Spreadsheet: 748772d1632332918-create-a-daily-rolling-schedules-from-multiple-worksheets-daily-work-schedule
Sheet: I&C

Available vs Scheduled Hours
Available Personnel and Hours
[NAME] |  |  | 8 | 8 | 8 | 8 | 0
[NAME] |  |  | 8 | 8 | 8 | 8 | 8
[NAME] |  |  | 8 | 8 | 8 | 8 | 8
[NAME] |  |  | 8 | 8 | 8 | 8 | 8
[NAME] |  |  | 0 | 0 | 0 | 0 | 0
[NAME] |  |  | 8 | 8 | 8 | 8 | 8
Darryol Jordan |  |  | 8 | 8 | 8 | 8 | 8
[NAME] |  |  | 8 | 8 | 8 | 8 | 8
I&C |  |  |  |  |  |  | Friday
 | Break In | Priority |  |  |  |  |  | Status / Issues
PMICE YEARLY  WINTER PREP ON UNIT 7 A & B SIDE SILO AIR SEPARATOR |  | B |  |  | Hold |  |  | 21-656855
U7 7-1 West #3 air cannon is stuck in the open position. |  |  |  |  | Hold |  |  | 21-659653
PMICE 2 months U8 ABSORBER MODULE PRESSURE TRANSMITTERS |  | B | IP | 16 | IP |  |  | 21-703781
PMICE 3 months U7 ABSORBER MODULE PRESSURE TRANSMITTERS |  | B | IP | 16 | IP |  |  | 21-703785
PMICE-monthly Environmental Compliance-LAWRENCEBURG LANDFILL P.M. |  | B |  | START | IP |  |  | 21-709980
U8 FGD Tower Level needs bumpless transition between X & Y to be sped up | X | A |  | Start | IP |  |  | SR 152639
PMICE 6 MONTHS Unit 7 - A & B Calibrate Differential Gauge  For The Fly Ash Bag House |  | B |  |  | start |  |  | 21-710026
Vacuum on 7Aside fly ash is reading erratically | X | A |  |  | Start |  |  | 21-725246
PMICE monthly  "A"  CONVEYOR  WEIGHTOMETER CALIBRATION |  | B |  | Hold |  |  |  | 21-709922- Needs Welded
(Forced Outage) ACR lvl 3 (lvl 9 on elevator) sonic horn #4 is leaking. pls investigate for repair planning next |  |  | WMAT |  |  |  |  | need air, performed visual inspection
Weekly PMs |  | A | Comp |  |  | start
UNIT 7 "B" HYDROVEYOR WATER SUPPLY VALVE WV-1B LEAKS THRU WHEN CLOSED |  |  |  |  |  |  |  | 21-680781
8-1 ID Fan Outlet Press Z [NAME]: troubleshoot and repair |  |  |  |  |  |  | start | 20-405103
CBTs |  | B
8-1 AR Pump TC | wmat | A
7-5C swing valve | w fluor | A |  |  |  | start |  | 21-715629  needs welder
U8 132 Valve jerking open causing [NAME] to run and cry and scream like a little kid | wops | A
7-2 AR Pump Motor Brg Temp TC needs changed |  | A
U8 8 all mill burner  flame scanners -several do not show lit -see long dis. | WMAT | A |  |  |  |  |  | 21-661953
8-3 Mill TC well | Outage | A
U7 [NAME] Make Up | WMAT | A |  |  |  |  |  | 21-612619
U8 Fly Ash Silo Dry Unloader Emergency Stop Gate | wmtl | A |  |  |  |  |  | SR 143590- Still an issue?
U7 ME 109 recycle vlv goes to bad quality when it opens | WMAT | A
UNIT 7 "B" HYDROVEYOR WATER SUPPLY VALVE WV-1B LEAKS THRU WHEN CLOSED |  | B |  |  |  |  |  | 21-680781
U8 outage - 8-1 ID fan suction pressure is reading +1.5 (#2 is -6.4@min load-16 at full load )#1 is |  | B |  |  |  |  |  | 20-292996
[NAME] UNLOADER BUCKET trolley needs to be reset if left in one position - losing logic |  | B |  |  |  |  |  | 21-95480- Still an issue?
7-1 lift station sump pump will not shut off in auto. Left in Man |  | B |  |  |  |  |  | 20-552524- Needs anti backflow valve
U7 Hydrogen Temp Control Regulator Not Working | WMAT | C |  |  |  |  |  | SR 142233
U7 B Side Ammonia Liquid Injection - Needs Local Pressure & Temp Gauge | WMAT | C |  |  |  |  |  | SR 135272
U7, 7A side ammonia liquid injection flow in BQ | WMAT | C |  |  |  |  |  | 21-169586
U8 1X Vibration Probe | WMAT | C |  |  |  |  |  | need probe help
Inspect and calibrate U7 9th & 11th stage cycle isolation valves - list attached | WMAT | C |  |  |  |  |  | 20-551025  --- cooper has list of follow up work needed, i will get quotes
U8 A & C Hopper sluice gates not operating from screen | MECH | C |  |  |  |  |  | Move to Mechanics- need to change the valve on A Hopper
Unit 8 Turbine #1 Bearing Seismic Probe 1X is in bad quality | WMAT | C |  |  |  |  |  | 21-184766
8-2 Ox Air Comp lube oil filter differential gauge | WMAT | C |  |  |  |  |  | 21-199563
U7, 9th stage extraction steam dump vlv |  | C |  |  |  |  |  | 20-567117
U8 B SCR- flow transmitter did not read anything when it was started tonight | WMAT | C |  |  |  |  |  | 20-552532
U7 FA Silo Truck Dry Loading Gate | WMAT | C |  |  |  |  |  | 21-127233- WMAT- Need to order
Inspect and calibrate U7 9th & 11th stage cycle isolation valves - list attached |  | B |  |  |  |  |  | 20-551025