Spreadsheet: 104812d1302271024-searching-and-comparing-text-string-in-2-columns-notional-sheet
Sheet: IRMP Table 4.1

 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 6148
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 7e | Emergency vent device exhausts indoors |  | Relocate emergency vent device to exhaust outdoors |  |  |  |  | 300 | 60 | 16 | 800 | 1160
 | 8c | Low melting temperature metals used in piping system |  | Replace brass valves with steel |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | 8i | Possible leak identified in piping system |  | Repair/replace leaking fittings |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | 9b | No isolation valve on supply line at tank |  | Install steel isolation valve on supply line at tank |  |  |  |  | 100 | 20 | 8 | 400 | 520
 | 9d/10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 400 | 80 | 8 | 400 | 880
 | 10g | No fire safety valve installed on fuel distribution lines |  | Install fire safety valves on fuel distribution lines |  |  |  |  | 400 | 80 | 8 | 400 | 880
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 6148
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 5684
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4a | Tank not protected from vehicular impact |  | Install vehicle protection |  |  |  |  | 2000 | 400 | 16 | 800 | 3200
 | 7e/f | Emergency vent gasket in need of replacement |  | Replace emergency vent gaskets |  |  |  |  | 100 | 20 | 4 | 200 | 320
 | 9d/10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 400 | 80 | 8 | 400 | 880
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 5684
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 5100
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 6h | Debris and product identified in tank containment |  | Remove debris and product from inside containment |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 7b | Vent piping used for other purposes than venting |  | Remove fill line from vent piping |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 7c | Plastic used to close tank openings |  | Replace plastic plug with steel |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 7e | No primary emergency vent device present |  | Install 3" UL-listed emergency vent device exhausting outdoors |  |  |  |  | 300 | 60 | 16 | 800 | 1160
 | 8i | Possible leak identified in piping system |  | Repair/replace leaking fittings |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | 9b | No isolation valve on supply line at tank |  | Install steel isolation valve on supply line at tank |  |  |  |  | 100 | 20 | 8 | 400 | 520
 | 9d/10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 400 | 80 | 8 | 400 | 880
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: Source of product in spill containment should be located and tank should be replaced if its integrity is compromised |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 5100
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3208
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2p | No fire diamond or fuel contents placards |  | Install fire diamond and fuel contents placards |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 7d | Normal vent device too small |  | Install 1-1/4" normal vent device exhausting outdoors |  |  |  |  | 250 | 50 | 8 | 400 | 700
 | 7e | No primary emergency vent device installed |  | Install 4" UL-listed emergency vent device exhausting outdoors |  |  |  |  | 300 | 60 | 16 | 800 | 1160
 | 8c | Low melting temperature metals used in piping system |  | Replace brass valves with steel |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: Minimum allowable venting size is 1-1/4" |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3208
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3208
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2p | No fire diamond or fuel contents placards |  | Install fire diamond and fuel contents placards |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 7d | Normal vent device too small |  | Install 1-1/4" normal vent device exhausting outdoors |  |  |  |  | 250 | 50 | 8 | 400 | 700
 | 7e | No primary emergency vent device installed |  | Install 4" UL-listed emergency vent device exhausting outdoors |  |  |  |  | 300 | 60 | 16 | 800 | 1160
 | 8c | Low melting temperature metals used in piping system |  | Replace brass valves with steel |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3208
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3308
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2p | No fire diamond or fuel contents placards |  | Install fire diamond and fuel contents placards |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 7b | Normal vent used for other purpose than venting |  | Remove return line from vent piping |  |  |  |  | 20 | 4 | 8 | 400 | 424
 | 7f | Secondary emergency vent improperly oriented |  | Relocate emergency vent so that it exhaust vertically above tank shell exhausting outside |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 9d/10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 400 | 80 | 8 | 400 | 880
 | 10a | No isolation valve located on distribution line at tank |  | Install steel isolation valve on distribution line at tank |  |  |  |  | 100 | 20 | 8 | 400 | 520
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3308
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3308
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2p | No fire diamond or fuel contents placards |  | Install fire diamond and fuel contents placards |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 7b | Normal vent used for other purpose than venting |  | Remove return line from vent piping |  |  |  |  | 20 | 4 | 8 | 400 | 424
 | 7f | Secondary emergency vent improperly oriented |  | Relocate emergency vent so that it exhaust vertically above tank shell exhausting outside |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 9d/10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 400 | 80 | 8 | 400 | 880
 | 10a | No isolation valve located on distribution line at tank |  | Install steel isolation valve on distribution line at tank |  |  |  |  | 100 | 20 | 8 | 400 | 520
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3308
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 2548
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond or fuel contents placards |  | Install fire diamond and fuel contents placards |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 7d | Normal vent device too small |  | Install 1-1/4" normal vent device exhausting outdoors |  |  |  |  | 250 | 50 | 8 | 400 | 700
 | 8d | Evidence of Teflon tape being used to seal joints |  | Reseal fittings with pipe sealant |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | 9d/10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 400 | 80 | 8 | 400 | 880
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 2548
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 5560
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2p | No fire diamond or fuel contents placards |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7d | Normal vent device too small |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7e | No primary emergency vent device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 8c | Low melting temperature metals used in piping system |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 8g | Possible fuel leaking from fuel filter |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 9d/10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 10g | No fire safety valve installed on fuel distribution lines |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 11e | No grounding system installed |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 |  | Tank can not be retrofitted to comply with applicable standards (see notes) |  | Replace tank with suitable UL-142 listed tank |  |  |  |  | 2800 | 560 | 24 | 1200 | 4560
 |  | Upon installation of new tank a Formal External Inspection is required |  | Perform a formal external inspection on newly installed tank |  |  |  |  | 0 | 0 | 20 | 1000 | 1000
 | Comments: TANK NEEDS TO BE REPLACED  This tank does not have a primary emergency vent or a port capable of providing adequate emergency venting capacity.  This tank not adequately vented, and is therefore not suited for continued use.  It is recommended that a new tank is be installed, and a Formal External Inspection should be performed prior to putting new tank into service. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 5560
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 5560
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2p | No fire diamond or fuel contents placards |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7d | Normal vent device too small |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7e | No primary emergency vent device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 8c | Low melting temperature metals used in piping system |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 8g | Possible fuel leaking from fuel filter |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 9d/10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 10g | No fire safety valve installed on fuel distribution lines |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 11e | No grounding system installed |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 |  | Tank can not be retrofitted to comply with applicable standards (see notes) |  | Replace tank with suitable UL-142 listed tank |  |  |  |  | 2800 | 560 | 24 | 1200 | 4560
 |  | Upon installation of new tank a Formal External Inspection is required |  | Perform a formal external inspection on newly installed tank |  |  |  |  | 0 | 0 | 20 | 1000 | 1000
 | Comments: TANK NEEDS TO BE REPLACED  This tank does not have a primary emergency vent or a port capable of providing adequate emergency venting capacity.  This tank not adequately vented, and is therefore not suited for continued use.  It is recommended that a new tank is be installed, and a Formal External Inspection should be performed prior to putting new tank into service. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 5560
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 5560
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2p | No fire diamond or fuel contents placards |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7d | Normal vent device too small |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7e | No primary emergency vent device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 8c | Low melting temperature metals used in piping system |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 9b | No isolation valve on supply line at tank |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 9d/10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 10g | No fire safety valve installed on fuel distribution lines |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 11e | No grounding system installed |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 |  | Tank can not be retrofitted to comply with applicable standards (see notes) |  | Replace tank with suitable UL-142 listed tank |  |  |  |  | 2800 | 560 | 24 | 1200 | 4560
 |  | Upon installation of new tank a Formal External Inspection is required |  | Perform a formal external inspection on newly installed tank |  |  |  |  | 0 | 0 | 20 | 1000 | 1000
 | Comments: TANK NEEDS TO BE REPLACED   This tank does not have a primary emergency vent or a port capable of providing adequate emergency venting capacity.  This tank not adequately vented, and is therefore not suited for continued use.  It is recommended that a new tank is be installed, and a Formal External Inspection should be performed prior to putting new tank into service. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 5560
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 4528
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2p | No fire diamond or fuel contents placards |  | Install fire diamond and fuel contents placards |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 4d | Coating failure |  | Prepare surface and repaint (Including piping) |  |  |  |  | 200 | 40 | 16 | 800 | 1040
 | 8i | Possible leak identified in piping system |  | Repair/replace leaking fittings |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | 9i | Error with ATGS system |  | Inspect/repair ATGS system |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 11c | Obvious electrical hazards present |  | Remove electrical conduit from pipe trench |  |  |  |  | 200 | 40 | 16 | 800 | 1040
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 4528
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 1708
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 8i | Possible leak identified in piping system |  | Repair/replace leaking fittings |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 1708
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 4440
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2p | No fire diamond placards |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7e | No primary emergency vent device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 8c | Low melting temperature metals used in piping system |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 9d/10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 10g | No fire safety valve installed on fuel distribution lines |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 11e | No grounding system installed |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 |  | Tank can not be retrofitted to comply with applicable standards (see notes) |  | Replace tank with suitable UL-142 listed tank |  |  |  |  | 2200 | 440 | 16 | 800 | 3440
 |  | Upon installation of new tank a Formal External Inspection is required |  | Perform a formal external inspection on newly installed tank |  |  |  |  | 0 | 0 | 20 | 1000 | 1000
