Spreadsheet: 888511d1739018944-struggling-with-vlookup-xlookup-what-am-i-doing-wrong-test1
Sheet: export

Inspection - GVI Pipework Checklist | Insp Report | Result | Component | Inspected | Est Line Length | Coat Brkd | Est Line Req ReCoating | Scale | Flange Bolt | Supp/Trunnions | Hangers / Cans | Insulation | Welds | Cracks | Vibes | Fretting | Fatigue | [NAME] | Pen Seal | Deadlegs | Valves | Well Supported | Ext Deposits | Leak | [NAME] | Comment | Inspection - CVI Photo Results M-Tasks | Insp Report | Result | Component | Inspected Date | Test Point | Damage Type | Damage Grade | Open Anomalies | New Anomaly Required | Inspection Comment | Inspection - Pipe Supports CVI Results | Insp Report | Result | Component | Inspected | T/P | Coding | P/Supp Coat Brk | P/Supp Scale | Type | Length in Contact | Metal-Metal | CUPS | Working | Anoms | CUPS Refurb Req | Dissimilar Mat | Comment | Anomaly Tasks | Inspection - Trunnion CVI Results | Insp Report | Result | Component | Inspected | T/P | Type | [NAME] | Orient | [NAME] | [NAME] | Pipe Coat Brk | Pipe Scale | Anoms | Weep Hole | [NAME] | [NAME] | Refurb | Comment | Inspection - Relief Device Results | Insp Report | Result | Component | Inspected | Type | Tag | P&ID Set Press | TAG in Place & Legible | TAG Set Pressure | Coat Brkd | Bolts | Damage | Good Cond & Matches P&ID Set Press | Comment | Inspection - Deck & Wall Penetrations Results | Insp Report | Result | Component | Inspected | Pen Loc Type | Pen Type | Condition | [NAME] | Coating | [NAME] | Pipe Dia | [NAME] | Location | Description | [NAME] | Comment | Inspection - RAD Thickness Results | Insp Report | Result | Component | Inspected | TP | Test Point | Test Point Description | Test Point | Pipe Spec Nominal WT | Pipe Spec Nominal WT | Nom WT | P/Meas Nom WT | Minimum WT measured thickness | Minimum WT measured thickness | Minimum WT measured thickness | CWT Applied | Defect Type | Wall Loss | Comment | Anomaly Tasks | Inspection - UT Inspection Results | Insp Report | Result | Component | Inspected | T/P | Component | Eq PW | [NAME] | Scan Pos | [NAME] | Nom WT | [NAME] | Min WT | Defect Type | Wall Loss | [NAME] | [NAME] | Comment | Inspected Date | Component Parent | Test Point | Shot Ident | Equipment Type - Pipework | Nominal WT | Pipe Measured Nominal WT | Minimum WT measured thickness | Generic Defect Type | Type of Wall Loss | Indications of Internal Fouling / Debris | Inspection Comment
Y | BRT-2024-4206-M-GVI | BRT-2024-6566-GVI-PChecks | 01.00-CM-28046-C6B1 | 2024-06-29 00:00:00 | 2 | Code : C -- PC: Ri 5 - Major Damage | 2 | Code : B -- Scale Height: 1-3mm Loose scale easily removed | Code : B -- Bolt: B2-Minor Damage volume loss <20% | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Insulated | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable |  | Yes | No | Pass | No | Line: 1"-CM-28046-C6B1 seen to have full CBD and in poor condition, with gross corrosion evident on this line. Valve condition is good with body bolting seen to be in poor condition. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-06-29 00:00:00 |  |  |  |  | 4.55 |  |  |  |  |  | Line: 1"-CM-28046-C6B1 seen to have full CBD and in poor condition, with gross corrosion evident on this line. Valve condition is good with body bolting seen to be in poor condition.
Y | BRT-2024-4207-M-GVI | BRT-2024-6599-GVI-PChecks | CM-28047-C6B1 | 2024-07-01 00:00:00 | 1 | Code : C -- PC: Ri 5 - Major Damage | 1 | Code : D -- Full Circ Scale at Weld, [NAME] | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Insulated | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable |  | Yes | No | Pass | No | Line: 1"-CM-28047-C6B1 seen to have full CBD and in poor condition, with gross corrosion evident on this line. Ri5 Code C / Corrosion noted as Code D due to scale height full circumference in line with procedure of -/+> 3mm. Valve condition is poor full CBD, heavy rust and associated scale / body bolting seen to be in poor condition. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-01 00:00:00 |  |  |  |  |  |  |  |  |  |  | Line: 1"-CM-28047-C6B1 seen to have full CBD and in poor condition, with gross corrosion evident on this line. Ri5 Code C / Corrosion noted as Code D due to scale height full circumference in line with procedure of -/+> 3mm. Valve condition is poor full CBD, heavy rust and associated scale / body bolting seen to be in poor condition.
Y | BRT-2024-4208-M-GVI | BRT-2024-6639-GVI-PChecks | CM-28048-C6B1 | 2024-07-01 00:00:00 | 1 | Code : C -- PC: Ri 5 - Major Damage | 1 | Code : C -- Scale Height: 3-6mm Moderate scaling | Code : B -- Bolt: B2-Minor Damage volume loss <20% | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Insulated | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable |  | Yes | No | Pass | Yes | Line: 1"-CM-28048-C6B1 seen to have full CBD and in poor condition, with gross corrosion evident on this line. Valve: SP0632 / V28175 condition is poor with areas of general CBD, heavy rust and light to moderate scale evident. Body bolting on valve seen to be in poor condition. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-01 00:00:00 |  |  |  |  |  |  |  |  |  |  | Line: 1"-CM-28048-C6B1 seen to have full CBD and in poor condition, with gross corrosion evident on this line. Valve: SP0632 / V28175 condition is poor with areas of general CBD, heavy rust and light to moderate scale evident. Body bolting on valve seen to be in poor condition.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4345-M-GVI | BRT-2024-7016-RDWP | 428/026/F/N-005 | 2024-07-21 00:00:00 | Deck | No Seal | Code : A -- Good Condition | Not Applicable | Code : C -- PC: Ri 4 - Minor Damage | 02.00-CM-28121-L1C2 | 2 | N/A | BRT Production [NAME] | Mezz | No | There is minor scale corrosion on the internal side of the penetration typical of Code B. No issues or hard contact visible with the penetration. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-21 00:00:00 |  |  |  |  |  |  |  |  |  |  | There is minor scale corrosion on the internal side of the penetration typical of Code B. No issues or hard contact visible with the penetration.
Y | BRT-2024-4341-M-GVI | BRT-2024-7078-GVI-PChecks | CM-28116-C1B1 | 2024-07-25 00:00:00 | 0.5 | Code : A -- Good Condition | 0 | Code : A -- Not Applicable | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Insulated | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Not Applicable |  | Yes | No | Pass | No | Overall this line is in good condition typical of Code A with minor staining visible on the top coat. - The associated PSV (28-PSV-0023) is in good condition and the set pressure on the ID tag matches what is stated on the P&ID. - The associated bolting is in as new condition typical of Code A. No issues to report. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-25 00:00:00 |  |  |  |  |  |  |  |  |  |  | The associated PSV (28-PSV-0023) is in good condition and the set pressure on the ID tag matches what is stated on the P&ID. The associated bolting is in as new condition typical of Code A. No issues to report.
Y | BRT-2024-4342-M-GVI | BRT-2024-7082-GVI-PChecks | CM-28117-C1B1 | 2024-07-25 00:00:00 | 0.5 | Code : B -- PC: Ri 3 - Superficial | 0.5 | Code : B -- Scale Height: 1-3mm Loose scale easily removed | Code : B -- Bolt: B2-Minor Damage volume loss <20% | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Insulated | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Not Applicable |  | Yes | No | Pass | No | Overall this lines coating condition is in average condition typical of Code B with scale corrosion visible typical of Code B. - The associated PSV (28-PSV-0024) is in good condition with minor corrosion visible typical of Code B. The set pressure on the name plate matches what is stated on the P&ID, however there is no ID Tag present on the PSV. - The associated bolting is in good condition with 100% surface oxidisation typical of Code B. No issues to report. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-25 00:00:00 |  |  |  |  |  |  |  |  |  |  | The associated PSV (28-PSV-0024) is in good condition with minor corrosion visible typical of Code B. The set pressure on the name plate matches what is stated on the P&ID, However there is no ID Tag present. The associated bolting is in good condition with 100% surface oxidisation typical of Code B. No issues to report.
Y | BRT-2024-4372-M-GVI | BRT-2024-7096-GVI-PChecks | CM-28119-C1B1 | 2024-07-26 00:00:00 | 2 | Code : B -- PC: Ri 2 - Superficial | 0.2 | Code : B -- Scale Height: 1-3mm Loose scale easily removed | Code : B -- Bolt: B2-Minor Damage volume loss <20% | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Insulated | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Not Applicable |  | Yes | No | Pass | No | Overall this line is in good condition typical of Code A with an isolated area of scale corrosion on the flange typical of Code B. The lines associated bolting is typical of Code B also. No issues to report. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-26 00:00:00 |  |  |  |  |  |  |  |  |  |  | Overall this line is in good condition typical of Code A with an isolated area of scale corrosion on the flange typical of Code B. The lines associated bolting is typical of Code B also. No issues to report.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4298-M-GVI | BRT-2024-7122-RDWP | 427/008/S/N-007 | 2024-07-27 00:00:00 | Grating | No Seal | Code : A -- Good Condition | Not Applicable | Code : A -- Good Condition | [NAME] | 4 | N/A | BRT Production Main Deck | South side P1 | No | Grating penetration. Line not in contact with grating though very close. No evidence of fretting. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  |  |  |  |  |  |  |  |  |  | Grating penetration. Line not in contact with grating though very close. No evidence of fretting.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4338-M-GVI | BRT-2024-7137-RDWP | 427/009/S/N-007 | 2024-07-28 00:00:00 | Grating | No Seal | Code : A -- Good Condition | Not Applicable | Code : A -- Good Condition | 04.00-CM-28115-L1C2 | 4 |  | BRT Production Main Deck | P1 Main Deck | No | Penetration found in good general condition. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-28 00:00:00 |  |  |  |  |  |  |  |  |  |  | Penetration found in good general condition.
Y | BRT-2024-4338-M-GVI | BRT-2024-7144-GVI-PChecks | CM-28115-L1C2 | 2024-07-28 00:00:00 | 10 | Code : B -- PC: Ri 2 - Superficial | 0.3 | Code : B -- Scale Height: 1-3mm Loose scale easily removed | Code : A -- Good Condition | Code : B -- Supp: Minor Damage/Corrosion | Code : A -- Not Applicable | Code : A -- Not Insulated | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Good Condition |  | Yes | No | Pass | No | Pipework was found with isolated areas of superficial damage & corrosion present, code B. Support brackets 514-PS-153 & 512-PS-253 were found with minor damage/corrosion present to pipework, code B. TP37S & TP49S. Flange arrangements were found in good general condition throughout line.  Pipework at grating penetration was found in good general condition. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-28 00:00:00 |  |  |  |  |  |  |  |  |  |  | Pipework was found with isolated areas of superficial damage & corrosion present, code B. Support brackets 514-PS-153 & 512-PS-253 were found with minor damage/corrosion present to pipework, code B. TP37S & TP49S. Flange arrangements were found in good general condition throughout line.  Pipework at grating penetration was found in good general condition.
Y | BRT-2024-4723-M-GVI | BRT-2024-6590-GVI-PChecks | CM-28121-C6B1 | 2024-06-30 00:00:00 | 0.4 | Code : C -- PC: Ri 5 - Major Damage | 0.4 | Code : C -- Scale Height: 3-6mm Moderate scaling | Code : B -- Bolt: B2-Minor Damage volume loss <20% | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Insulated | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Good Condition | Code : A -- Not Present | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable |  | Yes | No | Pass | No | Complete coating breakdown along with uniform corrosion present to the valve with a measured scale height of 5mm. Galvanic corrosion to valve body as a result of dissimilar metal contact with the threaded hex plug being the most noble material. Valve bolting is intact, scale removed from nut revealed minimal material loss at flanged connections. Flanged connections are of dissimilar material. A cross sectional minimum measurement of 24.0mm and a height of 12.0mm was recorded from the nuts post corrosion removal on the valve body. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-06-30 00:00:00 |  |  |  |  |  |  |  |  |  |  | Complete coating breakdown along with uniform corrosion present to the valve with a measured scale height of 5mm. Galvanic corrosion to valve body as a result of dissimilar metal contact with the threaded hex plug being the most noble material. Valve bolting is intact, scale removed from nut revealed minimal material loss at flanged connections. Flanged connections are of dissimilar material. A cross sectional minimum measurement of 24.0mm and a height of 12.0mm was recorded from the nuts post corrosion removal on the valve body.
