Spreadsheet: 822998d1679640131-need-to-search-multiple-cell-value-and-fill-it-all-into-another-cell-guide-for-suffering
Sheet: Teikoku Guide

 | Possible Problem
 | Motor |  |  |  |  |  |  | Pump |  |  |  |  |  | Noise and vibration
 | Not energized | Over current | Over heat | Poor insulation | TRG indicates red zone | Abnormal wear of bearing | Seizure of bearing | No liquid pump | Required capacity not pumped | Required pressure not emitted | Performance goes down | Cavitation occurs | Serging occurs | Abnormal vibrations | Vibration increasing | Abnormal noise | Noise increasing
 |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Possible Cause |  |  |  | No | Eq.
 |  |  |  | A |  |  |  |  |  |  |  |  |  |  |  |  |  | Poor drying of coil |  |  |  | 1 | Motor
 |  |  |  | B |  |  |  |  |  |  |  |  |  |  |  |  |  | Rain water comes in |  |  |  | 2
 |  | C | C |  |  |  |  |  | C | C |  |  |  |  |  |  |  | Motor size not suited |  |  |  | 3
 |  | D |  |  |  |  | D |  | D | D | D |  |  |  | D |  | D | Corrosion |  |  |  | 4 | Pump
 |  |  |  |  | E | E | E |  | E | E | E |  |  |  | E |  | E | Wear & tear |  |  |  | 5
 |  |  |  |  |  | F | F |  |  |  |  |  |  |  |  |  |  | Abnormal thrust load on bearing |  |  |  | 6
 |  |  |  |  | G |  |  |  |  |  | G |  |  | G | G |  |  | Deformation of shaft |  |  |  | 7
 |  |  |  |  |  |  |  |  |  |  |  |  |  | H | H |  |  | Unbalance of rotating unit |  |  |  | 8
 | I |  |  |  |  | I | I | I | I | I | I |  |  | I | I |  |  | Foreign matter clogged |  |  |  | 9
 |  | C | C |  |  | C |  |  | C | C |  |  |  |  |  |  |  | Pump size not suited |  |  |  | 10
 |  |  |  |  |  |  |  |  | J | J | J | J |  | J | J | J | J | Suction loss is too big |  |  |  | 11 | Operating Condition
 |  |  |  |  |  | K |  |  | K | K |  | K |  | K |  | K |  | NPSHA is not enough |  |  |  | 12
 |  |  |  |  |  |  |  |  | J | J | J |  | J |  |  |  |  | Discharge loss it too big |  |  |  | 13
 |  | L |  |  |  |  |  |  |  | L |  | L |  |  |  |  |  | Discharge loss it too small |  |  |  | 14
 | I |  |  |  |  |  |  | I | I | I | I | I |  |  |  |  |  | Foreign matter clogged |  |  |  | 15
 |  |  |  |  |  | M |  |  |  |  |  |  |  |  |  |  |  | Liquid contain slurry |  |  |  | 16
 |  | H |  |  |  |  |  |  | H | H |  |  |  |  |  |  |  | Specific gravity is too big |  |  |  | 17
 |  | H |  |  |  | H | H |  | H | H |  | H |  |  |  |  |  | Viscosity is too high |  |  |  | 18
 |  |  |  |  |  | N | N | N | N | N |  |  |  |  |  | N | N | Air venting not completed |  |  |  | 19
 |  |  |  |  |  | O |  | O | O | O | O | O |  |  |  | O | O | Air comes in from suction |  |  |  | 20
 |  |  | P |  |  |  |  |  |  |  |  |  |  |  |  |  |  | Shortage  or cut off of coolant |  |  |  | 21
 |  |  |  |  |  |  |  | Q | Q | Q |  | Q | Q | Q |  | Q |  | Poor piping |  |  |  | 22
 | R |  |  |  | R |  |  | R |  |  |  |  |  |  |  |  |  | Single phase |  |  |  | 23
 |  |  |  |  | S |  |  |  | S | S |  |  |  |  |  |  |  | Anti phase |  |  |  | 24
 | T |  |  |  |  |  |  | T |  |  |  |  |  |  |  |  |  | Not switched on |  |  |  | 25
 | No | Corrective Actions
 | A | Send back to service shop for drying.
 | B | Repair gasket of terminal box or change into packing type conduit.
 | C | Send back complete unit for replacing it with the correct unit.
 | D | Change material after having consultation.
 | E | Repair or change wear parts, or change materials.
 | F | Please consult us.
 | G | Repair the deformation.
 | H | Please consult us.
 | I | Take out foreign matter and take measures to prevent occurence of the same trouble.
 | J | Clean up pipeline and strainers or review design of piping.
 | K | Check liquid level and friction loss in suction side and take measures. Please consult us.
 | L | Review design of piping and consult us.
 | M | Take measures not slurry mix in the liquid or change pump with slurry type.
 | N | Air venting should be done again in a correct manner.
 | O | Check causes and take measures.
 | P | Provide relay for coolant cut off or increase coolant capacity when fluctuation of flow rate is too big.
 | Q | Correct piping.
 | R | Correct into three phases.
 | S | Correct conection of electric wires.
 | T | Check and/or repair wiring and instruction