5Y6 40 Amp 4 Pole Normally Open NEMA 600V HVAC Definite Purpose Contactor – 110-120VAC Coil, Inductive 40A, Resistive 50A (Pack of 2)
Brand: 5Y6
<b>Pack of 2 40 Amp 4 Pole Normally Open NEMA 600V HVAC Definite Purpose Contactors</b> for heating, refrigeration and lighting installations.<br>Complies with NEMA 2 standard.<br><br><b>Technical Specifications:</b><br>– AC 40A. Definite Purpose. 600V<br>– Max 2 HP Single Phase @ 115V, 10 HP @ 230V, 15 HP Three Phase @ 480V<br>– DC 30A 24VDC<br>– Coil:120VAC, 67VA inrush, 15VA sealed<br>– Normally Open (N.O.) main contacts<br>– UL Listed<br>– Coil 110/120 VAC<br>– Weight: 1.08 lb (0.55 kg)<br>– Dimensions: 77.00 x 95.80 x 77.00 mm (3.00'' x 3.77'' x 3.00')<br><br><b>Compliance:</b><br>CSA C22.2 No. 14, EN 60947-4-1, EN 60947-5-1, IEC 947-2, IEC 60947-4-1, IEC 60947-5-1, UL 508, VDE 0660
INDUSTRIAL QUALITY COMPONENTS – Pack of 2 40Amp 4 Pole Normally Open (NO) Definite Purpose Contactors for HVAC (Heating, Ventilating and Air Conditioning) installations in home and industry. Complies with NEMA 2 standard for consistent and reliable setting. Suitable for 8-pole connections
APPLICATIONS – Heating, refrigeration and lighting. AC-1 for resistance furnaces, incandescent lamps or electric heaters; and AC-3 for air conditioners, compressors or fans
FULL AMP LOAD – Inductive/Motor Load: 40Amp. Resistive/Incandescent Load: 50Amp. DC Load: 30Amp @ 24VDC. Power Lug Terminal Capacity AWG # 4
COIL VOLTAGE AND LOAD – Voltage: AC 110V/120V, 50/60Hz. Load: 67 VA Inrush and 15VA Sealed
DIMENSIONS (approx.) – 77.00 x 95.80 x 77.00 mm / 3.00'' x 3.77'' x 3.00'' (Width x Height x Depth)