Spreadsheet: 84433d1284485152-formatting-cells-232-1b-2b4
Sheet: 232-1B-2B4

Panel Name: 232-1B-2B4
Con | Wire | Neu | Gnd | Description | CB | Load | Ckt# | Phase | Ckt# | Load | CB | Description | Wire | Neu | Gnd | Con
1/2" | 12 | 12 | 12 | RECEPTACLES | 20 | 1 | 1 | A | 2 | 0.6 | 20 | RECEPTACLES | 12 | 12 | 12 | 1/2"
1/2" | 12 | 12 | 12 | RECEPTACLES | 20 | 1 | 3 | B | 4 | 0.4 | 20 | RECEPTACLES | 12 | 12 | 12 | 1/2"
1/2" | 12 | 12 | 12 | RECEPTACLES | 20 | 0.8 | 5 | C | 6 | 1 | 20 | RECEPTACLES | 12 | 12 | 12 | 1/2"
1/2" | 12 | 12 | 12 | RECEPTACLES | 20 | 1 | 7 | A | 8 | 1 | 20 | RECEPTACLES | 12 | 12 | 12 | 1/2"
1/2" | 12 | 12 | 12 | RECEPTACLES | 20 | 1 | 9 | B | 10 | 1 | 20 | RECEPTACLES | 12 | 12 | 12 | 1/2"
1/2" | 12 | 12 | 12 | RECEPTACLES | 20 | 1 | 11 | C | 12 | 1 | 20 | RECEPTACLES | 12 | 12 | 12 | 1/2"
1/2" | 12 | 12 | 12 | RECEPTACLES | 20 | 1 | 13 | A | 14 | 1 | 20 | RECEPTACLES | 12 | 12 | 12 | 1/2"
1/2" | 12 | 12 | 12 | RECEPTACLES | 20 | 1 | 15 | B | 16 | 1 | 20 | RECEPTACLES | 12 | 12 | 12 | 1/2"
1/2" | 12 | 12 | 12 | RECEPTACLES | 20 | 1 | 17 | C | 18 | 1 | 20 | RECEPTACLES | 12 | 12 | 12 | 1/2"
1/2" | 12 | 12 | 12 | RECEPTACLES | 20 | 1 | 19 | A | 20 | 1 | 20 | RECEPTACLES | 12 | 12 | 12 | 1/2"
1/2" | 12 | 12 | 12 | RECEPTACLES | 20 | 1 | 21 | B | 22 | 1 | 20 | RECEPTACLES | 12 | 12 | 12 | 1/2"
1/2" | 12 | 12 | 12 | RECEPTACLES | 20 | 0.8 | 23 | C | 24 | 1 | 20 | RECEPTACLES | 12 | 12 | 12 | 1/2"
1/2" | 12 | 12 | 12 | RECEPTACLES | 20 | 0.8 | 25 | A | 26 | 1 | 20 | RECEPTACLES | 12 | 12 | 12 | 1/2"
1/2" | 12 | 12 | 12 | RECEPTACLES | 20 | 0.8 | 27 | B | 28 | 1 | 20 | RECEPTACLES | 12 | 12 | 12 | 1/2"
1/2" | 12 | 12 | 12 | RECEPTACLES | 20 | 0.8 | 29 | C | 30 | 1 | 20 | RECEPTACLES | 12 | 12 | 12 | 1/2"
1/2" | 12 | 12 | 12 | RECEPTACLES | 20 | 0.6 | 31 | A | 32 | 0.6 | 20 | RECEPTACLES | 12 | 12 | 12 | 1/2"
1/2" | 12 | 12 | 12 | RECEPTACLES | 20 | 0.7 | 33 | B | 34 | 1 | 20 | RECEPTACLES | 12 | 12 | 12 | 1/2"
1/2" | 12 | 12 | 12 | PROJECTOR SCREENS | 20 | 0.7 | 35 | C | 36 | 0.2 | 20 | RECEPTACLES | 12 | 12 | 12 | 1/2"
 |  |  |  | SPARE | 20 |  | 37 | A | 38 | 1 | 20 | DOOR MOTOR | 12 | 12 | 12 | 1/2"
 |  |  |  | SPARE | 20 |  | 39 | B | 40 | 0.2 | 20 | RECEPTACLES | 12 | 12 | 12 | 1/2"
