Spreadsheet: 75ea298f-4ce0-4282-a7e0-bed64d98be78
Sheet: Sheet1

UL Short Circuit Rating of Open Components for use in Industrial Control Panels | Unnamed: 1 | Unnamed: 2 | Unnamed: 3 | Unnamed: 4 | Unnamed: 5 | Unnamed: 6 | Unnamed: 7 | Unnamed: 8 | Unnamed: 9 | Unnamed: 10 | Unnamed: 11 | Unnamed: 12 | Unnamed: 13 | Unnamed: 14 | Unnamed: 15
Product Group | Component Type |  | [NAME] ([NAME]) | Description |  |  | Partial Catalog Number(s) |  | Maximum Horsepower Ratings |  |  |  |  |  | Standard Fault Short Circuit Rating
 |  |  |  |  |  |  |  |  | 1 Phase |  | 3 Phase
 |  |  |  |  |  |  |  |  | 120V | 240V | 200V | 240V | 480V | 600V
Intelligent Technologies | Nema 00 Contact Block |  | 45 | Non-reversing, 3 pole |  |  | N04NBSAX3N |  | 1/3 | 1 | 1.5 | 1.5 | 2 | 2 | 5kA
 | Nema 0 Contact Block |  | 45 |  |  |  | N04NBS0X3N |  | 1 | 2 | 3 | 3 | 5 | 5 | 5kA
 | Nema 1 Contact Block |  | 54 |  |  |  | N04NCS1X3N |  | 2 | 3 | 7.5 | 7.5 | 10 | 10 | 5kA
 | Nema 2 Contact Block |  | 76 |  |  |  | N04NDS2X3N |  | 3 | 7.5 | 10 | 15 | 25 | 25 | 5kA
 | Nema 3 Contact Block |  | 105 |  |  |  | N04NES3X3N |  | 7.5 | 15 | 25 | 30 | 50 | 50 | 5kA
 | Nema 4 Contact Block |  | 105 |  |  |  | N04NES4X3N |  | - | - | 40 | 50 | 100 | 100 | 10kA
Intelligent Technologies | IEC Contact Block |  | 45 | Non-reversing, 3 pole |  |  | E04NB18X3N |  | 1 | 3 | 5 | 5 | 10 | 10 | 5kA
 | IEC Contact Block |  | 45 |  |  |  | E04NB25X3N |  | 2 | 3 | 5 | 7.5 | 15 | 15 | 5kA
 | IEC Contact Block |  | 45 |  |  |  | E04NB32X3N |  | 2 | 5 | 7.5 | 10 | 20 | 20 | 5kA
 | IEC Contact Block |  | 54 |  |  |  | E04NC40X3N |  | 3 | 7.5 | 10 | 10 | 25 | 25 | 5kA
 | IEC Contact Block |  | 54 |  |  |  | E04NC50X3N |  | 3 | 10 | 15 | 15 | 30 | 30 | 5kA
 | IEC Contact Block |  | 76 |  |  |  | E04ND65X3N |  | 5 | 10 | 20 | 20 | 50 | 50 | 10kA
 | IEC Contact Block |  | 76 |  |  |  | E04ND85X3N |  | 7.5 | 15 | 25 | 30 | 60 | 60 | 10kA
 | IEC Contact Block |  | 76 |  |  |  | E04ND10X3N |  | 10 | 20 | 30 | 30 | 75 | 75 | 10kA
 | IEC Contact Block |  | 105 |  |  |  | E04NE12X3N |  | 10 | 25 | 40 | 40 | 100 | 100 | 10kA
 | IEC Contact Block |  | 105 |  |  |  | E04NE16X3N |  | 15 | 30 | 50 | 60 | 125 | 125 | 10kA
 | IEC Contact Block |  | 105 |  |  |  | E04NE20X3N |  | - | 40 | 60 | 75 | 150 | 150 | 10kA
Intelligent Technologies | Nema Overload Relay Module |  | 45 | Non-reversing, 3 pole |  |  | N05NBXRB*3* |  | - | - | - | - | - | - | 5kA
 | Nema Overload Relay Module |  | 54 |  |  |  | N05NCXRC*3* |  | - | - | - | - | - | - | 5kA
