Spreadsheet: gerald_nemec__11378__Substdat
Sheet: Sheet2

 | DATA SHEET
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Number
 |  | LOST CREEK GATHERING COMPANY, L.L.C. |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Sheet |  |  |  | 2 |  |  |  |  |  | of |  |  |  | 2
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Date |  |  |  |  | By |  |  |  |  |  |  |  |  | Rev. |  |  |  |  |  |  | Date
 | LOST CREEK COMPRESSOR STATION |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Approved |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | P.O. Number
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Approved |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | P.O. Item No.
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  | SUBSTATION |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Spec. No.
 | SWITCHGEAR ENCLOSURE REQUIREMENTS
 |  | X |  | Walk-in Elclosure as Specified |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Remarks:
 |  |  |  | NEMA 3R Switchgear
 |  | Exterior Paint: |  |  |  |  |  |  |  |  | X |  | ANSI  61, light gray |  |  |  |  |  |  |  |  |  |  |  |  | ANSI 70, sky gray
 |  | Utility Company: |  |  |  |  |  |  |  | TBA
 |  | Contact: |  |  |  |  | TBA
 |  | Telephone: |  |  |  |  |  | TBA
 | CONSTRUCTION REQUIREMENTS
 |  | [NAME]: |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Foundations:
 |  |  |  |  |  | [NAME] |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | X |  | Base Quotation on |  |  |  |  |  |  |  |  | 1500 |  |  |  |  |  |  |  |  |  |  |  |  |  | PSI
 |  |  |  |  |  | Maximum Length |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | See Attached Soils Report
 |  |  |  |  |  | See attached Drawing |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Grounding:
 |  |  |  | X |  | As specified by Turnkey Vendor |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | X |  | Assume Soils Resistivity of |  |  |  |  |  |  |  |  |  |  |  |  |  | TBA |  |  |  |  |  |  |  |  | Ohm-cm
 |  | Fencing Requirements: |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | See Attached Soils Report
 |  |  |  | X |  | Fencing As Specified |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Phase Conductor and Deadending Materials:
 |  |  |  |  |  | Fencing As Indicated On Attached Drawings |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | X |  | Provided by Turnkey Vendor
 |  |  |  |  |  | Other: |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Provided by Local Utility
 | AUXILARY POWER REQUIREMENTS
 |  | X |  | Vendor to Supply Batteries and Charger for Switchgear at |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 120 |  |  |  |  |  |  |  | [NAME].
 |  |  |  | Purchaser to Supply DC for Switchgear at |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | [NAME].
 |  |  |  | Turnkey Vendor to Supply Transformer for All Substation |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Volts AC Requirements.
 |  |  |  | Purchaser to Supply |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Volts AC to Turnkey Vendor Supplied AC Panelboard.
SUBSTATION CONDUIT REQUIREMENTS
 |  |  | PVC Coated Rigid Below Grade |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | X | Extend Conduits for Purchaser's Connection |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 10 |  |  | Ft beyond Fence
 |  | X | PVC Schedule |  |  |  |  |  |  |  | 40 |  |  |  |  | Acceptable Below Grade |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Turnkey Vendor shall Install |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Each |  |  |  |  |  |  | Conduits from
 |  |  | All PVC Schedule |  |  |  |  |  |  |  |  |  |  |  |  | Must be encased In Concrete |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Switchgear Building To Substation Boundary for Controls.
ADDITIONAL REQUIREMENTS
 |  |  | Provide Foundation, Grounding, Installation, and Connection of Purchaser Supplied Variable Speed Drive DC Link Reactors
 |  |  | Provide Foundation, Grounding, Installation, and Connection of Purchaser Supplied Variable Speed Drive Isolation Transformer.
 |  | X | Provide Foundation, Grounding, Installation, and Connection of Purchaser Supplied Harmonic Filter / Power Factor Correction Equipment.
 |  | X | Provide Foundation, Grounding, Installation, and Connection of |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | 300 |  |  | KVA 480 V Auxilary Transformer and [NAME].
 |  |  |  |  | See Attached Specifications for Equipment
 |  |  |  |  | Purchaser To Supply Information at a Later Date.  Turnkey Vendor to finalize after receipt of information.
COMMENTS/ADDITIONAL INFORMATION
 |  |  | UTIILITY COMPANY CONTACT: [NAME]
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Pacific Power and Light (PacifiCorp)
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | (307) 352-5201