Y | BRT-2024-4209-M-GVI | BRT-2024-6677-GVI-PChecks | 01.00-CM-28049-C6B1 | 2024-07-02 00:00:00 | 1 | Code : C -- PC: Ri 5 - Major Damage | 1 | Code : C -- Scale Height: 3-6mm Moderate scaling | Code : B -- Bolt: B2-Minor Damage volume loss <20% | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Insulated | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable |  | Yes | No | Pass | No | Line: 1"-CM-28049-C6B1 seen to have full CBD and in poor condition, with gross corrosion evident on this line. Valve: V28085, seen to be in poor condition. Body bolting seen to be in poor condition with heavy rust and scale present. Handles are corroded and have seized. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-02 00:00:00 |  |  |  |  | 4.55 |  |  |  |  |  | Line: 1"-CM-28049-C6B1 seen to have full CBD and in poor condition, with gross corrosion evident on this line. Valve: V28085, seen to be in poor condition. Body bolting seen to be in poor condition with heavy rust and scale present. Handles are corroded and have seized.
Y | BRT-2024-4210-M-GVI | BRT-2024-6712-GVI-PChecks | CM-28051-C6B1 | 2024-07-03 00:00:00 | 4 | Code : C -- PC: Ri 5 - Major Damage | 2 | Code : B -- Scale Height: 1-3mm Loose scale easily removed | Code : B -- Bolt: B2-Minor Damage volume loss <20% | Code : D -- Supp: CUPS present with scale height visible at pipe support. | Code : A -- Not Applicable | Code : A -- Not Insulated | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable |  | Yes | No | Pass | No | Line: 1"-CM-28051-C6B1 seen to have full CBD and in poor condition, with gross corrosion evident on this line. Body bolting on valve seen to be in poor condition with Heavy rust and light scale on the graylok clamp at TP-22W and the upper flange of Valve: V28174. Upper flange bolting - Code B Pipe-supports are in poor condition. CUPS / potential for CUPS noted along with defective U-Bolt fitting, 2 of 3 have sheared and offer no support at these location. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-03 00:00:00 |  |  |  |  |  |  |  |  |  |  | Line: 1"-CM-28051-C6B1 seen to have full CBD and in poor condition, with gross corrosion evident on this line. Body bolting on valve seen to be in poor condition with Heavy rust and light scale on the graylok clamp at TP-22W and the upper flange of Valve: V28174. Upper flange bolting - Code B Pipe-supports are in poor condition. CUPS / potential for CUPS noted along with defective U-Bolt fitting, 2 of 3 have sheared and offer no support at these location.
Y | BRT-2024-4366-M-GVI | BRT-2024-6732-GVI-PChecks | CM-28135-L1C2 | 2024-07-04 00:00:00 | 0.5 | Code : A -- Good Condition | 0 | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Insulated | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable |  | Yes | No | Pass | No | Ri1 coating with topcoat breakdown. Undercoat appears to be intact. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-04 00:00:00 |  |  |  |  |  |  |  |  |  |  | Ri1 coating with topcoat breakdown. Undercoat appears to be intact.
Y | BRT-2024-4211-M-GVI | BRT-2024-6733-GVI-PChecks | CM-28058-C6B1 | 2024-07-03 00:00:00 | 1 | Code : C -- PC: Ri 5 - Major Damage | 1 | Code : C -- Scale Height: 3-6mm Moderate scaling | Code : B -- Bolt: B2-Minor Damage volume loss <20% | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Insulated | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable |  | Yes | No | Pass | No | Line: 1"-CM-28058-C6B1 seen to have full CBD and in poor condition, with gross corrosion evident on this line. Valve: V28182 coating condition was seen to be relatively good with full CBD, heavy rust and light to moderate scale evident on upper / lower flanges. No weeps / or seeps evident. Body bolting on valve seen to be in poor condition with Heavy rust and light scale. Upper flange bolting - Code B Lower flange bolting - Code A |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-03 00:00:00 |  |  |  |  |  |  |  |  |  |  | Line: 1"-CM-28058-C6B1 seen to have full CBD and in poor condition, with gross corrosion evident on this line. Valve: V28182 coating condition was seen to be relatively good with full CBD, heavy rust and light to moderate scale evident on upper / lower flanges. No weeps / or seeps evident. Body bolting on valve seen to be in poor condition with Heavy rust and light scale. Upper flange bolting - Code B Lower flange bolting - Code A
Y | BRT-2024-4365-M-GVI | BRT-2024-6735-GVI-PChecks | CM-28135-C1B1 | 2024-07-05 00:00:00 | 4 | Code : A -- Good Condition | 0 | Code : A -- Not Applicable | Code : B -- Bolt: B2-Minor Damage volume loss <20% | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Not Insulated | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable |  | Yes | No | Pass | No | Pipework has a Ri1 coating with no external corrosion noted. All the Flange bolting is in good condition with at worst code B condition with less than 20% material loss noted across the flats of the nuts. V28054 - Ri3 coating to valve body with light corrosion noted. Ri5 coating to blanked flange to top of valve with CAT A corrosion. V28053 - Ri5 coating breakdown to valve with up to 4mm of scale noted. 28-PSV-0058 - Ri3 coating breakdown to PSV with light corrosion. No tag present with ID and set pressure. Name plate has information scratched off and some information is not visible. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-05 00:00:00 |  |  |  |  |  |  |  |  |  |  | 28-PSV-0058 - Ri3 coating breakdown to PSV with light corrosion.  No tag present with ID and set pressure.  Name plate has information scratched off and some information is not visible.
Y | BRT-2024-4212-M-GVI | BRT-2024-6765-GVI-PChecks | CM-28074-C1B1 | 2024-07-05 00:00:00 | 0.5 | Code : A -- Good Condition | 0.1 | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Insulated | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable |  | Yes | No | Pass | No | Line: 0.75"-CM-28074-C1B1 seen to be in good condition, with no areas of gross corrosion evident on this line. Valve: V28210 - CBD, heavy rust and light to moderate scale Ri4-5 / Code B. Handle corroded but useable. Flange Bolting / connections - No weeps / or seeps evident and bolting fully coated and in good condition. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-05 00:00:00 |  |  |  |  |  |  |  |  |  |  | Line: 0.75"-CM-28074-C1B1 seen to be in good condition, with no areas of gross corrosion evident on this line. Valve: V28210 - CBD, heavy rust and light to moderate scale Ri4-5 / Code B. Handle corroded but useable. Flange Bolting / connections - No weeps / or seeps evident and bolting fully coated and in good condition.
Y | BRT-2024-4213-M-GVI | BRT-2024-6794-GVI-PChecks | CM-28074-L1C2 | 2024-07-05 00:00:00 | 0.5 | Code : A -- Good Condition | 0.1 | Code : A -- Good Condition | Code : B -- Bolt: B2-Minor Damage volume loss <20% | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Not Insulated | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable |  | Yes | No | Pass | No | Line: 0.75"-CM-28074-L1C2 seen to be in good condition, with no areas of gross corrosion evident on this line. â€¢ Valve: V281622 - CBD, heavy rust and light to moderate scale Ri3-4 / Code B. Handle corroded but useable. Flange Bolting / connections - No weeps / or seeps evident and bolting fully coated and in good condition with exception to bolting associated with the above valve that has rust evident but no loss recorded. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-05 00:00:00 |  |  |  |  |  |  |  |  |  |  | Line: 0.75"-CM-28074-L1C2 seen to be in good condition, with no areas of gross corrosion evident on this line. â€¢ Valve: V281622 - CBD, heavy rust and light to moderate scale Ri3-4 / Code B. Handle corroded but useable. Flange Bolting / connections - No weeps / or seeps evident and bolting fully coated and in good condition with exception to bolting associated with the above valve that has rust evident but no loss recorded.
Y | BRT-2024-4358-M-GVI | BRT-2024-6949-GVI-PChecks | 03.00-CM-28128-C1B1 | 2024-07-15 00:00:00 | 2 | Code : B -- PC: Ri 3 - Superficial | 1 | Code : C -- Scale Height: 3-6mm Moderate scaling | Code : B -- Bolt: B2-Minor Damage volume loss <20% | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Insulated | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Present â€“ Operational/Valve Isolated Deadleg |  | Yes | No | Pass | No | Overall this line is in average condition typical of Code B. There are isolated areas of corrosion typical of Code B/C. - 3 of the associated valves have scale corrosion present typical of Code B/C. - The associated bolting is in average condition typical of Code B and after descaling no measurable loss was noted. FM Recommended on this line. Note: There is a reducer on this line at TP11R as mentioned on the note on isometric. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-15 00:00:00 |  |  |  |  | 5.49 |  |  |  |  |  | Overall this line is in average condition typical of Code B. There are isolated areas of corrosion typical of Code B/C. - 3 of the associated valves have scale corrosion present typical of Code B/C. - The associated bolting is in average condition typical of Code B and after descaling no measurable loss was noted. FM Recommended on this line. Note: There is a reducer on this line at TP11R as mentioned on the note on isometric.
Y | BRT-2024-4373-M-GVI | BRT-2024-7128-GVI-PChecks | CM-28119-L1C2 | 2024-07-27 00:00:00 | 15 | Code : B -- PC: Ri 3 - Superficial | 5 | Code : B -- Scale Height: 1-3mm Loose scale easily removed | Code : B -- Bolt: B2-Minor Damage volume loss <20% | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Insulated | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Good Condition | Code : D -- Signs of wear due to contact | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Good Condition |  | Yes | No | Pass | No | Overall this line is in average condition with a coating breakdown typical of Code B. There are isolated areas of scale corrosion typical of Code B also. FM recommended. - The lines associated valves are in good condition with minor scale corrosion noted on the valve handles typical of Code A. - The lines associated PSV (28-PSV-0075) is in poor condition with a 100% surface corrosion visible typical of Code C. The PSV's ID tag is present and the pressure rating matches what is stated on the P&ID. - The lines associated bolting is in good condition typical of Code A. - There is possible fretting on the line at TP59S. - There are 10 x pipe supports on the is line. All 10 pipe supports were descaled and there were no signs of mechanical damage or perforations. 4 of the pipe supports (527-PS-016 / 527-PS-110 / 512-PS-248 / 516-PS-118) have a coating condition typical of Code B and have the possibility of CUPS.  The U-Bolt pipe support at TP150S needs to added to the Isometric Drawing. The line is secure with no signs of movement. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  |  |  |  |  |  |  |  |  |  | Needs adding to isometric.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2022-1368-M-GVI | BRT-2022-1369-MCVIR | 03.00-CM-28119-C1B1 | 2022-04-03 00:00:00 | Pump head 2 seal face | Mechanical Damage Internal |  |  | Yes |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2022-04-03 00:00:00 |  | Pump head 2 seal face |  |  | 5.49 |  |  |  |  |  | D4 FILM USED AS SENSITIVITY WAS REQUESTED BY THE CLIENT. FILMS WERE PROCESSED @ 22Â° USING MANUAL DEVELOPING
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4297-M-GVI | BRT-2024-4731-MCVIR | SP-04-044 | 2024-07-18 00:00:00 | EVI SP-04-44 | Flange Face Internal |  | BRT-2021-347-PS |  | Component not stripped so inspection was limited to external examination only. No damage to gasket or leaks were visible throughout inspection. Minor coating breakdown was noted on the main body and associated bolting code B. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-18 00:00:00 |  | EVI SP-04-44 |  |  |  |  |  |  |  |  | Component not stripped so inspection was limited to external examination only. No damage to gasket or leaks were visible throughout inspection. Minor coating breakdown was noted on the main body and associated bolting code B.
