Spreadsheet: 329815d1404409729-help-setiing-up-this-commands-in-excell-find-and-copy-text-between-sheets-tag_id-with-info
Sheet: Sheet1

Tag ID |  | FLOC | Drawing Description | PLC | Node Address | Wire Number | Equipment | Old Tag Name | I/O Rack | I/O SLOT | I/O CHANNEL | Equipment Physical Location (FL) | Base Location | Base Floor | Description | Unit | New/Existing | Safety PLC | Note | Xreference | System Tag Name | System Description | I/O Type | Supply Voltage | Scaled Range & Units of Measure | [NAME] | Manufacturer | Model | Serial | Asset | Year of Manuf. | Use Existing ? | Purchase New ? | Replacement Cost | On [NAME] ? | HOA | FTR | FTO | FTC | Equip_Runtime | DELAVAL_PID
 | 1
 |  |  | Ethernet
GRND66.00 |  | COF-SD2 | [NAME] | PLC37 | 10.10.37.30 |  | Motor, VFD | MOT3701B |  |  |  | 3 |  |  | [NAME] |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | HOA[13].9 | [44] |  |  | [44]
FAN16.08 |  | COF-SD2 | Egron Exhaust Fan (Bucket A34) | PLC37 | 10.10.37.41 |  | Motor, VFD | M3706A |  |  |  | 4 | 1 | 2 | Collector System - Exhaust blower | Collector System | Existing |  | [NAME] hot at all time | Y224 | M-A34 | O/P Delaval Exhaust Fan | DO | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421086 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].1 | [2] |  |  | [2]
 |  |  | [NAME]
 |  | COF-SD2 | AZO vacuum pump E-Stop | PLC37 |  | AZO_1_0 | DI | PB3702A | AZO | 1 | 0 | 1 | Profi | 1 | AZO vacuum pump E-Stop | AZO | Existing |  |  | X320 | STOP PB | Stop Push Button | DI | 0 | 0 | 1st | [NAME] push botton | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
 |  | COF-SD2 | Enable SW left | PLC37 |  | AZO_1_1 | DI | PB3702B | AZO | 1 | 1 | 1 | Profi | 1 | Enable SW left | AZO | Existing |  |  | X324 | ENB.SW LT | Enable Left Slide Gate | DI | 0 | 0 | 1st | Square-D push botton | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
 |  | COF-SD2 | Enable SW right | PLC37 |  | [NAME] | DI | PB3702C | AZO | 1 | 2 | 2 | Profi | 1 | Enable SW right | AZO | Existing |  |  | X323 | RIGHT SW | Diverter Gate Switch (Right) 2nd Floor | DI | 0 | 0 | 2nd | [NAME] switch  802T-AP | 0 | 0 | 0 | 0 | 0 | x | 0 | 0
 |  | COF-SD2 | Diverter left gate enable | PLC37 |  | AZO_1_3 | DI | LS3702G | AZO | 1 | 3 | 1 | Profi | 1 | Control system shutdown PB on 2nd fl witte | AZO | Existing |  |  | X325 | ENB SW RT | Enable Right Slide Gate | DI | 0 | 0 | 1st | Square-D push botton | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
ZS54.50 |  | COF-SD2 | Diverter Gate Enable | PLC37 |  | AZO_1_4 | DI | ZS3702F | AZO | 1 | 4 | 2 | Profi | 1 | Diverter right gate enable | AZO | Existing |  |  | X322 | LEFT SW | Diverter Gate Switch (Left) 2nd Floor | DI | 0 | 0 | 2nd | [NAME] switch  802T-AP | 0 | 0 | 0 | 0 | 0 | x | 0 | 0
 |  | COF-SD2 | AZO E-Stop | PLC37 |  | AZO_1_5 | DI | AZO_ESTOP | AZO | 1 | 5 | 2 | Profi | 1 | AZO E-Stop | AZO | Existing |  |  | X321 | E-STOP | Emergency Stop | DI | 0 | 0 | 1st | [NAME] push botton | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
MOT54.37 |  | COF-SD2 | Baghouse Product Vacuum Pump Motor Aux | PLC37 |  | AZO_1_6 | DI | M3702H_AUX | AZO | 1 | 6 | 2 | Profi | 1 | Vacuum pump pulling the product into baghouse Aux | AZO | Existing |  |  | X313 | MS1500 | Motor Feedback | DI | 0 | 0 | 1st | Telemecanique | LB1-LB03p | 0 | 0 | 0 | x | 0 | 0 | 0
MOT54.18 |  | COF-SD2 | Baghouse Outlet Star Valve Aux | PLC37 |  | AZO_1_7 | DI | M3702F_AUX | AZO | 1 | 7 | 2 | Profi | 1 | Star valve at the baghouse outlet aux | AZO | Existing |  |  | X314 | MS1210 | Motor Feedback | DI | 0 | 0 | 1st | Telemecanique | LB1-LB03p | 0 | 0 | 0 | x | 0 | 0 | 0
PSH54.45 |  | COF-SD2 | Vacuum High Pressure Switch | PLC37 |  | AZO_1_8 | DI | PSH3702A | AZO | 1 | 8 | 2 | Profi | 1 | Vacuum High Pressure Switch | AZO | Existing |  |  | X315 | VSH-1400 | [NAME] limit [NAME] | DI | 0 | 0-30"hg | 2nd | Dwyer | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
PSL54.46 |  | COF-SD2 | Vacuum Low Pressure Switch | PLC37 |  | AZO_1_9 | DI | PSL3702B | AZO | 1 | 9 | 2 | Profi | 1 | Vacuum Low Pressure Switch | AZO | Existing |  |  | X316 | VSL-1400 | [NAME] limit [NAME] | DI | 0 | 0-30"hg | 2nd | Dwyer | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
LSH54.07 |  | COF-SD2 | Baghouse High Level Sensor | PLC37 |  | AZO_1_10 | DI | LSH3702B | AZO | 1 | 10 | 2 | Profi | 1 | Level sensor in the baghouse high level | AZO | Existing |  |  | X318 | LSH-1200 | Low level [NAME] | DI | 0 | 0 | 2nd | Drexelbrook | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
LS54.09 |  | COF-SD2 | Witte Discharge Hopper Level Sensor | PLC37 |  | AZO_1_11 | DI | LS3702D | AZO | 1 | 11 | 1 | Profi | 1 | Witte discharge hopper level sensor | AZO | Existing |  | ? | X317 | LSL-1000 | High level [NAME] | DI | 0 | 0 | 1st | Drexelbrook | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
 |  | COF-SD2 | AZO Start Push Button (Illuminated) | PLC37 |  | AZO_1_12 | DI | PB3702F | AZO | 1 | 12 | 1 | Profi | 1 | AZO Start Push Button (Illuminated) | AZO | Existing |  |  | X319 | SPBI | Start Push Button (Illuminated) | DI | 0 | 0 | 1st | [NAME] push botton | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
[NAME] |  | COF-SD2 | Baghouse Filter Pulse Solenoid Valve | PLC37 |  | AZO_2_0 | DO | SV3702B | AZO | 2 | 0 | 2 | Profi | 1 | [NAME] valve on wet scrubber water line | AZO | Existing |  | one output | Y332 | YV-1200 | Filter Clean [NAME] | DO | 0 | 0 | 2nd | Mac | 811c-pp-111ca-152 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[20].0
YV54.19 |  | COF-SD2 | Air Unloading Solenoid Valve | PLC37 |  | AZO_2_1 | DO | SV3702M | AZO | 2 | 1 | 2 | Profi | 1 | Air unloading valve solenoid | AZO | Existing |  | one output | Y334 | YV-1300 | Unloader [NAME] | DO | 0 | 0 | 2nd | Mac | 811c-pp-111ca-152 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[20].1
YV54.22 |  | COF-SD2 | Diverter Solenoid Valve | PLC37 |  | AZO_2_2 | DO | SV3702H | AZO | 2 | 2 | 1 | Profi | 1 | Diverter valve solenoid | AZO | Existing |  |  | Y333 | YV-1250 | Diverter Gate Solenoid 2nd Floor | DO | 0 | 0 | 2nd | Mac | 811c-pp-111ca-152 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[20].2
YV54.26 |  | COF-SD2 | Feed hopper Right Vibrator Solenoid Valve | PLC37 |  | AZO_2_3 | DO | SV3702K | AZO | 2 | 3 | 1 | Profi | 1 | Feed hopper right vibrator | AZO | Existing |  |  | Y342 | 0 | Right Divert Vibrator - AZO | DO | 0 | 0 | 1st | [NAME] | 0 | F67241 | 0 | 0 | x | 0 | 0 | 0 | HOA[20].3
YV54.25 |  | COF-SD2 | Feed hopper Left Vibrator [NAME] | PLC37 |  | AZO_2_4 | DO | SV3702L | AZO | 2 | 4 | 1 | Profi | 1 | Feed hopper left vibrator | AZO | Existing |  |  | Y341 | STROBE | Alarm Indicating Strobe Light | DO | 0 | 0 | 1st | Federal Singal | 225 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[20].4
YV54.17 |  | COF-SD2 | STRV54.18 Air Purge Solenoid Valve | PLC37 |  | AZO_2_6 | DO | SV3702N | AZO | 2 | 6 | 2 | Profi | 1 | Star valve at the baghouse outlet air purge solenoid | AZO | Existing |  | one output | Y336 | YV-1210 | Rv-1210 Discharge Rotary Valve Air Purge | DO | 0 | 0 | 1st | Mac | 811c-pp-111ca-152 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[20].5
YV54.24 |  | COF-SD2 | [NAME] | PLC37 |  | AZO_3_0 | DO | SV3702A | AZO | 3 | 0 | 2 | Profi | 1 | Vacuum pump discharge valve purge solenoid | AZO | Existing |  | FC | Y331 | YV-1100 | Discharge Rotary Valve Solenoid | DO | 0 | 0 | 1st | Mac | 811c-pp-111ca-152 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[20].6
YV54.06 |  | COF-SD2 | [NAME] Discharge Vibrator [NAME] | PLC37 |  | AZO_3_1 | DO | SV3702P | AZO | 3 | 1 | 1 | Profi | 1 | Vacuum pump discharge vibrator solenoid | AZO | Existing |  | FC | Y335 | YV-1000 | HPR-1000 Impactor [NAME] | DO | 0 | 0 | 1st | Mac | 811c-pp-111ca-152 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[20].7
STRV54.18 |  | COF-SD2 | Baghouse Outlet Star Valve | PLC37 |  | AZO_3_2 | Motor | [NAME] | AZO | 3 | 2 | 2 | Profi | 1 | Star valve at the baghouse outlet | AZO | Existing |  |  | Y330 | RV-1210 | Discharge Rotary Valve | DO | 0 | 0 | 1st | Telemecanique | LB1-LB03p | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[21].0 | [42] |  |  | [42]
PUMP54.37 |  | COF-SD2 | Baghouse Product Vacuum Pump | PLC37 |  | AZO_3_3 | Motor | M3702H | AZO | 3 | 3 | 2 | Profi | 1 | Vacuum pump pulling the product into baghouse | AZO | Existing |  |  | Y329 | BL-1500 | Vacuum Pump Motor | DO | 0 | 0 | 1st | Telemecanique | LB1-LB03p | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[21].1 | [43] |  |  | [43]
 |  | COF-SD2 | Azo System Running Pilot Light | PLC37 |  | AZO_3_4 | DO | PL3702D | AZO | 3 | 4 | 1 | Profi | 1 | Azo System Running Pilot Light | AZO | Existing |  |  | Y337 | PL-1 | System Running Pilot Light | DO | 0 | 0 | 1st | [NAME] pilot light | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
 |  | COF-SD2 | [NAME] | PLC37 |  | AZO_3_5 | DO | PL3702C | AZO | 3 | 5 | 1 | Profi | 1 | [NAME] | AZO | Existing |  |  | Y338 | PL-2 | System High Vacuum | DO | 0 | 0 | 1st | [NAME] pilot light | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
 |  | COF-SD2 | [NAME] | PLC37 |  | AZO_3_6 | DO | PL3702B | AZO | 3 | 6 | 1 | Profi | 1 | [NAME] | AZO | Existing |  |  | Y339 | PL-3 | [NAME] | DO | 0 | 0 | 1st | [NAME] pilot light | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
 |  | COF-SD2 | [NAME] | PLC37 |  | AZO_3_7 | DO | PL3702A | AZO | 3 | 7 | 1 | Profi | 1 | [NAME] | AZO | Existing |  |  | Y340 | STROBE | Alarm Indicating Strobe Light | DO | 0 | 0 | 1st | Federal Singal | 225 | 0 | 0 | 0 | x | 0 | 0 | 0
 |  |  | [NAME]
 |  | COF-SD2 | Egron High Temp. | PLC37 |  | BUR_1_0 | DI | BUR_DCHT | BUR | 1 | 0 | 5 | 5 | 1 | [NAME] High Temp. | [NAME] | Existing |  |  | X634 | DCHT-RX634 | Dryer High Temp. | DI | 0 | 0 | 1st | Square-D relay | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0
 |  | COF-SD2 | Egron North Cyclone High Temp. Safety | PLC37 |  | BUR_1_1 | DI | BUR_NCHT | BUR | 1 | 1 | 5 | 5 | 1 | [NAME] Collector High Temp Safety | [NAME] | Existing |  |  | X635 | NCHT-RX635 | North Collector High Temp Safety | DI | 0 | 0 | 1st | Square-D relay | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0
 |  | COF-SD2 | Egron South Cyclone High Temp. Safety | PLC37 |  | BUR_1_2 | DI | BUR_SCHT | BUR | 1 | 2 | 5 | 5 | 1 | [NAME] Collector High Temp Safety | [NAME] | Existing |  |  | X636 | SCHT-RX636 | South Collector High Temp Safety | DI | 0 | 0 | 1st | Square-D relay | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0
 |  | COF-SD2 | Cold Side HX High Temp. [NAME] Fl4 | PLC37 |  | BUR_1_3 | DI |  | BUR | 1 | 3 | 5 | 5 | 1 | [NAME] (Process Air to Dryer) (HX) Failed Alarm Switch SetPoint 800 F | [NAME] | Existing |  |  | X637 | TS-637 | Cold Side (Process Air to Dryer) (HX) Failed Alarm Switch SetPoint 800 F | DI | 0 | 0 | 4th | Honeywell Annunciator | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
 |  | COF-SD2 | Hot Side HX Hight Temp?1000F  4Fl. | PLC37 |  | BUR_1_4 | DI |  | BUR | 1 | 4 | 5 | 5 | 1 | [NAME] (Air In to HX) Failed Alarm Switch / SetPoint 1000 F | [NAME] | Existing |  |  | X638 | TS-638 | Hot Side (Air In to HX) Failed Alarm Switch / SetPoint 1000 F | DI | 0 | 0 | 4th | Honeywell Annunciator | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
 |  | COF-SD2 | Burner Panel E-stop | PLC37 |  | BUR_1_5 | DI | PB3705D | BUR | 1 | 5 | 1 | 5 | 1 | [NAME] | [NAME] | Existing |  |  | X639 | E-STOP-2 | E-Stop Push Button | DI | 0 | 0 | 1st | Square-D push botton | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0
 |  | COF-SD2 | [NAME] Start PushButton | PLC37 |  | BUR_1_7 | DI | PB3705E | BUR | 1 | 7 | 5 | 5 | 1 | [NAME] Egron Burner Start PB | [NAME] | Existing |  |  | X641 | PB-126 | [NAME] Start PB | DI | 0 | 0 | 1st | Square-D push botton | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
 |  | COF-SD2 | Egron Burner Stop PB | PLC37 |  | BUR_1_8 | DI | PB3705F | BUR | 1 | 8 | 5 | 5 | 1 | [NAME] Egron Burner Stop PB | [NAME] | Existing |  |  | X642 | PB-127 | [NAME] | DI | 0 | 0 | 1st | Square-D push botton | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
PS16.06 |  | COF-SD2 | Exhaust Fan Neg. Press. SW. Above Col. (BUR_PS9) | PLC37 |  | BUR_1_9 | DI | PS3706A | BUR | 1 | 9 | 5 | 5 | 1 | [NAME] | [NAME] | Existing |  |  | X609 | PS-9 | Exhaust Fan Negative Pressure Switch | DI | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0
PS16.10 |  | COF-SD2 | [NAME]. Pres. Sw. (BUR_PS8) | PLC37 |  | BUR_1_10 | DI | PS3700A | BUR | 1 | 10 | 5 | 5 | 1 | [NAME] Negative Pressure Switch | [NAME] | Existing |  |  | X610 | PS-8 | Dryer Negative Pressure Switch | DI | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0
 |  | COF-SD2 | PLC Safety Interlock Safety Shower Ready | PLC37 |  | BUR_1_11 | DI |  | BUR | 1 | 11 | 5 | 5 | 1 | Egron Burner - PLC Safety Interlock (Deluge System armed and Ready) | [NAME] | Existing |  |  | X611 | DFS-100 | PLC Safety Interlock (Deluge System armed and Ready) | DI | 0 | 0 | 1st | Square-D relay | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0
 |  | COF-SD2 | OK to Ramp Relay | PLC37 |  | BUR_1_12 | DI |  | BUR | 1 | 12 | 5 | 5 | 1 | [NAME] to [NAME] | [NAME] | Existing |  |  | X620 | RX-620 | OK to [NAME] | DI | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0
 |  | COF-SD2 | [NAME] Alarm | PLC37 |  | BUR_1_13 | DI |  | BUR | 1 | 13 | 5 | 5 | 1 | [NAME] Relay Alarm | [NAME] | Existing |  |  | X621 | RX-621 | [NAME] Alarm | DI | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0
 |  | COF-SD2 | OK to Start Burner Relay | PLC37 |  | BUR_1_14 | DI |  | BUR | 1 | 14 | 5 | 5 | 1 | [NAME] to [NAME] | [NAME] | Existing |  |  | X622 | RX-622 | OK to [NAME] | DI | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0
 |  | COF-SD2 | Modulator High Fire Relay Contact | PLC37 |  | BUR_1_15 | DI |  | BUR | 1 | 15 | 5 | 5 | 1 | [NAME] High Fire Relay | [NAME] | Existing |  |  | X623 | RX-623 | Modulator High Fire Relay | DI | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0
MOT07.04 |  | COF-SD2 | Combustion Blower Motor Aux | PLC37 |  | BUR_2_0 | DI | FAN3705B | BUR | 2 | 0 | 4 | 5 | 1 | Egron Burner - Combustion blower aux | [NAME] | Existing |  | FL1_3_14 | X619 | CAB-M2 | Combustion Blower Run Aux. | DI | 0 | 0 | 4th | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
 |  | COF-SD2 | Process Air Fan D/P Sw. Relay | PLC37 |  | BUR_2_1 | DI | PS3705A | BUR | 2 | 1 | 4 | 5 | 1 | [NAME] pressure across the burner | [NAME] | Existing |  | FL1_3_15 | X612 | PS-5 | Process Air Fan D/P Air Flow Pressure Switch | DI | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0
BLOW06.03 |  | COF-SD2 | Recirculation Air Blower Motor Aux | PLC37 |  | BUR_2_2 | DI | FAN3705A | BUR | 2 | 2 | 4 | 5 | 1 | [NAME] air blower aux | [NAME] | Existing |  | FL1_4_0 | X618 | PAB-M1 | Process Air Blower Aux. | DI | 0 | 0 | 4th | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
ZSO06.12 |  | COF-SD2 | V2 Open to Outside Limit Sw. | PLC37 |  | BUR_2_3 | DI | ZSO3705A | BUR | 2 | 3 | 4 | 5 | 1 | [NAME] gate to atomosphere open | [NAME] | Existing |  | FL1_4_1 | X614 | LS4-O | V2 Valve Open to Outside Limit Switch | DI | 0 | 0 | 4th | Turk | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
ZSC06.12 |  | COF-SD2 | V2 Closed to Outside Limit Sw. | PLC37 |  | BUR_2_4 | DI | ZSC3705A | BUR | 2 | 4 | 4 | 5 | 1 | [NAME] gate to atomosphere closed | [NAME] | Existing |  | FL1_4_2 | X615 | LS4-C | V2 Valve Closed to Outside Limit Switch | DI | 0 | 0 | 4th | Turk | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
 |  | COF-SD2 | EM. Divert PB 5th Fl. Divert to Atmosphere | PLC37 |  | BUR_2_5 | DI | PB3705A | BUR | 2 | 5 | 5 | 5 | 1 | [NAME] gate to atomosphere e-stop | [NAME] | Existing |  | FL1_4_3 | X645 | ESTOP-1 | Emergency Divert to Atmosphere PB 5th Floor | DI | 0 | 0 | 5th | Square-D push botton | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
ZSO06.13 |  | COF-SD2 | V1 Open to Dryer Inlet Limit Sw. | PLC37 |  | BUR_2_6 | DI | [NAME] | BUR | 2 | 6 | 4 | 5 | 1 | [NAME] gate to the dryer open | [NAME] | Existing |  | FL1_4_4 | X616 | LS1-O | V1 Valve Open to Dryer Inlet Limit Switch | DI | 0 | 0 | 4th | Turk | 0 | 0 | 0 | 0 | 0 | x | 0 | 0
ZSC06.13 |  | COF-SD2 | V1  Closed to Dryer Inlet Limit Sw. | PLC37 |  | BUR_2_7 | DI | ZSC3705B | BUR | 2 | 7 | 4 | 5 | 1 | [NAME] gate to the dryer closed | [NAME] | Existing |  | FL1_4_5 | X617 | LS3-C | V1 Valve Closed to Dryer Inlet Limit Switch | DI | 0 | 0 | 4th | Turk | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
