150KVA ID:01 08:00 ◄ Output Module Input Batt State ► A B C Phase Voltage(v) 220 221 221 Phase Current(A) 16 10 18 Frequency(HZ) 50 Active Power(kw) 5.0 5.2 5.6 Apparent Power(KVA) 3.7 3.9 4.1 Load percent(%) 50 52 53 Rate 1.3 1.5 1.8 150KVA ID:01 08:00 ◄ Output Module Input Batt State ► Module01 Online Module02 Online Module03 Online Module04 Online Module05 Online Module06 Offline Module07 Offline Module08 Offline Module09 Offline Module09 Offline Module10 Offline Output data Modules data 150KVA ID:01 08:00 ◄ Output Module Input Batt State ► Module Invert Voltage(V) 220 220 220 Invert Current(A) 0 0 0 Frequency(HZ) 50 Positive Bus Voltage(V) 370 Negative Bus Voltage(V) 370 Code 8000-8000 D800-8000 0000-0000 0000-0000 Back 150KVA ID:01 08:00 ◄ Output Module Input Batt State ► Mains A B C Phase Voltage(V) 220 220 220 Phase Current(A) 2 2 2 Frequency(HZ) 50 Bypass Phase Voltage(V) 220 220 220 Frequency(HZ) 50 Detailed module data Input data 150KVA ID:01 08:00 ◄ Output Module Input Batt State ► Positive Voltage (V) 239.9 Negative Voltage (V) 241.0 Positive Current (A) 15.1 Negative Current (A) 14.8 Charge Temperature (℃) 0.0 Lasting(min) 0 150KVA ID:01 08:00 ◄ Output Module Input Batt State ► Input Output Bypass Switch OFF Manu-Bypass Switch OFF Inside Temperature (℃) 30 Battery data Status data
150KVA ID:01 08:00 ◄ Setting Record Version ► Test Buzzer Default Set 150KVA ID:01 08:00 ◄ Command Setting Record Version ► Language/English Change Password Date Setting 2012-05-23 08:00 Back-Light Delay 10 min Contrast 20 Self-Test Date disable Timing of ON/OFF disable Back Next Command data Setting data1 150KVA ID:01 08:00 ◄ Setting Record Version ► Parallel ID 01 UPS Output Enable Float Volt Revise 0.001 Parallel Amount 04 Internal Module amount 05 Back Next 150KVA ID:01 08:00 ◄ Command Setting Record Version ► Work Mode Parallel System Voltage Level 220V System Frequency Level 50HZ Auto Turn-on Enable Bypass Frequency Range 10% Bypass Volt. Upper Limit 15% Back Bypass Volt. Lower Limit -45% O/P Volt Regulation 0% Next Setting data2 Setting data3 150KVA ID:01 08:00 ◄ Setting Record Version ► Single Volt. 12V Number 20 Group 1 Single Capa. 100AH Boost Upper Limit Volt. 2.31 Float Base Volt. 2.25 Protect Volt. 1.70 Boost Charge Enable Back Boost Last Time 231 Min Max Charge Current Next 150KVA ID:01 08:00 ◄ Command Setting Record Version ► 0004 05-23 07:16:05 On Line 0002 05-23 07:16:01 Back Nomal 0003 05-23 07:06:00 Int.Input Switc.. 0004 05-23 07:00:00 Int.Bypass Swit.. .. Back Next Setting data4 Record data
150KVA ID:01 08:00 ◄ Setting Record Version ► SYS Version: V02×10 LCD Version: 701× 150KVA ID:01 08:00 ◄ Command Setting Record Version ► Version data Module detailed record data 150KVA ID:01 08:00 ◄ Setting Record Version ► Test Buzzer Set Default Set 150KVA ID:01 08:00 ◄ Setting Record Version ► Test Buzzer Set Default Set Setting of battery test Setting of Buzzer 150KVA ID:01 08:00 ◄ Setting Record Version ► Test Buzzer Default 150KVA ID:01 08:00 ◄ Setting Record Version ► Restore default setting Password setting
150KVA ID:01 08:00 ◄ Command Setting Record Version ► 150KVA ID:01 08:00 ◄ Command Setting Record Version ► Language/English Change Password Date Setting 08:00:00 Back-light Delay 10Min Contrast 20 Self-Test Date disable Back Timing of ON/OFF disable Next Date setting Back-Light Delay setting 150KVA ID:01 08:00 ◄ Setting Record Version ► Language/English Change Password Date Setting 08:00:00 Back-light Delay 10Min Contrast 20 Self-Test Date disable Back Timing of ON/OFF disable Next 150KVA ID:01 08:00 ◄ Setting Record Version ► Work Mode Single System Voltage Level 220V System Frequence Level 50HZ Auto Turn-on Enable Bypass Frequence Range 2% Bypass Volt. Upper Limit 10% Back Bypass Volt. Lower Limit -30% O/P Volt Regulation 0% Next Contrast setting Setting of work mode 150KVA ID:01 08:00 ◄ Setting Record Version ► Work Mode Single System Voltage Level 220V System Frequence Level 50H Auto Turn-on Ena Bypass Frequence Range 2% Bypass Volt. Upper Limit 10% Back Bypass Volt. Lower Limit -30 O/P Volt Regulation 0% Next 150KVA ID:01 08:00 ◄ Setting Record Version ► Work Mode Single System Voltage Level 220V System Frequence Level 50 Auto Turn-on Ena Bypass Frequence Range 2% Bypass Volt. Upper Limit 10% Back Bypass Volt. Lower Limit -3 O/P Volt Regulation 0% Next
