관               보
                         제15349호                                                                     2003. 3. 18. (화요일)
                      b. Only the representatives or those who                  should be written in Korean.
                        mandated (must hold ID) can get the guide             f. For any detailed information on the Project
                        book of the Project Ability Evaluation of               Ability Evaluation and the Project Schedule,
                        Attendance and should register by                       please contact Mr. C. W. Lim (Phone 02-
                        themselves.                                             3149-2257), Equipment Team, Seoul
                      c. Only the representatives or those who                  Architecture Office, KNR). Selected
                        mandated (must hold ID) can hand in the                 candidates after the evaluation of the
                        application form for participation in                   project ability will be individually informed
                        theProject by themselves.                               later.
                      d. The Project Ability Evaluation of
                        Attendance form should be filled out as the        ◉한국전력공사공고제K2003-8호
                        directions which will be released by Seoul                KEDO원전보조기기유자격업체등록
                        Construction Office. Any agent who fill out               안내공고
                        incorrectly or falsely might be disadvantageous,      우리공사의KEDO원전 기자재공급 유자격업체등
                        such as restricted participation in the later
                                                                           록요강을다음과같이공고합니다.
                        bids.                                                     2003년 3 월18일
                      e. In principle, all the documents of this bid                                한국전력공사사장
                    1. Package Name
                      ○Stand-by and Unit Auxiliary Transformer(E202)
                    2. Quality Class:T&S
                      ○T:O.L.T.C Control devices
                      ○R:Stand-by and Unit Auxiliary Transformers
                    3. Scope of Supply 
                      ○Eight (8) outdoor power transformers
                      ○Four (4) stand-by auxiliary transformer and four (4) unit auxiliary transformer outdoor power
                        transformers and all accessories(Including neutral grounding facilities and spare parts)
                    4. Applicable Codes, Standards and Regulation 
                      ○ANSI
                        C57.12.00/C57.12.70/C57.12.80/C57.13/C57.97/C62.11/C76.1/C76.1/C62.11/C57.12.90
                      ○IEEE PAS-86 No.12/4/ 32, IEEE C37.90.1/C57.19.01/C57.19.00/C37.90
                      ○ASME NQA-1, ANSI/AWS D1.1/ D1.3 , ICEA S-19-81, NEMA 250/LA-1/MG1/TR-1
                    5. Technical Requirement
                      ○Type
                        Three windings, three phase, 60 Hz, oil immersed, self-cooled/forced-air cooled (OA/FA),
                        outdoor,air seal cell ordiaphragm type, with automatic on-load tap-changing equipmentwith
                        seventeen(17)full capacity 1-1/4 percent taps, including eight above nominal and eight below
                        nominal voltage ratings, on H.V. side, Three phase tank type, And buried delta tertiary winding
                        for stand-by auxiliary transformers only
                                                                         50