Spreadsheet: 73081d1273744707-the-source-currently-evaluates-to-an-error-bs7671-v7
Sheet: Tables 4DX-4EX

 |  |  |  |  |  |  |  |  |  |  | 1 | 2 | 3 | 4 | 5 | 6 | 7 | 8 | 9 | 10 | 11 | 12 | 13 | 14 | 15 | 16 | 17 | 18 | 19 | 20 | 21 | 22 | 23 | 24 | 25 | 26 | 27 | 28 | 29 | 30 | 31 | 32 | 33 | 34 | 35 | 36 | 37 | 38 | 39 | 40 | 41 | 42 | 43 | 44 | 45 | 46 | 47 | 48 | 49 | 50 | 51 | 52 | 53 | 54 | 55 | 56 | 57 | 58 | 59 | 60 | 61 | 62 | 63 | 64 | 65 | 66 | 67 | 68 | 69 | 70 | 71 | 72 | 73 | 74 | 75 | 76 | 77 | 78 | 79 | 80 | 81 | 82 | 83 | 84 | 85 | 86 | 87 | 88 | 89 | 90 | 91 | 92 | 93 | 94 | 95 | 96 | 97 | 98 | 99 | 100 | 101 | 102 | 103 | 104 | 105 | 106 | 107 | 108 | 109 | 110 | 111 | 112 | 113 | 114 | 115 | 116 | 117 | 118 | 119 | 120 | 121 | 122 | 123 | 124 | 125 | 126 | 127 | 128 | 129 | 130 | 131 | 132 | 133 | 134 | 135 | 136 | 137 | 138 | 139 | 140 | 141 | 142 | 143 | 144 | 145 | 146 | 147 | 148 | 149 | 150 | 151 | 152 | 153 | 154 | 155 | 156 | 157 | 158 | 159 | 160 | 161 | 162 | 163 | 164 | 165 | 166 | 167 | 168 | 169 | 170 | 171 | 172 | 173 | 174 | 175 | 176 | 177 | 178 | 179 | 180 | 181 | 182 | 183 | 184 | 185 | 186 | 187 | 188 | 189 | 190 | 191
4DXA |  |  | 4DXb
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 30 - On horizontal/vertical unperforated tray*Configuration: *Flat Touching and Trefoil | 6 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 30 - On horizontal/vertical unperforated tray*Configuration: *Flat Touching and Trefoil | 6 |  |  |  |  |  | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1A
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Horizontal Flat Spaced | 10 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Horizontal Flat Spaced | 8 |  |  |  |  |  | Conductor CSA | Reference method A  Enclosed in conduit in thermally insulating wall etc) |  | Reference method B Enclosed in conduit on a wall or in trunking etc) |  | Reference method C Clipped direct |  | Reference method F (in free air or on perforated cable tray horizontal or vertical)
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Vertical Flat Spaced | 11 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Vertical Flat Spaced | 8 |  |  |  |  |  |  |  |  |  |  |  |  | Touching |  |  | Spaced by one diameter
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Trefoil | 9 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Trefoil | 6 |  |  |  |  |  |  | 2 cables, single-phase a.c. or d.c. | 3 or 4 cables, three-phase a.c. | 2 cables, single-phase a.c. or d.c. | 3 or 4 cables, three-phase a.c. | 2 cables, single-phase a.c. or d.c. flat and touching | 3 or 4 cables, three-phase a.c. flat and touching and trefoil | 2 cables, single-phase a.c. or d.c. flat | 3 cables, three-phase a.c. flat | 3 cables, three-phase a.c. trefoil | 2 cables, single-phase a.c. or d.c. or 3 cables three-phase a.c. flat
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Flat Touching | 8 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Flat Touching | 7 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Horizontal | Vertical
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Horizontal Flat Spaced | 10 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Horizontal Flat Spaced | 8 |  |  |  |  |  | 1 | 11 | 10.5 | 13.5 | 12 | 15.5 | 14
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Vertical Flat Spaced | 11 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Vertical Flat Spaced | 8 |  |  |  |  |  | 1.5 | 14.5 | 13.5 | 17.5 | 15.5 | 20 | 18
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Trefoil | 9 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Trefoil | 6 |  |  |  |  |  | 2.5 | 20 | 18 | 24 | 21 | 27 | 25
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Flat Touching | 8 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Flat Touching | 7 |  |  |  |  |  | 4 | 26 | 24 | 32 | 28 | 37 | 33
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Horizontal Flat Spaced | 10 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Horizontal Flat Spaced | 8 |  |  |  |  |  | 6 | 34 | 31 | 41 | 36 | 47 | 43
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Vertical Flat Spaced | 11 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Vertical Flat Spaced | 8 |  |  |  |  |  | 10 | 46 | 42 | 57 | 50 | 65 | 59
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Trefoil | 9 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Trefoil | 6 |  |  |  |  |  | 16 | 61 | 56 | 76 | 68 | 87 | 79
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Flat Touching | 8 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Flat Touching | 7 |  |  |  |  |  | 25 | 80 | 73 | 101 | 89 | 114 | 104 | 131 | 114 | 110 | 146 | 130
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Horizontal Flat Spaced | 10 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Horizontal Flat Spaced | 8 |  |  |  |  |  | 35 | 99 | 89 | 125 | 110 | 141 | 129 | 162 | 143 | 137 | 181 | 162