Coming to Interval transfer Allows transfer to bypass or inverter with 3/4 cycle break. Use of this command will drop load. Coming to over load due to inverter off When the inverter is turned off manually, the load will exceed the power capacity. Coming to Interval transfer due to inverter off When the inverter is turned off manually, the load will exceed the power capacity. Inverter invalid due to over load The load exceeds the capability of the single or parallel modules. Inverter Master It indicates the Master Inverter. Transfer Times-out Latched load transfer to bypass as a result of too many successive transfers within the current hour. Automatic reset attempt within the next hour. UPS In shutdown Due To Overload. The load exceeded the power capacity. The UPS has been shutdown UPS In Bypass Due To Overload. The load exceeded the power capacity. The UPS has switched to Bypass Mode. Parallel in Bypass The parallel system has switched to bypass mode LBS Activated LBS has been activated. Lightning Protection Lightning protector has been activated. Battery low to UPS OFF battery voltage lower than protection point UPS timing on UPS on at certain time UPS timing OFF UPS off at certain time timing self-test start start to self-test at certain time Stop self-test self-test stops manual OFF turn off UPS manually remote OFF turn off UPS remotely module connected module is connected module removed module is removed Cabinet Alarm Information No. Display Message Meaning Rectifier Fault Rectifier detected faulty. Rectifier and inverter and charger shut down. Rectifier Over Temperature The temperature of heat sink is too high to keep the rectifier running. Charger and inverter shut down. Inverter Over temperature The temperature of the inverter heat sink is too high to keep inverter running. Rectifier over-current Rectifier failure due to over-current Input thyristor failure Failure of input thyristor Battery discharge thyristor failure Failure of battery discharge thyristor Battery charge thyristor failure Failure of battery charge thyristor Fan fault At least one of the cooling fans fails. Rectifier and inverter and charger shut down.
6 UPS modules alarm 24 ‘CAN communication fault’ when setting the qty of modules more than 2 units, but only work one module If only operate one module, reset the qty of modules to ‘ 7 UPS modules alarm 45 ‘Inverter off’ Inverter disconnection within 2 minutes in normal mode, UPS in maintenance mode more than 2 minutes change the maintenance mode to normal mode 8 The UPS module can not transfer to bypass or inverter Module does not well inserted; The left coronal screw is not tight. Output breaker do not switch on Pull out the module and insert again; Tighten the screw; Switch on the output breaker. 9 The UPS module fault LED remains ON The module is already damaged Take out this module, replace with a new module. 10 Utility LED is flashing Utility voltage exceeds UPS input range. If the UPS operates at battery mode, please pay attention to the remaining backup time needed for your system. 11 Battery LED is flashing but no charge voltage and current Battery breaker does not switch on, or batteries are damaged, or battery is reversely connected. battery number and capacity are not set correctly. Switch on the battery breaker. If batteries are damaged, need to replace whole group batteries, Connect the battery cables correctly; Go to LCD setting of the battery number and capacity, set the correct data. 12 Buzzer beeps every 0.5 seconds and LCD display “output overload” Overload remove some load 13 Buzzer long beeps, LCD display “output short circuit” The UPS output is in short circuit Make sure the load is not in short circuit, then restart the UPS. 14 The LED of the Module with RED light The module is not inserted properly. Pull out the module and insert properly. 15 The UPS only works on bypass mode The UPS is set to ECO mode, or the UPS is under maintenance mode. Set the UPS working mode to Single Module mode, change the maintenance mode to normal mode. 16 Can not Black start Battery switch is not properly closed； Battery fuse is not open； Or Battery low Close the battery switch； Change the fuse； Recharge the battery 17 Buzzer beeps continuously and LCD indicates Rectifier fault or output fault UPS is out of order Consult with your local agent for repair