MEDICAL SURVEILLANCE PROGRAM SUMMARY RECORDED BY: Brian Roethlisberger UIC NUMBER: N93171 COMMAND: MCCS SIGNATURE: //S// Shop Process Recommended Medical Surveillance # Of Personnel Barbers Physical Activity Center, Russell Knox Fitness Center Fitness training/instruction, laundry Blood and Body Fluids 31 Bowling Center Cleaning pin setting equipment, Customizing bowling balls Food preparation/handling Food Preparation and Service 2 5 Building & Grounds Groundskeeping, pressure washing Noise 7 Development Centers Child care Food preparation/handling Blood and Body Fluids Food Preparation and Service 178 178 Clubs of Quantico Food preparation/handling Janitorial/Custodial Food Preparation and Service and Body Fluids 34 6 Director’s Office Janitorial/Custodial Blood and Body Fluids 1 Golf Course Maintenance Mixing and applying pesticides, herbicides, and fungicides Respirator User 1 Golf Course Maintenance Groundskeeping 6 Marina Sanding and painting watercraft hulls Respirator User 2 Marine Corps Exchange Warehouse Materials supply and handling Forklift Operator 4 Mulligan’s Food preparation/handling Food Preparation and Service 5 Starbucks (MCX and Hawkins) Food preparation/handling Food Preparation and Service 15 Little Hall Theater Food preparation/handling Food Preparation and Service 4 Marine Mart (Mainside and TBS) Food preparation/handling Food Preparation and Service 20 Package Food preparation/handling Food Preparation and Service 15 Swimming Pool Swimming pool operation Blood and Body Fluids 30 Youth Services Child care Blood and Body Fluids 10
LOCAL EXHAUST VENTILATION EVALUATION SUMMARY COMMAND: MCCS BUILDING/LOCATION: 2080, Room 116 SHOP: Auto Skills Shop DATE: 17 December 2014 TYPE: Movable Welding Exhaust Hood Measurement Type Measurement Location Test Face Velocity, vertical Top Middle Bottom Adequate capture 1340 fpm 1660 fpm 1560 fpm Face Velocity, horizontal Left Center Right 1780 fpm 1660 fpm 1560 fpm Area of hood face: 2.67 ft2 Calculated volumetric flow (Q): 4,202 cubic feet per minute (cfm) Required volumetric flow (Q) at 16”: 1,916 cfm Results: When hood is positioned 16” or closer to the source, velocity is sufficient for the capture of welding fumes of moderate toxicity Note: fpm=feet per minute LOCAL EXHAUST VENTILATION EVALUATION SUMMARY COMMAND: MCCS BUILDING/LOCATION: 3167, Wood Shop SHOP: Facilities Maintenance DATE: 17 December 2014 TYPE: Stationary Woodworking Equipment Equipment Measured Volumetric Flow Rate (cfm) Required Volumetric Flow Rate (cfm) Meets Required Standard? Test Comments Rockwell Delta 10” UniSaw 1277 545 Y Adequate Capture All other component blast gates CLOSED during measurement 521 545 N Adequate Capture All other component blast gates OPEN during measurements Delta 12” Radial Arm Saw 504 430 Y Adequate Capture All other component blast gates CLOSED during measurement. Although the available dust capture hood meet specified requirements, it was located to far from the saw blade to provide adequate capture. The blade shroud ventilation available on the saw was not connected to the ventilation system. 398 430 N Adequate Capture All other component blast gates OPEN during measurements Milwaukee 12” Saw 109 100 Y Adequate Capture All other component blast gates CLOSED during measurement 47 100 N Adequate Capture All other component blast gates OPEN during measurements
Powermatic 15” Planer 790 785 Y Adequate Capture All other component blast gates CLOSED during measurement 262 785 N Adequate Capture All other component blast gates OPEN during measurements EXHAUST VENTILATION EVALUATION SUMMARY COMMAND: MCCS BUILDING/LOCATION: 3167, Wood Shop SHOP: Facilities Maintenance DATE: 17 December 2014 TYPE: Stationary Woodworking Equipment Equipment Measured Volumetric Flow Rate (cfm) Required Volumetric Flow Rate (cfm) Meets Required Standard? Smoke Test Comments Dewalt Compound Mitre Saw 110 100 Y Adequate Capture All other component blast gates CLOSED during measurement 28 100 N Adequate Capture All other component blast gates OPEN during measurements Note: fpm=feet per minute