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Vertical Flat Spaced | 11 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Vertical Flat Spaced | 8 |  |  |  |  |  | 50 | 119 | 108 | 151 | 134 | 182 | 167 | 196 | 174 | 167 | 219 | 197
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Trefoil | 9 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Trefoil | 6 |  |  |  |  |  | 70 | 151 | 136 | 192 | 171 | 234 | 214 | 251 | 225 | 216 | 281 | 254
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Flat Touching | 8 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Flat Touching | 7 |  |  |  |  |  | 95 | 182 | 164 | 232 | 207 | 284 | 261 | 304 | 275 | 264 | 341 | 311
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 1 - In conduit in a thermally insulated wall | 2 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 1 - In conduit in a thermally insulated wall | 5 |  |  |  |  |  | 120 | 210 | 188 | 269 | 239 | 330 | 303 | 352 | 321 | 308 | 396 | 362
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 4 - In conduit on a wooden/masonry wall | 4 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 4 - In conduit on a wooden/masonry wall | 5 |  |  |  |  |  | 150 | 240 | 216 | 300 | 262 | 381 | 349 | 406 | 372 | 356 | 456 | 419
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 41 - In conduit in a building void | 4 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 41 - In conduit in a building void | 5 |  |  |  |  |  | 185 | 273 | 245 | 341 | 296 | 436 | 400 | 463 | 427 | 409 | 521 | 480
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 42 - In conduit in a building void | 4 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 42 - In conduit in a building void | 5 |  |  |  |  |  | 240 | 321 | 286 | 400 | 346 | 515 | 472 | 546 | 507 | 485 | 615 | 569
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 54 - In conduit in an unventilated cable channel | 4 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 54 - In conduit in an unventilated cable channel | 5 |  |  |  |  |  | 300 | 367 | 328 | 458 | 394 | 594 | 545 | 629 | 587 | 561 | 709 | 659
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 55 - In conduit in open/ventilated floor channel | 4 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 55 - In conduit in open/ventilated floor channel | 5 |  |  |  |  |  | 400 |  |  | 546 | 467 | 694 | 634 | 754 | 689 | 656 | 852 | 795
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 59 - In conduit in masonry | 4 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 59 - In conduit in masonry | 5 |  |  |  |  |  | 500 |  |  | 626 | 533 | 792 | 723 | 868 | 789 | 749 | 982 | 920
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 6 - In horizontal trunking on a wooden/masonry wall | 4 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 6 - In horizontal trunking on a wooden/masonry wall | 5 |  |  |  |  |  | 630 |  |  | 720 | 611 | 904 | 826 | 1005 | 905 | 855 | 1138 | 1070
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 7 - In vertical trunking on a wooden/masonry wall | 4 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 7 - In vertical trunking on a wooden/masonry wall | 5 |  |  |  |  |  | 800 |  |  |  |  | 1030 | 943 | 1086 | 1020 | 971 | 1265 | 1188
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 10 - In suspended trunking | 4 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 10 - In suspended trunking | 5 |  |  |  |  |  | 1000 |  |  |  |  | 1154 | 1058 | 1216 | 1149 | 1079 | 1420 | 1337
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 13 - In skirting trunking | 4 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 13 - In skirting trunking | 5
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 43 - In ducting in a building void | 4 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 43 - In ducting in a building void | 5
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 45 - In ducting in masonry | 4 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 45 - In ducting in masonry | 5
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 50 - In flush trunking in floor | 4 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 50 - In flush trunking in floor | 5 |  |  |  |  | Cable Size: | 25
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 52 - In flush trunking | 4 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 52 - In flush trunking | 5
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 40 - In a building void | 4 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 40 - In a building void | 5
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 47 - In a ceiling void or suspended floor | 4 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 47 - In a ceiling void or suspended floor | 5 |  |  |  |  | Supply Voltage | 400 |  | Length of cable | 10 | m