 | Comments: TANK NEEDS TO BE REPLACED  This tank does not have a primary emergency vent or a port capable of providing adequate emergency venting capacity.  This tank not adequately vented, and is therefore not suited for continued use.  It is recommended that a new tank is be installed, and a Formal External Inspection should be performed prior to putting new tank into service. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 4440
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3748
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2p | No fire diamond or fuel contents placards |  | Install fire diamond and fuel contents placards |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 7e | No primary emergency vent device present |  | Replace current normal vent device with UL-listed emergency vent device and label vent port |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 9d/10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 400 | 80 | 8 | 400 | 880
 | 10g | No fire safety valve installed on fuel distribution lines |  | Install fire safety valves on fuel distribution lines |  |  |  |  | 400 | 80 | 8 | 400 | 880
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: Ensure vent port is labeled as "Emergency Vent" |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3748
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 2968
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 7f | No secondary emergency device present |  | Install 3" UL-listed emergency vent device on interstice |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 7g | Tank interstice vented to the atmosphere |  | Remove normal vent device from tank interstice and replace with steel cap |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 8c | Low melting temperature metals used in piping system |  | Replace brass valves with steel |  |  |  |  | 100 | 20 | 4 | 200 | 320
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 2968
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 2628
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 7b | Vent piping used for other purposes than venting |  | Remove return line from vent piping |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 8h | Piping coating failure |  | Prepare surface and repaint piping |  |  |  |  | 100 | 20 | 16 | 800 | 920
 | 8i | Overfill alarms require maintenance/ not audible at fill location |  | Repair and relocate alarm annunciator to be audible from fill location |  |  |  |  | 150 | 30 | 8 | 400 | 580
 | 10a | No isolation valve located on distribution line at tank |  | Install steel isolation valve on distribution line at tank |  |  |  |  | 100 | 20 | 8 | 400 | 520
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 2628
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 840
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2v | Tank out of service |  | Drain tank, remove piping, drill quarter inch hole in cap and schedule for removal |  |  |  |  | 200 | 40 | 12 | 600 | 840
 | Comments:  Tank is currently out of service. If the tank is to be put back into service the above recommendations should be addressed prior to refilling the tank and an FEI should be performed before the tank is used. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 840
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 8100
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2p | No fire diamond placards |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 4a | Tank not protected from vehicular impact |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 4d | Coating failure |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7d | No normal vent device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7e | No primary emergency vent device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 |  | Tank can not be retrofitted to comply with applicable standards (see notes) |  | Replace tank with suitable UL-142 listed tank |  |  |  |  | 5250 | 1050 | 16 | 800 | 7100
 |  | Upon installation of new tank a Formal External Inspection is required |  | Perform a formal external inspection on newly installed tank |  |  |  |  | 0 | 0 | 20 | 1000 | 1000
 | Comments: TANK NEEDS TO BE REPLACED  This tank does not have a primary emergency vent or a port capable of providing adequate emergency venting capacity.  This tank not adequately vented, and is therefore not suited for continued use.  It is recommended that a new tank is be installed, and a Formal External Inspection should be performed prior to putting new tank into service. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 8100
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3592
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond or fuel contents placards |  | Install fire diamond and fuel contents placards |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 6f | Containment drain not locked or capped to prevent unauthorized opening |  | Lock or cap containment drain |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 7e | No primary emergency vent device present |  | Install 3" UL-listed emergency vent device exhausting outdoors |  |  |  |  | 300 | 60 | 16 | 800 | 1160
 | 8i | Possible leak identified in piping system |  | Repair/replace leaking fittings |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: Ensure Emergency vent is labeled at port |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3592
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 2604
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 7e | No primary emergency vent device present |  | Install 3" UL-listed emergency vent device exhausting outdoors |  |  |  |  | 300 | 60 | 16 | 800 | 1160
 | 7f | No secondary emergency device present |  | Install 3" UL-listed emergency vent device on interstice exhausting outdoors |  |  |  |  | 300 | 60 | 16 | 800 | 1160
 | Comments: Ensure Emergency vent is labeled at port |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 2604
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 840
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2o | No fire extinguisher in vicinity of AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2p | No fire diamond or fuel contents placards |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7e | No primary emergency vent device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2v | Tank out of service |  | Drain tank, remove piping, drill quarter inch hole in cap and schedule for removal |  |  |  |  | 200 | 40 | 12 | 600 | 840
 | Comments:  Tank is currently out of service. If the tank is to be put back into service the above recommendations should be addressed prior to refilling the tank and an FEI should be performed before the tank is used. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 840
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 5504
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 7e | No primary emergency vent device present |  | Install 3" UL-listed emergency vent device exhausting outdoors |  |  |  |  | 300 | 60 | 16 | 800 | 1160
 | 8c | Low melting temperature metals used in piping system |  | Replace brass valves with steel |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | 8d | Evidence of Teflon tape being used to seal joints |  | Reseal fittings with pipe sealant |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | 9d/10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 400 | 80 | 8 | 400 | 880
 | 10g | No fire safety valve installed on fuel distribution lines |  | Install fire safety valves on fuel distribution lines |  |  |  |  | 400 | 80 | 8 | 400 | 880
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 5504
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 8400
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2g | Tank does not meet spacing requirements to adjacent tanks |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2o | No fire extinguisher in vicinity of AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 4d | Coating failure |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 9g | Level gauge not readable during transfer |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 11e | No grounding system installed |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 |  | Tank rated for aboveground use is encased in concrete |  | Abandon tank use and replace with UL-listed alternative |  |  |  |  | 5000 | 1000 | 48 | 2400 | 8400
 | Comments: TANK NEEDS TO BE REPLACED  This tank was not designed to be buried.  It is recommended that a new tank is be installed, and a Formal External Inspection should be performed prior to putting new tank into service. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 8400
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 8400
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2g | Tank does not meet spacing requirements to adjacent tanks |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2o | No fire extinguisher in vicinity of AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 4d | Coating failure |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 9g | Level gauge not readable during transfer |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 11e | No grounding system installed |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 |  | Tank rated for aboveground use is encased in concrete |  | Abandon tank use and replace with UL-listed alternative |  |  |  |  | 5000 | 1000 | 48 | 2400 | 8400
 | Comments: TANK NEEDS TO BE REPLACED   This tank was not designed to be buried.  It is recommended that a new tank is be installed, and a Formal External Inspection should be performed prior to putting new tank into service. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 8400
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3508
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2g | Tank does not meet spacing requirements to adjacent buildings |  | Relocate tank a minimum of 5' away from building |  |  |  |  | 100 | 20 | 16 | 800 | 920
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4d | Coating failure |  | Prepare surface and repaint |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 8c | Low melting temperature metals used in piping system |  | Replace brass valves with steel |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 11e | Grounding wire loose |  | Re-secure grounding wire to tank |  |  |  |  | 0 | 0 | 2 | 100 | 100
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3508
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 11800
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2g | Tank does not meet spacing requirements to adjacent tanks |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2j | No fuel capacity labeled on AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2o | No fire extinguisher in vicinity of AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2p | No fire diamond placards |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2s | Holes in walking platform present fall risk to workers |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 3f | Ladder missing anchoring bolt |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 5b | Tank supports taller than 12" are not fireproofed |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7d | No normal vent device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7e | No primary emergency vent present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 8h | Piping coating failure |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 9d/10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 10d | No oil safety valve on lines exiting the bottom of the tank under suction |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 |  | Tank can not be retrofitted to comply with applicable standards (see notes) |  | Replace tank with suitable UL-142 listed tank |  |  |  |  | 7000 | 1400 | 48 | 2400 | 10800
 |  | Upon installation of new tank a Formal External Inspection is required |  | Perform a formal external inspection on newly installed tank |  |  |  |  | 0 | 0 | 20 | 1000 | 1000
 | Comments: TANK NEEDS TO BE REPLACED  This tank does not have a primary emergency vent or a port capable of providing adequate emergency venting capacity.  This tank not adequately vented, and is therefore not suited for continued use.  It is recommended that a new tank is be installed, and a Formal External Inspection should be performed prior to putting new tank into service. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 11800
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 11800
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2g | Tank does not meet spacing requirements to adjacent tanks |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2j | No fuel capacity labeled on AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2o | No fire extinguisher in vicinity of AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2p | No fire diamond placards |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2s | Holes in walking platform present fall risk to workers |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 3f | Ladder missing anchoring bolt |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 5b | Tank supports taller than 12" are not fireproofed |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7d | No normal vent device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7e | No primary emergency vent present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 8h | Piping coating failure |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 9d/10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 10d | No oil safety valve on lines exiting the bottom of the tank under suction |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 |  | Tank can not be retrofitted to comply with applicable standards (see notes) |  | Replace tank with suitable UL-142 listed tank |  |  |  |  | 7000 | 1400 | 48 | 2400 | 10800
 |  | Upon installation of new tank a Formal External Inspection is required |  | Perform a formal external inspection on newly installed tank |  |  |  |  | 0 | 0 | 20 | 1000 | 1000
 | Comments: TANK NEEDS TO BE REPLACED  This tank does not have a primary emergency vent or a port capable of providing adequate emergency venting capacity.  This tank not adequately vented, and is therefore not suited for continued use.  It is recommended that a new tank is be installed, and a Formal External Inspection should be performed prior to putting new tank into service. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 11800
