Reverse-Osmosis Systems Packaged Reverse-Osmosis systems De-Alkalizing Systems Package Water De-Alkalizing systems HVAC Noise and Vibration Control Noise and vibration levels for critical equipment such as Air Handlers, Chillers, Cooling Towers, Boilers, Generators, etc. will be commissioned as part of the system commissioning Direct Digital Control System** Operator Interface Computer, Operator Work Station (including graphics, mapping, trends, alarms), Network Communications Modules and Wiring, Integration Panels. [DDC Control panels will be commissioned with the systems controlled by the panel] Chilled Water System** Chillers (centrifugal, rotary screw, pumps (primary, secondary, variable primary), VFDs associated with chilled water system components, DDC Control Panels (including integration with Building Control System) Condenser Water System** Cooling Towers, Fluid Coolers, heat exchangers/economizers, pumps, VFDs associated with condenser water system components, DDC control panels. Steam/Heating Hot Water System** Boilers, boiler feed water system, economizers/heat recovery equipment, condensate recovery, water treatment, boiler fuel system, controls, interface with facility DDC system. HVAC Air Handling Systems** Air handling Units, packaged rooftop AHU, Outdoor Air conditioning units, humidifiers, DDC control panels
Grounding & Bonding Systems Witness 3rd party testing, review reports Electric Power Monitoring Systems Metering, sub-metering, power monitoring systems, PLC control systems Electrical System Protective Device Review reports, verify settings consistent with Study Secondary Unit Substations Medium-voltage components, transformers, distribution, verify breaker testing results (injection current, etc) Low-Voltage Distribution System Normal power distribution system, Life-safety power distribution system, critical power distribution system, equipment power distribution system, switchboards, distribution panels, panelboards, verify breaker testing results (injection current, etc) Emergency Generation Systems Generators, Generator paralleling switchgear, automatic transfer switches, PLC and other control systems Lighting & Lighting Control** Systems Emergency lighting, occupancy sensors, lighting control systems, architectural dimming systems, theatrical dimming systems, exterior lighting and controls Cathodic Protection Systems Review 3rd party testing results. Lightning Protection System Witness 3rd party testing, review reports Communications Grounding & Bonding System Witness 3rd testing, review reports Structured Cabling System Witness 3rd party testing, review reports
Master Antenna Television System Witness 3rd testing, review reports Public Address & Mass Notification Systems Witness 3rd party testing, review reports Intercom & Program Systems Witness 3rd party testing, review reports Call & Code Blue Systems Witness 3rd party testing, review reports Security Emergency Call Systems Witness 3rd party testing, review reports Duress Alarm Systems Witness 3rd party testing, review reports Electronic Safety and Security Grounding & Bonding Witness 3rd party testing, review reports Physical Access Control Systems Witness 3rd party testing, review reports Access Control Systems Witness 3rd party testing, review reports Security Access Detection Systems Witness 3rd testing, review reports Surveillance System Witness 3rd party testing, review reports Electronic Personal Protection System Witness 3rd party testing, review reports Fire Detection