Y | BRT-2024-4215-M-GVI | BRT-2024-6831-GVI-PChecks | CM-28075-C1B1 | 2024-07-08 00:00:00 | 15 | Code : A -- Good Condition | 0 | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Not Insulated | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Good Condition |  | Yes | No | Pass | No | Line: 6" & 2"-CM-28075-C1B1 seen to be coated and in good condition, with no areas of gross corrosion / pitting on this line. Bolting was seen to be in good condition with superficial surface rusting evident on flange connection fittings @ TP-01W, TP-29W & TP-35W. Code A. Flange connections at these locations are also suffering from localised CBD, heavy surface rust and Light scale Ri3 Code B. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-08 00:00:00 |  |  |  |  |  |  |  |  |  |  | Line: 6" & 2"-CM-28075-C1B1 seen to be coated and in good condition, with no areas of gross corrosion / pitting on this line. Bolting was seen to be in good condition with superficial surface rusting evident on flange connection fittings @ TP-01W, TP-29W & TP-35W. Code A. Flange connections at these locations are also suffering from localised CBD, heavy surface rust and Light scale Ri3 Code B.
Y | BRT-2024-4360-M-GVI | BRT-2024-6941-GVI-PChecks | CM-28129-C1B1 | 2024-07-15 00:00:00 | 4 | Code : B -- PC: Ri 3 - Superficial | 0.5 | Code : B -- Scale Height: 1-3mm Loose scale easily removed | Code : A -- Good Condition | Code : B -- Supp: Minor Damage/Corrosion | Code : A -- Not Applicable | Code : A -- Not Insulated | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Not Applicable |  | Yes | No | Pass | No | Overall this line is in good condition typical of Code B with minor isolated areas of scale corrosion typical of Code A. - The associated valves are in good condition with minor scale corrosion noted on the valve handles typical of Code B. - The lines associated valve bolting is in good condition typical of Code A. - The lines associated trunnion pipe support is in good condition with isolated areas of scale corrosion typical of Code A visible. The supporting steelwork is in good condition also typical of Code A.  Note: There was no weep hole visible for an internal trunnion inspection. There are no integrity threats visible on this line. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-15 00:00:00 |  |  |  |  |  |  |  |  |  |  | Supporting steelwork in good condition also. No issues.
Y | BRT-2024-4359-M-GVI | BRT-2024-6948-GVI-PChecks | CM-28128-L1C2 | 2024-07-15 00:00:00 | 1 | Code : B -- PC: Ri 2 - Superficial | 0.3 | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Insulated | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Not Applicable |  | Yes | No | Pass | No | No issues with this line. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-15 00:00:00 |  |  |  |  |  |  |  |  |  |  | No issues with this line.
Y | BRT-2024-4217-M-GVI | BRT-2024-6969-GVI-PChecks | CM-28113-L1C2 | 2024-07-17 00:00:00 | 15 | Code : C -- PC: Ri 4 - Minor Damage | 1 | Code : B -- Scale Height: 1-3mm Loose scale easily removed | Code : B -- Bolt: B2-Minor Damage volume loss <20% | Code : C -- Supp: U-Bolts Missing/Loose | Code : A -- Not Applicable | Code : A -- Not Insulated | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Good Condition |  | Yes | No | Pass | No | Valve arrangement [NAME] was found with superficial damage and loose scale easily removed. Valve handle found with Material loss, code C. Pipe support brackets BRT-CM-28113-PS1 & BRT-CM-28113-PS2 were found with material loss and rounding of nuts, code C. TP04S & TP16S. Restricted access due to type of supports. Pipe support bracket BRT-CM-28113-PS5 was found with indication of onset of corrosion under pipe support (CUPS), code C. TP44S. Pipe support bracket BRT-CM-28113-PS6 was found with corrosion present, code B. TP67S. Photograph shows 28-PSV-0075. This was found with 100% surface corrosion present & dissimilar metal contact from data plate, code B. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-17 00:00:00 |  |  |  |  |  |  |  |  |  |  | Valve arrangement [NAME] was found with superficial damage and loose scale easily removed. Valve handle found with Material loss, code C. Pipe support brackets BRT-CM-28113-PS1 & BRT-CM-28113-PS2 were found with material loss and rounding of nuts, code C. TP04S & TP16S. Restricted access due to type of supports. Pipe support bracket BRT-CM-28113-PS5 was found with indication of onset of corrosion under pipe support (CUPS), code C. TP44S. Pipe support bracket BRT-CM-28113-PS6 was found with corrosion present, code B. TP67S. Photograph shows 28-PSV-0075. This was found with 100% surface corrosion present & dissimilar metal contact from data plate, code B.
Y | BRT-2024-4297-M-GVI | BRT-2024-6979-GVI-PChecks | CM-28114-C1B1 | 2024-07-17 00:00:00 | 25 | Code : C -- PC: Ri 5 - Major Damage | 5 | Code : C -- Scale Height: 3-6mm Moderate scaling | Code : B -- Bolt: B2-Minor Damage volume loss <20% | Code : B -- Supp: Minor Damage/Corrosion | Code : A -- Not Applicable | Code : A -- Not Insulated | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Not Applicable |  | Yes | No | Pass | No | Valve arrangement V-28011 was found with no valve handle present code C 4x pipe supports associated with the line were all noted to have light corrosion on supporting steelwork code B, no corrosion barriers were present. Trunnion support 513-PS-206 had no weephole so no internal inspection was carried out. The line between features 11S - 14E was found to have Ri5 code C scale build-up 3-6mm. [NAME] was inspected externally as strainer not stripped for internal examination, no leaks or damage noted |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-17 00:00:00 |  |  |  |  |  |  |  |  |  |  | Valve arrangement V-28011 was found with no valve handle present code C 4x pipe supports associated with the line were all noted to have light corrosion on supporting steelwork code B, no corrosion barriers were present. Trunnion support 513-PS-206 had no weephole so no internal inspection was carried out. The line between features 11S - 14E was found to have Ri5 code C scale build-up 3-6mm. [NAME] was inspected externally as strainer not stripped for internal examination, no leaks or damage noted
Y | BRT-2024-4345-M-GVI | BRT-2024-6991-GVI-PChecks | CM-28121-L1C2 | 2024-07-18 00:00:00 | 12 | Code : B -- PC: Ri 3 - Superficial | 3 | Code : B -- Scale Height: 1-3mm Loose scale easily removed | Code : A -- Good Condition | Code : D -- Supp: Scale height visible at pipe support 3-6mm (not CUPS). | Code : A -- Not Applicable | Code : A -- Not Insulated | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Not Applicable |  | Yes | No | Pass | No | Overall this line is in good condition with a coating breakdown typical of Code B / Ri3. There are isolated areas of scale corrosion typical of Code B, notably at TP105W, TP112S & TP117S. [NAME] to pictures. FM is recommended. - The lines associated flange bolting is in good condition typical of Code A. No issues. - Pipe supports at 117S, 126S & 133S possible CUPS. - Pipe support at 104T U-Bolt supports typical condition of Code A. No issues. - Pipe support at 112S Rest is typical of Code B. - Trunnion Pipe support at 84T is typical of Code A. There is a weep hole present and the weep hole is sealed. The supporting steelwork for this trunnion is typical of Code D as the scale height is between 3-6mm. After descaling there was no signs of mechanical damage or perforations visible. The line is secure with no signs of movement. FM is recommended on the supports. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-18 00:00:00 |  |  |  |  |  |  |  |  |  |  | Overall this line is in good condition with a coating breakdown typical of Code B / Ri3. There are isolated areas of scale corrosion typical of Code B, notably at TP105W, TP112S & TP117S. [NAME] to pictures. FM is recommended. - The lines associated flange bolting is in good condition typical of Code A. No issues. - Pipe supports at 117S, 126S & 133S possible CUPS. - Pipe support at 104T U-Bolt supports typical condition of Code A. No issues. - Pipe support at 112S Rest is typical of Code B. - Trunnion Pipe support at 84T is typical of Code A. There is a weep hole present and the weep hole is sealed. The supporting steelwork for this trunnion is typical of Code D as the scale height is between 3-6mm. After descaling there was no signs of mechanical damage or perforations visible. The line is secure with no signs of movement. FM is recommended on the supports.
Y | BRT-2024-4337-M-GVI | BRT-2024-7121-GVI-PChecks | CM-28115-C1B1 | 2024-07-27 00:00:00 | 15 | Code : B -- PC: Ri 3 - Superficial | 2 | Code : B -- Scale Height: 1-3mm Loose scale easily removed | Code : C -- Bolt: B3-Intermediate Damage volume loss 20-30% | Code : B -- Supp: Minor Damage/Corrosion | Code : A -- Not Applicable | Code : A -- Not Insulated | Code : A -- Not Applicable | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Not Present | Code : A -- Not Applicable | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Good Condition |  | Yes | No | Pass | No | Nuts & studs found with corrosion/scale present on V-28016 & V-28018. Scale removed and calliper readings taken 20%< nut volume <30%, code C. Various sections of pipework throughout line were found with <3[NAME] scale height present. Loose scale easily removed, code B.  Trunnion support 512-PS-264 was found with minor damage & corrosion present, code B. No weep hole present. Support brackets 516-PS-118 & 512-PS-248 were found with minor damage/corrosion present, code B. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  |  |  |  |  |  |  |  |  |  | Nuts & studs found with corrosion/scale present on V-28016 & V-28018. Scale removed and calliper readings taken 20%< nut volume <30%, code C. Various sections of pipework throughout line were found with <3[NAME] scale height present. Loose scale easily removed, code B.  Trunnion support 512-PS-264 was found with minor damage & corrosion present, code B. No weep hole present. Support brackets 516-PS-118 & 512-PS-248 were found with minor damage/corrosion present, code B.
Y | BRT-2024-4298-M-GVI | BRT-2024-7124-GVI-PChecks | [NAME] | 2024-07-27 00:00:00 | 25 | Code : B -- PC: Ri 3 - Superficial | 2 | Code : C -- Scale Height: 3-6mm Moderate scaling | Code : B -- Bolt: B2-Minor Damage volume loss <20% | Code : B -- Supp: Minor Damage/Corrosion | Code : A -- Not Applicable | Code : A -- Not Insulated | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Good Condition | Code : A -- Not Present | Code : A -- Not Applicable | Code : A -- Not Applicable | Code : A -- Good Condition | Code : A -- Not Applicable |  | Yes | No | Pass | No | In general pipework coating is Ri2, though it has isolated areas of heavier breakdown and associated Code B corrosion. There are 2 areas of Code C corrosion; 17S and 25S. Flanges are all in good condition; Ri3 coating breakdown at worst. The bolts on the flange at 16W have Code B corrosion. All other bolts are in good condition. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  |  |  |  |  |  |  |  |  |  | 2 areas of Code C corrosion; 17S & 25S.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4297-M-GVI | BRT-2024-6976-MCVIR | 04.00-CM-28114-C1B1 | 2024-07-17 00:00:00 | 49W | Flange Face Internal |  | BRT-2021-347-PS |  | Component not stripped so inspection was limited to external examination only. No damage to gasket or leaks were visible throughout inspection |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-17 00:00:00 |  | 49W |  |  | 6.02 |  |  |  |  |  | Weld feature 32W was specified in the RAD task BRT-2024-4676 however, OIE advised to select bend feature 33E, which is adjacent to feature 32W.  Lowest reading found was 5.8mm on the external of the bend. No evidence of internal corrosion was noted.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4345-M-GVI-CM-28121-L1C2 | BRT-2024-7024-RPSUPP | 527-PS-016 | 2024-07-21 00:00:00 | 133S | Code : C -- Supp: Indication of CUPS | Code : C -- PC: Ri 4 - Minor Damage | Code : B -- Scale Height: 1-3mm Loose scale easily removed | Rest Only | Greater than 60mm | Yes | Possible | Yes | BRT-2024-231-PS | Yes | No | Possible CUPS. | 1 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-21 00:00:00 |  | 133S |  |  |  |  |  |  |  |  | Possible CUPS.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4298-M-GVI-CM-28114-L1C2 | BRT-2024-7113-RPSUPP | 514-PS-079 | 2024-07-27 00:00:00 | 514-PS-079 | Code : B -- Supp: Minor Damage/Corrosion | Code : B -- PC: Ri 2 - Superficial | Code : A -- Scale Height: Less than 1mm Loose scale easily removed | Welded no repad | Greater than 60mm | Yes | No | Yes |  | No | No | Isolated Ri3 coating breakdown and Code B corrosion. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  | 514-PS-079 |  |  |  |  |  |  |  |  | Isolated Ri3 coating breakdown and Code B corrosion.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4298-M-GVI-CM-28114-L1C2 | BRT-2024-7114-RPSUPP | 514-PS-081 | 2024-07-27 00:00:00 | 514-PS-081 | Code : A -- Good Condition | Code : B -- PC: Ri 3 - Superficial | Code : A -- Good Condition | Clamp | Greater than 60mm | No | No | Yes |  | No | No | Support generally in good condition. Support and pipework have coating defects (approx. Ri3). |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  | 514-PS-081 |  |  |  |  |  |  |  |  | Support generally in good condition. Support and pipework have coating defects (approx. Ri3).
