Spreadsheet: 748772d1632332918-create-a-daily-rolling-schedules-from-multiple-worksheets-daily-work-schedule
Sheet: Ops Priorities

Unit | WO# (if applicable) | Pln | SR# | Description | OPS Priority | Ops Request Date | Planner Comments | Planner Comment Date
7 | 21-169586 | ENV | 135271 | U7 A Side Ammonia Liquid Injection Flow Meter In BQ | A | 2021-04-08 00:00:00 | IN PROGRESS
7 | 21-178303 | ENV | 135272 | U7 B Side Ammonia Liquid Injection - Needs Local Pressure & Temp Gauge | A | 2021-04-08 00:00:00 | IN PROGRESS
7 | 21-14625 | BOP1 | 125893 | (Safety) U7 [NAME]. Air Isolation Valves to Sluice Gate Valves | A | 2021-04-12 00:00:00
7 | 20-453460 | [NAME] | 116742 | There is a leak on a threaded fitting in the gray cabinet at the hydrogen farm | B |  | Ready for work | 2021-04-12 00:00:00
7 | 21-109805 | BOP1 | 131756 | 7-1 centac farthest west drain all is blowing through | B | 2021-03-23 00:00:00
7 | 21-132920 | BOP1 | 133659 | Fire protection vertical header near elevator shaft rusting needs repair | A
7 |  | FACILITIES | 136864 | U-7 plant heating first isolation valve will not isolate valve is located on platform above boiler | C
7 |  |  | 149901 | U7  bottom ash C hopper top of doghouse leaking
7 |  |  | 142838 | 7-5 CF air register position BQ in DCS
7 |  |  | 142841 | Unit 7 (5) HP heater drain valves showing a fault in DCS
7 |  | [NAME] | 146749 | 7-6A H.P feedwater heater continuous vent has a pin hole leak.  It is located on the feeder floor
7 |  | BOP1 | 147060 | U7 Fire protection pressurizing pump recirc line has a hole
7 |  | BOP1 | 147174 | 7-1 Centac CCW return valve is broken in the closed position | A
7 |  | BOILER | 147306 | 7-2 PA Fan VIV Damper Drive is Erratic | A
7 |  | I&C | 147337 | 7-1 BFP IB bearing has erratic temperature  - 7TEFW054 | B
7 |  | FACILITIES | 147361 | U7 turbine room floor grating is NOT fastened properly.  Since the outage these pieces have been in | B
7 |  | BOP1 | 147686 | 7-2 Centac Safety Valve
7 |  | I&C | 147584 | The TR set north insulator pipe is noisy (tapping).  Pls troubleshoot and repair.
7 |  | ENV | 148164 | U -7 7A layer 1 # 3 sonic not blowing | B
7 |  | BOP1 | 148169 | UNIT 7 7-2 CENTAC / OIL LEAK ON FLEXABLE HOSE CONECTION / BELOW SEAL AIR PRESSURE GAUGE / CAN'T MISS | A
7 |  | BOP1 | 148311 | UNIT 7 ''A'' WET-AIR SEPERATOR / HAS A PIN HOLE LEAK IN ELBOW GOING INTO TANK 7TH FLOOR | B
7 |  |  | 149257 | 7-1 ash sluice pump has a hole in the discharge line | B
7 |  |  | 150864 | UNIT 7 ''A'' SIDE FLYASH LINE / LEAK
7 |  |  | 151615 | Unit 7 C bottom ash hopper inspection plate after the jet pulsion pump gasket is blown out
8 |  |  | 149895 | 8-1 Steam packing exhauster drains are plugged - water is coming out of the shaft seals
8 |  | [NAME] | 136606 | Unit 8 Bearing 1 in the seismic probe 1X is in bad quality and needs replaced | B
8 | 20-325199 | BOP1 | 108814 | Several scabs on U8 Ash sluice line | B
8 | 21-291088 | BOP1 | 136689 | U8 BOTTOM ASH C HOPPER HAS A SMALL HOLE IN OUTER DOOR | B
8 | 21-79436 | [NAME] | 130385 | u8 - 8-1 id FAN LUBE OIL SKID HEATER IS NOT WORKING -checked the bkr ok and turned the heater all
8 | 21-22957 | BOP1 | 125503 | 8-2 sluice pump discharge manual handwheel keeps falling off. |  |  | Needs Planned
8 | 20-567069 | [NAME] | 123436 | Unit 8 cold reheat pipe hanger outside of the oil room is pulled out of the wall
8 | 20-572930 | IC | 123564 | 8 Primary Preheating Coil Regulator After Valve Very Hard to Operate
8 | 21-38420 | BOP1 | 128032 | U8 pit basement. Fire prot pump has excess water coming out of the inboard and ouboard pump bearings |  |  | Needs planned
8 |  |  | 142646 | U8 8-2 tr sets -several grounding straps needs to be held in place with ties to keep  it from ground
8 |  |  | 142649 | U8 precip roof -gutters are all plugged on both sides (see kent)
8 |  |  | 143134 | The drain plug on south overflow (weir) box has rusted away and missing.