 | Nema Overload Relay Module |  | 76 |  |  |  | N05NDXRD*3* |  | - | - | - | - | - | - | 10kA
 | Nema Overload Relay Module |  | 105 |  |  |  | N05NEXRE*3* |  | - | - | - | - | - | - | 10kA
Intelligent Technologies | Nema Overload Relay Module |  | 45 | Reversing, 3 pole |  |  | N06NBXRB*3* |  | - | - | - | - | - | - | 5kA
 | Nema Overload Relay Module |  | 54 |  |  |  | N06NCXRC*3* |  | - | - | - | - | - | - | 5kA
 | Nema Overload Relay Module |  | 76 |  |  |  | N06NDXRD*3* |  | - | - | - | - | - | - | 10kA
 | Nema Overload Relay Module |  | 105 |  |  |  | N06NEXRE*3* |  | - | - | - | - | - | - | 10kA
Intelligent Technologies | IEC Overload Relay Module |  | 45 | Non-reversing, 3 pole |  |  | E05NBXRB*3* |  | - | - | - | - | - | - | 5kA
 | IEC Overload Relay Module |  | 54 |  |  |  | E05NCXRC*3* |  | - | - | - | - | - | - | 5kA
 | IEC Overload Relay Module |  | 76 |  |  |  | E05NDXRD*3* |  | - | - | - | - | - | - | 10kA
 | IEC Overload Relay Module |  | 105 |  |  |  | E05NEXRE*3* |  | - | - | - | - | - | - | 10kA
Intelligent Technologies | IEC Overload Relay Module |  | 45 | Reversing, 3 pole |  |  | E06NBXRB*3* |  | - | - | - | - | - | - | 5kA
 | IEC Overload Relay Module |  | 54 |  |  |  | E06NCXRC*3* |  | - | - | - | - | - | - | 5kA
 | IEC Overload Relay Module |  | 76 |  |  |  | E06NDXRD*3* |  | - | - | - | - | - | - | 10kA
 | IEC Overload Relay Module |  | 105 |  |  |  | E06NEXRE*3* |  | - | - | - | - | - | - | 10kA
Intellignet Technologies | Nema 00 - Complete Contactor |  | 45 | Non-reversing, 3 pole |  |  | N111BSAX3N |  | 1/3 | 1 | 1.5 | 1.5 | 2 | 2 | 5kA
 | Nema 0 - Complete Contactor |  | 45 |  |  |  | N111BS0X3N |  | 1 | 2 | 3 | 3 | 5 | 5 | 5kA
 | Nema 1 - Complete Contactor |  | 54 |  |  |  | N111CS1X3N |  | 2 | 3 | 7.5 | 7.5 | 10 | 10 | 5kA
 | Nema 2 - Complete Contactor |  | 76 |  |  |  | N111DS2X3N |  | 3 | 7.5 | 10 | 15 | 25 | 25 | 5kA
 | Nema 3 - Complete Contactor |  | 105 |  |  |  | N111ES3X3N |  | 7.5 | 15 | 25 | 30 | 50 | 50 | 5kA
 | Nema 4 - Complete Contactor |  | 105 |  |  |  | N111ES4X3N |  | - | - | 40 | 50 | 100 | 100 | 10kA
 | Nema 5 - Complete Contactor |  | 140 |  |  |  | N111FS5X3N |  | - | - | 75 | 100 | 200 | 200 | 18kA
Intellignet Technologies | Nema 00 - Complete Contactor |  | 45 | Reversing, 3 pole |  |  | N511BSAX3N |  | 1/3 | 1 | 1.5 | 1.5 | 2 | 2 | 5kA
 | Nema 0 - Complete Contactor |  | 45 |  |  |  | N511BS0X3N |  | 1 | 2 | 3 | 3 | 5 | 5 | 5kA
