Spreadsheet: 73081d1273744707-the-source-currently-evaluates-to-an-error-bs7671-v7
Sheet: Installation Methods

Table 4D1 |  |  |  |  |  |  |  |  | Table 4D1
Item | Supply |  | Step 1 | Step 2 | Ref Method | CONCATENATED Version | Collumn |  | Item | Supply |  | Step 1 | Step 2 | Ref Method | CONCATENATED Version | Collumn
1 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 30 - On horizontal/vertical unperforated tray*Configuration: *Flat Touching and Trefoil | C | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 30 - On horizontal/vertical unperforated tray*Configuration: *Flat Touching and Trefoil | 6 |  | 1 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 30 - On horizontal/vertical unperforated tray*Configuration: *Flat Touching and Trefoil | C | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 30 - On horizontal/vertical unperforated tray*Configuration: *Flat Touching and Trefoil | 6
2 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 31 - On horizontal/vertical perforated tray*Configuration: *Horizontal Flat Spaced | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Horizontal Flat Spaced | 10 |  | 2 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 31 - On horizontal/vertical perforated tray*Configuration: *Horizontal Flat Spaced | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Horizontal Flat Spaced | 8
2.1 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 31 - On horizontal/vertical perforated tray*Configuration: *Vertical Flat Spaced | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Vertical Flat Spaced | 11 |  | 2.1 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 31 - On horizontal/vertical perforated tray*Configuration: *Vertical Flat Spaced | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Vertical Flat Spaced | 8
2.2 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 31 - On horizontal/vertical perforated tray*Configuration: *Trefoil | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Trefoil | 9 |  | 2.2 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 31 - On horizontal/vertical perforated tray*Configuration: *Trefoil | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Trefoil | 6
2.3 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 31 - On horizontal/vertical perforated tray*Configuration: *Flat Touching | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Flat Touching | 8 |  | 2.3 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 31 - On horizontal/vertical perforated tray*Configuration: *Flat Touching | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Flat Touching | 7
3 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 32 - On horizontal/vertical wire mesh tray*Configuration: *Horizontal Flat Spaced | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Horizontal Flat Spaced | 10 |  | 3 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 32 - On horizontal/vertical wire mesh tray*Configuration: *Horizontal Flat Spaced | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Horizontal Flat Spaced | 8
3.1 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 32 - On horizontal/vertical wire mesh tray*Configuration: *Vertical Flat Spaced | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Vertical Flat Spaced | 11 |  | 3.1 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 32 - On horizontal/vertical wire mesh tray*Configuration: *Vertical Flat Spaced | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Vertical Flat Spaced | 8
3.2 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 32 - On horizontal/vertical wire mesh tray*Configuration: *Trefoil | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Trefoil | 9 |  | 3.2 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 32 - On horizontal/vertical wire mesh tray*Configuration: *Trefoil | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Trefoil | 6
3.3 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 32 - On horizontal/vertical wire mesh tray*Configuration: *Flat Touching | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Flat Touching | 8 |  | 3.3 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 32 - On horizontal/vertical wire mesh tray*Configuration: *Flat Touching | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Flat Touching | 7
4 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 33 - Spaced from a wall*Configuration: *Horizontal Flat Spaced | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Horizontal Flat Spaced | 10 |  | 4 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 33 - Spaced from a wall*Configuration: *Horizontal Flat Spaced | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Horizontal Flat Spaced | 8
4.1 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 33 - Spaced from a wall*Configuration: *Vertical Flat Spaced | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Vertical Flat Spaced | 11 |  | 4.1 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 33 - Spaced from a wall*Configuration: *Vertical Flat Spaced | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Vertical Flat Spaced | 8
4.2 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 33 - Spaced from a wall*Configuration: *Trefoil | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Trefoil | 9 |  | 4.2 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 33 - Spaced from a wall*Configuration: *Trefoil | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Trefoil | 6
4.3 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 33 - Spaced from a wall*Configuration: *Flat Touching | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Flat Touching | 8 |  | 4.3 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 33 - Spaced from a wall*Configuration: *Flat Touching | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Flat Touching | 7
5 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 34 - On a ladder*Configuration: *Horizontal Flat Spaced | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Horizontal Flat Spaced | 10 |  | 5 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 34 - On a ladder*Configuration: *Horizontal Flat Spaced | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Horizontal Flat Spaced | 8
5.1 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 34 - On a ladder*Configuration: *Vertical Flat Spaced | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Vertical Flat Spaced | 11 |  | 5.1 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 34 - On a ladder*Configuration: *Vertical Flat Spaced | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Vertical Flat Spaced | 8
5.2 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 34 - On a ladder*Configuration: *Trefoil | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Trefoil | 9 |  | 5.2 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 34 - On a ladder*Configuration: *Trefoil | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Trefoil | 6