 |  |  |  | SPARE | 20 |  | 41 | C | 42 |  | 20 | SPARE
 | Panel Name: 232-1B-2B4 section 2
 |  |  |  | SPARE | 20 |  | 43 | A | 44 |  |  | SPARE | 20
 |  |  |  | SPARE | 20 |  | 45 | B | 46 |  |  | SPARE | 20
 |  |  |  | SPARE | 20 |  | 47 | C | 48 |  |  | SPARE | 20
 |  |  |  | SPARE | 20 |  | 49 | A | 50 |  |  | SPARE | 20
 |  |  |  | SPARE | 20 |  | 51 | B | 52 |  |  | SPARE | 20
 |  |  |  | SPARE | 20 |  | 53 | C | 54 |  |  | SPARE | 20
 |  |  |  | SPACE ONLY |  |  | 55 | A | 56 |  |  | SPACE ONLY
 |  |  |  | SPACE ONLY |  |  | 57 | B | 58 |  |  | SPACE ONLY
 |  |  |  | SPACE ONLY |  |  | 59 | C | 60 |  |  | SPACE ONLY
 |  |  |  | SPACE ONLY |  |  | 61 | A | 62 |  |  | SPACE ONLY
 |  |  |  | SPACE ONLY |  |  | 63 | B | 64 |  |  | SPACE ONLY
 |  |  |  | SPACE ONLY |  |  | 65 | C | 66 |  |  | SPACE ONLY
 |  |  |  | SPACE ONLY |  |  | 67 | A | 68 |  |  | SPACE ONLY
 |  |  |  | SPACE ONLY |  |  | 69 | B | 70 |  |  | SPACE ONLY
 |  |  |  | SPACE ONLY |  |  | 71 | C | 72 |  |  | SPACE ONLY
 |  |  |  | SPACE ONLY |  |  | 73 | A | 74 |  |  | SPACE ONLY
 |  |  |  | SPACE ONLY |  |  | 75 | B | 76 |  |  | SPACE ONLY
 |  |  |  | SPACE ONLY |  |  | 77 | C | 78 |  |  | SPACE ONLY
 |  |  |  | SPACE ONLY |  |  | 79 | A | 80 |  |  | SPACE ONLY
 |  |  |  | SPACE ONLY |  |  | 81 | B | 82 |  |  | SPACE ONLY
 |  |  |  | SPACE ONLY |  |  | 83 | C | 84 |  |  | SPACE ONLY
Voltage:   120-208V/3Ph/60Hz |  |  |  | [NAME]:   3#1
Bus Amps:   100 Amps |  |  |  | Main Neutral:   1#1
Main breaker:   100 Amps |  |  |  | [NAME]:   1#8
Type:   Branch Circuits |  |  |  | Main Conduit:   1-1/2"
Mounting:   Flush |  |  |  | Feeder types:   Copper, THHN, EMT
Nema Rating:   1
System:   Normal
 |  |  |  |  |  |  |  |  |  |  |  | Connected Loads
 |  |  |  |  |  |  |  |  |  |  |  | KW Phase A: |  |  | 11.6
 |  |  |  |  |  |  |  |  |  |  |  | KW Phase B: |  |  | 11.1
 |  |  |  |  |  |  |  |  |  |  |  | KW Phase C: |  |  | 10.3
 |  |  |  |  |  |  |  |  |  |  |  | Total KW: |  |  | 33
Voltage drop was calculated using the formula found in 2005 NEC®, [NAME], Chapter 9, Example 2 per foot.  Zc = (R x cos Ѳ) + (Xl  x sin Ѳ) ±5%
Conduit fill is based on 2005 NEC® 310-15.  ±5%.  Table 1 in Chapter 9 shows maximum percentage fill factor.
