Spreadsheet: 18538d25-0073-4cc5-8349-982ba8ce2d49
Sheet: Sheet1

Unnamed: 0 | Unnamed: 1 | Unnamed: 2 | PM | Unnamed: 4 | Unnamed: 5 | Unnamed: 6 | Unnamed: 7 | Unnamed: 8 | Unnamed: 9 | Unnamed: 10 | Unnamed: 11 | Unnamed: 12 | Unnamed: 13 | Unnamed: 14 | Unnamed: 15 | Unnamed: 16 | Unnamed: 17 | Unnamed: 18 | Unnamed: 19 | Unnamed: 20 | Unnamed: 21 | Unnamed: 22 | Unnamed: 23 | Unnamed: 24 | Unnamed: 25 | Unnamed: 26
AIRS | Facility ID | Name | 2006 | 2007 | 2008 | avg
003 |  | Coal.  P101 - 106
 |  |  | 2.09 | 2.15 | 2.15 | 2.13
004 |  | Ash.  P301a-d, P302a-d; P303a-b
 |  |  | 8.91 | 10.62 | 10.62 | 10.05
006 | 401 | Unit 1-3 Cooling Tower
 |  |  | 37.5 | 23.7 | 0.34 | 20.51333333333334
008 | 402 | Unit 4 [NAME]
 |  |  | 9.8 | 9.8 | 9.8 | 9.8
 |  |  | SO2- tons |  |  |  | [NAME] |  |  |  | PM - tons |  |  |  | PM10 - tons
AIRS | Facility ID | Name | 2006 | 2007 | 2008 | avg | 2006 | 2007 | 2008 | avg | 2006 | 2007 | 2008 | avg | 2006 | 2007 | 2008 | avg
001 | B004 | Unit 4 Boiler | 1509.4 | 1230.4 | 1265.7 | 1335.166666666667 | 1716 | 1598 | 1711.4 | 1675.133333333333 | 57.1 | 54 | 55 | 55.36666666666667 | 41.6 | 39.4 | 40.24 | 40.41333333333333
 |  |  | Sulfur in Coal |  |  |  | Ash in Coal |  |  |  | Moisture Content |  |  |  | Heat Content Btu/lb |  |  |  | Heat Content btu/scf |  |  |  | Heat Content Btu/gal
AIRS | Facility ID | Name | 2006 | 2007 | 2008 | avg | 2006 | 2007 | 2008 | avg | 2006 | 2007 | 2008 | avg | 2006 | 2007 | 2008 | avg | 2006 | 2007 | 2008 | avg | 2006 | 2007 | 2008 | avg
001 | B004 | Unit 4 Boiler | 0.9 | 0.9 | 0.7 | 0.8333333333333334 | 19.75 | 19.75 | 20.34 | 19.94666666666667 |  |  |  |  | 10721 | 10433 | 10480 | 10544.66666666667 |  |  |  |  | 90500 | 90500 | 90500 | 90500
 |  |  | Ton coal Burned |  |  | NG Burned ([NAME]) |  |  | [NAME] (MGal)
AIRS | Facility ID | Name | 2006 | 2007 | 2008 | 2006 | 2007 | 2008 | 2006 | 2007 | 2008
001 | B004 | Unit 4 Boiler | 408906 | 397660 | 403060 |  |  |  | 229.8 | 317.6 | 271.4
 |  |  |  | avg: | 403208.6666666667
 |  |  | MMBTUs - Coal |  |  | MMBTUs - NG |  |  | MMBTUs - Oil
AIRS | Facility ID | Name | 2006 | 2007 | 2008 | 2006 | 2007 | 2008 | 2006 | 2007 | 2008
001 | B004 | Unit 4 Boiler | 8767762.452 | 8297573.56 | 8448137.6 | 0 | 0 | 0 | 20796.9 | 28742.8 | 24561.7
 |  |  | Operating Hours |  |  | Capacity Factor
AIRS | Facility ID | Name | 2006 | 2007 | 2008 | 2006 | 2007 | 2008
001 | B004 | Unit 4 Boiler | 8179 | 7731 | 7874 | 93.4 | 88.3 | 89.9
 |  |  | MMBtu/yr - from CAMD |  |  |  |  |  | MMBtu/yr - from total APEN
AIRS | Facility ID | Name | 2006 | 2007 | 2008 | average |  |  | 2006 | 2007 | 2008 | average
001 | B004 | Unit 4 Boiler | 9275770 | 8638028 | 8621841 | 8845213 |  |  | 8788559.352 | 8326316.359999999 | 8472699.299999999 | 8529191.670666665
 |  |  | SO2- lb/[NAME] |  |  |  | NOx - lb/[NAME] |  |  |  | PM - lb/MMBtu |  |  |  | PM10 - lb/[NAME]
AIRS | Facility ID | Name | 2006 | 2007 | 2008 | avg | 2006 | 2007 | 2008 | avg | 2006 | 2007 | 2008 | avg | 2006 | 2007 | 2008 | avg
001 | B004 | Unit 4 Boiler | 0.3443067734244313 | 0.2965686272264876 | 0.2996400058635409 | 0.31350513550482 | 0.3914339626317239 | 0.3851728432281594 | 0.4051543857429595 | 0.3939203972009476 | 0.0130249879174076 | 0.01301585327554481 | 0.01302062125503259 | 0.01302048748266166 | 0.009489308185011489 | 0.009122452485683075 | 0.009334433330422122 | 0.009315398000372227
 | Uncontrolled SO2 EF (based on the underfeed stoker EF from AP-42, which is recommended for CFBs when no sorbent is injected)
 |  |  | SO2- lb/[NAME]
AIRS | Facility ID | Name | 2006 | 2007 | 2008 | avg
001 | B004 | Unit 4 Boiler | 1.301184590989646 | 1.337103421834563 | 1.03530534351145 | 1.224531118778553
 |  | per ton of coal basis | 27.9 | 27.9 | 21.7 | 25.83333333333333
 | AP42 NOx EF:
 |  |  | AP42 EF (lb/ton)* | AP42 EF (lb/MMBtu)
AIRS | Facility ID | Name
001 | B004 | Unit 4 Boiler | 5 | 0.2370866788898021
 | *uses 2006 - 2008 average coal heat content
 | Note controlled vs uncontrolled NOx is not useful since we don't know how often they run SNCR
 | Uncontrolled PM EF:
 |  |  | 2006 - 2008 Average Ash | AP42 EF (lb/ton)* | AP42 EF (lb/MMBtu)*
AIRS | Facility ID | Name
001 | B004 | Unit 4 Boiler | 19.94666666666667 | 17 | 0.8060947082253272
 | *uses 2006 - 2008 averages of sulfur content and coal heat content
 |  |  | 2002 Stack Test Result |  | 0.014 | 0.9826323137254902
 | Uncontrolled PM10 EF:
 |  |  | 2006 - 2008 Average Ash | AP42 EF (lb/ton)* | AP42 EF (lb/MMBtu)*
 | Facility ID | Name
 | B004 | Unit 4 Boiler | 19.94666666666667 | 12.4 | 0.5879749636467093
 | *uses 2006 - 2008 averages of sulfur content and coal heat content
 | Control Efficiencies (average, 2006 - 2008)
 |  |  | SO2 | NOx | PM | PM10
 | Facility ID | Name
 | B004 | Unit 4 Boiler | 0.7439794459306714 |  | 0.9838474470185679 | 0.9838610335954487