ㆍPSM 대상 : X
            ㆍReference P&ID :
             CGFC-30000-ME-1DW-002-PID11 Process&Instrument
             Diagram_Rev.1


        (5) COOLING TOWER
                                                                       삼중테크㈜
            ㆍME-TW-001                                                                1식      Outdoor
                                                                         2024.03
            ㆍType : Cross Flow Open Circuit
            ㆍCapacity : 72.6 m3/h(120 CTRT)
            ㆍSize(m) : 3.9W x 1.8L x 2.6H
            ㆍWeight(ton) : Static(Empty) 1.8 Dynamic(Full) 3.2
            ㆍPower(kW) : BHP - , Rating : 5.5
            ㆍPSM 대상 : X
            ㆍReference P&ID :
             CGFC-30000-ME-1DW-002-PID11 Process&Instrument
             Diagram_Rev.1


    5       SWGR & TR

        (1) VCB/MOF Panel
                                                                       LS일렉트릭                  전기동
            EL-HV-001~003, EL-HV-101~801                                              11면
                                                                        2024.3.18.             전기실
            Type : 22.9kV Incoming/Main/Feeder VCB Panel, MOF Panel
             · 정격전압/전류/차단전류 : 3P 24kV, 1250/630A, 25kA
             · 표준동작책무 : O-0.3s-CO-15s-CO
             · 정격차단시간 : ≤40ms
             · 조작방식(투입/트립) : Motor Spring Charging/Shunt Trip
            Size(m) : VCB Panel 0.8W x 2.4L x 2.4H
            Size(m) : MOF Panel 1.3W x 2.4L x 2.4H
            Weight(ton) : Static(Empty) 1.3, Dynamic(Full) -
            Power(kW) : BHP -, Rating -
            PSM 대상 : X
            Reference DWG. : CGFC-30000-EL-1DW-001-ERL01

        (2) ACB Panel
                                                                       비앤디솔루션                  전기동
            EL-LV-101~801                                                             8면
                                                                        2024.3.18.             전기실
            Type : Incoming ACB Panel
             · 정격전압/전류/차단전류 : 3P 690V, 5000/4000A, 85kA
             · 정격전압/전류/차단전류 : (4P 690V, 1600A, 65kA)
             · 표준동작책무 : O-CO-CO
             · 정격차단시간 : ≤40ms
             · 조작방식(투입/트립) : Motor Spring Charging/Shunt Trip
            Size(m) : 1.2W x 2.5L x 3.3H
            Weight(ton) : Static(Empty) 1.3, Dynamic(Full) -
            Power(kW) : BHP -, Rating -
            PSM 대상 : X
            Reference DWG. : CGFC-30000-EL-1DW-001-ERL01

                                                                      제 작 자
일련      번
            명칭 · 종류 · 구조 · 규격 · 형식 · 용량                               제작번호           수량     설치장소
호
                                                                      제작일자
        (3) MCCB Panel                                                 비앤디솔루션                  전기동
                                                                                      10면
            EL-LV-102~702, EL-LV-802~804                                2024.3.18.             전기실
            Type : Outgoing MCCB Panel
             · 정격전압/전류/차단전류 : 3P 480V, 630AF/500AT, 100kA
             · 조작방식(투입/트립) : Thermal Magnetic
            Size(m) : 1.2W x 2.5L x 2.4H
            Weight(ton) : Static(Empty) 1.3, Dynamic(Full) -
            Power(kW) : BHP -, Rating -
            PSM 대상 : X
            Reference DWG. : CGFC-30000-EL-1DW-001-ERL01