Spreadsheet: 72214d1272918864-tables-drilling-down-and-interrogation-copy-of-table-interogation-1
Sheet: Sheet1

 |  | 1Ph + N | 3Ph | 1Ph + N | 3Ph | 1Ph + N | 3Ph | 1Ph + N | 3Ph | 3Ph | 1Ph + N | 1Ph + N
 |  | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1
 |  | In conduit |  |  | In conduit |  | Cable tray, ladder system, cleats, wire mesh tray |  |  | Cable tray, ladder system, cleats, wire mesh tray
 |  |  |  |  | In trunking/ducting (reference B)
 |  |  |  |  | Direct in wall. Ceiling void
 | Table | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1” | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1” | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1” | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1” | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1” | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1” | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1” |  | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1” | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1”
 | Conductor CSA | Reference method A  Enclosed in conduit in thermally insulating wall etc) |  | Reference method B Enclosed in conduit on a wall or in trunking etc) |  | Reference method C Clipped direct |  | Reference method F (in free air or on perforated cable tray horizontal or vertical) |  |  |  |  |  | amps | Supply | Cable type | Step 1 | [NAME]
 |  |  |  |  |  |  |  | Touching |  |  | Spaced by one diameter |  |  | 220 | 1Ph + N | Single-core, 70°C thermoplastic, non-arm Cu, Table 4D1 | Cable tray, ladder system, cleats, wire mesh tray
 |  | 1Ph + N | 3Ph | 1Ph + N | 3Ph | 1Ph + N | 3Ph | 1Ph + N | 3Ph | 3Ph | 1Ph + N
 |  |  |  |  |  |  |  |  |  |  | Horizontal | Vertical |  |  | Cable Size:
 | 1 | 11 | 10.5 | 13.5 | 12 | 15.5 | 14 |  |  |  |  |  |  |  | #N/A
 | 1.5 | 14.5 | 13.5 | 17.5 | 15.5 | 20 | 18
 | 2.5 | 20 | 18 | 24 | 21 | 27 | 25
 | 4 | 26 | 24 | 32 | 28 | 37 | 33
 | 6 | 34 | 31 | 41 | 36 | 47 | 43
 | 10 | 46 | 42 | 57 | 50 | 65 | 59
 | 16 | 61 | 56 | 76 | 68 | 87 | 79
 | 25 | 80 | 73 | 101 | 89 | 114 | 104 | 131 | 114 | 110 | 146 | 130
 | 35 | 99 | 89 | 125 | 110 | 141 | 129 | 162 | 143 | 137 | 181 | 162
 | 50 | 119 | 108 | 151 | 134 | 182 | 167 | 196 | 174 | 167 | 219 | 197
 | 70 | 151 | 136 | 192 | 171 | 234 | 214 | 251 | 225 | 216 | 281 | 254
 | 95 | 182 | 164 | 232 | 207 | 284 | 261 | 304 | 275 | 264 | 341 | 311
 | 120 | 210 | 188 | 269 | 239 | 330 | 303 | 352 | 321 | 308 | 396 | 362
 | 150 | 240 | 216 | 300 | 262 | 381 | 349 | 406 | 372 | 356 | 456 | 419
 | 185 | 273 | 245 | 341 | 296 | 436 | 400 | 463 | 427 | 409 | 521 | 480
 | 240 | 321 | 286 | 400 | 346 | 515 | 472 | 546 | 507 | 485 | 615 | 569
 | 300 | 367 | 328 | 458 | 394 | 594 | 545 | 629 | 587 | 561 | 709 | 659
 | 400 |  |  | 546 | 467 | 694 | 634 | 754 | 689 | 656 | 852 | 795
 | 500 |  |  | 626 | 533 | 792 | 723 | 868 | 789 | 749 | 982 | 920
 | 630 |  |  | 720 | 611 | 904 | 826 | 1005 | 905 | 855 | 1138 | 1070
 | 800 |  |  |  |  | 1030 | 943 | 1086 | 1020 | 971 | 1265 | 1188
 | 1000 |  |  |  |  | 1154 | 1058 | 1216 | 1149 | 1079 | 1420 | 1337