Spreadsheet: larry_campbell__20953__Line 300 Liquid Sample SummaryFeb01TW
Sheet: Hinkley District, 2000

LINE | [NAME] | Description | Sample Date | Sample Type | Result (All results as [NAME] 1016 unless otherwise noted) | Comments
300 A | 116.48 A | [NAME] |  | None |  | Tap not inspected or sampled
300 A | 130.37 A | PLS 2XA Insertion Meter | 2000-02-16 00:00:00 | Wipe | ND <0.7 ug/100cm2
300 A | 131.94 A | [NAME] Community Tap | 2000-02-09 00:00:00 | Wipe | ND <1ug/wipe | Removed primary regulator; opened it and obtained wipe sample - non quantitative
300 A | 134.00 A | Southwest Gas (Martino) |  | None |  | Tap not inspected or sampled
300 A | 135.98 A | Southwest Gas (Masimini) |  | None |  | Tap not inspected or sampled
300 A | 137.00 A | Southwest Gas |  | None |  | Tap not inspected or sampled
300 A | 137.50 A | Southwest Gas |  | None |  | Tap not inspected or sampled
300 A | 141.03 A | Lucerne Valley - Main #313 XA | 2000-02-11 00:00:00 | None |  | Sample taps located immediately upstream and downstream of orifice plate. Both taps were dry.
300 A | 147.91 A | Barstow B Meter | 2000-02-11 00:00:00 | Liquid | 11 ppm
300 A | 147.91 A | Barstow B Meter | 2000-02-28 00:00:00 | Liquid |  | Insufficient Sample
300 A | 147.91 A | Barstow B Meter | 2000-03-10 00:00:00 | Liquid | 16 ppm
300 A | 147.91 A | Barstow B Meter | 2000-03-21 00:00:00 | Liquid | 13 ppm
300 A | 147.91 A | Barstow B Meter | 2000-04-05 00:00:00 | Liquid | 18 ppm
300 A | 147.91 A | Barstow B Meter | 2000-04-19 00:00:00 | Liquid | 10 ppm
300 A | 147.91 A | Barstow B Meter | 2000-05-01 00:00:00 | Liquid | 11 ppm
300 A | 147.91 A | Barstow B Meter | 2000-05-14 00:00:00 | Liquid | 18 ppm
300 A | 147.91 A | Barstow B Meter | 2000-05-30 00:00:00 | Liquid | 11 ppm
300 A | 147.91 A | Barstow B Meter | 2000-06-14 00:00:00 | Liquid | 24 ppm
300 A | 147.91 A | Barstow B Meter | 2000-06-30 00:00:00 | Liquid | 25 ppm
300 A | 147.91 A | Barstow B Meter | 2000-07-29 00:00:00 | Liquid | 8 ppm
300 A | 147.91 A | Barstow B Meter | 2000-08-18 00:00:00 | Liquid | 10 ppm
300 A | 147.91 A | Barstow B Meter | 2000-09-05 00:00:00 | Liquid | 14 ppm | <10 mls
300 A | 147.91 A | Barstow B Meter | 2000-09-19 00:00:00 | Liquid | 15 ppm | <10 mls (trace)
300 A | 147.91 A | Barstow B Meter | 2000-12-18 00:00:00 | Liquid | 18 ppm | ~10 mls (trace)
300 A | 151.05 A | Barstow "A" Filter | 2000-02-17 00:00:00 | Liquid | 6 ppm
300 A | 151.05 A | Barstow "A" Filter | 2000-02-28 00:00:00 | Liquid | 13 ppm
300 A | 151.06 A | Barstow "A" Filter | 2000-03-10 00:00:00 | Liquid | 15 ppm
300 A | 151.06 A | Barstow "A" Filter | 2000-03-21 00:00:00 | Liquid | 15 ppm
300 A | 151.06 A | Barstow "A" Filter | 2000-04-05 00:00:00 | Liquid | 22 ppm
300 A | 151.06 A | Barstow "A" Filter | 2000-04-18 00:00:00 | Liquid | 11 ppm
300 A | 151.06 A | Barstow "A" Filter | 2000-05-01 00:00:00 | Liquid | 7 ppm
300 A | 151.06 A | Barstow "A" Filter | 2000-05-14 00:00:00 | Liquid | 26 ppm
300 A | 151.06 A | Barstow "A" Filter | 2000-05-30 00:00:00 | Liquid | 10 ppm
300 A | 151.06 A | Barstow "A" Filter | 2000-06-14 00:00:00 | Liquid | 18 ppm
300 A | 151.06 A | Barstow "A" Filter | 2000-11-20 00:00:00 | Liquid | 23 ppm | ~ 45 mls
300 A | 151.06 A | Barstow "A" Filter | 2000-12-18 00:00:00 | Liquid | 18 ppm | ~ 260 mls
300 A | 151.06 A | Barstow "A" Meter | 2000-02-17 00:00:00 | Liquid | 9 ppm
300 A | 151.06 A | Barstow "A" Meter | 2000-02-28 00:00:00 | Liquid | 20 ppm
300 A | 151.06 A | Barstow "A" Meter | 2000-03-10 00:00:00 | Liquid | 16 ppm
300 A | 151.06 A | Barstow "A" Meter | 2000-03-21 00:00:00 | Liquid | 15 ppm
300 A | 151.06 A | Barstow "A" Meter | 2000-04-05 00:00:00 | Liquid | 18 ppm
300 A | 151.06 A | Barstow "A" Meter | 2000-04-18 00:00:00 | Liquid | 8 ppm
300 A | 151.06 A | Barstow "A" Meter | 2000-05-01 00:00:00 | Liquid | 17 ppm
300 A | 151.06 A | Barstow "A" Meter | 2000-05-14 00:00:00 | Liquid | 33 ppm
300 A | 151.06 A | Barstow "A" Meter | 2000-05-30 00:00:00 | Liquid | 5 ppm
300 A | 151.06 A | Barstow "A" Meter | 2000-06-14 00:00:00 | Liquid | 17 ppm
300 A | 151.06 A | Barstow "A" Meter | 2000-06-30 00:00:00 | Liquid | 15 ppm
300 A | 151.06 A | Barstow "A" Meter | 2000-07-29 00:00:00 | Liquid | 16 ppm
300 A | 151.06 A | Barstow "A" Meter | 2000-08-10 00:00:00 | Liquid | 1 ppm
300 A | 151.06 A | Barstow "A" Meter | 2000-08-16 00:00:00 | Liquid | 2 ppm
300 A | 151.06 A | Barstow "A" Meter | 2000-08-18 00:00:00 | Liquid | 9 ppm
300 A | 151.06 A | Barstow "A" Meter | 2000-08-24 00:00:00 | Liquid | 3 ppm
300 A | 151.06 A | Barstow "A" Meter | 2000-08-30 00:00:00 | Liquid | 4 ppm
300 A | 151.06 A | Barstow "A" Meter | 2000-09-05 00:00:00 | Liquid | 15 ppm | < 10 mls
300 A | 151.06 A | Barstow "A" Meter | 2000-09-19 00:00:00 | Liquid | 14 ppm | ~ 20 mls
300 A | 151.06 A | Barstow "A" Meter | 2000-10-02 00:00:00 | Liquid | 13 ppm | ~ 20 mls
300 A | 151.06 A | Barstow "A" Meter | 2000-10-16 00:00:00 | Liquid | 13 ppm | ~ 20 mls
300 A | 151.06 A | Barstow "A" Meter | 2000-10-26 00:00:00 | Liquid | 8 ppm | ~ 5 mls
300 A | 151.06 A | Barstow "A" Meter | 2000-11-20 00:00:00 | Liquid | 15 ppm | ~ 25 mls (sample recv'd. brkn.)
300 A | 151.06 A | Barstow "A" Meter | 2000-12-18 00:00:00 | Liquid | 14 ppm | ~ 25 mls (sample recv'd. brkn.)
300 A | 151.06 A | Barstow "A" Meter | 2001-01-23 00:00:00 | Liquid | 20 ppm as Aroclor 1242 | ~ 30 mls (sample recv'd. brkn.)
300 A | 154.70 A | Barstow "D" Meter | 2000-02-18 00:00:00 | Liquid | 38 ppm
300 A | 154.70 A | Barstow "D" Meter | 2000-02-28 00:00:00 | Liquid | 39 ppm
300 A | 154.70 A | Barstow "D" Meter | 2000-03-10 00:00:00 | Liquid | 34 ppm
300 A | 154.70 A | Barstow "D" Meter | 2000-03-21 00:00:00 | Liquid | 45 ppm
300 A | 154.70 A | Barstow "D" Meter | 2000-04-05 00:00:00 | Liquid | 29 ppm
300 A | 154.70 A | Barstow "D" Meter | 2000-04-18 00:00:00 | Liquid | 27 ppm
300 A | 154.70 A | Barstow "D" Meter | 2000-05-01 00:00:00 | Liquid | 28 ppm
300 A | 154.70 A | Barstow "D" Meter | 2000-05-14 00:00:00 | Liquid | 33 ppm
300 A | 154.70 A | Barstow "D" Meter | 2000-05-25 00:00:00 | Liquid | 19 ppm
300 A | 154.70 A | Barstow "D" Meter | 2000-06-14 00:00:00 | Liquid | 33 ppm
300 A | 154.70 A | Barstow "D" Meter | 2000-06-30 00:00:00 | Liquid | 22 ppm
300 A | 154.70 A | Barstow "D" Meter | 2000-07-29 00:00:00 | None
300 A | 154.70 A | Barstow "D" Meter | 2000-09-19 00:00:00 | Liquid | 30 ppm | 20 mls
300 A | 154.70 A | Barstow "D" Meter | 2000-10-02 00:00:00 | Liquid | 31 ppm | 20 mls
300 A | 154.70 A | Barstow "D" Meter | 2000-10-16 00:00:00 | Liquid | 34 ppm | 20 mls
300 A | 154.70 A | Barstow "D" Meter | 2000-10-26 00:00:00 | Liquid | 38 ppm | ~10 mls
300 A | 154.70 A | Barstow "D" Meter | 2000-11-20 00:00:00 | Liquid | 44 ppm | ~20 mls
300 A | 154.70 A | Barstow "D" Meter | 2000-12-18 00:00:00 | Liquid | 30 ppm as Aroclor 1242 | ~25 mls
300 A | 154.70 A | Barstow "D" Meter | 2000-12-18 00:00:00 | Liquid |  | Sample container received broken - no analysis
300 A | 154.70 A | Barstow "D" East Filter | 2000-02-11 00:00:00 | Liquid | ND < 1 ppm
300 A | 154.70 A | Barstow "D" East Filter | 2000-02-28 00:00:00 | Liquid |  | Insufficient Sample
300 A | 154.70 A | Barstow "D" East Filter | 2000-03-21 00:00:00 | Liquid | 0.45
300 A | 154.70 A | Barstow "D" East Filter | 2000-04-05 00:00:00 | Liquid | < 1 ppm
300 A | 154.70 A | Barstow "D" East Filter | 2000-07-29 00:00:00 | None
300 A | 154.70 A | Barstow "D" East Filter | 2000-08-10 00:00:00 | Liquid | 3 ppm
300 A | 154.70 A | Barstow "D" East Filter | 2000-08-16 00:00:00 | Liquid | 2 ppm
300 A | 154.70 A | Barstow "D" East Filter | 2000-08-24 00:00:00 | Liquid | 3 ppm
300 A | 154.70 A | Barstow "D" East Filter | 2000-08-30 00:00:00 | Liquid | 2 ppm
300 A | 154.70 A | Barstow "D" East Filter | 2000-09-07 00:00:00 | Liquid | 2 ppm
300 A | 159.33 A | Emergency Fuel |  | None |  | Tap not inspected or sampled
300 A | 159.33 A | Hinkley, K-11 Crankcase | 2000-05-01 00:00:00 | Liquid | ND < 1 ppm
300 A | 159.33 A | Hinkley, [NAME] | 2000-05-01 00:00:00 | Liquid | 6 ppm
300 A | 159.33 A | Hinkley Compressor Station 300A Suction Drip, Inlet 211 | 2000-01-27 00:00:00 | Liquid | 4 ppm
300 A | 159.33 A | Hinkley Compressor Station 300A Suction Drip, Inlet 211 | 2000-02-10 00:00:00 | Liquid | 3 ppm | Black; liquid obtained. Drip was emptied after sample was obtained Sample tap was plugged and was replaced with metric valve.
