Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: Building 04 - Amenities (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 78 - m2 Sample #: N10101-S04 Position Installed: Fascia Condition: - Sample Result: No Asbestos Detected Primary Location: External Friability: - Risk Rating: Secondary Location: Perimeter of building Surface Treatment: - Recommendation: - Comments: Sampled during prior assessment Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: Building 04 - Amenities (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 5 - m2 Sample #: 32324 Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: Social area Friability: - Risk Rating: Secondary Location: Fridge cupboard Surface Treatment: - Recommendation: - Comments: Wall sheeting to east elevation. Both sides of partition wall between cupboards. Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: Building 04 - Amenities (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Quantity: 6 - m2 Sample #: 32325 Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: Social area Friability: - Risk Rating: Secondary Location: Server storage cavity Surface Treatment: - Recommendation: - Comments: Wall sheeting to and west elevations Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: Building 05 - Toilets/Locker Rooms (DEMOLISHED) Material Type: - Status of ACM: - Elevation: Ground Floor Quantity: - - - Sample #: - Position Installed: - Condition: - Sample Result: - Primary Location: - Friability: - Risk Rating: Secondary Location: - Surface Treatment: - Recommendation: - Comments: Building Identification Entry Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: Building 05 - Toilets/Locker Rooms (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 6 - m2 Sample #: 21506 Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: Locker room Friability: - Risk Rating: Secondary Location: Old doorway to Cleaners Store Surface Treatment: - Recommendation: - Comments: Wall infill Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: Building 05 - Toilets/Locker (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 15 - m2 Sample #: 34348 / 21511 / 21512 Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: Cleaners storeroom Friability: - Risk Rating: Secondary Location: Throughout Surface Treatment: - Recommendation: - Comments: Non-masonry wall sections to all elevations. Includes wall below timber shelving to east elevation (Sample ID 34348: NAD - South elevation / Sample ID 21511: NAD - North elevation / Sample ID 21512: NAD - West elevation). Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: Building 05 - Toilets/Locker Rooms (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 3 - m2 Sample #: N10101-S11 Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: External Friability: - Risk Rating: Secondary Location: Surrounding door to cleaners storeroom Surface Treatment: - Recommendation: - Comments: Wall sheeting surrounding door to cleaners room. Sampled during a previous assessment. Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: Building 05 - Toilets/Locker Rooms (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Quantity: 1 - items Sample #: N10101-S13 Position Installed: Preformed Moulded Product Condition: - Sample Result: Chrysotile Primary Location: External Friability: - Risk Rating: Secondary Location: North elevation Surface Treatment: - Recommendation: - Comments: Surround to pipe beneath metal louvres to north elevation. Sampled during previous assessment. Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: Building 05 - Toilets/Locker Rooms (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 4 - m2 Sample #: N10101-S07 Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: External Friability: - Risk Rating: Secondary Location: East elevation Surface Treatment: - Recommendation: - Comments: Infill panels above doors to the east elevation. Sampled during a previous assessment Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: Building 05 - Toilets/Locker Rooms (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Quantity: 2 - lm Sample #: N10101-S10 Position Installed: Pipe Condition: - Sample Result: Chrysotile, Crocidolite, Amosite Primary Location: Hot water cupboard within male amenities Friability: - Risk Rating: Secondary Location: Servicing hot water heater Surface Treatment: - Recommendation: - Comments: Vent pipe to hot water heater. Sampled during previous assessment. Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: Building 06 - Electrical Workshop (DEMOLISHED) Material Type: - Status of ACM: REMOVED Elevation: Ground Floor Quantity: - - - Sample #: - Position Installed: - Condition: - Sample Result: - Primary Location: - Friability: - Risk Rating: Secondary Location: - Surface Treatment: - Recommendation: - Comments: Building Identification Entry Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: Building 06 - Electrical Workshop (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 16 - m2 Sample #: 32416 Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: Stairwell to mezzanine level Friability: - Risk Rating: Secondary Location: Throughout Surface Treatment: - Recommendation: - Comments: Wall sheeting to east and west elevations Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: Building 06 - Electrical Workshop (DEMOLISHED) Material Type: Vinyl Tile / Adhesive Status of ACM: REMOVED Elevation: Ground Floor Quantity: 50 - m2 Sample #: 08223 Position Installed: Floor Finish / Covering Condition: - Sample Result: Chrysotile Primary Location: Electrical Workshop offices Friability: - Risk Rating: Secondary Location: Southwest elevation Surface Treatment: - Recommendation: - Comments: Brow vinyl floor tiles beneath green vinyl flooring to