*For branch circuits in EPS Lite, you must add the voltage drop from the service conductors with the drop on feeders for total drop.
 |  |  |  |  | Voltage drop and conduit fill calcs table
Feeder calcs: |  | Voltage Drop = (30'), 0.7384 Volts / 0.355%
 |  | Conduit fill = 32.5% Fill
Circuit number |  |  |  |  |  |  | Circuit number
1 |  | Voltage Drop = (30'), 0.9817 Volts / 0.8181% |  |  |  |  | 2 |  | Voltage Drop = (30'), 0.589 Volts / 0.4908%
 |  | Conduit fill = 13.1% Fill |  |  |  |  |  |  | Conduit fill = 13.1% Fill
3 |  | Voltage Drop = (30'), 0.9817 Volts / 0.8181% |  |  |  |  | 4 |  | Voltage Drop = (30'), 0.3927 Volts / 0.3273%
 |  | Conduit fill = 13.1% Fill |  |  |  |  |  |  | Conduit fill = 13.1% Fill
5 |  | Voltage Drop = (30'), 0.7854 Volts / 0.6545% |  |  |  |  | 6 |  | Voltage Drop = (30'), 0.9817 Volts / 0.8181%
 |  | Conduit fill = 13.1% Fill |  |  |  |  |  |  | Conduit fill = 13.1% Fill
7 |  | Voltage Drop = (30'), 0.9817 Volts / 0.8181% |  |  |  |  | 8 |  | Voltage Drop = (30'), 0.9817 Volts / 0.8181%
 |  | Conduit fill = 13.1% Fill |  |  |  |  |  |  | Conduit fill = 13.1% Fill
9 |  | Voltage Drop = (30'), 0.9817 Volts / 0.8181% |  |  |  |  | 10 |  | Voltage Drop = (30'), 0.9817 Volts / 0.8181%
 |  | Conduit fill = 13.1% Fill |  |  |  |  |  |  | Conduit fill = 13.1% Fill
11 |  | Voltage Drop = (30'), 0.9817 Volts / 0.8181% |  |  |  |  | 12 |  | Voltage Drop = (30'), 0.9817 Volts / 0.8181%
 |  | Conduit fill = 13.1% Fill |  |  |  |  |  |  | Conduit fill = 13.1% Fill
13 |  | Voltage Drop = (30'), 0.9817 Volts / 0.8181% |  |  |  |  | 14 |  | Voltage Drop = (30'), 0.9817 Volts / 0.8181%
 |  | Conduit fill = 13.1% Fill |  |  |  |  |  |  | Conduit fill = 13.1% Fill
15 |  | Voltage Drop = (30'), 0.9817 Volts / 0.8181% |  |  |  |  | 16 |  | Voltage Drop = (30'), 0.9817 Volts / 0.8181%
 |  | Conduit fill = 13.1% Fill |  |  |  |  |  |  | Conduit fill = 13.1% Fill
17 |  | Voltage Drop = (30'), 0.9817 Volts / 0.8181% |  |  |  |  | 18 |  | Voltage Drop = (30'), 0.9817 Volts / 0.8181%
 |  | Conduit fill = 13.1% Fill |  |  |  |  |  |  | Conduit fill = 13.1% Fill
19 |  | Voltage Drop = (30'), 0.9817 Volts / 0.8181% |  |  |  |  | 20 |  | Voltage Drop = (30'), 0.9817 Volts / 0.8181%
 |  | Conduit fill = 13.1% Fill |  |  |  |  |  |  | Conduit fill = 13.1% Fill
