LED display of Central Monitor Unit EPO switch O/P Switch UPS Module 1 UPS Module 2 UPS Module 3 UPS Module4 UPS Module 5 UPS Module 6 UPS Module 7 UPS Module 8 UPS Module 9 UPS Module 10 Maintenance Switch Maintenance switch & its cover Bottom cover for front door Main Switch for UPS Module 1 Main Switch for UPS Module 2 Main Switch for UPS Module 3 Main Switch for UPS Module 4 Main Switch for UPS Module 5 Main Switch for UPS Module 6 Main Switch for UPS Module 7 Main Switch for UPS Module 8 RS485 port （33）RS485 port Dry Contact Port LCD connecting port RS232 port OPTION port Intelligent Network Port SNMP port Terminal block for bypass& output Terminal block for Input, battery & GND Back blind cover Bypass switch for power module 1 Bypass switch for power module 2 Bypass switch for power module 3 Bypass switch for power module 4 Bypass switch for power module 5 Bypass switch for Module 6 Bypass switch for Power module 7 Bypass switch for power module 8 Bypass switch for power module 9 Bypass switch for power module 10 Parallel port （54）SCI Update port Bypass choke module Switch for input EMI capacitance
◄ Setting Record ► SYS Version: V02×10 LCD Version: 701×02F 100KVA 23-05-2012 ID:01 08:00 ◄ Command Setting Record Version ► Version data Module detailed record data 100KVA 23-05-2012 ID:01 08:00 ◄ Setting Record ► Battery Test Buzzer Set Default Set 100KVA 23-05-2012 ID:01 08:00 ◄ Setting Record ► Battery Test Buzzer Set Default Set Setting of battery test Setting of Buzzer 100KVA 23-05-2012 ID:01 08:00 ◄ Setting Record ► Battery Test Buzzer Default 100KVA 23-05-2012 ID:01 08:00 ◄ Setting Record ► Restore default setting Password setting
100KVA 23-05-2012 ID:01 08:00 ◄ Command Setting Record ► 100KVA 23-05-2012 ID:01 08:00 ◄ Command Setting Record ► Language/English Change Password Date Setting 2008-12-22 08:00:00 Back-light Delay 10Min Contrast 20 Self-Test Date disable Back Timing of ON/OFF disable Next Date setting Back-Light Delay setting 100KVA 23-05-2012 ID:01 08:00 ◄ Setting Record ► Language/English Change Password Date Setting 2008-12-22 08:00:00 Back-light Delay 10Min Contrast 20 Self-Test Date disable Back Timing of ON/OFF disable Next 100KVA 23-05-2012 ID:01 08:00 ◄ Setting Record ► Work Mode Single System Voltage Level 220V System Frequence Level 50HZ Auto Turn-on Enable Bypass Frequence Range 2% Bypass Volt. Upper Limit 10% Back Bypass Volt. Lower Limit -30% O/P Volt Regulation 0% Next Contrast setting Setting of work mode 100KVA 23-05-2012 ID:01 08:00 ◄ Setting Record ► Work Mode Single System Voltage Level 220V System Frequence Level 50H Auto Turn-on Ena Bypass Frequence Range 2% Bypass Volt. Upper Limit 10% Back Bypass Volt. Lower Limit -30 O/P Volt Regulation 0% Next 100KVA 23-05-2012 ID:01 08:00 ◄ Setting Record ► Work Mode Single System Voltage Level 220V System Frequence Level 50 Auto Turn-on Ena Bypass Frequence Range 2% Bypass Volt. Upper Limit 10% Back Bypass Volt. Lower Limit -3 O/P Volt Regulation 0% Next Setting of system volt. Level Setting of system freq. level
100KVA 23-05-2012 ID:01 08:00 ◄ Setting Record ► Work Mode Single System Voltage Level 220V System Frequence Level 50 Auto Turn-on Ena Bypass Frequence Range 2% Bypass Volt. Upper Limit 10% Back Bypass Volt. Lower Limit -3 O/P Volt Regulation 0% Next 100KVA 23-05-2012 ID:01 08:00 ◄ Setting Record ► Work Mode Single Method Normal System Voltage Level 220V System Frequence Level 50HZ Auto Turn-on Enable Bypass Frequence Range 2% Bypass Volt. Upper Limit 10% Back Bypass Volt. Lower Limit -30% O/P Volt Regulation 0% Next Setting of auto turn-on Setting of bypass freq.rang 100KVA 23-05-2012 ID:01 08:00 ◄ Setting Record ► Work Mode Single System Voltage Level 220V System Frequence Level 50 Auto Turn-on Enable Bypass Frequence Range 2% Bypass Volt. Upper Limit 10% Back Bypass Volt. Lower Limit -30 O/P Volt Regulation 0% Next 100KVA 23-05-2012 ID:01 08:00 ◄ Setting Record ► Work Mode Single Method Normal System Voltage Level 220V System Frequence Level 50 Auto Turn-on Ena Bypass Frequence Range 2% Bypass Volt. Upper Limit 10% Back Bypass Volt. Lower Limit -30 O/P Volt Regulation 0% Next Setting of bypass volt. Upper limit Setting of bypass volt. Lower limit 100KVA 23-05-2012 ID:01 08:00 ◄ Setting Record ► Work Mode Single System Voltage Level 220V System Frequence Level 50 Auto Turn-on Ena Bypass Frequence Range 2% Bypass Volt. Upper Limit 10% Back Bypass Volt. Lower Limit -30 O/P Volt Regulation 0% Next 100KVA 23-05-2012 ID:01 08:00 ◄ Setting Record ► Parallel ID 01 UPS Output Enable Float Volt Revise 0.001 Parallel Amount 04 Internal Module amount 05 Back Next Setting of output volt. Regulation Whole system ID (parallel ID) setting