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 840
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2g | Tank does not meet spacing requirements to adjacent tanks |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2j | No fuel capacity labeled on AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2o | No fire extinguisher in vicinity of AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2p | No fire diamond placards |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2v | Tank out of service |  | Drain tank, remove piping, drill quarter inch hole in cap and schedule for removal |  |  |  |  | 200 | 40 | 12 | 600 | 840
 | Comments:  Tank is currently out of service. This tank was designed as a pressure vessel, and is not intended for current use. Tank should be replaced or reinspected according to pressure vessel standards |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 840
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 1248
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2g | Tank does not meet spacing requirements to adjacent tanks |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 5b | Tank supports taller than 12" are not fireproofed |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7d | No normal vent device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7e | No primary emergency vent device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 11e | No grounding system installed |  |  |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: This tank appears to be an in-process tank and therefore would not fall under the jurisdiction of NFPA 30. If this tank is not in-process the existing manway should be utilized as a long-bolt manway emergency vent device. Refer to UL 142 Section 8.8 for manway requirements |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 1248
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 1248
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2g | Tank does not meet spacing requirements to adjacent tanks |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 5b | Tank supports taller than 12" are not fireproofed |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7d | No normal vent device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7e | No primary emergency vent device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 11e | No grounding system installed |  |  |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: This tank appears to be an in-process tank and therefore would not fall under the jurisdiction of NFPA 30. If this tank is not in-process the existing manway should be utilized as a long-bolt manway emergency vent device. Refer to UL 142 Section 8.8 for manway requirements |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 1248
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 9308
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 5b | Tank supports taller than 12" are not fireproofed |  | Install fireproofing on tank supports |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 7d | Normal vent device too small |  | Install 2" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 7e | No primary emergency vent device present |  | Install 4" UL-listed emergency vent device exhausting outdoors |  |  |  |  | 300 | 60 | 16 | 800 | 1160
 | 8c | Low melting temperature metals used in piping system |  | Replace copper piping and bronze valves with steel |  |  |  |  | 800 | 160 | 16 | 800 | 1760
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | 9i | No overfill alarm or overfill shutoff valve installed |  | Install overfill alarm and overfill shutoff valve initiating at 90% and 95% capacities |  |  |  |  | 1500 | 300 | 16 | 800 | 2600
 | 10d | No oil safety valve installed on lines exiting the bottom of the tank under suction |  | Install oil safety valve on line exiting the bottom of the tank |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 9308
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 2544
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4d | Coating failure |  | Prepare surface and repaint (Including piping) |  |  |  |  | 300 | 60 | 8 | 400 | 760
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 8c | Low melting temperature metals used in piping system |  | Replace brass valves with steel |  |  |  |  | 100 | 20 | 8 | 400 | 520
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 2544
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 2240
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 3c | No filling platform present |  | Install permanent filling platform |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | 7e | Primary emergency vent device not function/ not UL-rated |  | Replace existing manway cover and install long-bolt manway for emergency venting |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | Comments: Ensure manway bolts are 1/2" diameter, not threaded in the middles, allow 1-1/2" of travel. Ensure manway is properly labeled and that a gasket is installed between the cover and the tank. Ensure a 2" normal vent is reinstalled on the tank after removing it from the manway cover. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 2240
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 124
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 |  | Tank contents not governed by NFPA 30 |  | Recommended Repair |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | Comments: Tank is used to collect a mixture of oil/water from an air compressor blowdown. Unable to verify that contents of tank are governed by NFPA30 (due to ignitability of material). It is suggested that tank owner verify the physical properties of the mixture and reinspect the tank to appropriate standard |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 124
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 2328
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2g | Tank does not meet spacing requirements to adjacent buildings |  | Relocate tank a minimum of 5' away from building |  |  |  |  | 100 | 20 | 16 | 800 | 920
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 7c | Plastic/rubber used to close tank opening |  | Replace plastic/rubber cap with steel |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 2328
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 5008
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4a | Tank not protected from vehicular impact |  | Install vehicle protection |  |  |  |  | 2000 | 400 | 16 | 800 | 3200
 | 7g | Tank interstice vented to the atmosphere |  | Remove normal vent device from tank interstice and replace with steel cap |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 9i | Overfill alarm does not pass self test |  | Service overfill alarm |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 5008
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 4128
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4a | Tank not protected from vehicular impact |  | Install vehicle protection |  |  |  |  | 2000 | 400 | 16 | 800 | 3200
 | 7c | Plastic cap used for venting |  | Replace plastic cap with steel vent device |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 7d | Fill size exceeds vent size |  | Reduce fill size to 1-1/2" |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 4128
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 2164
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 7e/f | No primary or secondary emergency vent devices present |  | Replace existing normal vent devices with UL-listed emergency vent devices |  |  |  |  | 400 | 80 | 8 | 400 | 880
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: Ensure that a 2" normal vent device is installed when the existing vent it replaced, or that the vent port is labeled as "Emergency Vent" |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 2164
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3704
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2g | Tank does not meet spacing requirements to adjacent buildings |  | Relocate tank a minimum of 5' away from building |  |  |  |  | 100 | 20 | 16 | 800 | 920
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4d | Coating failure |  | Prepare surface and repaint |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 7d | Normal vent device too small |  | Install 2" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 7e | No primary emergency vent device present |  | Install 3" UL-listed emergency vent device |  |  |  |  | 300 | 60 | 16 | 800 | 1160
 | 7f | No secondary emergency device present |  | Install 3" UL-listed emergency vent device on interstice |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | Comments: If tank is listed as "closed top diked generator base tank" then a secondary emergency vent does not need to be installed |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3704
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 2468
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 7c | Plastic cap used for venting |  | Replace plastic cap with steel vent device |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 7d | Fill size exceeds vent size |  | Reduce fill size to 1-1/2" |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 7f | No secondary emergency device present |  | Install 3" UL-listed emergency vent device on interstice |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 8c | Generator fuel hose deteriorating |  | Replace exiting hose with fuel-rated hose |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: If tank is listed as "closed top diked generator base tank" then a secondary emergency vent does not need to be installed |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 2468
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3552
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 7c | Plastic used to close tank openings |  | Replace plastic plug with steel |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 8c | Low melting temperature metals used in piping system |  | Replace brass valves with steel |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | 8h | Piping coating failure |  | Prepare surface and repaint piping |  |  |  |  | 100 | 20 | 16 | 800 | 920
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3552
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 840
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  |  |  |  |  |  | 0 | 0 | 2 | 0 | 0
 | 2p | No fire diamond placards |  |  |  |  |  |  | 0 | 0 | 2 | 0 | 0
 | 4d | Coating failure |  |  |  |  |  |  | 0 | 0 | 8 | 0 | 0
 | 7e | Primary emergency vent gasket in need of replacement |  |  |  |  |  |  | 0 | 0 | 2 | 0 | 0
 | 9i | ATGS does not pass self-test |  |  |  |  |  |  | 0 | 0 | 4 | 0 | 0
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  |  |  |  |  |  | 0 | 0 | 4 | 0 | 0
 | 2v | Tank out of service |  | Drain tank, remove piping, drill quarter inch hole in cap and schedule for removal |  |  |  |  | 200 | 40 | 12 | 600 | 840
 | Comments:  Tank is currently out of service. If the tank is to be put back into service the above recommendations should be addressed prior to refilling the tank and an FEI should be performed before the tank is used. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 840
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 1224
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 3d | Evidence of chronic spillage due to filling setup |  | Develop procedures to prevent spillage due to filling |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7c | Plastic used to close tank openings |  | Replace plastic plug with steel |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 1224
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 16404
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 7b | Vent piping used for other purposes than venting |  |  |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 7e | No primary emergency vent device present |  |  |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 8d | Evidence of Teflon tape being used to seal joints |  |  |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | 9i | No overfill alarm or overfill shutoff valve installed |  |  |  |  |  |  | 1500 | 300 | 16 | 800 | 2600
 | 10g | No fire safety valve installed on fuel distribution lines |  |  |  |  |  |  | 400 | 80 | 8 | 400 | 880
 |  | Tank can not be retrofitted to comply with applicable standards (see notes) |  | Replace tank with suitable UL-142 listed tank |  |  |  |  | 7000 | 1400 | 48 | 2400 | 10800
 |  | Upon installation of new tank a Formal External Inspection is required |  | Perform a formal external inspection on newly installed tank |  |  |  |  | 0 | 0 | 20 | 1000 | 1000
 | Comments: TANK NEEDS TO BE REPLACED  This tank does not have a primary emergency vent or a port capable of providing adequate emergency venting capacity.  This tank not adequately vented, and is therefore not suited for continued use.  It is recommended that a new tank is be installed, and a Formal External Inspection should be performed prior to putting new tank into service. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 16404
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 10200
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 4a | Tank not protected from vehicular impact |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7d | Normal vent device too small/ not proper type/ not proper height/ exhaust inside |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7e | No primary emergency vent device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 8c | Low melting temperature metals used in piping system |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 8f | Piping not protected from potential damage |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 9g | Level gauge not readable during transfer |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 9i | No overfill alarm or overfill shutoff valve installed |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 11e | No grounding system installed |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 |  | Tank can not be retrofitted to comply with applicable standards (see notes) |  | Replace tank with suitable UL-142 listed tank |  |  |  |  | 7000 | 1400 | 16 | 800 | 9200
