Station Telemetry Data Frequency Mode Reference/Comments Station Switching Device status 10 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements. (High side Typical TSP telemetry point; Low side typical QSE telemetry point) RE Comment: Station Breaker status 10 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements. (Typical QSE telemetry point) RE Comment: Generation Resource High Side bus voltage 10 sec ICCP Protocol Section 3.15, Voltage Support. May be supplied by the TDSP (Typical TDSP telemetry point) or Low Side voltage with appropriate transformer model may be substituted (Typical QSE telemetry point). RE Comment: Station Static and/or Dynamic Reactive Device(s) status for each device 10 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements.(Typical QSE telemetry point) RE Comment: Station Static and/or Dynamic Reactive Device(s) MVAR output for each device 10 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements.(Typical QSE telemetry point) RE Comment: Generator Step-Up (GSU) Transformer High-Side MW and MVAR for each modeled GSU 10 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements.(Typical QSE telemetry point) RE Comment: Generation Resource auxiliary load and/or station service MW and MVAR for each modeled load 10 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements.(Typical QSE telemetry point) RE Comment: Transmission Line Flow 10 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements. (RE has confirmed that TSP is providing required points; Transmission Line Flow has telemetry for both the sending and receiving end of the interconnecting line if the Generation Resource is registered at a different station in the Network Operations Model). RE Comment: By signing below I attest that information provided on this form (PART 1) is true, correct and complete, and that any substantial changes in such information will promptly be provided to the Electric Reliability Council of Texas (ERCOT). Signature: (RE Authorized Representative)
Station Static and/or Dynamic Reactive Device(s) status for each device 10 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements.(Typical QSE telemetry point) RE Comment: Station Static and/or Dynamic Reactive Device(s) MVAR output for each device 10 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements.(Typical QSE telemetry point) RE Comment: Generator Step-Up (GSU) Transformer High-Side MW and MVAR for each modeled GSU 10 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements.(Typical QSE telemetry point) RE Comment: Generation Resource auxiliary load and/or station service MW and MVAR for each modeled load 10 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements.(Typical QSE telemetry point) RE Comment: Transmission Line Flow 10 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements. (RE has confirmed that TSP is providing required points; Transmission Line Flow has telemetry for both the sending and receiving end of the interconnecting line if the Generation Resource is registered at a different station in the Network Operations Model). RE Comment: New Generator Telemetry Data Frequency Mode Reference/Comments Real Time data accuracy Real Time data for reliability purposes must be accurate to within three percent (3%). This telemetry may be provided from relaying accuracy instrumentation transformers. QSE Comment: Generation Resource gross and net MW output 2 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements. Net Generation is preferred. Otherwise, aux load should also be provided. QSE Comment: Generation Resource gross and net MVar output 2 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements. Net Generation is preferred. Otherwise, aux load should also be provided. QSE Comment:
Transmission Line Flow 10 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements. (RE has confirmed that TSP is providing required points; Transmission Line Flow has telemetry for both the sending and receiving end of the interconnecting line if the Generation Resource is registered at a different station in the Network Operations Model). RE Comment: New Generator Telemetry Data Frequency Mode Reference/Comments Real Time data accuracy Real Time data for reliability purposes must be accurate to within three percent (3%). This telemetry may be provided from relaying accuracy instrumentation transformers. QSE Comment: Generation Resource gross and net MW output 2 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements. Net Generation is preferred. Otherwise, aux load should also be provided. QSE Comment: Generation Resource gross and net MVar output 2 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements. Net Generation is preferred. Otherwise, aux load should also be provided. QSE Comment: Switching Device status other than reported in PART 1 2 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements. QSE Comment: Breaker status other than reported in PART 1 2 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements QSE Comment: Generation Resource High Sustainable Limit 2 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements. QSE Comment: Generation Resource Low Sustainable Limit 2 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements. QSE Comment: Generation Resource Automatic Voltage Regulator status 2 sec ICCP Protocol Section 3.15.3, QSE Responsibilities Related to Voltage Support. Applies to Generation Resources required to provide VSS. QSE Comment: