PSF Fixed 5% 14 QIF Fixed 9.2% 4 MF Fixed 10% 20 DuctSF Fixed 18% 14 CF Fixed 70% 6 DSF Fixed 2.9% 7 HSPFb Fixed Baseline = 7.7 8 HSPFq Variable EDC Data Gathering AEPS Application; EDC’s Data Gathering COPg Variable EDC Data Gathering AEPS Application; EDC’s Data Gathering GSOP Fixed 3.413 9 GSPK Fixed 0.8416 10 EDSH Fixed 1842 kWh 11 PDSH Fixed 0.34 kW 12 Cooling - CAC Time Period Allocation Factors Fixed Summer/On-Peak 64.9% Summer/Off-Peak 35.1% Winter/On-Peak 0% Winter/Off-Peak 0% 13 Cooling – ASHP Time Period Allocation Factors Fixed Summer/On-Peak 59.8% Summer/Off-Peak 40.2% Winter/On-Peak 0% Winter/Off-Peak 0% 13 Cooling – GSHP Time Period Allocation Factors Fixed Summer/On-Peak 51.7% Summer/Off-Peak 48.3% Winter/On-Peak 0% Winter/Off-Peak 0% 13 Heating – ASHP & GSHP Time Period Allocation Factors Fixed Summer/On-Peak 0.0% Summer/Off-Peak 0.0% Winter/On-Peak 47.9% Winter/Off-Peak 52.1% 13 GSHP Desuperheater Time Period Allocation Factors Fixed Summer/On-Peak 4.5% Summer/Off-Peak 4.2% Winter/On-Peak 43.7% Winter/Off-Peak 47.6% 13 Capyq Variable EDC Data Gathering AEPS Application; EDC’s Data Gathering
Multi-Zone kWh = kWhcool + kWhheat kWhheat = [CAPY/1000 X (1/HSPFb - 1/HSPFe ) X EFLH X LF]ZONE1 + [CAPY/1000 X (1/HSPFb - 1/HSPFe ) X EFLH X LF]ZONE2 + [CAPY/1000 X (1/HSPFb - 1/HSPFe ) X EFLH X LF]ZONEn kWhcool = [CAPY/1000 X (1/SEERb – 1/SEERe ) X EFLH X LF]ZONE1 + [CAPY/1000 X (1/SEERb – 1/SEERe ) X EFLH X LF]ZONE2 + [CAPY/1000 X (1/SEERb – 1/SEERe ) X EFLH X LF]ZONEn Note, that if the customer did not have a cooling system installed prior, there may be a negative cooling energy impact. kWpeak = [CAPY/1000 X (1/EERb – 1/EERe ) X CF]ZONE1 + [CAPY/1000 X (1/EERb – 1/EERe ) X CF]ZONE2 + [CAPY/1000 X (1/EERb – 1/EERe ) X CF]ZONEn Definition of Terms CAPY = The capacity of the indoor unit is given in BTUH EFLH = Equivalent Full Load Hours – If the unit is installed as the primary heating system; that is, in a living room or large room of the house, the EFLH will be equivalent to those for a central heating system. If the unit is installed as a secondary heating system, the EFLH will be equivalent to a room unit (ie. for cooling, equivalent to a room AC system). HSPFb = Heating efficiency of baseline unit HSPBe = Efficiency of the installed DHP SEERb = Cooling efficiency of baseline unit SEERe = Efficiency of the installed DHP EERb = The Energy Efficiency Ratio of the baseline unit EERe = The Energy Efficiency Ratio of the efficient unit LF = Load factor
The baseline is the existing fluorescent fixtures with the existing lamps and ballast as defined in Lighting Audit and Design Tool shown in Appendix C. Other factors required to calculate savings are shown in and . Note that if EFLH is stated and verified by logging lighting hours of use groupings, actual hours should be applied. The IF factors shown in are to be used only when the facilities are air conditioned and only for fixtures in conditioned or refrigerated space. The EFLH for refrigerated spaces are to be estimated or logged separately. Table 35: Lighting EFLH and CF by Building Type or Function Building Type EFLH CF Source Daycare 2,590 0.77* 6 Education – Primary School 1,440 0.57 1 Education – Secondary School 2,305 0.57 1 Education – Community College 3,792 0.64 1 Education – University 3,073 0.64 1 Grocery 5,824 0.94 1 Hospitals 6,588 0.84 1 Industrial Manufacturing – 1 