Spreadsheet: 6bfa9a99-172c-4232-b88e-219f47e034a0
Sheet: Sheet1

UL Short Circuit Rating of Open Components for use in Industrial Control Panels | Unnamed: 1 | Unnamed: 2 | Unnamed: 3 | Unnamed: 4 | Unnamed: 5 | Unnamed: 6 | Unnamed: 7 | Unnamed: 8 | Unnamed: 9
Product Group | Frame Size | Description | Fuse Class | Catalog No. | [NAME] | [NAME]. 3 Ph. Horsepower Ratings |  |  | Standard Fault Short Circuit Current Rating
 |  |  |  |  |  | 240V | 480V | 600V
C362 | M | Non-fusible rotary switch - base mounted | - | C362NM16 | 16 | 2 | 7.5 | 7.5 | 5kA when protected by  30 A. RK5 fuses
 |  |  |  | C362NM20 | 20 | 3 | 7.5 | 10
 |  |  |  | C362NM25 | 25 | 5 | 10 | 15
C362 | M | Non-fusible rotary switch - back/door mounted | - | C362NM16D | 16 | 2 | 7.5 | 7.5 | 5kA when protected by 30 A. RK5 fuses
 |  |  |  | C362NM20D | 20 | 3 | 7.5 | 10
 |  |  |  | C362NM25D | 25 | 5 | 10 | 15
C362 / C462 | R | Non-fusible rotary switch - base mounted | - | C362NR30 | 30 | 7.5 | 15 | 25 | 10kA when protected by 80A. RK5 fuses.
 |  |  |  | C462NR30 | 30 | 7.5 | 15 | 25
 |  |  |  | C362NR40 | 40 | 10 | 20 | 30
 |  |  |  | C462NR40 | 40 | 10 | 20 | 30
 | W |  |  | C362NW60 | 60 | 15 | 30 | 40 | 10kA when protected by 150A. RK5 fuses.
 |  |  |  | C362NW80 | 80 | 20 | 40 | 50
 |  |  |  | C362NW100 | 100 | 25 | 50 | 60
 |  |  |  | C362NW125 | 125 | 25 | 50 | 60
C362 / C462 | R | Non-fusible toggle switch - base mounted | - | C362TR30 | 30 | 7.5 | 15 | 25 | 10kA when protected by 80A. RK5 fuses.
 |  |  |  | C462TR30 | 30 | 7.5 | 15 | 25
 |  |  |  | C362TR40 | 40 | 10 | 20 | 30
 |  |  |  | C462TR40 | 40 | 10 | 20 | 30
 | W |  |  | [NAME] | 60 | 15 | 30 | 40 | 10kA when protected by 150A. RK5 fuses.
 |  |  |  | C362TW80 | 80 | 20 | 40 | 50
 |  |  |  | [NAME] | 100 | 25 | 50 | 60
 |  |  |  | C362TW125 | 125 | 25 | 50 | 60
C362 | C | Non-fusible rotary switch - base mounted | - | C362UC30 | 30 | 7.5 | 15 | 20 | 50kA when protected bu 30A. CC or J fuses.
 | V | Non-fusible rotry switch - base mounted |  | C362UV60 | 60 | 15 | 30 | 50 | 200kA when protected by 200 A. J fuses
 |  |  |  | C362UV100 | 100 | 30 | 60 | 75
 |  |  |  | C362UV200 | 200 | 60 | 125 | 150
 | S | Non-fusible rotary switch - base mounted |  | C362US400 | 400 | 125 | 250 | 350 | 200kA when protected by 400A. J fuses.
 |  |  |  | C362US600 | 600 | 200 | 400 | 350 | 200 [NAME] when protected by 600A. J fuses
 |  |  |  | C362US800 | 800 | 250 | 500 | 500 | 100kA when protected by 800A. L fuses
 |  |  |  | C362US1000 | 1000 | 250 | 500 | 500 | 100kA when protected by 1000A. L fuses
 |  |  |  | C362US1200 | 1200 | 250 | 500 | 500 | 100kA when protected by 1200A. L fuses
C363 | C | Fusible switch - base mounted | CC | C363UC30CT | 30 | 7.5 | 15 | 20 | 50kA with 30A. CC fuses
 |  |  | J | C363UC30JT | 30 | 7.5 | 15 | 20 | 50kA with 30A. J fuses
C363 | V | Fusible switch - base mounted | CC | C363UV30C | 30 | 7.5 | 15 | 20 | 100kA with 30A. CC fuses
 |  |  | J | C363UV30J | 30 | 7.5 | 15 | 20 | 200kA  with 30A. J fuses
 |  |  | J | C363UV60J | 60 | 15 | 30 | 50 | 200kA with 60A. J fuses
 |  |  | J | C363UV100J | 100 | 30 | 60 | 75 | 200kA with 100A. J fuses
 |  |  | J | C363UV200J | 200 | 60 | 125 | 150 | 200kA with 200A. J fuses
 |  |  | J | C363UV400J | 400 | 125 | 250 | 350 | 200kA with 400A. J fuses
 |  |  | J | C363UV30CT | 30 | 7.5 | 15 | 20 | 100kA with 30A. CC fuses
 |  |  | J | C363UV30JT | 30 | 7.5 | 15 | 20 | 200kA  with 30A. J fuses
 |  |  | J | C363UV60JT | 60 | 15 | 30 | 50 | 200kA with 60A. J fuses
 |  |  | J | C363UV100JT | 100 | 30 | 60 | 75 | 200kA with 100A. J fuses
 |  |  | J | C363UV200JT | 200 | 60 | 125 | 150 | 200kA with 200A. J fuses
 |  |  | J | C363UV400JT | 400 | 125 | 250 | 350 | 200kA with 400A. J fuses
C363 | F | Fusible switch - base mounted | J | C363UF600J | 600 | 250 | 500 | 500 | 200kA  with 600A. J fuse
 |  |  | L | C363UF800L | 800 | 250 | 500 | 500 | 100kA with 800A. J fuse