Spreadsheet: 849750d1700148004-similar-to-protection-of-cells-can-you-mark-them-for-bulk-editing-to-refresh-a-report-ms-office-example
Sheet: CH 13e

NFPA 25  INSPECTION, TESTING, AND [NAME]
 |  |  |  |  |  |  |  |  | of Water Based Fire Protection Systems
13 Valves, Valve Components, and Trim | Pressure Reducing and Relief Valves |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | YES
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | NO
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | N/A
 | Sprinkler pressure reducing valves shall be inspected to verify that they are in the following condition: |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | SEE NOTE
 | 61 | *   In the open position. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | REPLACE
 | 62 | *   Not leaking. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | REPAIR
 | 63 | *   Maintaining downstream pressures in accordance with the design criteria. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | CORRECT
 | 64 | *   In good condition, with hand wheels installed and undamaged.
 | 65 | Has a full flow test been conducted within the last 5 years and compared to previous test results?
 | 66 | Has the annual partial flow test been conducted otherwise?
 | [NAME] connection pressure reducing valves shall be inspected to verify that the following:
 | 67 | *   The hand wheel is not damaged or missing.
 | 68 | *   The outlet [NAME] threads are not damaged.
 | 69 | *   No leaks are present.
 | 70 | *   The cap and / or reducer are not missing.
 | 71 | Has a full flow test been conducted within the last 5 years and compared to previous test results?
 | 72 | Has the annual partial flow test been conducted otherwise?
 | [NAME] rack assembly pressure reducing valves shall be inspected to verify that the following:
 | 73 | *   The hand wheel is not damaged or missing.
 | 74 | *   No leaks are present.
 | 75 | Has a full flow test been conducted within the last 5 years and compared to previous test results?
 | 76 | Has the annual partial flow test been conducted otherwise?
 | Master pressure reducing valves shall be inspected to verify that they are in the following condition:
 | 77 | *   The downstream pressures are maintained in accordance with the design criteria.
 | 78 | *   The supply pressure is in accordance with the design criteria.
 | 79 | *   The valves are not leaking.
 | 80 | *   The valve and trim are in good condition.
 | 81 | Has the annual full flow test been conducted and compared to previous test results?
 | Fire pump pressure relief valves
 | 82 | Do circulating relief valves flow water under churn conditions to prevent the pump from overheating?
 | 83 | Do circulating relief valves close in accordance with manufacturer's specifications?
 | 84 | Do pressure relief valves maintain downstream pressures that do not exceed design requirements?
 | Comments: