Spreadsheet: larry_campbell__20970__PG&E Samples
Sheet: PG&E Page 1

CONFIDENTIAL
[NAME] and PG&E Samples and Analytical Results
Date | Sample ID |  | Volume Drained |  | Comments |  |  |  | PG&E PCB | TW PCB | Location of sample point
 |  |  |  |  |  |  |  |  |  |  | Filter Scrubbers Downstream of
1999-01-29 00:00:00 | SLX-TW | 1-29-99-L | 6 oz |  |  |  |  |  | 55 PPM | 55 PPM | Solexol Plant
 |  |  |  |  |  |  |  |  |  |  | TW's Filter Scrubber at TW/PG&E
1999-01-29 00:00:00 | PGE-TW2 | 1-29-99-L | 1/2 gallon |  |  |  |  |  | 68 PPM | 69 PPM | Metering Station
 |  |  |  |  |  |  |  |  |  |  | PG&E's Seperator at PG&E's
1999-01-29 00:00:00 | PGE-Top3 | 1-29-99-L | 1 gallon |  |  |  |  |  | 64 PPM | 75 PPM | Compressor Station
 |  |  |  |  |  |  |  |  |  |  | PG&E's 34" Line A
1999-01-29 00:00:00 | PGE 10.84A | 1-29-99-L | 7 gallons |  |  |  |  |  | 2 PPM | < 1 PPM
 |  |  |  |  |  |  |  |  |  |  | PG&E's 34" Line B
1999-01-29 00:00:00 | PGE 10.84B |  | - |  | No sample taken per PG&E
 |  |  |  |  |  |  |  |  |  |  | Filter Scrubbers Downstream of
1999-02-05 00:00:00 | SLX-TW | 2-5-99-L | 6 oz. |  |  |  |  |  | 58 PPM | 55 PPM | Solexol Plant
 |  |  |  |  |  |  |  |  |  |  | TW's Filter Scrubber at TW/PG&E
1999-02-05 00:00:00 | PGE-TW2 | 2-5-99-L | 0 |  | No liquid for the sample |  |  |  |  |  | Metering Station
 |  |  |  |  | Per PG&E's request - Volume will |  |  |  |  |  | PG&E's Seperator at PG&E's
1999-02-05 00:00:00 | PGE-Top3 | 2-5-99-L | 2 gallons |  | recorded next week |  |  |  | 90 PPM | 92 PPM | Compressor Station
 |  |  |  |  |  |  |  |  |  |  | PG&E's Line A TCS
1999-02-05 00:00:00 | PGE-A6 | 2-5-99-L | - |  | No sample taken per PG&E |  |  |  |  |  | Downstream Scrubber
 |  |  |  |  |  |  |  |  |  |  | PG&E's Line B TCS
1999-02-05 00:00:00 | PGE-B6 | 2-5-99-L | 2 gallons |  |  |  |  |  | 17 PPM | 16 PPM | Downstream Scrubber
 |  |  |  |  |  |  |  |  |  |  | PG&E's 34" Line A
1999-02-05 00:00:00 | PGE 10.84A | 2-5-99-L | 2 gallons |  |  |  |  |  | 2 PPM | < 1 PPM
 |  |  |  |  |  |  |  |  |  |  | PG&E's 34" Line B
1999-02-05 00:00:00 | PGE 10.84B | 2-5-99-L | 2 gallons |  |  |  |  |  | 1 PPM | < 1 PPM
 |  |  |  |  |  |  |  |  |  |  | PG&E's 34" Line A
1999-02-05 00:00:00 | PGE 8.58A | 2-5-99-L | 8 oz |  |  |  |  |  | 2 PPM | 1 PPM
 |  |  |  |  |  |  |  |  |  |  | Filter Scrubbers Downstream of
1999-02-12 00:00:00 | SLX-TW | 2-12-99-L | 0 |  | No liquid for the sample |  |  |  |  |  | Solexol Plant
 |  |  |  |  |  |  |  |  |  |  | TW's Filter Scrubber at TW/PG&E
1999-02-12 00:00:00 | PGE-TW2 | 2-12-99-L | 0 |  | No liquid for the sample |  |  |  |  |  | Metering Station
 |  |  |  |  |  |  |  |  |  |  | PG&E's Seperator at PG&E's
1999-02-12 00:00:00 | PGE-Top3 | 2-12-99-L | 1 gallon |  |  |  |  |  | 92 PPM | 102 PPM | Compressor Station
 |  |  |  |  |  |  |  |  |  |  | PG&E's Line A TCS
1999-02-12 00:00:00 | PGE-A6 | 2-12-99-L |  |  | No sample taken per PG&E |  |  |  |  |  | Downstream Scrubber
 |  |  |  |  |  |  |  |  |  |  | PG&E's Line B TCS
1999-02-12 00:00:00 | PGE-B6 | 2-12-99-L |  |  | No sample taken per PG&E |  |  |  |  |  | Downstream Scrubber
 |  |  |  |  |  |  |  |  |  |  | PG&E's 34" Line A
1999-02-12 00:00:00 | PGE 10.84A | 2-12-99-L | 10 oz |  |  |  |  |  | 1 PPM | 1 PPM
 |  |  |  |  |  |  |  |  |  |  | PG&E's 34" Line B
1999-02-12 00:00:00 | PGE 10.84B | 2-12-99-L | 8 oz |  |  |  |  |  | ND | ND
 |  |  |  |  |  |  |  |  |  |  | PG&E's 34" Line B
1999-02-12 00:00:00 | PGE 8.58A | 2-12-99-L |  |  | No sample taken per PG&E
 |  |  |  |  |  |  |  |  |  |  | TW 20" 1st Siphon
1999-02-12 00:00:00 | PGE-TW4 | 2-12-99-L | 0 |  | No liquid for the sample
 |  |  |  |  |  |  |  |  |  |  | TW 20" 2nd siphon
1999-02-12 00:00:00 | PGE-TW5 | 2-12-99-L | 0 |  | No liquid for the sample
 |  |  |  |  |  |  |  |  |  |  | TW 20" 3rd Siphon
1999-02-12 00:00:00 | PGE-TW6 | 2-12-99-L | 0 |  | No liquid for the sample