 |  | Upon installation of new tank a Formal External Inspection is required |  | Perform a formal external inspection on newly installed tank |  |  |  |  | 0 | 0 | 20 | 1000 | 1000
 | Comments: TANK NEEDS TO BE REPLACED  This tank does not have a primary emergency vent or a port capable of providing adequate emergency venting capacity.  This tank not adequately vented, and is therefore not suited for continued use.  It is recommended that a new tank is be installed, and a Formal External Inspection should be performed prior to putting new tank into service. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 10200
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3812
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 3c | Tank filling platform does not have handrails |  | Install handrails on filling platform or ensure that employee tie-off procedures are being utilized |  |  |  |  | 1000 | 200 | 16 | 800 | 2000
 | 4d | Coating failure |  | Prepare surface and repaint |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 9g | Tank level gauge in need of repair |  | Repair/replace level gauge so that it is readable during transfer |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 9 | Tank drain not locked or capped to prevent unauthorized draining |  | [NAME] or lock drain valve |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3812
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3584
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond or fuel contents placards |  | Install fire diamond and fuel contents placards |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 4a | Tank not protected from vehicular impact |  | Install vehicle protection |  |  |  |  | 2000 | 400 | 16 | 800 | 3200
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3584
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 1968
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond or fuel contents placards |  | Install fire diamond and fuel contents placards |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 4d | Coating failure |  | Prepare surface and repaint |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 7c | Plastic used to close tank openings |  | Replace plastic plug with steel |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 1968
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 4248
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | Fire diamond not properly labeled |  | Install numbers on fire diamond |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4a | Tank not protected from vehicular impact |  | Install vehicle protection |  |  |  |  | 2000 | 400 | 16 | 800 | 3200
 | 4d | Coating failure |  | Prepare surface and repaint |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 4248
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3604
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4d | Coating failure |  | Prepare surface and repaint |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 8c | Low melting temperature metals used in piping system |  | Replace brass valves with steel |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | 10a | No isolation valve located on distribution line at tank |  | Install steel isolation valve on distribution line at tank |  |  |  |  | 100 | 20 | 8 | 400 | 520
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3604
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 1260
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 4d | Coating failure |  | Prepare surface and repaint |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 1260
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 1248
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  |  |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2o | No fire extinguisher in vicinity of AST |  |  |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  |  |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2v | Tank out of service |  | Drain tank, remove piping, drill quarter inch hole in cap and schedule for removal |  |  |  |  | 200 | 40 | 12 | 600 | 840
 | Comments:  Tank is currently out of service. If the tank is to be put back into service the above recommendations should be addressed prior to refilling the tank and an FEI should be performed before the tank is used. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 1248
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 6400
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2p | No fire diamond placards |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 4d | Coating failure |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7d | Normal vent device too small |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7f | No secondary emergency device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7g | Tank interstice vented to the atmosphere |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 9g | Level gauge not readable during transfer |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 11c | Potential ignition source located near tank |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 11e | No grounding system installed |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 6c | Tank containment compromised/ creates a spill risk |  | Replace tank with suitable UL-142 listed tank |  |  |  |  | 3500 | 700 | 24 | 1200 | 5400
 |  | Upon installation of new tank a Formal External Inspection is required |  | Perform a formal external inspection on newly installed tank |  |  |  |  | 0 | 0 | 20 | 1000 | 1000
 | Comments: TANK NEEDS TO BE REPLACED Tank interstice is filled with water and is unable to be repaired. Water in interstice encourages corrosion and could lead to a product release, tank is not suited for continued use |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 6400
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 6400
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2p | No fire diamond placards |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 4d | Coating failure |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7d | Normal vent device too small |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7f | No secondary emergency device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7g | Tank interstice vented to the atmosphere |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 9g | Level gauge not readable during transfer |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 11e | No grounding system installed |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 6c | Tank containment compromised/ creates a spill risk |  | Replace tank with suitable UL-142 listed tank |  |  |  |  | 3500 | 700 | 24 | 1200 | 5400
 |  | Upon installation of new tank a Formal External Inspection is required |  | Perform a formal external inspection on newly installed tank |  |  |  |  | 0 | 0 | 20 | 1000 | 1000
 | Comments: TANK NEEDS TO BE REPLACED Tank interstice is filled with water and is unable to be repaired. Water in interstice encourages corrosion and could lead to a product release, tank is not suited for continued use |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 6400
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3468
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 8c | Low melting temperature metals used in piping system |  | Replace brass valves with steel |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 8i | Possible leak identified in piping system |  | Repair/replace leaking fittings |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 11e | Grounding wire not connected |  | Reattach grounding wire and secure from potential foot-traffic damage |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3468
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3528
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 8c | Low melting temperature metals used in piping system |  | Replace brass valves with steel |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 8e | Piping appears to be in need of additional support |  | Install piping supports between tank and building |  |  |  |  | 100 | 20 | 8 | 400 | 520
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 11e | Grounding wire loose |  | Reattach grounding wire and secure from potential foot-traffic damage |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3528
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3052
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 7c | Plastic used to close tank openings |  | Replace plastic plug with steel |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 8e | Piping appears to be in need of additional support |  | Install piping supports between tank and building |  |  |  |  | 100 | 20 | 8 | 400 | 520
 | 8i | Possible leak identified in piping system |  | Repair/replace leaking fittings |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3052
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3948
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4d | Coating failure |  | Prepare surface and repaint |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 8c | Low melting temperature metals used in piping system |  | Replace brass valves with steel |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3948
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 2768
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4d | Coating failure |  | Prepare surface and repaint |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | 9g | ATGS system in need of maintenance |  | Service ATGS system |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 2768
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 5988
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 6c | Concrete containment integrity failure |  | Repair concrete in accordance with manufacturer's recommendations |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 8c | Low melting temperature metals used in piping system |  | Replace brass valves with steel |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | 9i | No overfill shutoff valve present |  | Install overfill shutoff valve initiating at 95% fill capacity |  |  |  |  | 1000 | 200 | 8 | 400 | 1600
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 5988
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 5304
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4d | Coating failure |  | Prepare surface and repaint |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 4i | Potential water identified in tank interstice |  | Remove water from interstice and determine entry point |  |  |  |  | 100 | 20 | 8 | 400 | 520
 | 6a | Tank interstice monitor device not connected |  | Reconnect interstice monitor |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | 7c | Plastic used to close tank openings |  | Replace plastic plug with steel |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 8c | Low melting temperature metals used in piping system |  | Replace brass valves with steel |  |  |  |  | 100 | 20 | 8 | 400 | 520
 | 8h | Piping coating failure |  | Prepare surface and repaint piping |  |  |  |  | 100 | 20 | 16 | 800 | 920
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 5304
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 4828
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4d | Coating failure |  | Prepare surface and repaint |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 7b | Vent piping used for other purpose than venting |  | Remove level monitor from emergency vent port |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | 8c | Low melting temperature metals used in piping system |  | Replace brass valves with steel |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 8i | Possible leak identified in piping system |  | Repair/replace leaking fittings |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | 10a | No isolation valve located on distribution line at tank |  | Install steel isolation valve on distribution line at tank |  |  |  |  | 100 | 20 | 8 | 400 | 520
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 11e | Grounding wire loose |  | Reattach grounding wire and secure from potential foot-traffic damage |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 4828
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 5288
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2g | Tank does not meet spacing requirements to adjacent buildings |  | Relocate tank a minimum of 5' away from building |  |  |  |  | 100 | 20 | 16 | 800 | 920
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4d | Coating failure |  | Prepare surface and repaint |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 7c | Plastic used to close tank openings |  | Replace plastic plug with steel |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 8c | Low melting temperature metals used in piping system |  | Replace brass valves with steel |  |  |  |  | 100 | 20 | 8 | 400 | 520
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 5288
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3144
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 8c | Low melting temperature metals used in piping system |  | Replace brass valves with steel |  |  |  |  | 100 | 20 | 8 | 400 | 520
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 10g | Insufficient number of fire valves installed |  | Install fire safety valve on distribution lines where piping enters building |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3144
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 1948
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 7c | Plastic used to close tank openings |  | Replace plastic plug with steel |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 9c | No check valve installed at remote fill location |  | Install check valve at remote fill location |  |  |  |  | 100 | 20 | 8 | 400 | 520
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 1948
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 840
