POTENTIAL SPILL PREDICTION Potential oil locations and a description of existing measures for the avoidance and/or containment of the release of oils from the facility are presented in this section. Specific facility recommendations for improved containment measures are presented in Section 10.0. Area/Source Total Volume (Gal.)/Source Potential Type of Failure Potential Spill Volume (gal.) Flow Direction* Secondary Containment TRANSFORMERS #1 ELS Building by PECO** 255 Mineral Oil Transformer failure 255 On concrete pad, west toward City Ave. None Spill during oil transfer 25 #2 Mandeville Hall Owned by PECO** 460 Mineral Oil Transformer failure 460 Onto concrete pad and ground. None Spill during oil transfer 46 #3 Ashwood Hall Owned by PECO** 255 Mineral Oil Transformer failure 255 Onto concrete pad and ground. None Spill during oil transfer 25 #4 Moore Hall 210 Mineral Oil Transformer failure 210 Onto concrete pad and ground. None Spill during oil transfer 21 #5 Quad T.H. 319 Mineral Oil Transformer failure 319 Onto concrete pad and ground. None Spill during oil transfer 31 #6 Boiler Room #134 Power Plant 150 Mineral Oil Transformer failure 150 On concrete pad, east toward retaining wall. None Spill during oil transfer 15 #7 Boiler Room #131 Power Plant 150 Mineral Oil Transformer failure 150 On concrete pad, east toward retaining wall. None Spill during oil transfer 15 #8 Gest Lawn 201 Mineral Oil Transformer failure 201 Onto concrete pad and ground. None Spill during oil transfer 20 #9 Post Hall 1 237 Mineral Oil Transformer failure 237 Onto concrete pad and ground. None Spill during oil transfer 23 #10 Post Hall 2 237 Mineral Oil Transformer failure 237 Onto concrete pad and ground. None Spill during oil transfer 23 #11 Xavier Hall 264 Mineral Oil Transformer failure 264 On concrete pad, east toward Lapsley Lane. None Spill during oil transfer 26
*Rate of flow would be instantaneous Secondary Containment Legend A To be contained by Speedi-Dry or absorbent material. B Spill contained by impervious nature of building's floor and/or walls. C Secondary containment. Generators Barbelin/Lonergan Generator 150 Diesel Tank failure 150 Toward access road to the North or grass to the Northwest. none Spill during transfer 15 LaFarge Generator 80 Diesel Tank failure 80 Double wall containment. C Spill during transfer 8 5320 City Avenue Generator-Lannon Hall 450 Diesel Tank failure 450 Double wall containment C Spill during transfer 45 Fieldhouse Generator 150 Diesel Spill during transfer 15 Toward asphalt to the East. C Container failure 150 Moore Hall 25 Diesel Tank failure 25 Double wall containment, On concrete pad. C Spill during transfer 30 Hawks Landing 225 Diesel Tank failure 225 Double wall containment, inside on concrete floor C Spill during transfer 23 McShain Hall 420 Diesel Tank failure 420 Double wall containment, outside on concrete floor C during transfer 42 Science Center 370 Diesel Tank failure 370 Double wall containment, outside on concrete floor C during transfer 37 Campion Hall 300 Diesel Tank failure 300 Double wall containment, exterior on concrete floor C Spill during transfer 30 Maguire Merion Garage Diesel Tank failure during transfer 222 22 Containment tank on generator C Fine Arts West Diesel Tank failure
Printed Name______________________________Signature____________________________ Date_____________________