300 A | 159.33 A | Hinkley Compressor Station A Inlet Drip V-211 | 2000-02-25 00:00:00 | Liquid | 7 ppm
300 A | 159.33 A | Hinkley Compressor Station A Inlet Drip V-211 | 2000-03-09 00:00:00 | Liquid | 8 ppm
300 A | 159.33 A | Hinkley Compressor Station A Inlet Drip V-211 | 2000-04-06 00:00:00 | Liquid | 7 ppm
300 A | 159.33 A | Hinkley Compressor Station A Inlet Drip V-211 | 2000-05-01 00:00:00 | Liquid | 10 ppm
300 A | 159.33 A | Hinkley Compressor Station A Inlet Drip V-211 | 2000-05-14 00:00:00 | Liquid | 15 ppm
300 A | 159.33 A | Hinkley Compressor Station A Inlet Drip V-211 | 2000-05-14 00:00:00 | Liquid | 15 ppm
300 A | 159.33 A | Hinkley Compressor Station A Inlet Drip V-211 | 2000-05-30 00:00:00 | Liquid | 6 ppm
300 A | 159.33 A | Hinkley Compressor Station A Inlet Drip V-211 | 2000-06-30 00:00:00 | Liquid | 9 ppm
300 A | 159.33 A | Hinkley Compressor Station A Inlet Drip V-211 | 2000-07-29 00:00:00 | Liquid | 9 ppm
300 A | 159.33 A | Hinkley Compressor Station A Inlet Drip V-211 | 2000-09-18 00:00:00 | Liquid | 14 ppm | ~ 40 mls
300 A | 159.33 A | Hinkley Compressor Station A Inlet Drip V-211 | 2000-10-02 00:00:00 | Liquid | 21 ppm | ~ 40 mls
300 A | 159.33 A | Hinkley Compressor Station A Inlet Drip V-211 | 2000-10-27 00:00:00 | Liquid | 19 ppm | ~10 mls
300 A | 159.33 A | Hinkley Compressor Station A Inlet Drip V-211 | 2000-12-19 00:00:00 | Liquid | 18 ppm as Aroclor 1242 | ~20 mls
300 A | 159.33 A | Hinkley Compressor Station A Inlet Drip V-211 | 2001-01-23 00:00:00 | Liquid | 16 ppm | ~20 mls
300 A | 159.33 A | Hinkley Compressor Station A Inlet Drip V-212 | 2000-05-01 00:00:00 | Liquid | 7 ppm
300 A | 159.33 A | Hinkley Compressor Station A Inlet Drip V-212 | 2000-08-10 00:00:00 | Liquid | 2 ppm
300 A | 159.33 A | Hinkley Compressor Station A Inlet Drip V-212 | 2000-08-16 00:00:00 | Liquid | 3 ppm
300 A | 159.33 A | Hinkley Compressor Station A Inlet Drip V-212 | 2000-08-24 00:00:00 | Liquid | 2 ppm
300 A | 159.33 A | Hinkley Compressor Station A Inlet Drip V-212 | 2000-08-30 00:00:00 | Liquid | 3 ppm
300 A | 159.33 A | Hinkley Compressor Station A Inlet Drip V-212 | 2000-09-07 00:00:00 | Liquid | 2 ppm
300 A | 159.33 A | Hinkley Compressor Station A Inlet Drip V-212 | 2000-10-02 00:00:00 | Liquid | 13 ppm | ~30 mls
300 A | 159.33 A | Hinkley Compressor Station A Inlet Drip V-212 | 2000-10-16 00:00:00 | Liquid | 19 ppm | ~10 mls
300 A | 159.33 A | Hinkley Compressor Station A Inlet Drip V-212 | 2000-11-20 00:00:00 | Liquid | 12 ppm | ~20 mls
300 A | 159.33 A | Hinkley Compressor Station A Inlet Drip V-212 | 2000-12-19 00:00:00 | Liquid | 12 ppm as Aroclor 1242 | ~40 mls
300 A | 159.33 A | Hinkley Compressor Station A Inlet Drip V-212 | 2001-01-23 00:00:00 | Liquid | 13 ppm as Aroclor 1242 | ~40 mls
300 A | 160.00 A | Southwest Gas 3 Customers (Neirmeirer - McCormack) |  | None |  | Tap not inspected or sampled
300 A | 161.93 A | A Line Drip | 2000-02-10 00:00:00 | Liquid | <1 ppm
300 A | 161.93 A | A Line Drip | 2000-02-24 00:00:00 | Liquid | 2 ppm
300 A | 161.93 A | A Line Drip | 2000-03-09 00:00:00 | Liquid | ND < 1 ppm
300 A | 161.93 A | A Line Drip | 2000-03-23 00:00:00 | Liquid | ND < 1 ppm
300 A | 161.93 A | A Line Drip | 2000-04-06 00:00:00 | Liquid | <1 ppm
300 A | 161.93 A | A Line Drip | 2000-04-19 00:00:00 | Liquid | <1 ppm
300 A | 161.93 A | A Line Drip | 2000-05-01 00:00:00 | Liquid | <1 ppm
300 A | 161.93 A | A Line Drip | 2000-05-14 00:00:00 | Liquid | <1 ppm
300 A | 161.93 A | A Line Drip | 2000-06-01 00:00:00 | Liquid | <1 ppm
300 A | 161.93 A | A Line Drip | 2000-06-14 00:00:00 | Liquid | 1 ppm
300 A | 161.93 A | A Line Drip | 2000-06-30 00:00:00 | Liquid | <1 ppm
300 A | 161.93 A | A Line Drip | 2000-07-23 00:00:00 | None
300 A | 161.93 A | A Line Drip | 2000-07-29 00:00:00 | Liquid | 1.7 ppm as [NAME], 0.5 ppm as [NAME] 1260
300 A | 161.93 A | A Line Drip | 2000-09-06 00:00:00 | Liquid | 1 ppm | ~40 mls
300 A | 161.93 A | A Line Drip | 2000-09-18 00:00:00 | Liquid | 2 ppm | ~20 mls
300 A | 161.93 A | A Line Drip | 2000-10-03 00:00:00 | Liquid | 2 ppm | ~10 mls
300 A | 161.93 A | A Line Drip | 2000-10-16 00:00:00 | Liquid | 2 ppm | <10 mls
300 A | 161.93 A | A Line Drip | 2000-10-27 00:00:00 | Liquid | 3 ppm | ~10 mls
300 A | 161.93 A | A Line Drip | 2000-11-21 00:00:00 | Liquid | 3 ppm | <10 mls (sample contr. recv'd. [NAME])
300 A | 161.93 A | A Line Drip | 2000-12-19 00:00:00 | Liquid | 3 ppm as Aroclor 1242 | ~20 mls
300 A | 161.93 A | A Line Drip | 2001-01-23 00:00:00 | Liquid | 3 ppm as Aroclor 1242 | ~20 mls
300 A | 164.71 A | A Line Drip | 2000-02-10 00:00:00 | Liquid | <1
300 A | 164.71 A | A Line Drip | 2000-02-24 00:00:00 | Liquid | 5 ppm
300 A | 164.71 A | A Line Drip | 2000-03-09 00:00:00 | Liquid | <1 ppm
300 A | 164.71 A | A Line Drip | 2000-03-28 00:00:00 | Liquid | <1 ppm
300 A | 164.71 A | A Line Drip | 2000-04-06 00:00:00 | Liquid | <1 ppm
300 A | 164.71 A | A Line Drip | 2000-04-19 00:00:00 | Liquid | < 1 ppm
300 A | 164.71 A | A Line Drip | 2000-05-14 00:00:00 | Liquid | < 1 ppm
300 A | 164.71 A | A Line Drip | 2000-06-01 00:00:00 | Liquid | < 1 ppm
300 A | 164.71 A | A Line Drip | 2000-06-15 00:00:00 | Liquid | 1 ppm
300 A | 164.71 A | A Line Drip | 2000-06-30 00:00:00 | Liquid | 1 ppm
300 A | 164.71 A | A Line Drip | 2000-07-23 00:00:00 | None
300 A | 164.71 A | A Line Drip | 2000-07-29 00:00:00 | Liquid | 1 ppm
300 A | 164.71 A | A Line Drip | 2000-08-21 00:00:00 | Liquid | 1 ppm
300 A | 164.71 A | A Line Drip | 2000-09-06 00:00:00 | Liquid | 1 ppm | ~ 20 mls
300 A | 164.71 A | A Line Drip | 2000-09-18 00:00:00 | Liquid | 1 ppm | ~ 40 mls
300 A | 164.71 A | A Line Drip | 2000-10-03 00:00:00 | Liquid | 1 ppm | ~ 50 mls
300 A | 164.71 A | A Line Drip | 2000-10-16 00:00:00 | Liquid | 1 ppm | ~ 30 mls
300 A | 164.71 A | A Line Drip | 2000-10-27 00:00:00 | Liquid | 1 ppm | ~ 20 mls
300 A | 164.71 A | A Line Drip | 2000-11-21 00:00:00 | Liquid | 1 ppm | ~ 20 mls
300 A | 164.71 A | A Line Drip | 2000-12-19 00:00:00 | Liquid | 2 ppm as Aroclor 1242 | ~ 30 mls
300 A | 167.37 A | A Line Drip | 2000-02-10 00:00:00 | Liquid | <1 ppm
300 A | 167.37 A | A Line Drip | 2000-02-24 00:00:00 | Liquid | 6 ppm
300 A | 167.37 A | A Line Drip | 2000-03-09 00:00:00 | Liquid | <1 ppm
300 A | 167.37 A | A Line Drip | 2000-03-23 00:00:00 | Liquid | ND < 1 ppm
300 A | 167.37 A | A Line Drip | 2000-04-06 00:00:00 | Liquid | < 1 ppm
300 A | 167.37 A | A Line Drip | 2000-04-19 00:00:00 | Liquid | 1 ppm
300 A | 167.37 A | A Line Drip | 2000-05-01 00:00:00 | Liquid | < 1 ppm
300 A | 167.37 A | A Line Drip | 2000-05-14 00:00:00 | Liquid | < 1 ppm
300 A | 167.37 A | A Line Drip | 2000-06-01 00:00:00 | Liquid | < 1 ppm
300 A | 167.37 A | A Line Drip | 2000-06-16 00:00:00 | Liquid | < 1 ppm
300 A | 167.37 A | A Line Drip | 2000-06-30 00:00:00 | Liquid | 1 ppm
300 A | 167.37 A | A Line Drip | 2000-07-29 00:00:00 | Liquid | 1 ppm
300 A | 167.37 A | A Line Drip | 2000-08-21 00:00:00 | Liquid | 1 ppm
300 A | 167.37 A | A Line Drip | 2000-09-06 00:00:00 | Liquid | 1 ppm | ~20 mls