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2o | No fire extinguisher in vicinity of AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2p | No fire diamond placards |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 4d | Coating failure |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 4i | Open penetration allowing rain water into tank |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7c | Plastic used to close tank openings |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2v | Tank out of service |  | Drain tank, remove piping, drill quarter inch hole in cap and schedule for removal |  |  |  |  | 200 | 40 | 12 | 600 | 840
 | Comments:  Tank is currently out of service. If the tank is to be put back into service the above recommendations should be addressed prior to refilling the tank and an FEI should be performed before the tank is used. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 840
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 1480
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2o | No fire extinguisher in vicinity of AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2p | No fire diamond placards |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 4d | Coating failure |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7c | Plastic used to close tank openings |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7d | No normal vent device installed |  |  |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 2v | Tank out of service |  | Drain tank, remove piping, drill quarter inch hole in cap and schedule for removal |  |  |  |  | 200 | 40 | 12 | 600 | 840
 | Comments:  Tank is currently out of service. If the tank is to be put back into service the above recommendations should be addressed prior to refilling the tank and an FEI should be performed before the tank is used. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 1480
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3088
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 3d | Fill platform presents a spill risk |  | Permanently install fill steps so that they are centered on fill port |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 4d | Coating failure |  | Prepare surface and repaint |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 7e/f | Emergency vent devices in need of servicing |  | Service or replace emergency vent devices as necessary |  |  |  |  | 400 | 80 | 8 | 400 | 880
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3088
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 2504
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 4d | Coating failure |  | Prepare surface and repaint |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 10g | No fire safety valve installed on fuel distribution lines |  | Install fire safety valves on fuel distribution lines |  |  |  |  | 400 | 80 | 8 | 400 | 880
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 2504
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 2728
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 4d | Coating failure |  | Prepare surface and repaint |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 7c | Plastic used to close tank openings |  | Replace plastic plug with steel |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 10g | No fire safety valve installed on fuel distribution lines |  | Install fire safety valves on fuel distribution lines |  |  |  |  | 400 | 80 | 8 | 400 | 880
 | 10 | Fuel return line not capped |  | Install cap or lock return line to prevent unauthorized opening |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | Comments: Verify that fill alarm can be heard at fill location. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 2728
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 1212
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4d | Coating failure |  | Prepare surface and repaint |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 7c | Plastic used to close tank openings |  | Replace plastic plug with steel |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 7g | Tank interstice has open penetration |  | Drain any liquid in the interstice and cap opening with steel |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 1212
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3408
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 7c | Plastic used to close tank openings |  | Replace plastic plug with steel |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 9g | No level gauge installed on tank |  | Install level gauge that is readable during transfer |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | 9i | No overfill alarm or overfill shutoff valve installed |  | Install overfill alarm and overfill shutoff valve initiating at 90% and 95% capacities |  |  |  |  | 1500 | 300 | 16 | 800 | 2600
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3408
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 988
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4d | Coating failure |  | Prepare surface and repaint |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 7c | Plastic used to close tank openings |  | Replace plastic plug with steel |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 988
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 5612
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2g | Tank does not meet spacing requirements to adjacent buildings |  | Relocate tank a minimum of 5' away from building |  |  |  |  | 1000 | 200 | 32 | 1600 | 2800
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 7c | Plastic used to close tank openings |  | Replace plastic plug with steel |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 9i | Error with ATGS system |  | Inspect/repair ATGS system |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 9h | Tank filling method promotes spilling and presents injury risk to filling personnel |  | Install alternate filling method |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 5612
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3072
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4d | Coating failure |  | Prepare surface and repaint (including piping) |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 7c | Plastic used to close tank openings |  | Replace plastic plug with steel |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 8d | Evidence of Teflon tape being used to seal joints |  | Reseal fittings with pipe sealant |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3072
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 5772
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2g | Tank does not meet spacing requirements to adjacent buildings |  | Relocate tank a minimum of 5' away from building |  |  |  |  | 1000 | 200 | 32 | 1600 | 2800
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 7c | Plastic used to close tank openings |  | Replace plastic plug with steel |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 8c | Low melting temperature metals used in piping system |  | Replace copper piping and brass valves with steel |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 5772
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 6608
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4a | Tank not protected from vehicular impact |  | Install vehicle protection |  |  |  |  | 2000 | 400 | 16 | 800 | 3200
 | 7c | Plastic used to close tank openings |  | Replace plastic plug with steel |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 9g | No level gauge installed on tank |  | Install level gauge that is readable during transfer |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | 9i | No overfill alarm or overfill shutoff valve installed |  | Install overfill alarm and overfill shutoff valve initiating at 90% and 95% capacities |  |  |  |  | 1500 | 300 | 16 | 800 | 2600
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 6608
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 5124
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4d | Coating failure |  | Prepare surface and repaint (including piping) |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 7c | Plastic used to close tank openings |  | Replace plastic plug with steel |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 9i | No overfill shutoff valve installed |  | Install overfill shutoff valve initiating at 95% capacity |  |  |  |  | 1000 | 200 | 8 | 400 | 1600
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 5124
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 4564
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4d | Coating failure |  | Prepare surface and repaint |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 7c | Plastic used to close tank openings |  | Replace plastic plug with steel |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 9i | No overfill shutoff valve installed |  | Install overfill shutoff valve initiating at 95% capacity |  |  |  |  | 1000 | 200 | 8 | 400 | 1600
 | 11d | Electrical conduit in need of additional support |  | Install additional support for electrical conduit |  |  |  |  | 100 | 20 | 8 | 400 | 520
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 4564
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 7664
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2g | Tank does not meet spacing requirements to adjacent buildings |  | Relocate tank a minimum of 5' away from building |  |  |  |  | 1000 | 200 | 32 | 1600 | 2800
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4d | Coating failure |  | Prepare surface and repaint |  |  |  |  | 100 | 20 | 8 | 400 | 520
 | 7e | No primary emergency vent device present |  | Install 3" UL-listed emergency vent device |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 7h | Vent opening discharges less than 5' from building opening |  | Relocate vent exhaust to a minimum of 5' from any building opening |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 8i | Possible leak identified in piping system |  | Repair/replace leaking fittings |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | 9 | Fuel supply piping leads to abandoned tank |  | Remove and cap fuel supply piping |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | 9g | Tank level gauge in need of repair |  | Repair/replace level gauge so that it is readable during transfer |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 10a | No isolation valve located on distribution line at tank |  | Install steel isolation valve on distribution line at tank |  |  |  |  | 100 | 20 | 8 | 400 | 520
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 7664
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3684
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2p | No fire diamond or fuel contents placards |  | Install fire diamond and fuel contents placards |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 7e | Primary emergency vent exhausts indoors |  | Relocate emergency vent device to exhaust outdoors |  |  |  |  | 200 | 40 | 16 | 800 | 1040
 | 8d | Evidence of Teflon tape being used to seal joints |  | Reseal fittings with pipe sealant |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | 10a | No isolation valve located on distribution line at tank |  | Install steel isolation valve on distribution line at tank |  |  |  |  | 100 | 20 | 8 | 400 | 520
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3684
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 5560
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2o | No fire extinguisher in vicinity of AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2p | No fire diamond or fuel contents placards |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7d | Normal vent device too small |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7e | No primary emergency vent device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 8g | Possible fuel leak from filter |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 8i | Possible leak identified in piping system |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 10a | No isolation valve located on distribution line at tank |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 9d/10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 10g | No fire safety valve installed on fuel distribution lines |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 11e | No grounding system installed |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 |  | Tank can not be retrofitted to comply with applicable standards (see notes) |  | Replace tank with suitable UL-142 listed tank |  |  |  |  | 2800 | 560 | 24 | 1200 | 4560
 |  | Upon installation of new tank a Formal External Inspection is required |  | Perform a formal external inspection on newly installed tank |  |  |  |  | 0 | 0 | 20 | 1000 | 1000
 | Comments: TANK NEEDS TO BE REPLACED  This tank does not have a primary emergency vent or a port capable of providing adequate emergency venting capacity.  This tank not adequately vented, and is therefore not suited for continued use.  It is recommended that a new tank is be installed, and a Formal External Inspection should be performed prior to putting new tank into service. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 5560
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 10588
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  |  |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2p | No fire diamond placards |  |  |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 3c | No filling platform present |  |  |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | 6h | Debris located inside containment |  |  |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | 7d | Vent piping used for other purpose than venting |  |  |  |  |  |  | 200 | 40 | 16 | 800 | 1040
 | 7e | No primary emergency vent device present |  |  |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 11e | No grounding system installed |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 |  | Tank can not be retrofitted to comply with applicable standards (see notes) |  | Replace tank with suitable UL-142 listed tank |  |  |  |  | 4500 | 900 | 16 | 800 | 6200