8 |  | BOP1 | 146007 | U8 B side fly ash dry air separator above silo. Equalizing valves not working.
8 |  | BOP1 | 146180 | U8 Both A and C bottom ash sluice gates will not work using the screen.
8 |  | BOP1 | 146331 | 8-3 ASP Outboard Mechanical Seal Leaking
8 |  | BOP1 | 146332 | U8 [NAME] Hopper Access Door Leaking
8 |  | ELECTRICAL | 147504 | 8-1-1B Power Plus TR Set trips immediately on Undervoltage. | A
8 |  | ELECTRICAL | 147505 | 8-1-3B Power Plus trips breaker: Troubleshoot | A
8 |  | ELECTRICAL | 147507 | 8-2-2B TR set blown fuse. Repair. | A
8 |  | BOP1 | 147556 | 8B Clinker [NAME] needs repacked next opportunity.
8 |  |  | 148600 | The raw coal line for 8-5 mill is leaking. See long descr. | A
8 |  |  | 148564 | U8 - DCS - on the exciter page for U7(IN 8 CONTROL ROOM) the mvars and the MW do not change | A
8 |  |  | 149182 | just about every prox switch on all three sluice gates are not working properly. | A
8 |  |  | 149130 | U8 SCR "B" side ammonia skid has a leak in the bypass line around the inlet shutoff valve. See photo | B
8 |  |  | 149235 | U8 8 all mill burner  flame scanners -several do not show lit -see long dis. | A
8 |  |  | 150034 | U8 basement. Suction and discharge valve hand wheels on all 3 ash pumps need reattached. | B
8 |  |  | 150723 | U8 basement. 8-3 ash pump outboard pump bearing will not hold an oil level. Has a new sight glass.
8 |  |  | 151145 | U8 IR46 just kept running over and over -ir 58 runs with it and failed to start but keeps trying
8 |  |  | 151144 | U8 keeps getting the alarm "INVERTER 120V OUTPUT GROUNDED" -has come in and cleared several times
8 |  |  | 151530 | 8-2 service water strainer in pit is leaking from the changeover valve handle on top of strainer.
8 |  |  | 151531 | U8 basement. 8-3 ash pump suction header has a leak directly above the suction valve.
8 |  |  | 151639 | U8 A side fly ash hopper #3 is full of mud and will need to be sucked out.
8 |  |  | 151888 | U8 8-1 mill B swing valve - the arm broke off -got it back on but needs adjusted cardboard is on it now to make up the switch
8 |  |  | 151947 | U8 flyash economizer line just north of #22 hopper needs replaced.
8 |  |  | 151948 | U8 #21 economizer hopper has a hole just above the hopper gate.
8 |  |  | 151950 | U8 flyash hole in pipe where SCR branch line connects to main line.
