Spreadsheet: larry_campbell__21007__PGEsample071101
Sheet: PG&E Samples

CONFIDENTIAL
[NAME] and PG&E Samples and Analytical Results
Date | Sample ID |  | Volume Drained |  | Comments |  |  |  | PGE PCB | TW PCB | Location of sample point
 |  |  |  |  |  |  |  |  |  |  | Filter Scrubbers Downstream of
2001-06-12 00:00:00 | SLX-TW | 6-12-01-L | 0 |  | No liquid for sample |  |  |  |  |  | Solexol Plant
 |  |  |  |  |  |  |  |  |  |  | TW's Filter Scrubber at TW/PG&E
2001-06-12 00:00:00 | PGE-TW2 | 6-12-01-L | 0 |  | No liquid for sample |  |  |  |  |  | Metering Station
 |  |  |  |  |  |  |  |  |  |  | PG&E's Seperator at PG&E's
2001-06-12 00:00:00 | PGE-Top3 | 6-12-01-L | 0 |  | No liquid for sample |  |  |  |  |  | [NAME] gal tank
 |  |  |  |  |  |  |  |  |  |  | Directly off PG&Es seperator
2001-06-12 00:00:00 | PGE-Top4 | 6-12-01-L | 0 |  | No liquid for sample |  |  |  |  |  | At PG&Es Compressor station
 |  |  |  |  |  |  |  |  |  |  | PG&E's Line A TCS
2001-06-12 00:00:00 | PGE-A6 | 6-12-01-L | 0 |  | No liquid for sample |  |  |  |  |  | Downstream Scrubber
 |  |  |  |  |  |  |  |  |  |  | PG&E's Line B TCS
2001-06-12 00:00:00 | PGE-B6 | 6-12-01-L | 0 |  | No liquid for sample |  |  |  |  |  | Downstream Scrubber
2001-06-12 00:00:00 | PGE-84.10A | 6-12-01-L | 0 |  | No liquid for sample |  |  |  |  |  | PG&E's 36" Line A
2001-06-12 00:00:00 | PGE-63.26A | 6-12-01-L | 2 oz |  |  |  |  |  | 3 PPM | 4 PPM | PG&E's 36" Line A
2001-06-12 00:00:00 | PGE-63.26B | 6-12-01-L | 4 oz |  |  |  |  |  | 2 PPM | 3 PPM | PG&E's 36" Line B
2001-06-12 00:00:00 | PGE-26.15A | 6-12-01-L | 0 |  | No liquid for sample |  |  |  |  |  | PG&E's 36" Line A
2001-06-12 00:00:00 | PGE-26.15B | 6-12-01-L | 0 |  | No liquid for sample |  |  |  |  |  | PG&E's 36" Line B
2001-06-12 00:00:00 | PGE-15.33A | 6-12-01-L | 8 oz |  |  |  |  |  | 1 PPM | 2 PPM | PG&E's 36" Line A
2001-06-12 00:00:00 | PGE 10.84A | 6-12-01-L | 1 oz |  |  |  |  |  | 5 PPM | 4 PPM | PG&E's 36" Line A
2001-06-12 00:00:00 | PGE 10.47B | 6-12-01-L | 0 |  | No liquid for sample |  |  |  |  |  | PG&E's 36" Line B
2001-06-12 00:00:00 | PGE 8.58A | 6-12-01-L |  |  | No sample taken per PG&E |  |  |  |  |  | PG&E's 36" Line B
2001-06-12 00:00:00 | [NAME] | 6-12-01-L | 0 |  | No liquid for sample |  |  |  |  |  | PG&E's 36" Line B
2001-06-12 00:00:00 | PGE-TW4 | 6-12-01-L | 0 |  | No liquid for sample |  |  |  |  |  | TW 20" 1st Siphon
2001-06-12 00:00:00 | PGE-TW5 | 6-12-01-L | 0 |  | No liquid for sample |  |  |  |  |  | TW 20" 2nd siphon
