Spreadsheet: 0957d92f-6889-4e82-b9a3-daa680dc38a9
Sheet: Sheet1

Unnamed: 0 | Unnamed: 1 | Unnamed: 2 | Unnamed: 3 | Unnamed: 4 | Unnamed: 5 | Unnamed: 6 | Unnamed: 7 | Unnamed: 8 | Unnamed: 9 | Unnamed: 10
 | Cryomodule | TESLA |  | ILC |  | TESLA |  | ILC Half Current
 | E, [MV/m] | 23.4 |  | 31.5 |  | 23.4 |  | 31.5
 | Q | 10000000000 |  | 10000000000 |  | 10000000000 |  | 10000000000
 | Rep rate, [Hz] | 5 |  | 5 |  | 5 |  | 5
 | Number of Cavities | 12 |  | 8 |  | 12 |  | 8
 | Fill time [µsec] | 420 |  | 565.4648231609503 |  | 420 |  | 1130.929646321901 |  | Tf
 | Beam pulse [µsec] | 950 |  | 1000 |  | 950 |  | 1000 |  | Tb
 | Number of bunches | 2820 |  | 2968 |  | 2820 |  | 1484 |  | Nb
 | Gfac |  |  | 2.082716137289119 |  |  |  | 2.885860054895428 |  | Stored Energy Factor = G^2*(Tb + 1.1*Tf)
 | Pfac |  |  | 1.602547005184068 |  |  |  | 2.453052755533585 |  | Input Power Factor = G * (Tb + 2*Tf)
 | Bfac |  |  | 1.052482269503546 |  |  |  | 0.526241134751773 |  | Bunch Factor = Nb
 | Cfac |  |  | 0.9998581560283688 |  |  |  | 0.4999290780141844 |  | Beam Current Factor = Nb/Tb
 |  | Static | Dynamic | Static | Dynamic | Static | Dynamic | Static | Dynamic
 | Temperature Level | 2K |  |  |  | 2K
 | RF load |  | 4.95 |  | 6.872963253054092 |  | 4.95 |  | 9.523338181154912 | Dynamic load scaled by the number of cavities and Gfac
 | Supports | 0.6 |  | 0.6 | 0 | 0.6 |  | 0.6 | 0 | Assume indepent of nuimber of cavities
 | Input coupler | 0.76 | 0.14 | 0.5066666666666667 | 0.1495710538171797 | 0.76 | 0.14 | 0.5066666666666667 | 0.228951590516468 | Static load scaled by number of cavities, dynamic by Pfac also
 | HOM coupler (cables) | 0.01 | 0.27 | 0.006666666666666667 | 0.1799744680851064 | 0.01 | 0.27 | 0.006666666666666667 | 0.08998723404255318 | Static and dynamic load scaled by number of cavities, dynamic by Cfac also
 | HOM absorber | 0.14 | 0.02 | 0.14 | 0.02104964539007092 | 0.14 | 0.02 | 0.14 | 0.01052482269503546 | Dynamic load scaled by Bfac
 | Beam tube bellows |  | 0.24 |  | 0.3332345819662589 |  | 0.24 |  | 0.4617376087832685 | Dynamic load scaled by the number of cavities and Gfac
 | Current leads | 0.03666666666666667 |  | 0.03666666666666667 |  | 0.03666666666666667 |  | 0.03666666666666667 |  | Weigh by a factor of 1/3 since only 1 in 3 modules have quads
 | HOM to structure |  | 1.68 |  | 1.178780141843971 |  | 1.68 |  | 0.5893900709219857 | Static load scaled by the number of cavities, dynamic by Bfac also
 | Coax cable (4) | 0.05 |  | 0.05 |  | 0.05 |  | 0.05 |  | Assume indepent of nuimber of cavities
 | Instrumentation taps | 0.07 |  | 0.07 |  | 0.07 |  | 0.07 |  | Assume indepent of nuimber of cavities
 | Scales as Gfac |  | 5.19 |  | 7.206197835020351 |  | 5.19 |  | 9.98507578993818
 | Scales as Pfac |  | 0.14 |  | 0.1495710538171797 |  | 0.14 |  | 0.228951590516468
 | Independent of G,Tf | 1.666666666666667 | 1.969999999999998 | 1.41 | 1.379804255319149 | 1.666666666666667 | 1.969999999999998 | 1.41 | 0.6899021276595755
 | 2K Sum [W] | 8.966666666666665 |  | 10.14557314415668 |  | 8.966666666666665 |  | 12.31392950811422
 |  | 5K |  |  |  | 5K
 | Radiation | 1.95 |  | 1.3 |  | 1.95 |  | 1.3 |  | Static load scaled by number of cavities
