Spreadsheet: 104824d1302274485-searching-and-comparing-text-string-in-2-columns-notional-sheet
Sheet: Data table

 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 0
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location
 | 2p | No fire diamond placards |  | Install fire diamond placards
 | 7e | Emergency vent device exhausts indoors |  | Relocate emergency vent device to exhaust outdoors
 | 8c | Low melting temperature metals used in piping system |  | Replace brass valves with steel
 | 8i | Possible leak identified in piping system |  | Repair/replace leaking fittings
 | 9b | No isolation valve on supply line at tank |  | Install steel isolation valve on supply line at tank
 | 9d/10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level
 | 10g | No fire safety valve installed on fuel distribution lines |  | Install fire safety valves on fuel distribution lines
 | 11e | No grounding system installed |  | Install permanent grounding system
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 0
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 0
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST
 | 2p | No fire diamond placards
 | 4a | Tank not protected from vehicular impact
 | 7e/f | Emergency vent gasket in need of replacement
 | 9d/10c | No anti-siphon valve located on lines extending below maximum fuel fill level
 | 11e | No grounding system installed
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 0
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 0
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B
 | 2p | No fire diamond placards |  | Install fire diamond placards
 | 6h | Debris and product identified in tank containment |  | Remove debris and product from inside containment
 | 7b | Vent piping used for other purposes than venting |  | Remove fill line from vent piping
 | 7c | Plastic used to close tank openings |  | Replace plastic plug with steel
 | 7e | No primary emergency vent device present |  | Install 3" UL-listed emergency vent device exhausting outdoors
 | 8i | Possible leak identified in piping system |  | Repair/replace leaking fittings
 | 9b | No isolation valve on supply line at tank |  | Install steel isolation valve on supply line at tank
 | 9d/10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level
 | 11e | No grounding system installed |  | Install permanent grounding system
 | Comments: Source of product in spill containment should be located and tank should be replaced if its integrity is compromised |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 0
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 0
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location
 | 2p | No fire diamond or fuel contents placards |  | Install fire diamond and fuel contents placards
 | 7d | Normal vent device too small |  | Install 1-1/4" normal vent device exhausting outdoors
 | 7e | No primary emergency vent device installed |  | Install 4" UL-listed emergency vent device exhausting outdoors
 | 8c | Low melting temperature metals used in piping system |  | Replace brass valves with steel
 | Comments: Minimum allowable venting size is 1-1/4" |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 0
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 0
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST
 | 2p | No fire diamond or fuel contents placards
 | 7d | Normal vent device too small
 | 7e | No primary emergency vent device installed
 | 8c | Low melting temperature metals used in piping system
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 0
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 0
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2p | No fire diamond or fuel contents placards |  | Install fire diamond and fuel contents placards
 | 7b | Normal vent used for other purpose than venting |  | Remove return line from vent piping
 | 7f | Secondary emergency vent improperly oriented |  | Relocate emergency vent so that it exhaust vertically above tank shell exhausting outside
 | 9d/10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level
 | 10a | No isolation valve located on distribution line at tank |  | Install steel isolation valve on distribution line at tank
 | 11e | No grounding system installed |  | Install permanent grounding system
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 0