Spreadsheet: 41266d1239754060-search-column-and-list-all-occurances-of-value-offset-from-string-97-copy
Sheet: HeatLoss

Project Name: | [NAME] |  |  |  |  |  | Sealed |  |  |  | Operable |  |  |  | Zone
Job Number: | ##-### |  |  |  |  | ►Window | L | H | Rs | UΔTs | L | H | Ro | UΔTo | Prefix▼
Engineer: | [NAME] |  |  |  |  | A | 2 | 2 | 2 | 35 | 12 | 2 | 1 | 70
Date: | ##/##/## |  |  |  |  | B | 2 | 4 | 3 | 23.33333333333333 | 1 | 2 | 3 | 23.33333333333333 | APT
 |  |  |  |  |  | C |  |  |  | 0 |  |  |  | 0 | Other
Outdoor (To) = | 0 |  | Legend ▼ |  |  | D |  |  |  | 0 |  |  |  | 0 | Zone Prefix▼
Indoor (Ti) = | 70 |  | Do Not Modify |  |  | E |  |  |  | 0 |  |  |  | 0 | Names▼
ΔT = | 70 |  | Error |  |  | F |  |  |  | 0 |  |  |  | 0 | MISC
NET HEAT LOSS = | 6944.736842105263 |  | Contents Modified |  |  | G |  |  |  | 0 |  |  |  | 0 | ROOF
NET AREA = | 300 |  |  |  |  | H |  |  |  | 0 |  |  |  | 0 | ATTIC
Btu/hr/ft² = | 23.14912280701754 |  |  |  |  | I |  |  |  | 0 |  |  |  | 0 | ELEVATOR
 |  |  |  |  |  | J |  |  |  | 0 |  |  |  | 0 | STAIRS
ENVELOPE | R | U | UΔT |  |  | K |  |  |  | 0 |  |  |  | 0 | A
Roof | 38 | 0.02631578947368421 | 1.842105263157895 |  |  | ►Door | L | H | Rd | UΔTd | Usage | OFactor |  |  | B
Wall (W1) | 19 | 0.05263157894736842 | 3.684210526315789 |  |  | 1 | 4 | 2 | 2 | 35 | Medium | 5000 |  |  | C
Wall (W2) | 22 | 0.04545454545454546 | 3.181818181818182 |  |  | 2 |  |  | 2 | 35 | Medium | 5000 |  |  | D
Wall (W3) |  | 0 | 0 |  |  | 3 |  |  | 2 | 35 | Medium | 5000 |  |  | E
Wall (W4) |  | 0 | 0 |  |  | 4 |  |  | 2 | 35 | Medium | 5000
Window Infiltration | (Sealed) | 0.1375 | 9.625 |  |  | 5 |  |  | 2 | 35 | Medium | 5000
Window Infiltration | (Operable) | 0.55 | 38.5 |  |  | 6 |  |  | 2 | 35 | Medium | 5000
Door Infiltration |  | 0.55 | 38.5 |  |  | 7 |  |  | 2 | 35 | Medium | 5000
[NAME] | Crawl Space |  | [N/A] | 0.0286
▼ Total Area | Space | Vented | [N/A] | 2
300 | Floor | Uninsulated | [N/A] | 4
 | Perimeter | Uninsulated | [N/A] | R-8.34
▼ Total Perimeter | [NAME] | 3 | [N/A] | 0.621
 | U-Ground | 0.077 | [N/A] | 50
 | T-Crawl Space | 0 | [N/A] | Insulated
▼ UΔT | U-Floor-Insulated | 0.076 | [N/A] | 0.48
0 | U-Floor-Uninsulated | 0.25 | [N/A] | 0.621
 | [N/A] | 0.1243 | [N/A] | No
100-ROOM |  | Floor/Roof Loss [Btu/hr] |  | External Wall Loss [Btu/hr] |  |  |  | Window/Door Loss [Btu/hr] |  |  |  |  |  | TOTAL | TOTAL | 100-ROOM | 100 | 3380.263157894737 | 990.670532042763
Room Area | Room Height | Floor Area | Roof Area | Tag | Length | Height | SubTotal | Tag | QTY | Type | Item | Area | SubTotal | [Btu/h] | [Watts]
100 | 8 | 100 | 100 | W1 | 11 | 8 | 221.0526315789474 | W1 | 1 | A | WIN | 28 | 2975
Zone ► | APT.001 | 0 | 184.2105263157895 | 221.0526315789474 |  |  |  | 2975 |  |  |  |  |  | 3380.263157894737 | 990.670532042763
200-ROOM |  | Floor/Roof Loss [Btu/hr] |  | External Wall Loss [Btu/hr] |  |  |  | Window/Door Loss [Btu/hr] |  |  |  |  |  | TOTAL | TOTAL | 200-ROOM | 200 | 3564.473684210526 | 1044.658026976974
Room Area | Room Height | Floor Area | Roof Area | Tag | Length | Height | SubTotal | Tag | QTY | Type | Item | Area | SubTotal | [Btu/h] | [Watts]
200 | 8 | 200 | 200 | W1 | 11 | 8 | 221.0526315789474 | W1 | 1 | A | WIN | 28 | 2975
Zone ► | APT.002 | 0 | 368.421052631579 | 221.0526315789474 |  |  |  | 2975 |  |  |  |  |  | 3564.473684210526 | 1044.658026976974