 | Nema 1 - Complete Contactor |  | 54 |  |  |  | N511CS1X3N |  | 2 | 3 | 7.5 | 7.5 | 10 | 10 | 5kA
 | Nema 2 - Complete Contactor |  | 76 |  |  |  | N511DS2X3N |  | 3 | 7.5 | 10 | 15 | 25 | 25 | 5kA
 | Nema 3 - Complete Contactor |  | 105 |  |  |  | N511ES3X3N |  | 7.5 | 15 | 25 | 30 | 50 | 50 | 5kA
 | Nema 4 - Complete Contactor |  | 105 |  |  |  | N511ES4X3N |  | - | - | 40 | 50 | 100 | 100 | 10kA
 | Nema 5 - Complete Contactor |  | 140 |  |  |  | N511FS5X3N |  | - | - | 75 | 100 | 200 | 200 | 18kA
Intelligent Technologies | IEC - Complete Contactor |  | 27 | Non-reversing, 3 pole |  |  | E111A06X3N |  | 1/4 | 1/2 | 1 | 1.5 | 3 | 3 | 5kA
 | IEC - Complete Contactor |  | 27 |  |  |  | E111A09X3N |  | 1/3 | 1 | 2 | 2 | 5 | 5 | 5kA
 | IEC - Complete Contactor |  | 27 |  |  |  | E111A12X3N |  | 1/2 | 2 | 3 | 3 | 7.5 | 7.5 | 5kA
 | IEC - Complete Contactor |  | 45 |  |  |  | E111B18X3N |  | 1 | 3 | 5 | 5 | 10 | 10 | 5kA
 | IEC - Complete Contactor |  | 45 |  |  |  | E111B25X3N |  | 2 | 3 | 5 | 7.5 | 15 | 15 | 5kA
 | IEC - Complete Contactor |  | 45 |  |  |  | E111B32X3N |  | 2 | 5 | 7.5 | 10 | 20 | 20 | 5kA
 | IEC - Complete Contactor |  | 54 |  |  |  | E111C40X3N |  | 3 | 7.5 | 10 | 10 | 25 | 25 | 5kA
 | IEC - Complete Contactor |  | 54 |  |  |  | E111C50X3N |  | 3 | 10 | 15 | 15 | 30 | 30 | 5kA
 | IEC - Complete Contactor |  | 76 |  |  |  | E111D65X3N |  | 5 | 10 | 20 | 20 | 50 | 50 | 10kA
 | IEC - Complete Contactor |  | 76 |  |  |  | E111D85X3N |  | 7.5 | 15 | 25 | 30 | 60 | 60 | 10kA
 | IEC - Complete Contactor |  | 76 |  |  |  | E111D10X3N |  | 10 | 20 | 30 | 30 | 75 | 75 | 10kA
 | IEC - Complete Contactor |  | 105 |  |  |  | E111E12X3N |  | 10 | 25 | 40 | 40 | 100 | 100 | 10kA
 | IEC - Complete Contactor |  | 105 |  |  |  | E111E16X3N |  | 15 | 30 | 50 | 60 | 125 | 125 | 10kA
 | IEC - Complete Contactor |  | 105 |  |  |  | E111E20X3N |  | - | 40 | 60 | 75 | 150 | 150 | 10kA
 | IEC - Complete Contactor |  | 140 |  |  |  | E111F25X3N |  | - | 50 | 75 | 100 | 200 | 200 | 18kA
 | IEC - Complete Contactor |  | 140 |  |  |  | E111F31X3N |  | - | - | 100 | 125 | 250 | 250 | 18kA
 | IEC - Complete Contactor |  | 140 |  |  |  | E111F42X3N |  | - | - | 150 | 150 | 350 | 350 | 18kA
Intelligent Technologies | IEC - Complete Contactor |  | 27 | Reversing, 3 pole |  |  | E511A06X3N |  | 1/4 | 1/2 | 1 | 1.5 | 3 | 3 | 5kA
 | IEC - Complete Contactor |  | 27 |  |  |  | E511A09X3N |  | 1/3 | 1 | 2 | 2 | 5 | 5 | 5kA