[NAME] |  | COF-SD2 | Start Blower Blower Relay | PLC37 |  | BUR_3_0 | DO | M3705B | BUR | 3 | 0 | 4 | 5 | 1 | [NAME] blower | [NAME] | Existing |  | FL1_6_7 | Y631 | RY-631 | Start Burner Blower (RY631) | DO | 0 | 0 | 1st | Square-D relay | RS14m1p14v20 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | HOA[17].0
V06.12 |  | COF-SD2 | V2 Divert Air (to Outside) Valve 4th FL. | PLC37 |  | BUR_3_1 | DO | SV3705A | BUR | 3 | 1 | 4 | 5 | 1 | [NAME] gate to atomosphere command | [NAME] | Existing |  | [NAME] | Y625 | DV2-ATMOS | V2 Valve Divert Air to Outside 4th Floor | DO | 0 | 0 | 4th | Numatic | 1525a400k | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[16].0
V06.13 |  | COF-SD2 | V1 Divert Air (to Dryer) Valve 4th FL. | PLC37 |  | BUR_3_2 | DO | SV3705B | BUR | 3 | 2 | 4 | 5 | 1 | [NAME] gate to the dryer command | [NAME] | Existing |  | FL1_6_9 | Y626 | DV1-DRYER | V1 Valve Divert Air to Dryer 4th Floor | DO | 0 | 0 | 4th | Numatic | 1525a400k | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[16].1
 |  | COF-SD2 | [NAME] Fl. | PLC37 |  | BUR_3_3 | DO |  | BUR | 3 | 3 | 1 | 3 | 1 | [NAME] General Alarm Horn 1st Floor | [NAME] | Existing |  |  | Y467 | HORN-467 | Delaval General Alarm Horn 1st Floor | DO | 0 | 0 | 1st | Sonalert | Sc11onp-9045-22 | 0 | 0 | 0 | x | 0 | 0 | 0
 |  | COF-SD2 | Main Burner on Pilot Light | PLC37 |  | BUR_3_4 | DO | PL3705E | BUR | 3 | 4 | 5 | 5 | 1 | [NAME] Burner On Pilot Light | [NAME] | Existing |  |  | Y628 | PL-628 | Main Burner On Pilot Light | DO | 0 | 0 | 1st | Square-D push botton | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0
 |  | COF-SD2 | General [NAME] Light 1st Fl. (White) | PLC37 |  | BUR_3_5 | DO |  | BUR | 3 | 5 | 1 | 3 | 1 | [NAME] General [NAME] (White)1st Floor | [NAME] | Existing |  |  | Y468 | STRB-468 | General [NAME] (White)1st Floor | DO | 0 | 0 | 1st | Federal Singal | vals | 0 | 0 | 0 | x | 0 | 0 | 0
 |  | COF-SD2 | [NAME]. | PLC37 |  | BUR_3_6 | DO |  | BUR | 3 | 6 | 1 | 3 | 1 | [NAME] Alarm Horn 1st Floor | [NAME] | Existing |  |  | Y469 | HORN-469 | O/P Burner Alarm Horn 1st Floor | DO | 0 | 0 | 1st | Sonalert | Sc11onp-9045-22 | 0 | 0 | 0 | x | 0 | 0 | 0
 |  | COF-SD2 | [NAME] Light 1st FL. (Red) | PLC37 |  | BUR_3_7 | DO |  | BUR | 3 | 7 | 1 | 3 | 1 | [NAME] Alarm Strobe Light (Red) 1st Floor | [NAME] | Existing |  |  | Y470 | STRB-470 | O/P Burner Alarm Strobe Light (Red) 1st Floor | DO | 0 | 0 | 1st | Federal Singal | vals | 0 | 0 | 0 | x | 0 | 0 | 0
 |  | COF-SD2 | Customer safety interlock to burner control | PLC37 |  | BUR_3_8 | DO |  | BUR | 3 | 8 | 1 | N/A | N/A | [NAME] safety interlock to burner control | [NAME] | New
 |  |  | [NAME]
ZSC45.01 |  | COF-SD2 | Liq. Feed Steam Sup. Block Valve Closed LS | PLC37 |  | FL1_3_0 | DI | ZSC3704B | FL1 | 3 | 0 | 1 | N/A | N/A | [NAME] valve to turn on steam to liquor line heat closed limit | [NAME] | New |  | FC
ZSO45.01 |  | COF-SD2 | Liq. Feed Steam Sup. Block Valve Open LS | PLC37 |  | FL1_3_1 | DI | ZSO3704B | FL1 | 3 | 1 | 1 | N/A | N/A | [NAME] valve to turn on steam to liquor line heat open limit | [NAME] | New |  | FC
LSL31.05 |  | COF-SD2 | Jacket 1 Water Makeup Low Level Sw. | PLC37 |  | FL1_3_2 | DI | LSL3700A | FL1 | 3 | 2 | 1 | 3 | 1 | Jacket System 1 - Level control on water tank | Jacket System 1 | Existing |  |  | X455 | PS-455 | Jacket 1 Water Make Up tank pressure switch | DI | 0 | 0 | 1st | United Electric | S136b | 0 | 0 | 0 | x | 0 | 0 | 0
LSH41.06 |  | COF-SD2 | South Liquor Tank High Level Sw. | PLC37 |  | FL1_3_3 | DI | LSH3704B | FL1 | 3 | 3 | 1 | 3 | 1 | [NAME] level sensor on South feed tank | [NAME] | Existing |  |  | X451 | SLTK-HL | South Liquor Tank High Level Switch | DI | 0 | 0 | 1st | Drexel Brook | 285-1-42 | 0 | 0 | 0 | x | 0 | 0 | 0
LSH41.01 |  | COF-SD2 | North Liquor Tank High Level Sw. | PLC37 |  | FL1_3_4 | DI | LSH3704A | FL1 | 3 | 4 | 1 | 3 | 1 | [NAME] level sensor on North feed tank | [NAME] | Existing |  |  | X452 | NLTK-HL | North Liquor Tank High Level Switch | DI | 0 | 0 | 1st | Drexel Brook | 285-1-42 | 0 | 0 | 0 | x | 0 | 0 | 0
PUMP48.16_AUX |  | COF-SD2 | Moyno Liquor Feed Pump VFD Aux | PLC37 |  | FL1_3_5 | DI | VFD3704F | FL1 | 3 | 5 | 1 | 3 | 1 | [NAME] feeder with VFD for feeding vibrator aux | [NAME] | Existing |  |  | X450 | 0 | Moyno Delaval Feed Pump VFD Aux | DI | 0 | 0 | 1st | Woods Drive | WFC-4005-0cht | 0 | 0 | 0 | x | 0 | 0 | 0
LS41.02 |  | COF-SD2 | North Liquor Tank Lid Closed LS | PLC37 |  | FL1_3_6 | DI | LS3704A | FL1 | 3 | 6 | 1 | 3 | 1 | [NAME] lid tank prox switch 1 | [NAME] | Existing |  | Interlock with M3704A | X454 | NLTK-CPRX | North Tank Lid Closed Prox. Switch | DI | 0 | 0 | 1st | Efector | Micro | 0 | 0 | 0 | x | 0 | 0 | 0
LS41.07 |  | COF-SD2 | South Liquor Tank Lid Closed LS | PLC37 |  | FL1_3_7 | DI | LS3704C | FL1 | 3 | 7 | 1 | 3 | 1 | [NAME] lid tank prox switch 1 | [NAME] | Existing |  | Interlock with M3704B | X453 | SLTK-CPRX | South Tank Lid Closed Prox. Switch | DI | 0 | 0 | 1st | Efector | Micro | 0 | 0 | 0 | x | 0 | 0 | 0
PB06.02-C |  | COF-SD2 | Close Dryer Inlet Damper PB | PLC37 |  | FL1_3_9 | DI | PB3705B | FL1 | 3 | 9 | 1 | 4 | 1 | [NAME] air baffle closed PB | [NAME] | Existing |  | control M3705D | X550 | PB-105 | Dryer Inlet Damper Close PB | DI | 0 | 0 | 1st | Square-D push botton | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
PB06.02-O |  | COF-SD2 | Open Dryer Inlet Damper PB | PLC37 |  | FL1_3_10 | DI | PB3705C | FL1 | 3 | 10 | 1 | 4 | 1 | [NAME] air baffle open PB | [NAME] | Existing |  | control M3705D | X549 | PB-104 | Dryer Inlet Damper Open PB | DI | 0 | 0 | 1st | Square-D push botton | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
PB79.09-C |  | COF-SD3 | Close Tower Exhaust Damper PB | PLC37 |  | FL1_3_11 | DI | PB3703E | FL1 | 3 | 11 | 1 | 4 | 1 | Agglom Tower - Tower Exhaust damper close command | [NAME] | Existing |  | control M3703H | X548 | PB-103 | Agglomerator Exhaust Damper Close PB | DI | 0 | 0 | 1st | Square-D push botton | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
PB79.09-O |  | COF-SD3 | Open Tower Exhaust Damper PB | PLC37 |  | FL1_3_12 | DI | PB3703F | FL1 | 3 | 12 | 1 | 4 | 1 | Agglom Tower - Tower Exhaust damper open command | [NAME] | Existing |  | control M3703H | X547 | PB-102 | Agglomerator Exhaust Damper Open PB | DI | 0 | 0 | 1st | Square-D push botton | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
 |  | COF-SD2 | Silence Horn PB | PLC37 |  | FL1_4_0 | DI |  | FL1 | 4 | 0 | 1 | N/A | N/A | Misc - Silence Horn PB | Misc | Existing |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZSO31.08 |  | COF-SD2 | V31.08 Open L.S. | PLC37 |  | FL1_4_1 | DI | [NAME] | FL1 | 4 | 1 | 1 | N/A | N/A | Jacket System 1 - Blocking valve for water supply side of jacket open limit | Jacket System 1 | New |  | FC, need LS |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZSC31.08 |  | COF-SD2 | V31.08 Closed L.S. | PLC37 |  | FL1_4_2 | DI | [NAME] | FL1 | 4 | 2 | 1 | N/A | N/A | Jacket System 1 - Blocking valve for water supply side of jacket close limit | Jacket System 1 | New |  | FC, need LS |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZSO31.33 |  | COF-SD2 | V31.33 Open L.S. | PLC37 |  | FL1_4_3 | DI | [NAME] | FL1 | 4 | 3 | 1 | N/A | N/A | Jacket System 1 - Blocking valve for steam supply open limit | Jacket System 1 | New |  | FC, need LS |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZSC31.33 |  | COF-SD2 | V31.33 Closed L.S. | PLC37 |  | FL1_4_4 | DI | ZSC3700D | FL1 | 4 | 4 | 1 | N/A | N/A | Jacket System 1 - Blocking valve for steam supply close limit | Jacket System 1 | New |  | FC, need LS |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
PS31.43 |  | COF-SD2 | Egron Chamber Negative Press. Sw. | PLC37 |  | FL1_4_5 | DI | PS3700B | FL1 | 4 | 5 | 1
 |  | COF-SD2 | Horn Output | PLC37 |  | FL1_6_0 | DO |  | FL1 | 6 | 0 | 1 | N/A | N/A | Misc - Horn Output | Misc | Existing
YV44.14 |  | COF-SD2 | CO2 Blocking Solenoid Valve | PLC37 |  | FL1_6_1 | DO | SV3704D | FL1 | 6 | 1 | 1 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | HOA[4].5
YV31.39 |  | COF-SD2 | Egron Air Knocker Sol. Valve | PLC37 |  | FL1_6_3 | DO | SV3700K | FL1 | 6 | 3 | 2 | 3 | 1 | Egron - Egron Tower air knocker solenoid | Egron | Existing |  | FC | Y422 | SV-422 | [NAME] for Dryer Air Knocker | DO | 0 | 0 | 2nd | Numatics | 0 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[4].0
YV31.06 |  | COF-SD2 | Jacket Tank 1 Make Up Water Sol. Valve | PLC37 |  | FL1_6_5 | DO | SV3700A | FL1 | 6 | 5 | 1 | 3 | 1 | Jacket System 1 - Water makeup for jacket tank solenoid valve | Jacket System 1 | Existing |  | FC | Y423 | SV-423 | Tank 1 Make Up Water Solenoid Valve | DO | 0 | 0 | 1st | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[4].1
PUMP48.16 |  | COF-SD2 | Moyno Liquor Feed Pump VFD Run Signal | PLC37 |  | FL1_6_6 | Motor, VFD | VFD3704F | FL1 | 6 | 6 | 1 | 3 | 1 | [NAME] feed pump for the halo VFD | [NAME] | Existing |  |  | Y457 | 0 | Moyno Delaval Feed Pump VFD Run | DO | 0 | 0 | 1st | Woods Drive | wfc4005-0cht | 0 | wm111153 | 0 | x | 0 | 0 | 0 | HOA[6].5 | [0] |  |  | [0]
V31.08 |  | COF-SD2 | Jacket 1 Supply Blocking Valve | PLC37 |  | FL1_6_7 | DO | SV3700G | FL1 | 6 | 7 | 1 | 3 | 1 | Jacket System 1 - Blocking valve for water supply side of jacket | Jacket System 1 | Existing |  | FC, need LS | Y471 | SVB-471 | Jacket Pump 1 Water Rec. Blocking Valve 1st Floor | DO | 0 | 0 | 1st | Numatics | 0 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[4].2 |  | FTO[0] | FTC[0]
V31.33 |  | COF-SD2 | Jacket 1 Steam Supply Blocking Valve | PLC37 |  | [NAME] | DO | SV3700D | FL1 | 6 | 8 | 1 | N/A | N/A | Jacket System 1 - Blocking valve for the steam supply | Jacket System 1 | New |  | FC |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | HOA[4].3 |  | FTO[1] | FTC[1]
V45.01 |  | COF-SD2 | Liquor Feed Steam Supply Blocking Valve | PLC37 |  | FL1_6_9 | DO | SV3704B | FL1 | 6 | 9 | 1 | N/A | N/A | [NAME] valve to turn on steam to liquor line heat | [NAME] | New |  | FC |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | HOA[4].4 |  | FTO[2] | FTC[2]
 |  | COF-SD2 | Bryair [NAME]. Control Relay | PLC37 |  | FL1_6_10 | DO |  | FL1 | 6 | 10 | 2 | 4 | 1 | Misc - Control for Air Unit For Dryer Room Bry-air Unit | Misc | Existing |  |  | Y542 | RY542 | Control for Air Unit For Dryer Room Bryair Unit | DO | 0 | 0 | 2nd | Square-D relay | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
 |  | COF-SD2 | Bryair Compressor Start Relay | PLC37 |  | FL1_6_11 | DO |  | FL1 | 6 | 11 | 2 | 4 | 1 | Misc - O/P Bry-Air Compressor | Misc | Existing |  |  | Y543 | RY543 | O/P Bry-Air Compressor | DO | 0 | 0 | 2nd | Square-D relay | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
 |  | COF-SD2 | EM. Bur SD & Divert To Atmosphere P.L. | PLC37 |  | FL1_6_12 | DO | PL3700U | FL1 | 6 | 12 | 5 | 4 | 1 | Egron - Emergency Divert to Atmosphere and [NAME] PL 5th Floor | Egron | Existing |  |  | Y541 | EDPB-541 | Emergency Divert to Atmosphere and [NAME] PL 5th Floor | DO | 0 | 0 | 5th | Square-D push botton | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
PT48.07 |  | COF-SD2 | Egron Spray Mix Pump Press Transmitter | PLC37 |  | FL1_7_0 | AI | PT3704B | FL1 | 7 | 0 | 5 | 4 | 1 | Egron - Spray Mix Pump Press 5th Fl. | Egron | Existing |  | PID control with M3706A VFD | WX553 | PT-103 | Delaval Chamber Pressure (-.25 to +.25" H2O) | AI | 0 | 0 | 1st | [NAME] | 1XLDP | 70510163 | 0 | 0 | 0 | x | 0 | 0
PT44.15 |  | COF-SD2 | CO2 Pressure Transmitter | PLC37 |  | FL1_7_1 | AI | PT3704C | FL1 | 7 | 1 | 1 | 4 | 1 | [NAME] pressure transmitter | [NAME] | Existing |  | Not use | WX554 | PT-104 | CO2 Pressure | AI | 0 | 0-400 psi | 1st | Rosemount | 0 | 0 | 0 | 0 | 0 | x | 0 | 0
SC48.16 |  | COF-SD2 | Liquor Feed Pump VFD (Actual Speed) | PLC37 |  | FL1_7_2 | AI | SC3704F | FL1 | 7 | 2 | 1 | 4 | 1 | [NAME] feed pump for the halo VFD sp command | [NAME] | Existing |  | VFD Speed reference (0-10 VDC) | WX555 | 0 | Feedback from Liquor Feed Pump VFD  (Pump P-A15) | AI | 0 | 0 | 1st | Woods Drive | WFC4005-0CHT | 0 | Wm111153 | 0 | x | 0 | 0 | 0
FT47.03 |  | COF-SD2 | Distillate Flow Transmitter | PLC37 |  | FL1_7_3 | AI | FT3704C | FL1 | 7 | 3 | 1 | 4 | 1 | [NAME] meter for distillate | [NAME] | Existing |  | PID control 11 | WX559 | 0 | Distillate Injection Flow Rate (MicroMotion 0-10 Lbs/Min) | AI | 0 | 0-10  min | 1st | Micro Motion | 2700R11buezzz | 0 | wm111776 | 0 | x | 0 | 0 | 0
DT47.03 |  | COF-SD2 | Distillate Density Transmitter | PLC37 |  | FL1_7_4 | AI | FT3704D | FL1 | 7 | 4 | 1 | 4 | 1 | [NAME] meter for distillate | [NAME] | Existing |  |  | WX560 | 0 | Distillate Injection Density (MicroMotion 0-5.00 SGU) | AI | 0 | 0-5 sgu | 1st | Micro Motion | 2700R11buezzz | 0 | wm111776 | 0 | x | 0 | 0 | 0
FT42.15 |  | COF-SD2 | Liquor Feed Flow Transmitter | PLC37 |  | FL1_7_5 | AI | FT3704A | FL1 | 7 | 5 | 1 | 4 | 1 | [NAME] meter for liquor | [NAME] | Existing |  | PID control 9 | WX556 | 0 | Liquor Feed Flow Rate (MicroMotion 0-50 Lbs/Min) | AI | 0 | 1-50min | 1st | Micro Motion | RFT9739E1300 | 0 | WM109567 | 0 | x | 0 | 0 | 0
DT42.15 |  | COF-SD2 | Liquor Feed Density Transmitter | PLC37 |  | FL1_7_6 | AI | FT3704B | FL1 | 7 | 6 | 1 | 4 | 1 | [NAME] meter for liquor | [NAME] | Existing |  |  | WX557 | 0 | Liquor Feed Flow Density (MicroMotion 0-5.00 SGU) | AI | 0 | 0-5sgu | 1st | Micro Motion | RFT9739E1300 | 0 | WM109567 | 0 | x | 0 | 0 | 0
CV54.39 |  | COF-SD2 | AZO Vacuum Control Valve | PLC37 |  | FL1_8_0 | AO | PCV3702A | FL1 | 8 | 0 | 1 | 3 | 1 | Vacuum control valve | AZO | Existing |  | No PID control.  Control from HMI only | WY476 | 0 | [NAME]. Control Valve | 0 | 0 | 0 | 2nd | Numatics Valve | 0 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[6].0
CV07.08 |  | COF-SD2 | Combustion Air Flow Control Valve (Burner) | PLC37 |  | FL1_8_1 | AO | FCV3705A | FL1 | 8 | 1 | 4 | 3 | 1 | Egron Burner - Combustion air flow modulation | [NAME] | Existing |  | PID control 1 | WY474 | TCV-100 | Combustion Air Flow Modulation | AO | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | HOA[6].1 |  |  |  |  | [0]
[NAME] |  | COF-SD2 | Jacket 1 Heat Exchanger Steam Ctrl. Valve | PLC37 |  | FL1_8_2 | AO | TCV3700A | FL1 | 8 | 2 | 1 | 3 | 1 | Jacket System 1 - heat exchanger steam control valve | Jacket System 1 | Existing |  | PID control 2, ordered | WY473 | TCV-101 | Dry Cine Heat Exchanger Steam Valve | AO | 0 | 0 | 1st | Kammer    1/2"   ATO  CV=2.5 [NAME] | 20047 | 1539a3 | 0 | 0 | 0 | Yes (TB) | 0 | 0 | HOA[6].2 |  |  |  |  | [1]
CV45.04 |  | COF-SD2 | Liquor Feed Jacket Steam Ctrl. Valve | PLC37 |  | FL1_8_3 | AO | TCV3704A | FL1 | 8 | 3 | 1 | 3 | 1 | [NAME] valve for steam to heat line water | [NAME] | Existing |  | PID control 10 | WY478 | 0 | Jacket Feed Temp Control I/P | AO | 0 | cv1.6 | 1st | Kammer | 20047 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[6].3 |  |  |  |  | [2]
PUMP4704_CMD |  | COF-SD2 | Moyno Distillate Direct Injection Pump Spd Cmd | PLC37 |  | FL1_8_4 | AO | SC3704E_CMD | FL1 | 8 | 4 | 1 | 3 | 1 | [NAME] distillate pump feeding distillate for direct injection | [NAME] | Existing |  | PID control 11 | WY479 | 0 | Speed for Distillate Injection Pump | AO | 0 | 0 | 1st | Sew smatr drive | 0 | 0 | WM111770 | 0 | x | 0 | 0 | 0 | HOA[9].2 |  |  |  |  | [9]
SC48.16_CMD |  | COF-SD2 | Liquor Feed Pump Speed Signal | PLC37 |  | FL1_8_5 | AO | SC3704F_CMD | FL1 | 8 | 5 | 1 | 3 | 1 | [NAME] feed pump for the halo VFD sp command | [NAME] | Existing |  | PID control 9 | WY477 | 0 | Liquor Feed Pump VFD | AO | 0 | 0 | 1st | Woods Drive | WFC4005-0CHT | 0 | WM111153 | 0 | x | 0 | 0 | 0 | HOA[6].5 |  |  |  |  | [10]
 |  | COF-SD2 | 0-5 VDC CO2 Control Setpoint to CO2 System | PLC37 |  | FL1_8_6 | AO |  | FL1 | 8 | 6 | 1 |  |  | [NAME] control setpoint | [NAME] | New |  | Brooks Instrument local controller connects to pin 22, 23 (remote setpoint input +, -) |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
TE77.06 |  | COF-SD3 | Tower Inlet Temperature Element | PLC37 |  | FL1_9_0 | TE | TE3703C | FL1 | 9 | 0 | 2 | 3 | 1 | Agglom Tower - Temp probe for inlet tower temp | [NAME] | Existing |  | PID control 8 | WX481 | TE-106 | Agglomerator Inlet Temp (RTD) | AI | 0 | 0 | 2nd | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