300 A | 167.37 A | A Line Drip | 2000-09-18 00:00:00 | Liquid | 1 ppm | ~20 mls
300 A | 167.37 A | A Line Drip | 2000-10-03 00:00:00 | Liquid | 3 ppm | ~50 mls
300 A | 167.37 A | A Line Drip | 2000-10-27 00:00:00 | Liquid | 2 ppm | ~20 mls
300 A | 167.37 A | A Line Drip | 2000-11-21 00:00:00 | Liquid | 3 ppm | ~20 mls
300 A | 167.37 A | A Line Drip | 2001-01-22 00:00:00 | Liquid | 3 ppm as Aroclor 1242 | ~10 mls
300 A | 170.61 A | A Line Drip | 2000-04-06 00:00:00 | Liquid | ND < 1ppm
300 A | 170.61 A | A Line Drip | 2000-04-19 00:00:00 | Liquid | ND < 1ppm
300 A | 170.61 A | A Line Drip | 2000-05-14 00:00:00 | Liquid | ND < 1ppm
300 A | 170.61 A | A Line Drip | 2000-06-01 00:00:00 | Liquid | ND < 1ppm
300 A | 170.61 A | A Line Drip | 2000-06-15 00:00:00 | Liquid | ND < 1ppm
300 A | 170.61 A | A Line Drip | 2000-06-30 00:00:00 | Liquid | ND < 1ppm
300 A | 170.61 A | A Line Drip | 2000-07-23 00:00:00 | None
300 A | 170.61 A | A Line Drip | 2000-08-21 00:00:00 | Liquid | 1 ppm
300 A | 170.61 A | A Line Drip | 2000-09-06 00:00:00 | Liquid | <1 ppm | ~10 mls
300 A | 170.61 A | A Line Drip | 2000-09-19 00:00:00 | Liquid | <1 ppm | <10 mls (trace)
300 A | 170.61 A | A Line Drip | 2000-10-03 00:00:00 | Liquid | <1 ppm | <10 mls (trace)
300 A | 170.61 A | A Line Drip | 2000-10-27 00:00:00 | Liquid | 18 ppm | ~20 mls (trace)
300 A | 170.61 A | A Line Drip | 2000-12-19 00:00:00 | Liquid | < 1 ppm | ~20 mls (trace)
300 A | 170.61 A | A Line Drip | 2001-01-23 00:00:00 | Liquid | 3 ppm as Aroclor 1242 | ~15 mls \
300 A | 170.62 A | Line 300 A Drip at Victorville Tap | 2000-02-10 00:00:00 | None |  | No liquids in drip
300 A | 175.49 A | Line 300 A Drip | 2000-02-10 00:00:00 | Liquid | ND < 1 ppm
300 A | 175.49 A | Line 300 A Drip | 2000-02-24 00:00:00 | Liquid | 7 ppm
300 A | 175.49 A | Line 300 A Drip | 2000-03-09 00:00:00 | Liquid | 1 ppm
300 A | 175.49 A | Line 300 A Drip | 2000-04-06 00:00:00 | Liquid | < 1 ppm
300 A | 175.49 A | Line 300 A Drip | 2000-04-19 00:00:00 | Liquid | 1 ppm
300 A | 175.49 A | Line 300 A Drip | 2000-05-14 00:00:00 | Liquid | < 1 ppm
300 A | 175.49 A | Line 300 A Drip | 2000-06-01 00:00:00 | Liquid | < 1 ppm
300 A | 175.49 A | Line 300 A Drip | 2000-06-15 00:00:00 | Liquid | 1 ppm
300 A | 175.49 A | Line 300 A Drip | 2000-06-29 00:00:00 | None | 1 ppm
300 A | 175.49 A | Line 300 A Drip | 2000-06-30 00:00:00 | Liquid | 1 ppm
300 A | 175.49 A | Line 300 A Drip | 2000-07-23 00:00:00 | Liquid | 1 ppm
300 A | 175.49 A | Line 300 A Drip | 2000-07-29 00:00:00 | Liquid | 1 ppm
300 A | 175.49 A | Line 300 A Drip | 2000-08-10 00:00:00 | Liquid | 2 ppm
300 A | 175.49 A | Line 300 A Drip | 2000-08-16 00:00:00 | Liquid | 2 ppm
300 A | 175.49 A | Line 300 A Drip | 2000-08-21 00:00:00 | Liquid | 1 ppm
300 A | 175.49 A | Line 300 A Drip | 2000-08-24 00:00:00 | Liquid | 2 ppm
300 A | 175.49 A | Line 300 A Drip | 2000-08-30 00:00:00 | Liquid | 2 ppm
300 A | 175.49 A | Line 300 A Drip | 2000-09-06 00:00:00 | Liquid | 2 ppm | ~20 mls
300 A | 175.49 A | Line 300 A Drip | 2000-09-07 00:00:00 | Liquid | 2 ppm
300 A | 175.49 A | Line 300 A Drip | 2000-09-19 00:00:00 | Liquid | 3 ppm | ~20 mls
300 A | 175.49 A | Line 300 A Drip | 2000-10-03 00:00:00 | Liquid | 3 ppm | ~50 mls
300 A | 175.49 A | Line 300 A Drip | 2000-10-16 00:00:00 | Liquid | 2 ppm | ~20 mls
300 A | 175.49 A | Line 300 A Drip | 2000-11-21 00:00:00 | Liquid | 2 ppm | ~20 mls
300 A | 175.49 A | Line 300 A Drip | 2000-12-19 00:00:00 | Liquid | 2 ppm as Aroclor 1242 | ~10 mls
300 A | 180.64 A | Trona - Main # 311 X | 2000-02-10 00:00:00 | None |  | No liquids in filter (east filter tap)
300 A | 181.79 A | Kramer Junction (4 Corners) | 2000-02-10 00:00:00 | Liquid | 4 ppm | Second Stage sample point - good liquid sample obtained
300 A | 181.79 A | Kramer Junction (4 Corners) | 2000-02-24 00:00:00 | Liquid | 5 ppm | Second stage Regulator
300 A | 181.79 A | Kramer Junction (4 Corners) | 2000-03-08 00:00:00 | Liquid | 7 ppm
300 A | 181.79 A | Kramer Junction (4 Corners) | 2000-03-21 00:00:00 | Liquid | 26 ppm
300 A | 181.79 A | Kramer Junction (4 Corners) | 2000-04-05 00:00:00 | Liquid | 11 ppm | [NAME]
300 A | 181.79 A | Kramer Junction (4 Corners) | 2000-04-18 00:00:00 | Liquid | 6 ppm
300 A | 181.79 A | Kramer Junction (4 Corners) | 2000-05-03 00:00:00 | Liquid | 12 ppm
300 A | 181.79 A | Kramer Junction (4 Corners) | 2000-05-15 00:00:00 | Liquid | 14 ppm
300 A | 181.79 A | Kramer Junction (4 Corners) | 2000-05-30 00:00:00 | Liquid | 26 ppm
300 A | 181.79 A | Kramer Junction (4 Corners) | 2000-07-25 00:00:00 | None
300 A | 181.79 A | Kramer Junction (4 Corners) | 2000-08-10 00:00:00 | Liquid | 8 ppm
300 A | 181.79 A | Kramer Junction (4 Corners) | 2000-08-21 00:00:00 | None
300 A | 181.79 A | Kramer Junction (4 Corners) | 2000-08-24 00:00:00 | Liquid | 4 ppm
300 A | 181.79 A | Kramer Junction (4 Corners) | 2000-09-06 00:00:00 | Liquid | 9 ppm | <10 mls
300 A | 181.79 A | Kramer Junction (4 Corners) | 2000-09-19 00:00:00 | None |  | Dry
300 A | 181.79 A | Kramer Junction (4 Corners) | 2000-10-04 00:00:00 | None |  | Dry
300 A | 181.79 A | Kramer Junction (4 Corners) | 2000-11-03 00:00:00 | None |  | Dry
300 A | 181.79 A | Kramer Junction (4 Corners) | 2000-12-05 00:00:00 | None |  | Dry
300 A | 181.79 A | Kramer Junction (4 Corners) | 2001-01-03 00:00:00 | None |  | Dry
300 A | 181.79 A | Kramer Junction (4 Corners) | 2001-02-02 00:00:00 | Liquid | 20 ppm as Aroclor 1242 | < 10 mls
300 A | 188.06 A | [NAME] |  | None |  | Tap not inspected or sampled
300 A | 188.06 A | [NAME] | 2000-06-01 00:00:00 | Liquid | 1 ppm
300 A | 191.09 A | US Borax and Chem. Co.,       [NAME] |  | None |  | Tap not inspected or sampled
300 A | 197.63 A | North Edwards - Red Barn | 2000-02-10 00:00:00 | None |  | Didn't sample
300 A | 200.97 A | Clay Mine Road (Muroc Motel) | 2000-02-10 00:00:00 | None |  | Didn't sample
300 A | 203.01 A | PLS 3A Insertion Meter | 2000-02-16 00:00:00 | Wipe | ND <0.7 ug/100cm2
300 A | 203.02 A | [NAME], from PLS #3, elbow | 2000-02-10 00:00:00 | Wipe | 1.3 ug/wipe | East Run - Two Wipe samples taken (semi-quantitative)
300 A | 203.02 A | [NAME], from PLS #3, elbow | 2000-08-10 00:00:00 | Wipe | 3 ppm
300 A | 203.02 A | [NAME], from PLS #3, valve | 2000-02-10 00:00:00 | Wipe | < 1ug/wipe | East Run - Two Wipe samples taken (semi-quantitative)
300 A | 203.02 A | [NAME], [NAME] | 2000-03-22 00:00:00 | Wipe | 2 ug /wipe as Aroclor 1016, 1 ug/wipe as Aroclor 1254
300 A | 203.02 A | [NAME], [NAME] | 2000-04-04 00:00:00 | Wipe | 0.8 ug /wipe as Aroclor 1016, 0.8 ug/wipe as Aroclor 1254
300 A | 203.02 A | [NAME], [NAME] | 2000-05-15 00:00:00 | Liquid | 1 ppm
300 A | 203.02 A | [NAME], [NAME] | 2000-06-01 00:00:00 | Liquid | 8 ppm
300 A | 203.02 A | [NAME], [NAME] | 2000-06-13 00:00:00 | Liquid | 3 ppm
300 A | 203.02 A | [NAME], [NAME] | 2000-07-24 00:00:00 | Liquid | 2.6 ppm as [NAME], 0.6 ppm as [NAME] 1260 | < 10 mls
300 A | 203.02 A | [NAME], [NAME] | 2000-08-07 00:00:00 | Liquid
300 A | 203.02 A | [NAME], [NAME] | 2000-08-22 00:00:00 | Liquid | 2 ppm as [NAME], 1 ppm as Aroclor 1254 | < 10 mls liquid
