Electronic governing type maximum 1,800 RPM at 60 Hz and average 1,500 RPM at 50 Hz Engine electrical System – Voltage 24, Ground negative Voltage – 230V/400V Frequency – 50 Hz (European standard only) Prime Power – 450 to 510 kVA Governing Class: ISO 8528 G2 (Generating sets that are used to generate electrical power for continuous, peak-load and standby applications) Fuel system - Diesel mandatory Oil Cooling method – water Control – Digital Diagnostic & Internet Monitoring System showing - power output: water temperature: oil pressure: running hours: Amps: Volts: Hertz Base Frame – Heavy Duty Fabricated Steel Circuit Breaker Type – 3 pole MCCB Fuel capacity – For a running time minimum of 24 hours at maximum 70% Load
Operative Frequency – 47-65 Hz Line input protection – Overcurrent, Low and High voltage protection Output Voltage – 380 VAC RMS+-%2 Overloading – 10sec. %200 load Correction Speed -90 Volt/sec Upturn speed – 90Volt.Sec. (160 VAC – 250 VAC) Output protection – protects load by opening the circuit when overburden, short circuit occurs Working Principle – Servo Motor, Microprocessor controlled, Full Automatic Measured Monitor – Output voltage and line voltage monitorization Warranty: 1 year starting from the date of its provisional acceptance by the EUMM Quantity: 3 units 4 Stabilizer (minimum 400 kVA) Full Automatic Triphase
3 phase IN, 3 phase OUT Regulates main voltage Non linear charges Fast regulation Load transfer to Bypass via pole charge switch Overcurrent and overload protection Digitally displayed status showing Input & Output of – Volts, Amps & Hertz Minimum Power kVA – 400 In. Voltage Current Interval – 275-450 VAC In. Voltage working Interval – 155-490 VAC Operative Frequency – 47-65 Hz Line protection – Overcurrent, Low and High voltage protection Output Voltage – 380 VAC RMS+-%1 Overloading – %200 load Correction - 90 Volt/sec Upturn – 90Volt.Sec. (160 VAC – 250 VAC)
ADMINISTRATIVE COMPLIANCE GRID [To be completed by the Evaluation Committee] Contract title : Supply, delivery, installation and commissioning of generators and stabilizers at various premises operated by the EUMM Georgia Publication reference : EUROPEAID/139244/DH/SUP/GE Tender envelope number Name of Tenderer Is tenderer (consortium) nationality eligible? (Y/N) Is documentation complete? (Y/N) Is language as required? (Y/N) Is tender submission form complete? (Y/N) Is tenderer's declaration signed (by all consortium members if a consortium)? (Yes/No/ Not Applicable) administrative requirements of the tender dossier? (Yes/No/Not applicable) Overall decision? (Accept / Reject) 1 2 3 4 5 6 7 Chairperson's name Chairperson's signature Date
EVALUATION GRID [To be completed by the Evaluation Committee] Contract title : Supply, delivery, installation and commissioning of generators and stabilizers at various premises operated by the EUMM Georgia Publication reference : EUROPEAID/139244/DH/SUP/GE Tender envelope No Name of Tenderer of origin respected? (Y/N) Economic & financial capacity? (OK/a/b/…) Professional capacity? (OK/a/b/…) Technical capacity? (OK/a/b/…) Compliance with technical specifications? (OK/a/b/…) Ancillary services as required? (OK/a/b/…/NA) Subcontracting statement in accordance with art 6 of the General Conditions? (Y/N) Other technical requirements in tender dossier? (Yes/No/Not applicable) Technically compliant? Y/N) Justification/ notes: 1 2 3 4 Evaluator's name & signature Evaluator's name & signature Evaluator's name & signature Date [PROVISIONAL / FINAL] ACCEPTANCE CERTIFICATE
4 STAFF RESOURCES Please provide the following personnel statistics for the current year and the two previous Annual manpower Year before past year Past year Current year Period average Overall Relevant fields Overall Relevant fields 22 Overall Relevant fields22 Overall Relevant fields22 Permanent Other staff Total Permanent staff as a proportion of total staff (%) % % % % % % % %