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4298-M-GVI-CM-28114-L1C2 | BRT-2024-7118-RPSUPP | BRT-CM-28114-PS1 | 2024-07-27 00:00:00 | BRT-CM-28114-PS1 | Code : B -- Supp: Minor Damage/Corrosion | Code : B -- PC: Ri 2 - Superficial | Code : A -- Good Condition | U-bolt | Greater than 60mm | Yes | No | Yes |  | No | No | [NAME] has Ri4 coating breakdown and Code B corrosion. U-bolt is in good condition. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  | BRT-CM-28114-PS1 |  |  |  |  |  |  |  |  | [NAME] has Ri4 coating breakdown and Code B corrosion. U-bolt is in good condition.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4298-M-GVI | BRT-2024-7127-MCVIR | [NAME] | 2024-07-28 00:00:00 | 17S & 25S | Scale External | Code : C -- Scale Height: 3-6mm Moderate scaling | BRT-2024-302-PS |  | 2 areas of Code C corrosion; 17S & 25S. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-28 00:00:00 |  | 17S & 25S |  |  |  |  |  |  |  |  | 2 areas of Code C corrosion; 17S & 25S.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4373-M-GVI-CM-28119-L1C2 | BRT-2024-7131-RPSUPP | 527-PS-110 | 2024-07-27 00:00:00 | 19W | Code : C -- Supp: Indication of CUPS | Code : B -- PC: Ri 3 - Superficial | Code : B -- Scale Height: 1-3mm Loose scale easily removed | Rest Only | Greater than 60mm | Yes | Possible | Yes | BRT-2024-256-PS | Yes | No | Possible CUPS. | 1 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  | 19W |  |  |  |  |  |  |  |  | Possible CUPS.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4373-M-GVI-CM-28119-L1C2 | BRT-2024-7136-RPSUPP | BRT-CM-28119-PS1 | 2024-07-27 00:00:00 | 69E | Code : B -- Supp: Minor Damage/Corrosion | Code : B -- PC: Ri 2 - Superficial | Code : A -- Good Condition | Welded with repad | Greater than 60mm | Yes | No | Yes |  | No | No | No issues. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  | 69E |  |  |  |  |  |  |  |  | No issues.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4337-M-GVI | BRT-2024-7200-MCVIR | 00.75-CM-28115-C1B1 | 2024-07-27 00:00:00 | 11O | Bolting | Code : C -- Bolt: B3-Intermediate Damage volume loss 20-30% | BRT-2024-242-PS |  | Nuts & studs found with corrosion/scale present on V-28018. Scale removed and calliper readings taken 20%< nut volume <30%, code C. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  | 11O |  |  | 3.91 |  |  |  |  |  | Nuts & studs found with corrosion/scale present on V-28018. Scale removed and calliper readings taken 20%< nut volume <30%, code C.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4337-M-GVI | BRT-2024-8425-MCVIR | 00.50-CM-28115-C1B1 | 2024-07-27 00:00:00 | 08O | Bolting | Code : C -- Bolt: B3-Intermediate Damage volume loss 20-30% | BRT-2024-259-PS |  | Nuts & studs found with corrosion/scale present on V-28016. Scale removed and calliper readings taken 20%< nut volume <30%, code C. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  | 08O |  |  | 3.73 |  |  |  |  |  | Nuts & studs found with corrosion/scale present on V-28016. Scale removed and calliper readings taken 20%< nut volume <30%, code C.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4345-M-GVI-CM-28121-L1C2 | BRT-2024-7019-RPSUPP | 528-PS-224 | 2024-07-21 00:00:00 | 84T | Code : D -- Supp: Scale height visible at pipe support 3-6mm (not CUPS). | Code : A -- Good Condition | Code : A -- Not Applicable | Unknown | Greater than 60mm | Yes | No | Yes | BRT-2024-229-PS | No | No | This is a Trunnion Pipe Support.  Pipe support at 84T is a Trunnion support typical of Code A. There is a weep hole present and the weep hole is sealed. The supporting steelwork for this trunnion is typical of Code D as the scale height is between 3-6mm. After descaling there was no signs of mechanical damage or perforations visible. The line is secure with no signs of movement. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-21 00:00:00 |  | 84T |  |  |  |  |  |  |  |  | This is a Trunnion Pipe Support.  Pipe support at 84T is a Trunnion support typical of Code A. There is a weep hole present and the weep hole is sealed. The supporting steelwork for this trunnion is typical of Code D as the scale height is between 3-6mm. After descaling there was no signs of mechanical damage or perforations visible. The line is secure with no signs of movement.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4345-M-GVI-CM-28121-L1C2 | BRT-2024-7021-RPSUPP | 512-PS-248 | 2024-07-21 00:00:00 | 112S | Code : B -- Supp: Minor Damage/Corrosion | Code : B -- PC: Ri 3 - Superficial | Code : B -- Scale Height: 1-3mm Loose scale easily removed | Rest Only | Greater than 60mm | Yes | No | Yes |  | No | No | No issues. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-21 00:00:00 |  | 112S |  |  |  |  |  |  |  |  | No issues.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4345-M-GVI-CM-28121-L1C2 | BRT-2024-7023-RPSUPP | 527-PS-110 | 2024-07-21 00:00:00 | 126S | Code : C -- Supp: Indication of CUPS | Code : C -- PC: Ri 4 - Minor Damage | Code : B -- Scale Height: 1-3mm Loose scale easily removed | U-bolt | Greater than 60mm | Yes | Possible | Yes | BRT-2024-232-PS | Yes | No | Possible CUPS. | 1 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-21 00:00:00 |  | 126S |  |  |  |  |  |  |  |  | Possible CUPS.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4337-M-GVI-CM-28115-C1B1 | BRT-2024-7095-RPSUPP | 512-PS-248 | 2024-07-26 00:00:00 | 512-PS-248 (TP32S) | Code : B -- Supp: Minor Damage/Corrosion |  | Code : A -- Good Condition | Rest Only | Less than 60mm | Yes | No | Yes |  | No | No | Support bracket 512-PS-248 was found with minor damage/corrosion present, code B. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-26 00:00:00 |  | 512-PS-248 (TP32S) |  |  |  |  |  |  |  |  | Support bracket 512-PS-248 was found with minor damage/corrosion present, code B.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4298-M-GVI-CM-28114-L1C2 | BRT-2024-7111-RPSUPP | 514-PS-111 | 2024-07-27 00:00:00 | 514-PS-111 | Code : B -- Supp: Minor Damage/Corrosion | Code : C -- PC: Ri 4 - Minor Damage | Code : B -- Scale Height: 1-3mm Loose scale easily removed | Clamp | Greater than 60mm | Yes | No | Yes |  | No | No | Isolated Ri3 coating breakdown and Code B corrosion. There is corrosion to the pipework but not at the contact points. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  | 514-PS-111 |  |  |  |  |  |  |  |  | Isolated Ri3 coating breakdown and Code B corrosion. There is corrosion to the pipework but not at the contact points.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4298-M-GVI-CM-28114-L1C2 | BRT-2024-7112-RPSUPP | 514-PS-108 | 2024-07-27 00:00:00 | 514-PS-108 | Code : B -- Supp: Minor Damage/Corrosion | Code : B -- PC: Ri 2 - Superficial | Code : A -- Good Condition | Clamp | Greater than 60mm | Yes | No | Yes |  | No | No | Isolated Ri3 coating breakdown and Code B corrosion. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  | 514-PS-108 |  |  |  |  |  |  |  |  | Isolated Ri3 coating breakdown and Code B corrosion.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4298-M-GVI-CM-28114-L1C2 | BRT-2024-7116-RPSUPP | 514-PS-084 | 2024-07-27 00:00:00 | 514-PS-084 | Code : A -- Good Condition | Code : B -- PC: Ri 2 - Superficial | Code : A -- Good Condition | Clamp | Greater than 60mm | Yes | No | Yes |  | No | No | Support in good condition. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  | 514-PS-084 |  |  |  |  |  |  |  |  | Support in good condition.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4373-M-GVI-CM-28119-L1C2 | BRT-2024-7133-RPSUPP | 512-PS-248 | 2024-07-27 00:00:00 | 32S | Code : C -- Supp: Indication of CUPS | Code : B -- PC: Ri 3 - Superficial | Code : B -- Scale Height: 1-3mm Loose scale easily removed | Rest Only | Greater than 60mm | Yes | Possible | Yes | BRT-2024-257-PS | Yes | No | Possible CUPS. | 1 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  | 32S |  |  |  |  |  |  |  |  | Possible CUPS.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4373-M-GVI-CM-28119-L1C2 | BRT-2024-7140-RPSUPP | BRT-CM-28119-PS2 | 2024-07-27 00:00:00 | 88S | Code : B -- Supp: Minor Damage/Corrosion | Code : B -- PC: Ri 3 - Superficial | Code : A -- Scale Height: Less than 1mm Loose scale easily removed | U-bolt | Less than 60mm | Yes | No | Yes |  | No | No | No issues. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  | 88S |  |  |  |  |  |  |  |  | No issues.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4373-M-GVI-CM-28119-L1C2 | BRT-2024-7142-RPSUPP | BRT-CM-28119-PS3 | 2024-07-27 00:00:00 | 123S | Code : B -- Supp: Minor Damage/Corrosion | Code : B -- PC: Ri 3 - Superficial | Code : A -- Good Condition | U-bolt | Greater than 60mm | Yes | No | Yes |  | No | No | No issues. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  | 123S |  |  |  |  |  |  |  |  | No issues.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4210-M-GVI-CM-28051-C6B1 | BRT-2024-6752-RPSUPP | BRT-CM-28051-PS7 | 2024-07-04 00:00:00 | TP-27S | Code : D -- Supp: CUPS present with scale height visible at pipe support. | Code : C -- PC: Ri 5 - Major Damage | Code : B -- Scale Height: 1-3mm Loose scale easily removed | U-bolt | Less than 60mm | Yes | Yes | Yes |  | Yes | No | Pipe support is coated and seen to be in poor condition, line is supported at this location. CBD, heavy rust and light to moderated scale on pipework around the support location indicating the potential of CUPS. U-Bolt has rubber gasket present but no gasket is in place between pipe and its support. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-04 00:00:00 |  | TP-27S |  |  |  |  |  |  |  |  | Pipe support is coated and seen to be in poor condition, line is supported at this location. CBD, heavy rust and light to moderated scale on pipework around the support location indicating the potential of CUPS. U-Bolt has rubber gasket present but no gasket is in place between pipe and its support.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4215-M-GVI-CM-28075-C1B1 | BRT-2024-6828-RPSUPP | 550-PS-728 | 2024-07-08 00:00:00 | TP-27S | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Good Condition | U-bolt | Greater than 60mm | Yes | No | Yes |  | No | No | Pipe support 550-PS-728 seen to be fully coated and in good condition, line is fully supported. U-Bolt in place and secure, with no rubber sleeve present. Bolts / nuts are in place, thread / nut definition apparent. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-08 00:00:00 |  | TP-27S |  |  |  |  |  |  |  |  | Pipe support 550-PS-728 seen to be fully coated and in good condition, line is fully supported. U-Bolt in place and secure, with no rubber sleeve present. Bolts / nuts are in place, thread / nut definition apparent.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4215-M-GVI-CM-28075-C1B1 | BRT-2024-6829-RPSUPP | 540-PS-266 | 2024-07-08 00:00:00 | TP-19S | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Good Condition | U-bolt | Greater than 60mm | Yes | No | Yes |  | No | Yes | Pipe support 550-PS-266 seen to be fully coated and in good condition, line is fully supported. U-Bolt in place and secure, with no rubber sleeve present. Bolts / nuts are in place, thread / nut definition apparent. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-08 00:00:00 |  | TP-19S |  |  |  |  |  |  |  |  | Pipe support 550-PS-266 seen to be fully coated and in good condition, line is fully supported. U-Bolt in place and secure, with no rubber sleeve present. Bolts / nuts are in place, thread / nut definition apparent.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4215-M-GVI-CM-28075-C1B1 | BRT-2024-6830-RPSUPP | 540-PS-267 | 2024-07-08 00:00:00 | TP-14T | Code : B -- Supp: Minor Damage/Corrosion | Code : A -- Good Condition | Code : A -- Good Condition | Guide Only | Greater than 60mm | Yes | No | Yes |  | No | No | Pipe support 540-PS-267 seen to be fully coated and in good condition, line is fully supported. Pipe-support at TP-14T, which was seen to be fully coated and in relatively good condition with some isolated area of CBD, heavy rust and light scale Ri3 Code B |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-08 00:00:00 |  | TP-14T |  |  |  |  |  |  |  |  | Pipe support 540-PS-267 seen to be fully coated and in good condition, line is fully supported. Pipe-support at TP-14T, which was seen to be fully coated and in relatively good condition with some isolated area of CBD, heavy rust and light scale Ri3 Code B
