Spreadsheet: 0427bd6a-4fcf-4c6e-856c-82e4ee94f3f3
Sheet: Sheet1

Quotation call for Akhuwa Khola MHP ,Amtek-2, [NAME] | Unnamed: 1 | Unnamed: 2 | Unnamed: 3 | Unnamed: 4 | Unnamed: 5
 | Project Location: | Amtek-2,Bhojpur
 | [NAME]: | 156
 | Altitude: | 1600 | m msl
 | Gross Head: | 90 | m
 | Design Flow: | 30 | Lps
 | Power Output: | 15 | kW
 | Quotation from: | ……….………………………….
 | Phone Number:
 | Date: | …………………………………..
SN | Description | Unit | Quantity | Rate | Amount
Mechanical Works
1 | Turbine
 | Pelton Turbine | Set | 1 |  | 0
 | Turbine Specification as per Consultant
 | Turbine Type:Double Jet Pelton Turbine,
 | Shaft O/P Power :19 kW
 | Turbine and Generator baseframe with underground tube and connecting acessories | Set | 1 |  | 0
 | Adapter | Set | 1 |  | 0
 | Butterfly valve, Gear Mechanism 160 mm ID | Set | 1 |  | 0
2 | Power Transmission
 | Direct Coupling with accessories | Set | 1 |  | 0
3 | Penstock Pipe |  |  |  | 0
 | MS pipe 160  mm Internal dia.[NAME] thickness | m | 100 |  | 0
 | MS pipe 160  mm Internal dia.,4.5 [NAME] thickness | m | 62 |  | 0
 | Tarpauline sheet | LS | 1 |  | 0
 | Expansion joints, 160 mm | Pcs. | 9 |  | 0
 | Pressure gauge (0-10 kg/Cm2) | Nos. | 1 |  | 0
 | Bell mouth with Air vent pipe (25 mm) | Set | 1 |  | 0
4 | [NAME], (500 mm x 1000 mm) for Intake | Set | 1 |  | 0
5 | Fine Trash Rack (1000 X 800 mm) for forebay | Nos. | 1 |  | 0
6 | Flushing cone, 180 mm MS pipe | Set | 2 |  | 0
 | Sub Total |  |  |  | 0
Electrical Works
1 | Generator
 | Synchronous, [NAME] less, 3 phase,30 [NAME], 400/230 V, 50 Hz & 1500 rpm. | Set | 1 |  | 0
2 | Control and Protection System |  |  |  | 0
 | ELC 15 kW, 3 phase with OV/UV, OF/UF, [NAME] and short circuit protection. The panel board should have gen Volt. [NAME], Ballast Volt meter, , [NAME] current meter, [NAME], [NAME],hour counter, Indicator,Semiconductor ballast fuse,energy meter | Set | 1 |  | 0
 | Ballast Unit (18 kW, 3 phase with its water supply accessories.) | Set | 1 |  | 0
 | Main Switch 50 A, 3 phase | Set | 1 |  | 0
 | MCCB 50 A, 3 phase on Consumer side | Set | 1 |  | 0
 | Power house wiring | LS | 1 |  | 0
3 | Earthing arrangements
 | Earthing plate copper 600x600x3 mm with 8 swg earthing wire and fittings | Set | 13 |  | 0
 | Lighting arrestor 0.5 kV with its accessories | Nos. | 29 |  | 0
4 | Wiring sytem
 | 16 mm2, 4 core copper armoured cable | m | 15 |  | 0
 | 25 mm2, 4 core Al  armoured cable | m | 15 |  | 0
 | Cable ties, Cable shoes etc | LS | 1 |  | 0
5 | Transmission & Distribution
 | ACSR conductors
 | Rabbit | m | 10120 |  | 0
 | Weasel | m | 3410 |  | 0
 | [NAME] | m | 8360 |  | 0
 | D-iron, nut, bolt & Insulator |  |  |  | 0
 | Small size shakle insulator | Set | 252 |  | 0
 | Medium size shakle insulator | Set | 408 |  | 0
 | Stay set |  |  |  | 0
 | 5/8"x1500 with its accessories(Stay wire of 7/14,MS rod, Stay bow, stay insulator, check nut,thimble and anchor plate | Set | 49 |  | 0
 | Service wire (6 mm2  concentric ) | m | 4680 |  | 0
 | Household control MCB(0.5 A) | Set | 156 |  | 0
 | Bitumin paint for Poles | LS | 1 |  | 0
5 | Tools
 | Digital clampmeter | Nos. | 1 |  | 0
 | Tools Slide wrench 10", a set of spanner for all size of nut & bolts on turbine, generator, penstocks & other equipments, screw driver set (small, medium, large), line tester, grease gun, flat & round file, rough file, chisel, hammer, [NAME] key, combination pliers 8", wire steeper etc | Set | 1 |  | 0
 | Sub Total |  |  |  | 0
 | Total |  |  |  | 0
 | [NAME] 13% |  |  |  | 0
8 | Installations and Testing-Commissioning | LS | 1 |  | 0
9 | Trasportation upto road head (Hile of Dhankutta  district) | LS | 1 |  | 0
10 | Material packing and forwarding | LS | 1 |  | 0
11 | Civil works supervision (Length of Headrace channel is 807.5 m) | LS | 1 |  | 0
Grand total |  |  |  |  | 0
 | In words: NRs. …………………………………………. Only.
 | Note:
 | *  Please specify validity period of the the Quotation.
 | *  Please include necessary VAT and other applicable taxes.
 | *  Please provide specification of the equipments (Turbine, generator) and other materials as much as possible.