TE77.04 |  | COF-SD3 | Tower Chamber Temperature Element | PLC37 |  | FL1_9_1 | TE | TE3703D | FL1 | 9 | 1 | 2 | 3 | 1 | Agglom Tower - Temp probe for tower | [NAME] | Existing |  |  | WX487 | TE-109 | Agglomeration [NAME] (RTD) | AI | 0 | 0 | 2nd | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
TE31.13 |  | COF-SD2 | Jacket 1 Cone Water Outlet Temperature Element | PLC37 |  | FL1_9_2 | TE | TE3700D | FL1 | 9 | 2 | 2 | 3 | 1 | Jacket System 1 - Cone outlet temperature | Jacket System 1 | Existing |  |  | WX484 | TE-107 | Cone Jacket Water Out Temp (RTD) | AI | 0 | 0 | 2nd | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
TE45.04 |  | COF-SD2 | Jacket Water Temperature Element | PLC37 |  | FL1_9_3 | TE | TE3704C | FL1 | 9 | 3 | 1 | 3 | 1 | [NAME] feed water temp for liquor feed | [NAME] | Existing |  | PID control 10 | WX489 | TE-132 | Jacket Feed Water RTD | AI | 0 | 0 | 1st | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
TE31.09 |  | COF-SD2 | Egron Jacket 1 Inlet Water Temperature Element | PLC37 |  | [NAME] | TE | TE3700A | FL1 | 9 | 4 | 1 | 3 | 1 | Jacket System 1 - Jacket inlet temp for steam control | Jacket System 1 | Existing |  | PID control 2 | WX485 | TE-101 | Jacket 1 Water Temp (RTD) | AI | 0 | 0 | 1st | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
TE59.05 |  | COF-SD2 | Witte Exhaust Process Temperature Element | PLC37 |  | FL1_9_5 | TE | TE3702D | FL1 | 9 | 5 | 2 | 3 | 1 | Witte - Witte exhaust process temp | Witte | Existing |  |  | WX486 | TE-108 | Witte Exhaust Air Temp (RTD) | AI | 0 | 0 | 2nd | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
TE58.06 |  | COF-SD2 | Witte Zone 1 Inlet Air Temperature Element | PLC37 |  | FL1_10_0 | TE | TE3702A | FL1 | 10 | 0 | 1 | 3 | 1 | Witte - Zone 1 inlet air temp | Witte | Existing |  | PID control 6 | WX482 | TE-104 | Witte Zone 1 Inlet Temp (RTD) | AI | 0 | 0 | 1st | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
TE58.08 |  | COF-SD2 | Witte Zone 2 Inlet Air Temperature Element | PLC37 |  | FL1_10_1 | TE | TE3702B | FL1 | 10 | 1 | 1 | 3 | 1 | Witte - Zone 2 inlet temp | Witte | Existing |  | PID control 7 | WX483 | TE-105 | Witte Zone 2 Inlet Temp (RTD) | AI | 0 | 0 | 1st | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
TE63.09 |  | COF-SD2 | North Collector Bottom Temperature Element | PLC37 |  | FL1_10_2 | TE | TE3706G | FL1 | 10 | 2 | 1
TE63.06 |  | COF-SD2 | South Collector Bottom Temperature Element | PLC37 |  | FL1_10_3 | TE | TE3706H | FL1 | 10 | 3 | 1
TE63.11 |  | COF-SD2 | Collector System Educator Surface Temperature Element | PLC37 |  | FL1_11_1 | TE | TE3706F | FL1 | 11 | 1 | 1 | N/A | N/A | Collector System - Surface temperature probe on eductor | Collector System | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | Rotex Eductor Surface Temp. | PLC37 |  | FL1_11_2 | TE | TE3701A | FL1 | 11 | 2 | 1 | N/A | N/A | Rotex - Rotex eductor surface temperature | Rotex | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
TE59.04 |  | COF-SD2 | Witte Cyclone Fines Eductor Surface Temperature Element | PLC37 |  | FL1_11_3 | TE | TE3702E | FL1 | 11 | 3 | 1 | N/A | N/A | Witte - Surface temp probe on eductor for cyclone fines 0-250 | Witte | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
TE31.41 |  | COF-SD2 | [NAME]. Temp. (Bryair unit) (1st floor) | PLC37 |  | FL1_11_4 | TE | TE3707A | FL1 | 11 | 4 | 2 | 3 | 1 | [NAME] room temperature (Bry-Air) | Misc | Existing |  |  | [NAME] | TE-110 | Delaval Room Temp (RTD) (Bry-Air Unit) | AI | 0 | 0 | 1st | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
TE16.01 |  | COF-SD2 | South Collector Process Outlet Temperature Element | PLC37 |  | FL1_12_0 | TE | TE3706E | FL1 | 12 | 0 | 3 | 4 | 1 | Collector System - Outlet north collector process | Collector System | Existing |  |  | WX517 | TE-114 | North Collector Temp 3rd Floor (TC) Type K | AI | 0 | 0 | 3rd | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
TE17.01 |  | COF-SD2 | North Collector Process Outlet Temperature Element | PLC37 |  | FL1_12_1 | TE | TE3706C | FL1 | 12 | 1 | 3 | 4 | 1 | Collector System - Outlet south collector process | Collector System | Existing |  |  | [NAME] | TE-115 | South Collector Temp 3rd Floor (TC) Type K | AI | 0 | 0 | 3rd | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
TE06.07 |  | COF-SD2 | Burner Coldside HX Outlet Air Temperature Element | PLC37 |  | [NAME] | TE | TE3705A | FL1 | 12 | 2 | 4 | 4 | 1 | [NAME] side HX out temp | [NAME] | Existing |  | PID control 1 | WX516 | TE-100 | Burner Outlet Air to Dryer Inlet 4th Floor (TC) Type K | AI | 0 | 0 | 4th | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
TE07.01 |  | COF-SD2 | Burner Hotside HX Inlet Air Temperature Element | PLC37 |  | FL1_12_3 | TE | TE3705D | FL1 | 12 | 3 | 4 | 4 | 1 | [NAME] side HX in temp | [NAME] | Existing |  |  | WX519 | TE-116 | Burner Hotside 1 Exhaust Air 4th Floor (TC) Type K | AI | 0 | 0 | 4th | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
TE31.01 |  | COF-SD2 | Egron Chamber Temperature Element | PLC37 |  | FL1_12_4 | TE | TE3700G | FL1 | 12 | 4 | 3 | 4 | 1 | Egron - Temp probe for tower | Egron | Existing |  |  | [NAME] | TE-113 | Dryer Chamber Temp 3rd Floor (TC) Type K | AI | 0 | 0 | 3rd | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
 |  |  | [NAME]
MOT71.04 |  | COF-SD2 | North CTI Feed Motor Contact | PLC37 |  | FL2_1_0 | DI | M3700F | FL2 | 1 | 0 | 5 | 1 | 2 | [NAME] feed motor | [NAME] | Existing |  |  | X267 | NORTH | NORTH AGGLOMERATOR MOTOR | DI | 0 | 0 | 2nd | [NAME] | 140-min-0160 | 0 | 0 | 0 | x | 0 | 0 | 0
MOT71.03 |  | COF-SD2 | Center CTI Feed Motor Contact | PLC37 |  | FL2_1_1 | DI | M3700L | FL2 | 1 | 1 | 5 | 1 | 2 | [NAME] feed motor | [NAME] | Existing |  |  | X268 | CENTER | CENTER AGGLOMERATOR MOTOR | DI | 0 | 0 | 2nd | [NAME] | 140-min-0160 | 0 | 0 | 0 | x | 0 | 0 | 0
MOT71.02 |  | COF-SD2 | South CTI Feed Motor Contact | PLC37 |  | FL2_1_2 | DI | M3700G | FL2 | 1 | 2 | 5 | 1 | 2 | [NAME] feed motor | [NAME] | Existing |  |  | X269 | SOUTH | SOUTH  AGGLOMERATOR MOTOR | DI | 0 | 0 | 2nd | [NAME] | 140-min-0160 | 0 | 0 | 0 | x | 0 | 0 | 0
MOT63.48 |  | COF-SD3 | Tower Baghouse Exhaust Fan Motor Aux | PLC37 |  | FL2_1_3 | DI | M3700H_AUX | FL2 | 1 | 3 | 5 | 1 | 2 | Agglom Tower - Baghouse exhaust fan aux | [NAME] | Existing |  |  | X153 | M-A39 | Agglomerator Exhaust Fan Aux. | DI | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421041 | 0 | 0 | x | 0 | 0 | 0
MOT63.61 |  | COF-SD3 | Tower Cyclone Flip-Flop Valve Motor Aux | PLC37 |  | FL2_1_4 | DI | M3703E_AUX | FL2 | 1 | 4 | 3 | 1 | 2 | Agglom Tower - Flip flop valve of cyclone system outlet aux | [NAME] | Existing |  |  | X119 | FLFP-A7 | Agglomerator [NAME]. | DI | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421013 | 0 | 0 | x | 0 | 0 | 0
MOT18.02 |  | COF-SD3 | Tower Inlet Air Blower Motor Aux. | PLC37 |  | FL2_1_5 | DI | M3703D_AUX | FL2 | 1 | 5 | 2 | 1 | 2 | Agglom Tower - Motor on inlet fan aux | [NAME] | Existing |  |  | X139 | M-A24 | Agglomerator Inlet Air Blower Aux. | DI | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421030 | 0 | 0 | x | 0 | 0 | 0
MOT79.08 |  | COF-SD3 | Tower Exhaust Air Blower Motor Aux. | PLC37 |  | FL2_1_6 | DI | M3703C_AUX | FL2 | 1 | 6 | 5 | 1 | 2 | Agglom Tower - Motor on outlet fan aux | [NAME] | Existing |  |  | X152 | M-A38 | Agglomerator Exhaust Fan Aux. | DI | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421040 | 0 | 0 | x | 0 | 0 | 0
MOT63.49 |  | COF-SD3 | CTI Baghouse Star Valve Motor Aux | PLC37 |  | FL2_1_7 | DI | M3700D_AUX | FL2 | 1 | 7 | 2 | 1 | 2 | Agglom Tower - Tower feed baghouse star valve aux | [NAME] | Existing |  |  | X121 | ROTVL-A9 | Baghouse Rotary Valve Aux. (Valve located on 5th Floor Delaval) | DI | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421015 | 0 | 0 | x | 0 | 0 | 0
MOT45.14 |  | COF-SD2 | Liquor Line Jacket Water Pump Motor Aux | PLC37 |  | FL2_1_8 | DI | M3704G_AUX | FL2 | 1 | 8 | 1 | 1 | 2 | [NAME] line jacket water pump | [NAME] | Existing |  |  | X123 | 0 | H2o Jacket pump | 0 | 0 | 0 | 2nd | Square-D starter mcca | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
[NAME] |  | COF-SD2 | CIP Pump Motor Aux. | PLC37 |  | FL2_1_9 | DI | M3707D_AUX | FL2 | 1 | 9 | 1 | 1 | 2 | CIP - CIP Pump aux | CIP | Existing |  |  | X117 | P-A43 | C.I.P Pump Aux. | DI | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421045 | 0 | 0 | x | 0 | 0 | 0
MOT76.04 |  | COF-SD3 | Tower Feed Auger VFD Motor Aux | PLC37 |  | FL2_1_10 | DI | M3703A_AUX | FL2 | 1 | 10 | 4 |  |  |  |  |  |  |  | X146 | M-A30
MOT65.10 |  | COF-SD2 | [NAME]. Pump Motor Aux | PLC37 |  | FL2_1_11 | DI | M3701F_AUX | FL2 | 1 | 11 | 5 | 1 | 2 | [NAME] for water circulation aux | Rotex | Existing |  |  | X113 | P-A2 | [NAME]. [NAME]. | DI | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421008 | 0 | 0 | x | 0 | 0 | 0
SC71.10_AUX |  | COF-SD2 | CTI Auger VFD Aux | PLC37 |  | FL2_1_12 | DI | SC3700F | FL2 | 1 | 12 | 5 |  |  |  | [NAME] | Existing |  |  | X147
MOT07.05 |  | COF-SD2 | Egron Burner Process Air Blower Motor Aux | PLC37 |  | FL2_1_13 | DI | M3705C | FL2 | 1 | 13 | 4 | 1 | 2 | [NAME] fan | [NAME] | Existing |  |  | X161 | M-C2 | Process Air Blower Run Aux. | DI | 0 | 0 | 2nd | Square-D starter mcca | 5 | E-909532 | 0 | 0 | x | 0 | 0 | 0
FS31.12 |  | COF-SD2 | Egron Jacket 1 Top Zone Flow Sw. 2nd FL | PLC37 |  | FL2_1_14 | DI | LS3700B | FL2 | 1 | 14 | 2 | 1 | 2 | Egron - Jacket system 1 top zone flow switch (FS-J1TZ) | Egron | Existing |  |  | X171 | LS1A | Level Switch 1 Jacket Water Supply Second Floor | DI | 0 | 0 | 2nd | Omega | LCV 512 | 0 | 0 | 0 | x | 0 | 0 | 0
FS31.11 |  | COF-SD2 | Egron Jacket 1 Bottom Zone Flow Sw. 1st FL | PLC37 |  | FL2_1_15 | DI | LS3700A | FL2 | 1 | 15 | 2 | 1 | 2 | Egron - Jacket system 1 bottom zone flow switch (FS-J1BZ) | Egron | Existing |  |  | X172 | LS1B | Level Switch 1 Jacket Water Supply Second Floor | DI | 0 | 0 | 2nd | Omega | LCV 512 | 0 | 0 | 0 | x | 0 | 0 | 0
MOT31.07 |  | COF-SD2 | Egron Jacket 1 Water Pump Motor Aux | PLC37 |  | FL2_2_0 | DI | PUMP3700A | FL2 | 2 | 0 | 1 | 1 | 2 | Jacket System 1 - Jacket water pump Aux | Jacket System 1 | Existing |  |  | X143 | P-A28 | Jacket Pump 1 Aux. | DI | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421034 | 0 | 0 | x | 0 | 0 | 0
MOT31.17 |  | COF-SD2 | Egron Jacket 2 Water Pump Motor Aux | PLC37 |  | FL2_2_1 | DI | M3700B_AUX | FL2 | 2 | 1 | 3 | 1 | 2 | Jacket System 2 - Jacket water pump Aux | Jacket System 2 | Existing |  |  | X142 | P-A27 | Jacket [NAME]. | DI | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421033 | 0 | 0 | x | 0 | 0 | 0
MOT31.26 |  | COF-SD2 | Egron Jacket 3 Water Pump Motor Aux | PLC37 |  | FL2_2_2 | DI | M3700C_AUX | FL2 | 2 | 2 | 4 | 1 | 2 | Jacket System 3 - Jacket water pump Aux | Jacket System 3 | Existing |  |  | X145 | P-A29 | Jacket 3 Pump Aux. | DI | 0 | 0 | 2nd | Square-D starter mcca | 5 | [NAME] | 0 | 0 | x | 0 | 0 | 0
 |  | COF-SD2 | Spare Receptacle 5th FL.(Bucket A5) | PLC37 |  | FL2_2_3 | DI | spare | FL2 | 2 | 3 | 5 | 1 | 2 | Agglom Tower - Tower feed baghouse star valve motion switch | [NAME] | Existing |  |  | X116 | 0 | Agglomerator Star Valve Aux. 5th Floor | 0 | 0 | 0 | 2nd | Square-D starter mcca | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
MOT47.04 |  | COF-SD2 | Distillate Inject. Pump Motor Aux. | PLC37 |  | FL2_2_4 | DI | M3704E_AUX | FL2 | 2 | 4 | 1 | 1 | 2 | [NAME] distillate pump feeding distillate for direct injection | [NAME] | Existing |  |  | X132 | P-A17 | Distillate Injection Pump | DI | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421023 | 0 | 0 | x | 0 | 0 | 0
MOT48.16 |  | COF-SD2 | Moyno Pump Motor Aux. | PLC37 |  | FL2_2_5 | DI | M3704F_AUX | FL2 | 2 | 5 | 1 | 1 | 2 | [NAME] feed pump for the halo motor aux | [NAME] | Existing |  |  | X129 | P-A15 | Moyno Pump Aux. | DI | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421021 | 0 | 0 | x | 0 | 0 | 0
MOT41.09 |  | COF-SD2 | S. Liquor Tank Slow Speed Motor Aux | PLC37 |  | FL2_2_6 | DI | M3704B_AUX | FL2 | 2 | 6 | 1 | 1 | 2 | [NAME] on south feed tank aux | [NAME] | Existing |  | On/Off no Auto | X166 | SSAG-A52 | South Agitator Liquor Tank Slow Speed Aux. | DI | 0 | 0 | 2nd | Square-D starter mcca | 5 | H-400433 | 0 | 0 | x | 0 | 0 | 0
MOT51.01 |  | COF-SD2 | Sweco Sifter Motor Aux | PLC37 |  | FL2_2_7 | DI | M3714F | FL2 | 2 | 7 | 1 | 1 | 1 | Agglom Tower - Sweco Sifter Aux | [NAME]
MOT41.04 |  | COF-SD2 | N. Liquor Tank Slow Speed Motor Aux | PLC37 |  | FL2_2_8 | DI | M3704A_AUX | FL2 | 2 | 8 | 1 | 1 | 2 | [NAME] on north feed tank aux | [NAME] | Existing |  | On/Off no Auto | X168 | NSAG-A55 | North Agitator Liquor Tank Slow Speed Aux. | DI | 0 | 0 | 2nd | Square-D starter mcca | 5 | H-400432 | 0 | 0 | x | 0 | 0 | 0
MOT48.01 |  | COF-SD2 | Oaks Mixer Motor Aux. | PLC37 |  | FL2_2_10 | DI | M3704D_AUX | FL2 | 2 | 10 | 1 | 1 | 2 | [NAME] mixer for mixing distillate and liquor aux | [NAME] | Existing |  |  | X118 | M-A6 | Oaks Mixer - Distillate Injection | DI | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421012 | 0 | 0 | x | 0 | 0 | 0
MOT42.08 |  | COF-SD2 | Stuffing Pump Motor Aux | PLC37 |  | FL2_2_11 | DI | PUMP3704C | FL2 | 2 | 11 | 1 | 1 | 2 | [NAME] pump for mayno aux | [NAME] | Existing |  |  | X131 | P-A16 | Stuffing Pump Aux. | DI | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421022 | 0 | 0 | x | 0 | 0 | 0
MOT64.03 |  | COF-SD2 | Rotex Fines Star Valve Motor Aux | PLC37 |  | FL2_2_13 | DI | STRV3701D | FL2 | 2 | 13 | 2 | 1 | 2 | Rotex - Fines star valve under rotex aux | Rotex | Existing |  |  | X114 | STAR-A3 | Fines Star Valve under Rotex Aux. | DI | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421009 | 0 | 0 | x | 0 | 0 | 0
MOT55.00 |  | COF-SD2 | Howes Sifter Motor Aux | PLC37 |  | FL2_2_14 | DI | M3701J_AUX | FL2 | 2 | 14 | 1 | 1 | 2 | Rotex - Overs grinder Howes Sifter SC-A35 | Rotex | Existing |  |  | X127 | HSFT-A13 | [NAME] | DI | 0 | 0 | 2nd | Square-D starter mcca | 5 | [NAME] | 0 | 0 | x | 0 | 0 | 0
MOT64.00 |  | COF-SD2 | Roots Blower Motor Aux. ([NAME]) | PLC37 |  | FL2_2_15 | DI | M3701E_AUX | FL2 | 2 | 15 | 3 | 1 | 2 | Rotex - Roots Blower Aux | Rotex | Existing |  |  | X141 | M-A26 | Agglomerator [NAME]. | DI | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421032 | 0 | 0 | x | 0 | 0 | 0
MOT51.00 |  | COF-SD2 | [NAME] | PLC37 |  | FL2_3_0 | DI | M3701A_AUX | FL2 | 3 | 0 | 1 | 1 | 2 | Rotex - Rotex | Rotex | Existing |  |  | X115 | M-A4 | [NAME]. | DI | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421010 | 0 | 0 | x | 0 | 0 | 0
MOT59.07 |  | COF-SD2 | Witte Exhaust Fan Motor Aux | PLC37 |  | FL2_3_1 | DI | M3702D_AUX | FL2 | 3 | 1 | 2 | 1 | 2 | Witte - Exhaust fan aux | Witte | Existing |  |  | X138 | M-A23 | Witte Exhaust Fan Aux. | DI | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421028 | 0 | 0 | x | 0 | 0 | 0
MOT58.05 |  | COF-SD2 | Witte Supply Air Blower Motor Aux | PLC37 |  | FL2_3_2 | DI | M3702C_AUX | FL2 | 3 | 2 | 2 | 1 | 2 | Witte - Supply fan aux | Witte | Existing |  |  | X140 | M-A25 | Witte Inlet Air Blower Aux. | DI | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421014 | 0 | 0 | x | 0 | 0 | 0
MOT19.08 |  | COF-SD2 | Witte Wet Scrubber Motor Aux 3rd FL | PLC37 |  | FL2_3_3 | DI | M3702B_AUX | FL2 | 3 | 3 | 2 | 1 | 2 | Witte - wet scrubber motor | Witte | Existing |  |  | X156 | M-A42 | Scrubber Aux. 3rd Floor | DI | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421044 | 0 | 0 | x | 0 | 0 | 0
MOT52.01 |  | COF-SD2 | Witte Vibration Motor Aux. | PLC37 |  | FL2_3_4 | DI | M3702A_AUX | FL2 | 3 | 4 | 1 | 1 | 2 | Witte - Witte vibration motor aux | Witte | Existing |  |  | X125 | M-A11 | Agglomerator [NAME]. | DI | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421017 | 0 | 0 | x | 0 | 0 | 0
MOT19.11 |  | COF-SD2 | Wet Scrubber Water Recirc. Pump Motor | PLC37 |  | [NAME] | DI | PUMP3702E | FL2 | 3 | 5 | 2 | 1 | 2 | Witte - wet scrubber water recirc pump | Witte | Existing |  |  | X150 | 0 | Dust Collector | 0 | 0 | 0 | 2nd | Square-D starter mcca | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
MOT63.22 |  | COF-SD2 | Total Fines Eductor B.H. Exhaust Motor 4th FL | PLC37 |  | FL2_3_7 | DI | M3701H_AUX | FL2 | 3 | 7 | 4 | N/A | N/A | Rotex - 4th floor exhaust motor for baghouse tie into witte exhaust aux | Rotex | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
MOT63.00 |  | COF-SD2 | Rotex Rotron Blower Motor | PLC37 |  | FL2_3_8 | DI | M3701C_AUX | FL2 | 3 | 8 | 3 | N/A | N/A | Rotex - Rotron Blower Aux | Rotex | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