Shift 2,857 0.77* 4 Industrial Manufacturing – 2 Shift 4,730 0.77* 4 Industrial Manufacturing – 3 Shift 6,631 0.77* 4 Medical – Clinic 4,212 0.86 1 Libraries 2,566 0.77* 2 Lodging –Guest Rooms 1,145 0.84 1 Lodging –Common Spaces 8,736 1.00 1 Light Manufacturing (Assy) 2,610 0.77* 5 Manufacturing – Light Industrial 4,290 0.63 1 Office- Large 2,808 0.84 1 Office-Small 2,808 0.84 1 Parking Garages 6,552 0.77* 4 Police and Fire Station – 24 Hour 7,665 0.77* 8 Police and Fire Station – Unmanned 1,953 0.77* 8 Public Order and Safety 5,366 0.77* 7 Religious Worship 1,810 0.77* 3, 4 Restaurant – Sit-Down 4,368 0.88 1 Restaurant – Fast-Food 6,188 0.88 1 Retail – 3-Story Large 4,259 0.89 1 Retail – Single-Story Large 4,368 0.89 1
Table 336: Shaded Pole to PSC Deemed Savings Measure Wbase (Shaded Pole) Wee (PSC) LF DCEvap DG COP per case Temp Demand Impact (kW) Energy Impact (kWh) Cooler: Shaded Pole to PSC: 1-14 Watt 50 22 0.9 100% 0.98 2.5 0.0355 311 Cooler: Shaded Pole to PSC: 16-23 Watt 93 48 0.9 100% 0.98 2.5 0.0574 503 Cooler: Shaded Pole to PSC: 1/20 HP (37 Watt) 142 90 0.9 100% 0.98 2.5 0.0660 578 Freezer: Shaded Pole to PSC: 1-14 Watt 50 22 0.9 94.4% 0.98 1.3 0.0425 373 Freezer: Shaded Pole to PSC: 16-23 Watt 93 48 0.9 94.4% 0.98 1.3 0.0687 602 Freezer: Shaded Pole to PSC: 1/20 HP (37 Watt) 142 90 0.9 94.4% 0.98 1.3 0.0790 692 Table 337: PSC to ECM Deemed Savings Measure Wbase (PSC) Wee (ECM) LF DCEvap DG COP per case Temp Demand Impact (kW) Energy Impact (kWh) Cooler: PSC to ECM: 1-14 Watt 22 14 0.9 100% 0.98 2.5 0.0105 92 Cooler: PSC to ECM: 16-23 Watt 48 30 0.9 100% 0.98 2.5 0.0228 200 Cooler: PSC to ECM: 1/20 HP (37 Watt) 90 56 0.9 100% 0.98 2.5 0.0433 380 Freezer: PSC to ECM: 1-14 Watt 22 14 0.9 94.4% 0.98 1.3 0.0126 110 Freezer: PSC to ECM: 16-23 Watt 48 30 0.9 94.4% 0.98 1.3 0.0273 239 Freezer: PSC to ECM: 1/20 HP (37 Watt) 90 56 0.9 94.4% 0.98 1.3 0.0518 454
Table 338: Shaded Pole to ECM Deemed Savings Measure Wbase (Shaded Pole) Wee (ECM) LF DCEvap DG COP per case Temp Demand Impact (kW) Energy Impact (kWh) Cooler: Shaded Pole to ECM: 1-14 Watt 50 14 0.9 100% 0.98 2.5 0.0461 404 Cooler: Shaded Pole to ECM: 16-23 Watt 93 30 0.9 100% 0.98 2.5 0.0802 703 Cooler: Shaded Pole to ECM: 1/20 HP (37 Watt) 142 56 0.9 100% 0.98 2.5 0.1093 958 Freezer: Shaded Pole to ECM: 1-14 Watt 50 14 0.9 94.4% 0.98 1.3 0.0551 483 Freezer: Shaded Pole to ECM: 16-23 Watt 93 30 0.9 94.4% 0.98 1.3 0.0960 841 Freezer: Shaded Pole to ECM: 1/20 HP (37 Watt) 142 56 0.9 94.4% 0.98 1.3 0.1308 1146 Table 339: Default High-Efficiency Evaporator Fan Motor Deemed Savings Measure Cooler Weighted Demand Impact (kW) Cooler Weighted Energy Impact (kWh) Freezer Weighted Demand Impact (kW) Freezer Weighted Energy Impact (kWh) Default Demand Impact (kW) Default Energy Impact (kWh) Shaded Pole to PSC 0.0380 333 0.0455 399 0.0404 354 PSC to ECM 0.0129 113 0.0154 135 0.0137 120 Shaded Pole to ECM 0.0509 446 0.0609 534 0.0541 474 Measure Life 15 years Sources:
Table 342: PSC to ECM Deemed Savings Measure Wbase (PSC) Wee (ECM) LF DCEvap DG COP per case Temp Demand Impact (kW) Energy Impact (kWh) Cooler: PSC to ECM: 1/40 HP (16-23 Watt) 48 30 0.9 100% 0.98 2.5 0.0228 189 Cooler: PSC to ECM: 1/20 HP (37 Watt) 90 56 0.9 100% 0.98 2.5 0.0431 356 Cooler: PSC to ECM: 1/15 HP (49 Watt) 120 75 0.9 100% 0.98 2.5 0.0570 472 Freezer: PSC to ECM: 1/40 HP (16-23 Watt) 48 30 0.9 94.4% 0.98 1.3 0.0273 226 Freezer: PSC to ECM: 1/20 HP (37 Watt) 90 56 0.9 94.4% 0.98 1.3 0.0516 427 Freezer: PSC to ECM: 1/15 HP (49 Watt) 120 75 0.9 94.4% 0.98 1.3 0.0682 565
