Because all devices in this series have similar functions, it would also be possible to work through the chapters of this document with a different device version in this series. Advanced Runtime Simulation can also be used to represent the TP700 Touch Panel on the PC (included in the product package of the SCE Trainer Package SIMATIC HMI TP700 COMFORT PANEL). Front view of the TP700 Comfort Touchscreen display Rear view of the TP700 Comfort ① Rating plate ② for SD memory cards Interfaces of the Comfort ① Connection for supply ② Connection for equipotential bonding (ground) ③ PROFIBUS (Sub-D RS422/485) ④ 2x USB type A ⑤ PROFINET (LAN), 10/100 Mbit, 2 ⑥ Audio Line IN/OUT ⑦ USB type Mini-B Memory concept The HMI devices can use the following memory: – Internal memory – System memory card – Memory card – USB mass storage connected to the USB port Internal memory The following data is stored here: – Operating system – Project file – License keys – User management
I 0.2 BOOL -S0 Mode selector manual (0)/ automatic (1) Manual = 0 Auto = 1 I 0.3 BOOL -S1 Pushbutton "Automatic Start" NO I 0.4 BOOL -S2 Pushbutton "Automatic Stop" NC I 0.5 BOOL -B1 Sensor cylinder -M4 retracted NO I 1.0 BOOL -B4 Sensor part at slide NO I 1.3 BOOL -B7 Sensor part at end of conveyor NO IW64 BOOL -B8 Sensor actual value speed of the motor +/-10V corresponds to +/- 50 rpm DO Type Identifier Function Q 0.2 BOOL -Q3 Conveyor motor M1 variable speed QW 64 BOOL -U1 Manipulated speed of the motor in two directions +/-10V corresponds to +/-50 rpm Legend for reference list DO Digital output AO Analog output O Output DI Digital input AI Analog input I Input NC Normally Closed NO NO Normally Open Structured step-by-step instructions You can find instructions on how to out planning below. If you already have a good understanding of everything, it will be sufficient to focus on the numbered steps. Otherwise, follow the individual instructions in the steps below. Retrieving an existing project Before you can expand the "SCE_EN_032-600_Global_Data_Blocks_R1508.zap13" project from chapter "SCE_EN_032-600_Global_Data_Blocks", you must retrieve this project from the archive. To retrieve an existing project that has been archived, you must
Under "Label" in "Properties", select  "Label". Under "Unit" select  rpm. Under "Decimal places", select  2. Under "Layout" in "Properties", adapt the position and size of the bar under  "Position & Size". Above the bar diagram, insert a  "Text field" for the description with text  "Actual speed value". In order to specify the speed setpoint, move the "IO field" object from  "Elements" in "Tools" to a location above and to the right of the bar display. Under "General" in "Properties" keep the "Type" as "Input/Output" and change the "Format pattern" to  s99.99. For the process connection, select the  "Program blocks" of the  "CPU_1516F" and the  "SPEED_MOTOR[DB2]" data block there. Now drag the "Speed setpoint" tag from the  "Detail view" into the field for "Tag". Under "Appearance" in "Properties", change the "Color" of the "Background" to  "Blue". "Text format" in "Properties", change the "Horizontal" setting of "Alignment" to  "Right". Under "Layout" in "Properties", adapt the position and size of the IO field under  "Position & Size". Above the bar diagram, insert a  "Text field" for the description with text  "Speed setpoint".
"General" in "Properties", activate "Pending alarms" and "Unacknowledged alarms". Activate "Errors", "Warnings" and "No Acknowledgment" as alarm classes. Note: You will create alarm classes of types "Errors" and "Warnings" in the panel itself in the following steps. The alarm class of the "No acknowledgment" type is produced automatically by the settings for the system diagnostics in the CPU 1516F. Under "Miscellaneous" in "Properties", change the "Name" to  "Alarm window_pending_not_acknowledged". "Mode" in "Properties", change the "Title" to  "Pending/not acknowledged alarms". Alarm indicator In addition to the alarm windows there is an  "Alarm indicator" in the "Global screen". This is used so that an alarm window that was closed by the user is displayed again. Under "General" in "Properties", activate the alarm classes "Errors: Pending alarms", "Errors: Acknowledged", "Warnings: Pending alarms" and "No Acknowledgment: Pending alarms". In  "Events", the display of the alarm window "Alarm window_pending_not_acknowledged" with function "ShowMessageWindow" has already been stored for "Click" and "Click when flashing". Alarms for system diagnostics of CPU 1516F Open the "Device configuration" of the "CPU_1516F" and select the  "System diagnostics" menu under  "General" in  "Properties". System diagnostics is always activated for devices of the SIMATIC S7-1500 series. Under  "Alarm setting", you see which alarm classes are being used. Here, the alarm class is "No Acknowledgment". These alarm classes are referenced in turn by the HMI systems in the alarm windows and for the other settings for the alarms. Select the analog output module  "AQ4xU/I" and activate  "Diagnostics"  "Missing voltage supply L+" for all channels under  "Outputs" in  Properties.
With menu command "Web Server", first select the "Start automatically after booting" option and click on  "User Administration". Assign the administrator password in the "Password" field  "100", confirm it in the "Confirm Password" field  "100" and apply it with  "Apply". With menu command "Remote", first select the "Start automatically after booting" option and click  "Change settings". Also assign  "100" for Password1 and  "100" for Password2 and put this into effect with  "Apply". Starting remote access to the TP700 Comfort Panel To the remote access to your panel, enter the IP address of the in your browser "192.168.0.10". Note: A current installation of Java Runtime Environment is required for secure access to the web services of the Comfort Panel. Enter the password that was previously set in the panel  "100". You then have the option of monitoring, and operating the panel remotely and even changing the settings in Windows CE of the device.
Reference list The following signals are required as global operands for this task. DI Type Identifier Function NC/NO I 0.0 BOOL -A1 Return signal emergency stop OK NC I 0.1 BOOL -K0 Main switch "ON" NO I 0.2 BOOL -S0 Mode selector manual (0)/ automatic (1) Manual = 0 Auto = 1 I 0.3 BOOL -S1 Pushbutton "Automatic Start" NO I 0.4 BOOL -S2 Pushbutton "Automatic Stop" NC I 0.5 BOOL -B1 Sensor cylinder -M4 retracted NO I 1.0 BOOL -B4 Sensor part at slide NO I 1.3 BOOL -B7 Sensor part at end of conveyor NO IW64 BOOL -B8 Sensor actual value speed of the motor +/-10V corresponds to +/- 50 rpm DO Type Identifier Function Q 0.2 BOOL -Q3 Conveyor M1 variable speed QW 64 BOOL -U1 Manipulated value speed of the motor in two directions +/-10V corresponds to +/-50 rpm Legend for reference list DO Digital output AO Analog output O Output DI Digital input AI Analog input I NC Normally Closed NO NO Normally Open Planning Plan the implementation of the task on your own.