Spreadsheet: 748772d1632332918-create-a-daily-rolling-schedules-from-multiple-worksheets-daily-work-schedule
Sheet: next week

21-632489 | CY CRUSHER #2 AIR CANNON 1 OUT 3 WORK | 8/16 ready for fluor | FDBM | I-SCHD | new  8/29
21-671000 | CY CONVEYOR "J" BELT return roller at 8-3 bunker broke in half -needs replaced | 8/18 ready for fluor | FDBM | P-PLAN | new  8/29
21-671007 | unit 7 bunker floor has opening when e- shuttle is all the way to the west | 8/18 ready fluor | FDBM | P-PLAN | new  8/29
20-123727 | U8, Pegging Steam - Collapsed and broken pipe hangers. 14th floor west of DA tank. | Ready | FDBM | P-PLAN | new  9/10
21-714233 | FGD 7-1 Ball Mill inlet chute leaking again | Ready for Fluor | FDBM | I-SCHD | new 9/17
20-453460 | Repair hydrogen leak at the hydrogen farm gauge cabinet | Ready | FDBM | I-SCHD
20-567069 | U8: Re-install pipe hanger for Cold Reheat piping outside of U8 oil room. | ready to schedule | FDBM | I-SCHD
21-632485 | CY structure repairs for coalyard DO NOT COMPLETE WO | ready as fill in work anytime 8/4 fluor | FDBM | P-PLAN
21-657727 | CY A CONVEYOR STRUCTURE INSPECTION | 8/12 FLUOR READY | FDBM | P-PLAN
21-714490 | U8 flyash economizer line just north of #22 hopper needs replaced. | READY, FLUOR 3X8HRS | FDBM | P-PLAN | new 9/17
21-715463 | U6 sump discharge line isolation valve leaking under insulation above 6-1 BFP. | READY / WELD REPAIR | FDBM | P-PLAN | new 9/17
21-716324 | UNIT 7 "B" SG4 SLUICE LINE LEAKING BAD right at first flange that bolts together after clinker grinder | READY, FLUOR | FDBM | I-SCHD | new 9/17
21-716325 | CY A conveyor weld repair on scale | fluor READY 9/15 | FDBM | I-SCHD | new 9/17
21-719710 | cy D conv CY REPLACE RETURN ROLLER BELOW TAKE UP PULLEY | 9/16 ready fluor | FDBM | I-PROG | new 9/17
21-720125 | u7 bottom ash leak at bell coupling (EXPANSION JOINT) between A and B hoppers. | READY FOR SCH. | FDBM | P-PLAN | new 9/17
21-183963 | U8 IK roller repairs (8 total) | ready to schedule | FDSM | I-PROG
21-182016 | 7-1 and 7-2 Dust Collectors | ready for schedule | GSCX | P-PLAN | new  9/10
21-155711 | 8-1 and 8-2 Dust Collectors | READY FOR SCHED SES | GXCX | P-PLAN | new  9/10
20-495270 | (Fall Outage) scaff 7B SCR Inlet Isolation Guillotine Did Not Operate | READY FOR BRAND TO BUILD SCAFFOLD | MRMF | I-SCHD | new 9/2
20-567088 | U8: Scaffold for [NAME] of pipe hanger for Cold Reheat piping outside of U8 oil room. | ready to schedule | MRMF | I-PROG
21-519691 | U8 8-1-3A. Perform open circuit test to determine area of problem. | ready | TUSE | P-PLAN | new 9/17
21-700282 | 8-1 precipitator heater "A" box internal element #3 fuse holder bad. Replace. | Ready. Parts on Dale's Desk. | TUSE | I-SCHD | new 9/17
21-166950 | U7 125V battery ground. Troubleshoot/ Repair | ready. | TUSE | I-SCHD | new 9/2
21-605541 | CY H- conveyor belt misalignment switch is not working South side | 8/20 ready switch at my desk | TUSE | P-PLAN | new 9/2
21-183998 | 7-6B HP heater extraction steam limitorque valve. Troubleshoot. | ready | TUSE | P-PLAN
21-445906 | UAT 7A has one cooling fan that is not working. Troubleshoot/Repair. | ready | TUSE | P-PLAN
21-570981 | Toubleshoot IR-55 | ready to schedule | TUSE | SR-APPRV
21-593451 | CY main brker 480v east side reclaim tunnel broke breaker | 7/19 ready for electricians to access and fix | TUSE | P-PLAN
21-612768 | U8 FLY ASH TRUCK LOADER Emergency Gate not working on ash load out | ready | TUSE | I-SCHD
21-721904 | j tripper 480 breaker mechanism needs repaired - when pushing up on breaker handle it will not go up to start | ready | TUSE | P-PLAN | new 9/17
21-680781 | UNIT 7 "B" HYDROVEYOR WATER SUPPLY VALVE WV-1B LEAKS THRU WHEN CLOSED | READY FOR I&C | TUSI | P-PLAN | new 9/2
20-405103 | 8-1 ID Fan Outlet Press Z [NAME]: troubleshoot and repair | ready to schedule | TUSI | I-SCHD
20-551025 | Inspect and calibrate U7 9th & 11th stage cycle isolation valves - list attached | Ready for I&C | TUSI | P-PLAN
21-630210 | 7-1 BFPT low pressure stop valve has a broken prox. switch | Ready - I&C | TUSI | P-PLAN
21-659653 | U7 7-1 West #3 air cannon is stuck in the open position. | Ready for I&C to troubleshoot this | TUSI | P-PLAN
21-659654 | U -7 7A layer 1 # 3 sonic not blowing | Ready for I&C to troubleshoot | TUSI | P-PLAN
21-718390 | Check Unit 7 EHC accumulator's charge pressure - recharge if necessary | Ready for I&C | TUSI | P-PLAN | new 9/17
21-719714 | Check Unit 8 EHC accumulator's charge pressure - recharge if necessary | Ready for I&C | TUSI | P-PLAN | new 9/17
21-692605 | U8 basement. 8-3 ash pump outboard pump bearing will not hold an oil level. Has a new sight glass. | READY | TUSM | I-SCHD | new  9/10
21-705262 | Replace quick disconnect on 8-1 #6 lighter | ready to schedule | TUSM | P-PLAN | new  9/10
21-705306 | 8-1 Ball Mill inlet seal/pipe is leaking | Ready for mechanics to patch leaking piping | TUSM | P-PLAN | new  9/10
21-708664 | 7-3 AR pump , 2 grease lines broke off of suction valve seals. they are laying below valve. | Ready for Mechanics after scaffold is built | TUSM | I-SCHD | new  9/10
21-708859 | 8-2 service water strainer in pit is leaking from the changeover valve handle on top of strainer. | READY/ADJUST PACKING | TUSM | P-PLAN | new  9/10
21-708909 | Replace 7-1 Lime Feeder | Ready for mechanics | TUSM | P-PLAN | new 9/10
21-513866 | U8: IK-44, replace pinion roller bearing | ready to schedule | TUSM | I-SCHD