Firmware Upgrade Kit: For Owner to use in modifying firmware to suit future power system revisions or advanced utility metering system revisions. Firmware updates, and necessary software tools for firmware updates, shall be downloadable from the internet. VA shall be able to update firmware, in equipment, without removing device from the equipment. VA shall be capable of updating firmware over the utility metering communication network or through local communication ports on the device. Software licenses and upgrades required by and installed for operating and programming digital and analog devices. Qualification Data: For installer and manufacturer Other Informational Submittals: System installation and setup guides, with data forms to plan and record options and setup decisions. Revise and update the Contract Drawings to include details of the system design. Drawings shall be on 17 by 11 inches sheets. Details to be shown on the Design Drawing include: Details on logical structure of the network. This includes logical location of all network hardware. Manufacturer and number for each piece of computer and network hardware. Physical location for each piece of network or computer hardware. Physical routing of LAN cabling. Physical and qualitative descriptions of connectivities. //Completed System Readiness Checklist provided by the Commissioning Agent and completed by the contractor, signed by a qualified technician and dated on the date of completion, in accordance with the requirements of Section 01 91 00, GENERAL COMMISSIONING REQUIREMENTS.// //Submit training plans and instructor qualifications in accordance with the requirements of Section 01 91 00, GENERAL COMMISSIONING REQUIREMENTS.// CLOSEOUT SUBMITTALS Operation and Maintenance Data: For advanced utility metering system components and meters, to include in emergency, operation, and maintenance manuals. Include the following: Operating and applications software documentation. Software licenses. Software service agreement.
AS-BUILT DOCUMENTATION SPEC WRITER NOTE: Coordinate O&M Manual requirements with Section 01 00 01, GENERAL REQUIREMENTS NCA Projects) or Section 01 00 02, GENERAL REQUIREMENTS (Minor NCA Projects). O&M manuals shall be submitted for content review as part of the close-out documents. Submit manufacturer’s literature and data updated to include submittal review comments and any equipment substitutions. Submit operation and maintenance data updated to include submittal review comments, substitutions and construction revisions be //in electronic version on CD or DVD// inserted into a three ring binder. All aspects of system operation and maintenance procedures, including applicable piping isometrics, wiring diagrams of all circuits, a written description of system design, control logic, and sequence of operation shall be included in the operation and maintenance manual. The operations and maintenance manual shall include troubleshooting techniques and procedures for emergency situations. Notes on all special systems or devices shall be included. A List of recommended spare parts (manufacturer, model number, and quantity) shall be furnished. Information explaining any special knowledge or tools the owner will be required to employ shall be inserted into the As-Built documentation. The installing contractor shall maintain as-built drawings of each completed phase for verification; and, shall provide the complete set at the time of final systems certification testing. As-built drawings are to be provided, and a copy of them in Auto-CAD version //____// provided on CD or DVD. Should the installing contractor engage the testing company to provide as-built or any portion thereof, it shall not be deemed a conflict of interest or breach of the ‘third party testing company’ requirement. Certification documentation shall be provided to COR 10 working days prior to submitting the request for final inspection. The documentation shall include all test results, the names of individuals performing work for the testing agency on this project, detailed procedures followed for all tests, and certification that all results of tests were within limits specified.
Meter shall be suitable for 25 percent warmer than the fluid operating temperature and for 25 percent higher than either the fluid’s operating pressure or 25 percent higher than the piping system’s safety valve set pressure, whichever is higher. Meter flanges shall be Class 300 or higher, if required by the piping system’s temperature and pressure Class. Meter shall be suitable for installation in ambient conditions ranging from -29 to 60 degrees C (-20 to 140 degrees F). Provide meter data head. Meters have digital readout of pressure-compensated flow rate and totalization located at transmitter and transmit flow rate and totalization digital signals to the Site Data Aggregation Device// and recorders//. Provide programmable microprocessor electronics with on-board programming. Output signals shall be immune to ambient temperature swings. Processor shall include continuous self-diagnostic routines that identify electronics problems and provide a warning. Electronics shall be replaceable in the field without affecting metering accuracy. Provide power supply as recommended by meter manufacturer. Mount electronics in a NEMA 4 enclosure separate from meter body in position accessible from platform or floor without the use of a portable ladder. Power supply to meter and transmitter shall be 120V/60Hz. Provide a Class 2 control voltage transformer for 24 VDC power to meter as needed. Provide an internal battery, provided for 24-month retention of RAM contents when all other power sources are removed. Performance: Transmitted signal from flowmeter and its transmitter shall have a total (rms) accuracy plus or minus 1.5 percent of flow rate. Flowmeter accuracy shall be no more than plus or minus 1 percent of span for gasses and plus or minus 0.7 percent of span for liquids. Flowmeter repeatability shall be no more than 0.2 percent of actual flow rate. Meter shall be designed to minimize vibration effect and to provide elimination of this effect. Minimum turndown ratio shall be 20:1 for gasses and liquids. Maximum fluid pressure drop shall be as scheduled.