300 A | 203.02 A | [NAME], [NAME] | 2000-09-06 00:00:00 | Liquid | 2 ppm as [NAME], 2 ppm as [NAME] | < 10 mls
300 A | 203.02 A | [NAME], [NAME] | 2000-09-19 00:00:00 | Liquid | 2 ppm | < 10 mls
300 A | 203.02 A | [NAME], [NAME] | 2000-10-03 00:00:00 | Liquid | 19 ppm | < 10 mls
300 A | 203.02 A | [NAME], [NAME] | 2000-11-03 00:00:00 | Liquid | <1 ppm | < 10 mls?
300 A | 203.02 A | [NAME], [NAME] | 2001-01-02 00:00:00 | Liquid | 1 ppm as Aroclor 1242, 0.7ppm as Aroclor 1254 | < 10 mls
300 A | 203.02 A | [NAME], [NAME] | 2001-02-02 00:00:00 | Liquid | 2 ppm as Aroclor 1242 | < 10 mls
300 A | 203.02 A | [NAME], Housing [NAME] | 2000-03-22 00:00:00 | Liquid | < 1 ppm
300 A | 203.02 A | [NAME], Housing [NAME] | 2000-04-04 00:00:00 | Liquid | < 1 ppm
300 A | 203.02 A | [NAME], Housing [NAME] | 2000-04-19 00:00:00 | Liquid | ND < 1 ppm
300 A | 203.02 A | [NAME], Housing [NAME] | 2000-05-04 00:00:00 | Liquid | ND < 1 ppm
300 A | 203.02 A | [NAME], Housing [NAME] | 2000-05-15 00:00:00 | Liquid |  | Insufficient Sample
300 A | 203.02 A | [NAME], Housing [NAME] | 2000-06-01 00:00:00 | Liquid |  | Insufficient Sample
300 A | 203.02 A | [NAME], Housing [NAME] | 2000-06-13 00:00:00 | Liquid | ND < 1 ppm
300 A | 203.02 A | [NAME], Housing [NAME] | 2000-06-27 00:00:00 | Liquid |  | Insufficient Sample
300 A | 203.02 A | [NAME], Housing [NAME] | 2000-07-24 00:00:00 | None
300 A | 203.02 A | [NAME], Housing [NAME] | 2000-08-21 00:00:00 | None
300 A | 203.02 A | [NAME], Housing [NAME] | 2000-09-06 00:00:00 | Liquid |  | Insuffient sample, <10 mls
300 A | 203.02 A | [NAME], Housing [NAME] | 2000-09-19 00:00:00 | None |  | no liquid
300 A | 203.02 A | [NAME], Housing [NAME] | 2000-10-03 00:00:00 | None |  | no liquid
300 A | 203.02 A | [NAME], Housing [NAME] | 2000-11-03 00:00:00 | Liquid | ND < 1ppm | <10 mls
300 A | 203.02 A | [NAME], Housing [NAME] | 2000-12-01 00:00:00 | Liquid | 1 ppm as [NAME], < 1ppm, as [NAME] | <10 mls
300 A | 203.02 A | [NAME], Housing [NAME] | 2001-01-02 00:00:00 | Liquid | ND < 1 ppm | <10 mls
300 A | 203.02 A | [NAME], Housing [NAME] | 2001-02-02 00:00:00 | Liquid | ND < 5 ppm | <10 mls
300 A | 210.47 A | All American Pipeline Filter | 2000-02-29 00:00:00 | Liquid | < 1 ppm | Sample from filter (Site shut-in as of 4/00)
300 A | 210.47 A | All American Pipeline Filter | 2000-02-29 00:00:00 | Liquid | 1 ppm | Additional sample obtained from filter (Site shut-in as of 4/00)
300 A | 218.73 A | [NAME] and [NAME], So. Cal Gas |  | None |  | Tap not inspected or sampled
300 A | 225.57 A | California Portland Cement | 2000-02-24 00:00:00 | Liquid | ND < 1ppm | Sample from Old Orifice meter (Left)
300 A | 225.57 A | California Portland Cement | 2000-05-15 00:00:00 | Liquid | 1 ppm | Tap meter
300 A | 225.57 A | California Portland Cement | 2000-06-10 00:00:00 | Liquid | 1 ppm | Tap meter
300 A | 225.57 A | California Portland Cement | 2000-06-26 00:00:00 | Liquid | 1 ppm | Tap meter
300 A | 225.57 A | California Portland Cement | 2000-07-24 00:00:00 | Liquid | 2 ppm | Tap meter, < 10 mls
300 A | 225.57 A | California Portland Cement | 2000-08-07 00:00:00 | Liquid | 2 ppm | Tap meter, < 10 mls
300 A | 225.57 A | California Portland Cement | 2000-08-21 00:00:00 | Liquid | 8 ppm | Tap meter, < 10 mls
300 A | 225.57 A | California Portland Cement | 2000-09-18 00:00:00 | Liquid | 2 ppm | Tap meter, < 10 mls
300 A | 225.57 A | California Portland Cement | 2000-10-02 00:00:00 | Liquid | 2 ppm | Tap meter, < 10 mls
300 A | 225.57 A | California Portland Cement | 2000-10-30 00:00:00 | Liquid | 1 ppm | Tap meter, < 10 mls
300 A | 225.57 A | California Portland Cement | 2000-12-01 00:00:00 | Liquid | 2 ppm | Tap meter, < 10 mls
300 A | 225.57 A | California Portland Cement | 2001-01-02 00:00:00 | Liquid | 2 ppm as Aroclor 1242 | Tap meter, < 10 mls
300 A | 225.57 A | California Portland Cement | 2001-02-02 00:00:00 | Liquid | 2 ppm as Aroclor 1242 | Tap meter, < 10 mls
300 A | 225.91 A | California Portland Cement | 2000-02-24 00:00:00 | Wipe | < 1 ug/100cm2 | Wipe sample from bottom of meter
300 A | 225.91 A | California Portland Cement | 2000-04-05 00:00:00 | Liquid | ND < 1 ppm | Primary, downstream
300 A | 225.91 A | California Portland Cement | 2000-05-04 00:00:00 | Liquid | ND < 1 ppm | Primary, downstream
300 A | 225.91 A | California Portland Cement | 2000-10-02 00:00:00 | Liquid | 4 ppm as [NAME] 1260 | 12 GT Meter, sample taken downstream
300 A | 225.91 A | California Portland Cement | 2000-10-02 00:00:00 | Liquid | 4 ppm as [NAME] 1260 | 12 GT Meter, sample taken downstream
300 A | 225.91 A | California Portland Cement Meter | 2000-04-19 00:00:00 | Liquid | ND < 1ppm
300 A | 225.91 A | California Portland Cement Meter | 2000-05-15 00:00:00 | Liquid |  | Insufficient Sample
300 A | 225.91 A | California Portland Cement Meter | 2000-06-10 00:00:00 | Liquid | 1 ppm
300 A | 225.91 A | California Portland Cement Meter | 2000-07-24 00:00:00 | None
300 A | 225.91 A | California Portland Cement Meter | 2000-08-21 00:00:00 | None
300 A | 225.91 A | California Portland Cement Meter | 2000-09-05 00:00:00 | Liquid | 1 ppm | <10 mls
300 A | 225.91 A | California Portland Cement Meter | 2000-09-18 00:00:00 | None |  | no liquid
300 A | 225.91 A | California Portland Cement Meter | 2000-10-02 00:00:00 | None |  | no liquid
300 A | 225.91 A | California Portland Cement Meter | 2001-01-02 00:00:00 | None |  | no liquid
300 A | 116.28 B | [NAME] ([NAME]) |  | None |  | Tap not inspected or sampled
300 B | 129.92 B | [NAME], [NAME] (Customer meter) | 2000-02-09 00:00:00 | None |  | No liquid; no wipe
300 B | 129.92 B | [NAME], [NAME] (TAP) | 2000-02-09 00:00:00 | None |  | No acceptable sampling point
300 B | 130.38 B | Line 300 B insertion meter | 2000-02-11 00:00:00 | Wipe | ND < 0.7 ug/100cm2 | Pulled insertion meter; measured exterior surface area (not including turbine wheel); took wipe sample of measured area
300 B | 130.38 B | PLS 2XA Mist Extractor | 2000-04-12 00:00:00 | Liquid | ND <1ppm
300 B | 131.37 B | RHEOX Chem. Co. | 2000-02-08 00:00:00 | Liquid | 6 ppm | Sample obtained from filter, downstream of regulator. Black thick liquid obtained  Good taps before and after meter available for sampling.
300 B | 131.37 B | RHEOX Chem. Co. | 2000-02-24 00:00:00 | Liquid | 14 ppm | [NAME], Filter
300 B | 131.37 B | RHEOX Chem. Co. | 2000-03-09 00:00:00 | Liquid | 10 ppm | [NAME], Filter
300 B | 131.37 B | RHEOX Chem. Co. | 2000-03-21 00:00:00 | Liquid | 17 ppm | [NAME], Filter
300 B | 131.37 B | RHEOX Chem. Co. | 2000-04-05 00:00:00 | Liquid | 13 ppm | [NAME], Filter
300 B | 131.37 B | RHEOX Chem. Co. | 2000-04-17 00:00:00 | Liquid | 13 ppm | [NAME], Filter
300 B | 131.37 B | RHEOX Chem. Co. | 2000-04-17 00:00:00 | Liquid | ND < 1ppm | [NAME]
300 B | 131.37 B | RHEOX Chem. Co. | 2000-05-03 00:00:00 | Liquid | 35 ppm | [NAME], Filter
300 B | 131.37 B | RHEOX Chem. Co. | 2000-05-16 00:00:00 | Liquid | 12 ppm | [NAME], Filter
300 B | 131.37 B | RHEOX Chem. Co. | 2000-05-30 00:00:00 | Liquid | 12 ppm | [NAME], Filter
300 B | 131.37 B | RHEOX Chem. Co. | 2000-06-13 00:00:00 | Liquid | 12 ppm | [NAME], Filter
300 B | 131.37 B | RHEOX Chem. Co. | 2000-06-27 00:00:00 | Liquid | 12 ppm | [NAME], Filter
300 B | 131.37 B | RHEOX Chem. Co. | 2000-07-25 00:00:00 | Liquid | 10 ppm | [NAME], Filter, < 10 mls
300 B | 131.37 B | RHEOX Chem. Co. | 2000-08-22 00:00:00 | None |  | no liquid - new filter separator installed
300 B | 131.37 B | RHEOX Chem. Co. | 2000-09-19 00:00:00 | None |  | no liquid - new filter separator installed
300 B | 131.37 B | RHEOX Chem. Co. | 2000-10-03 00:00:00 | None |  | no liquid - new filter separator installed
300 B | 131.37 B | RHEOX Chem. Co. | 2000-10-03 00:00:00 | None |  | no liquid - new filter separator installed
300 B | 131.37 B | RHEOX Chem. Co. | 2000-12-05 00:00:00 | None |  | no liquid - new filter separator installed
300 B | 131.37 B | RHEOX Chem. Co. | 2001-01-03 00:00:00 | None |  | no liquid - new filter separator installed
300 B | 131.37 B | RHEOX Chem. Co. | 2001-02-05 00:00:00 | Liquid | 22 ppm as Aroclor 1242 | < 10 mls from separator
300 B | 131.37 B | Interto Co. [NAME], (American Transel Co.) |  | None |  | Tap not inspected or sampled - Line Abandoned
300 B | 135.65 B | Southwest Gas Corp. (Cirano Farm) |  | None |  | Tap not inspected or sampled
300 B | 137.55 B | SWG, Daggett Airport Tap | 2000-02-11 00:00:00 | None |  | Sample tap available from bottom of filter - No liquids were found.
300 B | 138.67 B | Hell's Acre Ranch |  | None |  | Tap not inspected or sampled - Service Tee and Valve only. Southwest Gas to furnish meter, etc.
300 B | 140.00 B | Kern River Daggett Intertie | 2000-02-10 00:00:00 | None |  | No liquid  from #7 Bypass valve next to filter separator. Separator is shut-in.
300 B | 140.65 B | SEGS 1 Meter Set | 2000-02-08 00:00:00 | Wipe | < 1ug/100cm2 | Wipe taken from 2 inches inside meter casing  on inlet side
300 B | 140.65 B | SEGS 1 Meter Set | 2000-02-08 00:00:00 | Liquid | 6 ppm | Small amount of clear liquid present at bottom of meter.
