Spreadsheet: kimberly_watson__20549__011025Al
Sheet: LegalSizeRegionLoc

ETS Planned And Unplanned Outages - May 1, 2001 Through May 31, 2002
Albuquerque Region Only - Sorted By Region/Location
The information provided is tentative and may be changed without further notice.  Northern Natural Gas, [NAME] and Florida Gas Transmission are not responsible for any reliance on this information.
Data Extracted October 25, 2001 |  |  |  |  |  |  |  |  |  |  |  | Est. Flow | Est. Vol. |  |  | Act. | Act. | Act. | Act.
No. | ID# | Region | Location | Units | Title | EstStart | EstComp | Duration | Line | Proj. Mgr | W.O. # | Affected | Affected | DescOfWork | DescOfWork2 | Start | Compl. | [NAME]. | Throughput | P/U | Pub | Ver
 |  |  |  |  |  |  |  |  |  |  |  | (Mmcfd) |  |  |  |  |  | mmcf/d | Affect
1 | 17756 | ALB | ARTESIA | AGAVE I/C | HOT TAP | 2001-11-27 08:00:00 | 2001-11-27 17:00:00 | 0.4 |  | OPS |  | 0 | 0 | Doing a hot tap on the 24" loop line. [NAME] pressure at needed during the work is 712#. |  |  |  | 0 |  | P | N | N
2 | 17144 | ALB | ATOKA 1 | 719 | HEAD EXCHANGE | 2002-03-05 08:00:00 | 2002-03-07 16:00:00 | 2.3 |  | OPS |  | 0 | 0 | Complete UX head exchange.  [NAME] will remove all power heads. Inspect combustion chambers  clean and reinstall new heads. |  |  |  | 0 |  | P | N | N
3 | 17142 | ALB | ATOKA 1 | 719 | OVERHAUL | 2002-03-12 08:00:00 | 2002-03-16 16:00:00 | 4.3 |  | OPS |  | 0 | 0 | Contractor will perform a complete compressor overhaul  replace rings  packing  R&R all valves  inspect cylinders for wear and check rod and main bearings. |  |  |  | 0 |  | P | N | N
4 | 17145 | ALB | ATOKA 1 | 737 | OVERHAUL | 2002-03-18 08:00:00 | 2002-03-22 16:00:00 | 4.3 |  | OPS |  | 0 | 0 | Contractor will perform a complete compressor overhaul.  Replace rings  packing  R&R all compressor valves  inspect cylinders for wear and check rod and main bearings. |  |  |  | 0 |  | P | N | N
5 | 17146 | ALB | ATOKA 1 | 761 | OVERHAUL | 2002-03-25 08:00:00 | 2002-03-29 16:00:00 | 4.3 |  | OPS |  | 0 | 0 | Contractor will perform a complete compressor overhaul.  Replace rings  packing  R&R all compressor valves  inspect cylinders for wear and check rod and main bearings. |  |  |  | 0 |  | P | N | N
6 | 17395 | ALB | CRAWFORD | 756 | CLEAN & INHIBIT THE CRAWFORD LOOP 16 | 2001-10-29 07:00:00 | 2001-11-01 16:00:00 | 3.4 |  | OPS |  | 0 | 0 | Flow will need to be cut from 54 mmcf/day to 40 mmcf/day. [NAME] Highlands [NAME] will be shut in so that no chemical will get into the system. |  |  |  | 0 |  | P | N | N
7 | 17148 | ALB | CRAWFORD | 751 | OVERHAUL | 2002-03-11 08:00:00 | 2002-03-13 16:00:00 | 2.3 |  | OPS |  | 0 | 0 | Complete UX turbine exchange.  [NAME] will remove old turbine and install and align new reconditioned turbine. |  |  |  | 0 |  | P | N | N
8 | 17092 | ALB | STATION 1 | MAINLINE | RED ROCK TIE-IN | 2002-03-04 08:00:00 | 2002-03-08 16:00:00 | 4.3 |  | OPS |  | 100 | 433.3 | New block and side valve assemblies for new compressor and scrubbers will be installed on the sucton side main and loop lines at each station. The tie-in will entail isolating a line segment within the plant yard. |  |  |  | 0 |  | P | N | N
9 | 17093 | ALB | STATION 1 | LOOP LINE | RED ROCK TIE-IN | 2002-03-11 08:00:00 | 2002-03-13 16:00:00 | 2.3 |  | OPS |  | 100 | 233.3 | New block and side valve assemblies for new compressor and scrubbers will be installed on the sucton side main and loop lines at each station. The tie-in will entail isolating a line segment within the plant yard. |  |  |  | 0 |  | P | N | N
10 | 17090 | ALB | STATION 2 | MAINLINE | RED ROCK TIE-IN | 2001-11-12 08:00:00 | 2001-11-15 16:00:00 | 3.3 |  | OPS |  | 130 | 433.3 | New block and side valve assemblies for new compressor and scrubbers will be installed on the suction side main and loop lines at each station. The tie-in will entail isolating a line segment within the plant yard. |  |  |  | 0 |  | P | N | N