Rf = the total R-value of all insulation after the additional insulation is installed EFLH = effective full load hours CF = coincidence factor EER = efficiency of the cooling system COP = efficiency of the heating system Table 352: Non-Residential Insulation – Values and References Component Type Values Sources A Variable Application AEPS Application; EDC Data Gathering HDD Fixed Allentown = 5318 Erie = 6353 Harrisburg = 4997 Philadelphia = 4709 Pittsburgh = 5429 Scranton = 6176 Williamsport = 5651 1 CDD Fixed Allentown = 787 Erie = 620 Harrisburg = 955 Philadelphia = 1235 Pittsburgh = 726 Scranton = 611 Williamsport = 709 1 24 Fixed 24 n/a 1000 Fixed 1000 n/a Ceiling Ri Existing:Variable New Construction: Fixed For new construction buildings and when variable is unknown for existing buildings: See and for values by building type AEPS Application; EDC Data Gathering; 2; 4 Wall Ri Existing:Variable New Construction: Fixed For new construction buildings and when variable is unknown for existing buildings: See and for values by building type AEPS Application; EDC Data Gathering; 3; 4 Rf Variable AEPS Application;
Small Office Warehouse 24.4 13.4 Small Retail Restaurant Convenience Store 20 9 Table 354: Wall R-Values by Building Type Building Type Wall Ri-Value (New Construction) Wall Ri-Value (Existing) Large Office 14 1.6 Small Office Large Retail Small Retail Convenience Store 14 3.0 Lodging Health Education Grocery 13 2.0 Restaurant 14 3.2 Warehouse 14 2.5
C&I Construction Commercial Lighting (Non-SSL) — New 15 Commercial Lighting (Non-SSL) — Remodel/Replacement 15 Commercial Lighting (SSL – 25,000 hours) — New 6 Commercial Lighting (SSL – 30,000 hours) — New 7 Commercial Lighting (SSL – 35,000 hours) — New 8 Commercial Lighting (SSL – 40,000 hours) — New 10 Commercial Lighting (SSL – 45,000 hours) — New 11 Commercial Lighting (SSL – 50,000 hours) — New 12 Commercial Lighting (SSL – 55,000 hours) — New 13 Commercial Lighting (SSL – 60,000 hours) — New 14 Commercial Lighting (SSL – ≥60,000 hours) — New 15* Commercial Lighting (SSL – 25,000 hours) — Remodel/Replacement 6 Commercial Lighting (SSL – 30,000 hours) — Remodel/Replacement 7 Commercial Lighting (SSL – 35,000 hours) — Remodel/Replacement 8 Commercial Lighting (SSL – 40,000 hours) — Remodel/Replacement 10 Commercial Lighting (SSL – 45,000 hours) — Remodel/Replacement 11 Commercial Lighting (SSL – 50,000 hours) — Remodel/Replacement 12 Commercial Lighting (SSL – 55,000 hours) — Remodel/Replacement 13 Commercial Lighting (SSL – 60,000 hours) — Remodel/Replacement 14 Commercial Lighting (SSL – ≥60,000 hours) — Remodel/Replacement 15* Commercial Custom — New 18* Commercial Chiller Optimization 18* Commercial Unitary HVAC — New - Tier 1 15 Commercial Unitary HVAC — Replacement - Tier 1 15 Commercial Unitary HVAC — New - Tier 2 15 Commercial Unitary HVAC — Replacement Tier 2 15 Commercial Chillers — New 20* Commercial Chillers — Replacement 20* Commercial Small Motors (1-10 horsepower) — New or Replacement 20* Commercial Medium Motors (11-75 horsepower) — New or Replacement 20* Commercial Large Motors (76-200 horsepower) — New or Replacement 20* Commercial Variable Speed Drive — New 15 Commercial Variable Speed Drive — Retrofit 15