and Alarm System 100% device acceptance testing, battery test, verify system monitoring, verify interface with other systems. Renewable Energy Sources Geothermal Energy Electrical Generation Systems ** Geothermal well, DC-AC Inverters, storage batteries, turbine generator modules, switchgear, combiner instrumentation, monitoring and control systems Solar Energy Electrical Power Generation Systems ** Solar collector modules, DC-AC inverter, storage batteries, combiners, Switchgear, instrumentation, monitoring and control systems
OA HW Valve Position AI 15 Min 24 hours 3 days N/A OA Flow AI 15 Min 24 hours 3 days P ±10% from SP 5 min RA Flow AI 15 Min 24 hours 3 days P ±10% from SP 5 min Initial UVC Intensity (%) AI None None None N/A Duct Pressure AI 15 Min 24 hours 3 days C ±25% from SP 6 min CO2 Level AI 15 Min 24 hours 3 days P ±10% from SP 10 min Supply Fan Status DI COV 24 hours 3 days C Status <> Command 10 min Return Fan Status DI COV 24 hours 3 days C Status <> Command 10 Min High Static Status DI COV 24 hours 3 days P True 1 min Fire Status DI COV 24 hours 3 days C True 5 min Freeze Stat Level 1 DI COV 24 hours 3 days C True 10 min Freeze Stat Level 2 DI COV 24 hours 3 days C True 5 min Freeze Stat 3 DI COV 24 hours 3 days P True 1 min Fire/Smoke Damper Status DI COV 24 hours 3 days P Closed 1 min Emergency AHU Shutdown DI COV 24 hours 3 days P True 1 min Exhaust Fan #1 Status DI COV 24 hours 3 days C Status <> Command 10 min Exhaust Fan #2 Status DI COV 24 hours 3 days C Status <> Command 10 min Exhaust Fan #3 Status DI COV 24 hours 3 days C Status <> Command 10 min OA DI COV 24 hours 3 days C True 10 min High Static Alarm DI COV 24 hours 3 days C True 10 min UVC Emitter Alarm DI COV 24 hours 3 days P True 10 min
CO2 DI COV 24 hours 3 days P True 10 min Power Failure DI COV 24 hours 3 days P True 1 min Supply Fan AO 15 Min 24 hours 3 days N/A Return Fan Speed AO 15 Min 24 3 days N/A RA CHW Valve Position AO 15 Min 24 hours 3 days N/A OA CHW Valve Position AO 15 Min 24 hours 3 days N/A OA HW Valve Position AO 15 Min 24 hours 3 days N/A Supply Fan S/S DO COV 24 hours 3 days N/A Return Fan S/S DO COV 24 hours 3 days N/A Fire/Smoke Dampers DO COV 24 3 days N/A Exhaust Fan S/S DO COV 24 hours 3 days N/A Exhaust Fan S/S DO COV 24 hours 3 days N/A Exhaust Fan S/S DO COV 24 hours 3 days N/A AHU Energy Calc 1 Hour 30 day N/A N/A Terminal Unit (VAV, CAV, etc.) Trending and Alarms Point Type Trend Interval Trend Duration Testing Trend Duration Alarm Type Alarm Range Alarm Delay Space Temperature AI 15 Min 12 hours 3 days P ±5°F from SP 10 min Air Flow AI 15 Min 12 hours 3 days P ±5°F from SP 10 min SA Temperature AI 15 Min 12 hours 3 days P ±5°F from SP 10 min Local Setpoint AI 15 Min 12 hours 3 days M ±10°F from SP 60 min
Humidity AI 15 Min 12 hours 3 days P > 60% RH 5 min Unoccupied Override DI COV 12 hours 3 days M N/A 12 Hours Refrigerator Alarm DI COV 12 hours 3 days C N/A 10 min Damper Position AO 15 Minutes 12 hours 3 days N/A Heating coil Valve Position AO 15 Minutes 12 hours 3 days N/A 4-Pipe Fan Coil Trending and Alarms Point Type Interval Trend Duration Testing Trend Duration Type Alarm Range Alarm Delay Space Temperature AI 15 Minutes 12 hours 3 days P ±5°F from SP 10 min SA Temperature AI 15 Minutes 12 3 days P ±5°F from SP 10 min Pre-Filter Status AI None None None M > SP 1 hour Water Sensor DI COV 12 hours 3 days M N/A 30 Min Cooling Coil Valve Position AO 15 Minutes 12 3 days N/A Heating coil Valve Position AO 15 Minutes 12 hours 3 days N/A Fan Coil ON/OFF DO COV 12 hours 3 days M Status <> Command 30 min