MAG54.31_FAL |  | COF-SD2 | Metal Detector Fault | PLC37 |  | FL2_3_9 | DI | MC3702A_FLT | FL2 | 3 | 9 | 2 |  |  | Metal detector internal fault | AZO | New
MAG54.31_ALM |  | COF-SD2 | Metal Detector Alarm | PLC37 |  | FL2_3_10 | DI | MD3702A_ALM | FL2 | 3 | 10 | 2 | N/A | N/A | Metal detector | AZO | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
MOT63.30 |  | COF-SD2 | Total Fines B.H. Star Valve Motor 4th FL | PLC37 |  | FL2_3_11 | DI | M3701G_AUX | FL2 | 3 | 11 | 3 | N/A | N/A | Rotex - 4th floor baghouse star valve aux | Rotex | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZSC58.10 |  | COF-SD2 | V58.10 Closed L.S. | PLC37 |  | FL2_3_12 | DI | ZSC3703B | FL2 | 3 | 12 | 2 | N/A | N/A | Agglom Tower - Steam blocking valve for tower inlet closed limit | [NAME] | New |  | FC |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZSO58.10 |  | COF-SD2 | V58.10 Open L.S. | PLC37 |  | FL2_3_13 | DI | [NAME] | FL2 | 3 | 13 | 2 | N/A | N/A | Agglom Tower - Steam blocking valve for tower inlet open limit | [NAME] | New |  | FC |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZSO18.05 |  | COF-SD3 | V18.05 Open L.S. | PLC37 |  | FL2_3_14 | DI | [NAME] | FL2 | 3 | 14 | 2 |  |  |  |  |  |  |  |  |  |  |  |  |  |  | N/A | N/A | N/A | N/A
ZSC18.05 |  | COF-SD3 | V18.05 Closed L.S. | PLC37 |  | FL2_3_15 | DI | [NAME] | FL2 | 3 | 15 | 2 |  |  |  |  |  |  |  |  |  |  |  |  |  |  | N/A | N/A | N/A | N/A
 |  |  |  | PLC37 |  | FL2_4_3 | DI | M3703F | FL2 | 4 | 3 | 1 | N/A | N/A | Agglom Tower - Swaco screener motor Aux. | [NAME] | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
MOT63.57 |  | COF-SD3 | Tower Baghouse Star Valve Motor Aux | PLC37 |  | FL2_4_4 | DI | M3703B_AUX | FL2 | 4 | 4 | 5
MOT55.02 |  | COF-SD2 | Overs Eductor Blower Motor Aux | PLC37 |  | FL2_4_5 | DI | M3701K_AUX | FL2 | 4 | 5 | 1 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | HOA[10].9
SIFT51.01 |  | COF-SD2 | [NAME] | PLC37 |  | FL2_5_0 | Motor | M3707A | FL2 | 5 | 0 | 5 | 1 | 2 | Agglom. Tower - Sweco Sifter | [NAME] | Existing |  | manual control | Y223 | M-EF2 | O/P Wall Exhaust Fan 5th Floor in box on wall | DO | 0 | 0 | 2nd | in box on wall | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | HOA[9].4 | [5] |  |  | [5]
STRV63.49 |  | COF-SD3 | CTI Baghouse Star Valve 5th FL. | PLC37 |  | FL2_5_1 | Motor | M3700D | FL2 | 5 | 1 | 2 | 1 | 2 | Egron - Penthouse baghouse star valve with motion switch | Egron | Existing |  | no aux??? | Y185 | ROTVL-A9 | Bag House Rotary Valve 5th Floor | DO | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421015 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].5 | [6] |  |  | [6]
 |  | COF-SD2 | West Roof Exhaust Fan 5th Fl. ([NAME]) | PLC37 |  | FL2_5_2 | Motor | M3707B | FL2 | 5 | 2 | 5 | 1 | 2 | Misc - O/P West Exhaust Fan 5th Floor | Misc | Existing |  | manual control | Y221 | M-C3 | O/P West Exhaust Fan 5th Floor | DO | 0 | 0 | 2nd | Square-D starter mccc | 5 | G-39692 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].6 | [7] |  |  | [7]
 |  | COF-SD2 | East Roof Exhaust Fan 5th Fl. (Bucket C4) | PLC37 |  | FL2_5_3 | Motor | M3707C | FL2 | 5 | 3 | 5 | 1 | 2 | Misc - O/P East Exhaust Fan 5th Floor | Misc | Existing |  | manual control | Y222 | M-C4 | O/P East Exhaust Fan 5th Floor | DO | 0 | 0 | 2nd | Square-D starter mccc | 5 | G-39693 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].7 | [8] |  |  | [8]
MIXR41.09 |  | COF-SD2 | South Liquor Feed Tank Mixer ([NAME]) | PLC37 |  | FL2_5_4 | Motor | M3704B | FL2 | 5 | 4 | 1 | 1 | 2 | [NAME] on south feed tank | [NAME] | Existing |  | On/Off no Auto | Y233 | SSAG-A52 | South Slow Agitator | DO | 0 | 0 | 2nd | Square-D starter mcca | 5 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].8 | [9] |  |  | [9]
PUMP45.14 |  | COF-SD2 | Liquor Feed Jacket Recirc Pump (Bucket A10) | PLC37 |  | FL2_5_5 | Motor | M3704G | FL2 | 5 | 5 | 2 | 1 | 2 | [NAME] line jacket water pump | [NAME] | Existing |  |  | Y180 | 0 | Agglomerator star Valve 5th Floor | 0 | 0 | 0 | 2nd | Square-D starter mcca | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
MIXR41.04 |  | COF-SD2 | North Liquor Feed Tank Mixer (Bucket A55) | PLC37 |  | FL2_5_6 | Motor | M3704A | FL2 | 5 | 6 | 1 | 1 | 2 | [NAME] on north feed tank | [NAME] | Existing |  | On/Off no Auto | Y235 | NSAG-A55 | North Slow Agitator | DO | 0 | 0 | 2nd | Square-D starter mcca | 5 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].10 | [10] |  |  | [10]
STRV63.57 |  | COF-SD3 | Tower Baghouse Star Valve | PLC37 |  | FL2_5_7 | Motor, VFD | M3703B | FL2 | 5 | 7 | 5 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | HOA[9].9 | [45] |  |  | [45]
PUMP55.02 |  | COF-SD2 | Overs Eductor Blower | PLC37 |  | FL2_5_8 | Motor | [NAME] | FL2 | 5 | 8 | 1 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | HOA[10].9
SCRW71.04 |  | COF-SD2 | North CTI Feeder Motor | PLC37 |  | FL2_6_0 | Motor | M3700F | FL2 | 6 | 0 | 5 | 1 | 2 | [NAME] feed motor | [NAME] | Existing |  |  | Y310 | N-M310 | North Agglomerator Feeder Motor | DO | 0 | 0 | 2nd | [NAME] | 140-min-0160 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].11 | [11] |  |  | [11]
SCRW71.03 |  | COF-SD2 | Center CTI Feeder Motor | PLC37 |  | FL2_6_1 | Motor | M3700L | FL2 | 6 | 1 | 5 | 1 | 2 | [NAME] feed motor | [NAME] | Existing |  |  | Y311 | C-M311 | Center Agglomeratof Feeder Motor | DO | 0 | 0 | 2nd | [NAME] | 140-min-0160 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].12 | [12] |  |  | [12]
SCRW71.02 |  | COF-SD2 | South CTI Feeder Motor | PLC37 |  | FL2_6_2 | Motor | M3700G | FL2 | 6 | 2 | 5 | 1 | 2 | [NAME] feed motor | [NAME] | Existing |  |  | Y312 | S-M312 | South Agglomerator Feeder Motor | DO | 0 | 0 | 2nd | [NAME] | 140-min-0160 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].13 | [13] |  |  | [13]
FAN63.48 |  | COF-SD3 | Tower Baghouse Exhaust Fan (Bucket A39) | PLC37 |  | FL2_6_3 | Motor | M3700H | FL2 | 6 | 3 | 5 | 1 | 2 | Agglom Tower - Baghouse exhaust fan | [NAME] | Existing |  |  | Y217 | M-A39 | Agglomerator Exhaust Fan | DO | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421042 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].14 | [14] |  |  | [14]
FAN18.02 |  | COF-SD3 | Tower Inlet Air Blower (Bucket A24) | PLC37 |  | FL2_6_4 | Motor | M3703D | FL2 | 6 | 4 | 2 | 1 | 2 | Agglom Tower - Motor on inlet fan | [NAME] | Existing |  |  | Y203 | M-A24 | O/P Agglomerator [NAME] Blower | DO | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421028 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].15 | [15] |  |  | [15]
FAN79.08 |  | COF-SD3 | Tower Exhaust Fan (Bucket A38) | PLC37 |  | FL2_6_5 | Motor | M3703C | FL2 | 6 | 5 | 5 | 1 | 2 | Agglom Tower - Motor on outlet fan | [NAME] | Existing |  |  | Y216 | M-A38 | Agglomerator Exhaust Fan | DO | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421040 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].16 | [16] |  |  | [16]
PUMP08.81 |  | COF-SD2 | CIP Pump (Bucket A43) | PLC37 |  | FL2_6_6 | Motor | M3707D | FL2 | 6 | 6 | 1 | 1 | 2 | CIP - CIP Pump | CIP | Existing |  |  | Y181 | P-A43 | CIP Pump | DO | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421045 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].17 | [17] |  |  | [17]
 |  | COF-SD2 | Spare | PLC37 |  | FL2_6_7 | Motor, VFD | M3703A | FL2 | 6 | 7 | 4 |  |  |  |  |  |  |  | Y210 | M-A30 |  |  |  |  |  |  |  |  |  |  |  |  |  |  | HOA[10].8 | [46] |  |  | [46]
MOT63.61 |  | COF-SD3 | Tower Cyclone Flip Flop Valve 3rd FL (Bucket A7) | PLC37 |  | FL2_6_8 | Motor | M3703E | FL2 | 6 | 8 | 3 | 1 | 2 | Agglom Tower - Flip flop valve of cyclone system outlet | [NAME] | Existing |  |  | Y183 | FLFP-A7 | Agglomerator [NAME] Valve 3rd Floor | DO | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421013 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].18 | [18] |  |  | [18]
PUMP65.10 |  | COF-SD2 | [NAME] water Circulation Pump (Bucket A2) | PLC37 |  | FL2_6_9 | Motor | M3701F | FL2 | 6 | 9 | 5 | 1 | 2 | [NAME] for water circulation | Rotex | Existing |  |  | Y177 | P-A2 | Circulation [NAME] | DO | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421008 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].19 | [19] |  |  | [19]
[NAME] |  | COF-SD2 | Egron Inlet Fan (Bucket C2) | PLC37 |  | FL2_6_10 | Motor | M3705C | FL2 | 6 | 10 | 4 | 1 | 2 | [NAME] fan | [NAME] | Existing |  |  | Y225 | M-C2 | O/P Delaval Inlet Fan | DO | 0 | 0 | 2nd | Square-D starter mccc | 5 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].20 | [20] |  |  | [20]
PUMP31.07 |  | COF-SD2 | Jacket 1 Water Pump 1st FL. ([NAME]) | PLC37 |  | FL2_6_11 | Motor | M3700A | FL2 | 6 | 11 | 1 | 1 | 2 | Jacket System 1 - Jacket water pump | Jacket System 1 | Existing |  |  | Y207 | P-A28 | O/P Jacket Pump 2 1st  Floor | DO | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421033 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].21 | [21] |  |  | [21]
PUMP31.17 |  | COF-SD2 | Jacket 2 Water Pump 3rd FL. (Bucket A27) | PLC37 |  | FL2_6_12 | Motor | M3700B | FL2 | 6 | 12 | 3 | 1 | 2 | Jacket System 2 - Jacket water pump | Jacket System 2 | Existing |  |  | Y206 | P-A27 | O/P Jacket Pump 1 3rd Floor | DO | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421032 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].22 | [22] |  |  | [22]
PUMP31.26 |  | COF-SD2 | Jacket 3 Water Pump (Bucket A29) | PLC37 |  | FL2_6_13 | Motor | M3700C | FL2 | 6 | 13 | 4 | 1 | 2 | Jacket System 3 - Jacket water pump | Jacket System 3 | Existing |  |  | Y209 | P-A29 | Jacket [NAME] 3 | DO | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421048 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].23 | [23] |  |  | [23]
 |  | COF-SD2 | Spare Receptacle [NAME] | PLC37 |  | FL2_6_14 | Motor | spare | FL2 | 6 | 14 | 1 | 1 | 2 | Egron - Spare | Egron | Existing |  |  | Y187 | 0 | H2o Jacket pump | 0 | 0 | 0 | 2nd | Square-D starter mcca | 0 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].24 | [24] |  |  | [24]
[NAME] |  | COF-SD2 | Oaks Mixer Motor ([NAME]) | PLC37 |  | FL2_6_15 | Motor | M3704D | FL2 | 6 | 15 | 1 | 1 | 2 | [NAME] mixer for mixing distillate and liquor | [NAME] | Existing |  |  | Y182 | M-A6 | Oaks Mixer Distillate Addition | DO | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421012 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].25 | [25] |  |  | [25]
PUMP42.08 |  | COF-SD2 | Stuffing [NAME] (Bucket A16) | PLC37 |  | FL2_7_0 | Motor | M3704C | FL2 | 7 | 0 | 1 | 1 | 2 | [NAME] pump for mayno | [NAME] | Existing |  |  | Y195 | P-A16 | Stuffing Pump Delaval feed Pump | DO | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421022 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].26 | [26] |  |  | [26]
STRV64.03 |  | COF-SD2 | Fines Star Valve (Under [NAME]) | PLC37 |  | FL2_7_1 | Motor | M3701D | FL2 | 7 | 1 | 1 | 1 | 2 | Rotex - Fines star valve under rotex | Rotex | Existing |  |  | Y178 | STAR-A3 | Fines Star Valve under Rotex | DO | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421009 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].27 | [27] |  |  | [27]
GRND55.00 |  | COF-SD2 | Overs Grinder Howes Sifter (Bcket A13) | PLC37 |  | FL2_7_2 | Motor | M3701J | FL2 | 7 | 2 | 1 | 1 | 2 | Rotex - Overs grinder Howes Sifter SC-A35 | Rotex | Existing |  |  | Y191 | SC(5)-A14 | Howes Sifter | DO | 0 | 0 | 2nd | Square-D starter mcca | 5 | [NAME] | 0 | 0 | x | 0 | 0 | 0 | HOA[9].28 | [28] |  |  | [28]
FAN64.00 |  | COF-SD2 | Fluid Lift Roots Blower (Bucket A26) | PLC37 |  | FL2_7_3 | Motor | M3701E | FL2 | 7 | 3 | 3 | 1 | 2 | Rotex - Roots Blower | Rotex | Existing |  |  | Y205 | M-A26 | O/P Agglomerator [NAME] | DO | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421014 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].29 | [29] |  |  | [29]
SIFT51.00 |  | COF-SD2 | [NAME] (Bucket A4) | PLC37 |  | FL2_7_4 | Motor | M3701A | FL2 | 7 | 4 | 1 | 1 | 2 | Rotex - Rotex | Rotex | Existing |  | 1st floor or second floor | Y179 | M-A4 | [NAME] | DO | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421010 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].30 | [30] |  |  | [30]
FAN59.07 |  | COF-SD2 | Witte Exhaust Fan (Bucket A23) | PLC37 |  | FL2_7_5 | Motor | M3702D | FL2 | 7 | 5 | 2 | 1 | 2 | Witte - Exhaust fan | Witte | Existing |  |  | Y202 | M-A23 | O/P Witte Exhaust Blower | DO | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421025 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].31 | [31] |  |  | [31]
PUMP58.05 |  | COF-SD2 | Witte Inlet Blower (Bucket A25) | PLC37 |  | FL2_7_6 | Motor | M3702C | FL2 | 7 | 6 | 2 | 1 | 2 | Witte - Supply fan | Witte | Existing |  |  | Y204 | M-A25 | Witte Inlet Blower | DO | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421030 | 0 | 0 | x | 0 | 0 | 0 | HOA[10].0 | [32] |  |  | [32]
BLOW19.08 |  | COF-SD2 | Wet Scrubber 3rd FL (Bucket A42) | PLC37 |  | FL2_7_7 | Motor | M3702B | FL2 | 7 | 7 | 2 | 1 | 2 | Witte - wet scrubber motor | Witte | Existing |  |  | Y220 | M-A42 | O/P Scrubber 3rd Floor | DO | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421044 | 0 | 0 | x | 0 | 0 | 0 | HOA[10].1 | [33] |  |  | [33]
MOT19.11 |  | COF-SD2 | Scrubber Water Pump (Bucket A37) | PLC37 |  | FL2_7_8 | Motor | M3702E | FL2 | 7 | 8 | 2 | 1 | 2 | Witte - wet scrubber water recirc pump | Witte | Existing |  |  | Y214 | M-A37 | Scrubber Water Pump | DO | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-4210 | 0 | 0 | x | 0 | 0 | 0 | HOA[10].2 | [34] |  |  | [34]
VBTR52.01 |  | COF-SD2 | Witte Vibrator Coil ([NAME]) | PLC37 |  | FL2_7_9 | Motor | M3702A | FL2 | 7 | 9 | 1 | 1 | 2 | Witte - Witte vibration motor | Witte | Existing |  |  | Y189 | FLFP-A12 | Agglomerator [NAME] | DO | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421017 | 0 | 0 | x | 0 | 0 | 0 | HOA[10].3 | [35] |  |  | [35]
PUMP47.04 |  | COF-SD2 | Distillate Injection Pump (Bucket A17) | PLC37 |  | FL2_7_10 | Motor, VFD | M3704E | FL2 | 7 | 10 | 1 | 1 | 2 | [NAME] distillate pump feeding distillate for direct injection | [NAME] | Existing |  |  | Y196 | P-A17 | Distillate Injection Pump | DO | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421023 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].2 | [3] |  |  | [3]
PUMP48.16 |  | COF-SD2 | Moyno Delaval Feed Pump (Bucket A15) | PLC37 |  | FL2_7_11 | Motor, VFD | M3704F | FL2 | 7 | 11 | 1 | 1 | 2 | [NAME] feed pump for the halo motor | [NAME] | Existing |  |  | Y193 | P-A15 | Moyno Delaval Feed Pump | DO | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421021 | 0 | 0 | x | 0 | 0 | 0 | HOA[9].3 | [4] |  |  | [4]
MOT51.02 |  | COF-SD2 | Sweco Screener Motor ([NAME] ??) | PLC37 |  | [NAME] | Motor | M3703F | FL2 | 7 | 12 | 1 | N/A | N/A | Agglom Tower - Swaco screener to sift powder for tower | [NAME] | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | HOA[10].4 | [36] |  |  | [36]
FAN63.22 |  | COF-SD2 | Total Fines Baghouse Exhaust Motor (Bucket A48) | PLC37 |  | FL2_7_13 | Motor | M3701H | FL2 | 7 | 13 | 4 | N/A | N/A | Rotex - 4th floor exhaust motor for baghouse tie into witte exhaust | Rotex | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | HOA[10].5 | [37] |  |  | [37]
FAN63.00 |  | COF-SD2 | Rotex Rotron Blower Motor (Bucket A8) | PLC37 |  | FL2_7_14 | Motor | [NAME] | FL2 | 7 | 14 | 3 | N/A | N/A | Rotex - Rotron Blower | Rotex | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | HOA[10].6 | [38] |  |  | [38]
STRV63.30 |  | COF-SD2 | Total Fines Baghouse Star Valve 4th FL (Bucket A15) | PLC37 |  | FL2_7_15 | Motor | [NAME] | FL2 | 7 | 15 | 3 | N/A | N/A | Rotex - 4th floor baghouse star valve | Rotex | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | HOA[10].7 | [39] |  |  | [39]
YV63.05 |  | COF-SD2 | South Collector Vibration Motor | PLC37 |  | FL2_8_0 | DO | SV3706B | FL2 | 8 | 0 | 2 | 3 | 1 | Collector System - Vibrator on the south collector | Collector System | Existing |  | FC | Y417 | VIB-A18 | North collector vibrator | DO | 0 | 0 | 1st | Vibco | spr-60 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[8].0
YV63.08 |  | COF-SD2 | North Collector Vibration Motor | PLC37 |  | FL2_8_1 | DO | SV3706C | FL2 | 8 | 1 | 2 | 3 | 1 | Collector System - Vibrator on the north collector | Collector System | Existing |  | FC | Y418 | VIB-A19 | South collector vibrator | DO | 0 | 0 | 1st | Vibco | spr-60 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[8].1