southwest corner of office adjacent testing workshops Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: Building 06 - Electrical Workshop (DEMOLISHED) Material Type: Cement Status of ACM: REMOVED Elevation: Ground Floor Quantity: 110 - m2 Sample #: Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: West workshop area Friability: - Risk Rating: Secondary Location: Throughout Surface Treatment: - Recommendation: - Comments: Wall sheeting to north, south and east elevations Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: Building 06 - Electrical Workshop (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 100 - m2 Sample #: Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: Electrical Workshop Friability: - Risk Rating: Secondary Location: South elevation Surface Treatment: - Recommendation: - Comments: Wall sheeting to office space at southern end of workshop Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: Building 06 - Electrical Workshop (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 70 - m2 Sample #: N10101-S14 Position Installed: Wall Condition: - Sample Result: Chrysotile Primary Location: Electrical Workshop space Friability: - Risk Rating: Secondary Location: Electrical testing area Surface Treatment: - Recommendation: - Comments: Wall sheeting to all of electrical testing area. Sampled during previous assessment (Refer to Site Map for precise locations) Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: Building 06 - Electrical Workshop (DEMOLISHED) Material Type: Textile Status of ACM: REMOVED Elevation: Ground Floor Quantity: 8 - lm Sample #: 32372 Position Installed: Gasket Condition: - Sample Result: No Asbestos Detected Primary Location: Electrical Workshop space Friability: - Risk Rating: Secondary Location: Martin brand drying oven Surface Treatment: - Recommendation: - Comments: Rope seals to doors to Martin brand drying oven Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: Building 06 - Electrical Workshop (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Mezzanine level Quantity: 1 - m2 Sample #: 32417 Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: A/C Plant Room Entrance Friability: - Risk Rating: Secondary Location: West elevation Surface Treatment: - Recommendation: - Comments: Wall behind powerpoint and light switch. Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: Building 06 - Electrical Workshop (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Mezzanine level Quantity: 2 - m2 Sample #: 32373 Position Installed: Wall Condition: - Sample Result: Chrysotile Primary Location: Electrical Workshop space Friability: - Risk Rating: Secondary Location: Mezzanine level above electrical testing area Surface Treatment: - Recommendation: - Comments: Wall sheeting to east elevation, southernmost only Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: Building 06 - Electrical Workshop (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 14 - m2 Sample #: N10101-S18 Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: External Friability: - Risk Rating: Secondary Location: West elevation Surface Treatment: - Recommendation: - Comments: Wall sheeting to west elevation, outside projects area. Sampled during previous assessment Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: Building 06 - Electrical Workshop (DEMOLISHED) Material Type: Spray Coating Status of ACM: REMOVED Elevation: Roof Quantity: 200 - m2 Sample #: 32380 Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: External Friability: - Risk Rating: Secondary Location: Lower roof level Surface Treatment: - Recommendation: - Comments: Brown textured paint to sheet metal wall cladding Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: Building 06 - Electrical Workshop (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 11 - m2 Sample #: N10101-S15 Position Installed: Soffit Condition: - Sample Result: Chrysotile Primary Location: External Friability: - Risk Rating: Secondary Location: West elevation Surface Treatment: - Recommendation: - Comments: Soffit sheeting to west elevation, outside projects area. Sampled during previous assessment Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: Building 06 - Electrical Workshop (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 22 - m2 Sample #: N10101-S16 Position Installed: Fascia Condition: - Sample Result: Chrysotile Primary Location: External Friability: - Risk Rating: Secondary Location: West elevation Surface Treatment: - Recommendation: - Comments: Fascia sheeting to west elevation, outside projects area. Sampled during previous assessment Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: Building 07 (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 40 - m2 Sample #: N10101-S20 Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: Office space Friability: - Risk Rating: Secondary Location: Throughout Surface Treatment: - Recommendation: - Comments: Internal wall sheeting to north, east & west elevations within office space. Sampled during previous assessment. (No evidence of second layer of wall sheeting within eastern wall cavity) Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: Building 07 (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Quantity: 45 - m2 Sample #: 32349 Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: Office space Friability: - Risk Rating: Secondary Location: External Surface Treatment: - Recommendation: - Comments: Wall sheeting to external of office space within workshop area. Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: Building 07 (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 1 - items Sample #: Position Installed: Other - Refer to Comments Condition: - Sample Result: Chrysotile Primary Location: External Friability: - Risk Rating: Secondary Location: East elevation - outside Building 7 Surface Treatment: - Recommendation: - Comments: Moulded cement from Telstra Pit - East elevation to Building 7 - Refer to CER1607271514 Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: Building 09 - Transmission and Project Services (DEMOLISHED) Material Type: - Status of ACM: REMOVED Elevation: Ground Floor Quantity: - - - Sample #: - Position Installed: - Condition: - Sample Result: - Primary Location: - Friability: - Risk Rating: Secondary Location: - Surface Treatment: - Recommendation: - Comments: Building Identification Entry - No Suspected Asbestos or ACM Identified Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: Building 09 - Transmission and Project Services (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 6 - lm Sample #: N10101-S25 Position Installed: Pipe Condition: - Sample Result: Chrysotile, Crocidolite, Amosite Primary Location: External Friability: - Risk Rating: Secondary Location: East elevation Surface Treatment: - Recommendation: - Comments: Breather pipe to toilets. Sampled during previous assessment. Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: Building 09 - Transmission and Project Services (DEMOLISHED) Material Type: Mastic / Filler Status of ACM: REMOVED Elevation: Ground Quantity: 2 - lm Sample #: N10101-S26 / 32418 Position Installed: Membrane Condition: - Sample Result: No Asbestos Detected Primary Location: External Friability: - Risk Rating: Secondary Location: East elevation Surface Treatment: - Recommendation: - Comments: Putty to window adjacent northernmost entrance door. Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: Building 09 - Transmission and Project Services (DEMOLISHED) Material Type: - Status of ACM: REMOVED Elevation: Ground Floor Quantity: - - - Sample #: - Position Installed: Floor Condition: - Sample Result: - Primary Location: Internal Friability: - Risk Rating: Secondary Location: Throughout Surface Treatment: - Recommendation: - Comments: Floors are carpet on concrete Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: Building 10/11 (DEMOLISHED) Material Type: - Status of ACM: - Elevation: Ground Floor Quantity: - - - Sample #: - Position Installed: - Condition: - Sample Result: - Primary Location: - Friability: - Risk Rating: Secondary Location: - Surface Treatment: - Recommendation: - Comments: Building Identification Entry - No Asbestos or ACM Identified Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: Building 10/11 (DEMOLISHED) Material Type: Cement Based Status of ACM: Not Present (Tested) Elevation: Ground Floor Quantity: 4 - m2 Sample #: 32361 Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: External Friability: - Risk Rating: Secondary Location: Above door to tiger tail storage Surface Treatment: - Recommendation: - Comments: Green painted infill panel above doors to tiger tail storage area Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: Building 10/11 (DEMOLISHED) Material Type: Cement Based Status of ACM: Not Present (Tested) Elevation: Ground Floor Quantity: 11 - m2 Sample #: 32353 Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: Field Operations Contracts office Friability: - Risk Rating: Secondary Location: Server room Surface Treatment: - Recommendation: - Comments: Wall sheeting to north, south and west elevations Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: Building 10/11 (DEMOLISHED) Material Type: Cement Status of ACM: Not Present (Tested) Elevation: Ground Quantity: 4 - m2 Sample #: 32359 Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: Male and unisex toilets Friability: - Risk Rating: Secondary Location: Throughout Surface Treatment: - Recommendation: - Comments: Ceilings throughout toilets and air locks Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: Building 10/11 (DEMOLISHED) Material Type: Cement Based Status of ACM: Not Present (Tested) Elevation: Ground Quantity: 3 - m2 Sample #: 32354 Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: Storeroom marked 'Danger 11000 Volts' Friability: - Risk Rating: Secondary Location: South west corner Surface Treatment: - Recommendation: - Comments: Lower wall sheeting in south west corner of storeroom Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: Building 10/11 (DEMOLISHED) Material Type: Cement Based Status of ACM: Not Present (Tested) Elevation: Ground Quantity: 9 - m2 Sample #: 32360 Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: The Hermitage office Friability: - Risk Rating: Secondary Location: Beneath elevation windows Surface Treatment: - Recommendation: - Comments: Infill panels beneath facing windows Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: Building 10/11 (DEMOLISHED) Material Type: Cement Based Status of ACM: Not Present (Tested) Elevation: Ground Quantity: 18 - m2 Sample #: 21513 Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: Western storeroom Friability: - Risk Rating: Secondary Location: elevation Surface Treatment: - Recommendation: - Comments: Lower wall sheeting to south elevation of west storeroom Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: Building 17 - Gatehouse (DEMOLISHED) Material Type: - Status of ACM: REMOVED Elevation: Ground Floor Quantity: - - - Sample #: - Position Installed: - Condition: - Sample Result: - Primary Location: - Friability: - Risk Rating: Secondary Location: - Surface Treatment: - Recommendation: - Comments: Building Identification Entry Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: Building 17 - Gatehouse (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 6 - m2 Sample #: N10101-S24 Position Installed: Soffit Condition: - Sample Result: Chrysotile Primary Location: External Friability: - Risk Rating: Secondary Location: To perimeter Surface Treatment: - Recommendation: - Comments: Soffit sheeting to all elevations. Sampled during previous assessment Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: Building 17 - Gatehouse (DEMOLISHED) Material Type: Vinyl Tile / Adhesive Status of ACM: REMOVED Elevation: Ground Floor Quantity: 5 - m2 Sample #: 32367A (VT) / 32367B (AD) Position Installed: Floor Finish / Covering Condition: - Sample Result: Chrysotile Primary Location: Storeroom Friability: - Risk Rating: Secondary Location: Interlaced with beige vinyl floor tiles Surface Treatment: - Recommendation: - Comments: Black vinyl tiles to floor in store room. No blackjack observed beneath (yellow non-asbestos tile adhesive present). Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: Building 17 - Gatehouse (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 8 - m2 Sample #: 32368 Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: Storeroom Friability: - Risk Rating: Secondary Location: Within former window cavities Surface Treatment: - Recommendation: - Comments: Infill panels to former window on elevation and surrounding window to east elevation Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: - Identified During Demolition - Site Grounds Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 5 - Sample #: CER1710111608-S02 Position Installed: Preformed Moulded Product Condition: - Sample Result: Chrysotile, Amosite Primary Location: External Friability: - Risk Rating: Secondary Location: Grounds Surface Treatment: - Recommendation: - Comments: Concrete Bollards Building 6 Exterior Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: - Identified During Demolition - Site Grounds Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 1 - lm Sample #: 53015 Position Installed: Stormwater Plumbing Condition: - Sample Result: Chrysotile Primary Location: External Friability: - Risk Rating: Secondary Location: Grounds Surface Treatment: - Recommendation: - Comments: Underground Stormwater Pipe Adjacent Building 6 Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: - Identified During Demolition - Site Grounds Material Type: Cement Status of ACM: REMOVED Elevation: Ground Floor Quantity: 57 - lm Sample #: Similar to 53018 Position Installed: Stormwater Plumbing Condition: - Sample Result: Chrysotile, Amosite Primary Location: External Friability: - Risk Rating: Secondary Location: Grounds Surface Treatment: - Recommendation: - Comments: Storm Water Pipe B7 NW Corner Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: - Identified During Demolition - Site Grounds Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 2 - lm Sample #: Similar to 53019 Position Installed: Stormwater Plumbing Condition: - Sample Result: Chrysotile, Amosite Primary Location: External Friability: - Risk Rating: Secondary Location: Grounds Surface Treatment: - Recommendation: - Comments: Water Pipe B6 West Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: - Identified During Demolition - Site Grounds Material Type: Cement Status of ACM: REMOVED Elevation: Ground Floor Quantity: 30 - lm Sample #: CER1711171156-S03 Position Installed: Stormwater Plumbing Condition: - Sample Result: Chrysotile, Amosite, Crocidolite Primary Location: External Friability: - Risk Rating: Secondary Location: Grounds Surface Treatment: - Recommendation: - Comments: B7 Underground Storm Water Pipe EW Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: - Identified During Demolition - Site Grounds Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 32 - lm Sample #: CER1711171156-S02 Position Installed: Pipe Condition: - Sample Result: Chrysotile, Crocidolite Primary Location: External Friability: - Risk Rating: Secondary Location: Grounds Surface Treatment: - Recommendation: - Comments: B9 Underground Conduit EW Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: - Identified During Demolition - Site Grounds Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 14 - m2 Sample #: Position Installed: - Refer to Comments Condition: - Sample Result: Chrysotile Primary Location: External Friability: - Risk Rating: Secondary Location: Grounds Surface Treatment: - Recommendation: - Comments: B6 Strip Footing Asbestos Formwork Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: - Identified During Demolition - Site Grounds Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 20 - m2 Sample #: Position Installed: - Refer to Comments Condition: - Sample Result: Chrysotile Primary Location: External Friability: - Risk Rating: Secondary Location: Grounds Surface Treatment: - Recommendation: - Comments: Building 6 Concrete Slab Packing Material (27 bins of contaminated concrete removed) Urgent Action Required? No
Location Details Material Details Results / Management Details Photographs Building ID: - Identified During Demolition - Site Grounds Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Quantity: Unknown - - Sample #: Similar to CER1711171156-S02 Position Installed: Pipe Condition: - Sample Result: Chrysotile, Crocidolite Primary Location: External Friability: - Risk Rating: Secondary Location: Outside of buildings B9 and B7 Surface Treatment: - Recommendation: - Comments: ACM conduit in ground out side of buildings B9 and B7 Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: - Identified During Demolition - Site Grounds Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 2 - items Sample #: CER1710171601-S04 Position Installed: Stormwater Plumbing Condition: - Sample Result: Chrysotile, Amosite Primary Location: External Friability: - Risk Rating: Secondary Location: Grounds Surface Treatment: - Recommendation: - Comments: B6 Stormwater Collar/Sleeve SW Corner Urgent Action Required? No