1 Efficacy ≥ 65 lm/W ≥ 85 lm/W (2020) ≥ 100 lm/W (2023) ≥ 100 lm/W ≥ 110 lm/W (2020) ≥ 120 lm/W (2023) 10 Average ≥ value specified CIE S025 LM79 accepted until July 2019 EN 2 Replacement Lamp Equivalence ONLY IF CLAIMING (1) Minimum Lumen output required when claiming equivalence to a specified GLS Tungsten Filament lamp 10W = 100 lm 15W = 150 lm 25W = 250 lm 30W = 350 lm 40W = 500 lm 60W = 800 lm 75W = 1000 lm 100W = 1500 lm ONLY IF CLAIMING (1) Minimum lumen output (as a percentage of GLS lamp equivalences of same wattage) required for claimed equivalent wattage reflector filament lamps of stated lamp shapes ONLY IF CLAIMING (1) Minimum lumen output required for claimed equivalence to linear fluorescent lamp. Bare lamp L ≤ 600mm: 800 lm *600 < L ≤ 900mm: 1200 lm 900 < L ≤ 1200mm:1600 lm 10 3 (Linear LED) Average Luminous flux ≥ the specified minimum light output (lm) of the claimed Equivalent wattage CIE S025 LM79 accepted until July 2019 EN
125W =2000 lm 150W = 2500 lm 175W = 3000 lm 200W = 3500 lm (2) Dimensions of the lamp must comply with equivalent lamp’s requirements in the relevant IEC lamp performance specification Standard (use linear interpolation between GLS wattage values listed) (2) Dimensions of the lamp must comply with equivalent lamp’s requirements in the relevant IEC lamp performance specification Standard *1200 < L ≤ 1500mm:2000 lm [Based on Design Lights Consortium DLC requirements with * extension] (2) Dimensions of the lamp must comply with equivalent lamp’s requirements in the relevant IEC lamp performance specification Standard 3 Centre beam luminous intensity N/A For MR or PAR lamps with a beam angle <65°, centre beam intensity should meet equivalent levels using the online tool: N/A 10 For MR or PAR lamps: Average ≥ equivalent level CIE S025 LM79 accepted until July 2019
6 Standby Power (For lamps with Standby mode only) PSTANDBY/PON ≤ 5% Capped at: < 0.5W < 0.3W (2023) 5 3 (Linear LED) Average ≥ value specified To be tested as supplied for sale (additional functionality may be supplied not activated). See also smart lamp criteria. AS/NZS IEC 62301 (or IEA 4E SSL Task 7 2016 publication 7 Smart Lighting: on-demand power consumption feature (smart lamps only) Device to provide energy consumption reporting that is accessible by owner. To be considered further following the outcomes of investigations by the IEA 4E SSL and G20 working groups. 1 Require device to provide energy consumption reporting that is accessible by owner Energy Star Lamps v2 Section 12.9 Colour
EN 10 Colour maintenance The shift in chromaticity co-ordinates after 6000 hours of operation, Δ u’,v’ (6000 hours), ≤ 0.007 LED Module or LED package test data (from an accredited lab) may be used, combined with ISTMT junction temperature test of lamp to be registered. 3 All samples satisfy conditions of the test method. Compliance testing may be an ISTMT junction temperature test and relevant test report or a full product test. ISTMT ((IEC 60598.1 Section 12.4.1 or UL 1598 Clause 14) & IESNA LM80 (test includes lens and phosphors) or IESNA LM84 Life 12 Endurance Must survive one switching cycle for every 2 hours of rated life Must survive temperature cycling test for 1,000 hours Must survive accelerated operational life test for 1,000 hours 10 Satisfy conditions of the test method. IEC 62612: 2013 Section 11.3.2-4
13 Lumen maintenance Lumen maintenance @ 6000 hrs Lx,6k ≥ 86.7% (based on L70B50 ≥ 15,000h) LED Module or LED package test data (from an accredited lab) may be used, combined with ISTMT junction temperature test of lamp to be registered. Lumen maintenance @ 6,000h Lx,6k ≥ 91.8% (based on L70B50 ≥ 25,000h) 10 Average Lx,6k ≥ value specified Compliance testing may be an ISTMT junction temperature test relating to test report or a full product test. IESNA LM80/TM21 & ISTMT (IEC 60598.1 Section 12.4.1 or UL 1598 Clause 14) or IESNA LM84/TM28 14 Rated Life Declaration (relates to packaging requirement) Packaging declaration of a minimum lifetime of 15,000 hours Packaging declaration of a minimum lifetime of 25,000 hours N/A Declaration Only N/A
Compliance may test. Health 21 Safety For ELV Lamps only (other lamps subject to similar safety regulation) Blue Light & UV hazards shall be either RG0 or RG1 unlimited (This is based on advice that Australian electrical safety regulators will regulate Safety for all but ELV lamps - awaiting advice on New Zealand) 1 Satisfy conditions of the test method. IEC 62471 / CIE S009 22 Dominant light modulation frequency (f) Modulation percent at this frequency (Mod%) includes Flicker effects) Maximum flicker modulation (based on the flicker frequency) 1 Satisfy conditions of the test method. IEEE 1789 or other if specified in biological biological