SC71.10 |  | COF-SD2 | CTI Auger VFD | PLC37 |  | FL2_8_2 | DO | SC3700F | FL2 | 8 | 2 | 5 |  |  |  | [NAME] | Existing |  |  | Y211 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | HOA[9].0 | [1] |  |  | [1]
V58.10 |  | COF-SD2 | Witte Inlet Steam Blocking Valve Sol. | PLC37 |  | FL2_8_3 | DO | SV3703B | FL2 | 8 | 3 | 2 | N/A | N/A | Agglom Tower - Steam blocking valve for tower inlet | [NAME] | New |  | FC |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | HOA[8].2 |  | [3] | [3]
YV54.05 |  | COF-SD2 | Witte Cyclone Vibrator | PLC37 |  | FL2_8_4 | DO | [NAME] | FL2 | 8 | 4 | 2 |  |  |  | Witte | New |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | HOA[8].3
V18.05 |  | COF-SD3 | Agg. Tower Steam Blocking Valve Sol. | PLC37 |  | FL2_8_5 | DO | SV3703L | FL2 | 8 | 5 | 2 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | HOA[8].4
PT18.04 |  | COF-SD3 | Tower Press. Trans. | PLC37 |  | FL2_9_0 | AI | PT3703C | FL2 | 9 | 0 | 2 | 2 | 2 | Agglom Tower - Pressure transmitter for tower pressure | [NAME] | Existing |  | (-0.25) to 0.25 | WX276 | PT-102 | Agglomeration Chamber Inlet Air Pressure | AI | 0 | 0 | 2nd | [NAME] | fdp10-t22a01f-m2l1 | 0 | WM107643 | 0 | No (TB) | x | 0 | 0
FT19.12 |  | COF-SD2 | Wet Scrubber Flow Meter (0-100 GPH) | PLC37 |  | FL2_9_2 | AI | FT3702A | FL2 | 9 | 2 | 2 | N/A | N/A | Witte - wet scrubber flow meter 0-100 gph | Witte | New |  | EPA regulation, currently have FI |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
PT19.13 |  | COF-SD2 | Wet Scrubber Press. Trans. (0-100 PSI) | PLC37 |  | FL2_9_3 | AI | PT3702A | FL2 | 9 | 3 | 2 | N/A | N/A | Witte - wet scrubber pressure transmitter 1-100 psi | Witte | New |  | EPA regulation, currently have PI |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
DPT77.01 |  | COF-SD3 | Agg. Tower Air Flow Diff Press Transmitter | PLC37 |  | FL2_9_4 | AI | PT3703D | FL2 | 9 | 4 | 2 | 2 | 2 | Agglomeration Tower Air Flow Differential Pressure | [NAME] | Existing |  | 0-3000 cfm | WX275
DPT77.07 |  | COF-SD3 | Agg. Tower Inlet Diff Press Transmitter | PLC37 |  | FL2_9_5 | AI | DPT3703C | FL2 | 9 | 5 | 2 | 2 | 2 | Agglomeration tower inlet D/P | [NAME] | Existing |  |  | [NAME]
PT63.58 |  | COF-SD3 | Agg. Tower Fluidizer Air Press. Transmitter | PLC37 |  | FL2_9_6 | AI | PT3703E | FL2 | 9 | 6 | 2 | 2 | 2 | Agglomerator Tower Fluidizer Air Pressure Transmitter | [NAME] | Existing |  |  | WX274
IT55.00 |  | COF-SD2 | Howes Sifter Motor Amps (A-13) | PLC37 |  | FL2_9_7 | AI | M3701J_AMP | FL2 | 9 | 7 | 1 |  |  |  | Rotex | Existing |  |  | WX273
CV18.07 |  | COF-SD3 | Tower Inlet Heater Steam Control Valve | PLC37 |  | FL2_10_0 | AO | TCV3703A | FL2 | 10 | 0 | 2 | 2 | 2 | Agglom Tower - Control valve fro controlling steam for tower temp | [NAME] | Existing |  | PID control 8 | WY281 | TCV-106 | Agglomerator Inlet Air Stream Valve I/P | AO | 0 | 0 | 2nd | [NAME]  1"  ATO  CV=5.0 [NAME] | 0 | 0 | 0 | 0 | 0 | Yes (TB) | 0 | 0 | HOA[11].0 |  |  |  |  | [3]
CV58.07 |  | COF-SD2 | Witte Zone 1 Steam Control Valve I/P | PLC37 |  | FL2_10_1 | AO | TCV3702A | FL2 | 10 | 1 | 2 | 2 | 2 | Witte - Control valve on the first zone heater steam | Witte | Existing |  | PID control 6 | WY282 | TCV-104 | Witte Zone 1 Steam Valve I/P | AO | 0 | 0 | 2nd | Research control  1/2"  ATO  B-Trim | 0 | 0 | 0 | 0 | 0 | Yes (TB) | 0 | 0 | HOA[11].1 |  |  |  |  | [4]
CV58.09 |  | COF-SD2 | Witte Zone 2 Steam Valve I/P | PLC37 |  | FL2_10_2 | AO | TCV3702B | FL2 | 10 | 2 | 2 | 2 | 2 | Witte - Control valve on the second zone heater steam | Witte | Existing |  | PID control 7 | WY283 | TCV-105 | Witte Zone 2 Steam Valve I/P | AO | 0 | 0 | 0 | Kammer    1/2"  ATO  [NAME] | 20037 | 0 | WM109832 | 0 | 0 | Yes (TB) | 0 | 0 | HOA[11].2 |  |  |  |  | [5]
SC71.10_CMD |  | COF-SD2 | CTI Auger Speed Signal | PLC37 |  | FL2_10_3 | AO | SC3700F | FL2 | 10 | 3 | 5 | 2 | 2 | [NAME] feed motor speed command | [NAME] | Existing |  | 0-100% | WY285 | SPC-300 | Delaval Nozzle Speed Control | AO | 0 | 0 | 2nd | [NAME] bradley | 1333 | 0 | 0 | 0 | 0 | x | 0 | 0
 |  |  | [NAME]
PB71.07_Start |  | COF-SD2 | North CTI Vib. 3 Start (5th Fl.) | PLC37 |  | FL4_1_0 | DI | PB3700G | FL4 | 1 | 0 | 5 | 6 | 4 | [NAME] feed nozzle vibrator 3 start pb | [NAME] | Existing |  |  | X719 | PB-134 | Nozzle Vibrator 1 5th Floor Start PB | DI | 0 | 0 | 5th | Telemecanique | ZB2BE101 | 0 | 0 | 0 | x | 0 | 0 | 0
PB71.07_Stop |  | COF-SD2 | North CTI Vib. 3 Stop PB | PLC37 |  | FL4_1_1 | DI | PB3700H | FL4 | 1 | 1 | 5 | 6 | 4 | [NAME] feed nozzle vibrator 3 stop pb | [NAME] | Existing |  |  | X720 | PB-135 | Nozzle Vibrator 1 5th Floor Stop PB | DI | 0 | 0 | 5th | Telemecanique | ZB2BE101 | 0 | 0 | 0 | x | 0 | 0 | 0
PB71.06_Start |  | COF-SD2 | Center CTI Vib. 2 Start PB | PLC37 |  | FL4_1_2 | DI | PB3700J | FL4 | 1 | 2 | 5 | 6 | 4 | [NAME] feed nozzle vibrator 2 start pb | [NAME] | Existing |  |  | X739 | PB-138 | Nozzle Vibrator 2 5th Floor Start PB | DI | 0 | 0 | 5th | Telemecanique | ZB2BE101 | 0 | 0 | 0 | x | 0 | 0 | 0
PB71.06_Stop |  | COF-SD2 | Center CTI  Vib. 2 Stop PB | PLC37 |  | FL4_1_3 | DI | PB3700K | FL4 | 1 | 3 | 5 | 6 | 4 | [NAME] feed nozzle vibrator 2 stop pb | [NAME] | Existing |  |  | X740 | PB-139 | Nozzle Vibrator 2 5th Floor Stop PB | DI | 0 | 0 | 5th | Telemecanique | ZB2BE101 | 0 | 0 | 0 | x | 0 | 0 | 0
PB71.05_Start |  | COF-SD2 | South CTI Vib. 1 Start PB | PLC37 |  | FL4_1_4 | DI | PB3700L | FL4 | 1 | 4 | 5 | 6 | 4 | [NAME] feed nozzel vibrator 1 start pb | [NAME] | Existing |  |  | X743 | PB-142 | Nozzle Vibrator 3 5th Floor Start PB | DI | 0 | 0 | 5th | Telemecanique | ZB2BE101 | 0 | 0 | 0 | x | 0 | 0 | 0
PB71.05_Stop |  | COF-SD2 | South CTI Vib. 1 Stop PB | PLC37 |  | FL4_1_5 | DI | PB3700M | FL4 | 1 | 5 | 5 | 6 | 4 | [NAME] feed nozzel vibrator 1 stop pb | [NAME] | Existing |  |  | X744 | PB-143 | Nozzle Vibrator 3 5th Floor Stop PB | DI | 0 | 0 | 5th | Telemecanique | ZB2BE101 | 0 | 0 | 0 | x | 0 | 0 | 0
PB71.04_Start |  | COF-SD2 | North CTI Feed Motor Start PB | PLC37 |  | FL4_1_6 | DI | PB3700N | FL4 | 1 | 6 | 5 | 6 | 4 | [NAME] agglom feed motor start pb | [NAME] | Existing |  |  | X717 | PB-132 | [NAME] | DI | 0 | 0 | 5th | Telemecanique | ZB2BE101 | 0 | 0 | 0 | x | 0 | 0 | 0
PB71.04_Stop |  | COF-SD2 | North CTI Feed Motor Stop PB | PLC37 |  | FL4_1_7 | DI | PB3700P | FL4 | 1 | 7 | 5 | 6 | 4 | [NAME] agglom feed motor stop pb | [NAME] | Existing |  |  | X718 | PB-133 | [NAME] PB | DI | 0 | 0 | 5th | Telemecanique | ZB2BE101 | 0 | 0 | 0 | x | 0 | 0 | 0
PB71.03_Start |  | COF-SD2 | Center CTI Feed Motor Start PB | PLC37 |  | FL4_1_8 | DI | PB3700Q | FL4 | 1 | 8 | 5 | 6 | 4 | [NAME] agglom feed motor start pb | [NAME] | Existing |  |  | X737 | PB-136 | [NAME]5th Floor Start PB | DI | 0 | 0 | 5th | Telemecanique | ZB2BE101 | 0 | 0 | 0 | x | 0 | 0 | 0
PB71.03_Stop |  | COF-SD2 | Center CTI Feed Motor Stop PB | PLC37 |  | [NAME] | DI | PB3700R | FL4 | 1 | 9 | 5 | 6 | 4 | [NAME] agglom feed motor stop pb | [NAME] | Existing |  |  | X738 | PB-137 | [NAME]5th Floor Stop PB | DI | 0 | 0 | 5th | Telemecanique | ZB2BE101 | 0 | 0 | 0 | x | 0 | 0 | 0
PB71.02_Start |  | COF-SD2 | South CTI Feed Motor Start PB | PLC37 |  | FL4_1_10 | DI | PB3700S | FL4 | 1 | 10 | 5 | 6 | 4 | [NAME] agglom feed motor start pb | [NAME] | Existing |  |  | X741 | PB-140 | [NAME]5th Floor Start PB | DI | 0 | 0 | 5th | Telemecanique | ZB2BE101 | 0 | 0 | 0 | x | 0 | 0 | 0
PB71.02_Stop |  | COF-SD2 | Sourth CTI Feed Motor Stop PB | PLC37 |  | FL4_1_11 | DI | PB3700T | FL4 | 1 | 11 | 5 | 6 | 4 | [NAME] agglom feed motor stop pb | [NAME] | Existing |  |  | X742 | PB-141 | [NAME]5th Floor Stop PB | DI | 0 | 0 | 5th | Telemecanique | ZB2BE101 | 0 | 0 | 0 | x | 0 | 0 | 0
ZS63.49 |  | COF-SD2 | CTI Baghouse Star Valve Motion Switch (PH) | PLC37 |  | FL4_1_12 | DI | STRV3700D | FL4 | 1 | 12 | 5 | 1 | 2 | Egron - Penthouse baghouse star valve with motion switch aux | Egron | Existing |  |  | X121 | ROTVL-A9 | Baghouse Rotary Valve Aux. (Valve located on 5th Floor Delaval) | DI | 0 | 0 | 2nd | Square-D starter mcca | 5 | F-421015 | 0 | 0 | x | 0 | 0 | 0
S_CTI_Dev |  | COF-SD2 | CTI Feed Devices Remote/Local Switch | PLC37 |  | FL4_1_13 | DI | SS3700A | FL4 | 1 | 13 | 5 | N/A | N/A | [NAME] motor local mode control (0-remote, 1-local) | [NAME] | New
FS31.24 |  | COF-SD2 | Egron Jacket 3 Top Zone Flow Sw. 5th FL | PLC37 |  | FL4_1_14 | DI | LS3700H | FL4 | 1 | 14 | 5 | 6 | 4 | Egron - Jacket system 3 top zone flow switch  (FS-J3TZ) | Egron | Existing |  |  | X682 | PS-3A | Jacket 3 No Flow Level Switch 3 5th Floor | DI | 0 | 0 | 5th | Omega | LCV512 | 0 | 0 | 0 | x | 0 | 0 | 0
FS31.31 |  | COF-SD2 | Egron Jacket 3 Middle Zone Flow Sw. 5th FL | PLC37 |  | FL4_1_15 | DI | LS3700G | FL4 | 1 | 15 | 5 | 6 | 4 | Egron - Jacket system 3 middle zone flow switch (FS-J3MZ) | Egron | Existing |  |  | X683 | PS-3B | Jacket 3 No Flow Level Switch 3 5th Floor | DI | 0 | 0 | 5th | Omega | LCV512 | 0 | 0 | 0 | x | 0 | 0 | 0
FS31.30 |  | COF-SD2 | Egron Jacket 3 Bot. Zone Flow Sw. 4th FL | PLC37 |  | FL4_2_0 | DI | LS3700F | FL4 | 2 | 0 | 4 | 6 | 4 | Egron - Jacket system 3 bottom zone flow switch (FS-J3BZ) | Egron | Existing |  |  | X684 | PS-3C | Jacket 3 No Flow Level Switch 3 4th Floor | DI | 0 | 0 | 4th | Omega | LCV512 | 0 | 0 | 0 | x | 0 | 0 | 0
FS31.23 |  | COF-SD2 | Egron Jacket 2 Top Zone Flow Sw. 4th FL | PLC37 |  | FL4_2_1 | DI | LS3700E | FL4 | 2 | 1 | 4 | 6 | 4 | Egron - Jacket system 2 top zone flow switch (FS-J2TZ) | Egron | Existing |  |  | X685 | PS-2A | Jacket Pump 2 Level Switch 4th Floor | DI | 0 | 0 | 4th | Omega | LCV512 | 0 | 0 | 0 | x | 0 | 0 | 0
FS31.22 |  | COF-SD2 | Egron Jacket 2 Mid.Zone Flow Sw. 4th FL | PLC37 |  | FL4_2_2 | DI | LS3700D | FL4 | 2 | 2 | 4 | 6 | 4 | Egron - Jacket system 2 middle zone flow switch (FS-J2MZ) | Egron | Existing |  |  | X686 | PS-2B | Jacket Pump 2 Level Switch 4th Floor | DI | 0 | 0 | 4th | Omega | LCV512 | 0 | 0 | 0 | x | 0 | 0 | 0
FS31.21 |  | COF-SD2 | Egron Jacket 2 Bot. Zone Flow Sw. 3rd FL | PLC37 |  | FL4_2_3 | DI | LS3700C | FL4 | 2 | 3 | 3 | 6 | 4 | Egron - Jacket system 2 bottom zone flow switch (FS-J2BZ) | Egron | Existing |  |  | X687 | [NAME] | Jacket Pump 2 Level Switch 3rd Floor | DI | 0 | 0 | 3rd | Omega | LCV512 | 0 | 0 | 0 | x | 0 | 0 | 0
LSL31.15 |  | COF-SD2 | Egron Jacket 2 Water Tank Level Switch | PLC37 |  | FL4_2_4 | DI | LSL3700B | FL4 | 2 | 4 | 3 | 6 | 4 | Jacket System 2 - Level control on water tank | Jacket System 2 | Existing |  |  | X691 | PS-691 | Tank 2 Water Level Pressure Switch 3rd Floor | DI | 0 | 0-50"wc | 3rd | United Electric | S136b | 0 | 0 | 0 | x | Yes (TB) | 0 | 0
LSL31.38 |  | COF-SD2 | Egron Jacket 3 Water Tank Level Switch | PLC37 |  | FL4_2_5 | DI | LSL3700C | FL4 | 2 | 5 | 4 | 6 | 4 | Jacket System 3 - Level control on water tank | Jacket System 3 | Existing |  |  | X690 | PS-690 | Pressure Switch Tank 3 MakeUp Water Supply 4th Floor | DI | 0 | 0-50"wc | 4th | N/A | S136b | 0 | 0 | 0 | x | Yes (TB) | 0 | 0
LS63.30 |  | COF-SD2 | Total Fines Baghouse Star Valve Limit Sw. | PLC37 |  | FL4_2_6 | DI | LS3701G | FL4 | 2 | 6 | 3 | N/A | N/A | Rotex - 4th floor baghouse star valve limit switch | Rotex | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZSO77.10 |  | COF-SD3 | V77.10 Open L.S. | PLC37 |  | FL4_2_11 | DI | ZSO3703C | FL4 | 2 | 11 | 4 | 7 | 4 | [NAME] - steam injection safety blocking valve open limit | [NAME] | Existing |  |  | X781 | SV-A100-LSO | Steam Blocking Valve Open LS | DI | 0 | 0 | 4th | Go Switch | 41-000-000   08-97 | 0 | 0 | 0 | x | 0 | 0 | 0
[NAME] |  | COF-SD3 | V77.10 Closed L.S. | PLC37 |  | FL4_2_12 | DI | ZSC3703C | FL4 | 2 | 12 | 4 | 7 | 4 | [NAME] - steam injection safety blocking valve closed limit | [NAME] | Existing |  |  | X782 | SV-A100-LSC | Steam Blocking Valve Closed LS | DI | 0 | 0 | 4th | Go Switch | 41-000-000   08-97 | 0 | 0 | 0 | x | 0 | 0 | 0
STRV63.57_AUX |  | COF-SD3 | Tower Baghouse Star Valve VFD | PLC37 |  | FL4_2_14 | DI | SC3703B | FL4 | 2 | 14 | 5 | 7 | 4 | Agglom Tower - Agglom Tower feed baghouse star valve with motion switch | [NAME] | Existing |  |  | X784 | STAR-A5 | VFD for Agglomerator Star Valve | DI | 0 | 0 | 5th | Woods Drive | WFC4002cht  54145 | 0 | 0 | 0 | x | 0 | 0 | 0
ZSO42.30 |  | COF-SD2 | V42.30 Dryer [NAME] ([NAME]) | PLC37 |  | FL4_3_0 | DI | ZSO3704A | FL4 | 3 | 0 | 5 | 7 | 4 | [NAME] way valve allowing liquor to dryer | [NAME] | Existing |  |  | X778 | PRX-778-O | 3-Way Product Divert Valve Diverted to Dyer | DI | 0 | 0 | 5th | Go Switch | 41-000-000   08-97 | 0 | 0 | 0 | x | 0 | 0 | 0
ZSC42.30 |  | COF-SD2 | V42.30 Recycle [NAME] (De-Ener) | PLC37 |  | FL4_3_1 | DI | ZSC3704A | FL4 | 3 | 1 | 5 | 7 | 4 | [NAME] way valve allowing liquor to recycle | [NAME] | Existing |  |  | X777 | PRX-777-C | 3-Way Product Divert Valve in Recycle | DI | 0 | 0 | 5th | Go Switch | 41-000-000   08-97 | 0 | 0 | 0 | x | 0 | 0 | 0
LS63.49 |  | COF-SD2 | CTI Baghouse Star Valve Prox Switch | PLC37 |  | FL4_3_3 | DI | LS3700J | FL4 | 3 | 3 | 5 | 6 | 4 | Egron - Penthouse baghouse star valve limit switch | Egron | Existing |  |  | X688 | PRX-688 | Bag House Rotary PROX. SWITCH | DI | 0 | 0 | Bag house | Efector | IF0301 | 0 | 0 | 0 | x | 0 | 0 | 0
ZSC05.03 |  | COF-SD2 | V05.03 Closed L.S. | PLC37 |  | FL4_3_4 | DI | ZSC3700T | FL4 | 3 | 4 | 5 | N/A | N/A | Egron Steam - Blocking valve for main steam to trun on agglom steam closed limit | Egron Steam | New
ZSO05.03 |  | COF-SD2 | V05.03 Open L.S. | PLC37 |  | FL4_3_5 | DI | ZSO3700T | FL4 | 3 | 5 | 5 | N/A | N/A | Egron Steam - Blocking valve for main steam to trun on agglom steam open limit | Egron Steam | New
 |  | COF-SD2 | Spare | PLC37 |  | FL4_3_6 | DI | ZSH3714A | FL4 | 3 | 6 | 4 | 4 | 4 | Bucket Elevator Chain Bucket Swtich (4th Floor) | [NAME] | New |  |  |  |  |  |  |  |  |  | N/A | N/A | N/A | N/A
ZSH78.03 |  | COF-SD2 | Bucket Elevator Zero Speed Switch | PLC37 |  | FL4_3_7 | DI | ZSH3714B | FL4 | 3 | 7 | 4 | 4 | 4 | Bucket Elevator Zero Speed Switch | [NAME] | New |  |  |  |  |  |  |  |  |  | N/A | N/A | N/A | N/A
[NAME] |  | COF-SD2 | Bucket Elevator Chain Bucket Swtich (1st Floor) | PLC37 |  | FL4_3_8 | DI | ZSH3714C | FL4 | 3 | 8 | 4 | 4 | 1 | Bucket Elevator Chain Bucket Swtich (1st Floor) | [NAME] | New |  |  |  |  |  |  |  |  |  | N/A | N/A | N/A | N/A
BuckElev_EStop1 |  | COF-SD2 | Bucket Elevator E-Stop (4th Floor) | PLC37 |  | FL4_3_9 | DI |  | FL4 | 3 | 9 | 4 | 4 | 4 | Bucket Elevator E-Stop (4th Floor) | [NAME] | New
BuckElev_EStop2 |  | COF-SD2 | Bucket Elevator E-Stop (1st Floor) | PLC37 |  | FL4_3_10 | DI |  | FL4 | 3 | 10 | 4 | 4 | 1 | Bucket Elevator E-Stop (1st Floor) | [NAME] | New
 |  | COF-SD2 | Bucket Elevator E-Stop Relay | PLC37 |  | FL4_3_11 | DI |  | FL4 | 3 | 11 | 4 | 4 | 4 | Bucket Elevator E-Stop Relay | [NAME] | New
VE71.07 |  | COF-SD2 | North CTI Feed Vibrator [NAME] | PLC37 |  | FL4_4_0 | DO | VE3700H | FL4 | 4 | 0 | 5 | 6 | 4 | [NAME] feed nozzle vibrator 3 coil | [NAME] | Existing |  |  | Y731 | 0 | [NAME] | 0 | 0 | 0 | 5th | Square-D relay | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
PL71.07 |  | COF-SD2 | North CTI Feed Vibrator 3 Pilot Light | PLC37 |  | FL4_4_1 | DO | PL3700A | FL4 | 4 | 1 | 5 | 6 | 4 | [NAME] feed nozzle vibrator 3 pl | [NAME] | Existing |  |  | Y724 | 0 | [NAME] | 0 | 0 | 0 | 5th | Square-D relay | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
VE71.06 |  | COF-SD2 | Center CTI Feed Vibrator [NAME] | PLC37 |  | FL4_4_2 | DO | VE3700J | FL4 | 4 | 2 | 5 | 6 | 4 | [NAME] feed nozzle vibrator 2 coil | [NAME] | Existing |  |  | Y727 | 0 | [NAME] | 0 | 0 | 0 | 5th | Square-D relay | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
PL71.06 |  | COF-SD2 | Center CTI Feed Vibrator 2 Pilot Light | PLC37 |  | FL4_4_3 | DO | PL3700B | FL4 | 4 | 3 | 5 | 6 | 4 | [NAME] feed nozzle vibrator 2 pl | [NAME] | Existing |  |  | Y728 | 0 | Vib 2 Pilot Light | 0 | 0 | 0 | 5th | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
VE71.05 |  | COF-SD2 | South CTI Feed Vibrator [NAME] | PLC37 |  | FL4_4_4 | DO | VE3700K | FL4 | 4 | 4 | 5 | 6 | 4 | [NAME] feed nozzel vibrator 1 coil | [NAME] | Existing |  |  | Y723 | 0 | [NAME] | 0 | 0 | 0 | 5th | Square-D relay | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
PL71.05 |  | COF-SD2 | South CTI Feed Vibrator 1 Pilot Light | PLC37 |  | FL4_4_5 | DO | PL3700C | FL4 | 4 | 5 | 5 | 6 | 4 | [NAME] feed nozzel vibrator 1 pl | [NAME] | Existing |  |  | Y732 | 0 | Vib 3 Pilot Light | 0 | 0 | 0 | 5th | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