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 57 - Direct in masonry (without capping)*Configuration: *Flat Touching and Trefoil | 6 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 57 - Direct in masonry (without capping)*Configuration: *Flat Touching and Trefoil | 6 |  |  |  |  | amps | 100 |  | Permissible Volt Drop | 5 | %
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 58 - Direct in masonry (with capping)*Configuration: *Flat Touching and Trefoil | 6 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 58 - Direct in masonry (with capping)*Configuration: *Flat Touching and Trefoil | 6 |  |  |  |  | Supply | 1Ph + N |  | [NAME] | 20 | mV/a/m
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 20 - Clipped direct on a wooden/masonry wall*Configuration: *Flat Touching and Trefoil | 6 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 20 - Clipped direct on a wooden/masonry wall*Configuration: *Flat Touching and Trefoil | 6 |  |  |  |  | Cable type | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 21 - Under a wooden/masonry ceiling | 4 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 21 - Under a wooden/masonry ceiling | 5 |  |  |  |  | Step 1 | On, or spaced from, wall of ceiling
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Horizontal Flat Spaced | 10 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Horizontal Flat Spaced | 8 |  |  |  |  | [NAME] | 22 - Spaced from a ceiling*Configuration: *Horizontal Flat Spaced
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Vertical Flat Spaced | 11 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Vertical Flat Spaced | 8
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Trefoil | 9 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Trefoil | 6
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Flat Touching | 8 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Flat Touching | 7
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Horizontal Flat Spaced | 10 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Horizontal Flat Spaced | 8
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Vertical Flat Spaced | 11 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Vertical Flat Spaced | 8
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Trefoil | 9 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Trefoil | 6
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Flat Touching | 8 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Flat Touching | 7
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In moulding, architrave or window frame 12 - In mouldings | 2 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In moulding, architrave or window frame 12 - In mouldings | 5
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In moulding, architrave or window frame 15 - In architrave | 2 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In moulding, architrave or window frame 15 - In architrave | 5 |  | cablesize | 25 | mm2
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In moulding, architrave or window frame 16 - In window frame | 2 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In moulding, architrave or window frame 16 - In window frame | 5
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Miscellaneous 35 - Suspended from/incorporating a support wire | 8 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Miscellaneous 35 - Suspended from/incorporating a support wire | 0 |  |  |  |  | mV/a/m [NAME]: | 2.5
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Miscellaneous 56 - In open/ventilated horizontal/vertical channel | 4 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Miscellaneous 56 - In open/ventilated horizontal/vertical channel | 5
3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 [NAME] through thermal insulation*Distance ([NAME]): *500 | 0 |  | 3Ph Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 [NAME] through thermal insulation*Distance ([NAME]): *500 | 0
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 30 - On horizontal/vertical unperforated tray*Configuration: *Flat Touching and Trefoil | 5 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 30 - On horizontal/vertical unperforated tray*Configuration: *Flat Touching and Trefoil | 3
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Horizontal Flat Spaced | 10 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Horizontal Flat Spaced | 4 |  |  |  |  |  | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1B
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Vertical Flat Spaced | 11 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Vertical Flat Spaced | 4 |  |  |  |  |  | Conductor CSA | 2 cables d.c. | 2 cables, single-phase a.c. |  |  | 3 or 4 cables, three-phase a.c.