5.3 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 34 - On a ladder*Configuration: *Flat Touching | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Flat Touching | 8 |  | 5.3 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 34 - On a ladder*Configuration: *Flat Touching | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Flat Touching | 7
6 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 1 - In conduit in a thermally insulated wall | A | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 1 - In conduit in a thermally insulated wall | 2 |  | 6 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 1 - In conduit in a thermally insulated wall | A | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 1 - In conduit in a thermally insulated wall | 5
7 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 4 - In conduit on a wooden/masonry wall | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 4 - In conduit on a wooden/masonry wall | 4 |  | 7 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 4 - In conduit on a wooden/masonry wall | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 4 - In conduit on a wooden/masonry wall | 5
8 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 41 - In conduit in a building void | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 41 - In conduit in a building void | 4 |  | 8 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 41 - In conduit in a building void | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 41 - In conduit in a building void | 5
9 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 42 - In conduit in a building void | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 42 - In conduit in a building void | 4 |  | 9 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 42 - In conduit in a building void | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 42 - In conduit in a building void | 5
10 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 54 - In conduit in an unventilated cable channel | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 54 - In conduit in an unventilated cable channel | 4 |  | 10 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 54 - In conduit in an unventilated cable channel | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 54 - In conduit in an unventilated cable channel | 5
11 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 55 - In conduit in open/ventilated floor channel | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 55 - In conduit in open/ventilated floor channel | 4 |  | 11 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 55 - In conduit in open/ventilated floor channel | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 55 - In conduit in open/ventilated floor channel | 5
12 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 59 - In conduit in masonry | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 59 - In conduit in masonry | 4 |  | 12 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 59 - In conduit in masonry | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 59 - In conduit in masonry | 5
13 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 6 - In horizontal trunking on a wooden/masonry wall | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 6 - In horizontal trunking on a wooden/masonry wall | 4 |  | 13 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 6 - In horizontal trunking on a wooden/masonry wall | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 6 - In horizontal trunking on a wooden/masonry wall | 5
14 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 7 - In vertical trunking on a wooden/masonry wall | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 7 - In vertical trunking on a wooden/masonry wall | 4 |  | 14 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 7 - In vertical trunking on a wooden/masonry wall | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 7 - In vertical trunking on a wooden/masonry wall | 5
15 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 10 - In suspended trunking | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 10 - In suspended trunking | 4 |  | 15 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 10 - In suspended trunking | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 10 - In suspended trunking | 5
16 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 13 - In skirting trunking | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 13 - In skirting trunking | 4 |  | 16 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 13 - In skirting trunking | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 13 - In skirting trunking | 5
17 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 43 - In ducting in a building void | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 43 - In ducting in a building void | 4 |  | 17 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 43 - In ducting in a building void | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 43 - In ducting in a building void | 5
18 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 45 - In ducting in masonry | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 45 - In ducting in masonry | 4 |  | 18 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 45 - In ducting in masonry | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 45 - In ducting in masonry | 5
19 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 50 - In flush trunking in floor | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 50 - In flush trunking in floor | 4 |  | 19 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 50 - In flush trunking in floor | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 50 - In flush trunking in floor | 5
20 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 52 - In flush trunking | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 52 - In flush trunking | 4 |  | 20 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 52 - In flush trunking | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 52 - In flush trunking | 5
21 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Direct in wall. Ceiling void | 40 - In a building void | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 40 - In a building void | 4 |  | 21 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Direct in wall. Ceiling void | 40 - In a building void | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 40 - In a building void | 5
22 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Direct in wall. Ceiling void | 47 - In a ceiling void or suspended floor | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 47 - In a ceiling void or suspended floor | 4 |  | 22 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Direct in wall. Ceiling void | 47 - In a ceiling void or suspended floor | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 47 - In a ceiling void or suspended floor | 5