100KVA 23-05-2012 ID:01 08:00 ◄ Command Setting Record ► Parallel ID 01 UPS Output Enable Float Volt Revise 0.00 Parallel Amount 04 Internal Module amount 05 Back Next 100KVA 23-05-2012 ID:01 08:00 ◄ Command Setting Record ► Parallel ID 01 UPS Output Enable Float Volt Revise 0.00 Parallel Amount 04 Internal Module amount 05 Back Next Setting of float charge volt. Compensation factor Setting of parallel modules amount 100KVA 23-05-2012 ID:01 08:00 ◄ Setting Record ► Parallel ID 01 UPS Output Enable Float Volt Revise 0.00 Parallel Amount 04 Internal Module amount 05 Back Next 100KVA 23-05-2012 ID:01 08:00 ◄ Command Setting Record ► Single Battery Volt. 12V Battery Number 20 Battery Group 1 Single Battery Capa. 100AH Boost Upper Limit Volt. 2.31 Float Base Volt. 2.25 Battery Protect Volt. 1.70 Boost Charge Enable Back Boost Last Time 231 Min Max Charge Current 25A Next Setting of internal module amount Setting of single battery voltage 100KVA 23-05-2012 ID:01 08:00 ◄ Setting Record ► Single Battery Volt. 12V Battery Number 20 Battery Group 1 Single Battery Capa. 100AH Boost Upper Limit Volt. 2.31 Float Base Volt. 2.25 Battery Protect Volt. 1.70 Boost Charge Enable Back Boost Last Time 231 Min Max Charge Current 25A Next 100KVA 23-05-2012 ID:01 08:00 ◄ Command Setting Record ► Single Battery Volt. 12V Battery Number 20 Battery Group 1 Single Battery Capa. 100AH Boost Upper Limit Volt. 2.31 Float Base Volt. 2.25 Battery Protect Volt. 1.70 Boost Charge Enable Back Boost Last Time 231 Min Max Charge Current 25A Next Setting of battery number Setting of battery group
module removed module is removed Cabinet Alarm Information No. Display message Meaning Rectifier Fault Rectifier detected faulty. Rectifier and inverter and charger shut down. Rectifier Over Temperature The temperature of heat sink is too high to keep the rectifier running. Charger and inverter shut down. Inverter Over temperature The temperature of the inverter heat sink is too high to keep inverter running. Rectifier over-current Rectifier failure due to over-current Input thyristor failure Failure of input thyristor Battery discharge thyristor failure Failure of battery discharge thyristor Battery charge thyristor failure Failure of battery charge thyristor Fan fault At least one of the cooling fans fails. Rectifier and inverter and charger shut down. DC Bus over-voltage Rectifier, inverter and battery converter are shutdown due to high DC bus voltage. DC Bus under-voltage Rectifier, inverter and battery converter are shutdown due to low DC bus voltage. DC bus unbalance If the difference between positive DC bus and negative DC bus exceeds 30V, this warning shall occur. Soft start fault Rectifier could not be started due to low DC bus voltage Input Neutral line missing If Input Neutral line is missing or disconnected while the UPS is in operation, the UPS will generate Neutral line failure alarm and go into Battery mode. Battery Reverse The polarity of the battery is reversed. No Battery Battery is disconnected Positive Battery Charger fault The positive battery Charger is fault. The charger will be shut down. Negative battery charger fault The negative battery charger is fault. The charger will be shut down. Battery under-voltage The battery voltage is too low and the charger has been deactivated. Battery over-voltage The battery voltage is too high and the charger has been deactivated. Battery under-voltage pre-warning The UPS is in battery operation and the battery voltage is low. Note: Runtime is limited in duration. Mains freq. abnormal Mains frequency is out of limit range and results in rectifier shutdown. Mains volt. Abnormal Mains Voltage exceeds the upper or lower limit and results in rectifier shutdown.
14 Can not Black start Battery switch is not properly closed； Battery fuse is not open； Or Battery low Close the battery switch； Change the fuse； Recharge the battery 15 Buzzer beeps continuously and LCD indicates Rectifier fault or output fault UPS is out of order Consult with your local agent for repair Appendix 4 RS232 communication port definition Definition of Male port: Connection between PC RS232 port and UPS RS232 port PC RS232 port UPS RS232 port Pin 2 Pin 2 UPS send,PC receive Pin 3 Pin 3 PC send,UPS receive Pin 5 Pin 5 ground Available function of RS232 Monitor UPS power status. Monitor UPS alarm info. Monitor UPS running parameters. Timing off/on setting.