 | IEC - Complete Contactor |  | 27 |  |  |  | E511A12X3N |  | 1/2 | 2 | 3 | 3 | 7.5 | 7.5 | 5kA
 | IEC - Complete Contactor |  | 45 |  |  |  | E511B18X3N |  | 1 | 3 | 5 | 5 | 10 | 10 | 5kA
 | IEC - Complete Contactor |  | 45 |  |  |  | E511B25X3N |  | 2 | 3 | 5 | 7.5 | 15 | 15 | 5kA
 | IEC - Complete Contactor |  | 45 |  |  |  | E511B32X3N |  | 2 | 5 | 7.5 | 10 | 20 | 20 | 5kA
 | IEC - Complete Contactor |  | 54 |  |  |  | E511C40X3N |  | 3 | 7.5 | 10 | 10 | 25 | 25 | 5kA
 | IEC - Complete Contactor |  | 54 |  |  |  | E511C50X3N |  | 3 | 10 | 15 | 15 | 30 | 30 | 5kA
 | IEC - Complete Contactor |  | 76 |  |  |  | E511D65X3N |  | 5 | 10 | 20 | 20 | 50 | 50 | 10kA
 | IEC - Complete Contactor |  | 76 |  |  |  | E511D85X3N |  | 7.5 | 15 | 25 | 30 | 60 | 60 | 10kA
 | IEC - Complete Contactor |  | 76 |  |  |  | E511D10X3N |  | 10 | 20 | 30 | 30 | 75 | 75 | 10kA
 | IEC - Complete Contactor |  | 105 |  |  |  | E511E12X3N |  | 10 | 25 | 40 | 40 | 100 | 100 | 10kA
 | IEC - Complete Contactor |  | 105 |  |  |  | E511E16X3N |  | 15 | 30 | 50 | 60 | 125 | 125 | 10kA
 | IEC - Complete Contactor |  | 105 |  |  |  | E511E20X3N |  | - | 40 | 60 | 75 | 150 | 150 | 10kA
 | IEC - Complete Contactor |  | 140 |  |  |  | E511F25X3N |  | - | 50 | 75 | 100 | 200 | 200 | 18kA
 | IEC - Complete Contactor |  | 140 |  |  |  | E511F31X3N |  | - | - | 100 | 125 | 250 | 250 | 18kA
 | IEC - Complete Contactor |  | 140 |  |  |  | E511F42X3N |  | - | - | 150 | 150 | 350 | 350 | 18kA
Intelligent Technologies | Nema 00 - Complete Starter |  | 45 | Non-reversing, 3 pole |  |  | N101BSAB*3* |  | 1/3 | 1 | 1.5 | 1.5 | 2 | 2 | 5kA
 | Nema 0 - Complete Starter |  | 45 |  |  |  | N101BS0B*3* |  | 1 | 2 | 3 | 3 | 5 | 5 | 5kA
 | Nema 1 - Complete Starter |  | 54 |  |  |  | N101CS1C*3* |  | 2 | 3 | 7.5 | 7.5 | 10 | 10 | 5kA
 | Nema 2 - Complete Starter |  | 76 |  |  |  | N101DS2D*3* |  | 3 | 7.5 | 10 | 15 | 25 | 25 | 5kA
 | Nema 3 - Complete Starter |  | 105 |  |  |  | N101ES3E*3* |  | 7.5 | 15 | 25 | 30 | 50 | 50 | 5kA
 | Nema 4 - Complete Starter |  | 105 |  |  |  | N101ES4E*3* |  | - | - | 40 | 50 | 100 | 100 | 10kA
 | Nema 5 - Complete Starter |  | 140 |  |  |  | N101FS5F*3* |  | - | - | 75 | 100 | 200 | 200 | 18kA
Intelligent Technologies | Nema 00 - Complete Starter |  | 45 | Reversing, 3 pole |  |  | N501BSAB*3* |  | 1/3 | 1 | 1.5 | 1.5 | 2 | 2 | 5kA
 | Nema 0 - Complete Starter |  | 45 |  |  |  | N501BS0B*3* |  | 1 | 2 | 3 | 3 | 5 | 5 | 5kA
 | Nema 1 - Complete Starter |  | 54 |  |  |  | N501CS1C*3* |  | 2 | 3 | 7.5 | 7.5 | 10 | 10 | 5kA