23 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Direct in wall. Ceiling void | 57 - Direct in masonry (without capping)*Configuration: *Flat Touching and Trefoil | C | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 57 - Direct in masonry (without capping)*Configuration: *Flat Touching and Trefoil | 6 |  | 23 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Direct in wall. Ceiling void | 57 - Direct in masonry (without capping)*Configuration: *Flat Touching and Trefoil | C | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 57 - Direct in masonry (without capping)*Configuration: *Flat Touching and Trefoil | 6
24 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Direct in wall. Ceiling void | 58 - Direct in masonry (with capping)*Configuration: *Flat Touching and Trefoil | C | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 58 - Direct in masonry (with capping)*Configuration: *Flat Touching and Trefoil | 6 |  | 24 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Direct in wall. Ceiling void | 58 - Direct in masonry (with capping)*Configuration: *Flat Touching and Trefoil | C | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 58 - Direct in masonry (with capping)*Configuration: *Flat Touching and Trefoil | 6
25 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 20 - Clipped direct on a wooden/masonry wall*Configuration: *Flat Touching and Trefoil | C | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 20 - Clipped direct on a wooden/masonry wall*Configuration: *Flat Touching and Trefoil | 6 |  | 25 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 20 - Clipped direct on a wooden/masonry wall*Configuration: *Flat Touching and Trefoil | C | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 20 - Clipped direct on a wooden/masonry wall*Configuration: *Flat Touching and Trefoil | 6
26 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 21 - Under a wooden/masonry ceiling | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 21 - Under a wooden/masonry ceiling | 4 |  | 26 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 21 - Under a wooden/masonry ceiling | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 21 - Under a wooden/masonry ceiling | 5
27 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 22 - Spaced from a ceiling*Configuration: *Horizontal Flat Spaced | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Horizontal Flat Spaced | 10 |  | 27 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 22 - Spaced from a ceiling*Configuration: *Horizontal Flat Spaced | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Horizontal Flat Spaced | 8
27.1 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 22 - Spaced from a ceiling*Configuration: *Vertical Flat Spaced | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Vertical Flat Spaced | 11 |  | 27.1 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 22 - Spaced from a ceiling*Configuration: *Vertical Flat Spaced | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Vertical Flat Spaced | 8
27.2 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 22 - Spaced from a ceiling*Configuration: *Trefoil | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Trefoil | 9 |  | 27.2 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 22 - Spaced from a ceiling*Configuration: *Trefoil | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Trefoil | 6
27.3 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 22 - Spaced from a ceiling*Configuration: *Flat Touching | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Flat Touching | 8 |  | 27.3 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 22 - Spaced from a ceiling*Configuration: *Flat Touching | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Flat Touching | 7
28 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 33 - Spaced from a wall*Configuration: *Horizontal Flat Spaced | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Horizontal Flat Spaced | 10 |  | 28 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 33 - Spaced from a wall*Configuration: *Horizontal Flat Spaced | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Horizontal Flat Spaced | 8
28.1 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 33 - Spaced from a wall*Configuration: *Vertical Flat Spaced | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Vertical Flat Spaced | 11 |  | 28.1 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 33 - Spaced from a wall*Configuration: *Vertical Flat Spaced | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Vertical Flat Spaced | 8
28.2 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 33 - Spaced from a wall*Configuration: *Trefoil | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Trefoil | 9 |  | 28.2 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 33 - Spaced from a wall*Configuration: *Trefoil | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Trefoil | 6
28.3 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 33 - Spaced from a wall*Configuration: *Flat Touching | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Flat Touching | 8 |  | 28.3 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 33 - Spaced from a wall*Configuration: *Flat Touching | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Flat Touching | 7
29 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In moulding, architrave or window frame | 12 - In mouldings | A | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In moulding, architrave or window frame 12 - In mouldings | 2 |  | 29 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In moulding, architrave or window frame | 12 - In mouldings | A | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In moulding, architrave or window frame 12 - In mouldings | 5
30 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In moulding, architrave or window frame | 15 - In architrave | A | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In moulding, architrave or window frame 15 - In architrave | 2 |  | 30 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In moulding, architrave or window frame | 15 - In architrave | A | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In moulding, architrave or window frame 15 - In architrave | 5
31 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In moulding, architrave or window frame | 16 - In window frame | A | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In moulding, architrave or window frame 16 - In window frame | 2 |  | 31 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In moulding, architrave or window frame | 16 - In window frame | A | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In moulding, architrave or window frame 16 - In window frame | 5
32 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Miscellaneous | 35 - Suspended from/incorporating a support wire | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Miscellaneous 35 - Suspended from/incorporating a support wire | 8 |  | 32 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Miscellaneous | 35 - Suspended from/incorporating a support wire | F | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Miscellaneous 35 - Suspended from/incorporating a support wire