PL71.04 |  | COF-SD2 | North CTI Feed Motor 2 Pilot Light | PLC37 |  | FL4_4_6 | DO | PL3700D | FL4 | 4 | 6 | 5 | 6 | 4 | [NAME] agglom feed motor pl | [NAME] | Existing |  |  | Y722 | 0 | Nozzle Cluch 1 Pilot Light | 0 | 0 | 0 | 5th | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
PL71.03 |  | COF-SD2 | Center CTI Feed Motor 2 Pilot Light | PLC37 |  | FL4_4_7 | DO | PL3700E | FL4 | 4 | 7 | 5 | 6 | 4 | [NAME] agglom feed motor pl | [NAME] | Existing |  |  | Y726 | 0 | Nozzle Cluch 2 Pilot Light | 0 | 0 | 0 | 5th | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
PL71.02 |  | COF-SD2 | South CTI Feed Motor 3 Pilot Light | PLC37 |  | FL4_4_8 | DO | PL3700F | FL4 | 4 | 8 | 5 | 6 | 4 | [NAME] agglom feed motor pl | [NAME] | Existing |  |  | Y730 | 0 | Nozzle Cluch 3 Pilot Light | 0 | 0 | 0 | 5th | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
DMP79.09-O |  | COF-SD3 | Tower Exhaust Damper Open Limit | PLC37 |  | FL4_4_9 | Motor | M3703H-O | FL4 | 4 | 9 | 5 | 6 | 4 | Agglom Tower - Motor on agglom exhaust air baffel close command | [NAME] | Existing |  |  | Y704 | RY-704 | Close Agglomeration Exhaust Damper 4th Floor | DO | 0 | 0 | 4th | Square-D relay | RS14m1p14v20 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[13].5
DMP79.09-C |  | COF-SD3 | Tower Exhaust Damper Close Limit | PLC37 |  | FL4_4_10 | Motor | M3703H-C | FL4 | 4 | 10 | 5 | 6 | 4 | Agglom Tower - Motor on agglom exhaust air baffel open command | [NAME] | Existing |  |  | Y703 | RY-703 | Open Agglomeration Exhaust Damper 4th Floor | DO | 0 | 0 | 4th | Square-D relay | RS14m1p14v20 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[13].6
V77.10 |  | COF-SD3 | Tower Nozzle Steam Blocking Valve | PLC37 |  | FL4_4_11 | DO | SV3703C | FL4 | 4 | 11 | 4 | 6 | 4 | [NAME] - steam injection safety blocking valve | [NAME] | Existing |  | FC | Y711 | 0 | Culinary Steam Blocking Valve | DO | 0 | 0 | 4th | Worcester | 20 39 sn | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[12].0 |  | [4] | [4]
MOT76.05 |  | COF-SD3 | Tower Powder Feed Vibrator [NAME]. | PLC37 |  | FL4_4_12 | Motor | M3703G | FL4 | 4 | 12 | 4 | 6 | 4 | Agglom Tower - Vibrator for feeding tower nozzle | [NAME] | Existing |  |  | Y710 | M-A31 | Agglomeration Tower Vibrator | DO | 0 | 0 | 4th | Square-D relay | RS14m1p14v20 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[13].4
YV31.16 |  | COF-SD2 | Jacket 2 Make-Up Water Sol. Valve 3rd Fl. | PLC37 |  | FL4_4_15 | DO | SV3700B | FL4 | 4 | 15 | 3 | 6 | 4 | Jacket System 2 - Water makeup for jacket tank solenoid valve | Jacket System 2 | Existing |  | FC | Y698 | SV-698 | Tank 2 Sol. Make-Up Water 3th Floor | DO | 0 | 0 | 3rd | [NAME] | 821020 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[12].1
YV63.52 |  | COF-SD2 | Total Fines Baghouse Solenoid (Vibrator) | PLC37 |  | FL4_5_0 | DO | SV3701E | FL4 | 5 | 0 |  |  |  | Total Fines Baghouse Solenoid (Vibrator)
YV31.37 |  | COF-SD2 | Jacket 3 Make-Up Water Sol. Valve 4th Fl. | PLC37 |  | FL4_5_1 | DO | SV3700C | FL4 | 5 | 1 | 4 | 6 | 4 | Jacket System 3 - Water makeup for jacket tank solenoid valve | Jacket System 3 | Existing, Replace |  | FC, Need to replace the valve.  [NAME] is ok | Y697 | SV-697 | Tank 3 Sol. Make-Up Water 4th Floor | DO | 0 | 0 | 4th | [NAME] | 821020 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[12].2
 |  | COF-SD2 | Spare | PLC37 |  | FL4_5_2 | DO | VE3703A | FL4 | 5 | 2 | 4 | N/A | N/A | [NAME] vibrator | [NAME] | Existing |  | existing vibrator, need to connect to PLC |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | HOA[13].0
YV63.51 |  | COF-SD3 | Tower Baghouse Pulse Solenoid Valve 1 5th Fl. | PLC37 |  | FL4_5_3 | DO | SV3703D | FL4 | 5 | 3 | 5 | 7 | 4 | Agglom Tower - Agglom tower feed baghouse solenoid for pulse 1 | [NAME] | Existing |  | FC | Y773 | SV-AGG1 | 5th FloorAgglomerator Baghouse Pulse 1 | DO | 0 | 0 | 5th | Numatic | 0825a415k000030 | 0 | 0 | 0 | x | 0 | 0 | 0
YV63.52 |  | COF-SD3 | Tower Baghouse Pulse Solenoid Valve 2 5th Fl. | PLC37 |  | FL4_5_4 | DO | SV3703E | FL4 | 5 | 4 | 5 | 7 | 4 | Agglom Tower - Agglom tower feed baghouse solenoid for pulse 2 | [NAME] | Existing |  | FC | Y774 | SV-AGG2 | 5th FloorAgglomerator Baghouse Pulse 2 | DO | 0 | 0 | 5th | Numatic | 0825a415k000030 | 0 | 0 | 0 | x | 0 | 0 | 0
[NAME] |  | COF-SD3 | Tower Baghouse Pulse Solenoid Valve 3 5th Fl. | PLC37 |  | FL4_5_5 | DO | SV3703F | FL4 | 5 | 5 | 5 | 7 | 4 | Agglom Tower - Agglom tower feed baghouse solenoid for pulse 3 | [NAME] | Existing |  | FC | Y775 | SV-AGG3 | 5th FloorAgglomerator Baghouse Pulse 3 | DO | 0 | 0 | 5th | Numatic | 0825a415k000030 | 0 | 0 | 0 | x | 0 | 0 | 0
YV63.54 |  | COF-SD3 | Tower Baghouse Pulse Solenoid Valve 3 5th Fl. | PLC37 |  | FL4_5_6 | DO | SV3703G | FL4 | 5 | 6 | 5 | 7 | 4 | Agglom Tower - Agglom tower feed baghouse solenoid for pulse 4 | [NAME] | Existing |  | FC | Y776 | SV-AGG4 | 5th FloorAgglomerator Baghouse Pulse 4 | DO | 0 | 0 | 5th | Numatic | 0825a415k000030 | 0 | 0 | 0 | x | 0 | 0 | 0
YV63.41 |  | COF-SD2 | CTI Baghouse Pulse Sol. Valve 1 (Penthouse) | PLC37 |  | FL4_5_7 | DO | SV3700M | FL4 | 5 | 7 | 5 | 7 | 4 | Egron - Penthouse baghouse solenoid for pulse 1 | Egron | Existing |  | FC | Y785 | SV-A501 | Solonoid Valve Penthouse Baghouse | DO | 0 | 0 | 5th | Automatic Switch | USM8260101 | 0 | WM53194 | 96 | x | 0 | 0 | 0
YV63.42 |  | COF-SD2 | CTI Baghouse Pulse Sol. Valve 2 (Penthouse) | PLC37 |  | FL4_5_8 | DO | SV3700N | FL4 | 5 | 8 | 5 | 7 | 4 | Egron - Penthouse baghouse solenoid for pulse 2 | Egron | Existing |  | FC | Y786 | SV-A502 | Solonoid Valve Penthouse Baghouse | DO | 0 | 0 | 5th | Automatic Switch | USM8260101 | 0 | WM53194 | 96 | x | 0 | 0 | 0
YV63.43 |  | COF-SD2 | CTI Baghouse Pulse Sol. Valve 3 (Penthouse) | PLC37 |  | FL4_5_9 | DO | SV3700P | FL4 | 5 | 9 | 5 | 7 | 4 | Egron - Penthouse baghouse solenoid for pulse 3 | Egron | Existing |  | FC | Y787 | SV-A503 | Solonoid Valve Penthouse Baghouse | DO | 0 | 0 | 5th | Automatic Switch | USM8260101 | 0 | WM53194 | 96 | x | 0 | 0 | 0
YV63.44 |  | COF-SD2 | CTI Baghouse Pulse Sol. Valve 4 (Penthouse) | PLC37 |  | FL4_5_10 | DO | SV3700Q | FL4 | 5 | 10 | 5 | 7 | 4 | Egron - Penthouse baghouse solenoid for pulse 4 | Egron | Existing |  | FC | Y788 | SV-A504 | Solonoid Valve Penthouse Baghouse | DO | 0 | 0 | 5th | Automatic Switch | USM8260101 | 0 | WM53194 | 96 | x | 0 | 0 | 0
V42.30 |  | COF-SD2 | 3-Way Liquor Divert Valve (Recycle/Feed) | PLC37 |  | FL4_5_11 | DO | SV3704A | FL4 | 5 | 11 | 5 | 7 | 4 | [NAME] way valve allowing liquor to dryer or recycle | [NAME] | Existing |  | FS | Y789 | PDV-789 | 3-Way Product Divert Valve Output | DO | 0 | 0 | 5th | Worcester | 10 39 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[12].3 |  | [5] | [5]
STRV63.57 |  | COF-SD3 | Tower Baghouse Star Valve VFD Run Ctrl | PLC37 |  | FL4_5_12 | Motor, VFD | VFD3703B | FL4 | 5 | 12 | 5 | 7 | 4 | Agglom Tower - Agglom Tower feed baghouse star valve with motion switch | [NAME] | Existing |  |  | Y792 | STAR-A5 | VFD for Agglomerator Star Valve | DO | 0 | 0 | 5th | Woods Drive | WFC4002-0CHT | 0 | WM54145 | 0 | x | 0 | 0 | 0 | HOA[13].1 | [40] |  |  | [40]
SCRW76.04_CMD |  | COF-SD3 | Tower [NAME] VFD Run Ctrl. | PLC37 |  | FL4_5_13 | Motor, VFD | VFD3703A | FL4 | 5 | 13 | 4 | 7 | 4 | Agglom Tower - Screw feeder with VFD for feeding vibrator | [NAME] | Existing |  | Relocate to 1st floor | Y791 | M-A30 | Agglomeration Tower VFD for [NAME] | DO | 0 | 0 | 4th | Woods Drive | WFC4002-0CHT | 0 | WM54147 | 0 | x | 0 | 0 | 0 | HOA[13].2 | [41] |  |  | [41]
DMP06.02-O |  | COF-SD2 | Egron Inlet Damper Open Relay | PLC37 |  | FL4_5_14 | DO | M3705D-O | FL4 | 5 | 14 | 4 | 6 | 4 | [NAME] air baffle open command | [NAME] | Existing |  |  | Y699 | RY-699 | Open Dryer Inlet Damper 4th Floor | DO | 0 | 0 | 4th | Square-D relay | RS14m1p14v20 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[13].7
DMP06.02-C |  | COF-SD2 | Egron Inlet Damper Close Relay | PLC37 |  | FL4_5_15 | DO | M3705D-C | FL4 | 5 | 15 | 4 | 6 | 4 | [NAME] air baffle close command | [NAME] | Existing |  |  | Y700 | RY-700 | Close Dryer Inlet Damper 4th Floor | DO | 0 | 0 | 4th | Square-D relay | RS14m1p14v20 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[13].8
ZT06.02 |  | COF-SD2 | Egron Inlet Air Damper Position Transmitter | PLC37 |  | FL4_6_0 | AI | ZT3705D | FL4 | 6 | 0 | 4 | 6 | 4 | [NAME] air baffle position | [NAME] | Existing |  | Try to control with M3705D-O and M3705D-C (0-100%) | WX674 | ST-204 | Delaval Inlet Air Damper Position Feedback 4th Floor | AI | 0 | 0 | 4th | [NAME] colman | mp-483-0-2-2 | 0 | 0 | 0 | x | 0 | 0 | 0
DPT79.04 |  | COF-SD3 | Tower Cyclone Diff. Press. Transmitter | PLC37 |  | FL4_6_1 | AI | [NAME] | FL4 | 6 | 1 | 4 | 6 | 4 | Agglom Tower - Differential pressure for cyclone | [NAME] | Existing |  | 0-20" H2O | WX664 | PT-110 | Agglomeration Collector D/P (0-20"H2O) 4th Floor | AI | 0 | 0 | 4th | [NAME] | 3400 | 0 | WM108536 | 0 | 0 | x | 0 | 0
DPT63.19 |  | COF-SD2 | Total Fines Baghouse Diff. Press. Transmitter | PLC37 |  | FL4_6_2 | AI | DPT3701A | FL4 | 6 | 2 | 4 | N/A | N/A | Rotex - 4th floor baghouse differential pressure transmitter for EPA monitoring | Rotex | New |  | 0-10" H2O (missing) |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
DPT63.55 |  | COF-SD3 | Tower Baghouse Diff. Press. Transmitter | PLC37 |  | FL4_6_3 | AI | DPT3703A | FL4 | 6 | 3 | 5 | N/A | N/A | Agglom Tower - Agglom tower baghouse differential pressure transmitter for EPA monitoring | [NAME] | New |  | 0-10" H2O |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZT79.09 |  | COF-SD3 | Tower Exhaust Air Damper Position Transmitter | PLC37 |  | FL4_6_4 | AI | ZT3703H | FL4 | 6 | 4 | 5 |  |  | Agglom Tower - Damper position on the tower exhaust air baffle | [NAME] | Existing |  | 0-100% (need label) | WX676 | ST-206 | Agglomerator Exhaust Damper Position Feedback 5th Floor | AI | 0 | 0 | 5th | [NAME] colman | mp-483-0-2-2 | 0 | 0 | 0 | x | 0 | 0 | 0
DPT16.05 |  | COF-SD3 | Egron Collector Diff. Press. Transmitter | PLC37 |  | FL4_6_5 | AI | DPT3706A | FL4 | 6 | 5 | 3 | 6 | 4 | Collector System - Differential pressure transmitter on collector | Collector System | Existing |  | (-10 to +10") H2O | WX659 | PT-105 | Delaval Collector Differential Pressure (0-20"H2O) 3rd Floor | AI | 0 | 0 | 3rd | [NAME]  (No Remote Seals) | 823dp43s1sl2 | 0 | WM112667 | 0 | 0 | Yes (TB) | 0 | 0
FT06.15 |  | COF-SD2 | [NAME] to Dryer Air Flow | PLC37 |  | FL4_6_6 | AI | FT3705A | FL4 | 6 | 6 | 4 | 6 | 4 | [NAME] air flow | [NAME] | Existing |  | 0-2.6" H2O | WX663 | PT-109 | BURNER Inlet Air Flow (CFM) (0-1000cfm);(0-2.6"H2O) | AI | 0 | 0-2.6" H2o | 4th | ABB | 600t | 0 | WM100822 | 0 | No (TB) | 0 | 0 | 0
PT05.21 |  | COF-SD2 | Egron Agg Nozzle Low Press Trans. | PLC37 |  | FL4_6_7 | AI | PT3700B | FL4 | 6 | 7 | 5 | 6 | 4 | Egron Steam - Pressure transmitter on the center jet side | Egron Steam | Existing |  | 0-15 psi | WX677 | PT-111 | Delaval Agglomerator Nozzle Low Pressure Steam | AI | 0 | 0 | 5th | Honey well  (With Remote Seal) | STG644-EIG-00000MB0FIC3-312 | 0 | wm101641 | 0 | 0 | Yes (??) | 0 | 0
PT05.33 |  | COF-SD2 | [NAME]. | PLC37 |  | FL4_6_8 | AI | PT3700C | FL4 | 6 | 8 | 5 | 6 | 4 | Egron Steam - Pressure transmitter on the steam body side | Egron Steam | Existing |  | 0-10 psi | WX678 | 0 | Delaval Agglomerator Nozzle High Pressure Steam | AI | 0 | 0 | 5th | Honey well  (With No Remote Seal ???) | STG644-EIG-00000MB-3137 | 0 | wm101640 | 0 | 0 | Yes (??) | 0 | 0
PT77.27 |  | COF-SD2 | [NAME]. Steam Press. Trans. | PLC37 |  | FL4_6_9 | AI | PT3703A | FL4 | 6 | 9 | 4 | 6 | 4 | Agglom Tower - Steam pressure on tower | [NAME] | Existing |  | 0-200 psi | WX680 | PT-112 | Steam Pressure Transmitter - Delaval Agglomeration | AI | 0 | 0 | 4th | ABB | 600t | 0 | [NAME] | 0 | No (TB) | 0 | 0 | 0
PT16.07 |  | COF-SD2 | Egron Exhaust Air Pressure Trans | PLC37 |  | FL4_6_10 | AI | PT3706B | FL4 | 6 | 10 | 5 | 6 | 4 | Collector System - Exhaust pressure sensor | Collector System | Existing |  | 0-20" H2O | [NAME] | PT-106 | Delaval Exhaust Air Pressure Negative (0-20" H2O) (Telmar) | AI | 0 | 0 | 4th | Telmar | 51000 | 89234204 | 0 | 0 | 0 | x | 0 | 0
PT06.14 |  | COF-SD2 | Egron Inlet Air Press. (0-100" H20) | PLC37 |  | FL4_6_11 | AI | PT3705 | FL4 | 6 | 11 | 5 | 6 | 4 | [NAME] transmitter for hot air pressure | [NAME] | Existing |  | 0-100" H2O | WX658 | b | Delaval Inlet Air Pressure (0-50"H2O) 5th Floor | AI | 0 | 0 | 5th | [NAME] | 823mp-13s1sm2 | 0 | WM100994 | 1999 | 0 | Yes (TB) | 0 | 0
 |  | COF-SD2 | Spare | PLC37 |  | FL4_6_12 | AI |  | FL4 | 6 | 12 | 5 | 6 | 4 | Spare |  |  |  | 0-500 psi | WX661 | PT-107 | Dryer Spray Mix Pump Pressure 5th Floor | AI | 0 | 0-500 lbs | 5th | [NAME]  (With Remote Seal) | 821g1s1sh1 | 0 | WM100990 | 0 | 0 | Yes (TB) | 0 | 0
PT48.17 |  | COF-SD2 | Egron Spray Mix Nozzle Presure Transmitter | PLC37 |  | FL4_6_13 | AI | PT3704A | FL4 | 6 | 13 | 5 | 6 | 4 | [NAME] transmitter measuring spray pressure | [NAME] | Existing |  | 0-150 psi | WX662 | PT-108 | Dryer Spray Mix Nozzle Pressure 5th Floor | AI | 0 | 0-150 psi | 5th | Honey well  (With Remote Seal) | 1443181712 | 0 | WM101549 | 0 | 0 | Yes (TB) | 0 | 0
DPT63.45 |  | COF-SD2 | CTI baghouse Differential Pressure Transmitter | PLC37 |  | FL4_6_14 | AI | DPT3700A | FL4 | 6 | 14 | 5 | N/A | N/A | Egron - Penthouse baghouse differential pressure | Egron | New |  | 0-10" H2O |  | N/A | N/A | N/A | N/A | N/A | 5th | [NAME] | 1XLdp | 30910038 | N/A | N/A | N/A | N/A | N/A | N/A
PT31.42 |  | COF-SD2 | Egron Chamber Press. Trans. | PLC37 |  | FL4_6_15 | AI | PT3700A | FL4 | 6 | 12 |  |  |  | Egron - Chamber Press. Trans. | Egron | Existing
 |  | COF-SD2 | AHU-19 Humidity Reading (4-20MA) | PLC37 |  | FL4_7_0 | AI | HVAC_I1 | FL4 | 7 | 0 | 4 |  |  | HVAC - HVAC Actual humidity reading | HVAC | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | [NAME]. Room Temp. (4-20MA) | PLC37 |  | FL4_7_1 | AI | HVAC_I2 | FL4 | 7 | 1 | 4 |  |  | HVAC - HVAC Actual room temperature 4th FL | HVAC | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | [NAME]. Room Temp. (4-20MA) | PLC37 |  | FL4_7_2 | AI | HVAC_I3 | FL4 | 7 | 2 | 4 |  |  | HVAC - HVAC Actual room temperature 5th FL | HVAC | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | [NAME] in CFM (4-20MA) | PLC37 |  | FL4_7_3 | AI | HVAC_I4 | FL4 | 7 | 3 | 4 |  |  | HVAC - HVAC Actual fan speed in CFM | HVAC | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
FT06.16 |  | COF-SD2 | [NAME] To Dryer Air Flow | PLC37 |  | FL4_7_4 | AI | FT3705B | FL4 | 7 | 4 |  |  |  | Egron - Burner To Dryer Air Flow | Egron
[NAME] |  | COF-SD3 | Tower [NAME] VFD Speed Ctrl. | PLC37 |  | FL4_8_0 | AO | SC3703A_CMD | FL4 | 8 | 0 | 4 | 6 | 4 | Agglom Tower - Screw feeder with VFD for feeding vibrator speed control | [NAME] | Existing |  | 0-100% | WY669 | VFD_A30 | [NAME] VFD Screw Conveyor M-A30 | AO | 0 | 0 | 4th | Woods Drive | WFC4005-0CHT | 54147 | 0 | 0 | x | 0 | 0 | 0
SC63.57 |  | COF-SD3 | Aggl. Tower Star Valve VFD Speed Ctrl. (M-A5) | PLC37 |  | FL4_8_1 | AO | SC3703B_CMD | FL4 | 8 | 1 | 5 | 6 | 4 | Agglom Tower - Agglom Tower feed baghouse star valve with motion switch | [NAME] | Existing |  | 0-100% | WY670 | VFD_A5 | [NAME] | AO | 0 | 0 | 5th | Woods Drive | WFC4005-0CHT | 54145 | 0 | 0 | x | 0 | 0 | 0
CV31.20 |  | COF-SD2 | Egron Jacket 2 Steam Control Valve | PLC37 |  | FL4_8_2 | AO | TCV3700B | FL4 | 8 | 2 | 3 | 6 | 4 | Jacket System 2 - heat exchanger steam control valve | Jacket System 2 | Existing |  | PID control 4, ordered | WY665 | TCV-102 | Jacket Water 2 Steam Control Valve (I/P) | AO | 0 | CV= ???? | 3rd | Research control     1/2"  ATO | 78s | 56487 | 0 | 0 | 0 | Yes (TB) | 0 | 0 | HOA[14].0 |  |  |  |  | [6]
CV31.29 |  | COF-SD2 | Egron Jacket 3 Steam Control Valve | PLC37 |  | FL4_8_3 | AO | TCV3700C | FL4 | 8 | 3 | 4 | 6 | 4 | Jacket System 3 - heat exchanger steam control valve | Jacket System 3 | Existing |  | PID control 5, ordered | WY666 | TCV-103 | Jacket Water 3 Steam Control Valve (I/P) | AO | 0 | CV=B-Trim | 4th | Research control    1/2"   ATO | 78s | 50944 | 0 | 0 | 0 | Yes (TB) | 0 | 0 | HOA[14].1 |  |  |  |  | [7]
CV65.13 |  | COF-SD2 | Chilled Water Supply Control Valve | PLC37 |  | FL4_8_4 | AO | TCV3701A | FL4 | 8 | 4 | 5 | N/A | N/A | [NAME] valve for chilled water supply | Rotex | Existing |  | Currently local control, need to tie into the PLC (new PID needed) |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | HOA[14].2 |  |  |  |  | [8]