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4345-M-GVI-CM-28121-L1C2 | BRT-2024-7020-RPSUPP | 512-PS-249 | 2024-07-21 00:00:00 | 104T | Code : A -- Good Condition | Code : B -- PC: Ri 2 - Superficial | Code : A -- Not Applicable | U-bolt | Greater than 60mm | Yes | No | Yes |  | No | No | No issues. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-21 00:00:00 |  | 104T |  |  |  |  |  |  |  |  | No issues.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4337-M-GVI-CM-28115-C1B1 | BRT-2024-7094-RPSUPP | 512-PS-249 | 2024-07-26 00:00:00 | 512-PS-249 (TP28S) | Code : A -- Good Condition |  | Code : A -- Good Condition | U-bolt | Less than 60mm | No | No | Yes |  | No | No | U bolt support bracket 512-PS-249 was found in good general condition. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-26 00:00:00 |  | 512-PS-249 (TP28S) |  |  |  |  |  |  |  |  | U bolt support bracket 512-PS-249 was found in good general condition.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4298-M-GVI-CM-28114-L1C2 | BRT-2024-7110-RPSUPP | 514-PS-114 | 2024-07-27 00:00:00 | 514-PS-114 | Code : B -- Supp: Minor Damage/Corrosion | Code : B -- PC: Ri 3 - Superficial | Code : B -- Scale Height: 1-3mm Loose scale easily removed | Clamp | Greater than 60mm | Yes | No | Yes |  | No | No | Isolated Ri3 coating breakdown and Code B corrosion. There is corrosion to the pipework nut it is not at the contact points. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  | 514-PS-114 |  |  |  |  |  |  |  |  | Isolated Ri3 coating breakdown and Code B corrosion. There is corrosion to the pipework nut it is not at the contact points.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4298-M-GVI-CM-28114-L1C2 | BRT-2024-7120-RPSUPP | 514-PS-153 | 2024-07-27 00:00:00 | 514-PS-153 | Code : A -- Good Condition | Code : C -- PC: Ri 4 - Minor Damage | Code : A -- Good Condition | Rest Only | Greater than 60mm | No | No | Yes |  | No | No | Ri3 coating breakdown and Code A corrosion. Pipework coating is defective but no corrosion present. Shim present between pipe and support. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  | 514-PS-153 |  |  |  |  |  |  |  |  | Ri3 coating breakdown and Code A corrosion. Pipework coating is defective but no corrosion present. Shim present between pipe and support.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4373-M-GVI-CM-28119-L1C2 | BRT-2024-7134-RPSUPP | 512-PS-249 | 2024-07-27 00:00:00 | 39S | Code : B -- Supp: Minor Damage/Corrosion | Code : B -- PC: Ri 3 - Superficial | Code : B -- Scale Height: 1-3mm Loose scale easily removed | U-bolt | Greater than 60mm | Yes | No | Yes |  | No | No | No issues. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  | 39S |  |  |  |  |  |  |  |  | No issues.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4338-M-GVI-CM-28115-L1C2 | BRT-2024-7141-RPSUPP | 514-PS-153 | 2024-07-28 00:00:00 | 514-PS-153 (TP49S) | Code : A -- Good Condition |  | Code : B -- Scale Height: 1-3mm Loose scale easily removed | Rest Only | Less than 60mm | Yes | No | Yes |  | No | No | Support bracket 514-PS-153 was found with minor damage/corrosion present to pipework, code B. TP49S. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-28 00:00:00 |  | 514-PS-153 (TP49S) |  |  |  |  |  |  |  |  | Support bracket 514-PS-153 was found with minor damage/corrosion present to pipework, code B. TP49S.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4210-M-GVI-CM-28051-C6B1 | BRT-2024-6753-RPSUPP | BRT-CM-28051-PS8 | 2024-07-04 00:00:00 | TP-27S | Code : C -- Supp: U-Bolts Missing/Loose | Code : C -- PC: Ri 4 - Minor Damage | Code : B -- Scale Height: 1-3mm Loose scale easily removed | U-bolt | Less than 60mm | Yes | No | No |  | Yes | No | Pipe support PS-8 is coated and seen to be in poor condition, line is not secure at this location. CBD, heavy rust and light scale on pipework around the support location indicating the potential of CUPS if left without intervention. U-Bolt has rubber gasket present but no gasket is in place between pipe and its support. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-04 00:00:00 |  | TP-27S |  |  |  |  |  |  |  |  | Pipe support PS-8 is coated and seen to be in poor condition, line is not secure at this location. CBD, heavy rust and light scale on pipework around the support location indicating the potential of CUPS if left without intervention. U-Bolt has rubber gasket present but no gasket is in place between pipe and its support.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4210-M-GVI-CM-28051-C6B1 | BRT-2024-6754-RPSUPP | BRT-CM-28051-PS9 | 2024-07-04 00:00:00 | TP-40S | Code : C -- Supp: U-Bolts Missing/Loose | Code : C -- PC: Ri 5 - Major Damage | Code : B -- Scale Height: 1-3mm Loose scale easily removed | U-bolt | Less than 60mm | Yes | Possible | No |  | Yes | No | Pipe support PS-9 is coated and seen to be in poor condition, line is not secure at this location. CBD, heavy rust and light scale on pipework around the support location indicating the potential of CUPS if left without intervention. U-Bolt has rubber gasket present but no gasket is in place between pipe and its support. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-04 00:00:00 |  | TP-40S |  |  |  |  |  |  |  |  | Pipe support PS-9 is coated and seen to be in poor condition, line is not secure at this location. CBD, heavy rust and light scale on pipework around the support location indicating the potential of CUPS if left without intervention. U-Bolt has rubber gasket present but no gasket is in place between pipe and its support.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4217-M-GVI-CM-28113-L1C2 | BRT-2024-6960-RPSUPP | BRT-CM-28113-PS1 | 2024-07-17 00:00:00 | BRT-CM-28113-PS1 (TP04S) | Code : C -- Supp: U-Bolts Missing/Loose |  | Code : A -- Good Condition | U-bolt | Less than 60mm | No | No | No | BRT-2024-303-PS | No | No | Pipe support bracket BRT-CM-28113-PS1 was found with material loss and rounding of nuts, code C. TP04S. Restricted access due to type of support. | 1 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-17 00:00:00 |  | BRT-CM-28113-PS1 (TP04S) |  |  |  |  |  |  |  |  | Pipe support bracket BRT-CM-28113-PS1 was found with material loss and rounding of nuts, code C. TP04S. Restricted access due to type of support.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4345-M-GVI-CM-28121-L1C2 | BRT-2024-7022-RPSUPP | 512-PS-253 | 2024-07-21 00:00:00 | 117S | Code : C -- Supp: Indication of CUPS | Code : C -- PC: Ri 4 - Minor Damage | Code : B -- Scale Height: 1-3mm Loose scale easily removed | Rest Only | Greater than 60mm | Yes | Possible | Yes | BRT-2024-230-PS | Yes | No | Possible CUPS. | 1 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-21 00:00:00 |  | 117S |  |  |  |  |  |  |  |  | Possible CUPS.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4337-M-GVI-CM-28115-C1B1 | BRT-2024-7093-RPSUPP | 516-PS-118 | 2024-07-26 00:00:00 | 516-PS-118 (TP20S) | Code : B -- Supp: Minor Damage/Corrosion |  | Code : A -- Good Condition | Rest Only | Less than 60mm | Yes | No | Yes |  | No | No | Support bracket 516-PS-118 was found with minor damage/corrosion present, code B. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-26 00:00:00 |  | 516-PS-118 (TP20S) |  |  |  |  |  |  |  |  | Support bracket 516-PS-118 was found with minor damage/corrosion present, code B.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4298-M-GVI-CM-28114-L1C2 | BRT-2024-7119-RPSUPP | 514-PS-157 | 2024-07-27 00:00:00 | 514-PS-157 | Code : A -- Good Condition | Code : C -- PC: Ri 4 - Minor Damage | Code : A -- Good Condition | Rest Only | Greater than 60mm | No | No | Yes |  | No | No | Support has Ri3 coating breakdown and Code A corrosion. Pipework coating is defective but no corrosion present. Shim present between pipe and support. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  | 514-PS-157 |  |  |  |  |  |  |  |  | Support has Ri3 coating breakdown and Code A corrosion. Pipework coating is defective but no corrosion present. Shim present between pipe and support.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4373-M-GVI-CM-28119-L1C2 | BRT-2024-7132-RPSUPP | 512-PS-253 | 2024-07-27 00:00:00 | 27S | Code : B -- Supp: Minor Damage/Corrosion | Code : B -- PC: Ri 3 - Superficial | Code : A -- Good Condition | U-bolt | Greater than 60mm | Yes | No | Yes |  | No | No | No issues. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  | 27S |  |  |  |  |  |  |  |  | No issues.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4338-M-GVI-CM-28115-L1C2 | BRT-2024-7138-RPSUPP | 512-PS-253 | 2024-07-28 00:00:00 | 512-PS-253 (TP37S) | Code : A -- Good Condition |  | Code : B -- Scale Height: 1-3mm Loose scale easily removed | Rest Only | Less than 60mm | No | No | Yes |  | No | No | Support bracket 512-PS-253 was found with minor damage/corrosion present top pipework, code B. TP37S. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-28 00:00:00 |  | 512-PS-253 (TP37S) |  |  |  |  |  |  |  |  | Support bracket 512-PS-253 was found with minor damage/corrosion present top pipework, code B. TP37S.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4338-M-GVI-CM-28115-L1C2 | BRT-2024-7139-RPSUPP | 514-PS-154 | 2024-07-28 00:00:00 | 514-PS-154 (TP46S) | Code : A -- Good Condition |  | Code : A -- Good Condition | Rest Only | Less than 60mm | No | No | Yes |  | No | No | Support bracket 514-PS-154 was found in good general condition, TP46S. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-28 00:00:00 |  | 514-PS-154 (TP46S) |  |  |  |  |  |  |  |  | Support bracket 514-PS-154 was found in good general condition, TP46S.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4373-M-GVI-CM-28119-L1C2 | BRT-2024-7143-RPSUPP | CM-28119-L1C2 | 2024-07-27 00:00:00 | 150S | Code : B -- Supp: Minor Damage/Corrosion | Code : B -- PC: Ri 3 - Superficial | Code : A -- Scale Height: Less than 1mm Loose scale easily removed | U-bolt | Less than 60mm | Yes | No | Yes |  | No | No | Needs adding to isometric. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  | 150S |  |  |  |  |  |  |  |  | Needs adding to isometric.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4213-M-GVI-CM-28074-L1C2 | BRT-2024-6795-RPSUPP | D118-PS-001 | 2024-07-05 00:00:00 | TP-08S | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Good Condition | U-bolt | Less than 60mm | No | No | Yes |  | No | No | Pipe support fully coated and seen to be in good condition, line is fully supported. U-Bolt in place and secure, with rubber sleeve present. Bolts / nuts are in place and in good condition. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-05 00:00:00 |  | TP-08S |  |  |  |  |  |  |  |  | Pipe support fully coated and seen to be in good condition, line is fully supported. U-Bolt in place and secure, with rubber sleeve present. Bolts / nuts are in place and in good condition.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4217-M-GVI-CM-28113-L1C2 | BRT-2024-6957-RPSUPP | BRT-CM-28113-PS3 | 2024-07-16 00:00:00 | BRT-CM-28113-PS3 (TP16S) | Code : A -- Good Condition | Code : A -- Good Condition | Code : A -- Good Condition | U-bolt | Less than 60mm | No | No | Yes |  | No | No | U bolt support bracket BRT-CM-28113-PS3 was found in good general condition. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-16 00:00:00 |  | BRT-CM-28113-PS3 (TP16S) |  |  |  |  |  |  |  |  | U bolt support bracket BRT-CM-28113-PS3 was found in good general condition.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4217-M-GVI-CM-28113-L1C2 | BRT-2024-6961-RPSUPP | BRT-CM-28113-PS2 | 2024-07-17 00:00:00 | BRT-CM-28113-PS2 (TP12S) | Code : C -- Supp: U-Bolts Missing/Loose |  | Code : A -- Good Condition | U-bolt | Less than 60mm | No | No | Yes | BRT-2024-304-PS | No | No | Pipe support bracket BRT-CM-28113-PS2 was found with material loss and rounding of nuts, code [NAME] access due to type of support. | 1 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-17 00:00:00 |  | BRT-CM-28113-PS2 (TP12S) |  |  |  |  |  |  |  |  | Pipe support bracket BRT-CM-28113-PS2 was found with material loss and rounding of nuts, code [NAME] access due to type of support.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4217-M-GVI-CM-28113-L1C2 | BRT-2024-6962-RPSUPP | BRT-CM-28113-PS4 | 2024-07-17 00:00:00 | BRT-CM-28113-PS4 (TP28T) | Code : A -- Good Condition |  | Code : A -- Good Condition | Welded with repad | Greater than 60mm | Yes | No | Yes |  | No | No | Pipe support bracket BRT-CM-28113-PS4 was found in good general condition. TP28T. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-17 00:00:00 |  | BRT-CM-28113-PS4 (TP28T) |  |  |  |  |  |  |  |  | Pipe support bracket BRT-CM-28113-PS4 was found in good general condition. TP28T.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4297-M-GVI-CM-28114-C1B1 | BRT-2024-6968-RPSUPP | 527-PS-012 | 2024-07-17 00:00:00 | 63S | Code : B -- Supp: Minor Damage/Corrosion | Code : A -- Good Condition | Code : A -- Good Condition | U-bolt | Less than 60mm | Yes | No | Yes |  | No | No | No corrosion barrier in place. Coating breakdown on U-bolt noted code B. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-17 00:00:00 |  | 63S |  |  |  |  |  |  |  |  | No corrosion barrier in place. Coating breakdown on U-bolt noted code B.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4297-M-GVI-CM-28114-C1B1 | BRT-2024-6972-RPSUPP | 527-PS-013 | 2024-07-17 00:00:00 | 46T | Code : B -- Supp: Minor Damage/Corrosion | Code : A -- Good Condition | Code : A -- Good Condition | U-bolt | Less than 60mm | Yes | No | Yes |  | No | No | Isolated areas of minor corrosion on supporting steelwork Code B. No corrosion barrier in place. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-17 00:00:00 |  | 46T |  |  |  |  |  |  |  |  | Isolated areas of minor corrosion on supporting steelwork Code B. No corrosion barrier in place.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4337-M-GVI-CM-28115-C1B1 | BRT-2024-7070-RPSUPP | 512-PS-264 | 2024-07-25 00:00:00 | 512-PS-264 (TP02S) | Code : B -- Supp: Minor Damage/Corrosion |  | Code : B -- Scale Height: 1-3mm Loose scale easily removed | Unknown | Greater than 60mm | Yes | No | Yes |  | No | No | Trunnion support 512-PS-264 was found with minor damage & corrosion present, code B. No weep hole present. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-25 00:00:00 |  | 512-PS-264 (TP02S) |  |  |  |  |  |  |  |  | Trunnion support 512-PS-264 was found with minor damage & corrosion present, code B. No weep hole present.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4298-M-GVI-CM-28114-L1C2 | BRT-2024-7097-RPSUPP | 513-PS-153 | 2024-07-26 00:00:00 | 513-PS-153 | Code : B -- Supp: Minor Damage/Corrosion | Code : B -- PC: Ri 2 - Superficial | Code : A -- Good Condition | Rest and Guide | Greater than 60mm | Yes | Possible | Yes |  | No | No | Guide/rest support. Ri4 coating breakdown and Code B corrosion. <2mm scale. There is corrosion staining at the contact point with the pipework but no clear evidence of corrosion to the pipework. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-26 00:00:00 |  | 513-PS-153 |  |  |  |  |  |  |  |  | Guide/rest support. Ri4 coating breakdown and Code B corrosion. <2mm scale. There is corrosion staining at the contact point with the pipework but no clear evidence of corrosion to the pipework.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4298-M-GVI-CM-28114-L1C2 | BRT-2024-7107-RPSUPP | 513-PS-154 | 2024-07-27 00:00:00 | 513-PS-154 | Code : B -- Supp: Minor Damage/Corrosion | Code : B -- PC: Ri 2 - Superficial | Code : A -- Good Condition | Rest and Guide | Greater than 60mm | Yes | Possible | Yes |  | No | No | Guide/rest support. Ri4 coating breakdown and Code B corrosion. Staining visible at the contact points but no signs of scale. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  | 513-PS-154 |  |  |  |  |  |  |  |  | Guide/rest support. Ri4 coating breakdown and Code B corrosion. Staining visible at the contact points but no signs of scale.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4373-M-GVI-CM-28119-L1C2 | BRT-2024-7135-RPSUPP | 516-PS-118 | 2024-07-27 00:00:00 | 48S | Code : C -- Supp: Indication of CUPS | Code : B -- PC: Ri 3 - Superficial | Code : B -- Scale Height: 1-3mm Loose scale easily removed | Rest Only | Greater than 60mm | Yes | Possible | Yes | BRT-2024-258-PS | Yes | No | Possible CUPS. | 1 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  | 48S |  |  |  |  |  |  |  |  | Possible CUPS.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2022-3232-M-RAD | BRT-2022-3233-RRADT | 01.00-CM-28058-C6B1 | 2022-11-28 00:00:00 | TP11S DOWN | TP11S DOWN |  |  | 4.55 | 4.55 | 4.55 | 4.55 | 2.7 | 2.7 | 2.7 |  | External | Code : C -- Corr: 33-67% Corrosion Allowance Lost | READING ABOVE CONC OF 2.48mm |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2022-11-28 00:00:00 |  | TP11S DOWN | DOWN | Test Point Section | 4.55 | 4.55 mm | 2.70 mm | External | Code : C -- Corr: 33-67% Corrosion Allowance Lost | No | READING BELOW CONC OF 2.48mm & ON THE BORDER WITH THE MAWT OF 1.13mm
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-5635-M-RAD | BRT-2024-6796-RRADT | 01.00-CM-28046-C6B1 | 2024-07-09 00:00:00 | 31S | 31S |  |  | 4.55 | 4.55 | 4.55 | 3.72 | 3.37 | 3.37 | 3.37 |  | External | Code : C -- Corr: 33-67% Corrosion Allowance Lost | External corrosion but with no internal corrosion. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-09 00:00:00 |  | 31S | 31S South | Straight | 4.55 | 3.72 mm | 3.37 mm | External | Code : C -- Corr: 33-67% Corrosion Allowance Lost | No | Line: 1"-CM-28046-C6B1 seen to have full CBD and in poor condition, with gross corrosion evident on this line. Valve condition is good with body bolting seen to be in poor condition.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4674-M-RAD | BRT-2024-6940-RRADT | 00.75-CM-28128-C1B1 | 2024-07-15 00:00:00 | TP08O SOUTH | TP08O SOUTH |  |  | 3.91 | 3.91 | 3.91 | 3.91 | 9.82 | 9.82 | 9.82 |  | External | Code : A -- Wall loss within [NAME] (12.5%) with no signs of internal corrosion | OVERSIZED FEATURE. WALL LOSS UNQUANTIFIABLE WITHOUT KNOWN NOMINAL |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-15 00:00:00 |  | TP08O SOUTH | SOUTH | Small Bore Branch / Weld O'Let | 3.91 | 3.91 mm | 9.82 mm | External | Code : A -- Wall loss within [NAME] (12.5%) with no signs of internal corrosion | No | OVERSIZED FEATURE. WALL LOSS UNQUANTIFIABLE WITHOUT KNOWN NOMINAL
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4217-M-GVI-CM-28113-L1C2 | BRT-2024-6963-RPSUPP | BRT-CM-28113-PS5 | 2024-07-17 00:00:00 | BRT-CM-28113-PS5 (TP44S) | Code : C -- Supp: Indication of CUPS |  | Code : B -- Scale Height: 1-3mm Loose scale easily removed | Rest Only | Less than 60mm | Yes | Yes | Yes | BRT-2024-305-PS | Yes | No | Photograph shows Pipe support bracket BRT-CM-28113-PS5. This was found with indication of onset of corrosion under pipe support (CUPS), code C. TP44S. | 1 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-17 00:00:00 |  | BRT-CM-28113-PS5 (TP44S) |  |  |  |  |  |  |  |  | Photograph shows Pipe support bracket BRT-CM-28113-PS5. This was found with indication of onset of corrosion under pipe support (CUPS), code C. TP44S.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4217-M-GVI-CM-28113-L1C2 | BRT-2024-6967-RPSUPP | BRT-CM-28113-PS6 | 2024-07-17 00:00:00 | BRT-CM-28113-PS6 (TP67S) | Code : B -- Supp: Minor Damage/Corrosion |  | Code : A -- Good Condition | U-bolt | Less than 60mm | No | No | Yes |  | No | No | Pipe support bracket BRT-CM-28113-PS6 was found with corrosion present, code B. TP67S. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-17 00:00:00 |  | BRT-CM-28113-PS6 (TP67S) |  |  |  |  |  |  |  |  | Pipe support bracket BRT-CM-28113-PS6 was found with corrosion present, code B. TP67S.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4297-M-GVI-CM-28114-C1B1 | BRT-2024-6970-RPSUPP | 527-PS-014 | 2024-07-17 00:00:00 | 55W | Code : B -- Supp: Minor Damage/Corrosion | Code : A -- Good Condition | Code : A -- Good Condition | Guide Only | Less than 60mm | Yes | No | Yes |  | No | No | No integrity issues with pipe support. Isolated areas of minor coating breakdown and general coating staining code B |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-17 00:00:00 |  | 55W |  |  |  |  |  |  |  |  | No integrity issues with pipe support. Isolated areas of minor coating breakdown and general coating staining code B
