Void coefficient
In nuclear engineering, the void coefficient (more properly called void coefficient of reactivity) is a number that can be used to estimate how much the reactivity of a nuclear reactor changes as voids (typically steam bubbles) form in the reactor moderator or coolant. Net reactivity in a reactor is the sum total of all these contributions, of which the void coefficient is but one. Reactors in which either the moderator or the coolant is a liquid typically will have a void coefficient value that is either negative (if the reactor is under-moderated) or positive (if the reactor  is over-moderated). Reactors in which neither the moderator nor the coolant is a liquid (e.g., a graphite-moderated, gas-cooled reactor) will have a void coefficient value equal to zero. It is unclear how the definition of 'void' coefficient applies to reactors in which the moderator/coolant is neither liquid nor gas (supercritical water reactor). Explanation. Nuclear fission reactors run on nuclear chain reactions, in which each nucleus that undergoes fission releases heat and neutrons. Each neutron may impact another nucleus and cause it to undergo fission. The speed of this neutron affects its probability of causing additional fission , as does the presence of neutron-absorbing material. On the one hand, thermal neutrons are more easily absorbed by fissile nuclei than fast neutrons, so a neutron moderator that slows neutrons will increase the reactivity of a nuclear reactor. On the other hand, a neutron absorber will decrease the reactivity of a nuclear reactor. These two mechanisms are used to control the thermal power output of a nuclear reactor. In order to keep a nuclear reactor intact and functioning, and to extract useful power from it, a cooling system must be used. Some reactors circulate pressurized water; some use liquid  metal, such as sodium, NaK, lead, or mercury; others use gases (see advanced gas-cooled reactor). If the coolant is a liquid, it may boil if the temperature inside the reactor rises. This boiling leads to "voids" inside the reactor. Voids may also form if coolant is lost from the reactor in some sort of accident (called a loss of coolant accident, which has other dangers). Some reactors operate with the coolant in a constant state of boiling, using the generated vapor to turn turbines. The coolant liquid may act as a neutron absorber, as a neutron moderator, usually as  both but with one or other role as the most influential. In either case, the amount of void inside the reactor can affect the reactivity of the reactor. The change in reactivity caused by a change of voids inside the reactor is directly proportional to the "void coefficient". A positive void coefficient means that the reactivity increases as the void content inside the reactor increases due to increased boiling or loss of coolant; for example, if the coolant acts predominantly as neutron absorber. This positive void coefficient causes a positive feedback loop, starting with the first occurrence of steam bubbles . This can quickly boil all the coolant in the reactor, if not countered by an (automatic) control mechanism, or if said mechanism's response time is too slow. This happened in the RBMK reactor that was destroyed in the Chernobyl disaster as the automatic control mechanism was mostly disabled (and the operators were trying somewhat recklessly to rapidly restore a high power level. Due to poor control rod design, the operators were unaware that there was a maximal level of neutron poison in the core). A negative void coefficient means that the reactivity decreases as the void content inside the  reactor increases - but it also means that the reactivity increases if the void content inside the reactor is reduced. In boiling-water reactors with large negative void coefficients, a sudden pressure rise (caused, for example, by unplanned closure of a streamline valve) will result in a sudden decrease in void content: the increased pressure will cause some of the steam bubbles to condense ("collapse"); and the thermal output will possibly increase until it is terminated by safety systems, by increased void formation due to the higher power, or, possibly, by system or component failures that relieve pressure, causing void content  to increase and power to decrease. Boiling water reactors are all designed (and required) to handle this type of transient. On the other hand, if a reactor is designed to operate with no voids at all, a large negative void coefficient may serve as a safety system. A loss of coolant in such a reactor decreases the thermal output, but of course heat that is generated is no longer removed, so the temperature could rise (if all other safety systems simultaneously failed). Thus, a large void coefficient, whether positive or negative, can be either a design issue (requiring more careful , faster-acting control systems) or a desired quality depending on reactor design. Gas-cooled reactors do not have issues with voids forming.