PROJECT: ADDITIONS TO THE LODGE AND MULL AT KIRKRIDGE
PROJECT NO: #9103.01

## BULLETIN NO. TWO

DATED: JANUARY 31, 1992

BIDS DUE: FEBRUARY 5, 1992

THE FOLLOWING CHANGES, REVISIONS AND/OR CORRECTIONS SHALL BE INCORPORATED INTO THE CONTRACT DOCUMENTS:

## REFER TO SPECIFICATIONS

ITEM NO. 1 - REFER TO SECTION 9B.3a: REVISE TO READ AS FOLLOWS = "a.FLOORS - THIN SET METHOD F142, WITH LATEX ADHESIVES FOR BOTH CERAMIC AND QUARRY TILE."

ITEM NO. 2 - REFER TO SECTION 9D.1: REVISE TO READ "VINYL ASBESTOS TILE SHALL BE 12"x 12"x 1/8" THICK".

## REFER TO DRAWINGS

DRAWING A-2 - INSTALL 4" AND 6" FOUNDATION DRAINAGE PIPING AS SHOWN ON ENCLOSED DRAWING A-2R (DATED 1-31-92). CONNECT ROOF WATER LEADERS (2) IN DINING ROOM/LOBBY ADDITION DIRECTLY INTO THIS SYSTEM.

DRAWING D-1 - NOTE THAT ALL EQUIPMENT, CABINETRY, WINDOWS, AND DOORS THAT ARE TO BE REMOVED SHALL REMAIN THE OWNER'S PROPERTY. ALL OTHER MATERIALS TO BE REMOVED SHALL BE LEGALLY DISPOSED OF BY THE CONTRACTOR.

DRAWING S-1 - NOTE THAT EXISTING TREES IN THE AREA FOR THE NEW BEDROOM ADDITION SHALL BE CUT BY THE OWNER. THE CONTRACTOR SHALL REMOVE AND BURY STUMPS ON THE PROJECT SITE AS DIRECTED BY THE OWNER.

DRAWING A-1 - WHERE EXISTING SIDING IS TO BE REMOVED ON THE LODGE BUILDING, NOTE THAT EXISTING WOOD TRIM AT CORNERS, WINDOWS, AND TOP OF WALL SHALL REMAIN WHEREVER FEASIBLE. EXISTING SOFFITS IN THESE AREAS SHALL REMAIN.

DRAWING A-3 AND A-4 - CARPETING SHALL BE INSTALLED BY THE OWNER AND IS NOT PART OF THIS CONTRACT.

DRAWING P-1, E-2 - THE EXISTING KITCHEN HOOD AND EXHAUST FAN SHALL BE REMOVED AND RE-USED IN THE NEW KITCHEN. THE CONTRACTOR SHALL BE RESPONSIBLE TO RE-INSTALL THE EXISTING SYSTEM, WITH ALL SWITCHES AND CONTROLS AS REQUIRED.

## Print E-1

1. Delete pad transformer. Trench to remain from building to new pole.

## Print E-2

2. Fixture Type K - change to VISA Cat No. CV1005 with (2) - 250W TH Lamps

New Prints F-1, F-2

1. Furnish and install complete operational fire alarm system per plans and specifications.

Print P-1

1. At contractor's option the specified Universal Runtal Vanity with the louvered door may be substituted with a paneled door.

2. Provide and install a J.R. Smith Model DX2010B floor drain in the handicapped showers. Follow the same installation detail as shown for the kitchen drains. Caulk between the tile and drain watertight.

Print P-2

3. Pipe between water storage tank and building shall be Type "K" copper with no-lead solder joints.

HVAC:

Print H-1

1. Provide and install a 4" dia. galvanized metal duct and wall cap for exhaust fans EF-5 and 6.

## Fire Alarm System

1. This Contractor shall furnish all equipment, material and labor necessary to install a complete signalling system including operating station, signals, control panels, etc., as herein specified and as shown on the drawing. The system shall comply with and be installed in strict accordance with rules and regulations governing fire alarm installations.

