Extracts from the Standards may be incorporated in specifications, however it must remain the consultant’s and contractor’s responsibility to fully investigate the needs of the University and produce designs and documents that are entirely ‘fit for purpose’ and which meet the ‘intent’ of the project brief. The Standards outline the University’s generic requirements above and beyond the above mentioned legislation. Where the Standards outline a higher standard than within the relevant legislation, the Standards will take precedence. If any discrepancies are found between any relevant legislation, the Standards and project specific documentation, these discrepancies should be highlighted in writing to the Associate Director Capital Works, Campus Management. The intent of the Standards is to achieve consistency in the quality of the design and construction of the University’s built forms. However, consultants and contractors are expected to propose ‘best practice / state of the art’ construction techniques, and introduce technological changes that support pragmatic, innovative design. In recognition of this, any departures from relevant legislation, or the Standards, if allowed, must be confirmed in writing by the Associate Director Capital Works, Campus Management. Any departures made without such written confirmation shall be rectified at no cost to UWA. For all works, it is expected that suitably qualified and experienced professionals are engaged to interpret and apply these Standards to UWA projects. Works cannot be carried out by unqualified and unlicensed consultants or contractors. This document is structured into 4 parts: Part 1 Introduction (this Section) Part 2 General Requirements – outlines the general requirements or design philosophies adopted at UWA Part 3 Checklist for project team (if applicable) – checklist of items for consideration at various stages of a project Part 4 Specifications (if applicable) – materials specifications and/or preferred lists for materials, processes or equipment used by UWA.
All fire and smoke walls shall comply with BCA requirements and the relevant standards as follows: Fire wall – Comply with AS 1530.4 to achieve a FRL Smoke wall – Comply with AS 1530.1 as non-combustible Floors – Comply with AS 1530.4 to achieve a FRL All services penetrations through a fire wall shall be sealed in accordance with BCA C3.15. All services penetrations through a smoke wall shall be sealed with appropriate fire rated mastic seals. The area of works shall be clearly labelled and marked with the following information: Standards the system is compliant with (i.e. AS 1530.4 and AS 4072.1) FRL of the system Name and contact details of the installer Installation date Reference number for the specific area Name and contact details of the manufacturer The following figure is an example of the expected label. Documentation Upon completion of the works, the area of works shall be inspected to ensure satisfactory completion. The Contractor is required to provide documentation as per AS 4072.1 as follows: The system used is identical with the tested specimen; AND The system has been correctly installed in accordance with the manufacturer’s specification In addition to the above documentation, the Contractor shall provide a record of each installation which outlines the following information as noted in AS 4072.1: Name, address and contact details of installation company Date of final inspection Description of system Identification of the position of the installation on a drawing Photo Fire Dampers Fire dampers shall be constructed and installed to meet all requirements of AS 1682 and AS 1668. Manufacturer certification of compliance is required. The free area of any fire damper shall not be less than 85% of the adjoining duct area. Where necessary the duct size shall be increased above the nominal airway size of the adjoining ductwork to accommodate the fire damper
Checklist for Project Team Activity Responsibility Stakeholder(s) Timeframe Determine if the building or area of works has previous Performance Solutions. Services consultants CM (Engineering Services) / CM (Building Operations) Gate 2 Feasibility Consult with UWA approved Fire Engineer to ascertain impact on previous solutions. Services consultants CM (Engineering Services) / CM (Building Operations) Gate 2 Feasibility Determine if an upgrade to current Australian Standards is required for works in existing buildings. Services consultants CM (Capital Works) Gate 2 Feasibility If not possible to comply, consult with UWA approved fire engineer to ascertain possible Performance Solutions. Services consultants CM (Engineering Services) Gate 2 Feasibility Provide baseline data for all fire safety systems to UWA Services consultants / Contractor CM (Engineering Services) / CM (Building Operations) Gate 3 Planning Fire Engineering Where Alternative Solutions are prepared, ensure a copy of FSER is provided to UWA for record. Contractor CM (Building Operations) Gate 5 Construction Fire Engineering Ensure FSER clearly outlines information in a separate section outlining list of non-compliances, fire safety strategies, maintenance requirements and Management in Use requirements Contractor CM (Building Operations) Gate 5 Construction Detection System Ensure detection system is Notifier panel with network capability Services consultants / Contractor CM (Building Operations) Gate 3 Planning Detection System Ensure interface to all existing systems has been retained Services consultants / Contractor CM (Building Operations) / CM (Security) Gate 3 Planning Detection System Ensure system been programmed to interface with other fire safety system including: Mechanical system shut down Secured doors unlocked Occupant warning system activated Fire/smoke curtains closing Services consultants / Contractor CM (Building Operations) / CM (Security) Gate 3 Planning
Smoke fans or vents activating. Occupant Warning System Ensure system has been provided with a digital voice command (DVC) capability. Services consultants / Contractor CM (Building Operations) / CM (Security) Gate 3 Planning Fire Hydrant System Ensure system is compliant with AS 2419.1. Services Consultant / Contractor Gate 3 Planning Fire Hydrant Water Supply Coordinate with UWA to test fire / irrigation system. Services Consultant / Contractor CM (Engineering Services) / CM (Building Operations) Gate 3 Planning Fire Hose Reel System Ensure system complies fully with AS 2441. Services consultants / Contractor Gate 3 Planning Fire Extinguisher Ensure dry powder provided unless risks require alternative extinguisher Services consultants / Contractor CM (Engineering Services) / CM (Building Operations) Gate 3 Planning Fire Extinguisher Ensure extinguishers are of appropriate weight not exceeding 5kg. Services consultants / Contractor CM (Engineering Services) / CM (Building Operations) Gate 3 Planning Mechanical Fire System Ensure smoke exhaust fans are selected and sized to comply with NCC Specification E2.2b requirements Services consultants / Contractor Gate 3 Planning Passive Fire Barriers Ensure barrier complies with AS1530.4 for fire barriers or is considered non-combustible for smoke barriers. Services consultants / Contractor Gate 3 Planning Fire / Smoke Walls Tag walls as per requirements outlined in this document. Contractor CM (Building Operations) Gate 5 Construction Fire / Smoke Doors Tag doors as required by AS1851. In relation to smoke doors, provide signage as appropriate. Contractor CM (Building Operations) Gate 5 Construction Fire / Smoke Doors Where secured during normal operation, ensure interface for door to fail open on alarm has been coordinated. Contractor CM (Building Operations) / CM (Security) Gate 5 Construction Fire & Smoke Curtains consultants / Gate 3 Planning