Spreadsheet: 173442d1344550859-if-and-function-to-list-out-production-depending-on-which-month-the-business-starts-srilanka-dc-phase-1-3-model-draft-internet
Sheet: Design Sheet 

 | Trimax- Presales - data Center
 | Date: 23-05-2011
 | TRIMAX_BANGALORE
A | NUMBER OF RACKS | Phase-1 |  | TOTAL RACKS
 | SERVER FARM
 | Server racks (600 x 1000x2100mm) with 6 [NAME] -- LD | 300
 | TOTAL RACKS - Server | 300
 | [NAME] (600 x 1000x2100mm) with 6 KVA | 10
 | TOTAL RACKS - Network | 10
 | TOTAL RACKS - SERVER + NETWORK
 | UPS power calculation for server and network equipments
B | IT loads
 | Server racks (600 x 1000 x 2100mm) with 6 [NAME] -- LD
 | [NAME] (600 x 1000 x 2100mm) with 6 KVA
 | UPS LOAD IN KVA
 | TOTAL UPS LOAD IN KVA
 | 90% Load utilisation
 | UPS for BMS / Emergency lighting & Staging Room. | 10 | KVA
C | Room Description | Area in sq.ft | Zones
 | Server Room | 10000 | Inside Zone
 | Critical Area of datacenter
 | Telco Room | 300
 | NOC Room | 500
 | Staging Room | 500 | Outside Zone
 | Electrical + UPS/Battery Room | 2500
 | BMS room | 250
 | [NAME] | 200
 | Store Room | 600
 | Help Desk Area | 200
 | Passage Area | 600
 | Operation and Support area
 | TOTAL AREA Critical+Non critical+UPS room (Excluding Partition Thickness)
D | Prec. A/C Load
 | Area of cooling | Phase-1 | Phase-2
 | PAC sizing for Server Room | TR | TR
 | Server racks (600 x 1000x2100mm) with 6 [NAME] -- LD   + Network Rack (600 x 1000x2100mm) with 6 [NAME]
 | TOTAL TR required
 | Number of Working units( 34TR) | 14 | 0
 | Number of stand by units ( 34TR) | 3
 | TOTAL Units Required ( 34 TR)
E | Comfort A/C load
 | Area of cooling | Stage 1
 | Semi-Critical area & Operaional Area
 | UPS/Electrical Room | 45
 | Room area
 | Total Comfort A/C for critical area
 | Total comfort A/C for critical and non critical area
 | SUMMARY of ELECTRICITY BOARD POWER
 | Electricity requirement | Phase-1 | Phase-2
 | Total Power- UPS for Server farm
 | Total Power- UPS for Workstation | 10 | 0
 | Total PAC PAHU requirement in KVA
 | [NAME] (N+1 ie.e 3x250TR)
 | Total Lighting and miscellaneous power | 10 | 0
 | Total EB power required for DC+ Office (KVA) |  | 0
 | Load after Diversity(0.95)
 | Grand Total with Diversity factor
 | Total Transfomer Power Required (KVA)( 1.1)
 | Grand Total Transformer capacity
 | Total DG Power Required (KVA)( 1.25)
 | Grand Total DG capacity
 | CAPACITY SIZING AND REDUNDANCY for TIER-III Std.
 | PAHU OPTION | Total Required | Total Recommended | Total Working | Total Standby | Redundancy level | Total with Redundancy
 | Transformer or Tapping from exisitng panel for  [NAME]. (N+1) | 3318 KVA | 3750 KVA | 3x1250KVA | 1x1250KVA | N+1 | 4 x 1250 KVA
 | DG set  (N+1) | 4147KVA | 4500 KVA | 2x1500KVA | 1x1500KVA | N+1 | 3x1500KVA | DG configuration is in Parallel mode and surfice the total load
 | UPS for Server Farm including UPS for workstation /BMS / [NAME] lighting | 1800KVA | 2000 KVA | 3x500KVA |  | N+N | 6 x 500KVA | One can reduce from each side, as the load is shared through both [NAME] and Secondary UPS. UPS configuration is parallel
 | Chiller Air Cooled Units | 500 TR | 500TR | 2x250TR | 1x250TR | N+1 | 3x250TR
 | Precision Cooling ( [NAME] based) for IT server room - 34 TR | 431TR |  | 14x34TR | 3 x 34TR | N+1 | 17 x 34TR
 | Comfort cooling ( [NAME] based) | 66TR |  | 4x 16.5TR | 1 x 16.5TR | N+1 | 5 x 16.5TR