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Flat Touching | 7 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 31 - On horizontal/vertical perforated tray*Configuration: *Flat Touching | 3 |  |  |  |  |  |  |  | Reference methods A & B (enclosed in conduit or trunking) | Reference method C & F (clipped direct, on tray or in free air) |  | Reference methods A & B (enclosed in conduit or trunking) | Reference method C & F (clipped direct, on tray or in free air)
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Horizontal Flat Spaced | 10 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Horizontal Flat Spaced | 4 |  |  |  |  |  |  |  |  | cables touching | cables spaced |  | cables touching, Trefoil | [NAME], flat | cables spaced, flat
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Vertical Flat Spaced | 11 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Vertical Flat Spaced | 4 |  |  |  |  |  | 1 | 44 | 44 | 44 | 44 | 38 | 38 | 38 | 38
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Flat Touching | 7 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 32 - On horizontal/vertical wire mesh tray*Configuration: *Flat Touching | 3 |  |  |  |  |  | 1.5 | 29 | 29 | 29 | 29 | 25 | 25 | 25 | 25
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Horizontal Flat Spaced | 10 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Horizontal Flat Spaced | 4 |  |  |  |  |  | 2.5 | 18 | 18 | 18 | 18 | 15 | 15 | 15 | 15
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Vertical Flat Spaced | 11 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Vertical Flat Spaced | 4 |  |  |  |  |  | 4 | 11 | 11 | 11 | 11 | 9.5 | 9.5 | 9.5 | 9.5
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Flat Touching | 7 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 33 - Spaced from a wall*Configuration: *Flat Touching | 3 |  |  |  |  |  | 6 | 7.3 | 7.3 | 7.3 | 7.3 | 6.4 | 6.4 | 6.4 | 6.4
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Horizontal Flat Spaced | 10 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Horizontal Flat Spaced | 4 |  |  |  |  |  | 10 | 4.4 | 4.4 | 4.4 | 4.4 | 3.8 | 3.8 | 3.8 | 3.8
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Vertical Flat Spaced | 11 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Vertical Flat Spaced | 4 |  |  |  |  |  | 16 | 2.8 | 2.8 | 2.8 | 2.8 | 2.4 | 2.4 | 2.4 | 2.4
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Flat Touching | 7 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Cable tray, ladder system, cleats, wire mesh tray 34 - On a ladder*Configuration: *Flat Touching | 3 |  |  |  |  |  | 25 | 1.75 | 1.8 | 1.75 | 1.8 | 1.55 | 1.5 | 1.55 | 1.55
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 1 - In conduit in a thermally insulated wall | 1 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 1 - In conduit in a thermally insulated wall | 2 |  |  |  |  |  | 35 | 1.25 | 1.3 | 1.25 | 1.3 | 1.1 | 1.1 | 1.1 | 1.15
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 4 - In conduit on a wooden/masonry wall | 3 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 4 - In conduit on a wooden/masonry wall | 2 |  |  |  |  |  | 50 | 0.93 | 1 | 0.95 | 0.97 | 0.85 | 0.82 | 0.84 | 0.86
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 41 - In conduit in a building void | 3 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 41 - In conduit in a building void | 2 |  |  |  |  |  | 70 | 0.63 | 0.72 | 0.66 | 0.69 | 0.61 | 0.57 | 0.6 | 0.63
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 42 - In conduit in a building void | 3 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 42 - In conduit in a building void | 2 |  |  |  |  |  | 95 | 0.46 | 0.56 | 0.5 | 0.54 | 0.48 | 0.43 | 0.47 | 0.51
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 54 - In conduit in an unventilated cable channel | 3 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 54 - In conduit in an unventilated cable channel | 2 |  |  |  |  |  | 120 | 0.36 | 0.47 | 0.41 | 0.45 | 0.41 | 0.36 | 0.4 | 0.44
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 55 - In conduit in open/ventilated floor channel | 3 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 55 - In conduit in open/ventilated floor channel | 2 |  |  |  |  |  | 150 | 0.29 | 0.41 | 0.34 | 0.39 | 0.36 | 0.3 | 0.34 | 0.4
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 59 - In conduit in masonry | 3 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In conduit 59 - In conduit in masonry | 2 |  |  |  |  |  | 185 | 0.23 | 0.37 | 0.29 | 0.35 | 0.32 | 0.26 | 0.31 | 0.36
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 6 - In horizontal trunking on a wooden/masonry wall | 3 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 6 - In horizontal trunking on a wooden/masonry wall | 2 |  |  |  |  |  | 240 | 0.18 | 0.33 | 0.25 | 0.31 | 0.29 | 0.22 | 0.27 | 0.34
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 7 - In vertical trunking on a wooden/masonry wall | 3 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 7 - In vertical trunking on a wooden/masonry wall | 2 |  |  |  |  |  | 300 | 0.145 | 0.31 | 0.22 | 0.29 | 0.27 | 0.19 | 0.25 | 0.32
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 10 - In suspended trunking | 3 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 10 - In suspended trunking | 2 |  |  |  |  |  | 400 | 0.105 | 0.29 | 0.2 | 0.27 | 0.25 | 0.175 | 0.24 | 0.31