2001-06-12 00:00:00 | PGE-TW6 | 6-12-01-L | 0 |  | No liquid for sample |  |  |  |  |  | TW 20" 3rd Siphon
 |  |  |  |  |  |  |  |  |  |  | Filter Scrubbers Downstream of
2001-07-11 00:00:00 | SLX-TW | 7-11-01-L | 0 |  | No liquid for sample |  |  |  |  |  | Solexol Plant
 |  |  |  |  |  |  |  |  |  |  | TW's Filter Scrubber at TW/PG&E
2001-07-11 00:00:00 | PGE-TW2 | 7-11-01-L | 0 |  | No liquid for sample |  |  |  |  |  | Metering Station
 |  |  |  |  |  |  |  |  |  |  | PG&E's Seperator at PG&E's
2001-07-11 00:00:00 | PGE-Top3 | 7-11-01-L | 0 |  | No liquid for sample |  |  |  |  |  | [NAME] gal tank
 |  |  |  |  |  |  |  |  |  |  | Directly off PG&Es seperator
2001-07-11 00:00:00 | PGE-Top4 | 7-11-01-L | 0 |  | No liquid for sample |  |  |  |  |  | At PG&Es Compressor station
 |  |  |  |  |  |  |  |  |  |  | PG&E's Line A TCS
2001-07-11 00:00:00 | PGE-A6 | 7-11-01-L | 0 |  | No liquid for sample |  |  |  |  |  | Downstream Scrubber
 |  |  |  |  |  |  |  |  |  |  | PG&E's Line B TCS
2001-07-11 00:00:00 | PGE-B6 | 7-11-01-L | 0 |  | No liquid for sample |  |  |  |  |  | Downstream Scrubber
2001-07-11 00:00:00 | PGE-84.10A | 7-11-01-L | 4 oz |  |  |  |  |  | 4 PPM | ND | PG&Es 36" Line A
2001-07-11 00:00:00 | PGE-63.26A | 7-11-01-L | 4 oz |  |  |  |  |  | 2 PPM | ND | PG&Es 36" Line A
2001-07-11 00:00:00 | PGE-63.26B | 7-11-01-L | 4 oz |  |  |  |  |  | 3 PPM | ND | PG&E's 36" Line B
2001-07-11 00:00:00 | PGE-26.15A | 7-11-01-L | 0 |  | No liquid for sample |  |  |  |  |  | PG&Es 36" Line A
2001-07-11 00:00:00 | PGE-26.15B | 7-11-01-L | 0 |  | No liquid for sample |  |  |  |  |  | PG&E's 36" Line B
2001-07-11 00:00:00 | PGE-15.33A | 7-11-01-L | 4 oz |  |  |  |  |  | 2 PPM | ND | PG&Es 36" Line A
2001-07-11 00:00:00 | PGE 10.84A | 7-11-01-L | 1 oz |  |  |  |  |  | 4 PPM | ND | PG&Es 36" Line A
2001-07-11 00:00:00 | PGE 10.47B | 7-11-01-L | 0 |  | No liquid for sample |  |  |  |  |  | PG&E's 36" Line B
2001-07-11 00:00:00 | PGE 8.58A | 7-11-01-L | 0 |  | No sample taken per PG&E |  |  |  |  |  | PG&E's 36" Line B
2001-07-11 00:00:00 | [NAME] | 7-11-01-L | 1 oz |  |  |  |  |  | 1 PPM | ND | PG&E's 36" Line B
2001-07-11 00:00:00 | PGE-TW4 | 7-11-01-L | 0 |  | No liquid for sample |  |  |  |  |  | TW 20" 1st Siphon
2001-07-11 00:00:00 | PGE-TW5 | 7-11-01-L | 0 |  | No liquid for sample |  |  |  |  |  | TW 20" 2nd siphon
2001-07-11 00:00:00 | PGE-TW6 | 7-11-01-L | 0 |  | No liquid for sample |  |  |  |  |  | TW 20" 3rd Siphon