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4297-M-GVI-CM-28114-C1B1 | BRT-2024-6978-RPSUPP | 513-PS-206 | 2024-07-17 00:00:00 | 02S | Code : B -- Supp: Minor Damage/Corrosion | Code : B -- PC: Ri 3 - Superficial | Code : B -- Scale Height: 1-3mm Loose scale easily removed | Unknown | Greater than 60mm | Yes | No | Yes |  | No | No | Ri3 coating breakdown noted with light scale 1-3mm on supporting steelwork and end plates code B. No weephole present for internal inspection. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-17 00:00:00 |  | 02S |  |  |  |  |  |  |  |  | Ri3 coating breakdown noted with light scale 1-3mm on supporting steelwork and end plates code B. No weephole present for internal inspection.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4298-M-GVI-CM-28114-L1C2 | BRT-2024-7108-RPSUPP | 513-PS-155 | 2024-07-27 00:00:00 | 513-PS-155 | Code : B -- Supp: Minor Damage/Corrosion | Code : B -- PC: Ri 2 - Superficial | Code : A -- Good Condition | Rest Only | Greater than 60mm | Yes | No | Yes |  | No | No | Isolated Ri3 coating breakdown and Code B corrosion. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  | 513-PS-155 |  |  |  |  |  |  |  |  | Isolated Ri3 coating breakdown and Code B corrosion.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4373-M-GVI-CM-28119-L1C2 | BRT-2024-7130-RPSUPP | 527-PS-016 | 2024-07-27 00:00:00 | 18S | Code : C -- Supp: Indication of CUPS | Code : B -- PC: Ri 3 - Superficial | Code : B -- Scale Height: 1-3mm Loose scale easily removed | Rest and Guide | Greater than 60mm | Yes | Possible | Yes | BRT-2024-239-PS | Yes | No | Possible CUPS. | 1 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  | 18S |  |  |  |  |  |  |  |  | Possible CUPS.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-7150-M-RAD | BRT-2024-7433-RRADT | 01.00-CM-28049-C6B1 | 2024-08-18 00:00:00 | TP18S North | TP18S North |  |  | 4.55 | 4.55 | 4.55 | 4.55 | 2.73 | 2.73 | 2.73 |  | External | Code : D -- Corr: 66-100% Corrosion Allowance Lost |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-08-18 00:00:00 |  | TP18S North | North | Straight | 4.55 | 4.55 mm | 2.73 mm | External | Code : D -- Corr: 66-100% Corrosion Allowance Lost | No | Line: 1"-CM-28049-C6B1 seen to have full CBD and in poor condition, with gross corrosion evident on this line. Valve: V28085, seen to be in poor condition. Body bolting seen to be in poor condition with heavy rust and scale present. Handles are corroded and have seized.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2022-3232-M-RAD | BRT-2022-3234-RRADT | 01.00-CM-28058-C6B1 | 2022-11-28 00:00:00 | TP11S NORTH | TP11S NORTH |  |  | 4.55 | 4.55 | 4.55 | 4.55 | 3.3 | 3.3 | 3.3 |  | External | Code : B -- Corr: <33% Corrosion Allowance Lost |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2022-11-28 00:00:00 |  | TP11S NORTH | NORTH | Test Point Section | 4.55 | 4.55 mm | 3.30 [NAME] | External | Code : B -- Corr: <33% Corrosion Allowance Lost | No | READING BELOW CONC OF 2.48mm & ON THE BORDER WITH THE MAWT OF 1.13mm
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2022-3232-M-RAD | BRT-2022-3235-RRADT | 01.00-CM-28058-C6B1 | 2022-11-28 00:00:00 | TP15S EAST | TP15S EAST |  |  | 4.55 | 4.55 | 4.55 | 4.55 | 2 | 2 | 2 |  | External | Code : C -- Corr: 33-67% Corrosion Allowance Lost | READING BELOW CONC OF 2.48mm |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2022-11-28 00:00:00 |  | TP15S EAST | EAST | Test Point Section | 4.55 | 4.55 mm | 2 mm | External | Code : C -- Corr: 33-67% Corrosion Allowance Lost | No | READING BELOW CONC OF 2.48mm & ON THE BORDER WITH THE MAWT OF 1.13mm
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2022-3232-M-RAD | BRT-2022-3236-RRADT | 01.00-CM-28058-C6B1 | 2022-11-28 00:00:00 | TP15S DOWN SOUTH HALF | TP15S DOWN SOUTH HALF |  |  | 4.55 | 4.55 | 4.55 | 4.55 | 1.2 | 1.2 | 1.2 |  | External | Code : D -- Corr: 66-100% Corrosion Allowance Lost | READING BELOW CONC OF 2.48mm & ON THE BORDER WITH THE MAWT OF 1.13mm |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2022-11-28 00:00:00 |  | TP15S DOWN SOUTH HALF | DOWN SOUTH HALF | Test Point Section | 4.55 | 4.55 mm | 1.20 mm | External | Code : D -- Corr: 66-100% Corrosion Allowance Lost | No | READING BELOW CONC OF 2.48mm & ON THE BORDER WITH THE MAWT OF 1.13mm
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2023-3380-M-RAD | BRT-2024-3414-RRADT | 01.00-CM-28047-C6B1 | 2024-03-17 00:00:00 | 30S Up | 30S Up |  |  | 4.55 | 4.55 | 4.55 | 4.08 | 2.89 | 2.89 | 2.89 |  | External | Code : D -- Corr: 66-100% Corrosion Allowance Lost | External corrosion but with no evidence of internal corrosion. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-03-17 00:00:00 |  | 30S Up | 30S Up | Straight | 4.55 | 4.08 mm | 2.89 mm | External | Code : D -- Corr: 66-100% Corrosion Allowance Lost | No | External corrosion but with no evidence of internal corrosion. Liquid level noted.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2023-3380-M-RAD | BRT-2024-3415-RRADT | 01.00-CM-28047-C6B1 | 2024-03-17 00:00:00 | 31S East | 31S East |  |  | 4.55 | 4.55 | 4.55 | 3.16 | 2.73 | 2.73 | 2.73 |  | External | Code : C -- Corr: 33-67% Corrosion Allowance Lost | External corrosion but with no evidence of internal corrosion. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-03-17 00:00:00 |  | 31S East | 31S East | Straight | 4.55 | 3.16 mm | 2.73 mm | External | Code : C -- Corr: 33-67% Corrosion Allowance Lost | No | External corrosion but with no evidence of internal corrosion. Liquid level noted.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2023-3380-M-RAD | BRT-2024-3416-RRADT | 01.00-CM-28047-C6B1 | 2024-03-17 00:00:00 | 30S East | 30S East |  |  | 4.55 | 4.55 | 4.55 | 3.52 | 2.83 | 2.83 | 2.83 |  | External | Code : D -- Corr: 66-100% Corrosion Allowance Lost | External corrosion but with no evidence of internal corrosion. Liquid level noted. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-03-17 00:00:00 |  | 30S East | 30S East | Straight | 4.55 | 3.52 mm | 2.83 mm | External | Code : D -- Corr: 66-100% Corrosion Allowance Lost | Yes | External corrosion but with no evidence of internal corrosion. Liquid level noted.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-5635-M-RAD | BRT-2024-6797-RRADT | 01.00-CM-28046-C6B1 | 2024-07-09 00:00:00 | 31S | 31S |  |  | 4.55 | 4.55 | 4.55 | 4.09 | 3.17 | 3.17 | 3.17 |  | External | Code : C -- Corr: 33-67% Corrosion Allowance Lost | External corrosion but with no internal corrosion. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-09 00:00:00 |  | 31S | 31S East | Straight | 4.55 | 4.09 mm | 3.17 mm | External | Code : C -- Corr: 33-67% Corrosion Allowance Lost | No | Line: 1"-CM-28046-C6B1 seen to have full CBD and in poor condition, with gross corrosion evident on this line. Valve condition is good with body bolting seen to be in poor condition.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4672-M-RAD | BRT-2024-9137-RRADT | 01.00-CM-28119-L1C2 | 2024-11-07 00:00:00 | TP152E SOUTH | TP152E SOUTH |  |  | 4.55 | 4.55 | 4.55 | 4.55 | 3.92 | 3.92 | 3.92 |  | External | Code : B -- Corr: <33% Corrosion Allowance Lost |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-11-07 00:00:00 |  | TP152E SOUTH | SOUTH | Bend | 4.55 | 4.55 mm | 3.92 mm | External | Code : B -- Corr: <33% Corrosion Allowance Lost | No | READING RECORDED ON THE BORDER OF BEING CODE C
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4672-M-RAD | [NAME] | 01.00-CM-28119-L1C2 | 2024-11-07 00:00:00 | TP154S SOUTH | TP154S SOUTH |  |  | 4.55 | 4.55 | 4.55 | 4.55 | 3.17 | 3.17 | 3.17 |  | External | Code : B -- Corr: <33% Corrosion Allowance Lost | READING RECORDED ON THE BORDER OF BEING CODE C |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-11-07 00:00:00 |  | TP154S SOUTH | SOUTH | Straight | 4.55 | 4.55 mm | 3.17 mm | External | Code : B -- Corr: <33% Corrosion Allowance Lost | No | READING RECORDED ON THE BORDER OF BEING CODE C
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4673-M-RAD | BRT-2024-9142-RRADT | 02.00-CM-28119-L1C2 | 2024-11-07 00:00:00 | TP61T NORTH | TP61T NORTH |  |  | 5.54 | 5.54 | 5.54 | 5.54 | 5.45 | 5.45 | 5.45 |  | Not Applicable | Code : A -- No Wall Loss noted | NO ISSUES |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-11-07 00:00:00 |  | TP61T NORTH | NORTH | Tee | 5.54 | 5.54 mm | 5.45 mm | Not Applicable | Code : A -- No Wall Loss noted | No | NO ISSUES
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2023-3380-M-RAD | BRT-2024-3417-RRADT | 01.00-CM-28047-C6B1 | 2024-03-17 00:00:00 | 31S East | 31S East |  |  | 4.55 | 4.55 | 4.55 | 3.14 | 2.74 | 2.74 | 2.74 |  | External | Code : D -- Corr: 66-100% Corrosion Allowance Lost | External corrosion but with no evidence of internal corrosion. Liquid level noted. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-03-17 00:00:00 |  | 31S East | 31S East | Straight | 4.55 | 3.14 mm | 2.74 mm | External | Code : D -- Corr: 66-100% Corrosion Allowance Lost | Yes | External corrosion but with no evidence of internal corrosion. Liquid level noted.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4675-M-RAD | BRT-2024-6958-RRADT | 03.00-CM-28129-C1B1 | 2024-07-15 00:00:00 | TP03T WEST | TP03T WEST |  |  | 5.49 | 5.49 | 5.49 | 5.49 | 5.93 | 5.93 | 5.93 |  | Not Applicable | Code : A -- No Wall Loss noted | NO ISSUES |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-15 00:00:00 |  | TP03T WEST | WEST | Tee | 5.49 | 5.49 mm | 5.93 mm | Not Applicable | Code : A -- No Wall Loss noted | No | NO ISSUES
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-5636-M-RAD | BRT-2024-7427-RRADT | 01.00-CM-28049-C6B1 | 2024-08-18 00:00:00 | TP18S NORTH | TP18S NORTH |  |  | 4.55 | 4.55 | 4.55 | 4.55 | 2.73 | 2.73 | 2.73 |  | External | Code : D -- Corr: 66-100% Corrosion Allowance Lost |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-08-18 00:00:00 |  | TP18S NORTH | NORTH | Straight | 4.55 | 4.55 mm | 2.73 mm | External | Code : D -- Corr: 66-100% Corrosion Allowance Lost | No | Line: 1"-CM-28049-C6B1 seen to have full CBD and in poor condition, with gross corrosion evident on this line. Valve: V28085, seen to be in poor condition. Body bolting seen to be in poor condition with heavy rust and scale present. Handles are corroded and have seized.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-5636-M-RAD | BRT-2024-7428-RRADT | 01.00-CM-28049-C6B1 | 2024-08-18 00:00:00 | TP18S UP | TP18S UP |  |  | 4.55 | 4.55 | 4.55 | 4.55 | 2.88 | 2.88 | 2.88 |  | External | Code : D -- Corr: 66-100% Corrosion Allowance Lost |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-08-18 00:00:00 |  | TP18S UP | UP | Straight | 4.55 | 4.55 mm | 2.88 mm | External | Code : D -- Corr: 66-100% Corrosion Allowance Lost | No | Line: 1"-CM-28049-C6B1 seen to have full CBD and in poor condition, with gross corrosion evident on this line. Valve: V28085, seen to be in poor condition. Body bolting seen to be in poor condition with heavy rust and scale present. Handles are corroded and have seized.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-5636-M-RAD | BRT-2024-7429-RRADT | 01.00-CM-28049-C6B1 | 2024-08-18 00:00:00 | TP22S NORTH | TP22S NORTH |  |  | 4.55 | 4.55 | 4.55 | 4.55 | 3.29 | 3.29 | 3.29 |  | External | Code : C -- Corr: 33-67% Corrosion Allowance Lost |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-08-18 00:00:00 |  | TP22S NORTH | NORTH | Straight | 4.55 | 4.55 mm | 3.29 mm | External | Code : C -- Corr: 33-67% Corrosion Allowance Lost | No | Line: 1"-CM-28049-C6B1 seen to have full CBD and in poor condition, with gross corrosion evident on this line. Valve: V28085, seen to be in poor condition. Body bolting seen to be in poor condition with heavy rust and scale present. Handles are corroded and have seized.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-5636-M-RAD | BRT-2024-7430-RRADT | 01.00-CM-28049-C6B1 | 2024-08-18 00:00:00 | TP22S EAST | TP22S EAST |  |  | 4.55 | 4.55 | 4.55 | 4.55 | 3.4 | 3.4 | 3.4 |  | External | Code : C -- Corr: 33-67% Corrosion Allowance Lost |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-08-18 00:00:00 |  | TP22S EAST | EAST | Straight | 4.55 | 4.55 mm | 3.40 mm | External | Code : C -- Corr: 33-67% Corrosion Allowance Lost | No | Line: 1"-CM-28049-C6B1 seen to have full CBD and in poor condition, with gross corrosion evident on this line. Valve: V28085, seen to be in poor condition. Body bolting seen to be in poor condition with heavy rust and scale present. Handles are corroded and have seized.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-7150-M-RAD | BRT-2024-7434-RRADT | 01.00-CM-28049-C6B1 | 2024-08-18 00:00:00 | TP18S Up | TP18S Up |  |  | 4.55 | 4.55 | 4.55 | 4.55 | 2.88 | 2.88 | 2.88 |  | External | Code : D -- Corr: 66-100% Corrosion Allowance Lost |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-08-18 00:00:00 |  | TP18S Up | Up | Straight | 4.55 | 4.55 mm | 2.88 mm | External | Code : D -- Corr: 66-100% Corrosion Allowance Lost | No | Line: 1"-CM-28049-C6B1 seen to have full CBD and in poor condition, with gross corrosion evident on this line. Valve: V28085, seen to be in poor condition. Body bolting seen to be in poor condition with heavy rust and scale present. Handles are corroded and have seized.