 |  | COF-SD2 | AHU-19 Humidity Setpoint (4-20MA) [NAME] | PLC37 |  | FL4_8_5 | AO | HVAC_O1 | FL4 | 8 | 5 | 4 |  |  | HVAC - HVAC Humidity setpoint | HVAC | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | [NAME]. Temp. [NAME] (4-20MA) [NAME] | PLC37 |  | FL4_8_6 | AO | HVAC_O2 | FL4 | 8 | 6 | 4 |  |  | HVAC - HVAC Room temperature setpoint | HVAC | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | [NAME] in CFM (4-20MA) J.C. | PLC37 |  | FL4_8_7 | AO | HVAC_O3 | FL4 | 8 | 7 | 4 |  |  | HVAC - HVAC Fan speed setpoint in CFM | HVAC | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
TE05.22 |  | COF-SD2 | Center Jet Header Steam Temperature Element | PLC37 |  | FL4_9_0 | TE | TE3700L | FL4 | 9 | 0 | 5 | 6 | 4 | Egron Steam - Temp probe on the center jet side | Egron Steam | Existing |  |  | WX767 | TE-129 | Low Pressure Header Steam Temp (RTD) | AI | 0 | 0 | 5th | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
TE05.32 |  | COF-SD2 | Body Side Header Steam Temperature Element | PLC37 |  | FL4_9_1 | TE | TE3700M | FL4 | 9 | 1 | 5 | 6 | 4 | Egron Steam - Temp probe on the steam body side | Egron Steam | Existing |  |  | WX768 | TE-130 | High Pressure Steam Temp (RTD) | AI | 0 | 0 | 5th | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
TE79.03 |  | COF-SD3 | Tower Exhaust Air Temperature Element | PLC37 |  | FL4_9_2 | TE | TE3703A | FL4 | 9 | 2 | 4 | 6 | 4 | Agglom Tower - Temp probe for tower exhaust | [NAME] | Existing |  |  | WX761 | TE-123 | Agglomeration Exhaust Air Temp (RTD) | AI | 0 | 0 | 4th | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
TE77.26 |  | COF-SD3 | Tower Nozzle Steam Temperature Element | PLC37 |  | FL4_9_3 | TE | TE3703F | FL4 | 9 | 3 | 4 | 6 | 4 | Agglom Tower - Steam temp probe on tower | [NAME] | Existing |  |  | WX760 | TE-131 | Agglomeration Nozzle Steam Temp (RTD) | AI | 0 | 0 | 4th | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
TE16.04 |  | COF-SD2 | Egron Dryer Exhaust Air Temperature Element | PLC37 |  | FL4_9_4 | TE | TE3706A | FL4 | 9 | 4 | 3 | 6 | 4 | Collector System - Exhaust air | Collector System | Existing |  |  | WX758 | TE-121 | [NAME] Exhaust Air Temp (RTD) | AI | 0 | 0 | 3rd | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
TE65.12 |  | COF-SD2 | [NAME] Temperature Element | PLC37 |  | FL4_9_5 | TE | TE3701E | FL4 | 9 | 5 | 5 | 6 | 4 | [NAME] probe for cooling water | Rotex | Existing |  | used to control TCV3701A | WX763 | TE-125 | Agglomerator [NAME] (RTD) | AI | 0 | 0 | 5th | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
TE65.06 |  | COF-SD2 | [NAME] | PLC37 |  | FL4_10_0 | TE | TE3701B | FL4 | 10 | 0 | 5 | 6 | 4 | [NAME] probe for cooling tube tank | Rotex | Existing |  |  | WX765 | TE-127 | Agglomerator [NAME] Water Temp (RTD) | AI | 0 | 0 | 5th | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
TE06.06 |  | COF-SD2 | Burner Inlet Air Temperature Element | PLC37 |  | FL4_10_1 | TE | TE3705C | FL4 | 10 | 1 | 4 | 6 | 4 | [NAME] probe for hot air hat temp | [NAME] | Existing |  |  | WX764 | TE-126 | Burner Inlet Air Temp (RTD) | AI | 0 | 0 | 4th | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
TE06.11 |  | COF-SD2 | Egron Dryer Inlet Air Temperature Element | PLC37 |  | FL4_10_2 | TE | TE3705B | FL4 | 10 | 2 | 5 | 6 | 4 | [NAME] probe for hot air hat temp | [NAME] | Existing |  |  | WX759 | TE-122 | Delaval Inlet Air Temp (RTD) | AI | 0 | 0 | 4th | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
TE31.19 |  | COF-SD2 | Egron Jacket 2 Inlet Water Temperature Element | PLC37 |  | FL4_10_3 | TE | TE3700B | FL4 | 10 | 3 | 3 | 6 | 4 | Jacket System 2 - Jacket Inlet Water Temp | Jacket System 2 | Existing |  | PID control 4 | WX753 | TE-102 | [NAME] (RTD) | AI | 0 | 0 | 3rd | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
TE31.14 |  | COF-SD2 | Egron Jacket 2 Outlet Water Temperature Element | PLC37 |  | FL4_10_4 | TE | TE3700E | FL4 | 10 | 4 | 4 | 6 | 4 | Jacket System 2 - Jacket outlet water temp | Jacket System 2 | Existing |  |  | WX754 | TE-118 | [NAME] (RTD) | AI | 0 | 0 | 4th | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
TE31.28 |  | COF-SD2 | Egron Jacket 3 Inlet Water Temperature Element | PLC37 |  | FL4_10_5 | TE | TE3700C | FL4 | 10 | 5 | 4 | 6 | 4 | Jacket System 3 - Jacket Inlet Water Temp | Jacket System 3 | Existing |  | PID control 5 | WX755 | TE-103 | [NAME] Outlet  Water Temp (RTD) | AI | 0 | 0 | 4th | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
TE31.25 |  | COF-SD2 | Egron Jacket 3 Outlet Water Temperature Element | PLC37 |  | FL4_11_0 | TE | TE3700F | FL4 | 11 | 0 | 5 | 6 | 4 | Jacket System 3 - Jacket outlet water temp | Jacket System 3 | Existing |  |  | WX756 | TE-119 | [NAME] Outlet  Water Temp (RTD) | AI | 0 | 0 | 5th | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
TE48.09 |  | COF-SD2 | Egron Spray Mix Temperature Element | PLC37 |  | FL4_11_1 | TE | TE3704B | FL4 | 11 | 1 | 5 | 6 | 4 | [NAME] probe measuring liquor temp | [NAME] | Existing |  |  | WX757 | TE-120 | [NAME] (RTD) | AI | 0 | 0 | 5th | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
TE63.21 |  | COF-SD2 | Total Fines Baghouse Temperature Element | PLC37 |  | FL4_11_2 | TE | TE3701D | FL4 | 11 | 2 | 4 | N/A | N/A | Rotex - 4th floor baghouse process monitoring | Rotex | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
TE79.06 |  | COF-SD3 | Tower Collector Exhaust Temperature Element | PLC37 |  | FL4_11_3 | TE | TE3703G | FL4 | 11 | 3 | 4 | N/A | N/A | Agglom Tower - Tower collector exhaust temp | [NAME] | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
TE63.47 |  | COF-SD2 | CTI Baghouse Exhaust Temperature Element | PLC37 |  | FL4_11_4 | TE | TE3700K | FL4 | 11 | 4 | 5 | N/A | N/A | Egron - Penthouse baghouse exhaust temp | Egron | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
TE35.40 |  | COF-SD2 | CO Tower Sample Heat Ex Cooling Media Temp | PLC37 |  | FL4_11_5 | TE | TE3701F | FL4 | 11 | 5 | 5 | 6 | 4 | Misc - 5th Floor Room Temp (RTD) | Misc | Existing |  | for monitoring only | WX766 | TE-128 | 5th [NAME] and Roof Exhaust Control (RTD) | AI | 0 | 0 | 5th | [NAME] | 0 | 0 | 0 | 0 | x | 0 | 0 | 0
V05.03 |  | COF-SD3 | Agg. Steam Blocking Valve Sol. | PLC37 |  | FL4_12_0 | DO | SV3700T | FL4 | 12 | 0 | 5 | N/A | N/A | Egron Steam - Blocking valve for main steam to trun on agglom steam | Egron Steam | New |  | FC, need LS |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | HOA[12].4 |  | [6] | [6]
YV63.13 |  | COF-SD2 | Total Fines Baghouse Pulse Solenoid Valve 1 | PLC37 |  | FL4_12_1 | DO | SV3701B | FL4 | 12 | 1 | 4 | N/A | N/A | Rotex - 4th floor baghouse air pulse system valve 1 | Rotex | New |  | FC |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
YV63.25 |  | COF-SD2 | Total Fines Baghouse Bottom Solenoid | PLC37 |  | FL4_12_2 | DO | SV3701C | FL4 | 12 | 2 | 4 | N/A | N/A | Rotex - 4th floor baghouse air pulse system valve 2 | Rotex | New |  | FC |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | HOA[12].11
YV66.02 |  | COF-SD2 | [NAME] | PLC37 |  | FL4_12_3 | DO | SV3701D | FL4 | 12 | 3 | 4 | N/A | N/A | Rotex - 4th floor baghouse air pulse system valve 3 | Rotex | New |  | FC |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
YV63.14 |  | COF-SD2 | Total Fines Baghouse Pulse Solenoid Valve 2 | PLC37 |  | FL4_12_4 | DO | SV3701B_02 | FL4 | 12 | 4 | 4 | N/A | N/A | Rotex - 4th floor baghouse air pulse system valve 4 | Rotex | New |  | FC |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
YV63.15 |  | COF-SD2 | Total Fines Baghouse Pulse Solenoid Valve 3 | PLC37 |  | FL4_12_5 | DO | SV3701B_03 | FL4 | 12 | 5 | 4 | N/A | N/A | Rotex - 4th floor baghouse air pulse system valve 5 | Rotex | New |  | FC |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
V31.18 |  | COF-SD2 | Egron Jacket 2 Supply Blocking Valve | PLC37 |  | FL4_12_6 | DO | SV3700H | FL4 | 12 | 6 | 3 | 6 | 4 | Jacket System 2 - Blocking valve for water supply side of jacket | Jacket System 2 | Existing |  | FC, need LS | Y709 | SVB-709 | Jacket [NAME]. Block Valve 3rd Floor | DO | 0 | 0 | 3rd | Numatic | 0825a415k000030 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[12].5 |  | [7] | [7]
V31.35 |  | COF-SD2 | Egron Jacket 2 Steam Supply Blocking Valve | PLC37 |  | FL4_12_7 | DO | SV3700E | FL4 | 12 | 7 | 3 | N/A | N/A | Jacket System 2 - Blocking valve for the steam supply | Jacket System 2 | New |  | FC, need LS |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | HOA[12].6 |  | [8] | [8]
V31.27 |  | COF-SD2 | Egron Jacket 3 Supply Blocking Valve | PLC37 |  | FL4_12_8 | DO | SV3700J | FL4 | 12 | 8 | 4 | 6 | 4 | Jacket System 3 - Blocking valve for water supply side of jacket | Jacket System 3 | Existing |  | FC, need LS | Y708 | SVB-708 | Jacket Pump 3 Water Rec. Block Valve 4th Floor | DO | 0 | 0 | 3rd | Numatic | 0825a415k000030 | 0 | 0 | 0 | x | 0 | 0 | 0 | HOA[12].7 |  | [9] | [9]
V31.36 |  | COF-SD2 | Egron Jacket 3 Steam supply Blocking Valve | PLC37 |  | FL4_12_9 | DO | SV3700F | FL4 | 12 | 9 | 4 | N/A | N/A | Jacket System 3 - Blocking valve for the steam supply | Jacket System 3 | New |  | FC |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | HOA[12].8 |  | [10] | [10]
 |  | COF-SD2 | Liquor Divert [NAME]. (From [NAME]) | PLC37 |  | FL4_12_10 | DO | SV3704C-O | FL4 | 12 | 10 | 5 | N/A | N/A | [NAME] valve allowing through halo recycle | [NAME] | New |  | FS, Ordering status, [NAME] is ordering (may not be in by startup) |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | HOA[12].9 |  | [11] | [11]
 |  | COF-SD2 | Liquor  Divert [NAME]. (From Halo Recycle) | PLC37 |  | FL4_12_11 | DO | SV3704C-C | FL4 | 12 | 11 | 5 | N/A | N/A | [NAME] valve allowing through halo recycle | [NAME] | New |  | FS, Ordering status, [NAME] is ordering (may not be in by startup) |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
YV63.16 |  | COF-SD2 | Total Fines Baghouse Pulse Solenoid Valve 4 | PLC37 |  | FL4_12_12 | DO | SV3701B_04 | FL4 | 12 | 12 | 5 | N/A | N/A | [NAME] valve allowing through halo recycle | [NAME] | New |  | FS, Ordering status, [NAME] is ordering (may not be in by startup) |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | [NAME] on/off command ([NAME]) | PLC37 |  | [NAME] | DO | HVAC_DO1 | FL4 | 12 | 13 | 4 |  |  | HVAC - Fan motor on/off command (Occupied/Unoccupied) | HVAC | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | AHU-19, R-5 E-Stop Relay | PLC37 |  | [NAME] | DO | HVAC_DO2 | FL4 | 12 | 14 | 4 |  |  | HVAC - E-Stop | HVAC | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
YV63.17 |  | COF-SD2 | Total Fines Baghouse Pulse Solenoid Valve 5 | PLC37 |  | FL4_12_15 | DO | SV3701B_05 | FL4 | 12 | 15 | 4 |  |  | HVAC - E-Stop | HVAC | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | 3-Way PDV to Dryer Position L.S. | PLC37 |  | FL4_13_0 | DI | ZSC3704C | FL4 | 13 | 0 | 5 | N/A | N/A | [NAME] way valve allowing liquor from halo recycle to dryer | [NAME] | New |  | Ordering status, [NAME] is ordering (may not be in by startup) |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | 3-Way PDV to Recycle Positon L.S. | PLC37 |  | FL4_13_1 | DI | ZSO3704C | FL4 | 13 | 1 | 5 | N/A | N/A | [NAME] way valve allowing liquor from feed system to recycle | [NAME] | New |  | Ordering status, [NAME] is ordering (may not be in by startup) |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
PS66.00 |  | COF-SD2 | Bauermister Air Press. [NAME] | PLC37 |  | FL4_13_2 | DI | PS3701B | FL4 | 13 | 2 | 3 | 6 | 4 | Rotex - Baurmeister Grinder Air Pressure Switch 3rd Floor | Rotex | Existing |  | Don't need it | X681 | PS-B1 | Baurmeister Grinder Air Pressure Switch 3rd Floor | DI | 0 | 1-75 lbs | 3rd | Square-D | [NAME] | 0 | 0 | 0 | x | 0 | 0 | 0
LS66.00 |  | COF-SD2 | [NAME] | PLC37 |  | FL4_13_3 | DI | LS3701D | FL4 | 13 | 3 | 3 | 6 | 4 | Rotex - Bauermeister Grinder Vibrator [NAME] Floor | Rotex | Existing |  | Hardwired | X693 | VSW-693 | Vibrator [NAME] Grinder 3rd Floor | DI | 0 | 0 | 3rd | Rochester Inst. | VT1215 | 0 | 0 | 0 | 0 | x | 0 | 0
 |  | COF-SD2 | AHU-19 Fan Motor R-3 Contact | PLC37 |  | FL4_13_4 | DI | HVAC_DI1 | FL4 | 13 | 4 | 4 |  |  | HVAC - Fan motor auxuilary contact | HVAC | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZSO31.18 |  | COF-SD2 | V31.18 Open L.S. | PLC37 |  | FL4_13_6 | DI | ZSO3700H | FL4 | 13 | 6 | 3 | N/A | N/A | Jacket System 2 - Blocking valve for water supply side of jacket open limit | Jacket System 2 | New |  | FC, need LS |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZSC31.18 |  | COF-SD2 | V31.18 Closed L.S. | PLC37 |  | FL4_13_7 | DI | ZSC3700H | FL4 | 13 | 7 | 3 | N/A | N/A | Jacket System 2 - Blocking valve for water supply side of jacket close limit | Jacket System 2 | New |  | FC, need LS |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZSO31.35 |  | COF-SD2 | V31.35 Open L.S. | PLC37 |  | FL4_13_8 | DI | ZSO3700E | FL4 | 13 | 8 | 3 | N/A | N/A | Jacket System 2 - Blocking valve for steam supply open limit | Jacket System 2 | New |  | FC, need LS |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZSC31.35 |  | COF-SD2 | V31.35 Closed L.S. | PLC37 |  | FL4_13_9 | DI | ZSC3700E | FL4 | 13 | 9 | 3 | N/A | N/A | Jacket System 2 - Blocking valve for steam supply close limit | Jacket System 2 | New |  | FC, need LS |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZSO31.27 |  | COF-SD2 | V31.27 Open L.S. | PLC37 |  | FL4_13_10 | DI | ZSO3700J | FL4 | 13 | 10 | 4 | N/A | N/A | Jacket System 3 - Blocking valve for water supply side of jacket open limit | Jacket System 3 | New |  | FC, need LS |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZSC31.27 |  | COF-SD2 | V31.27 Closed L.S. | PLC37 |  | FL4_13_11 | DI | ZSC3700J | FL4 | 13 | 11 | 4 | N/A | N/A | Jacket System 3 - Blocking valve for water supply side of jacket close limit | Jacket System 3 | New |  | FC, need LS |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZSO31.36 |  | COF-SD2 | V31.36 Open L.S. | PLC37 |  | FL4_13_12 | DI | ZSO3700F | FL4 | 13 | 12 | 4 | N/A | N/A | Jacket System 3 - Blocking valve for steam supply open limit | Jacket System 3 | New |  | FC, need LS |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZSC31.36 |  | COF-SD2 | V31.36 Closed L.S. | PLC37 |  | FL4_13_13 | DI | ZSC3700F | FL4 | 13 | 13 | 4 | N/A | N/A | Jacket System 3 - Blocking valve for steam supply close limit | Jacket System 3 | New |  | FC, need LS |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
S05.03-O |  | COF-SD2 | V05.03 Local Open Command | PLC37 |  | FL4_13_14 | DI | ZSO3700F | FL4 | 13 | 14 | 4 | N/A | N/A | Jacket System 3 - Blocking valve for steam supply open limit | Jacket System 3 | New |  | FC, need LS |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
S05.03-C |  | COF-SD2 | V05.03 Local Close Command | PLC37 |  | FL4_13_15 | DI | ZSC3700F | FL4 | 13 | 15 | 4 | N/A | N/A | Jacket System 3 - Blocking valve for steam supply close limit | Jacket System 3 | New |  | FC, need LS |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
CV77.28 |  | COF-SD3 | Agglomeration Tower Steam Control Valve | PLC37 |  | FL4_14_0 | DI | ZSO3700F | FL4 | 14 | 0 | 4 | N/A | N/A | Jacket System 3 - Blocking valve for steam supply open limit | Jacket System 3 | New |  | FC, need LS |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  |  | Safety PLC
FS06.05 |  | COF-SD2 | Central Nozzle Cooling Air Flow Sw. | PLC37 |  | SAF_2_3 | DI | FS3705A | SAF | 2 | 3 | 4 | 6 | 4 | [NAME] switch for safety on the central cooling | [NAME] | Existing | yes |  | X696 | not used | [NAME]. | DI | 0 | In tee on 5 th floor | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0 | 0