300 B | 140.65 B | SEGS 1 Meter Set | 2000-02-23 00:00:00 | Liquid | 2 ppm
300 B | 140.65 B | SEGS 1 Meter Set | 2000-03-21 00:00:00 | Liquid | 4 ppm
300 B | 140.65 B | SEGS 1 Meter Set | 2000-04-05 00:00:00 | Liquid | 6 ppm
300 B | 140.65 B | SEGS 1 Meter Set | 2000-04-17 00:00:00 | Liquid | 4 ppm
300 B | 140.65 B | SEGS 1 Meter Set | 2000-05-03 00:00:00 | Liquid | 5 ppm
 | 140.65 B | SEGS 1 Meter Set | 2000-06-13 00:00:00 | Liquid | 6 ppm
300 B | 140.65 B | SEGS 1 Primary drip Pot | 2000-02-08 00:00:00 | Wipe | < 1ug/100cm2 | Wipe sample taken from East filter only filter was degraded
300 B | 140.65 B | SEGS 1 Primary drip Pot | 2000-03-09 00:00:00 | Liquid | 2 ppm
300 B | 140.65 B | SEGS 1 Primary drip Pot | 2000-06-13 00:00:00 | Liquid | 6 ppm
300 B | 140.65 B | SEGS 1 Primary drip Pot | 2000-06-27 00:00:00 | Liquid | 5 ppm
300 B | 140.65 B | SEGS 1 Primary drip Pot | 2000-07-25 00:00:00 | None
300 B | 140.65 B | SEGS 1 Primary drip Pot | 2000-08-21 00:00:00 | None
300 B | 140.65 B | SEGS 1 Primary drip Pot | 2000-09-19 00:00:00 | None |  | Dry
300 B | 140.65 B | SEGS 1 Primary drip Pot | 2000-10-03 00:00:00 | None |  | Dry
300 B | 140.65 B | SEGS 1 Primary drip Pot | 2000-11-03 00:00:00 | None |  | Dry
300 B | 140.65 B | SEGS 1 Primary drip Pot | 2000-12-05 00:00:00 | None |  | Dry
300 B | 140.65 B | SEGS 1 Primary drip Pot | 2001-01-03 00:00:00 | Liquid | 5 ppm | < 10 mls
300 B | 140.65 B | SEGS 1 Primary drip Pot | 2001-02-05 00:00:00 | Liquid | 9 ppm as [NAME] 1016 | < 10 mls
300 B | 140.91 B | SWG,  [NAME] | 2000-02-10 00:00:00 | None |  | Sample tap available from bottom of filter - No liquids were found.
300 B | 159.33 B | Hinkley Compressor Station K-7, B Outlet | 2000-02-15 00:00:00 | Liquid | ND < 1 ppm
300 B | 159.33 B | Hinkley Compressor Station K-7, B Outlet | 2000-02-15 00:00:00 | Wipe | < 1ug/wipe
300 B | 159.33 B | Hinkley Compressor Station K-7, B Inlet | 2000-02-15 00:00:00 | Liquid | 1 ppm
300 B | 159.33 B | Hinkley Compressor Station 300B Suction Drip | 2000-01-27 00:00:00 | Liquid | 4 ppm
300 B | 159.33 B | Hinkley Compressor Station 300B Suction Drip | 2000-02-10 00:00:00 | Liquid | 4 ppm | Black liquid obtained. Drip was emptied after sample was obtained
300 B | 159.33 B | Hinkley Compressor Station B        V-211 Inlet Drip | 2000-04-20 00:00:00 | Liquid | 11 ppm
300 B | 159.33 B | Hinkley Compressor Station B        V-211 Inlet Drip | 2000-05-02 00:00:00 | Liquid | 10 ppm
300 B | 159.33 B | Hinkley Compressor Station B        V-211 Inlet Drip | 2000-06-15 00:00:00 | Liquid | 8 ppm
300 B | 159.33 B | Hinkley Compressor Station B        V-211 Inlet Drip | 2000-08-18 00:00:00 | Liquid | 9 ppm
300 B | 159.33 B | Hinkley Compressor Station B        V-211 Inlet Drip | 2000-09-05 00:00:00 | Liquid | 12 ppm | 50 mls
300 B | 161.02 B | Hinkley Compressor Station B        V-212 Inlet Drip | 2000-02-25 00:00:00 | Liquid | 7 ppm
300 B | 161.02 B | Hinkley Compressor Station B        V-212 Inlet Drip | 2000-03-09 00:00:00 | Liquid | 8 ppm
300 B | 161.02 B | Hinkley Compressor Station B       V-212 Inlet Drip | 2000-03-23 00:00:00 | Liquid | 12 ppm
300 B | 161.02 B | Hinkley Compressor Station B       V-212 Inlet Drip | 2000-04-06 00:00:00 | Liquid | 7 ppm
300 B | 161.02 B | Hinkley Compressor Station B       V-212 Inlet Drip | 2000-04-20 00:00:00 | Liquid | 7 ppm
300 B | 161.02 B | Hinkley Compressor Station B       V-212 Inlet Drip | 2000-05-01 00:00:00 | Liquid | 7 ppm
300 B | 161.02 B | Hinkley Compressor Station B       V-212 Inlet Drip | 2000-05-14 00:00:00 | Liquid | 11 ppm
300 B | 161.02 B | Hinkley Compressor Station B       V-212 Inlet Drip | 2000-05-30 00:00:00 | Liquid | 7 ppm
300 B | 161.02 B | Hinkley Compressor Station B       V-212 Inlet Drip | 2000-06-15 00:00:00 | Liquid | 8 ppm
300 B | 161.02 B | Hinkley Compressor Station B       V-212 Inlet Drip | 2000-06-30 00:00:00 | Liquid | 8 ppm
300 B | 161.02 B | Hinkley Compressor Station B       V-212 Inlet Drip | 2000-08-18 00:00:00 | Liquid | 9 ppm
300 B | 161.02 B | Hinkley Compressor Station B       V-212 Inlet Drip | 2000-08-18 00:00:00 | Liquid | 10 ppm | ~40 mls
300 B | 161.02 B | Hinkley Compressor Station B       V-212 Inlet Drip | 2000-09-18 00:00:00 | Liquid | 10 ppm | ~40 mls
300 B | 161.02 B | Hinkley Compressor Station B       V-212 Inlet Drip | 2000-10-16 00:00:00 | Liquid | 12 ppm | ~20 mls
300 B | 161.02 B | Hinkley Compressor Station B       V-212 Inlet Drip | 2000-10-26 00:00:00 | Liquid | 13 ppm | ~15 mls
300 B | 161.02 B | Hinkley Compressor Station B       V-212 Inlet Drip | 2000-11-20 00:00:00 | Liquid | 21 ppm | ~ 40 mls
300 B | 161.02 B | Hinkley Compressor Station B       V-212 Inlet Drip | 2000-12-19 00:00:00 | Liquid | 12 | ~ 30 mls
300 B | 168.39 B | SWG, [NAME] lake [NAME] | 2000-02-10 00:00:00 | Liquid | 1ppm | Sample obtained from bottom of inlet filter to 8" meter run.
300 B | 168.39 B | SWG, [NAME] lake [NAME] | 2000-02-25 00:00:00 | Liquid | 2 ppm | Sample obtained from 8" filter
300 B | 168.39 B | SWG, [NAME] lake [NAME] | 2000-03-09 00:00:00 | Liquid | 1 ppm | Sample obtained from 8" filter
300 B | 168.39 B | SWG, [NAME] lake [NAME] | 2000-03-23 00:00:00 | Liquid | 2 ppm | Sample obtained from 8" filter
300 B | 168.39 B | SWG, [NAME] lake [NAME] | 2000-04-23 00:00:00 | Liquid | <1 ppm | Sample obtained from 8" filter
300 B | 168.39 B | SWG, [NAME] lake [NAME] | 2000-05-01 00:00:00 | Liquid | 1 ppm | Sample obtained from 8" filter
300 B | 168.39 B | SWG, [NAME] lake [NAME] | 2000-05-14 00:00:00 | Liquid | 1 ppm | Sample obtained from 8" filter
300 B | 168.39 B | SWG, [NAME] lake [NAME] | 2000-06-01 00:00:00 | Liquid | 1 ppm | Sample obtained from 8" filter
300 B | 168.39 B | SWG, [NAME] lake [NAME] | 2000-06-15 00:00:00 | Liquid | 2 ppm | Sample obtained from 8" filter
300 B | 168.39 B | SWG, [NAME] lake [NAME] | 2000-06-30 00:00:00 | Liquid | 1 ppm | Sample obtained from 8" filter
300 B | 168.39 B | SWG, [NAME] lake [NAME] | 2000-07-29 00:00:00 | Liquid | 1 ppm | Sample obtained from 8" filter
300 B | 168.39 B | SWG, [NAME] lake [NAME] | 2000-08-21 00:00:00 | Liquid | 2 ppm | Sample obtained from 8" filter
300 B | 168.39 B | SWG, [NAME] lake [NAME] | 2000-09-05 00:00:00 | Liquid | 2 ppm | Sample obtained from 8" filter, ~10 mls
300 B | 168.39 B | SWG, [NAME] lake [NAME] | 2000-09-19 00:00:00 | Liquid | 2 ppm | Sample obtained from 8" filter, ~10 mls
300 B | 168.39 B | SWG, [NAME] lake [NAME] | 2000-10-03 00:00:00 | Liquid | 2 ppm | Sample obtained from 8" filter, < 10 mls
300 B | 168.39 B | SWG, [NAME] lake [NAME] | 2000-10-17 00:00:00 | Liquid | 2 ppm | Sample obtained from 8" filter, < 10 mls
300 B | 168.39 B | SWG, [NAME] lake [NAME] | 2000-10-27 00:00:00 | Liquid | 3 ppm | Sample obtained from 8" filter, < 10 mls
300 B | 168.39 B | SWG, [NAME] lake [NAME] | 2000-12-19 00:00:00 | Liquid | 2 ppm as Aroclor 1242 | Sample obtained from 8" filter, ~10 mls (sample container received broken)
300 B | 168.39 B | SWG, [NAME] lake [NAME] | 2001-01-22 00:00:00 | Liquid | 2 ppm as Aroclor 1242 | Sample obtained from 8" filter, ~10 mls
300 B | 168.39 B | SWG, [NAME] lake [NAME] | 2000-02-25 00:00:00 | Liquid | ND < 1ppm | Sample taken from 10" filter
300 B | 168.39 B | SWG, [NAME] lake [NAME] | 2000-03-09 00:00:00 | Liquid | ND < 1ppm | Sample taken from 10" filter
300 B | 168.39 B | SWG, [NAME] lake [NAME] | 2000-03-23 00:00:00 | Liquid |  | Sample container received broken - no analysis
300 B | 168.39 B | SWG, [NAME] lake [NAME] | 2000-04-18 00:00:00 | Liquid | 2 ppm | Sample taken from 10" filter
300 B | 168.39 B | SWG, [NAME] lake [NAME] | 2000-07-29 00:00:00 | None |  | Sample taken from 10" filter
300 B | 169.95 B | Line 300 B Drip at Victorville Tap | 2000-02-10 00:00:00 | Liquid | 1 ppm
300 B | 169.95 B | Line 300 B Drip at Victorville Tap | 2000-02-10 00:00:00 | Liquid | 1 ppm | Liquids obtained from drip. Drip completely drained after sampling. Drip was also drained during first week of 2/2000.