Table 2 – Integrated LED luminaires Attribute Requirement Sample size Compliance criteria Test method Ref Small Large Planar, Battens & Troffers (P/B/T) Energy Efficiency & Photometric 1 Efficacy Directional ≥ 65 lm/W ≥ 85 lm/W (2020) ≥100 lm/W (2023) Non-directional ≥ 65 lm/W (2019) ≥ 85 lm/W (2021) ≥100 lm/W (2023) ≥ 110 lm/W (2020) ≥ 120 lm/W (2023) ≥ 90 lm/W (2019) ≥ 110 lm/W (2021) ≥ 120 lm/W (2023) 4 (Small) 2 (Large & P/B/T) Average ≥ value specified CIE S025 LM79 accepted until July 2019 EN 2 Replacement Lamp Equivalence ONLY IF CLAIMING. Where claiming replacement equivalence to a specific lamp based fixture the luminaire must meet minimum lumen output provided for lamps in table 1. (eg for halogen downlights replacements, use None provided ONLY IF CLAIMING. Luminaire lumens (per lamp) for claimed number of tubular fluorescent lamp equivalents must meet minimum lumen output provided in the lamp table 1. 3 (Small) 1 (P/B/T) Average Luminous flux ≥ Claimed Equivalent wattage specified minimum light output (lm) CIE S025 LM79 accepted until July 2019 EN
equivalence of MR16 directional lamp) 3 Centre beam luminous intensity ONLY IF CLAIMING. For luminaires claiming equivalence to MR or PAR lamps with a beam angle <65°, centre beam intensity should meet equivalent levels using the online tool: ONLY IF CLAIMING Centre beam luminous intensity ≥ declared value ONLY IF CLAIMING Centre beam luminous intensity ≥ declared value N/A 3 (Small) 1 (Large) For MR or PAR lamp claimed equivalence: Average ≥ of equivalent level For other lamps: Average ≥ of declared value CIE S025 LM79 accepted until July 2019 EN
4 Light distribution ONLY for Directional luminaires: Beam angle is ± 25% of declared beam angle and 50% of flux shall be in declared beam angle None provided 3 All samples meet the specified requirements CIE S025 LM79 accepted until July 2019 EN Energy conservation 5 Standby Power (For luminaires with Standby mode only) PSTANDBY/PON ≤ 5% capped at: < 0.5W < 0.3W (2023) < 0.1.1W < 0.0.5W (2023) Note: Where only 1 standby product/parameter is applicable, e.g. DALI, then test data from control gear/module may be used. Where a luminaire incorporates more than standby 3 (Small) 1 (Large & P/B/T) All samples ≤ value specified To be tested as supplied for sale (additional functionality may be supplied not AS/NZS IEC 62301 (or IEA 4E SSL Task 7 2016 publication)
product/parameter, e.g. DALI and sensor, luminaire is to be measured. activated). See also smart lamp criteria. 7 Smart Lighting – controlled variations in power consumption (smart luminaires only) To be considered following the outcomes of investigations by the IEA 4E SSL and G20 working groups 1 Require device to provide energy consumption reporting that is accessible by owner Energy Star Lamps v2 Section 12.9 Colour 8 Colour Rendering Ra ≥80 3 (Small) 1 (Large & P/B/T) Average ≥ value specified CIE S025 (refers to CIE 13.3) 9
Life 12 Endurance Must survive one switching cycle for every 1 hours of rated life Must survive temperature cycling test for 1,000 hours Must survive accelerated operational life test for 1,000 hours 3 (Small) 1 (Large & P/B/T) Satisfy conditions of the test method. IEC 62722.2.1: 2011 Section 10.3.2-4 Test data from module and driver accepted (IEC 62717 Section 10.3) 13 Lumen maintenance Lumen maintenance @ 6,000h Lx,6k ≥ 93.1% (based on Lumen maintenance @ 6,000h (Lx,6k) ≥ 95.4% of initial (based on L70B50 ≥ 45,000h) 3 Average Lx,6k ≥ value specified Compliance testing may be a ISTMT junction temperature test and relevant module/package IESNA LM80/TM21 & ISTMT (IEC 60598.1 Section 12.4.1 or UL 1598 Clause 14) or
L70B50 ≥ 30,000h) Module or LED package test data (from an accredited lab) may be used, combined with ISTMT junction temperature test of lamp to be registered. Module or LED package test data (from an accredited lab) may be used, combined with ISTMT junction temperature test of lamp to be registered. test report or a full product test. IESNA LM84/TM28 Consider allowing use of thermal imaging camera 14 Rated Life Declaration (relates to packaging requirement) Packaging declaration of a minimum of 30,000 hours Packaging declaration of a minimum of 45,000 hours N/A Declaration Only N/A 15 Minimum Rated Life, F50 < 50% at 30,000 hours Not to be applied until a practical test method becomes available < 50% at 45,000 hours Not to be applied until a practical test method becomes available To be Average ≤ value specified To be determined Electrical