DIVISION 14 CONVEYING SYSTEMS SECTION 142423 - HYDRAULIC PASSENGER ELEVATOR RELATED DOCUMENTS Drawings and general provisions of the Contract, Standard General and Supplementary General Conditions, Division 1 Specification Sections, and other applicable Specification Sections including the Related Sections listed below, apply to this Section. OF WORK The work of this division shall consist of the complete installation (or replacement) of one hydraulic passenger elevator in the _______________ Building. Bidders shall include all labor, materials, and services required for the complete installation of all the elevator equipment as herein specified, including hoistway entrances and elevator car enclosure. In all cases where a device or part of the equipment is herein referred to in the singular, it is intended that such reference shall apply to as many of such devices or parts as are required to make a complete installation. Soil testing: The soil around existing piston is to be tested by University of Michigan's OSEH Department. This contractor is to coordinate related work with Owner and notify the Owner, through the project manager, when pit soil is accessible for sampling and testing. Outline of work by University of Michigan's OSEH Department: Analysis and testing of soil contamination. Transport of removed contaminated soil to a dumping site with MDEQ permit. Contact number at OSEH is (734) 763-4642. GENERAL These specifications cover the complete installation of the elevator system, in accordance with the drawings and as specified herein. The elevator contractor shall include all work and materials, except that listed under "Related Work By Other Contractors", for a complete and operational job. ACCEPTABLE ELEVATOR INSTALLERS * Kone Elevator Co. Detroit Elevator Co. City Elevator Co.
Unless otherwise specified, control wiring shall be minimum size #18 AWG. Wire size shall be large enough so that the voltage drop under inrush conditions will not adversely affect operation of the controls. Electrical Receptacle in Car: Provide duplex electrical receptacle in car. Locate receptacle approximately 2" above finished floor below car station. Provide matching face plate on receptacle Protection: Provide 3-phase power monitor for elevator power supply, which monitors phase loss, low voltage, phase reversal, phase unbalance, and has an automatic reset. The three-phase power monitor shall be Time Mark Corp. model 257 or model approved by the Elevator Shop. Execution: Install all wiring in raceway systems. No exposed wiring or conduit shall be run in finished areas without prior written approval of owner. Splice cables and wires only in outlet boxes, junction boxes or pull boxes. (Note - No wire splicing allowed in raceway or wire ducts). Install supports for all vertical feeders in accordance with the NEC. Provide Kellum GRIP type supports, which firmly clamp each individual cable and tighten due to cable weight. All terminal strip connections shall be identified with corresponding reference numbers from cable termination chart and electrical straight-line diagrams. MACHINE FINISH AND PAINTING All exposed surfaces of machines and motors, controllers, etc., shall be repainted after field installation and before acceptance by Owner with rust resisting gloss enamel paint. EMERGENCY ALARM BELL An alarm bell shall be provided and mounted on the car. When the emergency alarm bell button in the car is pressed, the alarm bell shall sound. bell should operate per ASME A17.1-2000 and State of Michigan Elevator Code. Planned steel tee guide rails shall be furnished and installed to meet ANSI A17.1-2000 requirements, including suitable brackets and clamps for attachment to the building structure. The guide rails and car frame shall be so located that the car is in balance with the guides. The machined tongue and groove joints shall be fitted with machined fishplates fastened to each rail with at least 4 through bolts. Rails are to be cleaned of any shipping or protective coatings at time of installation.