2-Pipe Fan Coil Unit Trending and Alarms Type Interval Trend Duration Testing Trend Duration Alarm Type Range Alarm Delay Temperature AI 15 Minutes 12 hours 3 days P ±5°F from SP 10 min SA Temperature AI 15 Minutes 12 hours 3 days P ±5°F from SP 10 min Pre-Filter Status AI None None None M > SP 1 hour Water Sensor DI COV 12 hours 3 days M N/A 30 Min Cooling Coil Valve Position AO 15 Minutes 12 hours 3 days N/A Fan Coil ON/OFF DO COV 12 hours 3 days M Status <> Command 30 min Unit Heater Trending and Alarms Point Type Trend Interval Trend Duration Testing Trend Duration Alarm Type Alarm Range Alarm Delay Space Temperature AI 15 Minutes 12 hours 3 days P ±5°F from SP 10 min Heating Valve Position AO 15 Minutes 12 hours 3 days N/A Unit Heater ON/OFF DO COV 12 hours 3 days M Status <> Command 30 min Steam and Condensate Pumps Trending and Alarms Point Type Trend Interval Trend Duration Testing Trend Duration Alarm Type Alarm Range Alarm Delay Flow (LB/HR) AI 15 Minutes 12 hours 3 days N/A Condensate Pump Run Hours AI 15 Minutes 12 hours 3 days N/A
Water Meter (GPM) AI 15 Minutes 12 3 days N/A Electric (KW/H) AI 15 Minutes 12 hours 3 days N/A Irrigation Meter (GPM) AI 15 Minutes 12 3 days N/A Chilled Water Flow (TONS) AI 15 Minutes 12 hours 3 days N/A Condensate Flow (GPM) AI 15 Minutes 12 hours 3 days N/A High Water Level Alarm DI COV 12 hours 3 days C True 5 Min Condensate Pump Start/Stop DO COV 12 hours 3 days P Status <> Command 10 min Domestic Hot Water Trending and Alarms Type Trend Interval Trend Duration Testing Trend Duration Type Alarm Range Alarm Delay Domestic HW Setpoint WH-1 AI 15 Minute 12 Hours 3 days N/A Domestic HW Setpoint WH-2 AI 15 Minute 12 Hours 3 days N/A Domestic HW Temperature AI 15 Minute 12 Hours 3 days C > 135 oF 10 Min Domestic HW Temperature AI 15 Minute 12 Hours 3 days P ±5°F from SP 10 Min Dom. Circ. Pump #1 Status DI COV 12 Hours 3 days M Status <> Command 30 min Dom. Circ. Pump #2 Status DI COV 12 3 days M Status <> Command 30 min Dom. Circ. Pump #1 DO COV 12 Hours 3 days N/A Dom. Circ. Pump #2 Start/Stop DO COV 12 Hours 3 days N/A
Domestic HW Start/Stop DO COV 12 3 days N/A Hydronic Hot Water Trending and Alarms Type Interval Trend Duration Testing Trend Duration Alarm Type Alarm Range Alarm Delay System HWS Temperature AI 15 min 12 hours 3 days C ±5°F from SP 10 Min System HWR Temperature AI 15 min 12 hours 3 days M ±15°F from SP 300 Min HX-1 Entering Temperature AI 15 min 12 hours 3 days P ±5°F from SP 10 Min HX-2 Entering Temperature AI 15 min 12 hours 3 days P ±5°F from SP 10 Min HX-2 Leaving Temperature AI 15 min 12 hours 3 days P ±5°F from SP 10 Min System Flow (GPM) AI 15 min 12 hours 3 days N/A System Differential Pressure AI 15 min 12 hours 3 days P ±10% from SP 8 Min 3 days HW Pump 1 Status DI COV 12 Hours 3 days C Status <> Command 30 min HW Pump 2 Status DI COV 12 Hours 3 days C Status <> Command 30 min HW Pump 1 VFD AO 15 Min 12 Hours 3 days N/A HW Pump 2 VFD AO 15 Min 12 Hours 3 days N/A Steam Station #1 1/3 Control Valve Position AO 15 Min 12 Hours 3 days N/A Steam Station #1 2/3 Control Valve Position AO 15 Min 12 Hours 3 days N/A
Steam Station #2 1/3 Control Valve Position AO 15 Min 12 Hours 3 days N/A Steam Station #2 2/3 Control Valve Position AO 15 Min 12 Hours 3 days N/A Steam Station Bypass Valve Position AO 15 Min 12 Hours 3 days N/A HW Pump 1 Start/Stop DO COV 12 Hours 3 days N/A HW Pump 2 Start/Stop DO COV 12 Hours 3 days N/A HWR #1 Valve DO COV 12 Hours 3 days N/A HWR #2 Valve DO COV 12 3 days N/A Chilled Water System Trending and Alarms Point Type Trend Interval Trend Duration Testing Trend Duration Alarm Type Alarm Range Alarm Delay Chiller 1 Entering Temperature AI 15 Minutes 12 Hours 3 days N/A Chiller 1 Leaving Temperature AI 15 Minutes 12 Hours 3 days P ±5°F from SP 10 Min Chiller 1 Flow AI 15 Minutes 12 Hours 3 days N/A Chiller 1 Percent Load AI 15 Minutes 12 Hours 3 days N/A Chiller 1 KW Consumption AI 15 Minutes 12 Hours 3 days N/A Chiller 1 Tonnage AI 15 Minutes 12 Hours 3 days N/A Chiller 2 Entering Temperature AI 15 Minutes 12 Hours 3 days N/A Chiller 2 Leaving Temperature AI 15 Minutes 12 Hours 3 days P ±5°F from SP 10 Min Chiller 2 Flow AI 15 Minutes 12 Hours 3 days N/A
Chiller 1 Evaporator Flow Switch DI COV 12 Hours 3 days N/A Chiller 1 Unit DI COV 12 Hours 3 days C True 10 Min Chiller 2 Status DI COV 12 Hours 3 days C Status <> Command 30 min Chiller 2 Evaporator Iso-Valve DI COV 12 Hours 3 days N/A Chiller 2 Evaporator Flow Switch DI COV 12 Hours 3 days N/A Chiller 2 Unit Alarm DI COV 12 3 days C True 10 Min Refrigerant Detector DI COV 12 Hours 3 days C True 10 Min Refrigerant Exhaust Fan Status DI COV 12 Hours 3 days M Status <> Command 30 min Emergency Shutdown DI COV 12 3 days P True 1 Min Primary Loop Pump 1 VFD Speed AO 15 Minutes 12 Hours 3 days N/A Primary Loop Pump 2 VFD Speed AO 15 Minutes 12 Hours 3 days N/A Secondary Loop Pump 1 VFD Speed AO 15 Minutes 12 Hours 3 days N/A Secondary Loop Pump 2 VFD Speed AO 15 Minutes 12 3 days N/A Primary Pump 1 / Stop DO COV 12 Hours 3 days N/A Primary Pump 2 Start / Stop DO COV 12 Hours 3 days N/A Secondary Pump 1 Start / Stop DO COV 12 Hours 3 days N/A Secondary Pump 2 Start / Stop DO COV 12 Hours 3 days N/A
Chiller 1 Enable DO COV 12 Hours 3 days N/A Chiller 1 Iso-Valve Command DO COV 12 Hours 3 days N/A Chiller 2 Enable DO COV 12 3 days N/A Chiller 2 Iso-Valve Command DO COV 12 Hours 3 days N/A Refrigerant Exhaust Fan Start / Stop DO COV 12 Hours 3 days N/A Condenser Water System Trending and Alarms Point Type Interval Duration Testing Trend Duration Alarm Type Alarm Range Alarm Delay Chiller 1 Condenser Entering Temp AI 15 Minutes 12 Hours 3 days N/A Chiller 1 Condenser Leaving Temp AI 15 Minutes 12 3 days N/A Chiller 2 Condenser Entering Temp AI 15 Minutes 12 Hours 3 days N/A Chiller 2 Condenser Leaving Temp AI 15 Minutes 12 Hours 3 days N/A Cooling Tower 1 Supply Temp AI 15 Minutes 12 Hours 3 days N/A Cooling Tower 1 Return Temp AI 15 Minutes 12 3 days N/A Cooling Tower 1 Basin Temp AI 15 Minutes 12 Hours 3 days P < 45 oF 10 Min Cooling Tower 2 Supply Temp AI 15 Minutes 12 3 days N/A Cooling Tower 2 Return Temp AI 15 Minutes 12 3 days N/A Cooling Tower 2 Basin Temp AI 15 Minutes 12 3 days P < 45 oF 10 Min Condenser Water Supply Temp AI 15 Minutes 12 Hours 3 days N/A
Condenser Water Return Temp AI 15 Minutes 12 3 days N/A Outdoor Air Wet Bulb AI 15 Minutes 12 Hours 3 days N/A Cooling 1 Fan Status DI COV 12 Hours 3 days P Status <> Command 1 min Cooling Tower 1 Basin Heat DI COV 12 Hours 3 days N/A Cooling 1 Heat Trace DI COV 12 3 days N/A Cooling 2 Fan Status DI COV 12 3 days P Status <> Command 1 min Cooling Tower 2 Basin Heat DI COV 12 Hours 3 days N/A Cooling Tower 2 Heat Trace DI COV 12 Hours 3 days N/A Chiller 1 Isolation Valve DI COV 12 Hours 3 days P Status <> Command 1 min Chiller 2 Isolation Valve DI COV 12 3 days P Status <> Command 1 min Condenser Water Pump 1 Status DI COV 12 Hours 3 days P Status <> Command 1 min Condenser Water Pump 2 Status DI COV 12 Hours 3 days P Status <> Command 1 min Chiller 1 Condenser Bypass Valve AO 15 Minutes 12 Hours 3 days N/A Chiller 2 Condenser AO 15 Minutes 12 Hours 3 days N/A Cooling Tower 1 Bypass Valve AO 15 Minutes 12 Hours 3 days N/A Cooling 1 Fan Speed AO 15 Minutes 12 3 days N/A Cooling Tower 2 Bypass Valve AO 15 Minutes 12 3 days N/A Cooling Tower 2 Fan Speed AO 15 Minutes 12 Hours 3 days N/A