300 B | 169.95 B | Line 300 B Drip at Victorville Tap | 2000-03-09 00:00:00 | Liquid | 1 ppm
300 B | 169.95 B | Line 300 B Drip at Victorville Tap | 2000-04-06 00:00:00 | Liquid | 1 ppm
300 B | 169.95 B | Line 300 B Drip at Victorville Tap | 2000-04-19 00:00:00 | Liquid | < 1 ppm
300 B | 169.95 B | Line 300 B Drip at Victorville Tap | 2000-05-01 00:00:00 | Liquid | ND < 1 ppm
300 B | 169.95 B | Line 300 B Drip at Victorville Tap | 2000-05-14 00:00:00 | Liquid | ND < 1 ppm
300 B | 169.95 B | Line 300 B Drip at Victorville Tap | 2000-06-01 00:00:00 | Liquid |  | Insufficient sample
300 B | 169.95 B | Line 300 B Drip at Victorville Tap | 2000-06-15 00:00:00 | Liquid | 1 ppm
300 B | 169.95 B | Line 300 B Drip at Victorville Tap | 2000-06-30 00:00:00 | Liquid | 1 ppm
300 B | 169.95 B | Line 300 B Drip at Victorville Tap | 2000-07-29 00:00:00 | Liquid | 1 ppm
300 B | 169.95 B | Line 300 B Drip at Victorville Tap | 2000-08-21 00:00:00 | Liquid | 1 ppm
300 B | 169.95 B | Line 300 B Drip at Victorville Tap | 2000-09-06 00:00:00 | Liquid | 1 ppm | ~20 mls
300 B | 169.95 B | Line 300 B Drip at Victorville Tap | 2000-09-19 00:00:00 | Liquid | 2 ppm | ~20 mls
300 B | 169.95 B | Line 300 B Drip at Victorville Tap | 2000-10-03 00:00:00 | Liquid | 2 ppm | ~20 mls
300 B | 169.95 B | Line 300 B Drip at Victorville Tap | 2000-10-17 00:00:00 | Liquid | 2 ppm | ~20 mls
300 B | 169.95 B | Line 300 B Drip at Victorville Tap | 2000-10-27 00:00:00 | Liquid | 2 ppm | ~40 mls
300 B | 169.95 B | Line 300 B Drip at Victorville Tap | 2000-11-21 00:00:00 | Liquid | 3 ppm | ~15 mls
300 B | 169.95 B | Line 300 B Drip at Victorville Tap | 2000-12-19 00:00:00 | Liquid | 2 ppm | ~30 mls
300 B | 169.95 B | Line 300 B Drip at Victorville Tap | 2001-01-23 00:00:00 | Liquid | < 1 ppm | ~25 mls
300 B | 170.44 B | South West Gas - Harper Lake Meter Station |  | None |  | Tap not inspected or sampled
300 B | 180.11 B | Trona - Main # 311 X |  | None |  | Tap not inspected or sampled
300 B | 182.00 B | [NAME] |  | None |  | Farm tap Reg. Set. Tap. Service tap not inspected or sampled and is abandoned
300 B | 182.58 B | SEGS 3 & 4 Primary Filter | 2000-02-10 00:00:00 | Liquid | 2 ppm | [NAME] generated during sampling (light coating in bottle only)
300 B | 182.58 B | SEGS 3 & 4 Primary Filter | 2000-02-24 00:00:00 | Liquid | 2 ppm
300 B | 182.58 B | SEGS 3 & 4 Primary Filter | 2000-03-08 00:00:00 | Liquid | 3 ppm
300 B | 182.58 B | SEGS 3 & 4 Primary Filter | 2000-03-22 00:00:00 | Liquid | 3 ppm
300 B | 182.58 B | SEGS 3 & 4 Primary Filter | 2000-04-05 00:00:00 | Liquid | 2 ppm
300 B | 182.58 B | SEGS 3 & 4 Primary Filter | 2000-04-17 00:00:00 | Liquid | 3 ppm
300 B | 182.58 B | SEGS 3 & 4 Primary Filter | 2000-05-04 00:00:00 | Liquid | 2 ppm
300 B | 182.58 B | SEGS 3 & 4 Primary Filter | 2000-05-16 00:00:00 | Liquid | 1 ppm
300 B | 182.58 B | SEGS 3 & 4 Primary Filter | 2000-05-30 00:00:00 | Liquid | 2 ppm
300 B | 182.58 B | SEGS 3 & 4 Primary Filter | 2000-06-13 00:00:00 | Liquid | 2 ppm
300 B | 182.58 B | SEGS 3 & 4 Primary Filter | 2000-06-27 00:00:00 | Liquid | 3 ppm
300 B | 182.58 B | SEGS 3 & 4 Primary Filter | 2000-07-25 00:00:00 | Liquid | 3 ppm | < 10 mls
300 B | 182.58 B | SEGS 3 & 4 Primary Filter | 2000-08-07 00:00:00 | Liquid | 4 ppm | ~10 mls
300 B | 182.58 B | SEGS 3 & 4 Primary Filter | 2000-08-22 00:00:00 | Liquid | 3 ppm | ~50 mls liquid
300 B | 182.58 B | SEGS 3 & 4 Primary Filter | 2000-09-06 00:00:00 | Liquid | 6 ppm as [NAME], 2 ppm as [NAME] | ~10 mls
300 B | 182.58 B | SEGS 3 & 4 Primary Filter | 2000-09-18 00:00:00 | Liquid | 6 ppm | ~10 mls
300 B | 182.58 B | SEGS 3 & 4 Primary Filter | 2000-10-04 00:00:00 | Liquid | 4 ppm | ~20 mls
300 B | 182.58 B | SEGS 3 & 4 Primary Filter | 2000-11-03 00:00:00 | Liquid | 3 ppm | ~20 mls
300 B | 182.58 B | SEGS 3 & 4 Primary Filter | 2000-12-04 00:00:00 | Liquid | 4 ppm | ~10 mls
300 B | 182.58 B | SEGS 3 & 4 Primary Filter | 2001-01-03 00:00:00 | Liquid | 13 ppm as Aroclor 1242 | ~10 mls
300 B | 182.58 B | SEGS 3 & 4 Primary Filter | 2001-02-05 00:00:00 | Liquid | 6 ppm as Aroclor 1242 | ~25mls
300 B | 182.58 B | SEGS 5,6 & 7 Primary | 2000-02-10 00:00:00 | None |  | Filter was dry
300 B | 182.58 B | SEGS 7 [NAME] | 2000-02-10 00:00:00 | None |  | Turbine mater sample - dry
300 B | 187.78 B | [NAME] | 2000-02-10 00:00:00 | Liquid | 1 ppm | Primary reg. filter, East run; good sample
300 B | 187.78 B | [NAME] | 2000-02-24 00:00:00 | Liquid | 2 ppm
300 B | 187.78 B | [NAME] | 2000-03-08 00:00:00 | Liquid | 1 ppm
300 B | 187.78 B | [NAME] | 2000-04-04 00:00:00 | Liquid | 1 ppm
300 B | 187.78 B | [NAME] | 2000-04-17 00:00:00 | Liquid | 1 ppm
300 B | 187.78 B | [NAME] | 2000-05-04 00:00:00 | Liquid | 1 ppm
300 B | 187.78 B | [NAME] | 2000-05-15 00:00:00 | Liquid | 1 ppm
300 B | 187.78 B | [NAME] | 2000-06-01 00:00:00 | Liquid | 1 ppm
300 B | 187.78 B | [NAME] | 2000-06-27 00:00:00 | None |  | Insufficient sample
300 B | 187.78 B | [NAME] | 2000-08-22 00:00:00 | None |  | no liquids
300 B | 187.78 B | [NAME] | 2000-09-06 00:00:00 | None |  | no liquids
300 B | 187.78 B | [NAME] | 2000-09-19 00:00:00 | None |  | no liquids
300 B | 187.78 B | [NAME] | 2000-10-03 00:00:00 | None |  | no liquids
300 B | 187.78 B | [NAME] | 2000-10-31 00:00:00 | None |  | no liquids
300 B | 187.78 B | [NAME] | 2000-12-05 00:00:00 | None |  | no liquids
300 B | 187.78 B | [NAME] | 2001-01-03 00:00:00 | None |  | no liquids
300 B | 187.78 B | Boron High School Dry Gas Meter No. 32707774 | 2000-03-15 00:00:00 | Wipe | ND < 1ug/wipe | [NAME] removed and replaced. Non-quantitative wipe taken on drain cover and inside of drain cover opening.
300 B | 187.78 B | [NAME], 26611 Nugent, [NAME] | 2000-03-13 00:00:00 | Wipe | ND < 1ug/wipe | Non-quantitative wipe inside filter
300 B | 191.14 B | US Borax (Bypass) |  | None |  | Tap not inspected or sampled
300 B | 191.18 B | [NAME] Borax | 2000-02-10 00:00:00 | None |  | Primary reg. filter, [NAME] run; dry (Recheck filter)
300 B | 191.18 B | US Borax |  | None |  | Tap not inspected or sampled
300 B | 197.70 B | [NAME], [NAME] |  | None |  | Tap not inspected or sampled; line abandoned
300 B | 198.88 B | Edgemont Road District (West Boron Area) Increase Capacity |  | None |  | [NAME], original farm tap and reg. Installed second farm tap and reg. in parallel with existing set. Taps not inspected or sampled.
300 B | 199.24 B | Fountain Trailer Court |  | None |  | Tap not inspected or sampled - line abandoned in 1987
300 B | 203.07 B | PLS 3B Insertion Meter | 2000-02-16 00:00:00 | Wipe | ND <0.7 ug/100cm2
300 B | 203.07 B | PLS 3B Mist Extractor | 2000-04-14 00:00:00 | Liquid | ND < 1ppm
300 B | 203.07 B | Emergency Tie-in to Main 300B |  | None |  | Tap not inspected or sampled
300 B | 239.04 B | Tehachapi |  | None |  | Tap not inspected or sampled - line abandoned
311 X | 54.88 | Ridgecrest West End Primary | 2000-02-22 00:00:00 | Wipe | < 1ug/100cm2 | Right Filter
311 X | 54.88 | Ridgecrest West End Primary | 2000-04-06 00:00:00 | Wipe | ND < 1ug/wipe | Right Filter (non-quantitative wipe)
311 X | 54.88 | Ridgecrest West End Primary | 2000-04-19 00:00:00 | Wipe | ND < 1ug/wipe | Right Filter (non-quantitative wipe)
311 X | 54.88 | Ridgecrest West End Primary | 2000-07-24 00:00:00 | None
311 X | 54.88 | Ridgecrest West End Primary | 2000-09-18 00:00:00 | None
311 X | 54.88 | Ridgecrest West End Primary | 2000-10-02 00:00:00 | None
311 X | 54.88 | Ridgecrest West End Primary | 2001-01-02 00:00:00 | None
311 X | 54.88 | IMC Chemical, Trona | 2000-04-03 00:00:00 | Wipe | 2.6 ug/wipe as Aroclor 1016, 1.2 ug/wipe as Aroclor 1254 | West End Turbine Meter
311 X | 54.88 | Ridgecrest West End Turbine Meter | 2000-04-19 00:00:00 | Liquid | 11 ppm as [NAME], 12 ppm as [NAME] 1260
311 X | 54.88 | Ridgecrest West End Turbine Meter | 2000-05-04 00:00:00 | Liquid | 11 ppm as [NAME], 8 ppm as [NAME]
311 X | 54.88 | Ridgecrest West End Turbine Meter | 2000-05-31 00:00:00 | Liquid | 13 ppm as [NAME], 9 ppm as Aroclor 1254
311 X | 54.88 | Ridgecrest West End Turbine Meter | 2000-06-12 00:00:00 | Liquid | 16 ppm as [NAME], 7 ppm as [NAME] 1260
311 X | 54.88 | Ridgecrest West End Turbine Meter | 2000-06-26 00:00:00 | Liquid | 11 ppm as [NAME], 17 ppm as [NAME] 1260