8 |  |  | 151737 | U8 demin room sump arm linkage to float is getting stuck before level switch can start pump
7Outage |  | ELECT | 132608 | 7-6B HP heater extraction steam valve not operating (shows a fault in DCS) |  | 2021-04-08 00:00:00 | In Progress. 4 wires are lifted in control room. | 2021-04-12 00:00:00
7outage |  | [NAME] | 146399 | 7-1 BFPT LOW PRESSURE STOP VALVE See long Discription
7outage |  |  | 150228 | [NAME]: PA Duct has a leak on the air side. Location in description | B
8Outage |  |  | 149894 | 8-2 EHC Pump discharge ball valve needs replaced. The stem is worn out | A
8outage |  | ENV | 148102 | 8A SCR Inlet Door Leak - 14th Floor | A
8Outage | 20-358260 | [NAME] | 107820 | Unit 8 both 005 valves are closed and still leaking through
8Outage | 20-296755 | BOP1 | 106362 | UNIT 8 BOTTOM ASH C HOPPER INNER CYLINDER DOOR HOUSEING IS LEAKING WATER
8Outage | 20-304582 | BOP1 | 107042 | 8-1 ccw heat exchanger has a leak above supply isolation valve.
8Outage |  |  | 142084 | U8 - extraction line to check valve - this is very hard to reach -can another valve be added that is easier to get to --see [NAME]
8outage |  | [NAME] | 147295 | U8 -(outage)MOT east supply to the cooler needs replaced - it is getting stuck closed(almost tripped | A
8outage |  | BOILER | 147627 | U8 - IK 30 needs replaced is stuck in the boiler - lance is bent over and motor is burnt up | A
8Outage |  | BOILER | 147681 | U8 - 8-2 ID fan expansion joint has pulled away from the frame on the top east -C clamps have been | A
8Outage |  |  | 142760 | 8 Primary Preheating Coil Return Valve Too Hard to Operate
8outage |  |  | 142771 | U8 - main steam lead drains -the regulator and the isolation vlvs need replaced
8outage |  |  | 148425 | U8 south hydrastep is now running with a fault - i believe it is the side with the bad leak so its probably getting wet - found RLC 819 bkr Z tripped -when put back in all lights red and green lit up from the top to the bottom  the north hydrastep is also out and has been out since the outage - can we get this one going ??  sr 142770   the DCS has also been running with the north and south hi deviation going in and out of alarm at the moment it is not in alarm the north is +2.2 and the south is -1.2  we need to get one working
8outage |  |  | 151785 | Unit 8 New Large Blowdown Does Not Operate
8outage |  |  | 151786 | Unit 8 Mills - Needed All Three Seal Air Fans to Bring on All Mills
8outage |  |  | 152135 | Unit 8 has a steam leak on the 14th floor extraction steam dump valve at 8-5 DC Heater
7 |  |  | 152182 | UNIT 7 SG4 SLUICE LINE LEAKING BAD
6 |  |  | 152313 | 6-2 sump discharge valve has a broken bonnet, needs new bonnet or valve.
7 |  |  | 152311 | U7 Flyash air/water separators discharge line leaking at 6th floor
8outage |  |  | 152258 | The 8FW034A water supply INSIDE valve south hydrastep is leaking at the packing.
7 |  |  | 152369 | u7 bottom ash leak at bell coupling (EXPANSION JOINT) between A and B hoppers.
8 |  |  | 152443 | U8 Flyash SCR line has a hole in the elbow just past the hoppers before the section gate
8 |  |  | 152452 | U8 Econ line branch line has large hole between branch gate and hopper
4 |  |  | 152447 | 3/4 pit sump green [NAME] leak, up closer to stand pipe
8 |  |  | 152671 | U8 A clinker grinder Inspection plate below the clinker grinder gasket blew out.
7 |  |  | 152641 | The vacuum transmitter on 7A side flyash is reading erratically and needs replaced quickly.
8 |  |  | 152535 | U8 Ash Sluice Gates close when dumping bottom ash