Spreadsheet: kevin_hyatt__19621__Sun Devil Operating Conditions020107
Sheet: Hp Sizing

Sun Devil Compressor Operating Points ( Rev 1 )  01/07/02
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Generic | MFGR
Station |  | SG | Isentr | amb | Ps | Pd | Ts | Compress | Ratio | H | Q | Q | Q | Q | Compr | TRV | Td | [NAME] | BHp | BHp |  | BHp | BHp | Data
& | Elev |  | Exp | °F | (Psig) | (Psig) | °F | ability |  | (feet) | (MMSCFD) | (ACFM) | (MMSCFD) | (ACFM) | [NAME] |  | * | Effcy | Req'd | Req'd | RPM | Avail | Margin | Date
Unit | Feet |  |  |  |  |  |  |  |  |  | Station | Station | New Unit | New Unit | Adiab |  | °F |  | New Unit | Mfgr |  | New Unit | New Unit
BLOOMFIELD | 5580 | 0.595 | 1.29 | 95 | 850 | 1050 | 85 |  |  |  | 525 |  |  |  | 0.83 |  |  | 0.96 |  |  | 8500 |  |  |  | Mars 100-15000 Hp 122°F Match
 |  | 0.595 | 1.29 | 95 | 870 | 1091 | 90 |  |  |  | 551 |  |  |  | 0.83 |  |  | 0.96 |  |  | 8500 |  |  |  | Mars 100-15000 Hp 122°F Match
 |  | 0.595 | 1.29 | 95 | 900 | 1195 | 95 |  |  |  | 575 |  |  |  | 0.83 |  |  | 0.96 |  |  | 8500 |  |  |  | Mars 100-15000 Hp 122°F Match
BISTI | 5798 | 0.595 | 1.29 | 95 | 970 | 1090 | 85 |  |  |  | 1590 |  |  |  | 0.83 |  |  | 0.96 |  | @Motor [NAME] | 0 | 0 |  |  | Rebundle
STANDING ROCK | 6250 | 0.595 | 1.29 | 95 | 976 | 976 | 82 |  |  |  | 0 |  |  |  | 0.83 |  |  | 0.98 |  |  | 8500 |  |  |  | Mars 100-15000 Hp 122°F Match
 |  | 0.595 | 1.29 | 95 | 976 | 976 | 85 |  |  |  | 0 |  |  |  | 0.83 |  |  | 0.98 |  |  | 8500 |  |  |  | Mars 100-15000 Hp 122°F Match
 |  | 0.595 | 1.29 | 95 | 976 | 976 | 88 |  |  |  | 0 |  |  |  | 0.83 |  |  | 0.98 |  |  | 8500 |  |  |  | Mars 100-15000 Hp 122°F Match
GALLUP | 6600 | 0.595 | 1.29 | 95 | 863 | 970 | 82 |  |  |  | 1590 |  |  |  | 0.83 |  |  | 0.96 |  | 5012 | 0 |  |  |  | New Comp
 |  | 0.595 | 1.29 | 95 | 863 | 970 | 0 |  |  |  | 0 |  |  |  | 0.83 |  |  | 0.96 |  | 5347 | 0 |  |  |  | New Comp
 |  | 0.595 | 1.29 | 95 | 863 | 970 | 82 |  |  |  | 1590 |  |  |  | 0.83 |  |  | 0.96 |  | 5836 | 0 |  |  |  | New Comp - LOW HEAD- HI Hp….LIKELY PROB W/ MOTOR CAPABILITY
CS#4 | 7300 | 0.595 | 1.29 | 95 | 830 | 1000 | 78 |  |  |  | 1762 |  |  |  | 0.83 |  |  | 0.98 |  | 5239 | 6100 |  |  |  | TurnDown? / New Bundle
CS#2 | 7450 | 0.595 | 1.29 | 95 | 820 | 1004 | 82 |  |  |  | 1747 |  |  |  | 0.83 |  |  | 0.98 |  | 10742 | 6100 |  |  |  | New Bundle
CS#1 | 5049 | 0.595 | 1.29 | 95 | 672 | 1005 | 85 |  |  |  | 1243 |  |  |  | 0.83 |  |  | 0.98 |  | 11586 | 6100 |  |  |  | New Bundle
CS#3 | 4768 | 0.595 | 1.29 | 95 | 775 | 1004 | 85 |  |  |  | 1758 |  |  |  | 0.83 |  |  | 0.98 |  |  | 6100 |  |  |  | New Bundle
CS#1.5 | 5120 | 0.595 | 1.29 | 95 | 901 | 901 | 75 |  |  |  | 0 |  |  |  | 0.83 |  |  | 0.98 |  | 5365 | 6100 |  |  |  | New Bundle
 |  | 0.595 | 1.29 | 95 | 901 | 901 | 92 |  |  |  | 0 |  |  |  | 0.83 |  |  | 0.98 |  | 5369 | 6100 |  |  |  | New Bundle
 |  | 0.595 | 1.29 | 95 | 901 | 901 | 95 |  |  |  | 0 |  |  |  | 0.83 |  |  | 0.98 |  | 5386 | 6100 |  |  |  | New Bundle
KINGMAN | 2610 | 0.595 | 1.29 | 95 | 895 | 895 | 85 |  |  |  | 0 |  |  |  | 0.83 |  |  | 0.98 |  | 5235 | 6100 |  |  |  | New Bundle
 |  | 0.595 | 1.29 | 95 | 895 | 895 | 92 |  |  |  | 0 |  |  |  | 0.83 |  |  | 0.98 |  | 5326 | 6100 |  |  |  | New Bundle
 |  | 0.595 | 1.29 | 95 | 895 | 895 | 98 |  |  |  | 0 |  |  |  | 0.83 |  |  | 0.98 |  | 5316 | 6100 |  |  |  | New Bundle
 |  | *Note:  When sizing gas coolers add 5°F to the shown gas discharge temp to account for any recycle and possible efficiency issues