11 | 17091 | ALB | STATION 2 | LOOP LINE | RED ROCK TIE-IN | 2001-11-15 08:00:00 | 2001-11-19 16:00:00 | 4.3 |  | OPS |  | 130 | 563.3 | New block and side valve assemblies for new compressor and scrubbers will be installed on the sucton side main and loop lines at each station. The tie-in will entail isolating a line segment within the plant yard. |  |  |  | 0 |  | P | N | N
12 | 17095 | ALB | STATION 3 | MAINLINE | RED ROCK TIE-IN | 2002-03-18 08:00:00 | 2002-03-22 16:00:00 | 4.3 |  | OPS |  | 80 | 346.7 | New block and side valve assemblies for new compressor and scrubbers will be installed on the sucton side main and loop lines at each station. The tie-in will entail isolating a line segment within the plant yard. |  |  |  | 0 |  | P | N | N
13 | 17096 | ALB | STATION 3 | LOOP LINE | RED ROCK TIE-IN | 2002-03-25 08:00:00 | 2002-03-27 16:00:00 | 2.3 |  | OPS |  | 80 | 186.7 | New block and side valve assemblies for new compressor and scrubbers will be installed on the sucton side main and loop lines at each station. The tie-in will entail isolating a line segment within the plant yard. |  |  |  | 0 |  | P | N | N
14 | 17128 | ALB | STATION 4 | 401 | OVERHAUL | 2002-04-01 08:00:00 | 2002-05-10 16:00:00 | 39.3 |  | OPS |  | 200 | 7866.7 | Contractor will disassemble unit all the way to the lower block.  Compressor will be overhauled with new rods  packing  ring and all new compressor valves  unit realigned and rechocked. |  |  |  | 0 |  | P | N | N
15 | 17129 | ALB | STATION 4 | 402 | OVERHAUL | 2002-05-15 08:00:00 | 2002-05-25 16:00:00 | 10.3 |  | OPS |  | 200 | 2066.7 | Contractor will provide coplete compressor overhaul with new rods  packing  ring and all new compressor valves. Turbo after coolers will be removed and cleaned. |  |  |  | 0 |  | P | N | N
16 | 17130 | ALB | STATION 4 | 403 | OVERHAUL | 2002-05-26 08:00:00 | 2002-06-04 16:00:00 | 9.3 |  | OPS |  | 200 | 1866.7 | Contractor will provide coplete compressor overhaul with new rods  packing  ring and all new compressor valves. Turbo after coolers will be removed and cleaned. |  |  |  | 0 |  | P | N | N
17 | 17132 | ALB | STATION 5 | 502 | OVERHAUL | 2002-05-01 08:00:00 | 2002-05-07 16:00:00 | 6.3 |  | OPS |  | 0 | 0 | Contractor will remove the old exhaust manifold system and replace with new exhaust manifold system. Also replace turbocharger and turbo coolers with the spare turbo and coolers at the station. |  |  |  | 0 |  | P | N | N
18 | 17131 | ALB | STATION 5 | 501   PHFU | OVERHAUL | 2002-05-10 08:00:00 | 2002-05-24 16:00:00 | 14.3 |  | OPS |  | 0 | 0 | Contractor will remove and replace both left and right bank upper blocks. Block replacement will result in a complete upper end overhaul. |  |  |  | 0 |  | P | N | N
19 | 17136 | ALB | STATION 7 | 701    PHFU | OVERHAUL | 2002-04-03 08:00:00 | 2002-04-11 16:00:00 | 8.3 |  | OPS |  | 0 | 0 | Contractor will remove the old exhaust manifold and replace with new exhaust manifold system. Both intake manifolds will also be replaced.  Intake manifolds will be supplied by Enron. Unit main frame bolts will be checked by ultrasound.  Bolts will be rep | laced if cracked or broken. |  |  | 0 |  | P | N | N
20 | 17137 | ALB | STATION 7 | 702    PHFU | OVERHAUL | 2002-04-15 08:00:00 | 2002-04-30 16:00:00 | 15.3 |  | OPS |  | 0 | 0 | Contractor will remove left and right intake manifolds and send them to Coopers shop in Odessa for repairs. Upon completion  contractor will reinstall. |  |  |  | 0 |  | P | N | N
21 | 17138 | ALB | STATION 7 | 721 | OVERHAUL | 2002-05-20 08:00:00 | 2002-05-28 16:00:00 | 8.3 |  | OPS |  | 0 | 0 | Contractor will perform a complete upper and lower end overhaul.  Ciontractor will remove generator and it will be sent in for complete restoration. |  |  |  | 0 |  | P | N | N
22 | 16752 | ALB | STATION 8 | ALL | AUTOMATION | 2001-09-04 08:00:00 | 2001-10-31 16:00:00 | 57.3 |  | OPS |  | 0 | 0 | Station 8 automation project. 8000 HP |  | 2001-09-04 08:00:00 |  | 0 |  | P | N | N
23 | 17694 | ALB | STATION 9 | 903 | EXHAUST MANIFOLD | 2001-11-05 08:00:00 | 2001-11-16 08:00:00 | 11 |  | OPS |  | 0 | 0 | Change out 903 exhaust manifold. |  |  |  | 0 |  | P | N | N