installing a time delay on compressor
The delay on power-up begins timing when low voltage power is supplied to the compressor control module through âCâ and âRâ terminals. The delay on power-up time is 2 minutes plus 10% of the delay on break period. Energize 1st and 2nd stage cooling. Compressor should not start until the delay on power-up has expired. The delay on break period begins whenever âYâ is de-energized. The time period for the delay on break period is set by the red knob. Run the unit for at least 5 minutes. The unit should not go into lockout. During routine operation of the unit with now power interruptions the compressor will operated on demand with no delay.