RELATED REQUIREMENTS Specifier Notes: Edit the following list of related sections as required for the Project. Limit the list to sections with specific information that the reader might expect to find in this Section, but is specified elsewhere. Section 22 13 00 – Facility Sanitary Sewerage. REFERENCE STANDARDS Specifier Notes: List reference standards used elsewhere in this Section, complete with designations and titles. Delete reference standards from the following list not used in the edited Section. CSA Group (CSA) (www.csagroup.org): CSA B481 – Series of Standards, Grease Interceptors. International Organization for Standardization (ISO) (): ISO 9001 – Quality management systems – Requirements. The American Society of Mechanical Engineers (ASME) (): ASME A112.14.3 – Grease Interceptors. The International Association of Plumbing & Mechanical Officials (IAPMO) (www.iapmo.org): IAPMO/ANSI Z1001 – Prefabricated Gravity Grease Interceptors. Specifier Notes: Include the following reference standard when specifying “SuperMax model SM-MI-G-PL-500” grease interceptor with the -PDI option. The Plumbing and Drainage Institute (PDI) (): PDI-G101 – Testing and Rating Procedure for Hydro Mechanical Grease Interceptors with Appendix of Installation and Maintenance. PREINSTALLATION MEETINGS Specifier Notes: Edit the Preinstallation Meetings article as required for the Project. Delete this article if not required. Convene preinstallation meeting [1 week] [2 weeks] before start of installation of interceptors. Require attendance of parties directly affecting Work of this Section, including Contractor, Architect, installer, and manufacturer’s representative. Review the Following: Materials. Installation. Protection. Coordination with other Work.
SUBMITTALS Specifier Notes: Edit the Submittals article as required for the Project. Delete submittals not required. Submittals: Comply with Division 01. Product Data: Submit manufacturer’s product data, including installation instructions. Manufacturer’s Certification: Submit manufacturer’s certification that materials comply with specified requirements and are suitable for intended application. Manufacturer’s Project References: Submit manufacturer’s list of 10 successfully completed interceptor projects of similar size and scope to this Project, including project name and location, name of architect, and type and quantity of interceptors furnished. Installer’s Project References: Submit installer’s list of 5 successfully completed interceptor projects of similar size and scope to this Project, including project name and location, name of architect, and type and quantity of interceptors installed. Warranty Documentation: Submit manufacturer’s standard warranty. QUALITY ASSURANCE Manufacturer’s Qualifications: Manufacturer regularly engaged in the manufacturing of interceptors of similar type to that specified for a minimum of 10 years. ISO 9001 certified company. Installer's Qualifications: Installer regularly engaged in installation of interceptors of similar type to that specified for a minimum of 5 years. Use persons trained for installation of interceptors. DELIVERY, STORAGE, AND HANDLING Delivery Requirements: Deliver materials to site in manufacturer’s original, unopened containers and packaging, with labels clearly identifying product name and manufacturer. Storage and Handling Requirements: Store and handle materials in accordance with manufacturer’s instructions. Keep materials in manufacturer’s original, unopened containers and packaging until installation. Store materials in clean, dry area indoors. Do not store materials directly on floor. Protect materials during storage, handling, and installation to prevent damage. WARRANTY Warranty Period: Limited lifetime.