21 |  | Voltage Drop = (30'), 0.9817 Volts / 0.8181% |  |  |  |  | 22 |  | Voltage Drop = (30'), 0.9817 Volts / 0.8181%
 |  | Conduit fill = 13.1% Fill |  |  |  |  |  |  | Conduit fill = 13.1% Fill
23 |  | Voltage Drop = (30'), 0.7854 Volts / 0.6545% |  |  |  |  | 24 |  | Voltage Drop = (30'), 0.9817 Volts / 0.8181%
 |  | Conduit fill = 13.1% Fill |  |  |  |  |  |  | Conduit fill = 13.1% Fill
25 |  | Voltage Drop = (30'), 0.7854 Volts / 0.6545% |  |  |  |  | 26 |  | Voltage Drop = (30'), 0.9817 Volts / 0.8181%
 |  | Conduit fill = 13.1% Fill |  |  |  |  |  |  | Conduit fill = 13.1% Fill
27 |  | Voltage Drop = (30'), 0.7854 Volts / 0.6545% |  |  |  |  | 28 |  | Voltage Drop = (30'), 0.9817 Volts / 0.8181%
 |  | Conduit fill = 13.1% Fill |  |  |  |  |  |  | Conduit fill = 13.1% Fill
29 |  | Voltage Drop = (30'), 0.7854 Volts / 0.6545% |  |  |  |  | 30 |  | Voltage Drop = (30'), 0.9817 Volts / 0.8181%
 |  | Conduit fill = 13.1% Fill |  |  |  |  |  |  | Conduit fill = 13.1% Fill
31 |  | Voltage Drop = (30'), 0.589 Volts / 0.4908% |  |  |  |  | 32 |  | Voltage Drop = (30'), 0.589 Volts / 0.4908%
 |  | Conduit fill = 13.1% Fill |  |  |  |  |  |  | Conduit fill = 13.1% Fill
33 |  | Voltage Drop = (30'), 0.6872 Volts / 0.5727% |  |  |  |  | 34 |  | Voltage Drop = (30'), 0.9817 Volts / 0.8181%
 |  | Conduit fill = 13.1% Fill |  |  |  |  |  |  | Conduit fill = 13.1% Fill
35 |  | Voltage Drop = (60'), 1.3744 Volts / 1.1453% |  |  |  |  | 36 |  | Voltage Drop = (30'), 0.1963 Volts / 0.1636%
 |  | Conduit fill = 13.1% Fill |  |  |  |  |  |  | Conduit fill = 13.1% Fill
37 |  |  |  |  |  |  | 38 |  | Voltage Drop = (30'), 0.9817 Volts / 0.8181%
 |  |  |  |  |  |  |  |  | Conduit fill = 13.1% Fill
39 |  |  |  |  |  |  | 40 |  | Voltage Drop = (30'), 0.1963 Volts / 0.1636%
 |  |  |  |  |  |  |  |  | Conduit fill = 13.1% Fill
41 |  |  |  |  |  |  | 42
43 |  |  |  |  |  |  | 44
45 |  |  |  |  |  |  | 46
47 |  |  |  |  |  |  | 48
49 |  |  |  |  |  |  | 50
51 |  |  |  |  |  |  | 52
53 |  |  |  |  |  |  | 54
55 |  |  |  |  |  |  | 56
57 |  |  |  |  |  |  | 58
59 |  |  |  |  |  |  | 60
61 |  |  |  |  |  |  | 62
63 |  |  |  |  |  |  | 64
65 |  |  |  |  |  |  | 66
67 |  |  |  |  |  |  | 68
69 |  |  |  |  |  |  | 70
71 |  |  |  |  |  |  | 72
73 |  |  |  |  |  |  | 74
75 |  |  |  |  |  |  | 76
77 |  |  |  |  |  |  | 78
79 |  |  |  |  |  |  | 80
81 |  |  |  |  |  |  | 82
83 |  |  |  |  |  |  | 84