 | Supports | 2.4 |  | 2.4 |  | 2.4 |  | 2.4 |  | Assume indepent of nuimber of cavities
 | Input coupler | 2.05 | 1.19 | 1.366666666666666 | 1.271353957446027 | 2.05 | 1.19 | 1.366666666666666 | 1.946088519389978 | Static load scaled by number of cavities, dynamic by Pfac also
 | HOM coupler (cables) | 0.4 | 2.66 | 0.2666666666666667 | 1.773081796690307 | 0.4 | 2.66 | 0.2666666666666667 | 0.8865408983451537 | Static and dynamic load scaled by number of cavities, dynamic by Cfac also
 | HOM absorber | 3.13 | 0.77 | 3.13 | 0.8104113475177305 | 3.13 | 0.77 | 3.13 | 0.4052056737588652 | Dynamic load scaled by Bfac
 | Diagnostic cable | 1.39 | 0 | 1.39 | 0 | 1.39 | 0 | 1.39 | 0 | Assume indepent of nuimber of cavities
 | Scales as Pfac |  | 1.19 |  | 1.271353957446027 |  | 1.19 |  | 1.946088519389978
 | Independent of G,Tf | 11.32 | 3.43 | 9.853333333333333 | 2.583493144208038 | 11.32 | 3.43 | 9.853333333333333 | 1.291746572104019
 | 5K Sum [W] | 15.94 |  | 13.7081804349874 |  | 15.94 |  | 13.09116842482733
 |  | 40K |  |  |  | 40K
 | Radiation | 44.99 |  | 29.99333333333333 |  | 44.99 |  | 29.99333333333333 |  | Static load scaled by number of cavities
 | Supports | 6 |  | 6 |  | 6 |  | 6 |  | Assume indepent of nuimber of cavities
 | Input coupler | 21.48 | 59.4 | 14.32 | 63.46086140528909 | 21.48 | 59.4 | 14.32 | 97.14088911912997 | Static load scaled by number of cavities, dynamic by Pfac also
 | HOM coupler (cables) | 2.55 | 13.22 | 1.7 | 8.812083215130023 | 2.55 | 13.22 | 1.7 | 4.406041607565012 | Static and dynamic load scaled by number of cavities, dynamic by Cfac also
 | HOM absorber | -3.27 | 15.27 | -3.27 | 16.07140425531915 | -3.27 | 15.27 | -3.27 | 8.035702127659574 | Dynamic load scaled by Bfac
 | Diagnostic cable | 2.48 |  | 2.48 |  | 2.48 |  | 2.48 |  | Assume indepent of nuimber of cavities
 | Current leads | 6 |  | 6 |  | 6 |  | 6 |  | Weigh by a factor of 1/3 since only 1 in 3 modules have quads
 | Scales as Pfac |  | 59.4 |  | 63.46086140528909 |  | 59.4 |  | 97.14088911912997
 | Independent of G,Tf | 80.23 | 28.49 | 57.22333333333333 | 24.88348747044918 | 80.23 | 28.49 | 57.22333333333333 | 12.44174373522459
 | 40K Sum [W] | 168.12 |  | 145.5676822090716 |  | 168.12 |  | 166.8059661876879
 | Fu | 1.5 |  |  |  | 1.5 |  |  |  | Uncertainty factor on static load
 | Fo | 1.4 |  |  |  | 1.4 |  |  |  | Overcapacity factor on net load
 | 2K Conversion | 773.3 |  |  |  | 773.3
 | 5K Conversion | 158.4 |  |  |  | 158.4
 | 40K Conversion | 15.3 |  |  |  | 15.3
 | Installed Power (kW / module) |  |  |  |  |  |  |  |  | Installed Power = Fo * (Fu * Static Load + Dynamic Load)*Conversion
 |  |  |  |  | fraction |  |  |  | fraction | where the units are kW per 8-cavity, ILC cryomodule
 | Scales as Gfac |  |  | 7.801573900149731 | 0.3978277258032282 |  |  | 10.81004275170287 | 0.485276805593917
 | Scales as Pfac |  |  | 1.803195719188078 | 0.09195083727002083 |  |  | 2.760190005916624 | 0.1239085006109225
 | Independent of G, Tf |  |  | 10.00566322417021 | 0.5102214369267509 |  |  | 8.705801512085104 | 0.3908146937951605
 | Total |  |  | 19.61043284350802 |  |  |  | 22.2760342697046