ZSO16.09 |  | COF-SD2 | V16.09 open L.S. | PLC37 |  | SAF_2_4 | DI | ZSO3706A | SAF | 2 | 4 | 4 | N/A | N/A | Collector System - Butterfly safety flap isolate dryer open limit | Collector System | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZSC16.09 |  | COF-SD2 | V16.09 Closed L.S. | PLC37 |  | SAF_2_5 | DI | ZSC3706A | SAF | 2 | 5 | 4 | N/A | N/A | Collector System - Butterfly safety flap isolate dryer closed limit | Collector System | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZSC16.09 |  | COF-SD2 | V58.04 Open L.S. | PLC37 |  | SAF_2_6 | DI | ZSO3702E | SAF | 2 | 6 | 2 | N/A | N/A | Witte - Butterfly valve safety open limit on inlet side | Witte | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZSC58.04 |  | COF-SD2 | V58.04 Closed L.S. | PLC37 |  | SAF_2_7 | DI | ZSC3702E | SAF | 2 | 7 | 2 | N/A | N/A | Witte - Butterfly valve safety closed limit on inlet side | Witte | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZSC19.01 |  | COF-SD2 | V19.01 Closed L.S. | PLC37 |  | SAF_2_8 | DI | ZSC3702C | SAF | 2 | 8 | 2 | N/A | N/A | Witte - Butterfly valve safety closed limit on outlet side | Witte | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZSO19.01 |  | COF-SD2 | V19.01 Open L.S. | PLC37 |  | SAF_2_9 | DI | ZSO3702C | SAF | 2 | 9 | 2 | N/A | N/A | Witte - Butterfly valve safety open limit on outlet side | Witte | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZSC79.07 |  | COF-SD3 | V79.07 Closed L.S. | PLC37 |  | SAF_2_10 | DI | ZSC3703J | SAF | 2 | 10 | 4 | N/A | N/A | Agglom Tower - Agglom tower safety exhaust valve closed limit | [NAME] | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZSO79.07 |  | COF-SD3 | V79.07 Valve Open L.S. | PLC37 |  | SAF_2_11 | DI | ZSO3703J | SAF | 2 | 11 | 4 | N/A | N/A | Agglom Tower - Agglom tower safety exhaust valve open limit | [NAME] | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZSC18.01 |  | COF-SD3 | V18.01 Closed L.S. | PLC37 |  | SAF_2_12 | DI | [NAME] | SAF | 2 | 12 | 2 | N/A | N/A | Agglom Tower - Agglom tower safety inlet valve closed limit | [NAME] | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZSO18.01 |  | COF-SD3 | V18.01 Open L.S. | PLC37 |  | SAF_2_13 | DI | [NAME] | SAF | 2 | 13 | 2 | N/A | N/A | Agglom Tower - Agglom tower safety inlet valve open limit | [NAME] | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZSC06.00 |  | COF-SD2 | V06.00Closed L.S. | PLC37 |  | SAF_3_1 | DI | ZSC3705C | SAF | 3 | 1 | 4 | N/A | N/A | [NAME] air hat safety blocking valve closed limit | [NAME] | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
ZSO06.00 |  | COF-SD2 | V06.00 Open L.S. | PLC37 |  | SAF_3_2 | DI | ZSO3705C | SAF | 3 | 2 | 4 | N/A | N/A | [NAME] air hat safety blocking valve open limit | [NAME] | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
FS35.72 |  | COF-SD3 | Tower Baghouse S.S. Flow Switch | PLC37 |  | SAF_3_3 | DI | FS3703A | SAF | 3 | 3 | 4 |  |  | Agglom Tower - Tower baghouse safety shower flow switch | [NAME] | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
FS35.82 |  | COF-SD3 | Tower S.S. Flow Switch | PLC37 |  | SAF_3_4 | DI | FS3703H | SAF | 3 | 4 | 4 |  |  | Agglom Tower - Tower safety shower flow switch | [NAME] | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
FS35.21 |  | COF-SD2 | Egron S.S. Flow Switch | PLC37 |  | SAF_3_5 | DI | FS3700R | SAF | 3 | 5 | 5 |  |  | Egron - Egron safety shower flow switch | Egron | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
V |  | COF-SD2 | Total Fines [NAME] | PLC37 |  | SAF_3_6 | DI | FS3701A | SAF | 3 | 6 | 4 |  |  | Rotex - Total fines baghouse safety shower flow switch | Rotex | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
FS35.09 |  | COF-SD2 | CTI BH S.S. Flow Switch | PLC37 |  | SAF_3_7 | DI | FS3700L | SAF | 3 | 7 | 5 |  |  | Egron - CTI baghouse safety shower flow switch | Egron | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
FS35.12 |  | COF-SD2 | Witte [NAME] | PLC37 |  | SAF_3_8 | DI | FS3702J | SAF | 3 | 8 | 1 |  |  | Witte - Witte safety shower flow switch | Witte | New | yes
. |  | COF-SD2 | Total Fines S.S. Blocking Valve | PLC37 |  | SAF_4_0 | DO | SV3701A | SAF | 4 | 0 | 4 | N/A | N/A | Rotex - 4th floor safety shower blocking valve | Rotex | New | yes | FS |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
V16.09 |  | COF-SD2 | Dryer Butterfly Valve | PLC37 |  | SAF_4_1 | DO | SV3706A | SAF | 4 | 1 | 4 | N/A | N/A | Collector System - Butterfly safety flap isolate dryer close in <2 sec | Collector System | New | yes | FC |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
YV35.02 |  | COF-SD2 | Egron S.S. Blocking Valve | PLC37 |  | SAF_4_2 | DO | SV3700R | SAF | 4 | 2 | 5 | N/A | N/A | Egron - safety shower blocking valve | Egron | New | yes | FS |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
YV35.11 |  | COF-SD2 | Witte S.S. Blocking Valve | PLC37 |  | SAF_4_3 | DO | SV3702J | SAF | 4 | 3 | 1 | N/A | N/A | Witte - Blocking valve for safety shower | Witte | New | yes | FS |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
V58.04 |  | COF-SD2 | Inlet Butterfly Valve | PLC37 |  | SAF_4_4 | DO | SV3702E | SAF | 4 | 4 | 2 | N/A | N/A | Witte - Butterfly valve safety close <2 sec on inlet side | Witte | New | yes | FC |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
V19.01 |  | COF-SD2 | Outlet Butterfly Valve | PLC37 |  | SAF_4_5 | DO | SV3702C | SAF | 4 | 5 | 2 | N/A | N/A | Witte - Butterfly valve safety close <2 sec on outlet side | Witte | New | yes | FC |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
YV35.71 |  | COF-SD3 | Tower BH S.S. Blocking Valve Sol. | PLC37 |  | SAF_4_6 | DO | SV3703A | SAF | 4 | 6 | 4 | N/A | N/A | Agglom Tower - Agglom Tower baghouse safety shower blocking valve | [NAME] | New | yes | FS |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
YV35.08 |  | COF-SD2 | CTI BH S.S. Blocking Valve Sol. | PLC37 |  | SAF_4_7 | DO | SV3700L | SAF | 4 | 7 | 5 | N/A | N/A | Egron - Penthouse baghouse safety shower blocking valve | Egron | New | yes | FS |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
YV35.81 |  | COF-SD3 | Tower S.S. Blocking Valve Sol. | PLC37 |  | SAF_4_8 | DO | SV3703H | SAF | 4 | 8 | 4 | N/A | N/A | Agglom Tower - Agglom tower safety shower blocking valve | [NAME] | New | yes | FS |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
V79.07 |  | COF-SD3 | Agg. Tower Safety Exhaust Valve | PLC37 |  | SAF_4_9 | DO | SV3703J | SAF | 4 | 9 | 4 | N/A | N/A | Agglom Tower - Agglom tower safety exhaust valve | [NAME] | New | yes | FC |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
V18.01 |  | COF-SD3 | Agg. Tower Safety Inlet Valve | PLC37 |  | SAF_4_10 | DO | SV3703K | SAF | 4 | 10 | 2 | N/A | N/A | Agglom Tower - Agglom tower safety inlet valve | [NAME] | New | yes | FC |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
V06.00 |  | COF-SD2 | Hot Air Hat Safety Blocking Valve | PLC37 |  | [NAME] | DO | SV3705C | SAF | 4 | 11 | 4 | N/A | N/A | [NAME] air hat safety blocking valve | [NAME] | New | yes | FC |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | CO System 1st & 2nd Take Off | PLC37 |  | SAF_4_12 | DO |  | SAF | 4 | 12 | 2 |  |  | CO - CO 1st take-off | CO | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | CO System Cip Enable | PLC37 |  | SAF_4_13 | DO |  | SAF | 4 | 13 | 2 |  |  | CO - CO 2nd take-off | CO | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | Spare | PLC37 |  | SAF_4_14 | DO |  | SAF | 4 | 14 | 2 |  |  | CO - CO CIP enable | CO | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | Safety Shower Trigger to Fire Alarm System | PLC37 |  | SAF_4_15 | DO |  | SAF | 4 | 15 | 1 |  |  | Misc - Safety shower trigger to fire alarm system | Misc | New | yes | can be relocated if needed |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
PT77.01 |  | COF-SD3 | Tower Press. Trans. | PLC37 |  | SAF_5_0 | AI | PT3703B SAFETY | SAF | 5 | 0 | 4 | N/A | N/A | Agglom Tower - Pressure transmitter for tower pressure safety | [NAME] | New | yes | (+/- 0.05" H2O) |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | CO 1st Take Off Reference | PLC37 |  | SAF_5_1 | AI |  | SAF | 5 | 1 | 2 | N/A | N/A | CO - CO 1st take-off delta | CO | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | CO 1st Take Off Delta | PLC37 |  | SAF_5_2 | AI |  | SAF | 5 | 2 | 2 | N/A | N/A | CO - CO 1st take-off reference | CO | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | CO 2nd Take off Reference | PLC37 |  | SAF_5_3 | AI |  | SAF | 5 | 3 | 2 | N/A | N/A | CO - CO 2nd take-off delta | CO | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | CO 2nd Take off Delta | PLC37 |  | SAF_5_4 | AI |  | SAF | 5 | 4 | 2 | N/A | N/A | CO - CO 2nd take-off reference | CO | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
PT31.40 |  | COF-SD2 | Egron Press. Trans. | PLC37 |  | SAF_5_5 | AI | PT3700D SAFETY | SAF | 5 | 5 | 5 | N/A | N/A | Egron - Pressure transmitter for tower safety | Egron | New | yes | Ordering status, (+/- 0.05" H2O) |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
TE17.02 |  | COF-SD2 | North Collector Outlet Temperature Element | PLC37 |  | SAF_6_0 | TE | TE3706D SAFETY | SAF | 6 | 0 | 3 | N/A | N/A | Collector System - Outlet north collector safety | Collector System | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
TE16.02 |  | COF-SD2 | South Collector Outlet Temperature Element | PLC37 |  | SAF_6_1 | TE | TE3706B SAFETY | SAF | 6 | 1 | 3 | N/A | N/A | Collector System - Outlet south collector safety | Collector System | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
TE79.02 |  | COF-SD3 | Agg. Tower Exhaust Temperature Element | PLC37 |  | SAF_6_2 | TE | TE3703B SAFETY | SAF | 6 | 2 | 4 | N/A | N/A | Agglom Tower - Temp probe for tower exhaust safety | [NAME] | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
TE77.05 |  | COF-SD3 | Agg. Tower Temperature Element | PLC37 |  | SAF_6_3 | TE | TE3703E SAFETY | SAF | 6 | 3 | 2 | N/A | N/A | Agglom Tower - Temp probe for tower safety | [NAME] | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
TE63.20 |  | COF-SD2 | 4th FL Baghouse Process Temperature Element | PLC37 |  | SAF_6_4 | TE | TE3701C SAFETY | SAF | 6 | 4 | 4 | N/A | N/A | Rotex - 4th floor baghouse process monitoring | Rotex | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
TE31.02 |  | COF-SD2 | Egron Temperature Element | PLC37 |  | SAF_6_5 | TE | TE3700H SAFETY | SAF | 6 | 5 | 3 | N/A | N/A | Egron - Temp probe for safety | Egron | New | yes | next to TE3700G |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
TE59.03 |  | COF-SD2 | Witte Cyclone Outlet Temperature Element | PLC37 |  | SAF_7_0 | TE | TE3702C SAFETY | SAF | 7 | 0 | 2 | N/A | N/A | Witte - Temp probe for outlet of cyclone for safety 0-250 | Witte | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
TE59.01 |  | COF-SD2 | Witte Exhaust Temperature Element | PLC37 |  | SAF_7_1 | TE | TE3702F SAFETY | SAF | 7 | 1 | 1 | N/A | N/A | Witte - Witte exhaust safety temp | Witte | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
TE79.05 |  | COF-SD3 | Agg. Collector Exhaust Temperature Element | PLC37 |  | SAF_7_2 | TE | TE3703H SAFETY | SAF | 7 | 2 | 4 | N/A | N/A | Agglom Tower - Agglom collector exhaust temp safety | [NAME] | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
TE63.46 |  | COF-SD2 | Egron CTI BH Exhaust Temperature Element | PLC37 |  | SAF_7_3 | TE | TE3700J SAFETY | SAF | 7 | 3 | 5 | N/A | N/A | Egron - Penthouse baghouse exhaust temp safety | Egron | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
TE58.30 |  | COF-SD2 | Witte Inlet Temperature Element | PLC37 |  | SAF_7_4 | TE | TE3702G SAFETY | SAF | 7 | 4 | 1 |  |  |  | Witte | New | yes
 |  | COF-SD2 | CO Common Alarm K3-1 | PLC37 |  | SAF_8_0 | DI |  | SAF | 8 | 0 | 2 | N/A | N/A | CO - CO common alarm | CO | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | CO 1st Take off Alarm 1  K4-1 | PLC37 |  | SAF_8_1 | DI |  | SAF | 8 | 1 | 2 | N/A | N/A | CO - CO 1st take-off alarm 1 | CO | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | CO 1st Take off [NAME] | PLC37 |  | SAF_8_2 | DI |  | SAF | 8 | 2 | 2 | N/A | N/A | CO - CO 1st take-off alarm 2 | CO | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | CO 1st Take off [NAME] | PLC37 |  | SAF_8_3 | DI |  | SAF | 8 | 3 | 2 | N/A | N/A | CO - CO 1st take-off alarm 3 | CO | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | CO maint/Warm up K7-1 | PLC37 |  | SAF_8_4 | DI |  | SAF | 8 | 4 | 2 | N/A | N/A | CO - CO Maint/warm up | CO | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | CO 2nd Take off Alarm 1  K8-1 | PLC37 |  | SAF_8_5 | DI |  | SAF | 8 | 5 | 2 | N/A | N/A | CO - CO 2nd take-off alarm 1 | CO | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | CO 2nd Take off Alarm 2 K9-1 | PLC37 |  | [NAME] | DI |  | SAF | 8 | 6 | 2 | N/A | N/A | CO - CO 2nd take-off alarm 2 | CO | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | CO 2nd Takd off [NAME]K10-1 | PLC37 |  | SAF_8_7 | DI |  | SAF | 8 | 7 | 2 | N/A | N/A | CO - CO 2nd take-off alarm 3 | CO | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | CO 1st Take off Minor [NAME] | PLC37 |  | SAF_8_8 | DI |  | SAF | 8 | 8 | 2 | N/A | N/A | CO - CO 1st take-off minor alarm | CO | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | CO 1st Take off Major [NAME] | PLC37 |  | SAF_8_9 | DI |  | SAF | 8 | 9 | 2 | N/A | N/A | CO - CO 1st take-off major alarm | CO | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | CO 2nd Take off Minor Alarm K13-1 | PLC37 |  | SAF_8_10 | DI |  | SAF | 8 | 10 | 2 | N/A | N/A | CO - CO 2nd take-off minor alarm | CO | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | Co 2nd Take off Major [NAME] | PLC37 |  | SAF_8_11 | DI |  | SAF | 8 | 11 | 2 | N/A | N/A | CO - CO 2nd take-off major alarm | CO | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | CO Tower Low Press. [NAME] | PLC37 |  | [NAME] | DI |  | SAF | 8 | 12 | 2 | N/A | N/A | CO - CO tower low pressure switch | CO | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | CO Fluidized Bed Low Press. Sw. | PLC37 |  | SAF_8_13 | DI |  | SAF | 8 | 13 | 2 | N/A | N/A | CO - CO fluidized bed low pressure switch | CO | New | yes |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | Tower Safety Shower PB 1st FL | PLC37 |  | SAF_9_0 | DI |  | SAF | 9 | 0 | 1 | N/A | N/A | Agglom Tower - Agglom tower E-stop PB 1st FL | [NAME] | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | Tower E-Stop PB 1st FL | PLC37 |  | SAF_9_1 | DI |  | SAF | 9 | 1 | 1 | N/A | N/A | Agglom Tower - Controlled shutdown PB 1st FL | [NAME] | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | Tower Controlled Shutdown PB 1st FL | PLC37 |  | SAF_9_2 | DI |  | SAF | 9 | 2 | 1 | N/A | N/A | Agglom Tower - Agglom tower safety shower PB 1st FL | [NAME] | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | Egron Safety Shower PB 1st. FL. | PLC37 |  | SAF_9_3 | DI |  | SAF | 9 | 3 | 1 | N/A | N/A | Egron - controlled shutdown PB 1st FL | Egron | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | [NAME] 1st Fl. | PLC37 |  | SAF_9_4 | DI |  | SAF | 9 | 4 | 1 | N/A | N/A | Egron - safety shower E-stop PB 1st FL | Egron | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | Egron Controlled Shutdown PB 1st Fl. | PLC37 |  | SAF_9_5 | DI |  | SAF | 9 | 5 | 1 | N/A | N/A | Egron - E-stop PB 1st FL | Egron | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | Egron CIP mode SS | PLC37 |  | SAF_9_6 | DI |  | SAF | 9 | 6 | 1 | N/A | N/A | Egron - CIP mode | Egron | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | [NAME] mode SS | PLC37 |  | SAF_9_7 | DI |  | SAF | 9 | 7 | 1 | N/A | N/A | Egron - Run Mode | Egron | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | Tower Safety Shower PB 4th Fl. | PLC37 |  | SAF_9_8 | DI |  | SAF | 9 | 8 | 4 | N/A | N/A | Agglom Tower - Agglom tower E-stop PB 4th FL | [NAME] | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | Tower E-Stop PB 4th Fl. | PLC37 |  | SAF_9_9 | DI |  | SAF | 9 | 9 | 4 | N/A | N/A | Agglom Tower - Controlled shutdown PB 4th FL | [NAME] | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | Tower Controlled Shutdown PB 4th Fl. | PLC37 |  | SAF_9_10 | DI |  | SAF | 9 | 10 | 4 | N/A | N/A | Agglom Tower - Agglom tower safety shower PB 4th FL | [NAME] | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | Egron Safety Shower PB 5th Fl. | PLC37 |  | SAF_9_11 | DI |  | SAF | 9 | 11 | 5 | N/A | N/A | Egron - controlled shutdown PB 5th FL | Egron | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | [NAME] 5th Fl. | PLC37 |  | SAF_9_12 | DI |  | SAF | 9 | 12 | 5 | N/A | N/A | Egron - safety shower E-stop PB 5th FL | Egron | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | Egron Controlled Shutdown PB 5th Fl. | PLC37 |  | SAF_9_13 | DI |  | SAF | 9 | 13 | 5 | N/A | N/A | Egron - E-stop PB 5th FL | Egron | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | Tower CIP mode SS | PLC37 |  | SAF_9_14 | DI |  | SAF | 9 | 14 | 1 | N/A | N/A | [NAME] mode | [NAME] | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A
 |  | COF-SD2 | Tower Run mode SS | PLC37 |  | SAF_9_15 | DI |  | SAF | 9 | 15 | 1 | N/A | N/A | Agglom Tower - Run mode | [NAME] | New |  |  |  | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A | N/A