311 X | 54.88 | Ridgecrest West End Turbine Meter | 2000-07-24 00:00:00 | Liquid | 8.4 ppm as [NAME], 7.9 ppm as [NAME] 1260
311 X | 54.88 | Ridgecrest West End Turbine Meter | 2000-08-08 00:00:00 | Liquid | 29 ppm as [NAME], 27 ppm as [NAME] | <10 mls
311 X | 54.88 | Ridgecrest West End Turbine Meter | 2000-09-05 00:00:00 | Liquid | 6 ppm as [NAME], 9 ppm as Aroclor 1254 | < 10 mls
311 X | 54.88 | Ridgecrest West End Turbine Meter | 2000-09-18 00:00:00 | Liquid | 7 ppm as [NAME], 9 ppm as [NAME] 1260 | < 10 mls
311 X | 54.88 | Ridgecrest West End Turbine Meter | 2000-10-02 00:00:00 | Liquid |  | < 10 mls (Insufficient sample)
311 X | 54.88 | Ridgecrest West End Process | 2000-05-04 00:00:00 | Liquid | 4 ppm as [NAME], 4 ppm as [NAME] | Turbine mater
311 X | 54.88 | Ridgecrest West End Process | 2000-05-16 00:00:00 | Liquid | 4 ppm as [NAME], 12 ppm as [NAME]
311 X | 54.88 | Ridgecrest West End Process | 2000-05-31 00:00:00 | Liquid | 5 ppm as [NAME], 8 ppm as [NAME]
311 X | 54.88 | Ridgecrest West End Process | 2000-08-21 00:00:00 | None |  | no liquids found
311 X | 54.88 | Ridgecrest West End Process | 2000-10-02 00:00:00 | Liquid | 10 ppm as Aroclor 1016, 7 ppm as [NAME] 1260 | < 10 mls
311 X | 54.88 | Ridgecrest West End Process | 2000-10-31 00:00:00 | Liquid | 6.7 ppm as [NAME], 5.8 ppm as [NAME] 1260 | < 10 mls
311 X | 54.88 | Ridgecrest West End Process | 2001-01-02 00:00:00 | Liquid | 3 ppm as Aroclor 1242, 3 ppm as Aroclor 1254 | < 10 mls
311 X | 54.88 | Ridgecrest West End Process | 2001-02-01 00:00:00 | Liquid | 12 ppm as Aroclor 1242, 12ppm as Aroclor 1254 | < 10 mls from filter
311 X | 54.44 | West End Plant (old [NAME] set) | 2000-06-12 00:00:00 | Wipe | ND < 1 ug/wipe | Semi-quantitative
311 X | 54.44 | West End Plant (old [NAME] set) | 2000-08-21 00:00:00 | None |  | no liquid found
311 X | 54.44 | West End Plant (old [NAME] set) | 2001-01-02 00:00:00 | None |  | no liquid found
311 X | 58.04 | IMC Chemical, Trona - Argus, Main Tap | 2000-05-31 00:00:00 | Liquid | 4 ppm as [NAME], 11 ppm as [NAME] | 12 GT Meter
311 X | 58.04 | IMC Chemical, Trona - Argus, Main Tap | 2000-06-12 00:00:00 | Liquid | 6 ppm as [NAME], 7 ppm as [NAME] 1260
311 X | 58.04 | IMC Chemical, Trona - Argus, Main Tap | 2000-06-26 00:00:00 | Liquid | 5 ppm as [NAME], 9 ppm as [NAME] 1260
311 X | 58.04 | IMC Chemical, Trona - Argus, Main Tap | 2000-08-08 00:00:00 | Liquid | 8 ppm as [NAME], 19 ppm as [NAME]
311 X | 58.04 | IMC Chemical, Trona - Argus, Main Tap | 2000-08-21 00:00:00 | Liquid | 8 ppm as [NAME], 27 ppm as [NAME] | <10 mls taken from meter drip
311 X | 58.04 | IMC Chemical, Trona - Argus, Main Tap | 2000-09-05 00:00:00 | Liquid | 3 ppm as [NAME], 11 ppm as [NAME] | < 10 mls
311 X | 58.04 | IMC Chemical, Trona - Argus, Main Tap | 2000-09-18 00:00:00 | Liquid | 3 ppm as [NAME], 12 ppm as [NAME] 1260 | < 10 mls
311 X | 58.04 | IMC Chemical, Trona - Argus, Main Tap | 2000-10-02 00:00:00 | Liquid | 2 ppm as [NAME], 8 ppm as [NAME] 1260 | < 10 mls
311 X | 58.04 | IMC Chemical, Trona - Argus, Main Tap | 2000-10-31 00:00:00 | Liquid | 2.8 ppm as [NAME], 8.9 ppm as [NAME] 1260 | < 10 mls
311 X | 58.04 | IMC Chemical, Trona - Argus, Main Tap | 2000-12-01 00:00:00 | Liquid | 4 ppm as [NAME], 9 ppm as Aroclor 1254 | < 10 mls
311 X | 58.04 | IMC Chemical, Trona - Argus, Main Tap | 2001-01-02 00:00:00 | Liquid | 5 ppm as [NAME], 17 ppm as [NAME] | < 10 mls
311 X | 58.04 | IMC Chemical, Trona - Argus, Main Tap | 2001-02-01 00:00:00 | Liquid | 7 ppm as Aroclor 1242, 14 ppm as [NAME] | < 10 mls from filter
313 X | 27.26 | SWG Rabbit Springs Rd. | 2000-02-09 00:00:00 | Liquid | 2 ppm, < 1ppm as Aroclor 1260. Semi quantitative results due to small sample | Obtained small amount of liquid obtained from bottom tap of meter. No liquid from gooseneck pipe on north filter.
313 X | 27.26 | SWG Rabbit Springs Rd. [NAME] | 2000-02-28 00:00:00 | Liquid | 4 ppm
313 X | 27.26 | SWG Rabbit Springs Rd. [NAME] | 2000-03-10 00:00:00 | Liquid | 10 ppm
313 X | 27.26 | SWG Rabbit Springs Rd. [NAME] | 2000-03-22 00:00:00 | Liquid | 5 ppm
313 X | 27.26 | SWG Rabbit Springs Rd. [NAME] | 2000-04-06 00:00:00 | Liquid | 9 ppm
313 X | 27.26 | SWG Rabbit Springs Rd. [NAME] | 2000-05-14 00:00:00 | Liquid | 4 ppm
313 X | 27.26 | SWG Rabbit Springs Rd. [NAME] | 2000-06-14 00:00:00 | Liquid | 11 ppm
313 X | 27.26 | SWG Rabbit Springs Rd. [NAME] | 2000-06-30 00:00:00 | Liquid | 9 ppm as [NAME], 2 ppm as [NAME]
313 X | 27.76 | SWG, Rabbit Springs Rd. [NAME] | 2000-07-29 00:00:00 | Liquid | 6.8 ppm, as [NAME], 1.1 ppm, as [NAME] 1260
313 X | 27.76 | SWG, Rabbit Springs Rd. [NAME] | 2000-09-05 00:00:00 | Liquid |  | <10 mls (insuffiient sample)
313 X | 29.08 | SWG Old Woman Springs | 2000-02-09 00:00:00 | None |  | North filter is dry (no way to sample bypass filter)
313 X | 34.34 | Mitsubishi Cement | 2000-02-09 00:00:00 | Liquid | 2 ppm, 3ppm as Aroclor 1260 | Sample taken from bottom of filter (gas flowing 6 mcf / hour)
313 X | 34.34 | Mitsubishi Cement | 2000-02-23 00:00:00 | None |  | [NAME] (check location)
313 X | 34.34 | Mitsubishi Cement | 2000-02-24 00:00:00 | Liquid | 3 ppm, 3ppm as Aroclor 1254 | Sample from meter set
313 X | 34.34 | Mitsubishi Cement | 2000-03-08 00:00:00 | Liquid | 4 ppm as [NAME], 3ppm as Aroclor 1260 | Sample from meter set
313 X | 34.34 | Mitsubishi Cement | 2000-03-20 00:00:00 | Liquid | 2 ppm as [NAME], 3ppm as Aroclor 1260 | Sample from meter set
313 X | 34.34 | Mitsubishi Cement | 2000-04-05 00:00:00 | Liquid | 3 ppm as [NAME], 3ppm as Aroclor 1254 | Sample from meter set
313 X | 34.34 | Mitsubishi Cement | 2000-04-05 00:00:00 | Liquid | 1 ppm as [NAME], 3ppm as Aroclor 1254 | Sample from meter set
313 X | 34.34 | Mitsubishi Cement | 2000-04-27 00:00:00 | Liquid | 7 ppm as [NAME], 2 ppm as [NAME] | Sampled Labeled as "Big Bear B" at MP 34.34
313 X | 34.34 | Mitsubishi Cement | 2000-05-01 00:00:00 | Liquid | 1 ppm as [NAME], 3 ppm as Aroclor 1254
313 X | 34.34 | Mitsubishi Cement | 2000-05-15 00:00:00 | Liquid | 2 ppm as [NAME], 4 ppm as [NAME]
313 X | 34.34 | Mitsubishi Cement | 2000-05-30 00:00:00 | Liquid | 3 ppm as [NAME], 3 ppm as Aroclor 1254
313 X | 34.34 | Mitsubishi Cement | 2000-06-13 00:00:00 | Liquid | 4 ppm as [NAME], 3 ppm as [NAME] 1260
313 X | 34.34 | Mitsubishi Cement | 2000-07-24 00:00:00 | Liquid | 1 ppm as [NAME], 0.6 ppm as [NAME] 1260 | < 10 mls
313 X | 34.34 | Mitsubishi Cement | 2000-08-08 00:00:00 | None |  | [NAME] set dry
313 X | 34.34 | Mitsubishi Cement | 2000-08-21 00:00:00 | Liquid | ND < 1 ppm | < 10 mls
313 X | 34.34 | Mitsubishi Cement | 2000-09-05 00:00:00 | Liquid | ND < 1 ppm | < 10 mls
313 X | 34.34 | Mitsubishi Cement | 2000-09-18 00:00:00 | Liquid | ND < 3 ppm | < 10 mls (reporting limit raised because of small sample size)
313 X | 34.34 | Mitsubishi Cement | 2000-10-04 00:00:00 | Liquid | 42 ppm | < 10 mls
313 X | 34.34 | Mitsubishi Cement | 2000-12-04 00:00:00 | None | 6 ppm as [NAME], 3 ppm as [NAME] 1260 | < 10 mls
313 X | 34.34 | Mitsubishi Cement | 2001-01-03 00:00:00 | None | 2 ppm as Aroclor 1242, 2 ppm as [NAME] | < 10 mls
313 X | 34.34 | Mitsubishi Cement | 2001-02-02 00:00:00 | None | 2 ppm as [NAME] 1016 | < 10 mls
314 X | 0.02 | Company Use |  |  |  | Tap not Inspected or sampled ([NAME])
314 X | 0.06 | SW Gas (Hinkley Tap) |  |  |  | Tap not Inspected or sampled
314 X | 8.76 | SW Gas (Zackey Farms) |  |  |  | Tap not inspected or sampled
314 X | 21.76 | SW Gas (La Delta, Helendale) |  |  |  | Tap not Inspected or sampled (San Joaquin Div. job)
314 X | 24.31 | TXI Riverside Cement PLS | 2000-02-09 00:00:00 | None |  | Active filter next to Valve 4. Bottom tap of filter is dry. Note: Clearance reqrd. for filter removal and wipe sampling
314 X | 24.31 | TXI Riverside Cement PLS | 2000-08-21 00:00:00 | None |  | no liquids
314 X | 24.31 | TXI Riverside Cement PLS | 2000-09-06 00:00:00 | None |  | no liquids
314 X | 24.31 | TXI Riverside Cement PLS | 2000-09-18 00:00:00 | None |  | no liquids
314 X | 24.31 | TXI Riverside Cement PLS | 2000-10-04 00:00:00 | None |  | no liquids
314 X | 24.31 | TXI Riverside Cement PLS | 2001-01-03 00:00:00 | None |  | no liquids
314 X | 24.31 | TXI Riverside Cement PLS | 2001-02-02 00:00:00 | None |  | no liquids