 |  | Upon installation of new tank a Formal External Inspection is required |  | Perform a formal external inspection on newly installed tank |  |  |  |  | 0 | 0 | 20 | 1000 | 1000
 | Comments: TANK NEEDS TO BE REPLACED  This tank does not have a primary emergency vent or a port capable of providing adequate emergency venting capacity.  This tank not adequately vented, and is therefore not suited for continued use.  It is recommended that a new tank is be installed, and a Formal External Inspection should be performed prior to putting new tank into service. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 10588
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 7200
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2p | No fire diamond placards |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 3c | No filling platform present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 6h | Debris located inside containment |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7d | Vent piping used for other purpose than venting |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7e | No primary emergency vent device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 11e | No grounding system installed |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 |  | Tank can not be retrofitted to comply with applicable standards (see notes) |  | Replace tank with suitable UL-142 listed tank |  |  |  |  | 4500 | 900 | 16 | 800 | 6200
 |  | Upon installation of new tank a Formal External Inspection is required |  | Perform a formal external inspection on newly installed tank |  |  |  |  | 0 | 0 | 20 | 1000 | 1000
 | Comments: TANK NEEDS TO BE REPLACED  This tank does not have a primary emergency vent or a port capable of providing adequate emergency venting capacity.  This tank not adequately vented, and is therefore not suited for continued use.  It is recommended that a new tank is be installed, and a Formal External Inspection should be performed prior to putting new tank into service. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 7200
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 4648
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 3d | Tank filling steps not centered on filling port |  | [NAME] filling steps to be centered on filling port |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 4d | Coating failure |  | Prepare surface and repaint |  |  |  |  | 100 | 20 | 8 | 400 | 520
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 9i | No overfill shutoff valve installed |  | Install overfill shutoff valve initiating at 95% capacity |  |  |  |  | 1000 | 200 | 8 | 400 | 1600
 | 10a | No isolation valve located on distribution line at tank |  | Install steel isolation valve on distribution line at tank |  |  |  |  | 100 | 20 | 8 | 400 | 520
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 4648
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3928
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond or fuel contents placards |  | Install fire diamond and fuel contents placards |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 7e | No primary emergency vent device present |  | Install 3" UL-listed emergency vent device exhausting outdoors |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 8c | Low melting temperature metals used in piping system |  | Replace brass valves with steel |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 8i | Possible leak identified in piping system |  | Repair/replace leaking fittings |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 10g | No fire safety valve installed on fuel distribution lines |  | Install fire safety valves on fuel distribution lines |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3928
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 5632
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 3c | No filling platform present |  | Install permanent filling platform |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | 7c | Plastic used to close tank openings |  | Replace plastic plug with steel |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 7e/f | Emergency vents device exhausts indoors |  | Relocate emergency vent devices to exhaust outdoors |  |  |  |  | 500 | 100 | 16 | 800 | 1400
 | 7g | Tank interstice vented to the atmosphere |  | Remove normal vent device from tank interstice and replace with steel cap |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 10a | No isolation valve located on distribution line at tank |  | Install steel isolation valve on distribution line at tank |  |  |  |  | 100 | 20 | 8 | 400 | 520
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 10g | No fire safety valve installed on fuel distribution lines |  | Install fire safety valves on fuel distribution lines |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 5632
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 5948
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 3c | No filling platform present |  | Install permanent filling platform |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | 4d | Coating failure |  | Prepare surface and repaint (including piping) |  |  |  |  | 100 | 20 | 8 | 400 | 520
 | 7g | Tank interstice vented to the atmosphere |  | Remove normal vent device from tank interstice and replace with steel cap |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 8c | Low melting temperature metals used in piping system |  | Replace plastic piping and bronze valves with steel |  |  |  |  | 400 | 80 | 8 | 400 | 880
 | 9i | No overfill alarm or overfill shutoff valve installed |  | Install overfill alarm and overfill shutoff valve initiating at 90% and 95% capacities |  |  |  |  | 1500 | 300 | 16 | 800 | 2600
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 5948
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 4404
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4d | Coating failure |  | Prepare surface and repaint (including piping) |  |  |  |  | 300 | 60 | 16 | 800 | 1160
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 8d | Evidence of Teflon tape being used to seal joints |  | Reseal fittings with pipe sealant |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | 8e | Piping appears to be in need of additional support |  | Install piping supports between tank and building |  |  |  |  | 100 | 20 | 8 | 400 | 520
 | 8f | Piping not protected from potential damage |  | Install additional supports/protection to prevent damage to piping system |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 4404
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 4108
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4d | Coating failure |  | Prepare surface and repaint |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 7e | Primary emergency vent device does not operate freely |  | Repair or replace emergency vent so that it operates freely. Install new gasket if necessary |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 8d | Evidence of Teflon tape being used to seal joints |  | Reseal fittings with pipe sealant |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 4108
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 2624
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4d | Coating failure |  | Prepare surface and repaint |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 10a | No isolation valve located on distribution line at tank |  | Install steel isolation valve on distribution line at tank |  |  |  |  | 100 | 20 | 8 | 400 | 520
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 2624
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 5560
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2o | No fire extinguisher in vicinity of AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2p | No fire diamond placards |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 4a | Tank in need of additional vehicle protection |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 4d | Coating failure |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7c | Plastic used to close tank openings |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7d | Normal vent device too small |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7e | No primary emergency vent device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7f | No secondary emergency vent device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 8h | Fuel hose showing signs of dry rotting |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 11e | No grounding system installed |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 |  | Tank can not be retrofitted to comply with applicable standards (see notes) |  | Replace tank with suitable UL-142 listed tank |  |  |  |  | 2800 | 560 | 24 | 1200 | 4560
 |  | Upon installation of new tank a Formal External Inspection is required |  | Perform a formal external inspection on newly installed tank |  |  |  |  | 0 | 0 | 20 | 1000 | 1000
 | Comments: TANK NEEDS TO BE REPLACED  This tank does not have a secondary emergency vent or a port capable of providing adequate emergency venting capacity.  This tank not adequately vented, and is therefore not suited for continued use.  It is recommended that a new tank is be installed, and a Formal External Inspection should be performed prior to putting new tank into service. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 5560
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 4440
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2o | No fire extinguisher in vicinity of AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2p | No fire diamond placards |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 4a | Tank not protected from vehicular impact |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 4d | Coating failure |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7e | No primary emergency vent device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 11e | No grounding system installed |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 |  | Tank can not be retrofitted to comply with applicable standards (see notes) |  | Replace tank with suitable UL-142 listed tank |  |  |  |  | 2200 | 440 | 16 | 800 | 3440
 |  | Upon installation of new tank a Formal External Inspection is required |  | Perform a formal external inspection on newly installed tank |  |  |  |  | 0 | 0 | 20 | 1000 | 1000
 | Comments: TANK NEEDS TO BE REPLACED  This tank does not have a primary emergency vent or a port capable of providing adequate emergency venting capacity.  This tank not adequately vented, and is therefore not suited for continued use.  It is recommended that a new tank is be installed, and a Formal External Inspection should be performed prior to putting new tank into service. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 4440
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 6948
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4a | Tank not protected from vehicular impact |  | Install vehicle protection |  |  |  |  | 2000 | 400 | 16 | 800 | 3200
 | 4d | Coating failure |  | Prepare surface and repaint |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 7e | No primary emergency vent device present |  | Install 3" UL-listed emergency vent device |  |  |  |  | 300 | 60 | 16 | 800 | 1160
 | 7f | No secondary emergency device present |  | Install 3" UL-listed emergency vent device on interstice |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 7g | Tank interstice vented to the atmosphere |  | Remove normal vent device from tank interstice and replace with steel cap |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: Ensure a 2" vent is installed if the current normal vent device is replaced with an emergency vent |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 6948
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 6384
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 7a | Tank fill/drain port not capped |  | Install vapor-tight cap on disconnectable coupling |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 7e | No primary emergency vent device present |  | Install 6" UL-listed emergency vent device |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 7f | No secondary emergency device present |  | Install 6" UL-listed emergency vent device on interstice |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 8d | Evidence of Teflon tape being used to seal joints |  | Reseal fittings with pipe sealant |  |  |  |  | 50 | 10 | 8 | 400 | 460
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | 9i | No overfill alarm or overfill shutoff valve installed |  | Install overfill alarm and overfill shutoff valve initiating at 90% and 95% capacities |  |  |  |  | 1500 | 300 | 16 | 800 | 2600
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: Ensure a 2" normal vent device is installed if the current vent is removed |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 6384
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 4564
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 7e | No primary emergency vent device present |  | Install 3" UL-listed emergency vent device exhausting outdoors |  |  |  |  | 300 | 60 | 8 | 400 | 760
 | 8f | Piping not protected from potential damage |  | Install additional supports/protection to prevent damage to piping system |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 8h | Piping coating failure |  | Prepare surface and repaint piping |  |  |  |  | 100 | 20 | 8 | 400 | 520
 | 9d/10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 400 | 80 | 8 | 400 | 880
 | 10g | No fire safety valve installed on fuel distribution lines |  | Install fire safety valves on fuel distribution lines |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 4564
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 2028
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4d | Coating failure |  | Prepare surface and repaint |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 7e | No primary emergency vent device present |  | Install 3" UL-listed emergency vent device |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 7f | No secondary emergency device present |  | Install 3" UL-listed emergency vent device on interstice |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 7g | Tank interstice vented to the atmosphere |  | Remove normal vent device from tank interstice and replace with steel cap |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | Comments: Ensure a 2" normal vent device is installed if existing vent is replaced |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 2028