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-7150-M-RAD | BRT-2024-7435-RRADT | 01.00-CM-28049-C6B1 | 2024-08-18 00:00:00 | TP22S | TP22S |  |  | 4.55 | 4.55 | 4.55 | 4.55 | 3.29 | 3.29 | 3.29 |  | External | Code : C -- Corr: 33-67% Corrosion Allowance Lost |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-08-18 00:00:00 |  | TP22S | North | Straight | 4.55 | 4.55 mm | 3.29 mm | External | Code : C -- Corr: 33-67% Corrosion Allowance Lost | No | Line: 1"-CM-28049-C6B1 seen to have full CBD and in poor condition, with gross corrosion evident on this line. Valve: V28085, seen to be in poor condition. Body bolting seen to be in poor condition with heavy rust and scale present. Handles are corroded and have seized.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-7150-M-RAD | BRT-2024-7436-RRADT | 01.00-CM-28049-C6B1 | 2024-08-18 00:00:00 | TP22S East | TP22S East |  |  | 4.55 | 4.55 | 4.55 | 4.55 | 3.4 | 3.4 | 3.4 |  | External | Code : C -- Corr: 33-67% Corrosion Allowance Lost |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-08-18 00:00:00 |  | TP22S East | East | Straight | 4.55 | 4.55 mm | 3.40 mm | External | Code : C -- Corr: 33-67% Corrosion Allowance Lost | No | Line: 1"-CM-28049-C6B1 seen to have full CBD and in poor condition, with gross corrosion evident on this line. Valve: V28085, seen to be in poor condition. Body bolting seen to be in poor condition with heavy rust and scale present. Handles are corroded and have seized.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4673-M-RAD | BRT-2024-9141-RRADT | 02.00-CM-28119-L1C2 | 2024-11-07 00:00:00 | TP61T NORTH | TP61T NORTH |  |  | 5.54 | 7.62 | 7.62 | 7.62 | 7.65 | 7.65 | 7.65 |  | Not Applicable | Code : A -- No Wall Loss noted | RESULTS FOR 3" SECTION ONLY |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-11-07 00:00:00 |  | TP61T NORTH | NORTH | Tee | 5.54 | 7.62 mm | 7.65 mm | Not Applicable | Code : A -- No Wall Loss noted | No | NO ISSUES
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4365-M-GVI | BRT-2024-6734-RTRUN | CM-28135-C1B1 | 2024-07-05 00:00:00 | 528-PS-226 | Pipe |  | Horizontal | Code : A -- Good Condition | Code : A -- Not Applicable | Code : A -- Good Condition | Code : A -- Good Condition |  | Yes | 3 Oclock | Yes | Not Required | Trunnion support found to be in good condition. Secure and in place with no external corrosion. Weep hole found to be sealed. Structural support has a Ri1 coating with light discoloration. Bolting all found to be secure and in place. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-05 00:00:00 |  | 528-PS-226 |  |  |  |  |  |  |  |  | 28-PSV-0058 - Ri3 coating breakdown to PSV with light corrosion.  No tag present with ID and set pressure.  Name plate has information scratched off and some information is not visible.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4365-M-GVI | BRT-2024-6736-RRELIEF | CM-28135-C1B1 | 2024-07-05 00:00:00 | D-PSV/PZV - Pressure Safety Valve | 28-PSV-0058 | 71 | Code : B -- Nameplate present but can not be read | 0 | Code : B -- PC: Ri 3 - Superficial | Code : A -- Good Condition | B | Fail | 28-PSV-0058 - Ri3 coating breakdown to PSV with light corrosion.  No tag present with ID and set pressure.  Name plate has information scratched off and some information is not visible. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-05 00:00:00 |  |  |  |  |  |  |  |  |  |  | 28-PSV-0058 - Ri3 coating breakdown to PSV with light corrosion.  No tag present with ID and set pressure.  Name plate has information scratched off and some information is not visible.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4363-M-GVI | BRT-2024-6835-RRELIEF | CM-28134-C6B1 | 2024-07-10 00:00:00 | D-PSV/PZV - Pressure Safety Valve | Not legible | 71 | Code : B -- Nameplate present but can not be read | 0 | Code : B -- PC: Ri 3 - Superficial | Code : B -- Bolt: B2-Minor Damage volume loss <20% | B | Fail | Coating to PSV is code B, 2-3mm of corrosion present. No issues noted with Gaskets. Outer-rings in good condition. No issues with nuts/studs.   ID tag is not legible. Cannot confirm if set pressure is same as what is noted on corresponding P&ID.  ID tag requires re-instating. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-10 00:00:00 |  |  |  |  |  |  |  |  |  |  | Coating to PSV is code B, 2-3mm of corrosion present. No issues noted with Gaskets. Outer-rings in good condition. No issues with nuts/studs.   ID tag is not legible. Cannot confirm if set pressure is same as what is noted on corresponding P&ID.  ID tag requires re-instating.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4674-M-RAD | BRT-2024-6939-RRADT | 00.75-CM-28128-C1B1 | 2024-07-15 00:00:00 | TP08O WEST | TP08O WEST |  |  | 3.91 | 3.91 | 3.91 | 3.91 | 8.96 | 8.96 | 8.96 |  | External | Code : A -- Wall loss within [NAME] (12.5%) with no signs of internal corrosion | OVERSIZED FEATURE. WALL LOSS UNQUANTIFIABLE WITHOUT KNOWN NOMINAL |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-15 00:00:00 |  | TP08O WEST | WEST | Small Bore Branch / Weld O'Let | 3.91 | 3.91 mm | 8.96 mm | External | Code : A -- Wall loss within [NAME] (12.5%) with no signs of internal corrosion | No | OVERSIZED FEATURE. WALL LOSS UNQUANTIFIABLE WITHOUT KNOWN NOMINAL
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4360-M-GVI | BRT-2024-6947-RTRUN | CM-28129-C1B1 | 2024-07-15 00:00:00 | 09E | Pipe |  | Horizontal | Code : B -- PC: Ri 3 - Superficial | Code : B -- Scale Height: 1-3mm Loose scale easily removed | Code : B -- PC: Ri 2 - Superficial | Code : A -- Not Applicable |  | No | No Weep Hole | No | Not Required | Supporting steelwork in good condition also. No issues. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-15 00:00:00 |  | 09E |  |  |  |  |  |  |  |  | Supporting steelwork in good condition also. No issues.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4341-M-GVI | BRT-2024-7079-RRELIEF | CM-28116-C1B1 | 2024-07-25 00:00:00 | D-PSV/PZV - Pressure Safety Valve | Yes | 8 | Code : A -- Good Condition | 8 | Code : A -- Good Condition | Code : A -- Good Condition | A | Pass | The associated PSV (28-PSV-0023) is in good condition and the set pressure on the ID tag matches what is stated on the P&ID. The associated bolting is in as new condition typical of Code A. No issues to report. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-25 00:00:00 |  |  |  |  |  |  |  |  |  |  | The associated PSV (28-PSV-0023) is in good condition and the set pressure on the ID tag matches what is stated on the P&ID. The associated bolting is in as new condition typical of Code A. No issues to report.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4342-M-GVI | BRT-2024-7083-RRELIEF | CM-28117-C1B1 | 2024-07-25 00:00:00 | D-PSV/PZV - Pressure Safety Valve | Yes | 8 | Code : A -- Good Condition | 8 | Code : B -- PC: Ri 2 - Superficial | Code : B -- Bolt: B2-Minor Damage volume loss <20% | B | Pass | The associated PSV (28-PSV-0024) is in good condition with minor corrosion visible typical of Code B. The set pressure on the name plate matches what is stated on the P&ID, However there is no ID Tag present. The associated bolting is in good condition with 100% surface oxidisation typical of Code B. No issues to report. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-25 00:00:00 |  |  |  |  |  |  |  |  |  |  | The associated PSV (28-PSV-0024) is in good condition with minor corrosion visible typical of Code B. The set pressure on the name plate matches what is stated on the P&ID, However there is no ID Tag present. The associated bolting is in good condition with 100% surface oxidisation typical of Code B. No issues to report.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-4373-M-GVI | BRT-2024-7129-RRELIEF | CM-28119-L1C2 | 2024-07-27 00:00:00 | D-PSV/PZV - Pressure Safety Valve | Yes | 19 | Code : A -- Good Condition | 19 | Code : C -- PC: Ri 4 - Minor Damage | Code : B -- Bolt: B2-Minor Damage volume loss <20% | B | Pass | 100% surface corrosion on PSV body. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-27 00:00:00 |  |  |  |  |  |  |  |  |  |  | Needs adding to isometric.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-7431-M-UT | BRT-2024-7516-RUTT | 04.00-CM-28114-C1B1 | 2024-08-19 00:00:00 | 33E | Good external condition | Bend |  | Vert - South | Coated - Paint | 6.02 | 6.02 | 5.8 |  | Code : A -- Wall loss within [NAME] (12.5%) with no signs of internal corrosion | . | Yes | Weld feature 32W was specified in the RAD task BRT-2024-4676 however, OIE advised to select bend feature 33E, which is adjacent to feature 32W.  Lowest reading found was 5.8mm on the external of the bend. No evidence of internal corrosion was noted. | 2024-08-19 00:00:00 |  | 33E |  | Bend | 6.02 | 6.02 mm | 5.80 mm |  | Code : A -- Wall loss within [NAME] (12.5%) with no signs of internal corrosion |  | Weld feature 32W was specified in the RAD task BRT-2024-4676 however, OIE advised to select bend feature 33E, which is adjacent to feature 32W.  Lowest reading found was 5.8mm on the external of the bend. No evidence of internal corrosion was noted.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Y | BRT-2024-7432-M-UT | BRT-2024-7521-RUTT | 04.00-CM-28115-C1B1 | 2024-08-19 00:00:00 | 22E | Good external condition | Bend |  | Vert - West | Coated - Paint | 6.02 | 6.02 | 5.5 |  | Code : A -- Wall loss within [NAME] (12.5%) with no signs of internal corrosion | . | Yes | Weld feature 21W was specified in the RAD task BRT-2024-4677 however, OIE advised to select bend feature 22E, which is adjacent to feature 21W.  Lowest reading found was 5.5mm on the external of the bend. No evidence of internal corrosion was noted. | 2024-08-19 00:00:00 |  | 22E |  | Bend | 6.02 | 6.02 mm | 5.50 mm |  | Code : A -- Wall loss within [NAME] (12.5%) with no signs of internal corrosion |  | Weld feature 21W was specified in the RAD task BRT-2024-4677 however, OIE advised to select bend feature 22E, which is adjacent to feature 21W.  Lowest reading found was 5.5mm on the external of the bend. No evidence of internal corrosion was noted.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-15 00:00:00 |  |  |  |  |  |  |  |  |  |  | Supporting steelwork in good condition also. No issues.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-15 00:00:00 |  |  |  |  |  |  |  |  |  |  | Supporting steelwork in good condition also. No issues.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-15 00:00:00 |  |  |  |  |  |  |  |  |  |  | Supporting steelwork in good condition also. No issues.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-15 00:00:00 |  |  |  |  |  |  |  |  |  |  | Supporting steelwork in good condition also. No issues.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-15 00:00:00 |  |  |  |  |  |  |  |  |  |  | Valve V28022 exhibiting scale corrosion on valve handle typical of Code B.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-15 00:00:00 |  |  |  |  |  |  |  |  |  |  | Valve V28022 exhibiting scale corrosion on valve handle typical of Code B.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 2024-07-15 00:00:00 |  |  |  |  |  |  |  |  |  |  | Valve V28022 exhibiting scale corrosion on valve handle typical of Code B.