[도로명주소] 경상북도 칠곡군 석적읍 강변대로 2383-5
        일반철골구조 판넬지붕 1층 발전시설 1층 175.56㎡


▲ 기계기구목록


                                                                            제 작 자
일련      번
            명칭 · 종류 · 구조 · 규격 · 형식 · 용량                                     제작번호           수량     설치장소
호
                                                                            제작일자
                                                                                                  경상북도 칠곡군 석적읍 강
    1       FUEL CELL                                                                             변대로 2383-5



        (1) FULL CELL
                                                                            Bloom Energy            Fuel Cell Area
            ㆍME-FC-A1~AA/B1~BA/C1~CA/D1~DA/E1~EA/F1~FA/G1~G6                                66식
                                                                              2023.02                 (Outdoor)
            ㆍType : SOFC(고체산화물 연료전지)
            ㆍRated Power Output : 300 kW/Unit
            ㆍVoltage and Frequency : 480 Volts, 60 Hz
            ㆍSize(m) : 10.0W x 1.3L x 2.1H
            ㆍWeight(ton) : Static(Empty) 12.89 Dynamic(Full) -
            ㆍPower(kW) : BHP - , Rating : -
            ㆍPSM 대상 : O
            ㆍReference P&ID :
             CGFC-30000-ME-1DW-002-PID04/PID05 Process&Instrument
             Diagram_Rev.1


        (2) WDM
                                                                            Bloom Energy            Fuel Cell Area
            ㆍME-WD-A1, A2 / B1,B2 / C1,C2 / D1,D2 / E1,E2 / F1,F2 / G1,G2                   14식
                                                                              2023.02                 (Outdoor)
            ㆍType : Water Distribution Module(Cabinet)
            ㆍOperating Pressure : 2.46~10.55 bar
            ㆍSize(m) : 0.96W x 0.75L x 2.0H
            ㆍWeight(ton) : Static(Empty) 0.34 Dynamic(Full) 0.565
            ㆍPower(kW) : BHP - , Rating : -
            ㆍPSM 대상 : X
            ㆍReference P&ID :
             CGFC-30000-ME-1DW-002-PID03 Process&Instrument
             Diagram_Rev.1


        (3) TC
                                                                            Bloom Energy            Fuel Cell Area
            ㆍTC-A / B / C / D / E / F / G                                                   7식
                                                                              2023.02                 (Outdoor)
            ㆍType : Telementry Cabinet
            ㆍSize(m) : 0.914W x 0.673L x 1.98H
            ㆍWeight(ton) : Static(Empty) 0.45 Dynamic(Full) -
            ㆍPower(kW) : BHP - , Rating : -
            ㆍPSM 대상 : X
            ㆍReference P&ID : -


    2       WATER SUPPLY SYSTEM(City Water Pump Package)

        (1) City Water Tank                                                    WILO         1식        Outdoor
            ㆍME-TK-001                                                        2024.03
            ㆍType : Rectangular
            ㆍCapacity : 1.0 m3
            ㆍSize(m) : 1.2W x 1.3L x 1.2H
            ㆍWeight(ton) : Static(Empty) 0.3 Dynamic(Full) 1.3
            ㆍPower(kW) : BHP - , Rating : -
            ㆍPSM 대상 : X
            ㆍReference P&ID :