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 2412
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4d | Coating failure |  | Prepare surface and repaint |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 7e | No primary emergency vent device present |  | Install 3" UL-listed emergency vent device |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 7f | No secondary emergency device present |  | Install 3" UL-listed emergency vent device on interstice |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 7g | Tank interstice vented to the atmosphere |  | Remove normal vent device from tank interstice and replace with steel cap |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 9g | Level gauge in need of repair |  | Repair/replace level gauge |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | Comments: Ensure a 2" normal vent device is installed if existing vent is replaced |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 2412
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3960
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2p | No fire diamond placards |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7c | Plastic used to close tank openings |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7d | Normal vent device too small |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7e | No primary emergency vent device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7f | No secondary emergency device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 11e | No grounding system installed |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 |  | Tank can not be retrofitted to comply with applicable standards (see notes) |  | Replace tank with suitable UL-142 listed tank |  |  |  |  | 1800 | 360 | 16 | 800 | 2960
 |  | Upon installation of new tank a Formal External Inspection is required |  | Perform a formal external inspection on newly installed tank |  |  |  |  | 0 | 0 | 20 | 1000 | 1000
 | Comments: TANK NEEDS TO BE REPLACED  This tank does not have a primary emergency vent or a port capable of providing adequate emergency venting capacity.  This tank not adequately vented, and is therefore not suited for continued use.  It is recommended that a new tank is be installed, and a Formal External Inspection should be performed prior to putting new tank into service. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3960
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3828
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2g | Tank does not meet spacing requirements to adjacent buildings |  | Relocate tank a minimum of 2-1/2' away from building |  |  |  |  | 200 | 40 | 16 | 800 | 1040
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 4d | Coating failure |  | Prepare surface and repaint |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 7c | Plastic used to close tank openings |  | Replace plastic plug with steel |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3828
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 5848
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4a | Tank not protected from vehicular impact |  | Install vehicle protection |  |  |  |  | 2000 | 400 | 16 | 800 | 3200
 | 7f | Secondary emergency vent improperly oriented |  | Relocate emergency vent so that it exhaust vertically above tank shell exhausting outside |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 7g | Tank interstice vented to the atmosphere |  | Remove normal vent device from tank interstice and replace with steel cap |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 8c | Low melting temperature metals used in piping system |  | Replace brass valves with steel |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 9d/10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 400 | 80 | 8 | 400 | 880
 | 10a | No isolation valve located on distribution line at tank |  | Install steel isolation valve on distribution line at tank |  |  |  |  | 100 | 20 | 8 | 400 | 520
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 5848
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 9944
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2p | No fire diamond or fuel contents placards |  | Install fire diamond and fuel contents placards |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 4a | Tank not protected from vehicular impact |  | Install vehicle protection |  |  |  |  | 2000 | 400 | 16 | 800 | 3200
 | 5a | Tank supports showing signs of deterioration |  | Repair/replace tank supports |  |  |  |  | 2000 | 400 | 24 | 1200 | 3600
 | 5b | Tank supports taller than 12" are not fireproofed |  | Install fireproofing on steel tank supports |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 9d | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 9g | Level gauge not readable during transfer |  | Install level gauge that is readable during transfer |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 9i | Overfill alarm not audible at fill location |  | Install annunciator at fill location |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 9944
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 5560
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2p | No fire diamond placards |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 6b | No permanent means to prevent overflow into building present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7d | Normal vent pipe manifolded with adjacent tank |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7e | No primary emergency vent device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 8h | Piping coating failure |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 8i | Possible leak identified in piping system |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 9c | No check valve installed at remote fill location |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 9g | Level gauge not readable during transfer |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 9i | No overfill alarm or overfill shutoff valve installed |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 10d | No oil safety valve installed on lines exiting the bottom of the tank under suction |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 11e | No grounding system installed |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 |  | Tank can not be retrofitted to comply with applicable standards (see notes) |  | Replace tank with suitable UL-142 listed tank |  |  |  |  | 2800 | 560 | 24 | 1200 | 4560
 |  | Upon installation of new tank a Formal External Inspection is required |  | Perform a formal external inspection on newly installed tank |  |  |  |  | 0 | 0 | 20 | 1000 | 1000
 | Comments: TANK NEEDS TO BE REPLACED  This tank does not have a primary emergency vent or a port capable of providing adequate emergency venting capacity.  This tank not adequately vented, and is therefore not suited for continued use.  It is recommended that a new tank is be installed, and a Formal External Inspection should be performed prior to putting new tank into service. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 5560
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 2944
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2g | Tank does not meet spacing requirements to adjacent buildings |  | Relocate tank a minimum of 5' away from building |  |  |  |  | 200 | 40 | 16 | 800 | 1040
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 7d | Normal vent device too small |  | Install 4" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 8h | Piping coating failure |  | Prepare surface and repaint piping |  |  |  |  | 100 | 20 | 16 | 800 | 920
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 2944
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 800
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 9c | No anti-siphon valve located on lines extending below maximum fuel fill level (supply) |  | Install anti-siphon valves on fuel supply line extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 800
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 4624
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4d | Coating failure |  | Prepare surface and repaint |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 7f | Secondary emergency vent improperly oriented |  | Relocate emergency vent so that it exhaust vertically above tank shell exhausting outside |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 9i | No overfill alarm or overfill shutoff valve installed |  | Install overfill alarm and overfill shutoff valve initiating at 90% and 95% capacities |  |  |  |  | 1500 | 300 | 16 | 800 | 2600
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 4624
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 668
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2j | No fuel capacity labeled on AST |  | Label accurate tank volume on tank visible from fill location |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 7c/d | Normal vent device too small/ made from plastic |  | Install 2" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 668
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 284
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 284
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 680
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 7d | Normal vent device too small |  | Install 2" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 7f | Secondary emergency vent improperly oriented |  | Relocate emergency vent so that it exhaust vertically above tank shell exhausting outside |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 680
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 4844
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4a | Tank in need of additional vehicle protection |  | Install additional vehicle protection |  |  |  |  | 1500 | 300 | 16 | 800 | 2600
 | 7d | Normal vent device too small |  | Install 2" normal vent device or reduce fill size. Fill size cannot exceed vent diameter |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 7e | Emergency vent gasket in need of replacement |  | Replace emergency vent gaskets |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | 7f | No secondary emergency device present |  | Install 4" UL-listed emergency vent device on interstice |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 4844
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3584
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond or fuel contents placards |  | Install fire diamond and fuel contents placards |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 4a | Tank not protected from vehicular impact |  | Install vehicle protection |  |  |  |  | 2000 | 400 | 16 | 800 | 3200
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3584
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3584
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond or fuel contents placards |  | Install fire diamond and fuel contents placards |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 4a | Tank not protected from vehicular impact |  | Install vehicle protection |  |  |  |  | 2000 | 400 | 16 | 800 | 3200
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3584
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 1640
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2g | Tank does not meet spacing requirements to adjacent tanks |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2j | No fuel capacity labeled on AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2o | No fire extinguisher in vicinity of AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2p | No fire diamond placards |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 4d | Coating failure |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7c | Plastic used to close tank openings |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7d | No normal vent device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7f | No secondary emergency device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7g | Tank interstice vented to the atmosphere/ open penetration on interstice |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | -- | Tank containment showing signs of deformation |  | Repair tank according to manufacturer's recommendations prior to reuse |  |  |  |  | 0 | 0 | 16 | 800 | 800
 | 2v | Tank out of service |  | Drain tank, remove piping, drill quarter inch hole in cap and schedule for removal |  |  |  |  | 200 | 40 | 12 | 600 | 840
 | Comments:  Tank is currently out of service. If the tank is to be put back into service the above recommendations should be addressed prior to refilling the tank and an FEI should be performed before the tank is used. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 1640
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 1640
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2g | Tank does not meet spacing requirements to adjacent tanks |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2j | No fuel capacity labeled on AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2o | No fire extinguisher in vicinity of AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2p | No fire diamond placards |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 4d | Coating failure |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7c | Plastic used to close tank openings |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7d | No normal vent device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7f | No secondary emergency device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7g | Tank interstice vented to the atmosphere |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | -- | Tank containment showing signs of deformation |  | Repair tank according to manufacturer's recommendations prior to reuse |  |  |  |  | 0 | 0 | 16 | 800 | 800