33 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Miscellaneous | 56 - In open/ventilated horizontal/vertical channel | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Miscellaneous 56 - In open/ventilated horizontal/vertical channel | 4 |  | 33 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Miscellaneous | 56 - In open/ventilated horizontal/vertical channel | B | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Miscellaneous 56 - In open/ventilated horizontal/vertical channel | 5
34 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Miscellaneous | Run through thermal insulation*Distance ([NAME]): *500 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 [NAME] through thermal insulation*Distance ([NAME]): *500 |  |  | 34 | 3Ph | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Miscellaneous | Run through thermal insulation*Distance ([NAME]): *500 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 [NAME] through thermal insulation*Distance ([NAME]): *500
50 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 30 - On horizontal/vertical unperforated tray*Configuration: *Flat Touching and Trefoil | C | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 30 - On horizontal/vertical unperforated tray*Configuration: *Flat Touching and Trefoil | 5 |  | 50 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 30 - On horizontal/vertical unperforated tray*Configuration: *Flat Touching and Trefoil | C | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 30 - On horizontal/vertical unperforated tray*Configuration: *Flat Touching and Trefoil | 3
51 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 31 - On horizontal/vertical perforated tray*Configuration: *Horizontal Flat Spaced | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Horizontal Flat Spaced | 10 |  | 51 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 31 - On horizontal/vertical perforated tray*Configuration: *Horizontal Flat Spaced | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Horizontal Flat Spaced | 4
52 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 31 - On horizontal/vertical perforated tray*Configuration: *Vertical Flat Spaced | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Vertical Flat Spaced | 11 |  | 52 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 31 - On horizontal/vertical perforated tray*Configuration: *Vertical Flat Spaced | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Vertical Flat Spaced | 4
53 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 31 - On horizontal/vertical perforated tray*Configuration: *Flat Touching | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Flat Touching | 7 |  | 53 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 31 - On horizontal/vertical perforated tray*Configuration: *Flat Touching | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Flat Touching | 3
54 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 32 - On horizontal/vertical wire mesh tray*Configuration: *Horizontal Flat Spaced | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Horizontal Flat Spaced | 10 |  | 54 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 32 - On horizontal/vertical wire mesh tray*Configuration: *Horizontal Flat Spaced | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Horizontal Flat Spaced | 4
55 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 32 - On horizontal/vertical wire mesh tray*Configuration: *Vertical Flat Spaced | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Vertical Flat Spaced | 11 |  | 55 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 32 - On horizontal/vertical wire mesh tray*Configuration: *Vertical Flat Spaced | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Vertical Flat Spaced | 4
56 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 32 - On horizontal/vertical wire mesh tray*Configuration: *Flat Touching | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Flat Touching | 7 |  | 56 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 32 - On horizontal/vertical wire mesh tray*Configuration: *Flat Touching | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Flat Touching | 3
57 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 33 - Spaced from a wall*Configuration: *Horizontal Flat Spaced | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Horizontal Flat Spaced | 10 |  | 57 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 33 - Spaced from a wall*Configuration: *Horizontal Flat Spaced | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Horizontal Flat Spaced | 4
58 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 33 - Spaced from a wall*Configuration: *Vertical Flat Spaced | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Vertical Flat Spaced | 11 |  | 58 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 33 - Spaced from a wall*Configuration: *Vertical Flat Spaced | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Vertical Flat Spaced | 4
59 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 33 - Spaced from a wall*Configuration: *Flat Touching | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Flat Touching | 7 |  | 59 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 33 - Spaced from a wall*Configuration: *Flat Touching | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Flat Touching | 3
60 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 34 - On a ladder*Configuration: *Horizontal Flat Spaced | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Horizontal Flat Spaced | 10 |  | 60 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 34 - On a ladder*Configuration: *Horizontal Flat Spaced | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Horizontal Flat Spaced | 4
61 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 34 - On a ladder*Configuration: *Vertical Flat Spaced | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Vertical Flat Spaced | 11 |  | 61 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 34 - On a ladder*Configuration: *Vertical Flat Spaced | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Vertical Flat Spaced | 4
62 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 34 - On a ladder*Configuration: *Flat Touching | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Flat Touching | 7 |  | 62 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray | 34 - On a ladder*Configuration: *Flat Touching | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Flat Touching | 3
63 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 1 - In conduit in a thermally insulated wall | A | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 1 - In conduit in a thermally insulated wall | 1 |  | 63 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 1 - In conduit in a thermally insulated wall | A | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 1 - In conduit in a thermally insulated wall | 2