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 13 - In skirting trunking | 3 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 13 - In skirting trunking | 2 |  |  |  |  |  | 500 | 0.086 | 0.28 | 0.185 | 0.26 | 0.25 | 0.16 | 0.23 | 0.3
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 43 - In ducting in a building void | 3 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 43 - In ducting in a building void | 2 |  |  |  |  |  | 630 | 0.068 | 0.27 | 0.175 | 0.25 | 0.24 | 0.15 | 0.22 | 0.29
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 45 - In ducting in masonry | 3 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 45 - In ducting in masonry | 2 |  |  |  |  |  | 800 | 0.053 |  | 0.165 | 0.25 |  | 0.145 | 0.22 | 0.29
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 50 - In flush trunking in floor | 3 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 50 - In flush trunking in floor | 2 |  |  |  |  |  | 1000 | 0.042 |  | 0.16 | 0.24 |  | 0.14 | 0.21 | 0.28
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 52 - In flush trunking | 3 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In trunking/ducting (reference B) 52 - In flush trunking | 2
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 40 - In a building void | 3 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 40 - In a building void | 2
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 47 - In a ceiling void or suspended floor | 3 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 47 - In a ceiling void or suspended floor | 2
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 57 - Direct in masonry (without capping)*Configuration: *Flat Touching and Trefoil | 5 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 57 - Direct in masonry (without capping)*Configuration: *Flat Touching and Trefoil | 3
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 58 - Direct in masonry (with capping)*Configuration: *Flat Touching and Trefoil | 5 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Direct in wall. Ceiling void 58 - Direct in masonry (with capping)*Configuration: *Flat Touching and Trefoil | 3
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 20 - Clipped direct on a wooden/masonry wall*Configuration: *Flat Touching and Trefoil | 5 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 20 - Clipped direct on a wooden/masonry wall*Configuration: *Flat Touching and Trefoil | 3
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 21 - Under a wooden/masonry ceiling | 3 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 21 - Under a wooden/masonry ceiling | 2
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Horizontal Flat Spaced | 10 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Horizontal Flat Spaced | 4
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Vertical Flat Spaced | 11 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Vertical Flat Spaced | 4
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Flat Touching | 7 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 22 - Spaced from a ceiling*Configuration: *Flat Touching | 3
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Horizontal Flat Spaced | 10 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Horizontal Flat Spaced | 4
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Vertical Flat Spaced | 11 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Vertical Flat Spaced | 4
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Flat Touching | 7 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 On, or spaced from, wall of ceiling 33 - Spaced from a wall*Configuration: *Flat Touching | 3
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In moulding, architrave or window frame 12 - In mouldings | 1 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In moulding, architrave or window frame 12 - In mouldings | 2
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In moulding, architrave or window frame 15 - In architrave | 1 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In moulding, architrave or window frame 15 - In architrave | 2
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In moulding, architrave or window frame 16 - In window frame | 1 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 In moulding, architrave or window frame 16 - In window frame | 2
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Miscellaneous 35 - Suspended from/incorporating a support wire | 0 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Miscellaneous 35 - Suspended from/incorporating a support wire | 0
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Miscellaneous 56 - In open/ventilated horizontal/vertical channel | 3 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 Miscellaneous 56 - In open/ventilated horizontal/vertical channel | 2
1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 [NAME] through thermal insulation*Distance ([NAME]): *500 | 0 |  | 1Ph + N Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 [NAME] through thermal insulation*Distance ([NAME]): *500 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0 | 0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0
0