 | 2v | Tank out of service |  | Drain tank, remove piping, drill quarter inch hole in cap and schedule for removal |  |  |  |  | 200 | 40 | 12 | 600 | 840
 | Comments:  Tank is currently out of service. If the tank is to be put back into service the above recommendations should be addressed prior to refilling the tank and an FEI should be performed before the tank is used. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 1640
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 1640
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2g | Tank does not meet spacing requirements to adjacent tanks |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2j | No fuel capacity labeled on AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2o | No fire extinguisher in vicinity of AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2p | No fire diamond placards |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 4d | Coating failure |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7c | Plastic used to close tank openings |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7d | No normal vent device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7f | No secondary emergency device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | -- | Tank containment showing signs of deformation |  | Repair tank according to manufacturer's recommendations prior to reuse |  |  |  |  | 0 | 0 | 16 | 800 | 800
 | 2v | Tank out of service |  | Drain tank, remove piping, drill quarter inch hole in cap and schedule for removal |  |  |  |  | 200 | 40 | 12 | 600 | 840
 | Comments:  Tank is currently out of service. If the tank is to be put back into service the above recommendations should be addressed prior to refilling the tank and an FEI should be performed before the tank is used. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 1640
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 840
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2g | Tank does not meet spacing requirements to adjacent tanks |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2j | No fuel capacity labeled on AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2o | No fire extinguisher in vicinity of AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2p | No fire diamond placards |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 4d | Coating failure |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2v | Tank out of service |  | Drain tank, remove piping, drill quarter inch hole in cap and schedule for removal |  |  |  |  | 200 | 40 | 12 | 600 | 840
 | Comments:  Tank is currently out of service. If the tank is to be put back into service the above recommendations should be addressed prior to refilling the tank and an FEI should be performed before the tank is used. Check tank for water and drain if necessary |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 840
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3324
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4a | Tank not protected from vehicular impact |  | Install vehicle protection |  |  |  |  | 2000 | 400 | 16 | 800 | 3200
 | Comments: Tank fill piping is missing protective cover |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3324
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3744
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4a | Tank not protected from vehicular impact |  | Install vehicle protection |  |  |  |  | 2000 | 400 | 16 | 800 | 3200
 | 7f | Secondary emergency vent improperly oriented |  | Relocate emergency vent so that it exhaust vertically above tank shell exhausting outside |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3744
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3744
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 4a | Tank not protected from vehicular impact |  | Install vehicle protection |  |  |  |  | 2000 | 400 | 16 | 800 | 3200
 | 7f | Secondary emergency vent improperly oriented |  | Relocate emergency vent so that it exhaust vertically above tank shell exhausting outside |  |  |  |  | 50 | 10 | 4 | 200 | 260
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3744
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 5940
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 7d | Normal vent device too small |  | Install 1-1/4" normal vent device exhausting outdoors |  |  |  |  | 250 | 50 | 8 | 400 | 700
 | 7e/f | Emergency vents device exhausts indoors |  | Relocate emergency vent devices to exhaust outdoors |  |  |  |  | 500 | 100 | 16 | 800 | 1400
 | 8c | Low melting temperature metals used in piping system |  | Replace copper piping and bronze valves with steel |  |  |  |  | 800 | 160 | 16 | 800 | 1760
 | 10c | No anti-siphon valve located on lines extending below maximum fuel fill level |  | Install anti-siphon valves on fuel lines extending below maximum fuel fill level |  |  |  |  | 200 | 40 | 4 | 200 | 440
 | 10g | No fire safety valve installed on fuel distribution lines |  | Install fire safety valves on fuel distribution lines |  |  |  |  | 200 | 40 | 8 | 400 | 640
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 5940
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 508
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 7c | Plastic used to close tank fill |  | Replace plastic cap with steel |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 508
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 840
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2g | Tank does not meet spacing requirements to adjacent tanks |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2j | No fuel capacity labeled on AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2o | No fire extinguisher in vicinity of AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2p | No fire diamond placards |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 4d | Coating failure |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7c | Plastic used to close tank openings |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2v | Tank out of service |  | Drain tank, remove piping, drill quarter inch hole in cap and schedule for removal |  |  |  |  | 200 | 40 | 12 | 600 | 840
 | Comments:  Tank is currently out of service. If the tank is to be put back into service the above recommendations should be addressed prior to refilling the tank and an FEI should be performed before the tank is used. Check tank for water and drain if necessary |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 840
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 4808
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond or fuel contents placards |  | Install fire diamond and fuel contents placards |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 3c | No filling platform present |  | Install permanent filling platform |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | 4a | Tank not protected from vehicular impact |  | Install vehicle protection |  |  |  |  | 2000 | 400 | 16 | 800 | 3200
 | 7c | Plastic used to close tank openings |  | Replace plastic plug with steel |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | Comments: Tank was still being installed at time of inspection. Some findings may have been already addressed. Ensure overfill alarm and shutoff devices are installed prior to use |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 4808
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 4484
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 3c | No filling platform present |  | Install permanent filling platform |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | 4a | Tank not protected from vehicular impact |  | Install vehicle protection |  |  |  |  | 2000 | 400 | 16 | 800 | 3200
 | Comments: Tank was still being installed at time of inspection. Some findings may have been already addressed. Ensure overfill alarm and shutoff devices are installed prior to use |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 4484
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 4484
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond placards |  | Install fire diamond placards |  |  |  |  | 20 | 4 | 2 | 100 | 124
 | 3c | No filling platform present |  | Install permanent filling platform |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | 4a | Tank not protected from vehicular impact |  | Install vehicle protection |  |  |  |  | 2000 | 400 | 16 | 800 | 3200
 | Comments: Tank was still being installed at time of inspection. Some findings may have been already addressed. Ensure overfill alarm and shutoff devices are installed prior to use |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 4484
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 3784
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fuel contents placards |  | Install fuel contents placards |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 4a | Tank not protected from vehicular impact |  | Install vehicle protection |  |  |  |  | 2000 | 400 | 16 | 800 | 3200
 | 9i | Overfill shutoff valve not installed |  | Install overfill shutoff valve |  |  |  |  | 0 | 0 | 4 | 200 | 200
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 3784
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 6400
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2g | Tank does not meet spacing requirements to adjacent tanks |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2j | No fuel capacity labeled on AST |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 2p | No fire diamond placards |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7d | Normal vent device too small |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7d | Normal vent pipe manifolded with adjacent tank |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 7e | No primary emergency vent device present |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 8h | Piping coating failure |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 8i | Possible leak identified in piping system |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 9c | No check valve installed at remote fill location |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 9f | Fill piping does  not have a vapor-tight cap |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 9g | Level gauge not readable during transfer |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 9i | No overfill alarm or overfill shutoff valve installed |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 10d | No oil safety valve installed on lines exiting the bottom of the tank under suction |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | 11e | No grounding system installed |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 |  | Tank can not be retrofitted to comply with applicable standards (see notes) |  | Replace tank with suitable UL-142 listed tank |  |  |  |  | 3500 | 700 | 24 | 1200 | 5400
 |  | Upon installation of new tank a Formal External Inspection is required |  | Perform a formal external inspection on newly installed tank |  |  |  |  | 0 | 0 | 20 | 1000 | 1000
 | Comments: TANK NEEDS TO BE REPLACED  This tank does not have a primary emergency vent or a port capable of providing adequate emergency venting capacity.  This tank not adequately vented, and is therefore not suited for continued use.  It is recommended that a new tank is be installed, and a Formal External Inspection should be performed prior to putting new tank into service. |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 6400
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 4584
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond or fuel contents placards |  | Install fire diamond and fuel contents placards |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 4a | Tank not protected from vehicular impact |  | Install vehicle protection |  |  |  |  | 2000 | 400 | 16 | 800 | 3200
 | 11e | No grounding system installed |  | Install permanent grounding system |  |  |  |  | 500 | 100 | 8 | 400 | 1000
 | Comments: Tank was still being installed at time of inspection. Some findings may have been already addressed. Ensure overfill alarm and shutoff devices are installed prior to use |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 4584
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 384
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | 2o | No fire extinguisher in vicinity of AST |  | Install fire extinguisher, Class B |  |  |  |  | 50 | 10 | 2 | 100 | 160
 | 2p | No fire diamond or fuel contents placards |  | Install fire diamond and fuel contents placards |  |  |  |  | 20 | 4 | 4 | 200 | 224
 | 11e | No grounding system installed |  |  |  |  |  |  | 0 | 0 | 0 | 0 | 0
 | Comments: Tank was still being installed at time of inspection. Some findings may have been already addressed. Ensure overfill alarm and shutoff devices are installed prior to use |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 384
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 1000
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | -- | Tank is in-process, pressurized tank |  | Reinspect to applicable pressure vessel standards |  |  |  |  | 0 | 0 | 20 | 1000 | 1000
 | Comments: This tank appears to be an in-process tank and therefore would not fall under the jurisdiction of NFPA 30. Tank system has multiple leaks that should be repaired. The system should be inspected to pressure vessel standards |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 1000
 | AST ID |  | Description |  | Contents |  | Capacity (gal) |  |  | STI Category |  | Date Inspected
 | 0 |  |  |  | #N/A |  | #N/A |  |  |  |  | #N/A |  |  | 6800
 | Inspection Findings and Recommended Repairs |  |  |  |  |  |  |  | Cost Estimate to Repair Findings
 | FIF Part & Section | AST System Inspection Findings |  | Recommended Repair |  |  |  |  | Materials | Indirects | Labor hours | Labor Cost | Totals
 | -- | Container rack system does not conform to UL standards, pertaining to inadequate venting and usage of poly tubing with combustible materials |  | Replace rack system with suitable UL-listed equivalents |  |  |  |  | 5000 | 1000 | 16 | 800 | 6800
 | Comments: |  |  |  |  |  |  | Totals | TOTAL: |  |  |  | 6800