 | Nema 2 - Complete Starter |  | 76 |  |  |  | N501DS2D*3* |  | 3 | 7.5 | 10 | 15 | 25 | 25 | 5kA
 | Nema 3 - Complete Starter |  | 105 |  |  |  | N501ES3E*3* |  | 7.5 | 15 | 25 | 30 | 50 | 50 | 5kA
 | Nema 4 - Complete Starter |  | 105 |  |  |  | N501ES4E*3* |  | - | - | 40 | 50 | 100 | 100 | 10kA
 | Nema 5 - Complete Starter |  | 140 |  |  |  | N501FS5F*3* |  | - | - | 75 | 100 | 200 | 200 | 18kA
Intelligent Technologies | IEC - Complete Starter |  | 27 | Non-reversing, 3 pole |  |  | E101A06A*3* |  | 1/4 | 1/2 | 1 | 1.5 | 3 | 3 | 5kA
 | IEC - Complete Starter |  | 27 |  |  |  | E101A09A*3* |  | 1/3 | 1 | 2 | 2 | 5 | 5 | 5kA
 | IEC - Complete Starter |  | 27 |  |  |  | E101A12A*3* |  | 1/2 | 2 | 3 | 3 | 7.5 | 7.5 | 5kA
 | IEC - Complete Starter |  | 45 |  |  |  | E101B18B*3* |  | 1 | 3 | 5 | 5 | 10 | 10 | 5kA
 | IEC - Complete Starter |  | 45 |  |  |  | E101B25B*3* |  | 2 | 3 | 5 | 7.5 | 15 | 15 | 5kA
 | IEC - Complete Starter |  | 45 |  |  |  | E101B32B*3* |  | 2 | 5 | 7.5 | 10 | 20 | 20 | 5kA
 | IEC - Complete Starter |  | 54 |  |  |  | E101C40C*3* |  | 3 | 7.5 | 10 | 10 | 25 | 25 | 5kA
 | IEC - Complete Starter |  | 54 |  |  |  | E101C50C*3* |  | 3 | 10 | 15 | 15 | 30 | 30 | 5kA
 | IEC - Complete Starter |  | 76 |  |  |  | E101D65D*3* |  | 5 | 10 | 20 | 20 | 50 | 50 | 10kA
 | IEC - Complete Starter |  | 76 |  |  |  | E101D85D*3* |  | 7.5 | 15 | 25 | 30 | 60 | 60 | 10kA
 | IEC - Complete Starter |  | 76 |  |  |  | E101D10D*3* |  | 10 | 20 | 30 | 30 | 75 | 75 | 10kA
 | IEC - Complete Starter |  | 105 |  |  |  | E101E12E*3* |  | 10 | 25 | 40 | 40 | 100 | 100 | 10kA
 | IEC - Complete Starter |  | 105 |  |  |  | E101E16E*3* |  | 15 | 30 | 50 | 60 | 125 | 125 | 10kA
 | IEC - Complete Starter |  | 105 |  |  |  | E101E20E*3* |  | - | 40 | 60 | 75 | 150 | 150 | 10kA
 | IEC - Complete Starter |  | 140 |  |  |  | E101F25F*3* |  | - | 50 | 75 | 100 | 200 | 200 | 18kA
 | IEC - Complete Starter |  | 140 |  |  |  | E101F31F*3* |  | - | - | 100 | 125 | 250 | 250 | 18kA
 | IEC - Complete Starter |  | 140 |  |  |  | E101F42F*3* |  | - | - | 150 | 150 | 350 | 350 | 18kA
Intelligent Technologies | IEC - Complete Starter |  | 27 | Reversing, 3 pole |  |  | E501A06A*3* |  | 1/4 | 1/2 | 1 | 1.5 | 3 | 3 | 5kA
 | IEC - Complete Starter |  | 27 |  |  |  | E501A09A*3* |  | 1/3 | 1 | 2 | 2 | 5 | 5 | 5kA
 | IEC - Complete Starter |  | 27 |  |  |  | E501A12A*3* |  | 1/2 | 2 | 3 | 3 | 7.5 | 7.5 | 5kA