2. The system shall be of the electrically operated and supervised ringing, closed circuit non-interferring type designed for Class "A" operation equal to Simplex Time Recorder Company 2001-8001 or approved equal as manufactured by Standard Electric Time Company or Kidde, when approved equal. This Contractor shall submit for approval descriptive data and detailed drawings must be approved by the Architect before execution of any work. Every part of this system shall be of the best grade on the market, both as to material and workmanship and shall be of rugged design, suitable for long life with minimum maintenance. The alarm stations and control panel shall be the product of one manufacturer. Assembled systems, i.e.; comprised of units of which any one of the major operation units noted herein are not of the same manufacture, will not be accepted.

3. The actuation of an alarm initiating device shall cause the following to occur:

A. Cause all local alarm devices to sound on a march time basis until manually silenced at the control panel or thru a built-in adjustable timer that automatically silences the signal.

B. Indicate the zone in alarm at the control panel. The lamps shall lock-in until the system is manually reset.

C. Energize an alarm reporting relay for notifying the local fire department of the alarm. The local reporting circuit shall have a bypass switch which when activated causes a system trouble condition. The reporting shall be via an automatic telephone dialer.

4. In addition to the above operation during alarm conditions, the system shall have the following features;

A. Alarm resound and trouble reporting.

B. Supervision of both positive and negative circuits of panel and field wiring.

C. Normal power failure monitoring shall be included.

D. The fire alarm system shall include battery back-up for a minimum of 24 hours during normal power outage.

E. All wiring shall be no smaller than No. 14 AWG copper and protected in all exposed areas.

F. The new control panel shall connect to the main power source through a 20 ampere breaker with lockable handle painted red with the words "Fire Alarm" in white letters.

G. All manual stations shall be mounted at a height not exceeding 4'-6" from the floor.

5. Equipment shall be as follows:

A. Fire Alarm Control Panel: furnish and install a new Simplex Life Alarm Control that is solid state, with the correct number of plug-in modules listed below:

2001-1007 Alarm/Trouble Control
2001-2066 Battery Monitor
2001-2044 Alarm Reporting
2001-1019 Zone Modules
2001-2076 Signal Modules
2001-3043 Timer and March Time Module
2001-3021 Power Supply
2001-3058 Transformer
2761-9838 Transformer
2001-3072 Battery Back-up, 24 hours
2001-3002 Charger
2001-4131 Cabinet
2001-9148 Back Box

B. Fire Alarm Stations: Simplex Type 2099-9225 double action on flush boxes. Station shall have tumbler type key for resetting and testing.

C. Fire Alarm Signal: Simplex Type 2903-9101 audio/visual device.

D. Smoke Detector: Simplex Type 2098-9201 photo electric smoke detector mounted on Type 2098-9636 base.

E. Heat Detector: Simplex Type 2098-9446 heat detector rated at 135 degrees F.

F. Telephone Dialer: Simplex type 2770-9000 automatic two channel telephone dialer with a pre-recorded emergency fire message to dial an emergency fire answering service upon fire alarm activation.

6. The Contractor shall furnish and install in accordance with the manufacturer's instruction, all wiring, conduit and outlet boxes required for the erection of a complete and operational system as described herein and as shown on the drawings. All wiring shall be No. 14 AWG copper wire, of quantity necessary for approved manufacturer's equipment. The power shall be derived from the main incoming voltage to the main distribution panel. A lockable circuit breaker shall be provided to supply the control panel. The equipment supplier shall provide to the Electrical Contractor wiring diagrams for the proper installation of the system. Final connections to the control panel and testing shall be under direct supervision of the equipment supplier.

7. The manufacturer shall furnish the service of an engineer for instructing the operating personnel in the operation, maintenance and supervise checking of the system. The manufacturer shall also furnish the services of an