관             보
                       제15334호                                                               2003. 2. 27. (목요일)
                  5. Reception Office
                                                                     ◉한국전력공사공고제2003-7호
                    Procurement Team, KEDO Nuclear Power
                                                                           KEDO원전보조기기유자격업체등록안내공고
                    Dept., 
                                                                       우리공사의KEDO원전기자재공급유자격업체등
                    Korea Electric Power Corporation
                                                                     록요강을다음과같이공고합니다.
                    (Tel:02-3456-5773, Fax:02-3456-5698,
                                                                           2003년 2 월27일
                    e-mail:leegn@kepco.co.kr)
                                                                                            한국전력공사 사장
                   No         Item         Package No                     Specifications
                    1      Fiber Optic         E256      1. Quality Class:S
                            Cable for                    2. Relevant Codes and Standards
                        Security System                    ○IEC 793-1
                                                           ○ASME NQA-1
                                                         3. Scope of Supply
                                                           ○Fiber Optic Cable(Single Mode, 4C) 18,000m
                                                           ○Fiber Optic Cable(Single Mode, 8C) 2,000m
                                                         4. Technical Requirements
                                                           ○Cores
                                                             ▼Cores shall be made of quartz glass and coated
                                                               on the surface once with resin.
                                                             ▼The materials coated shall pass the continuous
                                                               proof test of more than 600g tensile strength.
                                                           ○Cable Strength Member
                                                             ▼Cable strength member shall be made of non-
                                                               conductive materials with sufficient material strength.
                                                             ▼Cable strength member shall be in the center of
                                                               cable outer jacket or shall be placed at the
                                                               appropriate space within the cable outer jacket.
                                                           ○Jacket
                                                             ▼Jacket shall be non-flammable.
                                                             ▼Jacket shall have the PE structure for withstanding
                                                               allowable tension weight and pressure.
                                                           ○Jelly Compound
                                                             ▼Jelly compound shall be filled in the cable to
                                                               prevent moisture. It shall not be poisonous,
                                                               conductive, or absorbent and shall have the
                                                               properties to serve the desired function of
                                                               preventing moisture in the cable.
                                                           ○Others
                                                             ▼Minimum bending radius shall be 20 times less
                                                               than the cable diameter.
                                                                  107