Cooling Tower 1 Fan Start / Stop DO COV 12 Hours 3 days N/A Cooling Tower 2 Fan Start / Stop DO COV 12 Hours 3 days N/A Condenser Water Pump 1 Start / Stop DO COV 12 3 days N/A Condenser Water Pump 2 Start / Stop DO COV 12 Hours 3 days N/A Steam Boiler System Trending and Alarms Point Type Trend Interval Duration Testing Trend Duration Alarm Type Alarm Range Delay Boiler 1 Steam Pressure AI 15 Minutes 12 Hours 3 days P ±5% from SP 10 Min Boiler 1 Steam Temperature AI 15 Minutes 12 Hours 3 days N/A Boiler 1 Fire Signal AI 15 Minutes 12 Hours 3 days N/A Boiler 2 Steam Pressure AI 15 Minutes 12 Hours 3 days P ±5% from SP 10 Min Boiler 2 Steam Temperature AI 15 Minutes 12 Hours 3 days N/A Boiler 2 Fire Signal AI 15 Minutes 12 Hours 3 days N/A System Steam Pressure AI 15 Minutes 12 Hours 3 days P ±5% from SP 10 Min Boiler 1 Enable DI COV 12 3 days N/A Boiler 1 Status DI COV 12 Hours 3 days P Status <> Command 10 min Boiler 1 Alarm DI COV 12 Hours 3 days C True 1 Min
Hot Water Boiler System Trending and Alarms Point Type Trend Interval Duration Testing Duration Type Alarm Range Alarm Delay Outside Air Temperature AI 15 Minutes 12 3 days N/A Boiler 1 Fire Signal AI 15 Minutes 12 Hours 3 days N/A Boiler 1 Entering Temperature AI 15 Minutes 12 3 days N/A Boiler 1 Leaving Water Temperature AI 15 Minutes 12 Hours 3 days N/A Boiler 2 Fire Signal AI 15 Minutes 12 Hours 3 days N/A Boiler 2 Entering Water Temperature AI 15 Minutes 12 Hours 3 days N/A Boiler 2 Leaving Water Temperature AI 15 Minutes 12 Hours 3 days N/A Hot Water Supply Temperature AI 15 Minutes 12 Hours 3 days P ±5 oF from SP 10 Min Hot Water Return Temperature AI 15 Minutes 12 Hours 3 days N/A Secondary Loop Differential Pressure AI 15 Minutes 12 Hours 3 days C ±5% from SP 10 Min Lead Boiler AI 15 Minutes 12 Hours 3 days N/A Boiler 1 Enable DI COV 12 Hours 3 days N/A Boiler 1 Status DI COV 12 Hours 3 days P Status <> Command 10 min Boiler 1 Isolation Valve DI COV 12 Hours 3 days N/A Boiler 1 on Fuel Oil DI COV 12 Hours 3 days N/A Boiler 1 Alarm DI COV 12 Hours 3 days C True 1 Min Boiler 2 Enable DI COV 12 Hours 3 days N/A
Boiler 2 Status DI COV 12 Hours 3 days P Status <> Command 10 min Boiler 2 Isolation Valve DI COV 12 Hours 3 days N/A Boiler 2 on Fuel Oil DI COV 12 3 days N/A Boiler 2 Alarm DI COV 12 Hours 3 days C True 1 Min Combustion Dampers Open DI COV 12 Hours 3 days P Status <> Command 10 min Primary Pump 1 Status DI COV 12 Hours 3 days P Status <> Command 10 min Primary Pump 2 Status DI COV 12 Hours 3 days P Status <> Command 10 min Secondary Pump 1 Status DI COV 12 3 days P Status <> Command 10 min Secondary Pump 2 Status DI COV 12 Hours 3 days P Status <> Command 10 min Primary Pump 1 VFD Speed AO COV 12 Hours 3 days N/A Primary Pump 2 VFD Speed AO COV 12 Hours 3 days N/A Secondary Pump 1 VFD AO COV 12 Hours 3 days N/A Secondary Pump 2 VFD AO COV 12 Hours 3 days N/A Hot Water System Enable DO COV 12 Hours 3 days N/A Combustion Dampers Command DO COV 12 Hours 3 days N/A Primary Pump 1 Start / Stop DO COV 12 Hours 3 days N/A Primary Pump 2 Start / Stop DO COV 12 Hours 3 days N/A