64 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 4 - In conduit on a wooden/masonry wall | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 4 - In conduit on a wooden/masonry wall | 3 |  | 64 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 4 - In conduit on a wooden/masonry wall | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 4 - In conduit on a wooden/masonry wall | 2
65 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 41 - In conduit in a building void | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 41 - In conduit in a building void | 3 |  | 65 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 41 - In conduit in a building void | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 41 - In conduit in a building void | 2
66 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 42 - In conduit in a building void | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 42 - In conduit in a building void | 3 |  | 66 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 42 - In conduit in a building void | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 42 - In conduit in a building void | 2
67 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 54 - In conduit in an unventilated cable channel | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 54 - In conduit in an unventilated cable channel | 3 |  | 67 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 54 - In conduit in an unventilated cable channel | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 54 - In conduit in an unventilated cable channel | 2
68 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 55 - In conduit in open/ventilated floor channel | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 55 - In conduit in open/ventilated floor channel | 3 |  | 68 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 55 - In conduit in open/ventilated floor channel | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 55 - In conduit in open/ventilated floor channel | 2
69 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 59 - In conduit in masonry | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 59 - In conduit in masonry | 3 |  | 69 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In conduit | 59 - In conduit in masonry | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 59 - In conduit in masonry | 2
70 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 6 - In horizontal trunking on a wooden/masonry wall | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 6 - In horizontal trunking on a wooden/masonry wall | 3 |  | 70 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 6 - In horizontal trunking on a wooden/masonry wall | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 6 - In horizontal trunking on a wooden/masonry wall | 2
71 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 7 - In vertical trunking on a wooden/masonry wall | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 7 - In vertical trunking on a wooden/masonry wall | 3 |  | 71 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 7 - In vertical trunking on a wooden/masonry wall | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 7 - In vertical trunking on a wooden/masonry wall | 2
72 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 10 - In suspended trunking | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 10 - In suspended trunking | 3 |  | 72 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 10 - In suspended trunking | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 10 - In suspended trunking | 2
73 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 13 - In skirting trunking | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 13 - In skirting trunking | 3 |  | 73 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 13 - In skirting trunking | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 13 - In skirting trunking | 2
74 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 43 - In ducting in a building void | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 43 - In ducting in a building void | 3 |  | 74 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 43 - In ducting in a building void | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 43 - In ducting in a building void | 2
75 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 45 - In ducting in masonry | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 45 - In ducting in masonry | 3 |  | 75 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 45 - In ducting in masonry | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 45 - In ducting in masonry | 2
76 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 50 - In flush trunking in floor | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 50 - In flush trunking in floor | 3 |  | 76 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 50 - In flush trunking in floor | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 50 - In flush trunking in floor | 2
77 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 52 - In flush trunking | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 52 - In flush trunking | 3 |  | 77 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In trunking/ducting (reference B) | 52 - In flush trunking | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 52 - In flush trunking | 2
78 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Direct in wall. Ceiling void | 40 - In a building void | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 40 - In a building void | 3 |  | 78 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Direct in wall. Ceiling void | 40 - In a building void | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 40 - In a building void | 2
79 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Direct in wall. Ceiling void | 47 - In a ceiling void or suspended floor | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 47 - In a ceiling void or suspended floor | 3 |  | 79 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Direct in wall. Ceiling void | 47 - In a ceiling void or suspended floor | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 47 - In a ceiling void or suspended floor | 2
80 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Direct in wall. Ceiling void | 57 - Direct in masonry (without capping)*Configuration: *Flat Touching and Trefoil | C | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 57 - Direct in masonry (without capping)*Configuration: *Flat Touching and Trefoil | 5 |  | 80 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Direct in wall. Ceiling void | 57 - Direct in masonry (without capping)*Configuration: *Flat Touching and Trefoil | C | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 57 - Direct in masonry (without capping)*Configuration: *Flat Touching and Trefoil | 3