 | IEC - Complete Starter |  | 45 |  |  |  | E501B18B*3* |  | 1 | 3 | 5 | 5 | 10 | 10 | 5kA
 | IEC - Complete Starter |  | 45 |  |  |  | E501B25B*3* |  | 2 | 3 | 5 | 7.5 | 15 | 15 | 5kA
 | IEC - Complete Starter |  | 45 |  |  |  | E501B32B*3* |  | 2 | 5 | 7.5 | 10 | 20 | 20 | 5kA
 | IEC - Complete Starter |  | 54 |  |  |  | E501C40C*3* |  | 3 | 7.5 | 10 | 10 | 25 | 25 | 5kA
 | IEC - Complete Starter |  | 54 |  |  |  | E501C50C*3* |  | 3 | 10 | 15 | 15 | 30 | 30 | 5kA
 | IEC - Complete Starter |  | 76 |  |  |  | E501D65D*3* |  | 5 | 10 | 20 | 20 | 50 | 50 | 10kA
 | IEC - Complete Starter |  | 76 |  |  |  | E501D85D*3* |  | 7.5 | 15 | 25 | 30 | 60 | 60 | 10kA
 | IEC - Complete Starter |  | 76 |  |  |  | E501D10D*3* |  | 10 | 20 | 30 | 30 | 75 | 75 | 10kA
 | IEC - Complete Starter |  | 105 |  |  |  | E501E12E*3* |  | 10 | 25 | 40 | 40 | 100 | 100 | 10kA
 | IEC - Complete Starter |  | 105 |  |  |  | E501E16E*3* |  | 15 | 30 | 50 | 60 | 125 | 125 | 10kA
 | IEC - Complete Starter |  | 105 |  |  |  | E501E20E*3* |  | - | 40 | 60 | 75 | 150 | 150 | 10kA
 | IEC - Complete Starter |  | 140 |  |  |  | E501F25F*3* |  | - | 50 | 75 | 100 | 200 | 200 | 18kA
 | IEC - Complete Starter |  | 140 |  |  |  | E501F31F*3* |  | - | - | 100 | 125 | 250 | 250 | 18kA
 | IEC - Complete Starter |  | 140 |  |  |  | E501F42F*3* |  | - | - | 150 | 150 | 350 | 350 | 18kA
Intelligent Technologies | Nema 00 Coil Controller |  | 45 | Non-reversing |  |  | N02NBXCXNN |  | - | - | - | - | - | - | 5kA
 | Nema 0 Coil Controller |  | 45 |  |  |  | N02NBXCXNN |  | - | - | - | - | - | - | 5kA
 | Nema 1 Coil Controller |  | 54 |  |  |  | N02NCXCXNN |  | - | - | - | - | - | - | 5kA
 | Nema 2 Coil Controller |  | 76 |  |  |  | N02NDXCXNN |  | - | - | - | - | - | - | 5kA
 | Nema 3 Coil Controller |  | 105 |  |  |  | N02NEXCXNN |  | - | - | - | - | - | - | 5kA
 | Nema 4 Coil Controller |  | 105 |  |  |  | N02NEXCXNN |  | - | - | - | - | - | - | 10kA
Intelligent Technologies | Nema 00 Coil Controller |  | 45 | Reversing |  |  | N03NBXCXNN |  | - | - | - | - | - | - | 5kA
 | Nema 0 Coil Controller |  | 45 |  |  |  | N03NBXCXNN |  | - | - | - | - | - | - | 5kA
 | Nema 1 Coil Controller |  | 54 |  |  |  | N03NCXCXNN |  | - | - | - | - | - | - | 5kA
 | Nema 2 Coil Controller |  | 76 |  |  |  | N03NDXCXNN |  | - | - | - | - | - | - | 5kA
 | Nema 3 Coil Controller |  | 105 |  |  |  | N03NEXCXNN |  | - | - | - | - | - | - | 5kA
 | Nema 4 Coil Controller |  | 105 |  |  |  | N03NEXCXNN |  | - | - | - | - | - | - | 10kA