314 X | 24.75 | TXI Riverside Tap Meter | 2000-02-09 00:00:00 | Liquid | 16 ppm, 4ppm as Aroclor 1260 | Sample taken from bottom of [NAME] amount of liquid
314 X | 24.75 | TXI Riverside Tap Meter | 2000-02-15 00:00:00 | Liquid | 9 ppm
314 X | 24.75 | TXI Riverside Tap Meter | 2000-02-23 00:00:00 | Liquid | 19 ppm as [NAME], 5 ppm as [NAME]
314 X | 24.75 | TXI Riverside Tap Meter | 2000-03-08 00:00:00 | Liquid | 45 ppm
314 X | 24.75 | TXI Riverside Tap Meter | 2000-03-22 00:00:00 | Liquid | 11 ppm
314 X | 24.75 | TXI Riverside Tap Meter | 2000-04-05 00:00:00 | Liquid | 24 ppm as [NAME], 7 ppm as [NAME]
314 X | 24.75 | TXI Riverside Tap Meter | 2000-04-18 00:00:00 | Liquid | 22 ppm, 5 ppm as [NAME] 1260
314 X | 24.75 | TXI Riverside Tap Meter | 2000-05-01 00:00:00 | Liquid | 6 ppm
314 X | 24.75 | TXI Riverside Tap Meter | 2000-05-15 00:00:00 | Liquid | 5 ppm, 2 ppm as [NAME] | Bottom inside [NAME]
314 X | 24.75 | TXI Riverside Tap Meter | 2000-05-15 00:00:00 | Liquid | < 1 ppm | Top of inside meter
314 X | 24.75 | TXI Riverside Tap Meter | 2000-05-30 00:00:00 | Liquid | 31 ppm, 3 ppm as Aroclor 1254 | Bottom inside [NAME]
314 X | 24.75 | TXI Riverside Tap Meter | 2000-06-12 00:00:00 | Liquid | 34 ppm, 3 ppm as Aroclor 1254
314 X | 24.75 | TXI Riverside Tap Meter | 2000-06-26 00:00:00 | Liquid | 30 ppm, 3 ppm as Aroclor 1254
314 X | 24.75 | TXI Riverside Tap Meter | 2000-07-24 00:00:00 | Liquid | 26 ppm, 2.5 ppm as [NAME] | < 10 mls
314 X | 24.75 | TXI Riverside Tap Meter | 2000-08-08 00:00:00 | Liquid | 40 ppm, 12 ppm as [NAME] | < 10 mls
314 X | 24.75 | TXI Riverside Tap Meter | 2000-08-21 00:00:00 | Liquid | 25 ppm, 14 ppm as [NAME] | < 10 mls
314 X | 24.75 | TXI Riverside Tap Meter | 2000-09-05 00:00:00 | Liquid | 16 ppm, 6 ppm as Aroclor 1254 | < 10 mls
314 X | 24.75 | TXI Riverside Tap Meter | 2000-09-18 00:00:00 | Liquid | 20 ppm, 3 ppm as [NAME] 1260 | < 10 mls
314 X | 24.75 | TXI Riverside Tap Meter | 2000-10-04 00:00:00 | Liquid | 22 ppm, 4 ppm as [NAME] | < 10 mls
314 X | 24.75 | TXI Riverside Tap Meter | 2000-11-03 00:00:00 | Liquid | 19 ppm, 3.5 ppm as [NAME] | < 10 mls
314 X | 24.75 | TXI Riverside Tap Meter | 2000-12-04 00:00:00 | Liquid | 22 ppm, 6 ppm as Aroclor 1254 | < 10 mls
314 X | 24.75 | TXI Riverside Tap Meter | 2001-01-03 00:00:00 | Liquid | 19 ppm as Aroclor 1242, 7 ppm as [NAME] | < 10 mls
314 X | 24.75 | TXI Riverside Tap Meter | 2001-02-01 00:00:00 | Liquid | 29 ppm as [NAME], 24 ppm as [NAME] | < 10 mls
314 X | 25.2 | SW Gas (Academy Road) |  |  |  | Tap not Inspected or sampled (San Joaquin Div. job)
314 X | 26 | SW Gas (Clanton) |  |  |  | Tap not Inspected or sampled (San Joaquin Div. job)
314 X | 26.8 | None |  |  |  | Tap not inspected or sampled (4" valve installed on original const. for SWG - capped)
314 X | 27.46 | Victorville "B" Meter | 2000-02-15 00:00:00 | Liquid | 5 ppm
314 X | 27.46 | Victorville "B" Meter | 2000-07-15 00:00:00 | Liquid | 3.5 ppm as [NAME], 0.6 ppm as [NAME] 1260
314 X | 28.76 | Southwest Portland Cement |  |  |  | Tap not inspected or sampled -Original Construction
314 X | 30.5 | [NAME] |  |  |  | Tap not inspected or sampled
314 X | 34.22 | Oro Grande - Victorville F | 2000-05-14 00:00:00 | Liquid | 35 ppm | [NAME]
314 X | 34.22 | Oro Grande - Victorville F | 2000-05-30 00:00:00 | Liquid | 6 ppm
314 X | 34.22 | Oro Grande - Victorville F | 2000-06-14 00:00:00 | Liquid | 11 ppm
314 X | 34.22 | Oro Grande - Victorville F | 2000-06-29 00:00:00 | Liquid | 10 ppm
314 X | 34.22 | Oro Grande - Victorville F | 2000-07-29 00:00:00 | None |  | Filter was dry
314 X | 34.22 | Oro Grande - Victorville F | 2000-08-21 00:00:00 | Liquid | 16 ppm
314 X | 34.22 | Oro Grande - Victorville F | 2000-10-02 00:00:00 | Liquid | 5 ppm | < 10 mls
314 X | 34.22 | Oro Grande - Victorville F | 2000-10-02 00:00:00 | Liquid | 21 ppm | < 10 mls
314 X | 34.22 | Oro Grande - Victorville F | 2000-10-26 00:00:00 | Liquid | 46 ppm | < 10 mls
314 X | 34.22 | Oro Grande - Victorville F | 2000-11-20 00:00:00 | Liquid | 16 ppm | < 10 mls
314 X | 34.22 | Oro Grande - Victorville F | 2000-12-18 00:00:00 | Liquid | 15 ppm | < 10 mls
314 X | 34.22 | Oro Grande - Victorville F | 2001-01-23 00:00:00 | Liquid | 16 ppm | < 10 mls
314 X | 34.34 | Big Bear "B" | 2000-02-09 00:00:00 | None |  | Two filters; both are dry
314 X | 34.34 | Big Bear "B" | 2000-04-27 00:00:00 | Liquid | 7 ppm as [NAME], 2 ppm as [NAME]
314 X | 34.34 | Big Bear "B" | 05/14/00. | Liquid | 38 ppm as [NAME], 3 ppm as Aroclor 1254 | Sample from meter set
314 X | 34.34 | Big Bear "B" | 2000-05-30 00:00:00 | Liquid | 6 ppm as [NAME], 2 ppm as [NAME]
314 X | 34.34 | Big Bear "B" | 2000-06-14 00:00:00 | Liquid | 16 ppm as [NAME], 2 ppm as [NAME] 1260
314 X | 34.34 | Big Bear "B" | 2000-06-29 00:00:00 | Liquid | 16 ppm as [NAME], 3 ppm as Aroclor 1254
314 X | 34.34 | Big Bear "B" | 2000-07-29 00:00:00 | Liquid | 15 ppm as [NAME], 2 ppm as [NAME]
314 X | 34.34 | Big Bear "B" | 2000-08-18 00:00:00 | Liquid | 16 ppm as [NAME], 2 ppm as [NAME] 1260
314 X | 34.34 | Big Bear "B" | 2000-09-05 00:00:00 | Liquid | 16 ppm as [NAME], 3 ppm as Aroclor 1254 | ~20 mls
314 X | 34.34 | Big Bear "B" | 2000-09-18 00:00:00 | Liquid | 17 ppm as [NAME], 3 ppm as Aroclor 1254 | ~20 mls
314 X | 34.34 | Big Bear "B" | 2000-10-02 00:00:00 | Liquid | 17 ppm as [NAME], 3 ppm as Aroclor 1254 | ~20 mls
314 X | 34.34 | Big Bear "B" | 2000-10-02 00:00:00 | Liquid | 15 ppm as [NAME], 2.4 ppm as [NAME] | ~10 mls
314 X | 34.34 | Big Bear "B" | 2000-10-26 00:00:00 | Liquid | 13.2 ppm as [NAME], 2.4 ppm as [NAME] | ~10 mls
314 X | 34.34 | Big Bear "B" | 2000-11-20 00:00:00 | Liquid | 7.2 ppm as [NAME], 2.6 ppm as [NAME] | ~10 mls
314 X | 34.34 | Big Bear "B" | 2000-12-18 00:00:00 | Liquid | 5 ppm as [NAME], 2 ppm as [NAME] | ~10 mls
314 X | 34.34 | Big Bear "B" | 2001-01-23 00:00:00 | Liquid | 7 ppm as Aroclor 1242 | <10 mls
314 X | 38.57 | Victorville "C" SWG | 2000-02-09 00:00:00 | None |  | Two filters; both are dry
314 X | 38.57 | Victorville "C" Meter | 2000-02-17 00:00:00 | Liquid | 5 ppm as [NAME], 4 ppm, as [NAME]
314 X | 38.57 | Victorville "C" Meter | 2000-03-22 00:00:00 | Liquid | 3 ppm, as [NAME]
314 X | 43.18 | Black Mountain Cement | 2000-02-09 00:00:00 | None |  | [NAME] tap is dry. Filter on low flow run is dry
314 X | 43.18 | Black Mountain Cement | 2000-03-23 00:00:00 | Liquid | 0.2 ppm as [NAME], 0.8 ppm, as [NAME] | Sample from Filter
314 X | 43.18 | Black Mountain Cement | 2000-03-23 00:00:00 | Wipe | 2 ug /wipe as Aroclor 1254 | semi-quantittative wipw inside filter canister
314 X | 43.18 | Black Mountain Cement | 2000-04-05 00:00:00 | Wipe | 2 ug /wipe as Aroclor 1254 | semi-quantittative wipw inside filter canister
314 X | 43.18 | Black Mountain Cement | 2000-03-23 00:00:00 | Liquid | 3 ppm as Aroclor 1254 | Sample from Filter
314 X | 43.18 | Black Mountain Cement | 2000-05-01 00:00:00 | Liquid |  | Insufficient Sample
314 X | 43.18 | Black Mountain Cement | 2000-05-15 00:00:00 | Solid | < 1 ppm | Dust from Filter
314 X | 43.18 | Black Mountain Cement | 2000-07-24 00:00:00 | None |  | Filter
314 X | 43.18 | Black Mountain Cement | 2000-08-21 00:00:00 | Wipe | ND < 1ug/100cm2
314 X | 43.18 | Black Mountain Cement | 2000-09-06 00:00:00 | None |  | No liquids
314 X | 43.18 | Black Mountain Cement | 2000-09-18 00:00:00 | None |  | No liquids
314 X | 43.18 | Black Mountain Cement | 2000-10-04 00:00:00 | None |  | No liquids
314 X | 43.18 | Black Mountain Cement | 2000-11-03 00:00:00 | None |  | No liquids
314 X | 43.18 | Black Mountain Cement | 2001-01-03 00:00:00 | None |  | No liquids
372 X (Line 311 branch) | 3.7 | R.C. Primary Reg. Station | 2000-05-04 00:00:00 | Wipe | ND < 1ug/100cm2 | Ridgecrest primary filter
372 X (Line 311 branch) | 3.7 | R.C. Primary Reg. Station | 2000-05-16 00:00:00 | Wipe | ND < 1ug/100cm2 | Ridgecrest primary filter
372 X (Line 311 branch) | 3.7 | R.C. Primary Reg. Station | 2000-05-16 00:00:00 | Liquid | < 1 ppm | Ridgecrest primary, liquid taken from orifice meter
372 X (Line 311 branch) | 3.7 | R.C. Primary Reg. Station | 2000-08-21 00:00:00 | None |  | Filter Dry
372 X (Line 311 branch) | 3.7 | R.C. Primary Reg. Station | 2000-10-02 00:00:00 | None |  | Filter Dry
372 X (Line 311 branch) | 3.7 | R.C. Primary Reg. Station | 2001-01-02 00:00:00 | None |  | Filter Dry