81 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Direct in wall. Ceiling void | 58 - Direct in masonry (with capping)*Configuration: *Flat Touching and Trefoil | C | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 58 - Direct in masonry (with capping)*Configuration: *Flat Touching and Trefoil | 5 |  | 81 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Direct in wall. Ceiling void | 58 - Direct in masonry (with capping)*Configuration: *Flat Touching and Trefoil | C | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 58 - Direct in masonry (with capping)*Configuration: *Flat Touching and Trefoil | 3
82 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 20 - Clipped direct on a wooden/masonry wall*Configuration: *Flat Touching and Trefoil | C | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 20 - Clipped direct on a wooden/masonry wall*Configuration: *Flat Touching and Trefoil | 5 |  | 82 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 20 - Clipped direct on a wooden/masonry wall*Configuration: *Flat Touching and Trefoil | C | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 20 - Clipped direct on a wooden/masonry wall*Configuration: *Flat Touching and Trefoil | 3
83 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 21 - Under a wooden/masonry ceiling | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 21 - Under a wooden/masonry ceiling | 3 |  | 83 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 21 - Under a wooden/masonry ceiling | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 21 - Under a wooden/masonry ceiling | 2
84 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 22 - Spaced from a ceiling*Configuration: *Horizontal Flat Spaced | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Horizontal Flat Spaced | 10 |  | 84 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 22 - Spaced from a ceiling*Configuration: *Horizontal Flat Spaced | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Horizontal Flat Spaced | 4
85 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 22 - Spaced from a ceiling*Configuration: *Vertical Flat Spaced | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Vertical Flat Spaced | 11 |  | 85 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 22 - Spaced from a ceiling*Configuration: *Vertical Flat Spaced | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Vertical Flat Spaced | 4
86 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 22 - Spaced from a ceiling*Configuration: *Flat Touching | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Flat Touching | 7 |  | 86 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 22 - Spaced from a ceiling*Configuration: *Flat Touching | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Flat Touching | 3
87 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 33 - Spaced from a wall*Configuration: *Horizontal Flat Spaced | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Horizontal Flat Spaced | 10 |  | 87 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 33 - Spaced from a wall*Configuration: *Horizontal Flat Spaced | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Horizontal Flat Spaced | 4
88 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 33 - Spaced from a wall*Configuration: *Vertical Flat Spaced | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Vertical Flat Spaced | 11 |  | 88 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 33 - Spaced from a wall*Configuration: *Vertical Flat Spaced | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Vertical Flat Spaced | 4
89 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 33 - Spaced from a wall*Configuration: *Flat Touching | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Flat Touching | 7 |  | 89 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | On, or spaced from, wall of ceiling | 33 - Spaced from a wall*Configuration: *Flat Touching | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Flat Touching | 3
90 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In moulding, architrave or window frame | 12 - In mouldings | A | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In moulding, architrave or window frame 12 - In mouldings | 1 |  | 90 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In moulding, architrave or window frame | 12 - In mouldings | A | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In moulding, architrave or window frame 12 - In mouldings | 2
91 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In moulding, architrave or window frame | 15 - In architrave | A | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In moulding, architrave or window frame 15 - In architrave | 1 |  | 91 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In moulding, architrave or window frame | 15 - In architrave | A | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In moulding, architrave or window frame 15 - In architrave | 2
92 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In moulding, architrave or window frame | 16 - In window frame | A | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In moulding, architrave or window frame 16 - In window frame | 1 |  | 92 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | In moulding, architrave or window frame | 16 - In window frame | A | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In moulding, architrave or window frame 16 - In window frame | 2
93 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Miscellaneous | 35 - Suspended from/incorporating a support wire | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Miscellaneous 35 - Suspended from/incorporating a support wire |  |  | 93 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Miscellaneous | 35 - Suspended from/incorporating a support wire | F | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Miscellaneous 35 - Suspended from/incorporating a support wire
94 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Miscellaneous | 56 - In open/ventilated horizontal/vertical channel | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Miscellaneous 56 - In open/ventilated horizontal/vertical channel | 3 |  | 94 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Miscellaneous | 56 - In open/ventilated horizontal/vertical channel | B | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Miscellaneous 56 - In open/ventilated horizontal/vertical channel | 2
95 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Miscellaneous | Run through thermal insulation*Distance ([NAME]): *500 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 [NAME] through thermal insulation*Distance ([NAME]): *500 |  |  | 95 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Miscellaneous | Run through thermal insulation*Distance ([NAME]): *500 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 [NAME] through thermal insulation*Distance ([NAME]): *500